Abstract:
This invention relates to a portable or fixed solar powered heating ventilation air conditioner (HVAC) system. The disclosed invention consists of the following major components. 1) Solar Hot Water Tank/Storage Tank, 2) Solar Generator, 3) Solar HVAC Heat Exchanger Unit, 4) Solar Grill, 5) Wireless Network Energy Monitoring System and 6) Supervisor Control and Data Acquisition (SCADA) system. Also included is a list of appliances that the HVAC system can be configured to function as: a) refrigerator, b) air purifier/fan, c) pressure cooker, d) drink dispenser, and e) pressurized hot water supply. The HVAC system and above listed appliances is designed to be used in homes, businesses, camping, military, hospitals, FEMA and in developing countries with very little electrical or plumbing infrastructure. The HVAC is capable of supplying all the above mention functions while being powered solely on solar power, solar hot water/fluid or geothermal and a chilled water source, therefore creating a NetZero Energy Machine™ that required no power from a utility grid when properly sized.

Description:
CROSS-REFERENCE TO RELATED APPLICATIONS (MPEP 201.11) 
       [0001]    None 
       STATEMENT REGARDING FEDERALLY SPONSORED RESEARCH OR DEVELOPMENT (MPEP 310) 
       [0002]    None 
         [0003]    The names of the parties to a joint research agreement (37 CFR 1.71 (g): 
         [0004]    None 
         [0005]    Reference to a “Sequence Listing,” a table, or a computer program listing appendix submitted on compact disc and an incorporation-by-reference of the material on the compact disc.: 
         [0006]    None 
         [0007]    Margins. The sheets must not contain frames around the sight (i.e., the usable surface), but should have scan target points (i.e., cross-hairs) printed on two cater-corner margin corners. 
       BACKGROUND OF THE INVENTION ((MPEP 608.01(c)) 
       [0008]    This invention was not made with government support. The government has no certain rights in the invention. A portion of the disclosure of this patent document contains material to which a claim for copyright is made. The copyright owner has no objection to the facsimile reproduction by anyone of the patent document or the patent disclosure, as it appears in the Patent and Trademark Office patent file or records, but reserves all other copyright rights whatsoever. U.S. Pat. No. 6,257,22 discloses an improvement useful with a portable or backyard-type barbecue grill that is used outdoors in backyards, camping, picnicking, or boating where hot water, steam, or power is not readily or conveniently available, U.S. Pat. No. 5,522,944 discloses an apparatus for converting solar energy to thermal and electrical energy including a substantially unsealed enclosure, an array of photovoltaic cells for converting solar energy to electrical energy located within an enclosure, and a plurality of interconnected heat collecting tubes located within the enclosure and disposed on the same plane as the array of photovoltaic cells for converting solar energy to thermal energy in a fluid disposed within the heat collecting tubes, U.S. Pat. No. 7,781,913 B2 disclose an uninterruptible power supply (UPS) including a first transfer switch, a first battery charger, a second transfer switch, a solar energy absorption board, and a second battery charger. The first transfer switch connects a power source to an electrical device. The first battery charger connects the power source to a storage battery for charging a storage battery. An output of the storage battery is connected to the first transfer switch via a DC/AC inverter. The first transfer switch controls the storage battery to supply power to electrical devices. The second transfer switch connects between the first battery charger and the storage battery. The second battery charger connects the solar energy absorption board to the second transfer switch. The second transfer switch controls the power source to charge the storage battery. U.S. Pat. No. 6,037,567 discloses a vehicle air-conditioning system includes electric heating devices to accelerate a rise in temperature of air for heating a passenger compartment by accelerating a rise in temperature of warm water used to heat the air and by directly heating the air. Electric heating devices are built into a heat exchanger for heating so that the devices can release heat into surrounding air through radiating fins. When the system is in a , heating operation region and the temperature of warm water available to flow through the heat exchanger is below a set temperature T2, the electric heating devices are turned on. A blower for blowing heating air into a passenger compartment through the heat exchanger is stopped, and a warm water valve is opened to allow the warm water to flow through the heat exchanger, whereupon heat from the electric heating devices is released through the radiating fins into the warm water inside the heat exchanger. When the temperature of the warm water rises above the set temperature T2, the blower starts, and heat from the electric heating devices is released through the radiating fins into the air blown by the blower. United States Patent 2010/003, 7888 discloses, a system for heating water including a water heater and a solar collector is provided. The water heater includes a water storage tank, a heating element positioned within the bottom end of the water tank and a lower thermostat Configured to selectively activate the heating element as a function of the water temperature sensed by the temperature sensor of the thermostat. A tank heat exchanger is also positioned within the bottom end portion of the water storage tank. The tank heat exchanger is configured to contain a fluid medium for heat exchange with water in the bottom end portion of the water storage tank. The solar collector is fluidly coupled to the tank heat exchanger of the water heater for circulating the fluid medium through the tank heat exchanger. 
