Abstract:
This document contains a specification for a substation relaying and control wide area network based on a SONET or possibly a T Carrier (Small Site) communication concept. At this level every device at the substation, plant or any place where control of high voltage ( 600  Volts and above) equipment, can be networked. Every secondary signal can be digitized for control, alarm, and indication. SCADA equipment can be interfaced or replaced with this concept. Metering equipment can be interfaced to SONET Protocol without actual secondary values at inputs to control house meter. Panel device(s) footprint will be reduced thereby reducing the control housing dimensions. Stub-up conduit quantity for the power equipment will be reduced thereby reducing labor and material costs. Inventory stock will be reduced thus minimizing storage fees. Reliability and security will be increased. Fault monitoring will be simplified. Surveillance will be more practical. Site to site communications can be approached with leased satellite space as optional communications. Much quicker relay response time to actual fault. All these are a benefit to this design concept.

Description:
FEDERALLY SPONSORED RESEARCH  
         [0001]    Not Applicable  
         SEQUENCE LISTING OR PROGRAM  
         [0002]    Not Applicable  
         BACKGROUND  
       Description of Prior Art  
         [0003]    The “Control System for An Electrical Power Line” in U.S. Pat. No. 3,852,532 to Giles et al. 1974 Dec. 3, had an application to a local and remote site via an analogue signal. This kind of application needed the aid of other relay(s) to protect a line that was, for the most part, electrical mechanical in nature. The “Control And Self-Monitoring System, In Particular For A Multiple Electrical Apparatus Such As A High Tension Circuit Breaker” in U.S. Pat. No. 5,384,678 to Ebersohl et al., 1995 Jan. 24, was an improvement in the use of then current technology, to the protection control of high voltage devices, such as breakers. Further, monitoring and fault protection devices such as “Monitoring and Fault Protection of High Voltage Switch Yards” in U.S. Pat. No. 5,408,176 to Blatt, 1995 Apr. 18, was patented to improve system performance derived from then “state-of-the-art” technology. In 1996 Feb. 13, the “Power Line Communicated System” was U.S. patented to Sargeant et al. This communicated via the power link itself, but still required other relays via hardwired copper size number ten (10) or number twelve (12) conductor for control and often times number eight (8) conductor for long circuit runs. Another U.S. Pat. No. 5,859,596 McRae, 1999 Jan. 12, “Switchyard Equipment Monitoring System and Communications Network Therefor” introduced a power line communication system dependent on signals transmitted and received via the power line. This particular patent demonstrates that a computer can exist in the switchyard. These improvements in the electric industry communications led to the next step in switchyard communications. My invention is an application of communications with a digital solution at the switchyard level.  
           [0004]    There have been other protection and control patents, not mentioned here, that touch on using either fiber (SONET) or microwave to communicate from site to site. My invention lends to applying fiber or 22 AWG copper wires to every piece of equipment in the yard. A synchronous communicated switchyard is a wide area network (WAN). For reason of security coupled with dependability and reliability relay engineers have long been reluctant to fully implement a fully digital solution to relay protection. My invention addresses these concerns and affords these areas, with promise.  
         SUMMARY OF INVENTION  
         [0005]    My invention introduces fiber or 22 AWG copper wires to the switchyard equipment from the control house. It creates an interface between equipment at the switchyard high voltage equipment and equipment in the control house through a WAN. It would require current relay technology modifications to include at least a T1 network interface card. My design includes a device that would convert a T1 protocol to an RS-232 serial interface used extensively in current relay technology. This invention eliminates the larger 30 ampere conductor reducing the installation to supply cable (AC and/or DC) and two communication links for control, one primary and one backup. The network processor ensures communication connectivity by switching from primary to backup fiber in the event of a communication failure. Another fiber link assures a separate and complete alarm and indication (optional) system from the control (and indication optional) fiber link. In the switchyard equipment a device will ensure OVERCURRENT protection in the event of network processor maintenance down time. These communication links isolate control house controls from switchyard controls, but integrate them through the fiber links. At the control house panel, this design reduces the need for a large 30 ampere switching control device(s) to one (1) ampere continuous rating. It reduces the footprint of these switching control device(s) making the panel real estate accommodate a larger control device(s) density. A substation with four (4) 40 MVA power transformers loaded at 80% of maximum line loading at 138 kV would allow all controls onto one simplex panel. 
