U.S. flag
        An official website of the United States government
          Here’s how you know
        Here’s how you know**Official websites use .gov**
              
              A **.gov** website belongs to an official government organization in the United States.
        **Secure .gov websites use HTTPS**
              
              A **lock** (  A locked padlock
) or **https://** means you’ve safely connected to the .gov website. Share sensitive information only on official, secure websites. https://www.nist.gov/el/energy-and-environment-division-73200/nist-multizone-modeling/applications-contam/iaq-analysis
  Search NIST
    Search
              Menu

      


Close
    Topics
        All Topics
                                                        Advanced communications
                                                        Artificial intelligence
                                                        Bioscience
                                                        Buildings and construction
                                                        Chemistry
                                                        Climate
                                                        Cybersecurity
                                                        Electronics
                                                        EnergyEnvironment
                                                        Fire
                                                        Forensic science
                                                        Health
                                                        Information technology
                                                        Infrastructure
                                                        Manufacturing
                                                        Materials
                                                        Mathematics and statisticsMetrology
                                                        Nanotechnology
                                                        Neutron research
                                                        Performance excellence
                                                        Physics
                                                        Public safety
                                                        Resilience
                                                        Standards
                                                        Transportation
            Publications
            Labs & Major Programs
        Laboratories
                                Communications Technology Laboratory
                                  Engineering Laboratory
                                  Information Technology Laboratory
                                  Material Measurement Laboratory
                                  Physical Measurement LaboratoryUser Facilities
                                NIST Center for Neutron Research
                                  CNST NanoFab
                                                        Research Test Beds
                                                        Research Projects
                                                        Tools & InstrumentsMajor Programs
                                Baldrige Performance Excellence Program
                                  CHIPS for America Initiative
                                  Manufacturing Extension Partnership (MEP)
                                  Office of Advanced Manufacturing
                                  Special Programs Office
                                  Technology Partnerships Office
            Services & Resources
        Standards and Measurements
                                Calibration Services
                                  Laboratory Accreditation (NVLAP)
                                  Quality System
                                  Standard Reference Materials (SRMs)
                                  Standards.gov
                                  Time Services
                                  Office of Weights and MeasuresSoftware
                                                        Data
                                Chemistry WebBook
                                  National Vulnerability Database
                                  Physical Reference Data
                                  Standard Reference Data (SRD)
                                                        Storefront
                                                        License & PatentsComputer Security Resource Center (CSRC)
                                                        NIST Research Library
            News & Events
        News
                                                        Events
                                                        Blogs
                                                        Feature Stories
                                                        AwardsVideo Gallery
                                                        Image Gallery
                                                        Media Contacts
            About NIST
        About Us
                                Leadership
                                  Organization Structure
                                  Budget & Planning
                                                        Contact Us
                                                        Visit
                                                        Careers
                                Student programsWork with NIST
                                                        History
                                NIST Digital Archives
                                  NIST Museum
                                  NIST and the Nobel
                                                        Educational Resources
 
 Engineering Laboratory /                  Building Energy & Environment Division
      NIST Multizone Modeling
    
      
  SOFTWARE
                            Expand or Collapse
          CONTAM
                                              Expand or Collapse
                Download
                                  Documentation
                                  Disclaimer
                                  Input Data
                                  Program Revisions
                                  Help
                                  Tutorials
                                  User Group
                      CFDO Editor
                      CONTAM 3D Exporter
                      Type98
                      CONTAM Weather File Creator
                      WPC Translator
                      ContamLink
                      CONTAM Particle Distribution Calculator
                      ContamRV
                      CONTAM Results Export Tool
                      1D Zone Data File Converter
                      LoopDA
                      Climate Suitability Tool
                      Particle Model - Single zone, Single size
                      Particle Model - Single zone, Size-resolved
                      VHP Mask Disinfection Tool
                      FaTIMA
                      ViPER
          APPLICATIONS
                            Expand or Collapse
          Airflow and Ventilation
                      IAQ Analysis
                      Smoke Management
          CASE STUDIES
          CHIMP



