SECTION

 PAGE 

 DATE

A Crane Co. Company USA: (937) 778-8947 • Canada: (905) 457-6223 • International: (937) 615-3598

Submersible Non-Clog Pumps

1

D

www.cranepumps.com

Professional Plumbing

2/15

Testing is performed with 

water specifi c gravity of 1.0 

@ 68 ̊F (20 ̊C), other fl uids 

may vary performance

DESCRIPTION:

SUBMERSIBLE NON-CLOG SEWAGE PUMP DESIGNED 

FOR TYPICAL RAW SEWAGE APPLICATIONS

Series SEV412

2" Spherical Solids Handling

Manual & Automatic

DISCHARGE ...............................2” NPT, Female, Vertical

LIQUID TEMPERATURE .............77°F (25°C) Continuous

MOTOR HOUSING ......................Cast Iron

PUMP BODY ...............................Cast Iron

IMPELLER: Design ....................Multi-Vane, Vortex 

Material ..................Cast Iron

SHAFT ........................................416 Stainless Steel

O-RINGS ......................................Buna-N

HARDWARE ................................300 Series Stainless Steel

PAINT ........................................... Air Dry Enamel

CORD ENTRY ..............................20 ft. (6m) Quick Disconnect Cord with 

plug on 115 Volt, Pressure Gromment for

 sealing and strain relief

SEAL: Design ....................Single Mechanical, Oil Filled Reservoir 

Material ...................Carbon/Ceramic/Buna-N

 Hardware - 300 Series Stainless

UPPER BEARING ........................Single Row, Ball, Oil Lubricated

LOWER BEARING .......................Single Row, Ball, Oil Lubricated 

MOTOR: Design ....................Oil Filled

Insulation ...............Class B

SINGLE PHASE ...........................Permanent Split Capacitor (PSC)

 Includes Overload Protection in Motor

LEVEL CONTROL:

 SEV412 ...................None

 SEV412A.................Wide Angle, Mechanical, 20 ft (6m) cord

 Pipe Mounted

 SEV412VF ..............Vertical Float, PVC, Snap Action

 SEV412VFT ............Attached Vertical Float, PVC, Snap Action

 SEV412AT ..............Wide Angle, Mechanical, 20 ft (6m) cord

 Pump Mounted

Series: SEV

0.5 HP, 3450RPM, 60Hz

CSA 108 - File No. LR16567

UL 778

NRTL\C
 SECTION

 PAGE

 DATE

Submersible Non-Clog Pumps

A Crane Co. Company USA: (937) 778-8947 • Canada: (905) 457-6223 • International: (937) 615-3598

2

D

www.cranepumps.com

Professional Plumbing

Series SEV412

2" Spherical Solids Handling

Manual & Automatic

inches

(mm)

2/15

IMPORTANT !

1.) PUMP MAY BE OPERATED “DRY” FOR EXTENDED PERIODS WITHOUT DAMAGE TO MOTOR AND/OR SEALS. 

2.) INSTALLATIONS SUCH AS DECORATIVE FOUNTAINS OR WATER FEATURES PROVIDED FOR VISUAL ENJOYMENT MUST BE INSTALLED IN ACCORDANCE 

 WITH THE NATIONAL ELECTRIC CODE ANSI/NFPA 70 AND/OR THE AUTHORITY HAVING JURISDICTION. THIS PUMP IS NOT INTENDED FOR USE IN 

 SWIMMING POOLS, RECREATIONAL WATER PARKS, OR INSTALLATIONS IN WHICH HUMAN CONTACT WITH PUMPED MEDIA IS A COMMON OCCURRENCE.

MODEL NO PART NO HP VOLT/PH Hz RPM

(Nom)

NEMA

START

CODE

FULL

LOAD

AMPS

LOCKED

ROTOR

AMPS

CORD

LENGTH

CORD

SIZE

CORD

TYPE

SEV412 101292 0.5 115/1 60 3450 H 10.50 18.6 20 ft. (6m) 14/3 SJTOW

SEV412A 101293 0.5 115/1 60 3450 H 10.50 18.6 20 ft. (6m) 14/3 SJTOW

SEV412VF 101294 0.5 115/1 60 3450 H 10.50 18.6 20 ft. (6m) 14/3 SJTOW

SEV412AT 103544 0.5 115/1 60 3450 H 10.50 18.6 20 ft. (6m) 14/3 SJTOW

SEV412VFT 110404 0.5 115/1 60 3450 H 10.50 18.6 20 ft. (6m) 14/3 SJTOW

SEV412VF

SEV412A

SEV412 (Less Float)

SEV412AT (Attached to Motor Housing)

SEV412VFT