Skip to main content    

An official website of the United States government

Here’s how you know

**Official websites use .gov**              A **.gov** website belongs to an official government organization in the United States.            

**Secure .gov websites use HTTPS**              A **lock** (  LockA locked padlock) or **https://** means you’ve safely connected to the .gov website. Share sensitive information only on official, secure websites.            

https://www.nist.gov/el/nist-report-test-fr-4016-test-11

            -  Topics  -  All Topics 
-  Advanced communications 
-  Artificial intelligence 
-  Bioscience 
-  Buildings and construction 
-  Chemistry 
-  Climate 
-  Cybersecurity 
-  Electronics 
-  Energy 
-  Environment 
-  Fire 
-  Forensic science 
-  Health 
-  Information technology 
-  Infrastructure 
-  Manufacturing 
-  Materials 
-  Mathematics and statistics 
-  Metrology 
-  Nanotechnology 
-  Neutron research 
-  Performance excellence 
-  Physics 
-  Public safety 
-  Resilience 
-  Standards 
-  Transportation 
 
            -  Publications 
            -  Labs & Major Programs  -  Laboratories    -  Communications Technology Laboratory 
  -  Engineering Laboratory 
  -  Information Technology Laboratory 
  -  Material Measurement Laboratory 
  -  Physical Measurement Laboratory 
-  User Facilities    -  NIST Center for Neutron Research 
  -  CNST NanoFab 
-  Research Test Beds 
-  Research Projects 
-  Tools & Instruments 
-  Major Programs    -  Baldrige Performance Excellence Program 
  -  CHIPS for America Initiative 
  -  Manufacturing Extension Partnership (MEP) 
  -  Office of Advanced Manufacturing 
  -  Special Programs Office 
  -  Technology Partnerships Office 
 
            -  Services & Resources  -  Standards and Measurements    -  Calibration Services 
  -  Laboratory Accreditation (NVLAP) 
  -  Quality System 
  -  Standard Reference Materials (SRMs) 
  -  Standards.gov 
  -  Time Services 
  -  Office of Weights and Measures 
-  Software 
-  Data    -  Chemistry WebBook 
  -  National Vulnerability Database 
  -  Physical Reference Data 
  -  Standard Reference Data (SRD) 
-  Storefront 
-  License & Patents 
-  Computer Security Resource Center (CSRC) 
-  NIST Research Library 
 
            -  News & Events  -  News 
-  Events 
-  Blogs 
-  Feature Stories 
-  Awards 
-  Video Gallery 
-  Image Gallery 
-  Media Contacts 
 
            -  About NIST  -  About Us    -  Leadership 
  -  Organization Structure 
  -  Budget & Planning 
-  Contact Us 
-  Visit 
-  Careers    -  Student programs 
-  Work with NIST 
-  History    -  NIST Digital Archives 
  -  NIST Museum 
  -  NIST and the Nobel 
-  Educational Resources 
 

## Engineering Laboratory

-  About EL  Expand or Collapse    -  Careers 
  -  Divisions & Offices 
  -  Research Opportunities 
  -  Research Facilities 
  -  Staff & Organization 
  -  Standards Activities 
  -  Contact Us 
-  Goals & Programs  Expand or Collapse    -  Advanced Manufacturing  Expand or Collapse      -  Measurement Science for Additive Manufacturing 
    -  Measurement Science for Manufacturing Robotics 
    -  Advanced Manufacturing Data Infrastructure and Analytics 
  -  Sustainable and Energy-Efficient Manufacturing, Materials, and Infrastructure  Expand or Collapse      -  Embedded Intelligence in Buildings 
    -  Net-Zero Energy, High-Performance Buildings  Expand or Collapse        -  Current Activities 
  -  Disaster-Resilient Buildings, Infrastructure, and Communities  Expand or Collapse      -  Community Resilience 
    -  Earthquake Risk Reduction in Buildings and Infrastructure 
    -  Engineered Materials for Resilient Infrastructure 
    -  Fire Risk Reduction in Buildings 
    -  Fire Risk Reduction in Communities 
    -  Structural Performance under Multi-hazards 
-  Products & Services  Expand or Collapse    -  Extramural Grants Program 
  -  Research Information Service 
  -  Software 
  -  Tools & Instruments 
-  Staff Directory 
-  Popular Links  Expand or Collapse    -  Applied Economics Office 
  -  Resilience  Expand or Collapse      -  Disaster Resilience Federal Funding Opportunity (FFO) 
  -  Fire.gov 
  -  NFRL 
  -  Net-Zero Energy Residential Test Facility 

## Connect with us

GovDelivery

# NIST Report of Test FR 4016: Test 11

## Share

Facebook

Linkedin

Twitter

Email

## Test Description

For details of the test structure, materials, fire source, and instrumentation, see the full NIST report: NIST Technical Note 1455-1, February 2008 Revision, Full Report (3/3/2008) Performance of Home Smoke Alarms Analysis of the Response of Several Available Technologies in Residential Fire Settings.

