Skip to main content    

An official website of the United States government

Here’s how you know

**Official websites use .gov**              A **.gov** website belongs to an official government organization in the United States.            

**Secure .gov websites use HTTPS**              A **lock** (  LockA locked padlock) or **https://** means you’ve safely connected to the .gov website. Share sensitive information only on official, secure websites.            

https://www.nist.gov/el/fire-research-division-73300/national-fire-research-laboratory-73306/fire-safety-challenges-0

            -  Topics  -  All Topics 
-  Advanced communications 
-  Artificial intelligence 
-  Bioscience 
-  Buildings and construction 
-  Chemistry 
-  Climate 
-  Cybersecurity 
-  Electronics 
-  Energy 
-  Environment 
-  Fire 
-  Forensic science 
-  Health 
-  Information technology 
-  Infrastructure 
-  Manufacturing 
-  Materials 
-  Mathematics and statistics 
-  Metrology 
-  Nanotechnology 
-  Neutron research 
-  Performance excellence 
-  Physics 
-  Public safety 
-  Resilience 
-  Standards 
-  Transportation 
 
            -  Publications 
            -  Labs & Major Programs  -  Laboratories    -  Communications Technology Laboratory 
  -  Engineering Laboratory 
  -  Information Technology Laboratory 
  -  Material Measurement Laboratory 
  -  Physical Measurement Laboratory 
-  User Facilities    -  NIST Center for Neutron Research 
  -  CNST NanoFab 
-  Research Test Beds 
-  Research Projects 
-  Tools & Instruments 
-  Major Programs    -  Baldrige Performance Excellence Program 
  -  CHIPS for America Initiative 
  -  Manufacturing Extension Partnership (MEP) 
  -  Office of Advanced Manufacturing 
  -  Special Programs Office 
  -  Technology Partnerships Office 
 
            -  Services & Resources  -  Standards and Measurements    -  Calibration Services 
  -  Laboratory Accreditation (NVLAP) 
  -  Quality System 
  -  Standard Reference Materials (SRMs) 
  -  Standards.gov 
  -  Time Services 
  -  Office of Weights and Measures 
-  Software 
-  Data    -  Chemistry WebBook 
  -  National Vulnerability Database 
  -  Physical Reference Data 
  -  Standard Reference Data (SRD) 
-  Storefront 
-  License & Patents 
-  Computer Security Resource Center (CSRC) 
-  NIST Research Library 
 
            -  News & Events  -  News 
-  Events 
-  Blogs 
-  Feature Stories 
-  Awards 
-  Video Gallery 
-  Image Gallery 
-  Media Contacts 
 
            -  About NIST  -  About Us    -  Leadership 
  -  Organization Structure 
  -  Budget & Planning 
-  Contact Us 
-  Visit 
-  Careers    -  Student programs 
-  Work with NIST 
-  History    -  NIST Digital Archives 
  -  NIST Museum 
  -  NIST and the Nobel 
-  Educational Resources 
 

Engineering LaboratoryFire Research Division

## National Fire Research Laboratory

-  Facility & Equipment 
-  Fire Calorimetry Database 
-  Projects 
-  Videos 
-  Employment 
-  Staff Contacts 

# Fire Safety Challenges of Tall Wood Buildings – Phase 2: Task 3 - Cross Laminated Timber Compartment Fire Tests

## Share

Facebook

Linkedin

Twitter

Email

Under the auspices of the Fire Protection Research Foundation, the National Research Council Canada and the National Institute of Standards and Technology jointly conducted a series of cross laminated timber (CLT) compartment fire tests. Technical input and review was provided by the Research Institute of Sweden and a Project Technical Panel. 

This study quantifies the contribution of CLT building elements to compartment fires and characterizes the effect of gypsum board on delaying or preventing involvement of the CLT in the fire under varied ventilation conditions. Six compartments (9.1 m long x 4.6 m wide x 2.7 m high) were assembled out of prefabricated CLT panels.  Each panel was factory assembled using five plies of 35 mm thick lumber for a total thickness of 175 mm. A polyurethane adhesive was used to hold the plies together. The compartment had a rough opening in Wall W2 (front) of 1.8 m wide x 2.0 m high in four tests and 3.6 m wide x 2.0 m high in two tests. The inside of the compartments was fully or partially lined using multiple layers of 15.9-mm thick Type X gypsum board. Real residential contents and furnishings were used to provide a fire load density of 550 MJ/m2. The fire tests were conducted without sprinklers and without firefighting intervention.

