Meets LEAD-FREE(1)

requirements!

AAPPLICATIONS

FEATURES F

Tel: 910-735-0000 s Fax: 910-738-3848 s titan@titanfci.com s www.titanfci.com

YOUR PIPELINE TO THE FUTURE!

TITAN FLOW CONTROL, INC.

SIZE RANGE : 1/4" ~ 3"

"Y" (WYE) STRAINER f THREADED ENDS

ALUMINUM BRONZE f ANSI CLASS 250 f LEAD FREE (1)

PRESSURE/ TEMPERATURE RATING (2)

AB - ASTM B148 GR. 9D - CLASS 250

YS 52-AB (THREADED)

WOG (Non-shock): 400 PSI @ 150 °F

s astm b148 body material

aluminum bro nze is stro nger and less likely to c o rro de than other

bro nze all oys , making them a pre f erred ch o ice f o r sea water and other

applicati o ns w here c o rro si o n is a c o ncern. because o f its c o pper

c o ntent, marine o rganisms cann ot c o l o nize o n the material . 

additi o nally, titan' s ys 52-ab is used f o r p otable water applicati o ns as it

meets lead free statutes re q uiring that the lead c o ntent in the wetted

surfaces is 0.25% o r less as determined by a weighted average .

s lar g e strai n i n g capac ity

with its large b o dy and sizable straining element, the ys 52 provides

e x cellent o pen area rati o s that are typically two -and-a-hal f times

larger than the c o rresp o nding pipeline , minimizing pressure dro p 

acro ss the valve .

s prec isi o n mac h i n ed seats

precisi o n machined screen seats in b oth the b o dy and cap help to

ensure accurate p o siti o ning o f the screen during reassembly after

cleaning. als o , the machined b o dy seats enable f iner f iltrati o n by

preventing debris bypass .

s sel f-c lea n i n g capabi l ity

with a tapped npt bl ow- o f f c o nnecti o n, this unit can be f itted with a

bl ow-d own valve w hich facilitates cleaning o f the straining element. 

please c o ntact facto ry f o r m o re inf o rmati o n.

g e n eral ap p l i cat i o n : y- strainers are installed in a piping system to rem ove unwanted debris fro m the

pipeline , protecting e x pensive e q uipment d ownstream such as pumps , meters , spray n o zzles , c o mpress o rs , and

turbines . they can be placed in a h o riz o ntal o r vertical pipeline as l o ng as the screen is in a d ownward

p o siti o n. straining is acc o mplished via an internal perf o rated o r mesh lined straining element, the size o f

w hich sh o uld be determined based o n the size o f the smallest particle to be rem oved.

serv i c i n g : the straining element needs regular cleaning to prevent debris build up . it is n ot advisable to

all ow the di f f erential pressure to increase by 20 psi . alth o ugh cleaning n o rmally re q uires the rem oval o f the

straining element, installing and using a titan bl ow- o f f drain valve can increase the time between cleanings .

The above data represents common market and service applications. No representation or guarantee, expressed or implied, is given due to the numerous 

variations of concentrations, temperatures and flow conditions that may occur during actual service.

TECHNICAL T

MODELS: YS 52-AB 

 (aluminum bro nze )

YS52-0615

®

TITAN

TITAN FLOW CONTROL, INC.

21⁄2" YS 52-AB

1. The YS 52-AB meets requirements for lead free use in 

potable water systems. The lead content in 

the wetted surfaces is 0.25% or less as determined by 

a weighted average. For more information on lead 

free requirements, contact Titan Flow Control, Inc.

2. The above listed temperatures are theoretical and

may vary during actual operating conditions. 
TITAN FLOW CONTROL, Inc.

290 Corporate Drive E-mail: titan@titanfci.com

Lumberton, NC 28358 Web: www.titanfci.com

Tel: 910.735.0000 Fax: 910.738.3848

YS52-0615

®

TITAN

BILL OF MATERIALS (1)

No. PART YS 52 - AB

1 Body Aluminum Bronze

ASTM B148 Gr. 9D

2 Cap Aluminum Bronze

ASTM B148 Gr. 9D

3 Straining Element (2) Stainless Steel

4 Gasket (2) Teflon

5 NPT Plug (Blow-off) Stainless Steel(3)

1. Bill of Materials represents standard materials. Equivalent

or better materials may be substituted at the manufacturer's 

discretion. 