       
    
    
     DRAWINGS  
     Drawing Figs.:  
       [0006]    The following drawings detail certain aspects of my invention. A complete system description would necessitate many drawings showing very fine detail to the hardware level. However, the following drawings detail enough of information for an individual trained in the art to understand the invention:  
         [0007]    [0007]FIG. 1 is a simplex relay one line showing how a channeled WAN would be interfaced to a high voltage system.  
         [0008]    [0008]FIG. 2A, 2B and  2 C are a simplex WAN with channel assignments, spacing, and equipment employed at a substation.  
         [0009]    [0009]FIG. 3A and 3B are a WAN control house layout showing a comparison between a conventional design and my design.  
         [0010]    [0010]FIG. 4A, 4B, and  4 C are a simplex primary control schematic and connection diagram of a breaker control as it relates to this invention.  
         [0011]    [0011]FIG. 5A, 5B, and  5 C are a simplex WAN panel assembly layout showing a true simplex system on a simplex panel. It also shows a variant of a conventional relay suited for my invention.  
         [0012]    [0012]FIG. 6 is a simplex WAN alarm monitor system.  
         [0013]    [0013]FIG. 7 is a T1/T3 protocol to RS-232 serial interface converter that can be used where needed in my invention.  
         [0014]    [0014]FIG. 8 is a voltage limiter that can be used in case an open circuit occurs on a current transformer circuit. 
     
    
     REFERENCE NUMERALS IN DRAWINGS  
       [0015]    [0015] 110  Line or Tie Breakers (a, b, c, d, e, &amp; f)  
         [0016]    [0016] 111  Trip signal number 1  
         [0017]    [0017] 112  Close signal  
         [0018]    [0018] 113  Status signal  
         [0019]    [0019] 114  Low Pressure Alarm  
         [0020]    [0020] 115  Loss of DC  
         [0021]    [0021] 116  Trip coil #1 monitor  
         [0022]    [0022] 117  Lockout close signal  
         [0023]    [0023] 118  Re-close  
         [0024]    [0024] 119  Re-Trip optional coils 1 or 2  
         [0025]    [0025] 120  Voltage Transformer (VT&#39;S)  
         [0026]    [0026] 130  Circuit Switchers (a, b, c, &amp; d)  
         [0027]    [0027] 140  Current Transformers (a, b, c, &amp; d) (external CT&#39;S)  
         [0028]    [0028] 150  Power Transformers (a, b, c, &amp; d)  
         [0029]    [0029] 160  Total Breakers (a, b, c, &amp; d)  
         [0030]    [0030] 170  Motor Operated Air Switch (optional)  
         [0031]    [0031] 180  Modified Communications Control Processor with OVERCURRENT Element from conventional  
         [0032]    [0032] 190  Channel Bank #1A (CB #1A) To Yard Equipment  110  through  170   
         [0033]    [0033] 200  Channel Bank #1B (CB #1B) To Yard Equipment  110  through  170   
         [0034]    [0034] 210  Digital Cross-Connect (DCS) Digital Switch Between  190  and  200   
         [0035]    [0035] 220  Channel Bank #2 (CB #2) Transformer Differential Relay #3 non-channeled  
         [0036]    [0036] 230  Channel Bank #3 (CB #3) Transformer Differential Relay #4 non-channeled  
         [0037]    [0037] 240  Channel Bank #4 (CB #4) Alarms  
         [0038]    [0038] 250  Channel Bank #5 (CB #5) Bus Differential Relay #7 BUS 1 non-channeled  
         [0039]    [0039] 260  Channel Bank #6 (CB #6) Current Transformers Internal  
         [0040]    [0040] 270  Channel Bank #7 (CB #7) To Existing SCADA/LAPTOP/METERS  
         [0041]    [0041] 280  Channel Bank #8 (CB #8) Transformer Differential Relay #5 non-channeled  
         [0042]    [0042] 290  Channel Bank #9 (CB #9) Transformer Differential Relay #6 non-channeled  
         [0043]    [0043] 300  Channel Bank #10 (CB #10) Line 1 Differential/Distance Relay #1 Primary non-channeled  
         [0044]    [0044] 310  Channel Bank #11 (CB #I1) Line 1 Differential/Distance Relay #2 Secondary non-channeled  
         [0045]    [0045] 320  Channel Bank #12 (CB #12) Bus Differential Relay #8 BUS 2 (optional) non-channeled  
         [0046]    [0046] 330  Channel Bank #13 (CB #13) Line 2 Differential/Distance Relay #1 Primary non-channeled  
         [0047]    [0047] 340  Channel Bank #14 (CB #14) Line 2 Differential/Distance Relay #2 Secondary non-channeled  
