Exhibit 10.18(b)

 



 

PRELIMINARY TENANT IMPROVEMENT ELECTRICAL INFRASTRUCTURE SUMMARY

 

	
DATE:   
    	
05-24-2010
    
	
PROJECT:   
    	
BOOT   BARN
    
	
BUILDING:   
    	
15776   LAGUNA CANTON RD.
    
	
SUITE   #: 
    	
—
    
	
SPACE   PLAN: 
    	
—
    


 

	
SERVICE EQUIPMENT:
    	
 
    
	
 
    	
 
    	
 
    
	
E1
    	
ELECTRICAL   SERVICE — 2000 AMP METER / MAIN
    	
EXISTING
    
	
 
    	
 
    	
 
    
	
STANDARD DISTRIBUTION:
    	
 
    
	
 
    	
 
    	
 
    
	
E9
    	
LIGHTING   CONTROL PANEL — (10 — RELAYS)
    	
EXISTING
    
	
 
    	
 
    	
 
    
	
E10
    	
277   / 480 VOLT, 3 PHASE, 4 WIRE PANEL
    	
EXISTING
    
	
 
    	
(1)   — (255 AMPS PANEL BOARD “1HA”)
    	
 
    
	
 
    	
 
    	
 
    
	
E11
    	
TRANSFORMER   — 480 PRIMARY TO 120/206 VOLT SECONDARY
    	
EXISTING
    
	
 
    	
(1)   75 KVA (“T1” K–13 RATED)
    	
 
    
	
 
    	
 
    	
 
    
	
E12
    	
120   / 206 VOLT, 3 PHASE, 4 WIRE PANELS.
    	
EXISTING
    
	
 
    	
(1)   — 225 AMPS PANEL BOARD “1LA”)
    	
 
    
	
 
    	
 
    	
 
    
	
E13
    	
120   / 206 VOLT, 3 PHASE, 4 WIRE PANELS.
    	
EXISTING
    
	
 
    	
(1)   — 225 AMPS PANEL BOARD “1LB”)
    	
 
    
	
 
    	
 
    	
 
    
	
E14
    	
TRANSFORMER   — 480 PRIMARY TO 120/206 VOLT SECONDARY
    	
EXISTING
    
	
 
    	
(1)   75 KVA (“T3” K–13 RATED)
    	
 
    
	
 
    	
 
    	
 
    
	
E15
    	
120   / 206 VOLT, 3 PHASE, 4 WIRE PANELS.
    	
EXISTING
    
	
 
    	
(1)   — 225 AMPS WITH 200 AMP MCB PANEL BOARD “3LA”)
    	
 
    
	
 
    	
 
    	
 
    
	
E16
    	
TRANSFORMER   — 480 PRIMARY TO 120/206 VOLT SECONDARY
    	
EXISTING
    
	
 
    	
(1)   75 KVA (“T4” K–13 RATED)
    	
 
    
	
 
    	
 
    	
 
    
	
E17
    	
120   / 206 VOLT, 3 PHASE, 4 WIRE PANELS.
    	
EXISTING
    
	
 
    	
(1)   — 225 AMPS WITH 200 AMP MCB PANEL BOARD “4LA”)
    	
 
    
	
 
    	
 
    	
 
    
	
E18
    	
TRANSFORMER   — 480 PRIMARY TO 120/206 VOLT SECONDARY
    	
EXISTING
    
	
 
    	
(1)   75 KVA (“T5” K–13 RATED)
    	
 
    
	
 
    	
 
    	
 
    
	
E19
    	
TRANSFORMER   — 480 PRIMARY TO 120/206 VOLT SECONDARY
    	
EXISTING
    
	
 
    	
(1)   75 KVA (“T6” K–13 RATED)
    	
 
    
	
 
    	
 
    	
 
    
	
E20
    	
TRANSFORMER   — 480 PRIMARY TO 120/206 VOLT SECONDARY
    	
EXISTING
    
	
 
    	
(1)   150 KVA (“T7” K–13 RATED)
    	
 
    
	
 
    	
 
    	
 
    
	
E21
    	
120   / 206 VOLT, 3 PHASE, 4 WIRE PANELS.
    	
EXISTING
    
	
 
    	
(1)   — 225 AMPS PANEL BOARD “5LA”)
    	
 
    
	
 
    	
 
    	
 
    
	
E22
    	
120   / 206 VOLT, 3 PHASE, 4 WIRE PANELS.
    	
EXISTING
    
	
 
    	
(1)   — 250 AMPS PANEL BOARD “6LA”)
    	
 
    
	
 
    	
 
    	
 
    
	
E23
    	
TRANSFORMER   — 480 PRIMARY TO 120/206 VOLT SECONDARY
    	
EXISTING
    
	
 
    	
(1)   150 KVA (“T2” K–13 RATED)
    	
 
    
	
 
    	
 
    	
 
    
	
E24
    	
120   / 206 VOLT, 3 PHASE, 4 WIRE PANELS.
    	