         [0009]    The above mentioned competitor&#39;s patents offer an independent solution to solar heating, air conditioning, hot water grill and an UPS. However, none of the competitor&#39;s offers a complete portable solar powered heating ventilation and air conditioning (HVAC) system with built-in all-in-one multiple appliances with wireless (or hardwired) network energy monitoring system and with a supervisory control and data acquisition systems. In addition to providing a portable fully functional HVAC system the system can be configured to perform the functions of the following appliances: a) means to heat, b) means for air conditioning, c) means for refrigeration, d) means for air purification, e) means for circulating air, f) means for cooking grill, g) means for pressure cooking, h) means for a drink dispenser, i) means for pressurized fluid supply, This portable HVAC system combines several energy technologies to produce what is believed to be the most efficient energy saving machine on the HVAC market today. The HVAC system needs to be connected to a combination of energy sources consisting of photovoltaic panels, solar hot water tank or geothermal and a chilled water source e.g. Home tap water, good water or similar clean water sources even lake water. In fact, a properly sized solar battery bank, solar panels, and solar hot water system and chilled water from a home tap water can create a NetZero Energy Machine where the unit can satisfy all of a user&#39;s electricity needs, hot water needs, cooking energy needs, air conditioner needs, heating needs, and refrigeration energy needs without requiring any connection to a utility electric grid. However, a grid connection is available as an option for those customers that may not live in a location where the sunlight maybe limited. The best application for this HVAC system is intended to be utilized in a living room in a home or apartment, business office space, campers in the field, military field personnel, FEMA, hospitals for quarantine patience&#39;s, people in developing countries with limited or no plumbing and/or electrical infrastructure. 
       BRIEF SUMMARY OF INVENTION 
     DESCRIPTION 
       [0010]    The solar powered HVAC with multiple appliances consist of the following major components. 1) Solar Hot Water Tank/Storage Tank, 2) Solar Generator, 3) Solar powered HVAC Unit, 4) Wireless Network Energy Monitoring System and 5) Supervisor Control and Data Acquisition (SCADA) system. Also included are the following list of appliances that the HVAC system can be configured to function as: a) refrigerator, b) air purifier with fan, c) pressure cooker, d) drink dispenser, and e) portable pressurized hot water supply. 1) The solar water/fluid tank is on wheels and can be cascaded together using garden type hoses or optional fix pipe to create any size hot water tank or storage tank. It also has its own fluid/water pump, electric heating elements, thermocouple, battery, water meter and temperature control unit with wireless network (or hardwired) communications to the main HVAC unit controller. The solar hot water tank&#39;s main function is to generate hot water from the sun&#39;s radiation or use its own electric heating elements to provide hot water to the main HVAC unit for heating. The solar hot water tank has a pressure relief valve, an input valve and outlet valve with standard type garden hose connectors (optional fix pipe for all connection) that allow a garden hose rated for hot water to be connected to corresponding input valve and outlet valves of the main HVAC unit completing a closed loop system. Furthermore, the solar water/fluid tank can be configured to operate as a standalone unit to provide an independent supply of pressurized hot water via a garden hose with a sprayer or shower adapter attached. To receive water or a fluid from a pressurized source, the inlet valve has a wye hose connector with an electric controlled valve that is controlled either by the local controller on the solar water/fluid tank or by the HVAC controller when the solar tank is part of the HVAC system. When the solar tank is part of the HVAC system the water/fluid level sensor is monitored by the HVAC controller. Therefore, if the preset water/level L1 in the solar water/fluid tank drops below level L1, the HVAC controller will open the electric valve on the intake valve to allow pressurized water/fluid to fill the tank to a preset level L2. 