ICSA-23-080-02: Delta Electronics InfraSuite Device Master
Delta Electronics InfraSuite Device Master versions prior to 1.0.5 contain a vulnerability in which the Device-status service listens on port 10100/ UDP by default. The service accepts the unverified UDP packets and deserializes the content, which could allow an unauthenticated attacker to remotely execute arbitrary code. CVE-2023-1133 has been assigned to this vulnerability. A CVSS v3 base score of 9.8 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:H/I:H/A:H). Delta Electronics InfraSuite Device Master versions prior to 1.0.5 are affected by a deserialization vulnerability targeting the Device-gateway service, which could allow deserialization of requests prior to authentication, resulting in remote code execution. CVE-2023-1139 has been assigned to this vulnerability. A CVSS v3 base score of 8.8 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:L/UI:N/S:U/C:H/I:H/A:H). Delta Electronics InfraSuite Device Master versions prior to 1.0.5 are affected by a deserialization vulnerability targeting the Device-DataCollect service, which could allow deserialization of requests prior to authentication, resulting in remote code execution. CVE-2023-1145 has been assigned to this vulnerability. A CVSS v3 base score of 7.8 has been calculated; the CVSS vector string is (AV:L/AC:L/PR:L/UI:N/S:U/C:H/I:H/A:H). Delta Electronics InfraSuite Device Master versions prior to 1.0.5 contain an improper access control vulnerability, which could allow an attacker to retrieve Gateway configuration files to obtain plaintext credentials. CVE-2023-1138 has been assigned to this vulnerability. A CVSS v3 base score of 7.5 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:H/I:N/A:N). Delta Electronics InfraSuite Device Master versions prior to 1.0.5 contains an improper access control vulnerability in which an attacker can use the Device-Gateway service and bypass authorization, which could result in privilege escalation. CVE-2023-1144 has been assigned to this vulnerability. A CVSS v3 base score of 8.8 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:L/UI:N/S:U/C:H/I:H/A:H). Delta Electronics InfraSuite Device Master versions prior to 1.0.5 contain a vulnerability in which a low-level user could extract files and plaintext credentials of administrator users, resulting in privilege escalation. CVE-2023-1137 has been assigned to this vulnerability. A CVSS v3 base score of 6.5 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:L/UI:N/S:U/C:H/I:N/A:N). In Delta Electronics InfraSuite Device Master versions prior to 1.0.5, an attacker could use Lua scripts, which could allow an attacker to remotely execute arbitrary code. CVE-2023-1143 has been assigned to this vulnerability. A CVSS v3 base score of 8.8 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:L/UI:N/S:U/C:H/I:H/A:H). Delta Electronics InfraSuite Device Master versions prior to 1.0.5 are affected by a path traversal vulnerability, which could allow an attacker to read local files, disclose plaintext credentials, and escalate privileges. CVE-2023-1134 has been assigned to this vulnerability. A CVSS v3 base score of 7.1 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:L/UI:N/S:U/C:N/I:L/A:H). In Delta Electronics InfraSuite Device Master versions prior to 1.0.5, an attacker could use URL decoding to retrieve system files, credentials, and bypass authentication resulting in privilege escalation. CVE-2023-1142 has been assigned to this vulnerability. A CVSS v3 base score of 7.5 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:H/I:N/A:N). In Delta Electronics InfraSuite Device Master versions prior to 1.0.5, an unauthenticated attacker could generate a valid token, which would lead to authentication bypass. CVE-2023-1136 has been assigned to this vulnerability. A CVSS v3 base score of 9.8 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:H/I:H/A:H). Delta Electronics InfraSuite Device Master versions prior to 1.0.5 contain a command injection vulnerability that could allow an attacker to inject arbitrary commands, which could result in remote code execution. CVE-2023-1141 has been assigned to this vulnerability. A CVSS v3 base score of 8.8 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:L/UI:N/S:U/C:H/I:H/A:H). In Delta Electronics InfraSuite Device Master versions prior to 1.0.5, an attacker could set incorrect directory permissions, which could result in local privilege escalation. CVE-2023-1135 has been assigned to this vulnerability. A CVSS v3 base score of 7.8 has been calculated; the CVSS vector string is (AV:L/AC:L/PR:L/UI:N/S:U/C:H/I:H/A:H). Delta Electronics InfraSuite Device Master versions prior to 1.0.5 contain a vulnerability that could allow an attacker to achieve unauthenticated remote code execution in the context of an administrator. CVE-2023-1140 has been assigned to this vulnerability. A CVSS v3 base score of 9.8 has been calculated; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:H/I:H/A:H).
CVSS v3.0: 9.8