EXISTING
    
	
 
    	
(1)   — 225 AMPS PANEL BOARD “2LA”)
    	
 
    
	
 
    	
 
    	
 
    
	
E25
    	
120   / 206 VOLT, 3 PHASE, 4 WIRE PANELS.
    	
EXISTING
    
	
 
    	
(1)   — 225 AMPS PANEL BOARD “2LC”)
    	
 
    
	
 
    	
 
    	
 
    
	
E26
    	
120   / 206 VOLT, 3 PHASE, 4 WIRE PANELS.
    	
EXISTING
    
	
 
    	
(1)   — 100 AMPS PANEL BOARD “2LB”)
    	
 
    
	
 
    	
 
    	
 
    
	
MISC. ITEMS:
    	
 
    
	
 
    	
 
    	
 
    
	
E31
    	
ALLOW   FOR (1) 120 VOLT, 20 AMP BREAKER AND (1) DEDICATED DUPLEX RECEPTACLE AND (1)   PHONE / DATA DEVICE PER EACH COPIER, FAX AND PRINTER LOCATION. REFER TO   ARCHITECTURAL PLAN FOR QUANTITIES. (LANDLORD / ENGINEER ASSUMPTION)
    
	
 
    	
 
    
	
E32
    	
CONTRACTOR   TO ALLOW FOR 1/2“C.O. FROM THERMOSTAT LOCATION TO 6” ABOVE CEILING. (LANDLORD   / ENGINEER ASSUMPTION)
    
	
 
    	
 
    
	
E33
    	
ALLOW   FOR A 4 CIRCUIT, 8 WIRE FURNITURE SYSTEM PER (8) WORKSTATIONS. REFER TO   ARCHITECTURAL PLAN FOR QUANTITIES AND LOCATIONS. (LANDLORD / ENGINEER   ASSUMPTION)
    
	
 
    	
 
    
	
E34
    	
ALLOW   PRICING TO RELOCATE EXISTING EXIT SIGNS AS REQUIRED WITH REMODEL ALLOW FOR   THE IRVINE COMPANY STANDARD TYPE “16” AS REQUIRED. REFER TO ARCHITECTURAL   DRAWINGS FOR QUANTITIES AND LOCATIONS. (LANDLORD / ENGINEER ASSUMPTION)
    
	
 
    	
 
    
	
E35
    	
ALL   PRICING TO RELOCATE EXISTING LIGHT FIXTURES AS REQUIRED WITH REMODEL ALLOW   FOR NEW 2X4 PRISMATIC THE IRVINE COMPLAINT STANDARD TYPE “3” AS REQUIRED WITH   REMODEL REFER TO ARCHITECTURAL DRAWINGS FOR QUANTITIES AND LOCATIONS. (LANDLORD   / ENGINEER ASSUMPTION)
    
	
 
    	
 
    
	
E36
    	
ELECTRICAL   CONTRACTOR TO ALLOW FOR LIGHTING FIXTURES TO BE APPROXIMATELY (1) PER 80   SQUARE FEET.
    
	
 
    	
 
    
	
E37
    	
PROVIDE   PRICING TO DEMOLISH ALL ASSOCIATED CONDUIT, WIRING AND RECEPTACLE LOCATIONS   ASSOCIATED WITH ANY WALLS BEING DEMOLISHED.
    
	
 
    	
 
    
	
E38
    	
ALLOW   FOR THE DEMOLITION OF FURNITURE SYSTEM FLOOR CORES WERE REQUIRED. REMOVE   CONDUIT AND CONDUCTORS BACK TO PANEL BOARD(S). REFER TO ARCHITECTURAL   DRAWINGS FOR QUANTITIES AND LOCATIONS. (LANDLORD / ENGINEER ASSUMPTION)
    
	
 
    	
 
    
	
E39
    	
PROVIDE   ALL NEW POWER DEVICES AND LIGHT SWITCH LOCATIONS TO MATCH EXISTING (LANDLORD   / ENGINEER ASSUMPTION)
    
	
 
    	
 
    
	
E40
    	
ELECTRICAL   CONTRACTOR TO ALLOW FOR THE DEMOLISHING OF ALL EXISTING NON BUILDING STANDARD   EXIT SIGNS AND ALLOW FOR NEW TIC BUILDING STANDARD WHITE EXIT SIGNS.
    
	
 
    	
 
    
	
GENERAL   NOTE:
    
	
 
    	
 
    
	
E45
    	
ELECTRICAL   CONTRACTOR TO REFER TO MECHANICAL, PLUMBING AND ARCHITECTURAL NOTES FOR   ADDITIONAL INFORMATION.
    