2) The solar generator operates as a portable solar generator, and optional uninterruptible power supply to provide alternating current and alternating voltage to electrical loads. The solar generator is the main power source for the HVAC unit and solar hot water tank. The unit has two ways to charge a bank of solar storage batteries. The first method is via an automatic transfer switch with inputs from a solar battery charger and second input from a filtered utility grid power source. The output of the first automatic transfer switch connects to a bank of solar storage batteries to provide it with the choice of charging with photovoltaic cells or grid power. When no solar energy from the sun is available or the batteries charge level is low, the unit switches automatically to the utility grid power source. There is also a manual switch for manually switching the first transfer switch from either solar power or grid power. There is a connector for connecting an external generator to the first transfer switch. A second automatic transfer switch provides electrical loads with a choice of utility grid power source or AC power from a DC/AC inverter. The DC/AC inverter also provides DC power and universal serial bus (USB) power. The charging status of the battery and modes of operation of the solar generator is monitored remotely via wireless or wired network with a Supervisory Control Data Acquisition system. 3) The Solar Powered HVAC unit has an insulated enclosure with a heat exchanger that consist of a plurality of rows of vertically mounted finned pipes that are connected to an upper and lower tank. The upper tank is separated from the lower tank by a plurality of finned tubes fluidly and mechanically connected to both the upper and lower tank. The upper tank has a thermocouple sensor and an electric heating element mechanically mounted inside the tank. The upper tank also has a garden hose type intake valve with a wye connector valve, a pressure relief valve with a valve controlled vent pipe. In the heating mode, the HVAC unit receives hot water via a water/fluid pump mounted either on the solar hot water tank or mounted on the HVAC unit that pumps water or a fluid into the intake wye valve or as an option the unit can receive water/fluid from an alternate pressurized fluid source connected to the wye valve. The lower tank has an outlet valve and garden hose connection back to the intake valve of the solar water/fluid tank to complete a closed fluid system. The HVAC temperature controllers monitor the temperature (T1) of the water in the solar water/fluid tank and the temperature of water in the HVAC upper tank T3. If T1 temperature is lower than its preset temperature T2, and T3 temperature is below its preset temperature T4, then the HVAC unit will activate its heating elements to bring the water temperature T3 to a preset temperature T4. If the temperature T1 of the water in the solar tank is equal to or greater than its preset T2 temperature, and temperature of the HVAC tank is below T4, after a preset check temperature time, then the HVAC temperature controller will activate the water/fluid pump for a predetermined amount of time (t) to refill the HVAC tank with water/fluid from the solar water/fluid tank. A water level sensor checks located in the upper tank of the heat exchanger monitor the water/fluid level in the HVAC upper tank. If the water/fluid level in the upper tank of the HVAC system drops below a preset level L3 then the water level controller will open the electric valve on the wye connector on intake of the valve HVAC system to allow a pressurized water/fluid source to fill the upper tank to a preset level L4. Alternately the water level controller can also activate the solar water/fluid tank pump to fill the HVAC upper tank with water/fluid from the solar water/fluid tank. The HVAC unit can also be optionally configured to operate with large external fluid storage tank when configured for large residential or commercial sized systems. When external storage tanks are utilized, they become a temporary holding place to store hot water/fluid from the solar hot water/fluid tanks before pumping the water/fluid into the HVAC heat exchanger and then back to another storage tank before being pump back into a solar hot water/fluid tank for reheating. In the heating mode of the HVAC system, heat is generated as result of hot water inside of the heat exchanger transferring heat to the finned heat exchanger pipes. There is a fan blower that is activated at a preset outside temperature T5. The activation of the fan blower causes outside air to be drafted into the intake vents and blown across a plurality of finned pipes. The outside air is heated via convection as air passes across the fined pipes as a result of the finned pipes radiating heat when filled with hot water/fluid. The heated air exits the unit through outlet vent. In the air conditioning mode, a thermoelectric cooling generator unit is mounted inside