Skip to main content    

An official website of the United States government

Here’s how you know

**Official websites use .gov**              A **.gov** website belongs to an official government organization in the United States.            

**Secure .gov websites use HTTPS**              A **lock** (  LockA locked padlock) or **https://** means you’ve safely connected to the .gov website. Share sensitive information only on official, secure websites.            

https://www.nist.gov/el/changes-nfpa-building-and-fire-codes-fy-2008-ncst-annual-report

            -  Topics  -  All Topics 
-  Advanced communications 
-  Artificial intelligence 
-  Bioscience 
-  Buildings and construction 
-  Chemistry 
-  Climate 
-  Cybersecurity 
-  Electronics 
-  Energy 
-  Environment 
-  Fire 
-  Forensic science 
-  Health 
-  Information technology 
-  Infrastructure 
-  Manufacturing 
-  Materials 
-  Mathematics and statistics 
-  Metrology 
-  Nanotechnology 
-  Neutron research 
-  Performance excellence 
-  Physics 
-  Public safety 
-  Resilience 
-  Standards 
-  Transportation 
 
            -  Publications 
            -  Labs & Major Programs  -  Laboratories    -  Communications Technology Laboratory 
  -  Engineering Laboratory 
  -  Information Technology Laboratory 
  -  Material Measurement Laboratory 
  -  Physical Measurement Laboratory 
-  User Facilities    -  NIST Center for Neutron Research 
  -  CNST NanoFab 
-  Research Test Beds 
-  Research Projects 
-  Tools & Instruments 
-  Major Programs    -  Baldrige Performance Excellence Program 
  -  CHIPS for America Initiative 
  -  Manufacturing Extension Partnership (MEP) 
  -  Office of Advanced Manufacturing 
  -  Special Programs Office 
  -  Technology Partnerships Office 
 
            -  Services & Resources  -  Standards and Measurements    -  Calibration Services 
  -  Laboratory Accreditation (NVLAP) 
  -  Quality System 
  -  Standard Reference Materials (SRMs) 
  -  Standards.gov 
  -  Time Services 
  -  Office of Weights and Measures 
-  Software 
-  Data    -  Chemistry WebBook 
  -  National Vulnerability Database 
  -  Physical Reference Data 
  -  Standard Reference Data (SRD) 
-  Storefront 
-  License & Patents 
-  Computer Security Resource Center (CSRC) 
-  NIST Research Library 
 
            -  News & Events  -  News 
-  Events 
-  Blogs 
-  Feature Stories 
-  Awards 
-  Video Gallery 
-  Image Gallery 
-  Media Contacts 
 
            -  About NIST  -  About Us    -  Leadership 
  -  Organization Structure 
  -  Budget & Planning 
-  Contact Us 
-  Visit 
-  Careers    -  Student programs 
-  Work with NIST 
-  History    -  NIST Digital Archives 
  -  NIST Museum 
  -  NIST and the Nobel 
-  Educational Resources 
 

## Engineering Laboratory

-  About EL  Expand or Collapse    -  Careers 
  -  Divisions & Offices 
  -  Research Opportunities 
  -  Research Facilities 
  -  Staff & Organization 
  -  Standards Activities 
  -  Contact Us 
-  Goals & Programs  Expand or Collapse    -  Advanced Manufacturing  Expand or Collapse      -  Measurement Science for Additive Manufacturing 
    -  Measurement Science for Manufacturing Robotics 
    -  Advanced Manufacturing Data Infrastructure and Analytics 
  -  Sustainable and Energy-Efficient Manufacturing, Materials, and Infrastructure  Expand or Collapse      -  Embedded Intelligence in Buildings 
    -  Net-Zero Energy, High-Performance Buildings  Expand or Collapse        -  Current Activities 
  -  Disaster-Resilient Buildings, Infrastructure, and Communities  Expand or Collapse      -  Community Resilience 
    -  Earthquake Risk Reduction in Buildings and Infrastructure 
    -  Engineered Materials for Resilient Infrastructure 
    -  Fire Risk Reduction in Buildings 
    -  Fire Risk Reduction in Communities 
    -  Structural Performance under Multi-hazards 
-  Products & Services  Expand or Collapse    -  Extramural Grants Program 
  -  Research Information Service 
  -  Software 
  -  Tools & Instruments 
-  Staff Directory 
-  Popular Links  Expand or Collapse    -  Applied Economics Office 
  -  Resilience  Expand or Collapse      -  Disaster Resilience Federal Funding Opportunity (FFO) 
  -  Fire.gov 
  -  NFRL 
  -  Net-Zero Energy Residential Test Facility 