 

ABOVE STANDARD (IN ADDITION TO STANDARD ITEMS) POWER REQUIREMENTS:

 

TELE ROOM

 

	
E48
    	
·      ALLOW FOR (1) 206 VOLT, 2 POLE, 50 AMP   BREAKER FOR HARDWIRED UPS EQUIPMENT. REFER TO ARCHITECTURAL NOTES FOR FURTHER   INFORMATION (LANDLORD / ENGINEER ASSUMPTION)

·      ALLOW FOR (1) 4 X 8 FIRE RATED PLYWOOD   TELEPHONE BACKBOARD. (LANDLORD / ENGINEER ASSUMPTION

·      ALLOW FOR (1) 3/4” CONDUIT WITH 1/1/0   LG. FROM GROUNDING BUS BAR (CHATSWORTH /13622-010) TO BUILDING MAN SERVICE   GROUND. (LANDLORD / ENGINEER ASSUMPTION)

·      ALLOW FOR (1) 4” CONDUIT TO MAN BUILDING   ELECTRICAL ROOM MPOE (LANDLORD /ENGINEER ASSUMPTION)

·      ALLOW FOR (1) 120 VOLT, 20 AMP BREAKER   AND (1) DEDICATED DOUBLE DUPLEX RECEPTACLE FOR TELEPHONE BACKBOARD POWER   (LANDLORD / ENGINEER ASSUMPTION)

·      ALLOW FOR (2) 4” CONDUIT SLEEVES TO   ACCESSIBLE 1ST FLOOR CEILING SPACE (LANDLORD / ENGINEER ASSUMPTION)
    
	
 
    	
 
    
	
FIRE ALARM SYSTEM:
    
	
 
    	
 
    
	
E49
    	
ELECTRICAL CONTRACTOR TO CONFIRM WITH THE APPROVED IRVINE   COMPANY FIRE ALARM VENDOR IF THE EXISTING FIRE LIFE SAFETY SYSTEM MEETS   CURRENT CODE REQUIREMENTS. IF EXISTING FIRE ALARM SAFETY SYSTEM DOES NOT MEET   CURRENT CODE REQUIREMENTS, CONTRACTOR TO INCLUDE ALL COSTS ASSOCIATED WITH   UPGRADING THE EXISTING SYSTEM AS REQUIRED TO ALLOW FOR A CODE MINIMUM CENTRAL   MONITORING SYSTEM. (LANDLORD / ENGINEER ASSUMPTION)
    
	
 
    	
 
    
	
ALTERNATE NOTES:
    
	
 
    	
 
    
	
x
    	
ELECTRICAL CONTRACTOR TO PROVIDE PRONG TO DEMOUSH LIGHTING   CONTROL PANEL AND PROVIDE ALL NEW HARD WALL OFFICES WILL HAVE DUAL RELAY WALL   MOUNTED OCCUPANCY SENSORS AND OPEN OFFICE AREA’S WILL HAVE CEILING MOUNTED   OCCUPANCY SENSORS. (LANDLORD / ENGINEER ASSUMPTION)
    
	
 
    	
 
    
	
CAPITAL NOTES:
    
	
 
    	
 
    
	
x
    	
ELECTRICAL CONTRACTOR TO PROVIDE PRONG TO DEMOLISH ALL   EXISTING CEILING AND WILL MOUNTED SECURITY ACCESS CONTROL DEVICES, CALL   BOXES, CARD READERS, CONDUIT AND CABLING.
    
	
 
    	
 
    
	
xx
    	
ALLOW FOR THE DEMOUSHING ALL EXISTING TELE/DATA   CABLING/DEVICES THROUGHOUT.
    


 

MECHANICAL ENGINEERING NOTES

 

MECHANICAL DEMOLITION

 

1.              REMOVE (4) EXISTING COMBINATION SMOKE AND FIRE CHAMPERS, RECONNECT DUCTWORK AND CAP OPENINGS.

 

2.              REMOVE ALL EXISTING THERMOSTATS (MINIMUM 26).

 

MECHANICAL NOTES

 

1.              MODIFY EXISTING AIR DISTRIBUTION INCLUDING RELOCATION OF CEILING DIFFUSERS, AND RETURN AIR REGISTERS TO CONFORM TO THE LATEST ARCHITECTURAL SPACE PLANS

 

2.              PROVIDE ROOF MOUNTED UPBLAST EXHAUST FAN, 400 CFM AT 0.25” TSP, COOK MODEL ACRUB OR EQUAL, FOR OFFICE 228. FAN SHALL BE PROVIDED COMPLETE WITH BACKDRAFT DAMPER AND ROOF CURB. PROVIDE EXHAUST INTAKE DUCT AND AIR DISTRIBUTION. FANS SHALL BE LOCATED WITHIN THE EXISTING ROOF SCREEN AREA. PROVIDE LINE VOLTAGE THERMOSTAT.

 

3.              PROVIDE THE FOLLOWING THERMAFUSERS WITH ALL ASSOCIATED CONTROLS:

 

(2) SIZE 12

(4) SIZE 10

 

4.              CLEAN ALL SUPPLY AND RETURN CEILING REGISTERS. REPAINT AS REQUIRED

 

5.              PROVIDE ALLOWANCE FOR REBALANCING ALL SUPPLY DIFFUSERS, RETURN AIR REGISTERS AND ROOFTOP UNITS WITHIN THE SCOPE OF WORK.

 

PLUMBING NOTES

 

1.              REMOVE EXISTING GARBAGE DISPOSER AND PROVIDE T.I.C. STANDARD GARBAGE DISPOSAL AT EXISTING FIRST FLOOR SINK.

