Abstract:
Intelligent HVAC register is an HVAC register outlet which can control the temperature in a space by operating independently. The Intelligent HVAC register works in network with other vents within the system using low power wireless technology and a smart application so that the temperature of multiple individual spaces can be controlled while operating on a single HVAC system. Intelligent HVAC register uses a solar strip to charge the battery which runs each vent&#39;s hardware. This enables more efficient use of energy as airflow to unused spaces can be blocked therefore keeping air pressure and efficiency higher in the spaces where temperature adjustments are necessary. Intelligent HVAC register can be controlled using a learning application on a smart device. By setting the time &amp; temperature needed in each space the Intelligent HVAC smart vane will automatically open or close to keep the room at the desired temperature.

Description:
CROSS-REFERENCE TO RELATED APPLICATIONS 
       [0001]    Not Applicable 
       STATEMENT REGARDING FEDERALLY SPONSORED RESEARCH OR DEVELOPMENT 
       [0002]    Not Applicable 
       THE NAMES OF THE PARTIES TO A JOINT RESEARCH AGREEMENT 
       [0003]    Not Applicable 
       INCORPORATION-BY-REFERENCE OF MATERIAL SUBMITTED ON A COMPACT DISC 
       [0004]    Not Applicable 
       BACKGROUND 
       [0005]    The background of this invention derives from the fact that improved energy efficiency within the home has become a necessity due to soaring costs and environmental issues. Existing products seek to cut energy bills through home automated controls, however many solutions are ineffective due to pre-existing structures or designs already installed within the home, such as central HVAC systems where ducts are unable to be modified due to the high labor cost of retrofitting original residential structures. On average 54% of a home&#39;s electrical power consumption is expended on space heating and cooling. 
         [0006]    Intelligent HVAC smart register enables home owners to retrofit their current HVAC systems and automate their homes systems in a cost effective and simple way. By replacing existing registers with the Intelligent HVAC smart registers, the home owner can turn a passive HVAC system into a smart system where they can manage their homes heating and cooling characteristics. 
         [0007]    The majority of HVAC systems operate off a single thermostat and AC (air conditioner) unit, which means that a home&#39;s various rooms are tied to one air circuit regardless of whether a room is occupied or not. Intelligent HVAC smart register is able to manage each space individually, thus optimising the energy used, by directing air flow to where it is needed, whilst blocking it off where heating or cooling is not required. 
         [0008]    The Intelligent HVAC smart registers system is able to be controlled by a single smart device, thus software programs are able to be developed and online resources such as weather reports or GPS utilised to enable maximum heating and cooling system effectiveness. 
         [0009]    The ease of which the system can be installed and set up is due to its low power design, where a self contained unit does not require hard-wiring for a power supply. The energy efficient design consists of low power wireless technology working with hardware that is optimized by a power conserving mechanical design. This means the Intelligent HVAC smart register is able to operate for years without regular battery replacement or maintenance. 
       PRIOR ART 
       [0010]    The following prior art is representative of what is published in the field of Intelligent HVAC smart register devices: 
         [0011]    U.S. Pat. No. 8,249,731 to inventor Tran, discloses a system to control energy consumption in a building which has a plurality of rooms. However, the disclosure of inventor Tran lacks a low power wireless solution. These technologies will enable the Intelligent HVAC smart register to operate for an extended period (multiple years) using a single power cell. The support of an energy harvester such as a solar cell will guarantee the Intelligent HVAC smart register can stay in full operational service for extended periods. Furthermore inventor Tran, lacks a mechanical solution which will utilize the air pressure from within the ventilation system to open the vent, thus eliminating the need for additional power usage which would be required to drive a motor or servo to open and also close the vent, further enhancing the low power solution of Intelligent HVAC smart register. 
         [0012]    Patent Number US 201010163633 A1 to inventor Barrett, Lingemann discloses an automatically balancing register for HVAC systems. However, the disclosure of inventor Barrett, Lingemann lacks a software application (App) which can be loaded onto a pre-existing smart device such as a cell phone or tablet. This enables the device with digital intelligence thereby interacting with software and systems such as Global Positioning System (GPS) to identify when a user is returning home prompting operation. In addition weather reports and temperature monitoring will enable the Intelligent HVAC smart register system to operate intelligently and continuously learn from past behavior and preferences. 
