MAINS SIGNALLING SYSTEMS

Abstract: A remote electricity metering system is known in which a central station (LC) communicates with meters (U1-U13) over the mains (10-14), with messages to remote meters being relayed by intermediate meters and the route of a message being determined by the central station. The present central station includes routing means which comprise, for each meter: a single route table (45-1) which contains a plurality of possible routes (46-1, etc) to the meter; route selector means (47) for selecting among those routes; and means (48, 49), operative if none of the routes in the table enable the meter to be reached, for generating a fresh route and inserting it in the table by displacing a single route from the table. A figure of merit may be stored (at 51) for each route, dependent on the quality of that route or simply on its length. Counters count (48) the number of successive failures of a route and (49) the number of successive failures of successive routes. Routes may be selected in dependence on the time and/or conditions in the mains system.

Description: JVI» iim Si s 1 "*-*-*-* 1 Hi »"»-___■ Sys-h-ei The present invention relates primarily to mains signalling systems, though it is also applicable to other systems having similar characteristics ( .The term mains ' applies primarily to the final consumer voltage portions of an electricity supply network, though the sigrialling can also extend over the higher voltage distribution parts of the network.) Such signalling is termed rndin*-*, mainsborne, or power line carrier (PLC) signalling. Remote metering A major application of mains signalling is remote meter reading, operated by electricity generating and distribution companies .electricity utilities . The term 'remote meter reading ' refers to what is normally the major function of such systems, but they may also be concerned more generally with load and system control. Also, while they will usually be concerned primarily with electricity meters, gas and other meters can in principle be coupled to the mains for this purpose (.preferably through electricity meters). A typical simple remote meter reading system will have a central station or local controller ( .which can co eniently be located at a distribution transformer) which communicates over the mams with the meters (.meter stations) of the various premises (largely housenold or domestic and small commercial) on the mains Such systems have twυ major problems: noise and attenuation. Mains noise arises from loads being switched on and off and the inherent characteristics of certain types ot loads. The noise problem can generally be overcome by a variety of known techniques, such as error detection and correc¬ tion techniques, requiring acknowledgement of reception, jnd repetition of lost messages. (.Some of these techniques also deal with problems of message col¬ lision.) Dissipation r attenuation at the preferred signal frequencies is significant; it is dependent on the particular operating conditions of the mains network and vanes according for example to the loading of the network. The attenuation will often be irregular; there may for example be potential "dead spots", due eg to signal reflections, close to the signal source wnile communication to more distant locations is still reasonably reliable. A system which largely overcomes these problems has been proposed in our earlier patent a plication no. PCT/GB94/01391 , WO 95/01030. Ii. that system, which we will for convenience call the standard system , substantially all meters nave a repeater function The p>resent system is a broadly a development of or improvement on that system. The topology of the standard system will normally be branched. That is, the central station will normally be able to communicate directly with several meters, each of those will normally be able to communicate with several further meters, and so on. (The topology of the communication system is somewhat abstract, and must be distinguisned from the physical or network topology of the mains network which supports the communication system. We will normally be concerned with the former, and will use the term "topology' alone for the for¬ mer.) A major feature of the standard system is that the message routing — le the determination of the routes which messages take through the network — is determined substantially entirely by the central station. This is the only station with any significant knowledge of the topology of the system, and is also the only station which can initiate a message. The central station includes, i each message, a route in the form of α meter list — a list of the meters through which the message is to pass. To read a meter (or otherwise communicate with it), the central station sends out a message to the eter, which inserts its reading into the message and sends it back to the centre! station. For present purposes, the route the meter list — can be taken as remaining unchanged in the message throughout the message s journey to the destination meter and back again to the central station. (In fact, the standard system preferably uses slight variations on this.) Topology monitoring and use The standard system can readily be made adaptive to changes of topology. This is particularly important for mains meter reading. The transmission char¬ acteristics of the mains network are liable to change (over time periods of the order of minutes to hours). Also, there will be occasional changes in the num¬ ber and locations of the meters of the system, and the mains network itself may be extended or modified over time. All these types of changes will change the topology of the system. The operations of the standard system can be broadly divided