Abstract:
A method of computer-based simulation of a cooling system includes receiving configuration data for a heat exchanger of the cooling system, customizing the configuration data for the heat exchanger; simulating cooling system performance by processing the customized configuration data through a model of the cooling system, and generating simulated cooling system performance data, based on the simulating, for evaluating operation of the cooling system.

Description:
CROSS-REFERENCE TO RELATED APPLICATIONS  
       [0001]     This application claims the benefit of U.S. Provisional Application No. 60/675,729, filed on Apr. 28, 2005. The disclosure of the above application is incorporated herein by reference. 
     
    
     FIELD  
       [0002]     The present teachings relate to cooling systems, and more particularly to simulating performance of a cooling system.  
       BACKGROUND  
       [0003]     Traditional cooling systems, such as refrigeration and air-conditioning systems, include a compressor, a condensing unit, an expansion device and an evaporator. The compressor compresses gaseous refrigerant exiting the evaporator and discharges the high pressure refrigerant to the condensing unit. The condensing unit operates as a heat exchanger enabling heat transfer from the gaseous refrigerant to a heat sink (e.g., air or water). The refrigerant condenses within the condensing unit and a state change occurs from gas to liquid. The liquid refrigerant exits the condensing unit and flows to the evaporator through the expansion device. The evaporator also operates as a heat exchanger enabling heat transfer from the atmosphere surrounding the evaporator to the liquid refrigerant. As the heat transfer occurs, the temperature of the refrigerant increases until a state change occurs from liquid to gas. The gaseous refrigerant is drawn into the suction side of the compressor and the cooling cycle continues.  
         [0004]     In order to competently design a new cooling system or maintain an existing cooling system, the potential performance of the individual components within the system need to be estimated. Traditionally, system components are selected based on the refrigerant type and ratings provided by the manufacturer. However, these ratings are determined under fixed conditions and not actual system operational conditions. Therefore, although the rating of a component may suggest that it is proper for the particular cooling system, the actual performance of that component within the cooling system may be far less than optimal.  
       SUMMARY  
       [0005]     Accordingly, a method of computer-based simulation of a cooling system is provided. The method includes receiving configuration data for a heat exchanger of the cooling system, customizing the configuration data for the heat exchanger; simulating performance of the cooling system by processing the customized configuration data through a model of the cooling system, and generating simulated cooling system performance data, based on the simulating, for evaluating operation of the cooling system.  
         [0006]     Additionally, another method of computer-based simulation of a cooling system includes receiving inputted parametric data for the cooling system corresponding to predetermined simulated operating conditions for the cooling system, simulating cooling system performance by processing the parametric data through a model of the cooling system, and generating simulated cooling system performance data, based on the simulating, for evaluating operation of the cooling system.  
         [0007]     Further, a method of computer-based simulation of a heat exchanger system is provided. The method includes receiving heat exchanger system configuration data, simulating heat exchanger system performance by processing the heat exchanger system configuration data through a model of the heat exchanger system, generating simulated heat exchanger system performance data based on the simulating, and rating the heat exchanger system based on the generated simulated performance data.  
         [0008]     Further areas of applicability will become apparent from the detailed description provided hereinafter. It should be understood that the detailed description and specific examples, while indicating a preferred embodiment, are intended for purposes of illustration only and are not intended to limit the scope of the teachings. 
     
    
     BRIEF DESCRIPTION OF THE DRAWINGS  
       [0009]     The present teachings will become more fully understood from the detailed description and the accompanying drawings, wherein:  
         [0010]      FIG. 1  is a schematic illustration of an exemplary cooling system;  
         [0011]      FIG. 2  is a flowchart illustrating general steps of a cooling system design simulator according to the present teachings;  
         [0012]      FIG. 3  is a screen-shot illustrating software-based input of cooling system component information;  
         [0013]      FIG. 4  is a screen-shot illustrating system type and operation mode inputs including single and dual capacity systems;  
         [0014]      FIG. 5  is a screen-shot illustrating refrigerant charge inputs;  
         [0015]      FIG. 6  is a screen-shot illustrating sub-cooling and superheat parameter inputs for flow control;  
         [0016]      FIG. 7  is a screen-shot illustrating capillary tube flow control device inputs;  
         [0017]      FIG. 8  is a screen-shot illustrating orifice flow control device inputs;  
         [0018]      FIG. 9  is a screen-shot illustrating exemplary outputs for flow control devices;  
         [0019]      FIG. 10  is a screen-shot illustrating exemplary selection criteria for a thermal expansion valve (TXV);  
         [0020]      FIG. 11  is a screen-shot illustrating evaporator entering air temperature and air flow inputs for a single capacity system;  
         [0021]      FIG. 12  is a screen-shot illustrating evaporator entering air temperature and air flow inputs for a dual capacity system;  
         [0022]      FIG. 13  is a screen-shot of an exemplary psychometric calculator;  
         [0023]      FIG. 14  is a screen-shot illustrating evaporator heat exchanger tubing inputs;  
         [0024]      FIG. 15  is a screen-shot illustrating evaporator heat exchanger fin inputs;  
         [0025]      FIG. 16  is a screen-shot illustrating an exemplary corrugated fin pattern for the heat exchanger;  
         [0026]      FIG. 17  is a screen-shot illustrating evaporator scaling factor inputs;  
         [0027]      FIG. 18  is a screen-shot illustrating condenser entering temperature and air flow inputs for a single capacity system;  
         [0028]      FIG. 19  is a screen-Shot illustrating condenser entering temperature and air flow inputs for a dual capacity system;  