       BRIEF SUMMARY OF THE INVENTION &amp; OBJECTIVES 
       [0013]    The first objective of the Intelligent HVAC smart register is to create a product capable of changing existing HVAC systems into smart HVAC systems which can manage heating and cooling of indoor spaces, thus saving users money on energy bills. 
         [0014]    To manage the hot and cold air flow within a traditional HVAC system, the Intelligent HVAC smart register is designed to block and open the outlets of the HVAC ducting at times when the temperature within a space is different to the temperature set within the Intelligent HVAC smart registers application. To achieve this objective while minimizing power consumption, the Intelligent HVAC smart registers mechanical design of the vanes use air pressure from within the HVAC duct to push open the registers veins when a release mechanism is triggered by a difference between the thermostats ambient temperature reading and desired ambient temperature set with in the Intelligent HVAC smart register application. 
         [0015]    To ensure adoption of Intelligent HVAC smart registers into homes, the Intelligent HVAC smart register needs to be easy to install and operate. 
         [0016]    To meet these objectives the Intelligent HVAC smart register must operate on an independent power source, requiring zero wiring. The independent power source should support the operation of the Intelligent HVAC smart register for extended periods of time utilizing the latest low power technologies to ensure long term operation. These include new low power wireless technologies as well as new low power sensor and servo technologies. 
         [0017]    To create a ‘smart’ register, an application is installed onto a smart device to manage the Intelligent HVAC smart register. Users can conveniently set-up Intelligent HVAC smart register in one initial step by entering the “zoning state” and walking throughout each room and hallway of the home with a smart handheld device. The Smart application sets up temperature requirements based on presence and time of day. Once the zone is defined, users can remotely monitor each room&#39;s temperature online, for instance to ensure a sleeping child or pet is being properly warmed or cooled. 
         [0018]    The Individual Intelligent HVAC smart registers automatically open or close relative to temperature, human presence, or set schedule. The ‘smart’ register learns the unique room requirements of each home and concentrates heating and cooling when and where energy is needed, thus reducing home energy costs and environmental impact. Each Intelligent HVAC smart register incorporates a thermal diode to estimate room temperature and communicates on a low energy network utilizing broad spectrum low power based wireless devices. To minimize electricity use, Intelligent HVAC smart register products include a solar strip, low power solenoids, and non-actuated registers that harness the air pressure from the HVAC fan to enable the register to open or close. 
         [0019]    Register based proximity sensors using pulse width modulation (PWM) of infra red (IR) are recorded by a smart phone, tablet, laptop or PC to build a data base of the users behavior within the home, including schedules and preferences so the Intelligent HVAC smart register can anticipate when and where to target your heating/cooling needs. 
         [0020]    When you are nearing your home, GPS location will trigger your Intelligent HVAC smart register application to prepare your home for your arrival. The Intelligent HVAC smart register application takes into account your user history, such as the rooms you usually occupy upon arrival and time you usually go to bed and heats and cools occupied spaces accordingly. Intelligent HVAC smart register can also track your energy consumption and build usage scenarios for you to meet your energy saving targets. 
     
    
     
       BRIEF DESCRIPTION OF THE SEVERAL VIEWS OF THE DRAWING(S) 
         [0021]      FIG. 1  Is a Top, and side view of the Intelligent HVAC (heating, Ventilation, Air conditioning) Smart register. 
           [0022]      FIG. 2  Is an 1st angle view of the Intelligent HVAC (heating, Ventilation, Air conditioning) Smart register 
           [0023]      FIG. 3  is a Oblique view of an example of a smart device used to control the Intelligent HVAC Smart register and a representation of the cloud service used to store the data. 
           [0024]      FIG. 4  is an oblique view of the AC heat pump and ducting and power control unit. 
           [0025]      FIG. 5  is a plan drawing of a residential HVAC ducting and scenario with multiple Intelligent HVAC smart registers installed. 
           [0026]      FIG. 6 . Is a front and oblique view of the AC power control unit. 
           [0027]      FIG. 7  is a flow chart showing the Intelligent HVAC Smart register hardware function process. 
           [0028]      FIG. 8  is a flow chart showing the Intelligent HVAC Smart register hardware logic process 
           [0029]      FIG. 9  is a flow chart showing the Intelligent HVAC Smart register software logic process 
       
    
    
     DETAILED DESCRIPTION OF THE INVENTION 
       [0030]    The following description should be read with reference to the drawings, whereby like elements in different drawings are numbered in like fashion. The drawings, which are not necessarily to scale, depict selected embodiments and are not intended to limit the scope of the Invention. 
