U.S. flag
        An official website of the United States government
          Here’s how you know
        Here’s how you know**Official websites use .gov**
              
              A **.gov** website belongs to an official government organization in the United States.
        **Secure .gov websites use HTTPS**
              
              A **lock** (  A locked padlock
) or **https://** means you’ve safely connected to the .gov website. Share sensitive information only on official, secure websites. https://www.nist.gov/el/fire-research-division-73300/firegov-fire-service/examination-thermal-conditions-wood-floor
  Search NIST
    Search
              Menu

      


Close
    Topics
        All Topics
                                                        Advanced communications
                                                        Artificial intelligence
                                                        Bioscience
                                                        Buildings and construction
                                                        Chemistry
                                                        Climate
                                                        Cybersecurity
                                                        Electronics
                                                        EnergyEnvironment
                                                        Fire
                                                        Forensic science
                                                        Health
                                                        Information technology
                                                        Infrastructure
                                                        Manufacturing
                                                        Materials
                                                        Mathematics and statisticsMetrology
                                                        Nanotechnology
                                                        Neutron research
                                                        Performance excellence
                                                        Physics
                                                        Public safety
                                                        Resilience
                                                        Standards
                                                        Transportation
            Publications
            Labs & Major Programs
        Laboratories
                                Communications Technology Laboratory
                                  Engineering Laboratory
                                  Information Technology Laboratory
                                  Material Measurement Laboratory
                                  Physical Measurement LaboratoryUser Facilities
                                NIST Center for Neutron Research
                                  CNST NanoFab
                                                        Research Test Beds
                                                        Research Projects
                                                        Tools & InstrumentsMajor Programs
                                Baldrige Performance Excellence Program
                                  CHIPS for America Initiative
                                  Manufacturing Extension Partnership (MEP)
                                  Office of Advanced Manufacturing
                                  Special Programs Office
                                  Technology Partnerships Office
            Services & Resources
        Standards and Measurements
                                Calibration Services
                                  Laboratory Accreditation (NVLAP)
                                  Quality System
                                  Standard Reference Materials (SRMs)
                                  Standards.gov
                                  Time Services
                                  Office of Weights and MeasuresSoftware
                                                        Data
                                Chemistry WebBook
                                  National Vulnerability Database
                                  Physical Reference Data
                                  Standard Reference Data (SRD)
                                                        Storefront
                                                        License & PatentsComputer Security Resource Center (CSRC)
                                                        NIST Research Library
            News & Events
        News
                                                        Events
                                                        Blogs
                                                        Feature Stories
                                                        AwardsVideo Gallery
                                                        Image Gallery
                                                        Media Contacts
            About NIST
        About Us
                                Leadership
                                  Organization Structure
                                  Budget & Planning
                                                        Contact Us
                                                        Visit
                                                        Careers
                                Student programsWork with NIST
                                                        History
                                NIST Digital Archives
                                  NIST Museum
                                  NIST and the Nobel
                                                        Educational Resources
 
 Engineering Laboratory /                  Fire Research Division
      Fire.Gov
    
      
  Electronic Safety Equipment
          Fire Dynamics
          Fire Fighting Tactics
          Fire Fighting Technology
          Fire Forensics
          Fire Protection
          Fire Studies
          Firefighter Fatality & Injury Studies
          Personal Protective Equipment
          Staffing Studies
          Structural Collapse
          Wind Driven Fires



  Connect with us
      
      TwitterExamination of the Thermal Conditions of a Wood Floor Assembly above a Compartment Fire

Share
  Facebook
                      Linkedin
                      Twitter
                      Email

Examination of the Thermal Conditions of a Wood Floor Assembly above a Compartment Fire  