         [0048]    [0048] 350  Microcomputer CPU (16-BIT)  
         [0049]    [0049] 360  Input/Output Port from T1/T3 8-BIT Data Bus  
         [0050]    [0050] 370  Input/Output Port to RS-232 Serial Interface  
         [0051]    [0051] 380  CPU Memory (RAM/ROM)  
         [0052]    [0052] 390  8-BIT Split Bus  
         [0053]    [0053] 400  Multiplexor-Third Generation or Better  
         [0054]    [0054] 410  Alarm Monitor Device-74ML (LOCAL, 1-14), 74MR (REMOTE, at Panel)  
         [0055]    [0055] 420  Simplex WAN Panel  
         [0056]    [0056] 430  Zero Signal Reference GRID (ZSRG)  
         [0057]    [0057] 440  Modified Differential/OVERCURRENT Relay from Conventional  
         [0058]    [0058] 450  Modified Line Distance/OVERCURRENT Relay from Conventional  
         [0059]    [0059] 460  Improvement in Square Footage at the Control House/Primary MVA Load  
         [0060]    [0060] 470  OVERVOLTAGE Limiter for Open Current Transformer Secondary  
         [0061]    [0061] 480  Digital Fault Recorder at the T3 Rate non-channeled  
         [0062]    [0062] 490  Other system components not referenced in drawings, but shown for their relevance  
       DETAILED DESCRIPTION  
     Description—FIGS.  1  through  5 C—Preferred Embodiment  
       [0063]    The preferred embodiment showing a system overview of the simplex WAN in the high voltage switchyard is shown in FIG. 1. This shows a relatively standard relay one line with a Line coming in and one Line leaving and devices Breakers  110  through Motor Operated Switch (optional)  170  connected to the 138 kV bus. FIG. 1 also shows at each device Breakers  110  through Motor Operated Switch (optional)  170  a device Modified Communication Control Processor  180 .  
         [0064]    [0064]FIG. 2A, 2B and  2 C show devices Channel Bank #1A  190  through Channel Bank #14  340  all connected to device Multiplexor  400  which is also connected to device Digital Fault Recorder 480, device Alarm Monitor-74MR  410 , and remotely to another site through an optical carrier system, SONET.  
         [0065]    [0065]FIG. 3A and 3B show a usual control house with device Simplex WAN Panel  420  placement and the required device Zero Signal Reference GRID  430  because of total digital solution. FIG. 3A and 3B also shows a comparison between conventional design and my new design invention and this item is listed in Improvement in Square Footage/Load Served at the Control House  460 . NOTE: Design of conventional design assumed known to examiner.  
         [0066]    [0066]FIG. 4A, 4B, and  4 C show controls for device Breakers  110  showing primary controls derived from the usual controls scheme, however, split via the optical fiber communication link to the Modified Communications Control Processor  180 . The breaker controls are restricted to the local breaker area and the Simplex WAN Panel  420  controls are restricted to the control house. Device OVERVOLTAGE Limiter  470  is shown attached to current input to Modified Communications Control Processor  180 . Device OVERVOLTAGE Limiter  470  is best located near a Current Transformer  140  secondary, placed in this case, at the breaker current transformer.  
         [0067]    [0067]FIG. 5A, 5B, and  5 C show a Simplex WAN Panel  420  assembly with all simplex system protection, metering and controls of device Breakers  110  through Motor Operated Switch (optional)  170  listed. A Modified Differential/OVERCURRENT Relay  440  and a Modified Line Distance/OVERCURRENT Relay  450  is also shown in FIG. 5C. It describes their distinct card differences from conventional.  
       FIGS.  6  through  8 —Additional Embodiments  
       [0068]    [0068]FIG. 6 shows an alarm monitor system with an Alarm Monitor Device-74ML (LOCAL, 1-14), 74MR (REMOTE, at panel)  410  and a separate optical fiber link through Channel Bank #4  240  to every switchyard equipment Breakers  110  through Motor Operated Switch (optional)  170 . The Alarm Monitor Device-74MR (REMOTE, at Panel) partial  410  shows a Control Line to the Digital Cross-Connect  210 , which will translate through the Multiplexor  400  for control of fiber path in the event of communication failure.  