         [0029]      FIG. 20  is a screen-shot illustrating condenser heat exchanger tubing inputs;  
         [0030]      FIG. 21  is a screen-shot illustrating condenser heat exchanger fin inputs;  
         [0031]      FIG. 22  is a screen-shot illustrating condenser scaling factor inputs;  
         [0032]      FIG. 23  is a screen-shot illustrating a condenser database;  
         [0033]      FIG. 24  is a screen-shot illustrating compressor search and selection inputs;  
         [0034]      FIG. 25  is a screen-shot illustrating compressor search results;  
         [0035]      FIG. 26  is a screen-shot illustrating compressor details for an exemplary compressor selected from the search results;  
         [0036]      FIG. 27  is a screen-shot illustrating compressor rated capacity values;  
         [0037]      FIG. 28  is a screen-shot illustrating compressor rated mass flow rate values;  
         [0038]      FIG. 29  is a screen-shot illustrating compressor rated EER values;  
         [0039]      FIG. 30  is a screen-shot illustrating compressor rated current values;  
         [0040]      FIG. 31  is a screen-shot illustrating compressor search inputs based on user specified capacity;  
         [0041]      FIG. 32  is a screen-shot illustrating compressor rated capacity;  
         [0042]      FIG. 33  is a screen-shot illustrating a compressor operating envelope;  
         [0043]      FIG. 34  is a screen-shot illustrating re-rated compressor capacity;  
         [0044]      FIG. 35  is a screen-shot illustrating a non-manufacturer specific compressor selection option;  
         [0045]      FIG. 36  is a screen-shot illustrating a non-manufacturer specific compressor library;  
         [0046]      FIG. 37  is a screen-shot illustrating rated performance of a non-manufacturer specific compressor selected from the library;  
         [0047]      FIG. 38  is a screen-shot illustrating tubing and line heat transfer inputs;  
         [0048]      FIG. 39  is a screen-shot illustrating tubing and line heat transfer inputs for a system including a reversing valve;  
         [0049]      FIG. 40  is a screen-shot illustrating an accumulator database;  
         [0050]      FIG. 41  is a screen-shot illustrating accumulator geometry inputs;  
         [0051]      FIG. 42  is a screen-shot illustrating line heat transfer inputs;  
         [0052]      FIG. 43  is a screen-shot illustrating a line heat transfer calculator  
         [0053]      FIG. 44  is a screen-shot illustrating device pressure drop inputs;  
         [0054]      FIG. 45  is a screen-shot illustrating exemplary parametric inputs;  
         [0055]      FIG. 46  is a screen-shot illustrating exemplary parametric outputs;  
         [0056]      FIG. 47  is a screen-shot illustrating an exemplary system EER curve;  
         [0057]      FIG. 48  is a screen-shot illustrating an exemplary parametric simulation summary;  
         [0058]      FIG. 49  is a screen-shot illustrating air-cooled condensing unit (ACU) selection;  
         [0059]      FIG. 50  is a screen-shot illustrating ACU selection inputs;  
         [0060]      FIG. 51  is a screen-shot illustrating a selected ACU summary;  
         [0061]      FIG. 52  is a screen-shot illustrating ACU components details;  
         [0062]      FIG. 53  is a screen-shot illustrating ACU compressor capacity based on evaporator temperature and condensing temperature;  
         [0063]      FIG. 54  is a screen-shot illustrating ACU compressor power based on evaporator temperature and condensing temperature;  
         [0064]      FIG. 55  is a screen-shot illustrating ACU condenser details;  
         [0065]      FIG. 56  is a screen-shot illustrating ACU key features;  
         [0066]      FIG. 57  is a screen-shot illustrating a key feature comparison between ACUs;  
         [0067]      FIG. 58  is a screen-shot illustrating ACU search results based on the ACU&#39;s capacity;  
         [0068]      FIG. 59  is a screen-shot illustrating refrigerant saturated properties inputs;  
         [0069]      FIG. 60  is a screen-shot illustrating refrigerant superheated properties inputs;  
         [0070]      FIG. 61  is a screen-shot illustrating refrigerant superheated enthalpy inputs;  
         [0071]      FIG. 62  is a screen-shot illustrating refrigerant liquid properties inputs;  
         [0072]      FIG. 63  is a screen-shot illustrating key simulation inputs;  
         [0073]      FIG. 64  is a screen-shot illustrating simulation results in graphical format;  
         [0074]      FIG. 65  is a screen-shot illustrating evaporator and condenser coil outputs;  
         [0075]      FIG. 66  is a screen-shot illustrating compressor performance data;  
         [0076]      FIG. 67  is a screen-shot illustrating seasonal energy efficiency ratio (SEER) selection;  
         [0077]      FIG. 68  is a screen-shot illustrating exemplary SEER inputs;  
         [0078]      FIG. 69  is a screen-shot illustrating an SEER summary;  
         [0079]      FIG. 70  is a screen-shot illustrating SEER inputs for a dual capacity system;  
         [0080]      FIG. 71  is a screen-shot illustrating an SEER summary for the dual capacity system;  
         [0081]      FIG. 72  is a screen-shot illustrating heating seasonal performance factor (HSPF) selection;  
         [0082]      FIG. 73  is a screen-shot illustrating HSPF inputs and calculation;  
         [0083]      FIG. 74  is a screen-shot illustrating an HSPF summary;  
         [0084]      FIG. 75  is a screen-shot illustrating HSPF inputs and calculation for a dual capacity system;  
         [0085]      FIG. 76  is a screen-shot illustrating an HSPF summary for a dual capacity system;  
         [0086]      FIG. 77  is a screen-shot illustrating a psychrometric calculator used to calculate moist air properties;  
         [0087]      FIG. 78  is a screen shot illustrating a psychrometric chart graphically displaying moist air properties;  
         [0088]      FIG. 79  is a screen-shot illustrating manufacturer engineering bulletins provided by the cooling system design simulator;  
         [0089]      FIG. 80  is a screen-shot illustrating heat exchanger fin inputs for a condenser model;  
         [0090]      FIG. 81  is a screen-shot illustrating heat exchanger tube inputs for the condenser model;  
         [0091]      FIG. 82  is a screen-shot illustrating heat exchanger header tank inputs for the condenser model;  
         [0092]      FIG. 83  is a screen-shot illustrating cooling air/refrigerant inputs for the condenser model;  
         [0093]      FIG. 84  is a screen-shot illustrating condenser geometry outputs of the condenser model;  
         [0094]      FIG. 85  is a screen-shot illustrating condenser performance maps of the condenser model; and  
         [0095]      FIG. 86  is a screen-shot illustrating condenser charts of the condenser model.  