the lid of the HVAC enclosure. The thermoelectric unit provides cooling as result of the thermoelectric effect. This effect happens when a difference in voltage across a material of different Serbect coefficient (N-doped, P-doped) semiconductors produces a temperature difference where absorb heat flows from one side of the junction making one side of the junction cool and the other side warm. The cool side of the thermoelectric unit is facing toward the opened upper tank with a fan that circulates cool air inside the heat exchanger. In this mode, the grill tank top of the heat exchanger is removed. Air circulates inside the heat exchanger by the thermoelectric unit&#39;s fan and cools the finned pipes of the heat exchanger by absorbing thermal energy from the finned pipes. The air condition air flow process is the same as describe above for the heating mode, except the intake air is warm and flows across cold finned pipes of the heat exchanger therefore cooling the air before exiting at the outlet vent. To enhance cooling, ice cubes can be added to the heat exchanger pipes of the upper tank which also fills the lower tank with ice. 4) The Solar Powered Grill requires the solar generator enclosure top to be removed. A grill cover is installed on the HVAC unit using the same hinges used to hinge the solar generator top. The grill cover has a glass opening for viewing while cooking and an electric light to light up the cooking grill. The grill surface tank top is a cooking surface installed on top of the HVAC&#39;s heat exchanger without its pressure seal and all air vents are covered with vent covers to thermally seal the HVAC unit. The grill mode also requires the pressure relief by-pass-valve to be closed to allow the water in the upper tank to vent via the vent pipe so that the fluid/water can reach temperatures above boiling. The grill surface is heated up as result of the grill tank top being in direct contact with the upper tank surface, therefore causing heat to transfer from the upper tank top to the grill surface when the upper tank is full of a hot water/fluid. The grill top also receives heat via convection as result of steam air circulating inside of the heat exchanger tank. 5) The network energy monitoring system uses electrical meters to measure the energy generated by an array of photovoltaic cells/solar panels and measures the energy consumed by all electrical loads. The data is collected by connecting electric meters to the solar generator to monitor the kilowatts hours of electricity generated. To measure the electric energy consumed an electric meter is connected to the output of the solar generator to measure the total kilowatt hours consumed by all the loads. Another meter is connected to solar generators storage batteries to measure the energy generated by the PV Array. To measure BTU&#39;s generated and the amount of hot water produced and consumed, a water meter is place in line with the solar water/fluid tank a long with a water temperature sensor. The water temperature is also measured inside the water tank of the HVAC system. The collected data is used to calculate the BTU&#39;s generated and BTU&#39;s consumed. The energy data is communicated through a wireless network (or hardwired network) to a centralized computer where the data is analyze, stored and graphically displayed to show data trends, 6) The Supervisory Control and Data Acquisition system utilizes a wireless network to send control signals via a touch screen control computer to the HVAC unit controller to control its devices and receives monitoring data over the wireless network from electronic devices and displays device statuses on a controls system screen map. The SCADA unit is also capable of wireless communication with mobile smart phones devices or handheld computers. The main HVAC unit can be configured to operate as the following appliances: 
         [0011]    a. Refrigerator mode—In this mode the thermoelectric unit located in the lid of the HVAC enclosure with its fan pointing down inside of the upper tank generates cool/air in the upper tank. In this mode the upper tank is opened and is used to store items for refrigeration. The air vents are blocked to thermally seal the HVAC enclosure. The refrigerator temperature is monitored by the temperature sensor inside the upper tank and controlled by the HVAC computer controller. Air is circulated inside the upper tank via the thermoelectric unit&#39;s fan. To achieve cooler temperatures, the fan blower is turned to a low speed which will cause air in the lower chamber of the enclosure to circulate around the finned pipes to improve the efficiency of heat transfer which causes the refrigerator unit to cool better. 