         [0069]    [0069]FIG. 7 shows a Microcomputer system with a CPU  350 , an Input/Output Port from T1/T3 8-BIT Data Bus  360 , and Input/Output Port to RS-232 Serial Interface  370 , CPU Memory  380 , and an 8-BIT Split Bus  390  to carry the shifted information with the proper format for RS-232 Communication.  
         [0070]    [0070]FIG. 8 shows a 1000 Volt Limiter  470  with two electrodes gapped, in a glass envelope filled with a neon gas.  
       Operation—FIGS.  1  through 5C  
       [0071]    A Modified Communications Control Processor  180  FIG. 1 will digitize all current, voltage and DC control at the each device Breakers  110  through Motor Operated Switch (optional)  170  into a T1.105 series optical fiber protocol that will be processed via Multiplexor  400  FIGS. 2A, 2B, and  2 C.  
         [0072]    Multiplexor  400 , FIGS. 2A, 2B, and  2 C, is at least a third generation device that has network processing capabilities. Channel Bank #A 190, used to connect controls from devices Breakers  110  through Motor Operated Switch  170  FIG. 1 to the WAN, is the primary optical fiber path for communications. Channel Bank #1B  200  is connected similar as #1A  190 , but is an alternate optical fiber path switched by the Digital Cross-Connect  210  device. This switch takes place in approximately 15 cycles to direct switchyard devices Breakers  110  through Motor Operated Switch (optional)  170  to their requested device Channel Bank #2  220  through Channel Bank #14  340  if the Alarm Monitor Device-74ML and -74MR system  410  detects a communications failure from the primary optical fiber path. Modified Communications Control Processor  180  will have a simple OVERCURRENT element to be switched into operation by a manual cutout contact at the Simplex WAN Panel that is derived from Breakers  110  or Circuit Switchers  130 . FIGS. 2A, 2B and  2 C show a channel assignment for equipment in the switchyard devices Breakers  110  through Motor Operated Switch (optional)  170 . Each frequency will allow synchronous communication through optical fiber (preferred embodiment) or copper (#22 AWG) wires.  
         [0073]    Presently, copper (#12 or #10) is used for the control conductors except in long runs where larger conductor is used. This is because voltage drop necessitates a larger wire size. By using what is shown in FIGS. 2A  2 B, and  2 C, this invention eliminates all but supply (AC &amp; DC) conductors. Even VT&#39;S  120  or CT&#39;S  140  FIG. 1, external or internal, can be digitized at the equipment and sent via the communication link to the appropriate devices in the control house Channel Banks #2  220  through #14  340  excluding #4  240 , and #7  270  FIGS. 2A, 2B, and  2 C.  
         [0074]    Relays devices  220 ,  230 ,  250  and  280  through  340 , in FIGS. 2A, 2B,  2 C,  4 A,  4 B,  4 C,  5 A,  5 B and  5 C will also send control signals to yard equipment devices  110  through  170  FIG. 1. For example, in FIGS. 4A, 4B, and  4 C a relay  300  and  310  or  330  and  340  combined with an integrated control system, that is, a relay for protection with a modification to include; control card, network interface card, and input/output card can be used to operate a line breaker or two  110  FIG. 1. Whether the relay &amp; control system is differential or distance or over-current or other, FIGS. 2A and 2B show how each yard equipment  110  through  170  FIG. 1 will be interfaced to the remainder of the WAN.  