2. Denotes recommended spare parts.

3. NPT Plug also available in other materials.

PRESSURE - TEMPERATURE RATING

ANSI Class 250 ASTM B148 Gr. 9D

WOG (Non-shock): 400 PSI @ 150 °F

Titan FCI makes every effort to ensure the information presented on our literature accurately reflects exact product specifications. However, as product changes occur, there may be short-term differences between actual product 

specifications and the information contained within our literature. Titan FCI reserves the right to make design and specification changes to improve our products without prior notification. When required, request certified drawings.

"Y" (WYE) STRAINER 

YS 52-AB - (Threaded)

Threaded Ends • ANSI Class 250 • Aluminum Bronze

ANSI Class

250

STANDARD SCREEN SELECTIONS

Size Liquid Open Area Steam Open Area

1/4" ~ 2" 20 mesh 51.8% 30 mesh 44.8%

2 1/2" ~ 3" 1/16 (.0625) 41% 3/64 (.045) 36%

1

3

4

2

5

1.	 Dimensions and weights are for reference only. When required,request certified drawings.

2. Face to face values have a tolerance of ±0.06 in (±2.0 mm).

DIMENSIONS AND PERFORMANCE DATA (1)

SIZE

in 1/4 3/8 1/2 3/4 1 1 1/4 1 1/2 2 2 1/2 3

mm 8 10 15 20 25 32 40 50 65 80

A DIMENSION FACE TO FACE (2)

in 2.75 2.75 2.75 3.00 3.75 4.43 5.00 5.68 9.00 9.00

mm 70 70 70 76 95 113 127 144 229 229

B DIMENSION CENTER LINE TO BOTTOM

in 2.18 2.18 2.18 2.34 2.91 3.5 3.78 4.39 6.44 6.44

mm 55 55 55 59 74 89 96 112 164 164

C DIMENSION SCREEN REMOVAL

in 4.00 4.00 4.00 4.25 4.75 5.25 6.00 7.00 10.00 10.00

mm 102 102 102 108 121 133 152 178 254 254

D NPT Plug BLOW-OFF

in 1/4 1/4 1/4 1/4 3/8 3/4 3/4 1 1 1/4 1 1/4

mm 8 8 8 8 10 20 20 25 32 32

APPROXIMATE 

ASSEMBLED WEIGHT

lb 0.5 0.5 0.5 1.0 1.8 2.5 4.0 5.6 15.9 15.9

kg 0.2 0.2 0.2 0.5 0.8 1.1 1.8 2.5 7.2 7.2

Flow Coefficient Cv 0.7 2 8 15 22 38 42 70 110 160

PRESSURE - TEMPERATURE RATINGS

-50 0 50 100 150 200 250 300 350 400 450

200

250

300

350

400

450

Pressure (PSI)

Temperature (°F)

SOURCE: ASME/ANSI B16.24

Aluminum Bronze

ASTM B148 Gr. 9D 

ANSI 250

Illustrations are representative of YS 52-AB (Threaded-end 

connections). Please ask for certified drawings when required.

REFERENCED STANDARDS & CODES

CODE DESCRIPTION

ASME/ANSI B16.15 Cast Bronze Threaded Fittings

ASME/ANSI B16.24 Cast Copper Alloy Pipe Flanges and Flanged Fittings

Body Material Application Notes:

•	 Aluminum Bronze (ASTM B148) is a preferred material for 		

lead-free wye strainers, meeting requirements for potable 

water systems by containing 0.25% lead or less by average 

weight on all wetted parts. 

•	 Aluminum Bronze is strong and corrosion resistant, meeting

the needs of many various applications, such as seawater and 

marine.