 

CAPITAL ALTERNATES

 

C1.     REPLACE 26 THERMOSTATS AT EXISTING AC UNITS TO TIC STANDARD EMS THERMOSTATS CONTRACTOR TO COORDINATE COST AND SCOPE OF WORK WITH AAS (714) 692-9003.

 

C2.     PROVIDE ALLOWANCE FOR INSTALLATION OF 110 VOLUME DAMPERS AT RETURN AIR REGISTERS OR DUCTS TO ALLOW AIR BALANCING.

 

C3.     PROVIDE ALLOWANCE FOR INSTALLATION OF 26 SMOKE DETECTORS ON EXISTING ROOFTOP UNITS.

 

C4.     CONTRACTOR TO PROVIDE ALLOWANCE TO REPLACE DAMAGED FLEXIBLE DUCTWORK FOR APPROXIMATELY 10,000 SQUARE FEET AREA. NEW DUCTWORK SHALL BE INSULATED PREFABRICATED SPIRAL SHEET METAL CONFORMING TO SMACNA STANDARD.

 

GENERAL NOTES

 

1.1       VERIFY EXISTING CONDITIONS AND NOTIFY H. HENDY ASSOCIATES OF ANY DISCREPANCIES.

 

1.2       PROVIDE PROTECTION AT ALL PENETRATIONS IN FIRE RATED WALLS TO MAINTAIN FIRE RATING.

 

DEMOLITION NOTES

 

2.1       DEMOLISH EXISTING MILLWORK.

 

PARTITIONS, DOORS, GLAZING NOTES

 

3.1       REPAIR EXTERIOR WINDOW COVERINGS.

 

3.2       PROVIDE 24” WIDE X HEIGHT OF DOOR SIDELIGHT WITH 1/4” CLEAR TEMPERED GLASS IN BUILDING STANDARD WESTERN INTEGRATED CLEAR ANODIZED ALUMNUM FRAME INTEGRAL TO DOOR FRAME.

 

3.3       EXISTING GLAZING TO REMAIN.

 

3.4       PROVIDE GYP. BOARD CASED OPENING. 

 

3.5       CONTRACTOR TO RELOCATE EXISTING GLAZING ASSEMBLY TO LOCATION SHOWN. 



 

MILLWORK NOTES

 

4.1       EXISTING MILLWORK TO REMAIN.

 

4.2       EXISTING MILLWORK TO REMAIN. PROVIDE NEW COUNTERTOP.

 

4.3       ROOM 123: PROVIDE + 11’-0” OF UPPER AND LOWER PLASTIC LAMINATE CABINETS, COUNTERTOP. BACK SPLASH, ADJUSTABLE SHELVES AND CONCEALED HINGES WITH MELAMINE INTERIOR. PROVIDE (1) BANK OF DRAWERS.

 

4.4       ROOM 121: PROVIDE + 10’-0” OF UPPER AND LOWER PLASTIC LAMINATE CABINETS, COUNTERTOP, BACK SPLASH, ADJUSTABLE SHELVES AND CONCEALED HINGES WITH MELAMINE INTERIOR. PROVIDE (1) BANK OF DRAWERS.

 



 

POWER & COMMUNICATION NOTES

 

5.1       TELEPHONE/DATA CABLING AND COVERPLATES TO BE PROVIDED AND INSTALLED BY TENANT. COLOR T.B.D.

 

5.2       PROVIDE LIGHT SENSORS PER TITLE 24. PAIRED IN DOUBLE GANG BOX, WHITE PLASTIC COVER, 42” A.F.F. TO SWITCH CENTER LINE.

 

5.3       PROVIDE REQUIRED RATED BOX/INSTALLATION AT RATED WALLS.

 

5.4       EXISTING ELECTRICAL TO REMAIN U.N.O.

 

5.5       EXISTING FLOOR CORE TO REMAIN. PROVIDE (1) 1-1/4” CONDUIT FROM FLOOR BOX TO TENANT PROVIDED PLASMA SCREEN.  

 

LIGHT & CEILING NOTES

 

6.1       PROVIDE ADEQUATE HVAC AND ZONING AS REQUIRED FOR PROPOSED LAYOUT. THERMOSTAT SHALL BE PROVIDED WITH SET POINT AS REQUIRED BY TITLE 24. CEILING DIFFUSERS AND RETURN PERFORATED FACE WITH 2x4 CEILING GRID. DISTRIBUTION, DROPS, BOX FROM SHELL SUPPLY MAIN LOOP.

 

6.2       PROVIDE FIRE DAMPERS AT ALL DUCT PENETRATIONS THROUGH ONE HOUR-RATED PARTITIONS.

 

6.3       DISTRIBUTE NEW BUILDING STANDARD FIRE SPRINKLERS (PENDANT SATIN CHROME PLATED, RECESSED HEADS, ADJUSTABLE CANOPIES, LOCATED AT CENTER OF SCORED CEILING TILE. CEILING DROPS FROM SHELL SUPPLY LOOP). AS REQUIRED FOR PROPOSED LAYOUT.