  Connect with us
      
      GovDeliveryIAQ Analysis and Contaminant Transport

Share
  Facebook
                      Linkedin
                      Twitter
                      Email

The prediction of contaminant concentrations can be used to determine the indoor air quality (IAQ) performance of a building before it is constructed and occupied, to investigate the impacts of various design decisions related to ventilation system design and building material selection, and to assess the indoor air quality performance of an existing building. Predicted contaminant concentrations can also be used to estimate personal exposure based on occupancy patterns in a building.

As previously described, CONTAM provides the ability to establish a model of the building geometry and modify other features of the building without having to redefine the building geometry. The features related to contaminant transport include sources, sinks, and filtration systems. CONTAM provides several different contaminant source models that enable the simulation of various contaminant emitting building materials (e.g. carpet, paint and pressed-wood products), episodic type sources such as building maintenance activities and even pressure driven sources (e.g. radon entry through building foundations). Some of the applications related to contaminant dispersal in buildings to which CONTAM lends itself are presented below.

As the name suggests, one of the main reasons that the CONTAM family of programs was developed was to provide a tool for simplifying the analysis of airborne contaminant transport within complex, multizone buildings. Contaminant behavior within buildings can be influenced by a number of factors including airflow, source and sink properties, contaminant filtration by various building components, and chemical reactions. CONTAM provides for the ability to address all of these mechanisms within a single analysis tool. This comprehensive set of contaminant analysis features makes CONTAM useful in understanding many contaminant-related building issues and solving or preventing contaminant related problems in the built environment.

IAQ Design Analysis
	Contaminant Source Isolation
	IAQ Investigations
	Exposure Analysis

IAQ Design Analysis

Typically, IAQ is dealt with during design by requiring minimum ventilation rates on a space or whole building level. The prescriptive approach contained in ASHRAE Standard 62.1-2019 and 62.2-2019 provide minimum ventilation requirements in cfm (L/s) per person and/or cfm/ft2 (L/s*m2). The IAQ Procedure in Standard 62.1 is a performance-based procedure that addresses designing to maintain acceptable levels of known contaminants. CONTAM can be useful in implementing this approach to designing for acceptable IAQ both from the point of view of ventilation system and building material impacts. Other features of IAQ design that can be addressed include the consideration of outdoor air contaminant levels, the potential use of contaminant filtration to treat outdoor and re-circulated air, consideration of intermittent or variable occupancy, and distribution of ventilation air to multiple spaces.

CONTAM can be useful in implementing prescriptive design methods by analyzing the impact of prescribed ventilation rates on resultant contaminant levels various indoor and outdoor contaminant sources. CONTAM can also be used to address prescriptive methods that allow for for intermittent or variable occupancy within a building. Ventilation rates can be adjusted by changing supply and outdoor air intake rates (i.e., varying damper positions or cycling the ventilation system fans on and off) to the intermittently occupied spaces. The variation in ventilation could be carried out in such a way as to maintain contaminant concentrations within acceptable levels at all times. The method by which the ventilation rate is varied depends upon the type of contaminant source that is being controlled, i.e., occupant related or not. The method involves lead or lag times of providing ventilation air depending on the type of source of the contaminant that is being controlled. CONTAM can be used to model the source and develop contaminant profiles. From this information, ventilation control strategies can be implemented in the CONTAM building model in the form of scheduled fan on/off times and system airflow rates. Simulations can be performed and results reviewed to determine if the ventilation strategy would maintain contaminant levels according to design requirements.