     
    
     DETAILED DESCRIPTION  
       [0096]     The following description is merely exemplary in nature and is not intended to limit the present disclosure, application, or uses.  
         [0097]     Referring now to  FIG. 1 , a generic cooling system  10  may include a compressor  12 , a condenser  14 , an expansion device  16  and an evaporator  18 . The compressor  12  may be controlled by a controller  20  and may compress gaseous refrigerant exiting the evaporator  18 . The compressor  12  may discharge the high pressure refrigerant to the condenser  14 . The condenser  14  may operate as a heat exchanger enabling heat transfer (Q 1 ) from the gaseous refrigerant to a heat sink (e.g. air or water). The refrigerant may condense within the condenser  14  and a state change may occur from gas to liquid. The liquid refrigerant may exit the condenser  14  and flow to the evaporator  18  through the expansion device  16 . The evaporator  18  may also operate as a heat exchanger enabling heat transfer (Q 2 ) from the atmosphere surrounding the evaporator  18  to the liquid refrigerant. As the heat transfer occurs, the temperature of the refrigerant may increase until a state change occurs from liquid to gas. The gaseous refrigerant may be drawn into the suction side of the compressor  12  and the cooling cycle may continue.  
         [0098]     The cooling system design simulator may include a series of sub-routines to determine the performance of the individual components of exemplary cooling systems and/or the cooling system  10  as a whole. More particularly, the design simulator may perform steady-state design and analysis of vapor compression air-to-air-systems operating in either heating or cooling modes. A cooling system model may be based on underlying physical principles and generalized correlations to avoid the limitations of empirical correlations derived from manufacturer specifications. As a hardware-based model, a user may specify the individual component parameters and define the geometry of tubing connecting the cooling system components. The design simulator may preferably be provided as a software-based computer program. More specifically, the design simulator may preferably include a Windows interface functionality integrated in the software to enable quick cooling system design. Other complimentary functions may be integrated to streamline design efforts. These include, but are not limited to look-up tables for refrigerant and psychrometric properties of air.  
         [0099]     Referring now to  FIG. 2 , a flowchart illustrates the general steps of the cooling system design simulator. In step  100 , the user may select the operating mode of the cooling system (i.e., cooling or heating). In step  102 , the user may specify the-refrigerant charge. The user may select the flow control in step  104 . In step  106 , the user may input evaporator data. In step  108 , the user may determine whether the cooling system includes an air-cooled condensing unit (ACU) in step  108 . If the cooling system does include an ACU, the simulator may continue in step  110 . If the cooling system does not include an ACU, the simulator may continue in step  112 .  
         [0100]     In step  110 , the user may input the ACU data. In step  112 , the user may input compressor data. The user may input condenser data in step  114 . In step  116 , the user may input tubing and line heat transfer data for the plumbing between components of the cooling system. In step  118 , the user may determine whether the cooling system includes an accumulator. If the cooling system does include an accumulator, the simulator may continue in step  120 . If the cooling system does not include an accumulator, the simulator may continue in step  122 . In step  120 , the user may input accumulator data. In step  122 , the user may input refrigerant properties. In step  124 , the user may run the simulation based on the input data and the simulation may end.  
         [0101]     Referring now to  FIGS. 3 through 86 , the cooling system design simulator will be described in further detail.  FIGS. 3 through 86  generally provide screen-shots of a software-based implementation of the cooling system design simulator. More particularly,  FIG. 3  is a screen-shot illustrating a generic cooling system schematic. As similarly described above with reference to  FIG. 1 , the cooling system schematic includes a condenser, a flow control device, an evaporator and a compressor. The cooling system may be simulated in either a cooling mode or a heating mode. The user may select the operating mode by clicking on Inputs in the toolbar and selecting the System Type and Operation Mode option.  FIG. 4  illustrates a screen-shot of a system type and mode screen. The user may select between an A/C system operating in respective cooling and heating modes or a refrigeration system operating in a cooling mode. The user may select between a single capacity system leg., high or low capacity) and a dual capacity system (e.g., high and low capacities). The user may also enter a simulation title and notes.  
         [0102]     The user may specify the refrigerant charge for the cooling system or may have the simulator calculate the refrigerant charge from the other system parameters. The user may input the refrigerant charge data by-clicking on Inputs in the toolbar and selecting the Specify Refrigerant Charge and Edit Inputs option.  FIG. 5  illustrates a screen-shot of the refrigerant charge menu. The user may input the refrigerant charge in lbs and either the sub-cooling temperature (° F.) at the condenser discharge or the superheat temperature (° F.) at the compressor inlet.  
         [0103]     The simulator enables the user to select between flow control device options. The options include capillary tube and orifice. Alternatively, the user may specify flow control parameters including the condenser discharge sub-cooling temperature (° F.) and the compressor inlet superheat temperature (° F.). The simulator may calculate the equivalent Thermal Expansion Valve (TXV), capillary tube and orifice sizes to achieve these conditions; as described in further detail below. The flow control may be selected by clicking on Inputs in the toolbar and choosing the Flow Control menu or by clicking on the flow control illustration.  