into two classes. First, there is topology determination; that is, sending SEARCH mes¬ sages designed primarily to discover or monitor the topology of the system — discovering which units can communicate with which and the appearance or disap¬ pearance of meters (The topology determination mode may be split into two sub-modes, initializing and maintenance.) Second, there is direct messaging; that is, the sending of messages to particular meters with the primary purpose being to transfer specific information between the central station and that meter (The main use of direct messaging will be to read the meter, but it may also be used for other purposes, eg to change a tariff at that meter) Direct messaging requires knowledge of the topology To determine the topology, the central station can send out search messages which request identification from meters receiving them. (Various details of this are described in the standard system.) The central station can therefore gradually construct a map of the system. The topology of the system can then be continuously maintained as a background process, so that changes in it (.eg meters gaining or losing communication with each other or appearing or disap¬ pearing) can be tracked. In the standard system, the map is typically storeo in the local controller in the form of a topology table, which is essentially a list of all directly communica¬ ting pairs of units. When the local controller wants to send out a message to a meter, it uses the topology table to determine a path to that meter, eg by starting with the entry for that unit and backtracking up the table until an entry for the local controller is reached. It may happen that the local controller finds difficulty in communicating with a meter; it may get no response after several re-sends, or it may have to re-send for most messages to that meter. In that case, it uses the topology table to try to find an alternative route to the meter. Route optimization It is desirable for the route to be optimal, mainly to maximize the chances of message reaching its destination .and returning therefrom), but also to mini- mice message density in the system. This requires an algorithm for determining an optimal route based on the hop qualities, and some form of hop quality evalu¬ ati n. There is a well-known algorithm for determining the shortest route through a network where the lengths of the connections between the nodes are given. To apply this algorithm, a suitable measure of hop or path "length or cost must be used. It is convenient to take this as inversely related to the hop quality. Hop quality άii be determined by various techniques. The receiving unit can measure the signal strength, or a noise signal can be deliberately added to the mains system to discover which hops fail as a result. The proportion of attempted transmissions over the hop which are successful can be determined. Each unit can record all messages which it receives (including those which are directed to other units' and, when it receives a message for itselt, report the results to the local controller as part of the return message. Test messages can be sent repeatedly and the number received monitored (a technique not described in the standard system). All these tecn tques have significant disadvantages. Signal strength measurement requires substantial elaboration of the receiving circuitry in every unit Using noise signals requires noise signal generators and reliable tech¬ niques for controlling them. Measuring the proportion of attempted transmis¬ sions over a hop which are successful yields information only about those hops which are actually being used, and is also slow. If all units are required to record all messages which they receive, this requires every unit to maintain α list of all units from which it receives messages together with rounts of the numoers of those messages, and considerably increases the amount ot information which has to be included in messages. Sending repeated test messages greatly increases the number of messages being sent, and so reduces the capacity of the system. These various techniques for measuring hop quality thus all have signifi¬ cant disadvantages. We have also realized that the information which they yield is inherently unreliable, as it is generally obtained from statistically small samples, and, as the hop qualities change unpredictably with time, tne information will normally be out of date to an appreciable extent. In addition, frequent recalculation of the optimum routes trom the hop qualities may impose an undue computational load on the local controller A further technique for determining routes through the network is des¬ cribed in Schlumberger, EP 0 395 495 A. in that system, a set of maps are gen¬ erated for different times, typically for 2 or 3 periods a day for some 2 months, by analysis of network conditions for cyclic repetitions, and are then selected at the appropriate times thereafter. Each map consists of a list or set of paths for all the meters in the network, so describing the network. Each map is simi¬ larly subdivided into a set of stacks' each of which is dedicated to a unique time slice for which the conditions of the network are constant Each stack contains lists of different possible paths for each meter, together with data characterizing the time period and/or network conditions when the map was made When a message is to be sent to a particular meter, the appropriate map is selected, a suitable stack is selected from that map, and the top path from the path list for that meter is chosen. If the message does not reach the meter and return from it (after a suitable number of retries at suitable intervals), that path is discarded from