         [0012]    b. Air Purifier/Fan—Air filters can be installed inside the vents of the intake air vent and outlet vents to filter air in a room when the fan blower is running. 
         [0013]    c. Drink Dispenser—With the HVAC unit configured as a standalone unit, the upper tank can be filled with any type of drink/liquid and dispensed via the inlet valve or outlet valve by gravity feed. 
         [0014]    d. Pressure Cooker—With the HVAC unit configured as a standalone unit, and the grill tank top installed with its pressure seal mounted between the grill tank top and rim of the upper tank. The pressure relief blocking valve is closed and the vent blocking valve is closed. A small cooking pot with items that are require to be pressure cooked can be placed inside the upper tank and the tank top closed and secured in place with thumb screws or optional hinge clamps. The upper tank is pressurized when a fluid/water inside the upper tank is heated up using the heating elements. 
         [0015]    e. Portable Pressurize Hot Water Supply can be achieved by either utilizing the solar hot water/storage tank or the HVAC units as standalone unit to supply pressurize hot water. A fluid/water pump is installed on either/both the solar water/fluid tank or HVAC unit to achieve a pressurize hot water source with a garden type hose. With a garden type hose connected to either the solar hot water tank or HVAC unit&#39;s outlet valve&#39;s with a water hose sprayer containing a pump switched mounted on the sprayer and wired to a pump, pressurize fluid can be achieved. An optional shower adapter can also be attached to the garden hose to function as a portable shower. 
       BRIEF DESCRIPTION OF DRAWINGS 
       [0016]      FIG. 1  Portable Solar HVAC Assembly—Illustrates the complete assembly of the HVAC system. Shows the heat exchange assembly, thermoelectric unit assembly and fan blower motor being installed in an insulated enclosure. 
         [0017]      FIG. 2  HVAC Enclosure—Illustrates parts of the insulated HVAC enclosure. 
         [0018]      FIG. 3  DC/AC inverter Assembly—Illustrates power DC/AC inverter assembly. 
         [0019]      FIG. 4  Thermoelectric Unit Assembly—Illustrates the complete assembly of the thermoelectric unit. 
         [0020]      FIG. 5  Control Unit Assembly—Illustrates the control unit assembly. 
         [0021]      FIG. 6  Heat Exchange Assembly—Illustrates the complete heat exchange assembly. 
         [0022]      FIG. 7  Solar Generator Block Diagram—Describes the complete block diagram of the solar generator and uninterrupted power supply option. 
         [0023]      FIG. 8  Overall HVAC System Schematic—Describes the overall power and controls schematic of the HVAC system. 
         [0024]      FIG. 9  Portable Solar Hot Water Tank Front View—Illustrates the front view of portable solar hot water tank. 
         [0025]      FIG. 10  Solar Hot Water Tank Rear View—Illustrates the rear view of the portable solar hot water tank. 
         [0026]      FIG. 11  Solar Hot Water Tank Left View—Illustrates the left side of the solar hot water tank. 
         [0027]      FIG. 12  Solar Hot Water Tank Right View—Illustrates the right side of the solar hot water tank. 
         [0028]      FIG. 13  Portable Solar HVAC System—Illustrates all the major components of a complete portable HVAC system installed inside a home with hoses and cabling routed through duct work in a window in a home. 
         [0029]      FIG. 14  Portable Solar Grill Assembly—Illustrates all the major components of a complete portable solar grill system installed inside a home with hoses and cabling routed through duct work in a window in a home. 