       Intelligent HVAC Smart Register Introduction 
       [0031]      FIG. 1  Shows the Intelligent HVAC Smart register  21  in top and side views. This component enables the airflow to be controlled; this is done by using the hinged vane  8  to moderate air flow. This component can be opened or closed by utilizing the on I off cycle of the main AC unit or air pump  17 . This can also be performed by the Intelligent HVAC Smart register Power controller  15  which serves as a backup. This device is wirelessly connected to the various Intelligent HVAC Smart registers around the home by a wireless network  11 , meaning that various Intelligent HVAC smart register(s), around the home can relay the information and settings required to provide automated &amp; intelligent operation. The Intelligent HVAC smart register  21  can also be controlled remotely by a smart device  9 . This is done by installing the Intelligent HVAC smart register application  10  onto the smart device  9 . A smart device is one which has an operating system (OS) and has online network capability. This application  10  is used to set-up the system and user preferences as well as monitor and adjust the system on the go. User data and information are stored on the Intelligent HVAC Smart register cloud storage  12  via the wireless network  11 . 
       First Angle Overview of the Intelligent HVAC Smart Register 
       [0032]      FIG. 2  Shows the Intelligent HVAC smart register  21 , and the hinged vane  8 , which is opened by air pressure caused when the main AC unit  17  is delivering air flow. When there is no airflow the hinged vane  8  can be pulled close by the pressure spring  3 . And if the hinged vane  8  needs to remain closed while there is air pressure in the system (i.e. while other rooms need to be ventilated) a locking pin or latch  7  is activated to keep the vanes  8  closed. When the register needs to re-open the locking pin or latch  7  is disengaged. This action is put into effect when an open or close signal is sent from the Intelligent HVAC Smart register Power controller  15  via the wireless network  11 . This signal is received by the unit&#39;s antenna  2 , which then relays the information to the electronics module I sensors unit  1 . These components are all powered by a battery  6  charge generated by a solar cell power feed  5 . The solar cell collects its charge from the ambient room light. The Intelligent HVAC Smart register  21  can also be automatically opened if presence is detected in the room by the Near-Infrared Reflectance (NIR) presence detect module  4 . 
       Smart Device, Cloud Storage and Wireless Network Relationship 
       [0033]      FIG. 3  Intelligent HVAC smart register  21  system are controlled via a smart device  9 , this device should support an operating system and have wireless capability. An Intelligent HVAC Smart register application  10  is installed on the device and user preferences are input to activate the Intelligent HVAC Smart register. The device is linked via a wireless network  11 , which means that the system can be controlled remotely while communicating the Intelligent HVAC smart register cloud service  12   
       Smart Device, Cloud Storage and Wireless Network Relationship 
       [0034]      FIG. 4  The Intelligent HVAC Smart register Power controller  15  enables the main AC unit  17 , to be activated and controlled without having to modify the existing unit. The Intelligent HVAC Smart register Power controller  15  is controlled via the smart device  8  via the wireless network  11 . The status LED  13  is a simple indicator that indicates power and operating status of the system. The system master power switch is also on the Intelligent HVAC smart register power controller  15 . The Plug hole for AC unit power plug  14  is where the power plug  18  for the main AC  17  unit is plugged into. 
       Home Floor Plan with Intelligent HVAC Smart Register System Installed 
       [0035]      FIG. 5  is a floor plan of a home scenario with multiple Intelligent HVAC smart registers  21  functioning within the existing heating system. The air pump  17  placed near the structure of the home or building  23 . The main HVAC air ducting into each room can have an Intelligent HVAC Smart register placed on the ducting  22  outlets to turn that space into a smart register controlled space. 
       Power Controller Overview 
       [0036]      FIG. 6  shows the HVAC smart register power controller  15  where the main AC unit  17  plugs into the main power plug inlet  14 . Upon establishing power, indicator LED  13  will turn on to show the power status. Using the power generated from the wall, the power controller will be able to communicate with the smart application  10 , via the smart register storage cloud  12  using the wireless network  11 . The power controller  15  features a master on &amp; off switch  16 . 