Test 1-1 served as a baseline for the tests with the 1.8 m x 2.0 m rough opening in the front wall of the structure (Wall W2). Three layers of the gypsum board were used to cover the CLT walls and ceiling in Test 1-1 so that the CLT would neither contribute to the fire nor develop char during the test. Test 1-2 served as a baseline for the tests with the 3.6 m x 2.0 m rough opening in the front wall of the structure (Wall W2). An exposed wall (W1) was tested in both ventilation configurations (Test 1-3 and Test 1-5). Test 1-4 and Test 1-6 involved an exposed ceiling and a combination of exposed ceiling and wall, respectively, with the 1.8 m x 2.0 m rough opening.

Information about the overall project can be found on the Fire Safety Challenges of Tall Wood Buildings – Phase 2 website.

### DATA

**Files updated March 13, 2018**                  - CLT Test 1-1
                  	
                  - CLT Test 1-2
                  	
                  - CLT Test 1-3
                  	
                  - CLT Test 1-4
                  	
                  - CLT Test 1-5
                  	
                  - CLT Test 1-6
                  

### 360° IMAGES

Click here to download 360° images. Post-fire images were not collected for Test 1-1 or Test 1-2.	(Images can be viewed using a 360 degree media viewer)

### VIDEO GALLERY

CLT Mock-up Room Corner (Test 2)

CLT Compartment Construction

CLT Compartment Furnishing

CLT Test 1-1: Wide View (Time Lapse)

CLT Test 1-1: Doorway View (Time Lapse)

CLT Test 1-1: Doorway View (Real Time)

CLT Test 1-1: Post-Test Drywall Removal

CLT Test 1-2: Wide View (Time Lapse)

CLT Test 1-2: Doorway View (Time Lapse)

CLT Test 1-3: Front View (Time Lapse)

CLT Test 1-3: Doorway View (Time Lapse)

CLT Test 1-4: Front View (Time Lapse)

CLT Test 1-4: Doorway View (Time Lapse)

CLT Test 1-4: Doorway View (Real Time)

CLT Test 1-5: Doorway View (Time Lapse)

CLT Test 1-5: Doorway View (Real Time)

CLT Test 1-6: Doorway View (Time Lapse)

CLT Compartment Deconstruction and Cleanup

How Can We Make Buildings More Resilient to Fire?

How NIST Captures Great Fire Video Footage

### RELATED PUBLICATIONS

                  - Su, J., Lafrance, P. S., Hoehler, M., Bundy, M.  Fire Safety Challenges of Tall Wood Buildings – Phase 2: Task 2 & 3 – Cross Laminated Timber Compartment Fire Tests , Fire Protection Research Foundation Report, FPRF-2018-01, February 2018.
                  	
                  - Hoehler, M.; Su, J., Lafrance, P. S., Bundy, M.; Kimball, A.;Brandon, D.; Ostman, B.  Fire Safety Challenges of Tall Wood Buildings: Large-Scale Cross Laminated Timber Compartment Fire Tests  SiF18 - The 10th International Conference on Structures in Fire, June 6-8, 2018, Blefast, UK.
                  

Fire dynamics and scienceStructural fire resistance

## Contacts

                -  Matthew Hoehler  matthew.hoehler@nist.gov      (301) 975-8517   
                -  Matthew Bundy  matthew.bundy@nist.gov      (301) 975-6880   

### HEADQUARTERS

301-975-2000

Webmaster | Contact Us | Our Other Offices

TwitterFacebookLinkedInInstagramYouTubeGiphyRSS FeedMailing List

Feedback

            -  Site Privacy 
            -  Accessibility 
            -  Privacy Program 
            -  Copyrights 
            -  Vulnerability Disclosure 
            -  No Fear Act Policy 
            -  FOIA 
            -  Environmental Policy 
            -  Scientific Integrity 
            -  Information Quality Standards 
            -  Commerce.gov 
            -  Science.gov 
            -  USA.gov 
            -  Vote.gov