     
    
     DETAILED DESCRIPTION OF INVENTION 
     DESCRIPTION 
       [0030]    The disclosed invention consists of the following major components. 1) Solar Hot Water Tank/Storage Tank  536 , 2) Solar Generator  535 , 3) Solar HVAC Unit  537 , 4) Solar Grill  538 , 5) Wireless Network Energy Monitoring System  361  and 6) Supervisor Control and Data Acquisition (SCADA) system  362 . Also included is the following list of appliances that the HVAC system  537  can be configured to function as: a) refrigerator, b) air purifier, c) pressure cooker, d) drink dispenser, and e) pressurized hot water supply. 
         [0031]    1) The solar water/fluid tank  536  is portable and on wheels  470  with cotter pins to secure the wheels in place  485  as described in  FIGS. 9, 10, and 11 . The body of the solar water/fluid tank has an insulated  495  frame  425 ; handle bar  430 , fluid/water pump  509 , thermocouple  491 , fluid level  492 , battery  510 , water meter  516 , electric heating element  490 , Low emission glass  435 , glass support moldings trim and seal  500  and a temperature control unit  515 . There is an upper tank  440  and lower tank  475  that is fluidly and mechanically connected to a plurality of vertically mounted tube pipes  450 . The solar hot water tank  536  has a pressure relief valve  445 , an intake valve  420  and outlet valve  465  with standard type garden hose connectors (optional fix pipe for all connections)  565  that allow a garden hose  525  rated for hot water to connect to the solar water/fluid tank&#39;s  536  corresponding intake valve  420  or outlet valves  465  of the main HVAC unit. The solar hot water tank&#39;s  536  main function is to generate hot water from the sun&#39;s radiation and pump  509  it to the main HVAC unit  537 . The solar water/fluid tanks  536  can be cascaded together using garden type hoses  525  to create any size hot water tank or storage tank  536 . Furthermore, the solar water/fluid tank  536  can be configured to operate as a standalone unit to provide an independent supply of pressurized hot water via a garden hose  525  with an optional sprayer  570  with a switch  575  mounted on the sprayer  570  to activate a water/fluid pump  509  or a shower adapter  577  can be attached to the hose. The solar water/fluid storage tanks  536  utilize a black body (painted flat black) on all exposed metal objects to absorb all wavelengths of the sun&#39;s radiation to assist with heating up the heat exchanger pipes  450 . There is low emission glass  435  mounted on the front of the tank  536 . This glass  435  helps heat up the heat exchanger pipes  450  by allowing short wavelength infrared sunlight to pass through the glass to heat the heat exchange pipes  450  but reflects long wavelength in heat waves inside the tank  536  glass  435  to keep the tank&#39;s heat from escaping. 
         [0032]    2) The solar generator  535  operates as a portable or fixed solar generator  535 , and uninterruptible power supply to provide alternating current and alternating voltage to electrical loads. The solar generator  536  is the main power source for the HVAC unit  537  and solar hot water tank  536 . The unit has two ways to charge the solar battery bank  325 . The first automatic transfer switch  320  has an input from a battery charger  315  that is connected to a filtered  300  utility grid power source  275  while the second input of the transfer switch is from an array of photovoltaic cells/solar panels  335  connected to a battery charge controller  340 . The output of the first automatic transfer switch  320  connects to a bank of solar storage batteries  325  for charging. When no solar charging is available or the batteries charge level is low, as an option the unit switches the charging source to the utility grid power  275 . There is also a manual switch  345  for manually switching the first transfer switch  320  from either solar powered charge or grid powered charge. There is an optional second automatic transfer switch  305  that provides the electrical loads with the choice of utility grid power source  275  or AC power from a DC/AC inverter  330 . 