Performance-based methods of designing for IAQ can also be addressed using CONTAM. For example, the Indoor Air Quality Procedure presented in ASHRAE Standard 62.1-2019 consists of identifying known contaminants of concern, specifying acceptable levels of these contaminants, and providing ventilation that prevents the acceptable levels from being exceeded. CONTAM can be useful in analyzing contaminant levels based on contaminant source strengths, design ventilation rates, and air filtration and cleaning system characteristics that might be implemented in the ventilation system design. While CONTAM could be useful in verifying ventilation system design, it could also provide a means of documenting the design.

*Building Material Impacts* - CONTAM can be used to analyze the IAQ impacts of building material emissions. Although designers might implement "low-emitting" materials in a design, it is often difficult to quantify the effects of using such materials. CONTAM enables the analysis of different materials within a building design on a quantitative basis.

Contaminant Source Isolation

Contaminant source isolation refers to the prevention of contaminant transport from one zone having a know source into another. Some examples of contaminant source isolation issues include parking garages, toilets, and radon entry from the soil. These situations involve establishing airflow or pressure differentials between different zones of a building to control contaminant migration. The ability to use CONTAM to define complicated multizone systems enables the analysis of contaminant transport not only between zones that are immediately adjacent to each other, but also the less obvious transport paths related to elevator and stair shafts, service chases, and duct leakage.

One example of a CONTAM source isolation problem is the analysis of radon entry into and transport within a building. CONTAM provides a pressure-driven source model that can be used to effectively simulate the transport of radon from the soil into the building through cracks in a building foundation. Because the source is pressure dependent, the relationship between the pressure differences associated with different ventilation scenarios, stack and wind induced flows and radon transport into the building can be analyzed. Further, CONTAM could then be used to investigate the implementation of various radon mitigation strategies including fan pressurization and depressurization techniques.

IAQ Investigations

CONTAM can be useful in investigating IAQ problems as they occur in existing buildings. Using CONTAM one can establish a building geometry and system features and use CONTAM to gain insight into why a building is behaving the way it does. For example, if a room in a building is experiencing elevated contaminant levels from a known source, CONTAM could be used to investigate potential transport paths and methods to mitigate the transport of the contaminant to occupied zones. CONTAM analysis can be particularly useful when coupled with the measurement of relevant parameters such as system airflow rates, differential pressure, contaminant concentrations, wind and indoor and outdoor temperatures. CONTAM has been used as a tool to investigate building operating conditions that lead to radon entry from the soil and to size a fan system to alleviate the problem.

Exposure Analysis

Exposure analysis refers to the determination of the amount (dose) of a contaminant to which a building occupant would be subjected within a building. This analysis requires knowledge of contaminant concentration time histories, occupancy patterns within a building and occupant ingestion rates. CONTAM provides the ability to calculate contaminant time histories using transient simulation techniques and to define occupant inhalation rates and occupancy patterns within a building. Together this information can be used to provide average and peak exposure levels as well as average and peak dosages of contaminants of concern.
  Buildings and Construction, Indoor air quality, Energy, Environment and Air / water / soil quality

    
    Contacts
      
        

Steven Emmerich
    
      
  steven.emmerich@nist.gov
  (301) 975-6459

  William Stuart Dols
    
      
  william.dols@nist.gov
  (301) 975-5860

  Brian Polidoro
    
      
  brian.polidoro@nist.gov
  (301) 975-6445

Created March 7, 2018, Updated August 11, 2020
 HEADQUARTERS
            100 Bureau Drive
              Gaithersburg, MD 20899301-975-2000
            Webmaster | Contact Us | Our Other Offices
        Twitter
            
Facebook
            
LinkedIn
            
Instagram
            
YouTube
            
Giphy
            
RSS Feed
            
Mailing List
                              How are we doing? Feedback

  
  Site Privacy
                      Accessibility
                      Privacy Program
                      Copyrights
                      Vulnerability Disclosure
                      No Fear Act Policy
                      FOIA
                      Environmental Policy
                      Scientific Integrity
                      Information Quality Standards
                      Commerce.gov
                      Science.gov
                      USA.gov
                      Vote.gov