Design and Optimal Sizing of a Hydrogen Uninterruptable Power Supply (UPS) System for Addressing Residential Power Cutoffs
Authors: Ali Dallia , Stewart Craig , Qadir Khurram , Jalisi Ismail 
Published: January 2025

Hydrogen (H2) offers a green medium for storing the excess from renewables production instead of dumping it, thus being crucial to decarbonisation efforts. Hydrogen also offers a storage medium for the grid’s cheap electricity to be used during grid peak demand or grid power cutoffs. Funded by the Scottish Government’s Emerging Energy Technologies, this paper presents the design and performance analysis of a hydrogen uninterruptible power supply (H2GEN) for Cygnas Solutions Ltd., which is intended to enable continuity of supply in the residential sector while eradicating the need for environmentally and health risky lead–acid batteries and diesel generator backup. This paper presents the design, optimal sizing and analysis of two H2Gen architectures, one powered by the grid alone and the other powered by both the grid and a renewable (PV) source. By developing a model of each architecture in the HOMER space and using residential location weather data, the home yearly load–demand profile, and the grid yearly power outages profile in the developed models, the optimal sizing of each H2Gen design was realised by minimising the costs while ensuring the H2Gen meets the home power demand during grid outages To enable HOMER to optimise its selection, the sizes, technical specifications and costs of all the market-available H2GEN components were added in the HOMER search space. Moreover, the developed models were also used in assessing the sensitivity of the simulation outputs to several changes in the modelled system design and settings. Using a residential home with frequent power outages in New Delhi, India as a case study, it was found that the optimal sizing of H2Gen Architecture 1 is comprised of a 2 kW electrolyser, a 0.2 kg type-I tank, and a 2 kW water-cooled fuel cell directly connected to the AC bus, offering an operational lifetime of 14.3 years. It was also found that the optimal sizing of Architecture 2 is comprised of a 1 kV PV utilised with the same 2 kW electrolyser, 0.2 kg type-I tank and 2 kW water-cooled fuel cell connected to the AC bus. While the second design was found to have a higher capital cost due to the added PV, it offered a more cost-effective and environmentally friendly architecture, which contributes to the ongoing energy transition. This paper further investigated the capacity expansion of each H2GEN architecture to meet higher load demands or increased grid power outages. From the analysis of the simulation results, it has been concluded that the most feasible and cost-effective H2GEN system expansion for meeting increased power demands or increased grid outages can be realised by using the developed models for optimally sizing the expanded H2Gen on a case-by-case basis because the increase in these profiles is highly time-dependent (for example, an increased load demand or increased grid outage in the morning can be met by the PV, while in the evening, it must be met by the H2GEN). Finally, this paper investigated the impact of other environmental variables, such as the temperature and relative humidity, on the H2GEN’s performance and provided further insights into increasing the overall system efficiency and cost benefit through utilising the H2GEN’s exhaust heat in the home space for heating/cooling and selling the electrolyser exhaust’s O2 as a commodity.