         [0033]    3) The Solar Powered HVAC unit  537  has an insulated enclosure  115  with a heat exchanger  534  that consist of a plurality of vertically mounted finned pipes  220  that are connected to an upper tank  225  and lower tank  270 . The upper tank  225  is separated from the lower tank  270  by a plurality of finned tubes  220  fluidly and mechanically connected to both the upper tank  225  and lower tank  270 . The upper tank  225  has a thermocouple sensor  235 , an electric heating element  230 , fluid level sensor  255 , pressure sensor  256  mechanically mounted inside the upper tank  225 . The upper tank  225  also has a garden hose  525  type with a garden hose connector intake valve  260  and pressure relief valve  265  with a valve  261  controlled vent pipe  262 . In the heating mode, the HVAC unit  537  receives hot water via a water/fluid pump  509  mounted either on the solar hot water tank  536  or mounted on the HVAC unit  537 . There is a garden hose  525  that connects from the outlet valve  465  on the solar water/fluid tank  536  to the intake valve  260  on the HVAC unit upper tank  225 . The lower tank  270  of the HVAC has an outlet valve  195  with a garden hose connection  565  back to the intake valve  420  of the solar water/fluid tank  536 . The HVAC temperature controllers  160  monitors the temperature (T1) of the water in the solar water/fluid tank  536  and the temperature of water in the HVAC upper tank  225  T3. If T1 temperature is lower than its preset temperature T2, and T3 temperature is below its preset temperature T4, then the HVAC unit  537  will activate its heating elements  230  to bring the water temperature T3 its to a preset temperature T4. If the temperature T1 of the water in the solar tank  536  is equal to or greater than its preset T2 temperature, then the HVAC temperature controller  160  will activate the fluid/water pump  509  for a predetermined amount of time (t) to refill the HVAC tank  537  with the water from the solar water/fluid tank  536 . The heat exchanger  539  is heated up by the hot water/fluid inside of it that comes from either the solar water/fluid storage tank  536  or from activation of heating elements  230 . There is a fan blower  190  that intakes outside air through the intake vents  15  and circulates the air through finned pipes  220  of the heat exchanger  539  where the air absorbs heat from the radiating heated finned pipes  220  and exits through the outlet vent  16 . In the air conditioning mode, a thermoelectric unit  534  mounted inside the lid of the HVAC&#39;s enclosure  115  is used to cool the air in the upper tank  225  of the heat exchanger  539  with the grill tank top  240  of the heat exchanger  539  removed. Cold air flows inside the heat exchanger  539  from the thermoelectric unit  534  and cools the finned pipes  220  of the heat exchanger  539  by absorbing heat energy from the finned pipes  220 . Therefore, when the fan blower circulates warm air flows into the intake vent  15  and across the cold finned pipes  220  of the heat exchanger  539 , heat is transferred to the finned pipes to cool the air that arrives at the outlet vent  16 . The HVAC unit creates condensation in both the air condition mode and refrigeration mode as result of warm air coming in contact with the heat exchanger finned pipes  220 . The condensation is collected in a drip pan  200  located at the bottom of the enclosure with a drain line  205  that drains fluid to a bottle  215  via gravity feed or optional via a water/fluid pump  205 . The drained fluid is stored in a water/fluid bottle  215 . Moreover, ice cubes can be added to the opened upper tank  225  of the heat exchanger  539  to enhance the cooling effect of the HVAC unit. 
         [0034]    4) The Solar Powered Grill  535  requires the solar generator  536  enclosure top  535  to be removed and mounted on top of the battery bank enclosure  325  using the same type of hinges and latches used on the HVAC enclosure. The grill covers  246  is installed on the HVAC unit  537  using the same hinges  247  and latches used to hinge the solar generator lid  535 . The grill surface tank top  240  is installed without its pressure seal  248  and the air vents  15  &amp;  16  are covered with vent covers  17  to thermally seal the HVAC enclosure  115 . The grill mode also requires the pressure relief by-pass-valve  265  to be closed to block any water/fluid from coming in contact with the pressure relief valve. The vent valve is opened to allow the water in the upper tank  225  to vent via the vent pipe  262  so that the fluid/water in the upper tank can reach temperatures above boiling. The grill surface  245  is heated up as result of the tank top  240  being in direct contact with the upper tank  225  when it is full of hot water/fluid, therefore causing heat to transfer from the upper tank top  225  to the grill surface  245  via direct contact and from convection as result of hot air circulating inside of the upper tank. 