the top of the path list, the remaining paths in the path list are moved up, and the new top path is chosen. If no path in the path list suc¬ ceeds in reaching the meter, a global topology determination is made, to investi¬ gate the topology of the network. Assuming that the meter is still present and reachable, this will result in a path to it being found, and this path will be entered in the path list tor that meter The global topology determination uses special search-type messages to determine the topology ot the entire network in detail. From this information, a variety of paths to all accessible meters can be generated. This allows any meter for which the path list is not full to have new paths added to its path list. Most of the path lists will therefore be kept reasonably full. The size of the path lists is kept small, not greater than 3 paths This is because all the paths in a path list have to be tried before a global topology determination is made, and trying several paths (with retries) takes a very consi¬ derable time. Since all the paths in a path list are determined under substan- - - tially similar network conditions, there is a good chance that if one path fails (due, eg, to an unexpected change in network conditions), the other paths in the path list will also fail So it may be worth trying 1 or 2 alternative paths, but not more, before performing a global network topology determination. The present invention The general object of tne present invention is to provide an improved routing technique for the standard system. Accordingly the present invention provides, in a standard system or the like, routing means comprising, for each meter. a single route table which contains a plurality of possible routes to the rneter; means for selecting among those routes; and means operative if none of the routes therein enable the meter to be reached for generating a fresh route and inserting it in the table by displacing a single route from the table. The routes are initially generated from a knowledge of the topology, eg as determined by means of SEARCH messages. These routes are routes which are . nown to work, in the sense that for at least some of the time they enable com¬ munication with the meter to be achieved with reasonable reliability. However, the routes used are not necessarily optimum. Better routes may be possible; but provided that the routes which are in the route tables work, i the sense just given, those routes will be used even though they may not be optimal The pre¬ sent system thus operates on the basis of practical criteria; routes which are found to work are maintained for future use. The route to a meter may be picked at random from the route table for that meter However, it may be desirable to generate merit figures for the various routes in each route table and to try the routes in order of merit Once a route is found to work, however, that route will generally continue to be used until it ceases to work; only then are other routes in the table tried If none of the stored routes to a meter are found to work — that is, if communication with a meter is found to be impossible through any of the stored routes for that rneter — then the meter is regarded as lost. In that situation, the topology of the system needs to be investigated more thoroughly. If the topology is maintained in the form of a list of pairs of stations which can communicate directly with each other, then it may be possible to determine a new route from that information Alternatively, SEARCH messages can be used to re¬ map the system and to attempt to tind the lost meter. It is worth noting that the routes are preferably stored as complete routes between the local controller end the desired meter. Obviously, it would be possible to split a route to α remote meter into two parts, a first part between the local controller and some intermediate meter and a second part between that intermediate meter and the remote eter However, it would be dangerous to store, for the remote rneter, only the second part of the route and try to com¬ plete the route Ly concatenating that with a route to the intermediate eter Since the topology of the system changes from time to time, some of the routes to the 'intermediate meter may in fact pass through the "remote" meter, so such concatenation could produce circularity. Although additional mechanisms could be introduced to avoid that, they would make the system considerably more compli¬ cated As discussed above, each message includes a eter list which defines its route through the system In the basic form of the standard system, this meter list is maintained unchanged throughout the life of the message. It is pointed out in the description of the standard system that addresses can be deleted from the meter list on the return journey of the message from the meter back to the local controller. This can of course be done in the present system. A further variant is also described in the standard system, where addresses are deleted one by one from the meter list in the message on its outbound .out¬ ward) journey and copied into the meters through which the message passes. On the return journey of the message, each meter though which it passes uses the retained address to torward the message to the next eter on its return journey to the local controller. If, in the present system, the local controller may send out a message before the previous message has returned to it (or sufficient time has elapsed for it to be certain that the previous message has been lost), the use of this last variant may cause a minor difficulty. The reason is similar to the reason why the stored routes are preferably complete routes between the local controller and the d