text: HZDP - 50K Ultra-tsawg zaus Voltage siab Generator hauv Suav teb - HZDP - 50 K Ultra-tsawg zaus Voltage siab Generator Manufacturers - Huazheng fais Manufacturing Co., Ltd (Baoding)
  III. khoom Introduction...4
  Soj cov List...15
  Ceeb toom: nyob rau cable voltage mas mus kuaj, yuav tsum yog cov tub ntxhais hlau thiab insulating txheej ntawm lub cev sib cais, tsis nrog rau lwm yam khoom rau hauv cov saum no, txwv tsis pub nws yuav ua tau rau
  1、0.1 Hz-50KV Ultra-tsawg zaus Voltage siab Generator
  Lub cev Boost: 50㎏
  15.75KVCables、Generator
  ★Data uas tam sim no thiab voltage no tau ncaj qha mus txog tus qauv ntawm sab tshuab muaj muaj zog thiab yog muaj tseeb thiab yog.
  ★over-voltage kev tiv thaiv: ntsuas yuav sib txuas rau kev tiv thaiv tsis pub dhau 20 ms thaum cov zis voltage yog qib limiting qhov tseem ceeb ntawm chaw.
  ★over-tam sim no kev tiv thaiv: tsim dual tiv thaiv ntawm high tsis voltage, downtime kev tiv thaiv yuav tsum yog teev hauv tshuab muaj muaj zog ces. Kaw mus tiv thaiv lub sij hawm no tsis pub dhau 20 ms thaum cov chaw uas muaj-voltage sab coob tshaj li tus nqi tam sim no reacted.
  ★High-voltage zis tiv thaiv resistor tsim nyob rau hauv lub cev boost thiab nws yuav tsis muaj mus ntxiv sab nraum resistor.
  ★Closed-voj negative tawm tswv yim tswj Circuit Court uas muaj thiab muaj voltage.
  Qhov tshuaj ntsuam zaus
  Qhov tshuaj ntsuam voltage
  Sijhawm txwv voltage
  Tam sim no tsuas pub sijhawm
  Qhov kuaj lub sij hawm
  Pib kuaj voltage
  Koj yuav teev cov xeem zaus, voltage tos thiab tiv thaiv qhov tseem ceeb ntawm tshaj siab hauv ob ntshav siab los qis, tiv thaiv qhov tseem ceeb ntawm tshaj voltage, kuaj times thiab lwm yam raws li ntawd yuav tsum tau nyob hauv lub interface txwv ntawm rooj 4
  ★Three xaiv rau zaus: 0.1、0.05、0.02. Nws yog tus ntsuas tso zis ntau zaus thiab chav tsev yog Hz
  ★The kuaj voltage no yog los ntawm 10KV nyob rau qhov tseem ceeb (thov tsis teev kuaj voltage hauv qab no 10KV). Ntsuas yuav tsis boost lawm thaum nws muaj nyob rau qhov tseem ceeb teev thiab koom tes amplitude sine yoj nyob hauv tus nqi no peaking tso zis.
  Qhov tseem ceeb tiv thaiv ★the ntawm voltage ntawm 0 yuav cov movies nqi thiab chav tsev yog kV. Nws yuav qhia qhov peaking qhov tseem ceeb ntawm kev tshuaj ntsuam cov khoom .the ntsuas yuav automotive kaw mus tso zis rau thaum lub voltage tshaj qhov chaw ntawd. Tsis muaj tej yam dab tsi, voltage tiv thaiv qhov tseem ceeb yog theem teev tseg ntau dua qhov kuaj voltage 4KV.
  Qhov tseem ceeb tiv thaiv ★the uas tam sim no nyob rau 0 cov movies nqi thiab chav tsev yog mA. Nws yuav qhia qhov tam sim no peaking qhov tseem ceeb ntawm kev tshuaj ntsuam cov khoom .the ntsuas yuav automotive kaw mus tso zis rau thaum cov chaw no tshaj qhov chaw ntawd.
  Qhov ★times yog lub 0-60 feeb thiab nws es lub sij hawm no, chav tsev no nas this.
  Saum voltage, tseem yog peaking qhov tseem ceeb, kuaj tej ntaub ntawv uas ntsuas
  Zaub thiab voltage, cov ntaub ntawv tseem nyob rau daim ntawv qhia txog kev xeem yog tag nrho peaking qhov tseem ceeb.
  Thov koj tshem tus cursor "pib kuaj voltage"thiab hais rau nws
  ces nkag mus rau hauv qab nrooj 5 boost interface.
  Boost tam sim no, tos li ib feeb
  Sij hawm poob
  Ntsuas tau nkag mus rau hauv txheej xwm boost thaum tas Court yuav kuaj tau zoo. Nws yuav siv ib zaug kom lub voltage kom mus zoo raws cov sijhawm yaam tseem ceeb nuav. Ntsuas yuav txuas voltage zis thiab nkag mus rau hauv interface pib yog nias lub pob kom nres thaum boost sai.
  Voltage tau kho los ntawm tej xovxwm rau hauv lub lag luam thiab nce thiab nqis
  Khawm pib los ntawm tej xovxwm timing rau paub meej tias nws
  Thov nias ntawm "rau thiab tsis ua"1 fiab khawm thiab kho cov voltage ces zoo nkaus li xovxwm confirm khawm, daim duab 7, ntsuas pib lub sij hawm, ntsuas yuav pib sij thiab daim cov ntawv no yuav sau thaum nws lawm. Rov qab mus rau qhov pib screen, tom qab pas shutdown ua ntej pib qhov kev ntsuas seb tom ntej no.
  ★another tsis muaj tsheb lawm ho voltage tiv thaiv shutdown, tam sim no shutdown. Lub taub interface yuav tshwm sim thaum uas ntsuas tsis lawm. Koj yuav rov muab lub voltage los yog tam sim no rov ntsuas seb tom ntej no.
  3、test voltage peaking qhov tseem ceeb: Umax = 3Uo,
  Uo yog cov movies voltage ua hauj lwm ntawm cov neeg xyuas pib rau-hauv av cable los yog hlau ntaub thaiv npog, rau piv txwv, nyob voltage 10KV cable, single-phase nyob voltage
  8 cov lus ntsuas ntawm daim duab single-phase kev twb kev txuas
  Tseem ceeb yog rau air-cooled unto, kev uas yuav nrhiav li tau los xyuas cov tsis muaj kev cuam tshuam cov rwb thaiv tsev generator tsis yog ib tug phenomenon zoo, xws li nplaim corona pas thiab sai.
  1、0.1 Hz/50KV tswj lub thawv (1pcs)
  2、0.1 Hz/50KV tshuaj (1pcs)
  3、0.1 Hz/50KV shunt capacitor (1pcs)
  4、50KV-voltage zis kab (1pcs)
  5、Shunt capacitance-voltage cables (1pcs)
  Tswj 6、Special cables (1pcs)
  7、power kab (1pcs)
  8、ground hlau (1pcs)
  XII. Hnyuv tws
  Cov movies voltage
  Pem xeem voltage
  Tshuaj tiv thaiv no voltage
  Voltage values(KV)
  Uo yog tus nominal theem voltage, UN rau cable tus nyob voltage kab.
  sim hawm: 1-5 feeb
  Hot Tags: hzdp - 50k ultra-tsawg zaus voltage siab generator, hauv lub teb chaws Suav, manufacturers, txo cheap