         [0035]    5) The network energy monitoring system  361  uses electrical meters  390  &amp;  391  to measure the energy generated by an array of photovoltaic cells/solar panels  335  and measures the energy consumed by the electrical loads  310 . The data is collected by connecting electric meters  390  &amp;  391  to the solar generator  535  to monitor the kilowatts hours generated. To measure the electric energy consumed, an electric meter is connected to the output of the solar generator or optionally to each individual electric load devices  310 . To measure the BTU generated and the amount of hot water produced and consumed, a water meter  516  is place in line with the solar water/fluid tank  536  along with a water thermocouple  491 . The water temperature is also measured inside the water tank  225  of the HVAC system  537  using thermocouple  235 . The collected data is used to calculate the BTU&#39;s generated and BTU&#39;s consumed. An energy data report is communicated through a wireless network (or hardwired network) to a centralized energy monitoring computer  361  where the data is analyzing, stored and graphically displayed to show data trends. 
         [0036]    6) The Supervisory Control and Data Acquisition (SCADA) system  362  utilizes a wireless network to send control signals to the HVAC unit controller  160  to control its devices and receives monitoring data over the wireless network  365  from electronic devices. There is a touch control pad with an electronic display on the HVAC unit  537  (not shown on the drawings) that allow an operator to control all the functions of the HVAC unit  537  and control the solar generator, heating, air conditioning, fan, refrigerator, air purifier, grill, pressure cooker and pressurized fluid supply. The SCADA system  362  is also capable of communicating with mobile handheld device like smart cell phones or handheld computers. The main HVAC unit  537  can be configured to operate as the following appliances: 
         [0037]    a. Refrigerator mode—In this mode the thermoelectric unit  534  installed in the lid of HVAC enclosure  115  with its fan  95  pointing down inside of the upper tank  225  creates cool air using a thermoelectric cooling generator. The upper tank  225  is opened and is use to storage items for refrigeration. The air vents  15  &amp; 16  are blocked to thermally seal the unit. The refrigerator temperature is monitored by a thermocouple  235  located inside the upper tank  225  and controlled by the HVAC computer controller  155  or optionally via a touch pad and display unit not shown on the drawings. 
         [0038]    b. Air Purifier/Fan—Air filters  17  can be installed inside the vents of the intake air vent  15  and outlet air vents  16  to filter air in a room when the fan blower is running. 
         [0039]    c. Drink Dispenser—The HVAC upper tank  225  can be filled with any type of drink liquid and dispensed via the outlet valve  195  and or inlet value  260 . 
         [0040]    d. Pressure Cooker—In this mode the grill tank top  240  is installed with its pressure seal  248  mounted between the tank top  240  an upper tank  225 . The pressure relief blocking valve is closed  266  and the vent blocking valve  261  is closed to create a pressurize enclosure inside the heat exchanger  539 . A small cooking pot with items requiring pressurize cooking can be placed inside the upper tank  225  and then securing the grill tank top  240  closed with thumb screws  250  or optional hinge clamps  251 . This step will allow the upper tank  225  to become pressurize when a fluid is heated up inside the upper tank  225  using heating elements  230 . 
         [0041]    e. Portable Pressurize Hot Water Supply can be configured by either utilizing the solar hot water tank  536  or the HVAC unit  537  to supply pressurized hot water. A fluid/water pump  509  can be installed on either on the solar water/fluid tank  536  or HVAC unit  537  to achieve a pressurized hot water supply. With a garden type hose  525  attached to the outlet valve of the HVAC unit, a shower adapter  577  can be attached to establish a means for showering or a water hose sprayer  570  with a switched mounted on it to activate a water/fluid pump can be attached to the hose to provide a mean to spray hot water. 
       SEQUENCE LISTING 
       [0042]    None