esired meter. If a message to one meter is sent out and then α message to another meter is sent out before the first message has returned, the second message may change the return route tor the first. However, although in this situation the return route may be unnecessarily lengthened, it is unlikely (except in very exceptional circumstances) to become circular. (In the standard system, this problem is negligible, because all routes are optimized in that system.) Specific Embodiment A communication system embodying the invention will now be described, by way of example, *ιth reference to the drawings, in which: Fig. 1 shows a mains power distribution network and metering system; Fig. 2 shows the topology of the Fig. 1 system; Fig 3 is a block diagram of the central station of the Fig. 1 system; and Fig. 4 is a more detailed block diagram of parts of Fig. 3. Mains network and system topology Fig. 1 shows a mains network powered from a substation 10. The network comprises a main branch 11 connected to the substation 10 via a line 12, a second branch 13, and a loop branch 14. A central station (local controller) LC _s connected to the network adjacent to the substation 10, and various user con¬ sumption meters Ul-Ull are connected throughout the network as shown. All the meters can also act as relay units. In practice, the mains network will typically extend over an area of the order of 1 km in diameter, and the number of meters will typically be in the region of 100 to 1000. Fig. 2 shows a typical topology for this network. The locai controller LC ran communicate with meters U1-U3; meter Ul can communicate onwards with meters U4 and U5; and so on. This tree corresponds roughly with the physical closeness of the meters in the physical network of Fig. 1, but the correspondence will in general not be exact. In practice, the maximum path length, le the maximum number of hops required for the local controller to reach ά eter, will typically be 3 or 4. In some systems, however, the number of hops required to reach the most remote rneter may be considerably greater than that. Message format and transmission To read the contents of a eter or to control it, the local controller sends a message to the meter, and the meter returns the message suitably modified. The message return occurs for all messages, acting as an acknowledgement so that the local controller knows that the message has been received. (If no message return occurs, the local controller does not know whether the message was lost on the outward or return journeys, and automatically re-sends the message.) The message format comprises three ain fields: a command field, a route field, and a data field. The route field defines the path which the message is to take through the system from the local controller to the rneter and back again, and comprises a control subfield and a meter list a sequence of meter addresses defining that path. The control subfield includes a direction indicator (eg O for outbound (outward) and I for inbound (inward, return)), a meter list length, and a marker which is effectively moved along the meter list as the message moves through the system to indicate the next eter which is to receive it as the message passes through the system. Thus for a message being sent to meter IJ7, for example, the data path field will initially consist of a control subfield 0-3-2 and a meter list LC-U3-U7. In the control subfield, the first cnaracter, , indicates that the message is an out¬ ward one, the second is the label sequence length, and the third is the pointer The following table summarizes the progress of the message: 1 : LC -U3 U7 2: LC U3 -U7 3: LC U3- U7 4: LC- U3 U7 This shows the four stages in the outward and return journeys of the message, with an arrow instead of the control subfield to indicate both the active address and the direction ot travel. At each stage, the message will normally be received by several stations, but only the station which matches the active add¬ ress accepts and (except for the local controller) retransmits it. Fig. 3 is a block diagram of the local controller LC. A modem 21' couples the mains line 12 to a message assembly and disassembly unit 22'. This has sections for the different fields of the message format: a command section 2 A' for the command field, a control subsection 22B' for the control subfield, a route subsection 22C for the rneter list subfield, and a data section 2ΞD' for the data field. The local controller is controlled by a (main) control unit 35. The data section 22D of the message unit 22 is coupled to a data memory 23' which is coupled to and controlled by the control unit 35. The control unit 35 is also coupled directly to the message unit 22', and specifically to the route subsection 2C The control unit is also coupled to a topology control unit 40, which is in turn coupled to a topology list memory 36. (In the standard system, the topology memory 36 is shown as being coupled directly to the control unit 35, but for present purposes it is more convenient to regard it as coupled to the topology control unit 40 as shown here In effect, we have here simply sepa¬ rated out the topology control functions of the control unit 35 and labelled them as the topology control unit 40.) In the standard system, the local controller generates various search mes¬ sages, under the control of the topology control unit 40, to discover the topo¬ logy of the system, in the form of a list of pairs of units which can communicate with each other with reasonable reliability. This list is stored in the topology memory 36. The topology control unit 40 also causes this list to be maintained and updated as a background process. In operation, the main control unit 35 generates