         [0104]      FIG. 6  provides a screen-shot of the Flow Control Devices screen with the sub-cooling/superheat parameters option selected. The user may input the sub-cooling and superheat temperatures.  FIG. 7  provides a screen-shot of the Flow Control Devices screen with the capillary tube device selected. The user may input the superheat temperature, number of parallel capillary tubes, inside diameter of the capillary tube(s) and the length of the capillary tube(s).  FIG. 8  provides a screen-shot of the Flow Control Devices screen with the orifice device selected. The user may input the superheat temperature, the number of parallel short tube orifices, the inside diameter of the short tube orifice(s) and the length of the short tube orifice(s).  FIG. 9  illustrates an output screen for the Flow control Devices including properties and property values for the TXV, capillary tube and orifice.  
         [0105]     Referring now to  FIG. 10 , the TXV may be selected by the user by accessing TXV Selection in the Tools menu. A TXV selection screen is provided and includes a Search button which searches available TXVs based on exemplary inputs of: refrigerant, percent bleed, evaporator, condensing, liquid temperature and system capacity and the like. Many of the above parameters may be entered automatically on the execution of the system simulation. A provision has been provided so that the user may choose to enter the required data manually for selecting TXV without running the system simulation. The user may also enter other criteria including valve type series, connection type, strainer, distributor type and valve loading range. The available TXVs are listed based on the input including the capacity, percent loading, port type and recommended application.  
         [0106]     The user may customize data for the evaporator. The data for the evaporator may be entered by opening the evaporator screen. The user may access this screen by either choosing Inputs on the toolbar and the Evaporator option or by clicking on the evaporator image. The evaporator may require several inputs that are grouped into four categories: (i) entering air condition (dry bulb and wet bulb temperature) and air flow rate/fan power, (ii) whether the fan motor is in or out of the air stream, (iii) heat exchanger physical properties and (iv) scaling factors to adjust simulation results to match with measured system performance data. Expert tips may be included on each input screen to help the user streamline their design efforts. The expert tips may be accessed by choosing the icon with question mark.  
         [0107]      FIG. 11  provides a screen-shot of an Entering Air and Fan input screen for a single capacity system.  FIG. 12  provides a screen-shot of an Entering Air and Fan input screen for a dual capacity system. The user may input the entering air information including the dry bulb temperature (° F.) and the wet bulb temperature (° F.). The user may also input the fan information including the air flow rate (Ft 3 /Min) and power input (Watts). The air flow rate and fan power inputs depend on whether the system is a single capacity or a dual capacity system. The Entering Air Fan input screen also provides access to a Psychrometric Calculator and the option of adding the evaporator fan motor heat to the conditioned air stream. The Psychrometric Calculator is illustrated in  FIG. 13  and may be accessed by choosing the button with a thermometer. The Psychometric Calculator provides accurate entering air condition information.  
         [0108]      FIG. 14  provides a screen-shot of a Heat Exchanger tubing input screen. The user may input customized geometry information including number of rows, number of equivalent, parallel refrigerant circuits (two-phase and liquid phase), horizontal tube spacing, vertical tube spacing and number of tubes per row, tubing outside diameter, tubing wall thickness, smooth or rifled and tube material (e.g., copper).  FIG. 15  provides a screen-shot of a Heat Exchanger fin input screen. The user may input geometry information including finned length, finned height, fin density, fin thickness, fin pattern, fin material, refrigerant flow configuration and coil part number.  FIG. 16  provides a screen illustrating fin customization.  
         [0109]      FIG. 17  provides a screen-shot of an Evaporator scaling factors input screen. The scaling factors may be divided into air side and refrigerant side groups. The air side group may include heat transfer, pressure drop and surface area scaling factors. The refrigerant side group may include heat transfer, pressure drop and surface area scaling factors. The scaling factors may enable the user to adjust the simulation results to match measured system performance.  
         [0110]     The user may customize data for the condenser. The data for the condenser may be entered by opening the condenser screen. The user may access this screen either by choosing Inputs on the toolbar and the Condenser menu or by clicking on the condenser image on the main screen. This opens a condenser dialog screen, which is illustrated in  FIG. 18  for a single capacity system and  FIG. 19  for a dual capacity system. Initially, the user may input entering air temperature data and fan parameters. The entering air temperature data may include dry bulb temperature (° F.) and wet bulb temperature (° F.). The fan parameters may include air flow rate (ft 3 /min) and power input (Watts).  
         [0111]      FIG. 20  provides a screen-shot of a Condenser Heat Exchanger tubing input screen. The user may customize the geometry information similar to that described above with regard to  FIG. 14 .  FIG. 21  provides a screen-shot of a Heat Exchanger fin input screen. The user may input geometry information similar to that described above with regard to  FIG. 15 .  FIG. 22  provides a screen-shot of a condenser Scaling Factors input screen. The scaling factors may be divided into air side and refrigerant side groups and may include those described above with regard to  FIG. 17 .  
         [0112]     Referring now to  FIG. 23 , the user may select a specific condenser from a list of available models. The user may access a database by clicking on the Show Condenser List button on the bottom left corner of tubing input screen. A table with condenser information appears. The user may scroll through the condenser list to find the condenser model that meets system requirements. The condenser list is initially ordered by condenser part number. The user may re-order the condenser list by another parameter by clicking on that parameter in the top row of condenser list. Condenser geometry parameters are automatically entered in the appropriate fields of the Condenser screen when user selects a condenser by double clicking on the condenser part number. An engineering drawing of a particular condenser (not shown) is provided upon the user&#39;s request.  