         [0075]    Control devices for  110  through  170  FIG. 1 at the Simplex WAN Panel  420  FIGS. 3A and 3B require one (1) ampere continuous to withstand and much less control contacts. Therefore, more devices can be mounted in less space on the Simplex WAN Panel  420 . FIG. 1 shows what I call a simplex design (based on the primary amperes of 900 ampere conductor at 138 kv for one line) on a simplex panel for the whole substation protection. FIGS. 5A, 5B, and  5 C show a modified protection relay  300  or  310  for line  1  and  330  or  340  that could be used for primary or secondary line protection with six (6) cards as follows:  
         [0076]    1). Primary or secondary line protection card  
         [0077]    2). Control primary or secondary card  
         [0078]    3). Input/output card  
         [0079]    4). Breaker-failure card  
         [0080]    5). Network interface card  
         [0081]    6). Regulated DC converter card  
         [0082]    The relay will be a standard nineteen inches by one and one-half inches. The reason it is small is because the AC system is left in the yard then digitized and transmitted. A replacement card 1, consisting of a bus or transformer differential relay card, can be used. An over-current card can replace card 4 and a control card, for the application, to replace card 2 can be switched. The input/output card will interface the panel&#39;s low amperes, low contacts manual controls to the LAN or WAN FIG. 4C. To devices Breakers  110  through Motor Operated Air Switch  170  on FIG. 1 would be a conduit entrance for one or two supply cables and some communications links. The simplex panel would require a zero signal reference grid (ZSRG)  430  FIG. 3A and 3B located just above the panel near the other cables. As an example of the signals to be functional for breaker controls, I use an 8-bit payload area of a T1.105 series byte synchronized protocol signal for the WAN (switchyard and possible plant through other devices on Multiplexor  400 ). This signal is then multiplexed to 28 T1 rate DS1s signals, of which one is cross-connected by DCS  210  FIG. 2A to two (2) 24 DS0 channel banks. These two consists of a normal fiber and an alternate fiber link for maintenance or communication failure. Two (2) other fibers are used, one for alarms and another for CT&#39;S FIGS. 2A, 2B, and  2 C. The payload for a 1 DSO (breaker controls)  110  FIG. 1 can be coded into the following signals:  
                                                                                                                      1).   Trip signal number 1   (111)            2).   Trip signal number 2 (Not used this case)            3).   Close signal   (112)            4).   Status signal   (113)            5).   Alarms (optional)                    A).   Gas low                   B).   Gas lockout               C).   Low pressure   (114)               D).   Loss of AC               E).   Loss of DC   (115)               F).   Trip coil #1 monitor   (116)               G).   Trip coil #2 monitor                 6).   Lockout close signal - much like   (117)               the software lockout on net-               worked computers, but initiated               by a manual control                 7).   CT-1X (140, FIG. 1)                8).   CT-2X (140)            9).   CT-3X (140)           10).   CT-4X (140)           11).   CT-5X (140)           12).   CT-6X (140)           13).   Re-close   (118)           14).   Re-Trip optional coils 1 or 2   (119)                      
 
         [0083]    Out of these 1, 2, 3, 6, 13 and 14 are receiving signals and the remainder with 4 and 5 as optional are transmitting. These 140 CT&#39;S are all external and on channel bank #1A or #1B  190  or  200  and can be integrated as part of these banks. A priority transmitting processing will take place of fault elements over status and alarms in this case to ensure control priority. Putting all internal CT&#39;S  260  on a separate channel bank #6  260  from the Communication Control Processor 180, to include separate fiber, will ensure a reliable system. Receive and transmit signals are each 64 KBPS. Therefore, there is plenty of payload space to allow these signals. This payload will encompass the coded control signals and will have its&#39; own individual time slot with respect to the WAN. The time limited signal, that is, the transmitter will send an update under a time limit within the given synchronous time slot and will be remembered as a previous state at the receiving equipment such as  250  or  320  will be referenced to a system clock kept by each device  110  through  170 . This time stamp will allow each device  110  through  170  to time error check every function and send an alarm if the update time is in error. Further, in a bus differential system one relay  250  or  320  will address, in this case, two breakers  110  FIG. 1 and three circuit switchers  130  FIG. 1 from its&#39; control card in their appropriate time slot. Sudden pressure relay in a transformer can address this differential relay and it in-turn the appropriate equipment  130  FIG. 1. In all relay applications fault elements will override status or alarms in a priority interrupt fashion from the devices  110  through  170  transmitting signals if that option is used. This means that status and alarms will be an option to Communications Control Processor  180 . The update will occur in a time frame outside of which the system will issue an outside time frame error for the control, status and alarms. This will ensure an efficient optical network performing optimal updates to reduce to only necessary transmissions.  