       How to Use Intelligent HVAC Smart Register Diagram 
       [0037]      FIG. 7  shows that Intelligent HVAC smart register can be purchased online or in a store  30 . Once purchased a download code is provided to access the Intelligent HVAC smart register website to download and install  31  the Intelligent HVAC Smart register application  10 . Once the application is installed the user will be able to access a step by step guide on how to safely and effectively install  32  the Intelligent HVAC Smart register system in their home or office. Once the intelligent HVAC smart register  21 , and Intelligent HVAC Smart register power controller  15  have been installed correctly according to the Intelligent HVAC smart register user guide, the user can then begin to zone  33  and set the thermal characteristics of their locations  34  within their environment, walking around the area to be zoned holding the smart device and following the prompts of the Intelligent HVAC Smart register self-learning system application  36 . Once the process completes the settings are saved  35 . Once use begins the Intelligent HVAC Smart register application  10  will begin to document user behaviors such as daily schedules, preferences and energy targets so that the Intelligent HVAC Smart register application  10  can begin to anticipate and efficiently run the system. If average user habits change  37  over a set period the system will provide an  38  update request to the system preferences  39  via the 8 Smart devices. Confirmed changes will be saved in the system  35 . If the user ignores the request the usage settings will remain, if settings changes are immediately required the user may change manually  40  via the Intelligent HVAC Smart register application  10 . 
       Intelligent HVAC Smart Register Hardware Function Logic Diagram 
       [0038]      FIG. 8  Is a logic diagram which shows that when the system is activated it will be placed on standby  51  by the Intelligent HVAC Smart register Power controller  15 , the system will then provide power and turn the AC on  52  the AC unit by enabling power via the Intelligent HVAC Smart register Power controller  15 . The Intelligent HVAC Smart register application  10  will then access each individual zones status and requirements, thus deciding whether to Open  54  the vane. For both instances air pressure within the ventilation ducts should be neutralized so the AC unit should be turned off  60  I  55  For a period of  20  seconds  61   156 , thus giving the locking pin or latch  7 , time to engage  58  or disengage  62  depending on the required action. To open the vane  8 . The low power  7  locking pin or latch will disengage and the AC unit will turn on  63  and the air pressure will blow against the vanes  8  overpowering the pressure spring tension  3 , thus opening the register. Afterward the locking pin or latch  7  will re-engage  65  once the air pressure has blown the register open  64  thus holding the Register in the open position. If the Register is to close when the air pressure delay of  20  seconds takes place the Pressure Spring  3  closes the vane  57 , where upon the locking pin or latch  7  will lock the vane closed  59   
       Intelligent HVAC Smart Register Software Logic Diagram 
       [0039]      FIG. 9  Shows the software logic which takes effect after the Intelligent HVAC smart register application  10  is activated, turn on the power controller  71 , this will turn the AC unit on  72  and the Intelligent HVAC Smart register system will be set on standby mode  73 . The Intelligent HVAC smart register application  10  will run through its system checks 74175176177 in order to gauge if it is ready for operation, by checking if its individual registers have enough power in their batteries  6 , and weather the NIR presence module  4  is working. If there is a problem a prompt will be sent to the smart device  8  recommending next steps for resolution. If the system check is all clear Intelligent HVAC smart register will start operation  78 . 
         [0040]    The system will begin by checking the room temperature using sensor unit  1  in the electronics module. If the room is at the set temperature  79  the vanes  8  will remain closed, and revert back to the Check system status  74 . If the temperature is not at the set temperature and presence mode is on  81 , the Intelligent HVAC Smart register will wait for presence in the room to be detected  80  using the NIR presence detect module  4  before opening the relevant Registers  84 . Once open the Intelligent HVAC Smart register application will gauge the multiple variables such as date and time of operation  87 , set Idesired temperature  88 , and presence  89  to gauge whether the vane  8  needs to remain open or closed. 
         [0041]    Once the system is in operation it immediately becomes self learning, the Intelligent HVAC smart register application  10  will begin to tabulate inputs like Date &amp; Time  87 , Temperature vs. Time  87 / 88 , etc. to build a user database which can then be measured and benchmarked in order for the system to learn and improve the service of the Intelligent HVAC smart register application  10 . All data is saved to the Intelligent HVAC smart register cloud storage service  90  where the data is analyzed and averaged over a week  91  If changes in a users behavior are recorded  92  a request is sent to the user to request a change in settings to match their behavioral patterns  93  where by the user can either confirm or deny these updates  94  user settings will be updated accordingly  95   
         [0042]    Having thus described the embodiments of the present Invention, those of skill in the art will readily appreciate that other embodiments may be made and used which fall within the scope of the claims attached hereto.