 

6.4       PROVIDE (12 TOTAL) NEW 2 x 4 FLUORESCENT 3 LAMP ENERGY SAVING BALLAST, PRISMATIC LENS FIXTURE. MATCH EXISTING.

 

6.5       PROVIDE (3) NEW BUILDING STANDARD ILLUMINATED EXIT SIGNS. (1ST FLOOR) MATCH EXISTING.

 

6.6       CONTRACTOR TO EXTEND EXISTING ACOUSTICAL GRID AND TILE, IN LOCATION SHOWN. 

 

FINISHES NOTES

 

7.1       CONTRACTOR TO LEVEL FLOOR WHERE VCT OR TILE ARE SPECIFIED.

 

7.2       PROVIDE VINYL TRANSITION STRIP AT VCT/CARPET TRANSITIONS.

 

7.3       CONTRACTOR TO PATCH AND REPAIR CONCRETE FLOOR AS REQUIRED, TO RECEIVE NEW FINISHES.

 

7.4       EXISTING FINISHES TO REMAIN CLEAN CERAMIC TILE ROOMS; 124, 125, 218, 222, 223

 

SPECIALTIES NOTES

 

8.1       PROVIDE BUILDING STANDARD KEYING AND TENANT SIGNAGE ALLOWANCE

 

8.2       PROVIDE NEW EXTERIOR GALVENIZED CHAIN LINK FENCING WITH BLACK VINYL SLATS. FENCE TO BE 6’ - 0” TALL PROVIDE (1) 32” WIDE SLIDING GATE WITH GUIDE TRACK ON GROUND AND (2) TELESCOPING/SWINGING GATES 12’ - 0” WIDE EACH.

 

8.3       VERIFY OPERATING CONDITION OF ALL EXTERIOR ROLL UP DOORS.

 

8.4       EXISTING SHOWER TO REMAIN.

 

8.5       CONTRACTOR TO PROVIDE NEW CONCRETE SIDEWALK (5’ - 0”W X 6’ - 0” LONG) TO ALIGN WITH EXISTING PAVER.

 

ALTERNATE NOTES

 

 

FINISH LEGEND

 

	

    	
ITEM:
    	
CARPET
    
	
MFR:
    	
J &   J INVISION
    
	
STYLE:
    	
MERGE
    
	
COLOR/No.:
    	
Z6356   / T.B.D.
    
	
INSTALLATION:
    	
DIRECT   GLUE - DOWN, STAIRS TO BE OVER PAD
    
	
CONTRACT:
    	
 
    


 

	

    	
ITEM:
    	
18’   X 18’ VINYL COMPOSITION TILE
    
	
MFR:
    	
ARMSTRONG
    
	
STYLE:
    	
STANDARD   EXCELON
    	

    
	
COLOR/No.:
    	
TND
    
	
INSTALLATION:
    	
PER.   MFR. SPECS.
    
	
CONTRACT:
    	
 
    


 

	

    	
ITEM:
    	
WALL   PAINT (FLAT)
    
	
MFR:
    	
BENJAMIN   MOORE
    
	
STYLE:
    	
AC   - 40
    
	
COLOR/No.:
    	
GLAZIER   WHITE
    
	
INSTALLATION:
    	
MINIMUM   2-COATS OVER PRIMER
    
	
CONTRACT:
    	
 
    


 

	

    	
ITEM:
    	
ACCENT   WALL
    
	
MFR:
    	
FRAZEE
    
	
STYLE:
    	
 
    
	
COLOR/No.:
    	
8684M/OAK   PLAZA
    
	
INSTALLATION:
    	
MINIMUM   2-COATS OVER PRIMER
    
	
CONTRACT:
    	
 
    


 

	

    	
ITEM:
    	
RUBBER   BASE (COVED)
    
	
MFR:
    	
BURKE   MERCER
    
	
STYLE:
    	
2   1/2” BASE
    
	
COLOR/No.:
    	
TO   BE SELECTED
    
	
INSTALLATION:
    	
PER.   MFR. SPECS.
    
	
CONTRACT:
    	
 
    


 

	

    	
ITEM:
    	
PLASTIC   LAMINATE
    
	
MFR:
    	
NEVAMAR
    
	
STYLE:
    	
TAXTURED
    
	
COLOR/No.:
    	
SMOKY   WHITE/#S-7-27T
    
	
INSTALLATION:
    	
PER.   MFR. SPECS.
    
	
CONTRACT:
    	
 
    


 

ELECTRICAL LEGEND

 

	

    	
TYPE:
    	
DUPLEX   OUTLET
    
	
POWER:
    	
120V,   20 AMP
    
	
MOUNTING:
    	
18”   A.F.F., U.N.O.
    
	
COLOR:
    	
SEE   NOTE #1 BELOW
    
	
NOTES:
    	
 
    
	
 
    	
 
    	
 
    
	

    	
TYPE:
    	
DUPLEX   OUTLET (COPIER)
    
	
POWER:
    	
120V,   20 AMP, SEPARATE CIRCUIT
    
	
MOUNTING:
    	
18”   A.F.F., U.N.O
    
	
COLOR:
    	
SEE   NOTE #1 BELOW
    
	
NOTES:
    	
 
    
	
 
    	
 
    	
 
    
	

    	
TYPE:
    	
FOURPLEX   OUTLET
    
	
POWER:
    	
120V,   20 AMP
    
	
MOUNTING:
    	
18”   A.F.F., U.N.O.
    