## Temperature

                  - Temperature. remote bedroom. 20 mm from ceiling
> 

                  - Temperature. remote bedroom. 300 mm from ceiling
> 

                  - Temperature. remote bedroom. 610 mm from ceiling
> 

                  - Temperature. remote bedroom. 900 mm from ceiling
> 

                  - Temperature. remote bedroom. 1220 mm from ceiling
> 

                  - Temperature. remote bedroom. 1520 mm from ceiling
> 

                  - Temperature. remote bedroom. 1820 mm from ceiling
> 

                  - Temperature. main bedroom. 20 mm from ceiling
> 

                  - Temperature. main bedroom. 300 mm from ceiling
> 

                  - Temperature. main bedroom. 610 mm from ceiling
> 

                  - Temperature. main bedroom. 900 mm from ceiling
> 

                  - Temperature. main bedroom. 1220 mm from ceiling
> 

                  - Temperature. main bedroom. 1520 mm from ceiling
> 

                  - Temperature. main bedroom. 1820 mm from ceiling
> 

                  - Temperature. hallway outside remote bedroom. 20 mm from ceiling
> 

                  - Temperature. hallway outside remote bedroom. 300 mm from ceiling
> 

                  - Temperature. hallway outside remote bedroom. 610 mm from ceiling
> 

                  - Temperature. hallway outside remote bedroom. 900 mm from ceiling
> 

                  - Temperature. hallway outside remote bedroom. 1220 mm from ceiling
> 

                  - Temperature. hallway outside remote bedroom. 1520 mm from ceiling
> 

                  - Temperature. hallway outside remote bedroom. position B
> 

                  - Temperature. hallway outside main bedroom. 20 mm from ceiling
> 

                  - Temperature. hallway outside main bedroom. 300 mm from ceiling
> 

                  - Temperature. hallway outside main bedroom. 610 mm from ceiling
> 

                  - Temperature. hallway outside main bedroom. 900 mm from ceiling
> 

                  - Temperature. hallway outside main bedroom. 1220 mm from ceiling
> 

                  - Temperature. hallway outside main bedroom. 1520 mm from ceiling
> 

                  - Temperature. hallway outside main bedroom. 1820 mm from ceiling
> 

                  - Temperature. living room. 20 mm from ceiling
> 

                  - Temperature. living room. 300 mm from ceiling
> 

                  - Temperature. living room. 610 mm from ceiling
> 

                  - Temperature. living room. 900 mm from ceiling
> 

                  - Temperature. living room. 1220 mm from ceiling
> 

                  - Temperature. living room. 1520 mm from ceiling
> 

                  - Temperature. living room. 1820 mm from ceiling
> 

                  - Temperature. front door hallway. 20 mm from ceiling
> 

                  - Temperature. front door hallway. 300 mm from ceiling
> 

                  - Temperature. front door hallway. 610 mm from ceiling
> 

                  - Temperature. front door hallway. 900 mm from ceiling
> 

                  - Temperature. front door hallway. 1220 mm from ceiling
> 

                  - Temperature. front door hallway. 1520 mm from ceiling
> 

                  - Temperature. front door hallway. 1820 mm from ceiling
> 

                  - Temperature. closed room
> 

                  - Temperature. directly above ignition point
> 

                  - Temperature at data acquisition system
> 

## Smoke Obscuration

                  - Smoke Obscuration. remote bedroom. 20 mm from ceiling
> 

                  - Smoke Obscuration. remote bedroom. 900 mm from ceiling
> 

                  - Smoke Obscuration. main bedroom. 20 mm from ceiling
> 

                  - Smoke Obscuration. main bedroom. 900 mm from ceiling
> 

                  - Smoke Obscuration. hallway outside remote bedroom. 900 mm from ceiling
> 

                  - Smoke Obscuration. hallway outside main bedroom. 20 mm from ceiling
> 

                  - Smoke Obscuration. hallway outside main bedroom. 900 mm from ceiling
> 

                  - Smoke Obscuration. front door hallway. 20 mm from ceiling
> 

                  - Smoke Obscuration. front door hallway. 900 mm from ceiling
> 

                  - Smoke Obscuration. closed room
> 

                  - Smoke Obscuration hallway outside remote bedroom. Near alarm board
> 

## CO Concentration

                  - Carbon Monoxide concentration. remote bedroom. Data
> 

                  - Carbon Monoxide concentration. hallway outside remote bedroom. Data
> 