messages to be sent out to the various meters and processes the messages on their return To generate a message, all the various sections and subsections of the message unit 22' have to be filled, including in particular the route subsection 22C In the standard system, the eter lists for routing control are generated from the list in the topology memory 36. (In the standard system, the control unit 28 is described as performing this task, but it is more convenient to regard this task as being performed by the topology control unit 40.) The meter list may be generated by a simple sequential look-up from the topology memory entries, or by a more ela¬ borate process such as the routing algorithm mentioned above. The present system in the present system, there is a set of route tables stored in a route tables memory 45, and the main control unit 35 obtains the desired routes from this memory. This memory contains a separate route table for each eter Ul, U2, U3, etc. Each route table consists of a list of possible routes by which the local controller can probably reach the eter. Fig. 4 shows the route table 45-1 for meter U9. As shown, this table consists of a set of route storage locations 46-1, 46-2, etc each of which contains a possible route tor reaching meter U9. The routes in α route table are routes which have been found in practice to be effective for reaching the meter These routes may be generated in any of the ways described in the standard system from the basic topolcgy list 36 and any other available information such as hop quality information. When the local controller wants to communicate with a meter, the control unit 35 selects the route table for that meter. A route selector 47 .Fig. 4) then selects a route for that meter le it selects a location in that route table. In principle, the route selector can select a route at random from the route table, but it is preferable for the route selection to be" made according to some form of algorithm, as discussed below. The route selector 47 maintains a pointer to the selected location (ie the selected route), so that the same route is selected for future communications with that meter There is a separate pointer for each rneter, ie for each route table The pointer can be regarded as being stored in a pointer location in the table, as indicated at 46-0 There is also a failure counter 48 which counts the number of attempts which have to be made to communicate with the meter before the local controller successfully receives a message back from the eter. In principle, there can be a single failure counter for all meters. However, it may be desirable for the local controller to try to communicate with a second meter while still awaiting the return of a message from the first. In this case, it is necessary to maintain separate failure counters for the different meters, and each failure count can then be regarded as being stored in a failure count location in the appropriate route table along with the pointers If a message is not received back within a suitable time, it is regarded as being lost. The count in the failure counter is incremented by 1, and the message is re-sent. If the count in the failure counter becomes too large, then the route is regarded as no longer valid. The route selector 47 thereupon sel¬ ects another route from the route table. Associated with the failure counter 48 there is a route failure counter 49. This counts the number of routes which are found to be invalid. If all routes in the route table are found to be invalid, ie all routes in the table have been tried, each for the appropriate number of times, and communication with the meter has still failed to be achieved, then the rneter is regarded as lost Obvi¬ ously, both counters 48 and 49 are reset as soon as a message is received back from the meter. If the meter is lost, this is signalled to the topology contrc! unit 40, for that unit to attempt to generate a new route to the meter or to initiate a search for the eter by means of SEARCH messages. Once a new route has been genei — ated, it is added to the route table 45 for that eter (displacing an existing route if the table is full), and used by the control unit 35 to attempt to commu¬ nicate with the meter. The routes in the route table 45 can be arranged in arbitrary order (eg the order in which they are generated). The route selector 47 can then select them in cyclic order, or sequentially starting from the top of the list each time a route which has been successful becomes invalid. However, it is obviously desirable to minimize the number of attempts needed to establish communication with a meter, and it is also generally desirable to minimize the number of hops per message. A better technique for selecting routes from the route table is therefore desirable This involves arranging the routes in an order of merit 'This can be thought of as involving a re-ordering of the routes in the route table, but in practice it can be achieved by a suitable pointer chaining mecha¬ With the routes arranged in an order of merit, the route selector 4 7 preferably selects them sequentially, starting from the top of the list each time a route which has been successful becomes invalid. The chosen route is then the best route at the time when it is chosen. However, as time goes on so the system conditions may change, and some better route may become available even though the current route remains successful. It may therefore also be desirable for the route selector to try routes of lower merit occasionally even though the current route remains valid This can be triggered by a timer or a message counter For the routes to be arranged in order of merit, each route in the list must have a merit figure