	
COLOR:
    	
SEE   NOTE #1 BELOW
    
	
NOTES:
    	
 
    
	
 
    	
 
    	
 
    
	

    	
TYPE:
    	
FOURPLEX   OUTLET
    
	
POWER:
    	
120V,   20 AMP, SEPARATE CIRCUIT
    
	
MOUNTING:
    	
18”   A.F.F., U.N.O.
    
	
COLOR:
    	
SEE   NOTE #1 BELOW
    
	
NOTES:
    	
 
    
	
 
    	
 
    	
 
    
	

    	
TYPE:
    	
DUPLEX   OUTLET
    
	
POWER:
    	
120V,   20 AMP
    
	
MOUNTING:
    	
42”   A.F.F., U.N.O.
    
	
COLOR:
    	
SEE   NOTE #1 BELOW
    
	
NOTES:
    	
 
    
	
 
    	
 
    	
 
    
	

    	
TYPE:
    	
DUPLEX   OUTLET
    
	
POWER:
    	
120V,   20 AMP, SEPARATE CIRCUIT
    
	
MOUNTING:
    	
42”   A.F.F., U.N.O
    
	
COLOR:
    	
SEE   NOTE #1 BELOW
    
	
NOTES:
    	
 
    
	
 
    	
 
    	
 
    
	

    	
TYPE:
    	
FOURPLEX   OUTLET
    
	
POWER:
    	
120V,   20 AMP
    
	
MOUNTING:
    	
42”   A.F.F., U.N.O.
    
	
COLOR:
    	
SEE   NOTE #1 BELOW
    
	
NOTES:
    	
 
    
	
 
    	
 
    	
 
    
	

    	
TYPE:
    	
DUPLEX   OUTLET GFI
    
	
POWER:
    	
120V,   20 AMP
    
	
MOUNTING:
    	
42”   A.F.F., U.N.O.
    
	
COLOR:
    	
SEE   NOTE #1 BELOW
    
	
NOTES:
    	
 
    
	
 
    	
 
    	
 
    
	

    	
TYPE:
    	
TELEPHONE   DATA OUTLET
    
	
POWER:
    	
N/A
    
	
MOUNTING:
    	
18”   A.F.F., U.N.O.
    
	
COLOR:
    	
SEE   NOTE #1 BELOW
    
	
NOTES:
    	
2   S BOX SIZE   PROVIDE RING AND PULL STRING
    
	
 
    	
 
    	
(COVERPLATE   BY TENANT’S VENDOR)
    
	
 
    	
 
    	
 
    
	

    	
TYPE:
    	
TELEPHONE   DATA OUTLET
    
	
POWER:
    	
N/A
    
	
MOUNTING:
    	
42”   A.F.F., U.N.O.
    
	
COLOR:
    	
SEE   NOTE #1 BELOW
    
	
NOTES:
    	
2   S BOX SIZE   PROVIDE RING AND PULL STRING
    
	
 
    	
 
    	
(COVERPLATE   BY TENANT’S VENDOR)
    
	
 
    	
 
    	
 
    
	

    	
TYPE:
    	
TELEPHONE   OUTLET
    
	
POWER:
    	
N/A
    
	
MOUNTING:
    	
48”   A.F.F., U.N.O.
    
	
COLOR:
    	
SEE   NOTE #1 BELOW
    
	
NOTES:
    	
2   S BOX SIZE   PROVIDE RING AND PULL STRING
    
	
 
    	
 
    	
(COVERPLATE   BY TENANT’S VENDOR)
    
	
 
    	
 
    	
 
    
	

    	
PROVIDE   J-BOX FOR BASE FEEDS AT WALLS/COLUMNS 4 CIRCUIT, 8 WRE CONFIGURATION ASSUMED   U.O.N. (1) 400 WATT COMPUTER PER WORKSTATION, MAX 8 WORKSTATIONS PER J-BOX,   U.O.N.
    
	
 
    	
 
    
	

    	
 
    	
PROVIDE   J-BOX FOR FLUSH FLOOR MOUNTED FLOOR FEED 4 CIRCUIT, 8 WRE CONFIGURATION   ASSUMED U.O.N. (1) 400 WATT COMPUTER PER WORKSTATION, MAX 8 WORKSTATIONS PER   J-BOX, U.O.N.
    
