BACOENG Bomba de circulación de agua caliente para sistema de calefacción central de 180 mm
Brand: BACOENG

Performance Data:
Inlet/Outlet Size: 1-1/2"
Rated Power(W): 93/ 67/ 46
Max Flow(L/min): 53/ 35/ 21
Max Head(FT): 20/ 16.5/ 10
Voltage/Frequency: 230V/ 50HZ
Installation length: 180mm
Materials:
- Pump housing: Cast Iron
- Impeller: Corrosion-resistant, Composite, PES
- Shaft: Ceramic
- Bearing: Carbon axial
Motor Feature:Single phase,Closed, externally ventilated
Heavy Duty Motor housing (Won't get overheat even continuous running)
Insulation class: F
Protection class: IP44
Application: Used in Suitable for city buildings, suburban villas, houses, water and pressurized with industrial equipment, air conditioning, boilers, hot water circulating warm and so on.

Advantages:
1. High temperature resistance, anti-fraying, high efficiency, high flow,leak-tightness, low consumption
2. Super silent, environmental protection, aesthetics, ease of installation.
3. Built-in high sensitive electronic sensors with three-speed control.

Specification:
1. Suitable for Medium: hot water and ethanol maximum ratio of 1:1
2. Performance: Liquid temperature range:-10~+110 Celsius,Maximum working pressure:10bar
3. Ambient Temperature: Not higher than 40 Celsius.
4. Mounting Position: Shaft horizontal mounting
5. Pump Settings: single-phase pipeline pump 3 files manually controlled single-phase motor is not overloaded casting pump length 180 mm.

Entrada / Salida: 1-1 / 2 ''; Voltaje / Frecuencia: 230 V / 50 HZ; Longitud de instalación: 180 mm
Potencia nominal (W): 93/67/46; Flujo (L / min): 53/35/21; Cabeza (FT): 20 / 16.5 / 10
Sensores electrónicos integrados de alta sensibilidad con control de tres velocidades.
Resistencia a altas temperaturas, anti-deshilachado, alta eficiencia, alto flujo, estanqueidad, bajo consumo
Super silencioso, protección del medio ambiente, estética, facilidad de instalación.