         [0113]     Referring now to  FIG. 24 , the user may access a database of manufacturer&#39;s compressors (both air-conditioning and refrigeration compressors models). The user may search and view the details of all available compressors. The compressor details may include compressor type (e.g., semi-hermetic, hermetic, scroll, etc.), application type (e.g., refrigeration and air-conditioning), temperature range (e.g., air-conditioning, medium temp. high temp., etc.), voltage, frequency, capacity, power, amps, compressor operating envelope and re-rating of compressor performance to a user specified condition. The compressor selection screen may be accessed either by choosing Inputs from the toolbar and Compressor menu or by clicking on the compressor image in the main screen.  
         [0114]     Referring now to  FIGS. 25 and 26 , the compressor database may be searched by entering a known compressor model in the Model Name field and clicking the Search button. The model name can be complete or partial. For example, if the user enters the model name as ZR34K3-PFV and Refrigerant R-22, the search is very specific and only the ZR34K3-PFV compressor will show up in the search result. However, if the user enters the model name as ZR, all the models starting with ZR will appear in the compressor result list. The search settings and the results include compressor model (e.g., ZR34K3), voltage, phase and frequency, application (e.g., air-conditioning), product type (e.g., scroll), capacity, power and energy efficiency ratio (EER) at a specified rating point (e.g., 45° F. Evaporator, 130° F. Condenser), record date and tested condition (e.g., return gas temperature/superheat and subcooling). Capacity, power and current (amp) data over the entire operating range of the compressor are shown in the Rated Capacity, Rated Power and other tabs (see  FIGS. 27 through 30 ), respectively, once a compressor model is selected from the generated compressor list.  
         [0115]     Referring now to  FIG. 31 , the user can search the compressor database based on a specified capacity range. The user enters a capacity and specifies a capacity tolerance (±5% to ±50%), refrigerant, application and product type and clicks on the Search button. For example, if the user enters the capacity as 34,000 Btu/hr with a capacity tolerance of −10% to +10%, 45° F. evaporator temperature, 130° F. condensing temperature, application type as air-conditioning, product type as scroll and refrigerant as R-22 the search lists several corresponding compressor models. Capacity, power and current information are displayed when the user selects a particular compressor model from the compressor list. Compressor models that are obsolete are highlighted.  FIGS. 32 through 34  illustrate relevant compressor information including rated capacity, operating envelope and re-rated capacity, respectively.  
         [0116]     Referring now to  FIG. 35 , the simulator may enable the user to input a non-manufacturer specific or user-specified compressor. Access to the framework for adding user specified compressor performance may be achieved by left clicking on the compressor image to open a compressor selection dialog screen illustrated (see  FIG. 36 ). Compressor performance is added via the 10 term ARI Coefficients for capacity (Btu/hr), refrigerant mass flow rate (lb/hr), power input (Watt) along with other inputs and may be saved for future use. Compressor performance is selected by double clicking the part number. The user may also view the compressor performance in the tab Rated Performance shown in  FIG. 37 .  
         [0117]     Referring now to  FIGS. 38 and 39 , the tubing connecting the main system components may require several inputs which change automatically depending upon system type (i.e., air-conditioner ( FIG. 38 ) or heat pump ( FIG. 39 )) and its operation mode (i.e., heating or cooling). The inputs required may be grouped in two categories: (i) tubing geometry and (ii) equivalent tubing lengths of connecting tubing of the system. The tubing geometry (i.e., wall thickness) is entered automatically when the user selects the tube size (i.e., outside diameter) from the drop down list. This list is based on standard tubing sizes used in the air-conditioning industry.  
         [0118]     Referring now to  FIGS. 40 and 41 , the user may add an accumulator to the cooling system simulation. To add an accumulator, the user may select the Accumulator under the Options menu in the main screen. An Accumulator image appears in the main screen between the evaporator and the compressor. To remove the accumulator, the user may unselect the Accumulator under the Options menu.  
         [0119]     The user may input the accumulator configuration parameters including shell, J-tube and compressor. The shell parameters include internal height and internal diameter. The J-tube parameters include internal diameter, oil return hole lower diameter, oil return hole upper diameter and spacing between oil return holes. The compressor parameters include estimated free internal volume.  
         [0120]     The user may select an accumulator from an accumulator database, which automatically inputs the configuration parameters. By clicking on the Show Accumulator List button, the user may browse the database of available accumulators. The database is initially ordered by part number (P/N) field. The user may re-order the list by clicking the desired parameter on the top row (header row). An accumulator is selected from the list by double clicking on the desired accumulator P/N.  
         [0121]     Connecting tubing Heat Transfer and Shell Loss Factors may be accessed by choosing the Line Heat Transfer tab (see  FIG. 42 ). The user may enter connecting tubing heat transfer data based on an estimation procedure or using the Line Heat Transfer Calculator provided in the simulator (see  FIG. 43 ). Shell heat loss rate is defined as a fraction of the compressor power input in the system. The Line Heat-Transfer Calculator may be accessed by choosing the Calculator button located near the heat transfer input for Liquid, Suction and Discharge Line inputs. This calculator reads the user inputs in the relevant screens and provides a convenient method of estimating the line heat transfer. The Calculated value can be automatically entered in the Line Heat Transfer screen when the user selects the results obtained from the Calculator. The Calculator&#39;s procedure is based on an American Society of Heating and Refrigeration Engineers publication.  
         [0122]     Referring now to  FIG. 44 , the simulator may enable evaluation of the effect of pressure drop on system performance due to system accessories. This capability is provided to assess the effect on system performance due to accessories such as reversing valve and other pressure drop inducing devices used in the refrigeration cycle. This function may be accessed by selecting any of the restrictor images in the main screen. This opens the Device Pressure Drop dialog screen illustrated in  FIG. 44 . The user may enter pressure drop data for rated refrigerant flow rate for the selected device(s). The user may also enter description notes about each of the selected devices. This data is generally obtained from the manufacturer of the device.  