A simple form of merit figure is to take the number of hops which a route involves, the fewer hops, the better the merit figure The choice between routes with the same number of hops can be arbitrary, depen¬ ding eg on which order they happened to be generated in This is simple and effective, though for distant meters, routes with few hops will be preferred even though those hops may be long and therefore somewhat less reliable than the hops of some routes with more hops Alternatively, the locations in the memory 45 may have extensions 51 for storing explicit merit figures It is desirable for the algorithm for maintaining the merit figures to be simple A convenient algorithm is for a success counter 50 to count the number of successful communications with the meter using the currently selected route When the route finally becomes invalid (as indicated by the count in the failure counter 48 reaching its limit), the merit figure for that route is read out from the appropriate location 51 in the table 45, divided by a constant k in a divider 52, added to the success count from counter 50 in an adder 53, and returned to the merit figure location 51 for that route. The success counter is also reset, to start counting successes for the next route se'ected by the route selector 47 There is a separate success counter for each meter, ie for each route table, the success count can be regarded as being stored in a success count location in the table, along with the pointers The constant ,-λ is chosen to be slightly smaller than 1, and can conveniently be of the form (1 - -n , eg 7/8, the division can then be performed by a shift and subtract operation The effect ot this algorithm is to form a kind of run¬ ning average of the success counts for the times when the route has been selec¬ ted, with the success counts for recent selections of the route having greater weights than for old selections The resulting merit figure follows recent suc¬ cess counts, but is not excessively disturbed if, for example, an isolated noise burst makes a normally successful route temporarily invalid. To avoid the merit figure becoming excessively large, an upper limit is set for it. If a route often requi res several attempts, it will usually not be that long before the number of attempts exceeds the limit and becomes invalid. The mer it figure for each route thus effectively takes account of the number of attempts wnic h fai l for that route (without exceeding the limit set by the fai l ure counter 48). If desi red, the meri t fi gure for each route may be adjusted i n accordance with the length of the route. However, this also i ncreases the complexity of the system. It wil l also be realized that since no hop is li kely to be completely reliable, the merit figu re wil l automatically be smaller for unnecessarily long routes. Other more elaborate techni ques can also be used. For example, the system conditions may vary i n a roughly regular manner over the course of a day or a week, so that certain routes may be satιsfactory r at certain times. The route selector can then be arranged to select routes in a sequence dependent on the time of day. However, all such elaborations increase the complexity of t he system.

Claims: Claim: 1 A remote metering system comprising a mains supply system ( .10-14) having a control unit (LC) and a plurality of consumer eter units fUl-UM) with messages passing between the eter units and the control unit, the control unit including routing means (35, 36) for determining routes to distant meters via intermediate meters, characterized in that the routing means comprises, for each meter a single route table (45-1) which contains α plurality of possible routes (46-1, etc) to the meter, route selector means (47) for selecting among those routes; and means (48, 49) operative if none of the routes therein enable the rneter to be reached for generating a fresh route and inserting it in the table by displacing a single route from the table 2 A remote metering system according to claim 1, characterized . π that the routing means includes locations (51) for storing, for each route, α figure of merit for that route 3 A remote metering system according to claim 2, characterized hy means ( O 52, 53) for adjusting the figure of merit for a route in dependence on the quality of that route. 4 A remote metering system according to claim 2, characterized m that the length of a route is taken as its figure of merit. A remote metering system according to claim 1, characterized m that the route selector selects routes in cyclic sequence. t> A remote metering system according to any previous claim, characterized by a failure counter (48) which counts the number of successive failures of a route 7 A remote metering system according to claim 5, characterized by a route failure counter (49) which counts the number of successive failures of successive routes. 3 A remote metering system according to claim 1, characterized m that the route selector selects routes in dependence on the time and/or conditions in the mains system. _• A remote metering system including route selection means substantially as herein described with reference to the drawings. ιu Any novel and inventive reature or combination of features specifically disclosed herein within the meaning of Article 4H of the International Convention 'Paris Convention).

Inventors: ALLISON ROBERT JOSEPH, SCHOLEFIELD DAVID ROGER, ALLISON, ROBERT, JOSEPH, SCHOLEFIELD, DAVID, ROGER
Applicants: ALLISON ROBERT JOSEPH, REMOTE METERING SYSTEMS LTD, SCHOLEFIELD DAVID ROGER, ALLISON, ROBERT, JOSEPH, REMOTE METERING SYSTEMS LTD., SCHOLEFIELD, DAVID, ROGER
Application year: 1995
Main classification: H02J13
IPC codes: G01R11, G08C19, H02J13, H04Q9