       Operation—FIGS.  6  through  8   
       [0084]    The Alarm Monitor Device-74MR (REMOTE, at panel)  410  FIG. 6 will do the following:  
         [0085]    1) Will operate at 43.232 MBPS selectable  
         [0086]    2) Will be able to address every device on WAN on command  
         [0087]    3) Device(s) 74ML (1-14)  410  will input a contact from device(s) alarms local to the device(s) to the 74MR, including a self checking contact that will initiate a DCS  210  automatic switch from Channel Bank #1A  190  to #1B  200  from 74MR through Multiplexor  400  in a failure of self check  
         [0088]    4) Will be able to self check system on command  
         [0089]    5) Will annunciate on monitor and issue a remote alarm where programmed and operate as a station annunciator  
         [0090]    6) Will have a reduced input for alarms on Simplex WAN Panel  420   
         [0091]    7) Will have separate cabling or fiber than control and indication  
         [0092]    8) Will input breaker counter information from 74ML (1-14) device(s)  110  and  130   
         [0093]    9) Will input trip coil monitors from device(s)  110  and  130   
         [0094]    10) Will have a five (5) inch screen with man/machine interface and an RS-232 Port in front.  
         [0095]    In FIG. 7 is shown a converter that will be applied throughout my system where a T1/T3 protocol to the familiar serial interface RS-232 is needed. Microcomputer CPU  350  will respond to input/output port  360  that is a low order 8-BIT Data Bus. This word will be stored in  380  CPU Memory by the processor  350 . A word 16-BIT containing the required 10-BIT for RS-232 control will be stored in a register from memory  380 . This system will have an 8-BIT Split Bus  390  that will see the 8-BIT Data Bus and the 2 bits from logically ANDING from  380  CPU Memory 16-BIT word and 8-BIT Data Bus. The CPU  380  will then perform the ANDING and output 10-BIT to the parallel to serial converter. This can then be processed serially.  
         [0096]    [0096]FIG. 8 shows device  470  OVERVOLTAGE Limiter used to limit over-voltage when a current transformer has unintentionally been left open. The rating of this device will vary and be established by allowing the saturation voltage to be maintained with no interference and the neon gas only conducting when the over-voltage is present. If, for example, this current transformer in question is a class 800 relaying CT and it&#39;s at its&#39; full tap with 800 volts saturation. I could allow 125% of saturation voltage which would give me 1000 volts. This device will then limit and conduct current only when there would be possible damage to equipment or personnel. This device, by the neon gas, will also give a visual indication to personnel.  
       Conclusion, Ramifications, and Scope  
       [0097]    Also, since the current and potential signals will be digitized the only place you would need a fault recorder  480  is at the control center. Since the triggers will be done digitally, there would be no need for shunts (usually larger part of equipment). Digital triggers, for example, for fault elements, much like relay elements, are picked up based on a digital number representing an analogue number. Since microwave delay, for example, is 186 miles/1 m-sec and copper delay is 12 miles/1 m-sec there will have to be time synchronization both at the remote substation and control center to compensate for the delay. This implies communication with other devices at the substation such as through a laptop or SCADA or meters via network interface to a channel bank as shown in FIG. 2B  270 . This document describes a Communications Control Processor  180  without an analogue input for density monitoring at breakers  110 , however, one could be provided. Using fiber instead of copper (#22) would give transient immunity for communication control conductors. The following benefits will occur:  
         [0098]    1). Less space requirements for equipment in control houses  
         [0099]    2). Less conduit &amp; cable requirements to equipment  
         [0100]    3). Easier install  
         [0101]    4). Small control device footprint  
         [0102]    5). Easy interface to existing equipment  
         [0103]    6). Less status contacts in breakers/switchers  
         [0104]    7). Better location for fault recorder  
         [0105]    8). Transient signal immunity for control conductors—fiber only  
         [0106]    9). Overall more reliable system errors 1 in 10 to the twelfth for fiber and 1 in 10 to the sixth for copper  
         [0107]    However, copper can be used along with the standard spark gaps and a design to include a separate Transient Voltage Suppression Device located at the supply entrance for the communications equipment Uninterruptible Power Supply. This will include proper system grounding and small K-Factor transformer for non-linear loading that will be small. When equipment is installed in yard equipment device(s) they can be mounted on shock absorbers to lessen vibration interference from switching device(s). Also, an interface device can be designed to allow existing SCADA control to marry my new designed control system. In this way subsystems consisting of partially my new design and partially existing designs can be implemented when an upgrade is desired. To extend the life and reduce maintenance in digital systems from leaky capacitors they will be replaced with solid-state capacitance devices with equivalent capacity. Power Line Carrier equipment can be interfaced very easily to my new system. This system idea can be applied at the Generation, Transmission, Distribution levels and commercial use. This use of controls can be applied to shipboard cabling and generally all apparatus where digital controls are applicable.