Patent GB-964760-A (GB)
Title: Nuclear reactor
Inventor: WILLIAMS RONALD PETER
IPC: G21C7/02
Filed: 1963-01-08
Abstract: 964, 760. Controlling reactors. UNITED KINGDOM ATOMIC ENERGY AUTHORITY. Dec. 20, 1963 [Jan. 8, 1963], No. 830/63. Heading G6C. A boiling coolant nuclear reactor having a recirculation line for forced circulation of liquid coolant is controlled by varying the recirculation rate by discharging coolant at a variable rate from the recirculation line directly into the boiling coolant (i.e. by-passing the core). The plant described is suitable for marine propulsion and the reactor coolant is water. Power output is controlled by varying the degree of moderation in the core in accordance with the degree of voidage produced in the water by steam bubbles. Nuclear plant. The boiling water reactor comprises a core 11 having fuel elements housed in fuel tubes 12, through which a closed cycle pressurized light water coolant is circulated. A second light water coolant is circulated downwards through an annular-space between the reactor wall and a central tubular baffle 13, and then upwards through the core. Neutron moderation is effected by both primary and secondary coolants. Heat is transferred to the secondary coolant in regions 11 and 15, and steam thus generated is separated in a steam dome 24; the hot water leaves the reactor through outlets 26. Control rods 29 are used for starting up, and normal and emergency shutdown; they are not used for power level control. Steam plant. The steam pipe 25 includes a flowmeter 62, two pressure transducers 54, 57 and a main turbine throttle valve 32. From turbine 31, the steam passes to a condensor 33. Liquid coolant then passes through line 37 to a feed heater 34, de-aereator 38, pump 39, flowmeter 63, control valve 45, and then into the re-circulation line 46, where it mixes with hot water from the reactor outlet 26. The re-circulation line includes a constant speed pump 47 and a throttle 48. A core by-pass line 49 includes a throttle 52, and passes coolant liquid to injectors within the upper region 23 of boiling water in the reactor; it could alternatively be injected into the central region above the heat transfer region 15. The water thus injected condenses steam, without lowering the temperature of the boiling water. If the pressure in line 25 rises excessively due to rapid shutting of valve 32, steam is vented through valve 36. Control. Power controller 50 causes the reactor power level to follow variations in turbine power output in such a way that steam pressure in the line 25 and the reactor steam dome remains constant. To increase reactor power level the steam content of the secondary coolant is lowered by increasing the recirculation rate, causing the reactor reactivity to increase, as the power output rises, the steam content of the secondary coolant rises until stable conditions again prevail, at a higher power rating. However, since the overall reactor temperature coefficient is negative, equilibrium at the new power level is reached at a somewhat lower steam output than at the previous lower power level. Clearly, the recirculation rate can be varied either by adjusting valve 48, or valve 52, or both (line 49 to injectors, line 27 to reactor core). It is not possible to control the reactor by valve 48 alone, with valve 52 permanently closed, since, due to reduction of enthalpy in the coolant entering at 27, the lower power level results in a decrease in the steam content of coolant in the core. Thus the power level is varied by means of valve 52 which causes a greater or lesser proportion of the recirculating coolant to by-pass the core and heat transfer area. To increase the power output, flow through the valve 52 is reduced, the increased flow rate through the core reduces the steam content in the core and increases the neutron moderation. If the valve 52 is opened, the coolant in the core contains more steam and moderation is decreased; the excess steam is condensed by coolant passing through the valve 52 to the injectors. If valves 48 and 52 are both open, the reactor can be controlled by varying the setting of valve 48, since it is in parallel with valve 52.