                  - Carbon Monoxide concentration. front door hallway. Data
> 

                  - Carbon Monoxide concentration. main bedroom. Data
> 

## CO2 Concentration

                  - Carbon Dioxide concentration. remote bedroom. Data
> 

                  - Carbon Dioxide concentration. hallway outside remote bedroom. Data
> 

                  - Carbon Dioxide concentration. front door hallway. Data
> 

                  - Carbon Dioxide concentration. main bedroom. Data
> 

## O2 Concentration

                  - Oxygen concentration. remote bedroom. Data
> 

                  - Oxygen concentration. hallway outside remote bedroom. Data
> 

                  - Oxygen concentration. front door hallway. Data
> 

                  - Oxygen concentration. main bedroom. Data
> 

## Heat Alarm

                  - Heat Alarm 1. remote bedroom
> 

## Smoke Alarm

                  - Carbon Monoxide Alarm 2. remote bedroom
> 

                  - Ionization Smoke Alarm 3. remote bedroom
> 

                  - Photoelectric Smoke Alarm 1. remote bedroom
> 

                  - Carbon Monoxide Alarm 3. remote bedroom
> 

                  - Photoelectric Smoke Alarm 3. remote bedroom
> 

                  - Ionization Smoke Alarm 4. remote bedroom
> 

                  - Carbon Monoxide Alarm 1. remote bedroom
> 

## Heat Alarm

                  - Heat Alarm 1. hallway outside remote bedroom
> 

## Smoke Alarm

                  - Carbon Monoxide Alarm 2. hallway outside remote bedroom
> 

                  - Ionization Smoke Alarm 3. hallway outside remote bedroom
> 

                  - Photoelectric Smoke Alarm 1. hallway outside remote bedroom
> 

                  - Carbon Monoxide Alarm 3. hallway outside remote bedroom
> 

                  - Photoelectric Smoke Alarm 3. hallway outside remote bedroom
> 

                  - Ionization Smoke Alarm 4. hallway outside remote bedroom
> 

                  - Carbon Monoxide Alarm 1. hallway outside remote bedroom
> 

## Heat Alarm

                  - Heat Alarm 1. hallway outside main bedroom
> 

## Smoke Alarm

                  - Carbon Monoxide Alarm 2. hallway outside main bedroom
> 

                  - Ionization Smoke Alarm 3. hallway outside main bedroom
> 

                  - Photoelectric Smoke Alarm 1. hallway outside main bedroom
> 

                  - Carbon Monoxide Alarm 3. hallway outside main bedroom
> 

                  - Photoelectric Smoke Alarm 3. hallway outside main bedroom
> 

                  - Ionization Smoke Alarm 4. hallway outside main bedroom
> 

                  - Carbon Monoxide Alarm 1. hallway outside main bedroom
> 

## Heat Alarm

                  - Heat Alarm 1. main bedroom
> 

## Smoke Alarm

                  - Carbon Monoxide Alarm 2. main bedroom
> 

                  - Ionization Smoke Alarm 3. main bedroom
> 

                  - Photoelectric Smoke Alarm 1. main bedroom
> 

                  - Carbon Monoxide Alarm 3. main bedroom
> 

                  - Photoelectric Smoke Alarm 3. main bedroom
> 

                  - Ionization Smoke Alarm 4. main bedroom
> 

                  - Carbon Monoxide Alarm 1. main bedroom
> 

                  - Aspirated Photoelectric Smoke Alarm 1. remote bedroom
> 

                  - Aspirated Photoelectric Smoke Alarm 1. hallway outside remote bedroom
> 

                  - Aspirated Photoelectric Smoke Alarm 1. hallway outside main bedroom
> 

                  - Aspirated Photoelectric Smoke Alarm 1. living room
> 

                  - Ionization Smoke Alarm 1. remote bedroom
> 

                  - Ionization Smoke Alarm 1. hallway outside remote bedroom
> 

                  - Ionization Smoke Alarm 1. hallway outside main bedroom
> 

                  - Ionization Smoke Alarm 1. main bedroom
> 

                  - Unmodified Photoelectric Smoke Alarm 2
> 

                  - Unmodified Ionization Smoke Alarm 2
> 

                  - Unmodified Ionization Smoke Alarm 4
> 

Fire detection

### HEADQUARTERS

301-975-2000

Webmaster | Contact Us | Our Other Offices

TwitterFacebookLinkedInInstagramYouTubeGiphyRSS FeedMailing List

Feedback

            -  Site Privacy 
            -  Accessibility 
            -  Privacy Program 
            -  Copyrights 
            -  Vulnerability Disclosure 
            -  No Fear Act Policy 
            -  FOIA 
            -  Environmental Policy 
            -  Scientific Integrity 
            -  Information Quality Standards 
            -  Commerce.gov 
            -  Science.gov 
            -  USA.gov 
            -  Vote.gov