	
 
    	
 
    	
 
    
	

    	
 
    	
FLUSH   FLOOR MOUNTED FLOOR FEED G.C. TO PROVIDE HARD-WRE CONNECTION
    
	
 
    	
 
    	
 
    
	

    	
 
    	
FLUSH   FLOOR MOUNTED COMBINATION ELECTRICAL DUPLEX & TELEPHONE/DATA. SEE   ELECTRICAL
    
	
 
    	
 
    	
 
    
	

    	
 
    	
CARD   READER IS LOW VOLTAGE WRING BY TENANT. GENERAL CONTRACTOR TO PROVIDE FLUSH 4S   BOX WITH SINGLE P_RING WITH CONDUIT AT EACH LOCATION. MOUNT AT +40” A.F.F.   COORDINATE WITH CUSTOMER FOR ANY ADDITIONAL REQUIREMENTS- SEE ELECTRICAL
    
	
 
    	
 
    
	

    	
4’   X 8’ FIRE RETARDANT TREATED PLYWOOD BACKBOARD, PANT TO MATCH ADJACENT   PARTITION
    
	
 
    	
 
    
	
(N)
    	
NEW
    
	
 
    	
 
    
	
(W)
    	
WALL   MOUNTED AT 48” A.F.F.
    
	
 
    	
 
    
	
NOTE:
    	
 
    
	
1.
    	
ALL   RECEPTACLES AND COVER PLATES TO BE (WHITE, IVORY, ALMOND, GREY, BROWN,   BLACK).
    
					


 

CONSTRUCTION LEGEND 

 

	

    	
EXISTING   PARTITION TO REMAIN.
    
	
 
    	
 
    
	

    	
EXISTING   PARTITION TO BE REMOVED.
    
	
 
    	
 
    
	

    	
NEW   INTERIOR PARTITION: 2-1/2” X 25 GAUGE METAL STUD FRAMING AT 24” O.C. WITH ONE   LAYER 5/8” TYPE ‘X’ GYP. BOARD EACH SIDE TO UNDERSIDE OF SUSPENDED CEILING.   PROVIDE SEISMIC BRACING TO STRUCTURE ABOVE.
    
	
 
    	
 
    
	

    	
NEW   INTERIOR PARTITION: 2-1/2” X 25 GAUGE METAL STUD FRAMING AT 24” O.C. WITH ONE   LAYER 5/8” TYPE ‘X’ GYP. BOARD EACH SIDE TO UNDERSIDE OF SUSPENDED CEILING.   PROVIDE SEISMIC BRACING TO STRUCTUR ABOVE.
    
	
 
    	
 
    
	

    	
NEW   1/4” COPPER WATER LINE WITH SHUT-OFF VALVE FOR REFRIGERATOR ICE, ICE MAKER   AND COFFEE MAKER (MILL WORKER TO DRILL HOLE IN COUNTER TOP FOR TUBING AT   COFFEE MAKER LOCATIONS WITH SHUT-OFF INSTALLED UNDER COUNTER).
    
	
 
    	
 
    
	

    	
NEW   BUILDING STANDARD SEMI-RECESSED FIRE EXTINGUISHER CABINET. SEE PLANS FOR   LOCATIONS.
    
	
 
    	
 
    
	

    	
NEW   MILLWORK TO BE CONSTRUCTED REFER TO “MILLWORK NOTES.”
    
	
 
    	
 
    
	

    	
TRANSITION   STRIP
    
	
 
    	
 
    
	
DOOR SCHEDULE
    
	
 
    	
 
    
	

    	
NEW   BUILDING STANDARD DOOR ASSEMBLY WITH FRAME, LATCHSET, 2 PAIR HINGES

AND   DOOR STOP. SEE PLAN FOR DOORS WITH INTEGRAL SIDELIGHT.
    
	
 
    	
 
    
	

    	
NEW   BUILDING STANDARD DOOR ASSEMBLY WITH FRAME, LOCKSET, 2-PAIR HINGES,

DOOR   STOP.
    
	
 
    	
 
    
	

    	
NEW   1 HOUR RATED DOOR ASSEMBLY WITH HOLLOW METAL DOOR FRAME,

LATCHSET,   CLOSER, DOOR STOP, GASKETS AND ALUMINUM THRESHOLD.
    
	
 
    	
 
    
	

    	
EXISTING   DOOR ASSEMBLY TO REMAIN.
    
	
 
    	
 
    
	

    	
RELOCATED   DOOR ASSEMBLY TOUCH UP AS REQUIRED.
    
	
 
    	
 
    
	

    	
NEW   PAIR OF STOREFRONT DOORS TO MATCH EXISTING. 
    
	
 
    	
 
    
	
 
    	
CONSTRUCTION LEGEND
    
	
 
    	
 
    
	

    	
REFRIGERATOR   (BY TENANT)
    
	
 
    	
 
    
	

    	
INSTA   HOT WATER HEATER
    
	
 
    	
 
    
	

    	
3/4   H.P. GARBAGE DISPOSAL
    
	
 
    	
 
    
	

    	
MICROWAVE   (BY TENANT)
    
	
 
    	
 
    
	

    	
COFFEE   MAKER (BY TENANT)
    
	
 
    	
 
    
	

    	
COPIER   (BY TENANT)
    
	
 
    	
 
    
	

    	
FAX   (BY TENANT)
    
	
 
    	
 
    
	

    	
PRINTER   (BY TENANT)
    
	
 
    	
 
    
	
 
    	
NOTE:  UNLESS NOTED OTHERWISE, ALL EQUIPMENT TO BE   PROVIDED AND

INSTALLED   BY GENERAL/ELECTRICAL CONTRACTOR.
    