         [0123]     Referring now to  FIGS. 45 through 48 , the simulator further provides parametric analysis. This capability is included to enable a user to automatically run multiple simulations. The objective is to find the best system design configuration for its operating condition. This is achieved by selecting the parameter from the parameter list that includes a plurality of available variables for the user to choose from. The user may choose the starting and ending values of the parameter and the number of simulations steps.  FIG. 45  lists the parameters available to the user for performing the analysis. In the example shown in  FIG. 45 , Subcooling at the Condenser Exit is selected as the parameter. In this case, the starting Subcooling value is 5° F., the final value is 30° F. and the number of steps is 6. Upon completion of the runs, the simulator may produce a summary of inputs used, outputs, charts showing the results in a graphical format and a summary of key output variables in a spreadsheet format.  FIGS. 46 through 48  show exemplary output screens.  
         [0124]     Referring now to FIGS.  49  to  55 , the system design simulator enables the user to design a system including an air-cooled condensing unit (ACU). The user may include an ACU by clicking on Condensing Unit under the Options menu in the main screen. The cooling system graphic is altered to illustrate the ACU (i.e., combined compressor and condenser).  
         [0125]     With particular reference to  FIG. 50 , the user may select an available ACU from an ACU database. A search tool is provided so that the user can quickly search and view the details of the available ACU&#39;s that meet the design need. The ACU selection screen shows a variety of search criteria available for finding the proper ACU. The search criteria may be a single parameter or a combination of parameters. The search criteria may include refrigerant type, temperature range, frequency, phase, voltage, ranges of physical dimensions (i.e., length, width, height), nominal horsepower (Hp) or capacity.  
         [0126]     The search may be initiated by choosing the Search button. The result yields a list of ACU&#39;s matching the user specified criteria. An ACU is selected by double clicking the model. The Component Details tab may provide pertinent information about the selected ACU. The Compressor tab under Components Detail shows the compressor performance (capacity and power) (see  FIGS. 53 and 54 ). The Condenser tab illustrates condenser geometry and the Accumulator tab provides accumulator geometry (see  FIG. 55 ). Accumulator details may be provided only if the particular ACU is equipped with an accumulator. The Condenser tab may enable the user to enter inputs for the entering air condition. The user may view a reference drawing of the ACU illustrating the component layout. As illustrated in  FIG. 52 , the user may view the details of the selected ACU by clicking on the ACU tab (e.g. C3AH-0303-TAC-001).  
         [0127]     Referring now to  FIGS. 56 and 57 , the system design simulator may identify the key features of the selected ACU. The key features may include shut-off valves, receiver, accumulator, pressure controls and the like. The key features may not impact the ACU&#39;s thermal performance but may be provided to enhance the ACU&#39;s functionality. The user may view the ACU&#39;s key features by moving the mouse over the lower half of-the screen. The check mark shows the key items included in the feature list for the selected ACU. The key features available may vary with the ACU model line. However, the thermal performance of both units is same as long as the first nine characters of the model and the operating frequency of the units are same. As illustrated in  FIG. 57 , the user may compare key features of multiple ACU&#39;s.  
         [0128]     Referring now to  FIG. 58 , the ACU search results maybe displayed either in an explorer tree by selecting Explorer Tree in the Results In field or in a Spread Sheet format (see  FIG. 50 ) by selecting Spread Sheet. The user selected format preference for display may remain in-force until the user changes the display format. It should be noted, however, that the search criteria for both formats are identical. The ACU model, ACU line (C, F, etc), unit&#39;s electrical characteristics, and/or capacity (Hp) may be color coded to assist user navigation.  
         [0129]     Referring now to  FIGS. 59 through 62 , the system design simulator may provide the thermodynamic properties of refrigerants including saturated properties, superheated properties and liquid properties. The refrigerants may include, but are not limited to, R-12, R-22, R-502, R-134a, R-404A, R-507, R-410A and R-407C. The saturation pressure may be determined based on temperature by choosing the Saturated Tab and entering the temperature (see  FIG. 59 ). The corresponding saturation pressure may be given by clicking on the Calculate button. The saturation temperature may similarly be determined based on pressure.  
         [0130]     The superheated properties may be determined by clicking on the Superheated Properties tab and inputting pressure and temperature (see  FIG. 60 ). The properties including specific volume, enthalpy and entropy may be provided by clicking on the Calculate button. The enthalpy may be determined based on the pressure and entropy by clicking on the corresponding Calculate button (see  FIG. 61 ). The liquid properties may be determined by clicking on the Liquid Properties tab and inputting temperature (see  FIG. 62 ). The properties including density, specific volume, enthalpy and latent heat vapor may be provided by clicking on the Calculate button.  
         [0131]     Referring now to  FIGS. 63 through 66 , after having configured the cooling system, the design simulator may be run by choosing the Run option on the menu bar and clicking Run Model. The design simulator may also be run by clicking the Run icon on the toolbar. The results may be provided in tabular and graphical formats. More particularly, a summary table may be provided, listing the key system inputs and the parameters for the individual components (see  FIG. 63 ). Alternatively, a graphical illustration of the cooling system is shown with the corresponding parameters listed adjacent to images of the individual components (see  FIG. 64 ). The results may be printed by choosing the File menu, Print and Outputs options from the main screen or by clicking on the Print icon. Additionally, the results may be saved to an electronic file by choosing the File menu, Save option or by clicking on the Save icon.  