Thermal Conditions of a Wood Floor Assembly above a Compartment Fire test
  Four real-scale experiments were conducted by NIST to measure the temperatures above and below a wood floor assembly exposed to fire conditions from below. The objectives of the experiments were: 1) to examine the heat transfer through a wood floor assembly and 2) to examine the ability of a thermal imager to determine the potential severity of the fire beneath the floor assembly and the ability to provide a sense of the structural integrity of the floor assembly in order to provide improved situational awareness. Each experiment was conducted in a wood framed two story structure. Each story consisted of a single compartment with interior dimensions of approximately 15.5 ft x 15.5 ft x 8 ft high. The initial fuel in each experiment consisted of six wood pallets and hay in the center of the lower level compartment. Three different floor assemblies were used. Three commercially available thermal imagers (TIs), each with a different type of sensor were used to view and record the thermal conditions of the top of the floor assembly from the open doorway in the upper compartment. Given the insulating effects of the OSB and the floor coverings, the temperature increase or thermal signatures viewed by the TIs were small given the fact that the ceiling temperatures below the OSB were in excess of 1100 oF. These experiments demonstrated that TIs alone cannot be relied upon to determine the structural integrity of a wood floor system. Therefore, it is critical for the fire service to review their practice of size-up and other fire ground tactics needed to enable the location of the fire prior to conducting fire operations inside a building.



Test 1 - Examination of the Thermal Conditions of a Wood Floor Assembly above a Compartment Fire

	The floor system installed for this experiment was laminate flooring over OSB with composite wood I-joists spaced 24 inches apart. Video views from top left: Side A, BST thermal imager showing upper level floor, aSi thermal imager showing upper level floor, Clock, video showing upper level floor, VOx thermal imager showing upper level floor, CD corner, thermal imager view of lower level interior, video view of lower level interior.

Ignition starts at 0 seconds. The first gypsum board is removed at 10 minutes, 10 seconds. The second gypsum board is removed from the doorway at 15 minutes, 35 seconds. Flashover occurs in the lower level at 17 minutes, 45 seconds. Flames come out of the lower level door at 18 minutes, 5 seconds. Thermal imagers are removed at 23 minutes, 25 seconds. The floor collapses at 24 minutes and 30 seconds. Extinguishment begins at 24 minutes, 50 seconds.

Test 2  - Examination of the Thermal Conditions of a Wood Floor Assembly above a Compartment Fire

	The floor cover examined was a carpet surfaced floor with composite wood I-joists spaced 406 mm (16 in) apart.
	Ignition starts at 0 seconds. The first gypsum board is removed at 600 seconds. The second gypsum board is removed at 1025 seconds. Localized flashover occurs at 1040 seconds. Thermal imagers are removed at 1090 seconds. Complete flashover occurs at 1110 seconds. The floor collapses at 1675 seconds. Extinguishment begins at 1695 seconds.

Test 3 - Examination of the Thermal Conditions of a Wood Floor Assembly above a Compartment Fire

	The floor examined was a carpet surfaced floor with solid wood joists spaced 406 mm (16 in) apart.
	Ignition starts at 0 seconds. The first gypsum board is removed at 600 seconds. The second gypsum board is removed at 930 seconds. Localized flashover occurs at 930 seconds. Complete flashover occurs at 965 seconds. Thermal imagers are removed at 1200 seconds. The floor collapses at 1485 seconds. Extinguishment begins at 1505 seconds.

Test 4 - Examination of the Thermal Conditions of a Wood Floor Assembly above a Compartment Fire

	The floor cover examined was a carpet surfaced floor with composite wood I-joists spaced 406 mm (16 in) apart.
	Ignition starts at 0 seconds. The first gypsum board is removed at 600 seconds. The second gypsum board is removed at 1025 seconds. Localized flashover occurs at 1040 seconds. Thermal imagers are removed at 1090 seconds. Complete flashover occurs at 1110 seconds. The floor collapses at 1675 seconds. Extinguishment begins at 1695 seconds.
  Disaster and failure studies

    
    Created February 15, 2013, Updated September 16, 2019
 HEADQUARTERS
            100 Bureau Drive
              Gaithersburg, MD 20899301-975-2000
            Webmaster | Contact Us | Our Other Offices
        Twitter
            
Facebook
            
LinkedIn
            
Instagram
            
YouTube
            
Giphy
            
RSS Feed
            
Mailing List
                              How are we doing? Feedback

  
  Site Privacy
                      Accessibility
                      Privacy Program
                      Copyrights
                      Vulnerability Disclosure
                      No Fear Act Policy
                      FOIA
                      Environmental Policy
                      Scientific Integrity
                      Information Quality Standards
                      Commerce.gov
                      Science.gov
                      USA.gov
                      Vote.gov