## Connect with us

GovDelivery

# Changes to the NFPA Building and Fire Codes - from the FY 2008 NCST Annual Report

## Share

Facebook

Linkedin

Twitter

Email

**Approved at the NFPA Annual Meeting and Standards Council Action on 2009 Documents, July 2008**

The following are the code changes consistent with the NIST WTC recommendations now required by the NFPA Codes.
                  - Full building evacuation (use of elevators). Permits elevators to remain in service (prior to FEO Phase I recall) and to be used by occupants for self-evacuation. Requires a package of protection measures including protected lobbies on every floor with direct access to a stair, real time monitoring and communication, secondary power, protection of wiring and cables, water protection, and full building sprinklers. Requirements contained in an adoptable annex; no thresholds or mandates, and no credit against egress requirements.
                  - Fire service access elevator (use of elevators). Requires a minimum of one fire service access elevator for buildings more than 120 ft in height. Includes a package of protection including protected lobbies on every floor, direct access to a stair with a standpipe, secondary power, protection of wires and cables, real time monitoring, and communications.
                  - Surviving burnout without collapse. Establishes a required performance-based design scenario that evaluates a high rise building for performance under a fully-developed fire event where the building must resist both local and global collapse.
                  - Supplemental evacuation equipment. Establishes a series of performance requirements to recognize (but not mandate nor give credit for) supplemental egress systems such as controlled descent devices and platform lifts; with references to ASTM standards.
                  - Situational awareness. Requirement establishes situational awareness as a fundamental requirement of egress planning and design.
                  - Managed evacuation. Provides advisory text on managed and unmanaged evacuations as well as partial, total, and protect-in-place strategies.
                  - Evacuation diagrams. Establishes a menu of provisions that can be mandated by occupancy chapters to require evacuation diagrams that reflect actual floor arrangements and exit locations.
                  - Luminescent exit stair markings (new buildings). Establishes a menu of provisions that can be mandated by occupancy chapters to deal with markings on stair treads, landings and handrails; perimeter demarcation, obstacles, door frames, and signage.
                  - Exit signage. Requires directional signage within horizontal components of exit enclosures (transfer corridors).
                  - Minimum width of transfer corridors. Establishes a minimum width of transfer corridors as 2/3 the width of the stair.
                  - Remoteness of stairways. Remoteness changed from walking path to direct line measurement with the criterion remaining at 1/3 the diagonal if sprinklered and 1⁄2 the diagonal if not.
                  - Remoteness applied to exit discharge. Applies remoteness criteria to exit discharge as well as exit access and the exits themselves.
                  - Risk assessment for buildings with substantial hazard. Annex note suggesting the conduct of a risk assessment for buildings greater than 420 ft or with more than 10,000 occupants that evaluates performance under extreme events.
                  - Field inspections of fireproofing. Requires special inspections of fireproofing for integrity where accessible, every 5 years, and a written report provided.
                  - Emergency responder radio communications in buildings (radio coverage requirements). Requires approved radio coverage in all buildings including requirements for signal strength and signal to noise ratio, by the installation of repeaters monitored by the fire alarm system. Includes requirements for commissioning and regular testing. Alternatively, the fire department can specify wired phones.

Disaster and failure studiesDisaster and failure studiesDisaster and failure studiesDisaster and failure studiesDisaster and failure studiesResilienceResilienceFireDisaster and failure studiesDisaster and failure studiesStructural engineering

### HEADQUARTERS

301-975-2000

Webmaster | Contact Us | Our Other Offices

TwitterFacebookLinkedInInstagramYouTubeGiphyRSS FeedMailing List

Feedback

            -  Site Privacy 
            -  Accessibility 
            -  Privacy Program 
            -  Copyrights 
            -  Vulnerability Disclosure 
            -  No Fear Act Policy 
            -  FOIA 
            -  Environmental Policy 
            -  Scientific Integrity 
            -  Information Quality Standards 
            -  Commerce.gov 
            -  Science.gov 
            -  USA.gov 
            -  Vote.gov