         [0132]     The overall system parameters include mode, system capacity, compressor power, evaporator fan power, condenser fan power, total power, system EER, sensible heat ratio, compressor model number, refrigerant and refrigerant charge. The condenser air flow parameters may include inlet air temperature, air flow rate and outlet air temperature. The condenser inlet refrigerant parameters may include pressure, temperature, saturation temperature and enthalpy. The condenser outlet refrigerant properties may include pressure temperature, saturation temperature and sub-cooling temperature. The flow control inlet refrigerant properties may include pressure, temperature, saturation temperature and sub-cooling temperature.  
         [0133]     The evaporator air flow properties may include inlet air temperature, air flow rate and outlet air temperature. The evaporator inlet refrigerant parameters may include pressure, temperature, enthalpy and refrigerant flow rate. The evaporator outlet refrigerant parameters may include pressure, temperature, saturation temperature, enthalpy and superheat temperature. The compressor suction refrigerant parameters may include pressure, temperature, saturation temperature, enthalpy and superheat temperature. The compressor discharge refrigerant properties may include pressure, temperature, saturation temperature and enthalpy.  
         [0134]      FIG. 65  provides evaporator and condenser coil outputs in tabular format. The outputs may include, but are not limited to, surface area of the fins, weight of the finned area, length of the tube, internal volume of the coil, weight of the tube, air-side pressure drop across the coil and heat rejection capacity.  FIG. 66  provides compressor performance information in tabular format including capacity and power at various condenser and evaporator temperatures.  
         [0135]     Referring now to  FIGS. 67 through 69 , the simulator may enable the user to determine a seasonal energy efficiency ratio (SEER) for a single capacity system operating in the cooling mode. The simulator may enable the user to enter the system data determined from their laboratory testing or from other procedures. Alternatively, the user may model the system performance and then use the system results to generate the SEER rating. The SEER calculation may be accessed by first selecting the system type as single capacity and choosing Cooling in the System Type and Mode Selection screen. The user may choose the Seasonal Energy Efficiency Ratio (SEER) selection from the Tools menu (see  FIG. 67 ). The SEER calculation may only be available for Air-Conditioners and Heat Pumps.  
         [0136]      FIG. 68  shows the inputs that may be required for the SEER calculation. Note that SEER calculation may require only the system performance for the 82° F. outdoor air condition (rating Condition B). Data for 95° F. outdoor air condition (rating condition A) is included as an example. As mentioned earlier, the user may enter their own data to calculate SEER. In such a case, the checkbox Tied To System Model&#39;s Output is unchecked. SEER computation may be performed by choosing the button Calculate SEER. The calculated SEER is shown in the lower left (e.g., 11.553). A report may be accessed by choosing the button Generate Reports (see  FIG. 69 ).  
         [0137]      FIGS. 70 and 71  show the SEER input screen and corresponding report for a dual capacity system. The procedure for computing SEER of a dual capacity system operating in the cooling mode may be similar to the single capacity SEER described above, however, the dual capacity SEER requires more inputs. The SEER capability may be accessed by selecting the system type as dual capacity and choosing Cooling in the System Type and Mode Selection screen. The user may choose the Seasonal Energy Efficiency Ratio (SEER) from the Tools menu.  FIG. 70  shows the user inputs required for the dual capacity SEER calculation. As is the case for the single capacity system, the user may enter their own data to calculate SEER. The dual capacity SEER report may be accessed by choosing the button Generate Reports (see  FIG. 71 ).  
         [0138]     Referring now to  FIGS. 72 through 76 , the simulator may enable the user to calculate a heating seasonal performance factor (HSPF) for both single and dual capacity systems. Similar to the procedure for the single capacity SEER calculation, the simulator may provide the user with a user friendly procedure for calculating the HSPF. The user may enter the data determined from their laboratory testing or from other procedures. Alternatively, the user may simulate the system performance and use the results to compute the HSPF rating automatically. This capability may be accessed by selecting the system type as single capacity and choosing Heating in the System Type and Mode Selection screen. The user may choose the Heating Seasonal Performance Factor (HSPF) selection from the Tools menu (see  FIG. 72 ). HSPF Calculation is available only for Heat Pump operating in the heating mode.  
         [0139]      FIG. 73  illustrates the inputs that may be required for the HSPF calculation. The HSPF calculation may require system performance data for several outdoor ambient air conditions (e.g., 47° F., 35° F. and 17° F.). Similar to SEER, the user may enter their own data to calculate HSPF. In such a case, the checkbox Tied To System Model&#39;s Output is unchecked. The HSPF computation may be performed by choosing the button Calculate HSPF and the result is provided in the lower left corner (e.g., 8.967). The user may view the Winter Heating Load Hours for various US locations.  FIG. 74  illustrates an exemplary HSPF report. The procedure for computing HSPF of a dual capacity System is similar to the single capacity HSPF described above, however, the dual capacity HSPF may require additional inputs (see  FIGS. 75 and 76 ).  