A

B

C

D

Exploded View

Front View
AAPPLICATIONS

FEATURES F

Tel: 910-735-0000 s Fax: 910-738-3848 s titan@titanfci.com s www.titanfci.com

290 Corporate Drive s PO Box 7408 s Lumberton, NC 28358

YOUR PIPELINE TO THE FUTURE!

TITAN FLOW CONTROL, INC.

"Y" (WYE) STRAINER f FLANGED ENDS, FLAT FACED

ALUMINUM BRONZE f ANSI CLASS 150 f LEAD FREE (1)

PRESSURE/ TEMPERATURE RATING (2)

AB - ASTM B148 GR. 9D - CLASS 150

YS 54-AB (FLANGED)

WOG (Non-shock): 225 PSI @ 150 °F

s ast m b148 body mater ial

aluminum bro nze is stro nger and less likely to c o rro de than other bro nze

all oys , making them a pre f erred ch o ice f o r sea water and other 

applicati o ns w here c o rro si o n is a c o ncern. because o f its c o pper c o ntent, 

marine o rganisms cann ot c o l o nize o n the material . additi o nally, titan' s

ys 54-ab is used f o r p otable water applicati o ns as it meets lead free statutes

re q uiring that the lead c o ntent in the wetted surfaces is 0.25% o r less as

determined by a weighted average .

s new desi gn w i t h gau ge taps

titan' s ys 54 has c o nvenient gauge taps f urnished with a plug o n b oth the

inlet and o utlet sides o f sizes 2" thro ugh 12". these taps all ow f o r easy

installati o n o f pressure gauges to m o nito r di f f erential pressure and 

determine w hen screen cleaning is necessary.

s lar ge st rai n i ng capac i ty

with its large b o dy and sizable straining element, the ys 54 provides 

e x cellent o pen area rati o s that are typically two -and-a-hal f times larger

than the c o rresp o nding pipeline , minimizing pressure dro p acro ss the valve .

s p rec isi on mac h i ned seats

precisi o n machined screen seats in b oth the b o dy and c over help to ensure

accurate p o siti o ning o f the screen during reassembly after cleaning. als o , 

the machined b o dy seats enable f iner f iltrati o n by preventing debris bypass .

s self-clean i ng capabili ty

with a tapped npt bl ow- o f f c o nnecti o n, this unit can be f itted with a

bl ow-d own valve w hich facilitates cleaning o f the straining element. please

c o ntact facto ry f o r m o re inf o rmati o n.

general ap pli cat i on : y- strainers are installed in a piping system to rem ove unwanted debris fro m the

pipeline , protecting e x pensive e q uipment d ownstream such as pumps , meters , spray n o z zles , c o mpress o rs , and

turbines . they can be placed in a h o riz o ntal o r vertical pipeline as l o ng as the screen is in a d ownward

p o siti o n. straining is acc o mplished via an internal perf o rated o r mesh lined straining element, the size o f

w hich sh o uld be determined based o n the size o f the smallest particle to be rem oved.

serv i c i ng : the straining element needs regular cleaning to prevent debris build up . it is n ot advisable to

all ow the di f f erential pressure to increase by 20 psi . alth o ugh cleaning n o rmally re q uires the rem oval o f the

straining element, installing and using a titan bl ow- o f f drain valve can increase the time between cleanings .

The above data represents common market and service applications. No representation or guarantee, expressed or implied, is given due to the numerous 

variations of concentrations, temperatures and flow conditions that may occur during actual service.

TECHNICAL T

MODELS: YS 54-AB 

 (aluminum bro nze )

YS54-0615

®

TITAN

TITAN FLOW CONTROL, INC.

1. The YS 54-AB meets requirements for lead free use in 

potable water systems. The lead content in 

the wetted surfaces is 0.25% or less as determined by 

a weighted average. For more information on lead 

free requirements, contact Titan Flow Control, Inc.

2. The above listed temperatures are theoretical and

may vary during actual operating conditions. 

Meets LEAD-FREE(1)

requirements!

New design includes 

gauge taps as standard 

on YS54-AB models

SIZE RANGE : 2" ~ 12"
TITAN FLOW CONTROL, Inc.