 

H. HendyAssociates

 

HHA

 

INTERIOR PLANNING AND DESIGN

 

4770 CAMPUS DRIVE SUITE ONE HUNDRED NEWPORT BEACH CA 92660

TELEPHONE 949-851-3060 FAX 948-851-0807 WWW.HHENDY.COM

 

THE IRVINE COMPANY

 

PROJECT

 



 

AGREED

 

ACCEPTED THIS DAY                      DAY OF                         , 2009

 

	
TENANT
    	
 
    	
 
    
	
 
    	
 
    	
 
    
	
BY:
    	
 
    	
 
    
	
 
    	
 
    	
 
    
	
TITLE:
    	
 
    	
 
    


 

NOTE UPON SIGNING THIS SPACE PLAN. ALL OF MY REQUIREMENTS HAVE BEEN ADDRESSED AND I HAVE FULL AUTHORITY TO END MY ORGANIZATION TO TO THIS PLAN. ANY CHANGES TO THIS PLAN AFTER THIS DATE WILL INCUR ADDITIONAL SPACE PLANNING COST TO ME. THE TENANT

 

ISSUES AND REVISIONS

 

	
NO.
    	
 
    	
DESCRIPTION
    	
 
    	
DATE
    
	
 
    	
 
    	
ISSUE   FOR PRICING
    	
 
    	
05/25/10
    
	

    	
 
    	
ADDENDUM   A
    	
 
    	
05/28/10
    
	

    	
 
    	
ADDENDUM   B
    	
 
    	
06/01/10
    


 

All specifications, drawings, concepts, designs, components, intellectual and written material represented herein constitute unique and unpublished work of H. Hendy Associates and may not be copied, used by or disclosed to others without written consent of H. Hendy Associates © 2007 H. Hendy Associates

 

	
JOB   NUMBER
    	
27000.125.10
    
	
 
    	
 
    
	
DATE
    	
MAY   25, 2010
    
	
 
    	
 
    
	
SCALE
    	
NONE
    
	
 
    	
 
    
	
FILE   NAME
    	
L157760100PPN
    
	
 
    	
 
    
	
DRAWN   BY
    	
DL
    
	
 
    	
 
    
	
APPROVED   BY
    	
KW
    


 

PROJECT

 

BOOT BARN

 

15776 LAGUNA CANYON ROAD IRVINE, CA

 

PRELIMINARY PRICING NOTES

 

PPN.0100.15776L

 









 



 

H. HendyAssociates

 

HHA

 

INTERIOR PLANNING AND DESIGN

 

4770 CAMPUS DRIVE SUITE ONE HUNDRED NEWPORT BEACH CA 92660

TELEPHONE 949-851-3060 FAX 948-851-0807 WWW.HHENDY.COM

 

THE IRVINE COMPANY

 

PROJECT

 



 

AGREED

 

ACCEPTED THIS DAY                      DAY OF                         , 2009

 

	
TENANT
    	
 
    	
 
    
	
 
    	
 
    	
 
    
	
BY:
    	
 
    	
 
    
	
 
    	
 
    	
 
    
	
TITLE:
    	
 
    	
 
    


 

NOTE UPON SIGNING THIS SPACE PLAN. ALL OF MY REQUIREMENTS HAVE BEEN ADDRESSED AND I HAVE FULL AUTHORITY TO END MY ORGANIZATION TO TO THIS PLAN. ANY CHANGES TO THIS PLAN AFTER THIS DATE WILL INCUR ADDITIONAL SPACE PLANNING COST TO ME. THE TENANT

 

ISSUES AND REVISIONS

 

	
NO.
    	
 
    	
DESCRIPTION
    	
 
    	
DATE
    
	
 
    	
 
    	
ISSUE   FOR PRICING
    	
 
    	
05/25/10
    
	

    	
 
    	
ADDENDUM   A
    	
 
    	
05/28/10
    
	

    	
 
    	
ADDENDUM   B
    	
 
    	
06/01/10
    


 

All specifications, drawings, concepts, designs, components, intellectual and written material represented herein constitute unique and unpublished work of H. Hendy Associates and may not be copied, used by or disclosed to others without written consent of H. Hendy Associates © 2007 H. Hendy Associates

 

	
JOB   NUMBER
    	
27000.125.10
    
	
 
    	
 
    
	
DATE
    	
MAY   25, 2010
    
	
 
    	
 
    
	
SCALE
    	
1/8”   = 1’ – 0”
    
	
 
    	
 
    
	
FILE   NAME
    	
L157760100PPN
    
	
 
    	
 
    
	
DRAWN   BY
    	
DL
    
	
 
    	
 
    
	
APPROVED   BY
    	
KW
    


 

PROJECT

 

BOOT BARN

 

15776 LAGUNA CANYON ROAD IRVINE, CA

2ND FLOOR

 

PRICING PLAN

 

PP.0200.15776L