         [0140]     Referring now to  FIG. 77 , the cooling system design simulator may provide a psychrometric calculator to calculate moist air properties. The user may click on the Psychrometric Calculator option under Tools in the main menu. The inputs to the psychrometric calculator may include altitude above sea level (ft), dry bulb temperature (° F.) and one of a plurality of air property inputs. The plurality of air property inputs include wet bulb temperature (° F.), relative humidity (%), humidity ratio (grains/lb), specific volume (ft 3 /lb), enthalpy (Btu/lb) and dew point temperature (° F.). The psychrometric calculator may calculate the remaining air properties and may calculate further air properties including density (lbs/ft 3 ), vapor pressure (in Hg) and absolute humidity (grains/ft 3 ). The air properties may be automatically transferred  
         [0141]     Referring now to  FIG. 78 , the moist air properties may also be determined using a psychrometric chart provided by the cooling system design simulator. The user clicks on the Psychrometric Chart option under Tools in the main menu. The inputs include minimum dry bulb temperature (° F.) and maximum dry bulb temperature (° F.). The cooling system design simulator generates the psychrometric chart based on the inputs. On the left hand side of the chart, a column may provide values for dry bulb temperature (DB), wet bulb temperature (WB), relative humidity (RH), humidity ratio (W), specific volume (v), enthalpy. (eh), dew point temperature (DP), density (d), vapor pressure (vp), absolute humidity (AW), parts per million by weight (ppmW) and parts per million by volume (ppmV). More specifically, as the user drags the pointer across the chart, the air properties listed in the left hand column may change based on the coordinates of the pointer on the chart. Therefore, the user may select a desired chart coordinate by moving the pointer to that coordinate on the chart and reading the air property values from the left hand column. The user may zoom in by double-clicking on the chart.  
         [0142]     Referring now to  FIG. 79 , the cooling system design simulator may further provide manufacturer engineering bulletins that are periodically updated. The engineering bulletins may be selected by clicking the AE Bulletins option under Help in the main menu. The user may select from various contents including, but not limited to, compressors, motors, accessories, recommendations, installation and the like. A corresponding bulletin may be displayed on the left half of the screen by clicking on the desired topic. In this manner, the user may continuously be updated on engineering considerations when designing the cooling system. These bulletins may provide helpful information to assist engineers and installers in selection and installation of cooling system components.  
         [0143]     Referring now to  FIGS. 80 through 86 , the simulator may include a stand alone condenser model that models the performance of ACU&#39;s based on micro-channel coil technology. Micro-channel heat exchanger coil technology has become more common in the industry. Originally introduced in the automotive industry, the micro-channel coil is composed of three key elements: flat multi-void micro-channel tube, the fin stock sandwiched between alternating layers of micro channel tube and two manifolds. The slotted manifolds may seat each tube in a parallel flow orientation. A one-pass-oil may have gas entering through one manifold and liquid exiting out of the other.  
         [0144]     Micro-channel heat exchangers have proven to be extremely reliable. Furthermore, this coil design typically enables equivalent system performance in a smaller condensing unit chassis (i.e., twenty to twenty-five percent smaller coil sizes resulting in units with smaller foot prints). Another benefit is that air-conditioning systems with micro-channel heat exchangers may typically require twenty-five to forty-five percent less refrigerant charge per system than with units equipped with standard round tube/flat fin technology.  
         [0145]     The simulator&#39;s condenser model may model ACU performance but may not model a complete refrigeration cycle system using the heat exchangers (i.e., evaporator, condensers) based on heat exchanger technology. The condenser model may compute the condenser performance dynamically as the user configures the condenser geometry, entering air flow rate and inlet air condition and refrigerant selection.  
         [0146]     The user may define the condenser geometry with inputs for: (i) fin pattern (see  FIG. 80 ), (ii) tubing (see  FIG. 81 ) and (iii) header (see  FIG. 82 ). In all cases, the user may be provided with default inputs which can be changed by the user to meet their design needs. The fin inputs may include, but are not limited to, fin height, fin depth, fin thickness, fin density, number of fins, header to header distance, material and fin pattern (e.g., flat, louvered, wave) and corresponding fin pattern geometry inputs. The tubing inputs may include, but are not limited to, tube length, outside minor diameter, outside major diameter, tube thickness, number of internal legs, leg thickness, material, micro-channels port (e.g., rectangle, triangle, round) and condenser passes. The header tank inputs may include, but are not limited to, outside diameter, thickness, material and header shape (e.g., D, round).  
         [0147]     Condenser air flow rate, inlet air condition and refrigerant selection may be accessed through the Cooling Air/Refrigerant tab (see  FIG. 83 ). The cooling air inputs may include, but are not limited to, flow rate, dry bulb temperature, wet bulb temperature, pressure, test type and humidity. The refrigerant inputs may include, but are not limited to, condensing temperatures, de-superheating degrees, sub-cooling degrees and evaporator performance for multiple evaporators. The evaporator performance inputs may include, but are not limited to, evaporate temperature, super-heating, capacity, refrigerant in temperature and refrigerant flow rate.  
         [0148]     The condenser model dynamically computes the heat exchanger performance as the user changes the inputs. The performance may be displayed in the three tabs: (i) Outputs, (ii) Performance Maps and (iii) Charts. The Outputs tab may display the performance in spreadsheet format (see  FIG. 84 ). This tab may also enable the user to save the heat exchanger geometry and calculated performance. The Performance Maps tab may show the heat exchanger segmentation relative to the: (i) de-superheating, (ii) two-phase and (iii) sub-cooling functions (see  FIG. 85 ). The Charts tab may show the condenser performance in graphical format (see  FIG. 86 ). A plurality of parameters (e.g., fifteen) may be available for the user&#39;s design analysis work. Exemplary parameters may include, but are not limited to, refrigerant mass flow rate, capacity, capacity rate, inlet refrigerant temperature, condensing temperature and outlet refrigerant temperature.  
         [0149]     The cooling system design simulator may simulate the performance of the individual components of a user-defined cooling system and the cooling system as a whole. The design simulator may perform steady-state design and analysis of vapor compression air-to-air-systems operating in either heating and cooling modes. As a hardware-based model, a user may specify the individual component parameters and define the geometry of tubing connecting the system components. The design simulator may preferably be provided as a software-based computer program and include other complimentary functions. These may include, but are not limited to, look-up tables for refrigerant and psychrometric properties of air.  
         [0150]     The description is merely exemplary in nature and, thus, variations are intended to be within the scope of the teachings. Such variations are not to be regarded as a departure from the spirit and scope of the teachings.