290 Corporate Drive E-mail: titan@titanfci.com

Lumberton, NC 28358 Web: www.titanfci.com

Tel: 910.735.0000 Fax: 910.738.3848

YS54-0615

®

TITAN

BILL OF MATERIALS (1)

No. PART YS 54-AB

1 Body Aluminum Bronze

ASTM B148 Gr. 9D

2 Cover Aluminum Bronze

ASTM B148 Gr. 9D

3 Straining Element (2) Stainless Steel

4 Gasket (2) Teflon

5 Cap Screw Stainless Steel or 

Silicon Bronze

6 NPT Plug (Blow-off) Aluminum Bronze

ASTM B148 Gr. 9D

7 NPT Plug (Gauge Taps) Stainless Steel(3)

1. Bill of Materials represents standard materials. Equivalent or better 

materials may be substituted at the manufacturer's discretion. 

2. Denotes recommended spare parts.

3. NPT Plug also available in other materials.

Titan FCI makes every effort to ensure the information presented on our literature accurately reflects exact product specifications. However, as product changes occur, there may be short-term differences between actual product 

specifications and the information contained within our literature. Titan FCI reserves the right to make design and specification changes to improve our products without prior notification. When required, request certified drawings.

"Y" (WYE) STRAINER 

YS 54-AB - (Flanged)

Flanged (Flat Faced) • ANSI Class 150 • Aluminum Bronze

ANSI Class

150

1.	 Dimensions and weights are for reference only. When required,request certified drawings.

2. Face to face dimension includes raised face. These values have a tolerance of ±0.06 in (±2.0 mm) for sizes 10" and lower and a tolerance of ±0.12 in (±3.0 mm) for sizes 12" and larger.

DIMENSIONS AND PERFORMANCE DATA (1)

SIZE

in 2 2 1/2 3 4 5 6 8 10 12

mm 50 65 80 100 125 150 200 250 300

A DIMENSION FACE TO FACE (2)

in 7.75 9.75 10.06 12.12 C/F 18.30 21.37 26.00 C/F

mm 197 248 256 308 C/F 465 543 660 C/F

B DIMENSION

CENTER LINE TO BOTTOM

in 5.25 6.50 7.00 8.25 C/F 13.50 15.50 18.50 C/F

mm 133 165 178 210 C/F 343 394 470 C/F

C DIMENSION SCREEN REMOVAL

in 7.00 9.75 10.00 12.00 C/F 20.00 22.75 28.00 C/F

mm 178 248 254 305 C/F 508 578 712 C/F

D NPT Plug BLOW-OFF

in 1/2 1 1 1 1/2 C/F 2 2 2 C/F

mm 15 25 25 40 C/F 50 50 50 C/F

E NPT Plug

GAUGE TAPS

in 1/4 1/4 1/4 1/4 C/F 1/4 1/4 1/4 C/F

mm 8 8 8 8 C/F 8 8 8 C/F

APPROXIMATE 

ASSEMBLED WEIGHT

lb 22.0 34.0 38.0 64.0 C/F 132.0 240.0 C/F C/F

kg 10.0 15.4 17.2 29.0 C/F 59.9 108.9 C/F C/F

Flow Coefficient Cv 70 110 160 260 C/F 570 950 1600 C/F

PRESSURE - TEMPERATURE RATINGS

Temperature °F

Pressure (PSI)

-50 0 50 100 150 200 250 300 350 400 450

140

160

180

200

220

240

Aluminum Bronze

ASTM B148 Gr. 9D 

SOURCE: ASME/ANSI B16.24 ANSI 150

PRESSURE - TEMPERATURE RATING

ANSI Class 150 ASTM B148 Gr. 9D

WOG (Non-shock): 225 PSI @ 150 °F

STANDARD SCREEN SELECTIONS

Size Liquid Open Area Steam Open Area

2" ~ 4" 1/16 (.0625) 41% 1/32 (.033) 28%

5" ~ 8" 1/8 (.125) 40% 3/64 (.045) 36%

10" ~ 12" 1/8 (.125) 40% 30 Mesh Lined 44.8%

REFERENCED STANDARDS & CODES

CODE DESCRIPTION

ASME/ANSI B16.24 Cast Copper Alloy Pipe Flanges and Flanged Fittings

Body Material Application Notes:

•	 Aluminum Bronze (ASTM B148) is a preferred material for lead-free wye 

strainers, meeting requirements for potable water systems by containing 

0.25% lead or less by average weight on all wetted parts. 

•	 Aluminum Bronze is strong and corrosion resistant, meeting the needs of 

many various applications, such as seawater and marine.

1

4

2

7

5

6

3

A

B

C

E

D

Front View

Exploded View

Illustrations are representative of YS 54-AB (Flanged Ends, 

Flat Faced). Please ask for certified drawings when required.
Tel: 910-735-0000 s Fax: 910-738-3848 s titan@titanfci.com s www.titanfci.com

290 Corporate Drive s PO Box 7408 s Lumberton, NC 28358

YOUR PIPELINE TO THE FUTURE!

TITAN FLOW CONTROL, INC.

"Y" (WYE) STRAINER f ANSI CLASS 125 

CAST BRONZE f THREADED AND SOLDER ENDS

YS5556-0315

®

TITAN

TITAN FLOW CONTROL, INC.

AAPPLICATIONS

FEATURES F

SIZE RANGE : 1/4" ~ 3"

PRESSURE/ TEMPERATURE RATING (1)

BZ - C84400 - ASTM B584 - CLASS 125

YS 55-BZ (THREADED)

WOG (Non-shock): 200 PSI @ 150 °F

PRESSURE/ TEMPERATURE RATING (1)

BZ - C84400 - ASTM B584 - CLASS 125

YS 56-BZ (SOLDER) (2)

WOG (Non-shock): 

400 PSI @ 100 °F (1/4" - 1 1/2")

315 PSI @ 100 °F (2" - 3")

1. The above listed temperatures are theoretical and may vary 

during actual operating conditions.

2. The internal working pressure rating for a solder joint strainer 

is dependent, not only on the strainer, but also on the 

composition of the solder used for the joint. The working 

pressure ratings shown for model YS 56-BZ (Solder) are 

representative of using an alloy Sb5 95-5 tin-antimony solder. 

For other solder joints, please consult factory.

s lar g e strai n i n g capac ity

with its large b o dy and sizable straining element, the ys 55 and ys 56

provide e x cellent o pen area rati o s that are typically two -and-a-hal f

times larger than the c o rresp o nding pipeline , minimizing pressure dro p

acro ss the valve .

s prec ision mac h i n ed seats

precisi o n machined screen seats in b oth the b o dy and cap help to

ensure accurate p o siti o ning o f the screen during reassembly after

cleaning. als o , the machined b o dy seats enable f iner f iltrati o n by

preventing debris bypass .

s self-clea n i n g capability

with a tapped npt bl ow- o f f c o nnecti o n, this unit can be f itted with a

bl ow-d own valve w hich facilitates cleaning o f the straining element. 

please c o ntact facto ry f o r m o re inf o rmati o n.

s threaded cap

titan' s ys 55 and ys 56 have straight threads to permit easy cap rem oval

f o r cleaning and pro per alignment w hen reassembling strainer.

g e n eral ap pli cat ion : y- strainers are installed in a piping system to rem ove unwanted debris fro m the

pipeline , protecting e x pensive e q uipment d ownstream such as pumps , meters , spray n o zzles , c o mpress o rs , and

turbines . they can be placed in a h o riz o ntal o r vertical pipeline as l o ng as the screen is in a d ownward

p o siti o n. straining is acc o mplished via an internal perf o rated o r mesh lined straining element, the size o f

w hich sh o uld be determined based o n the size o f the smallest particle to be rem oved.

serv i c i n g : the straining element needs regular cleaning to prevent debris build up . it is n ot advisable to

all ow the di f f erential pressure to increase by 20 psi . alth o ugh cleaning n o rmally re q uires the rem oval o f the

straining element, installing and using a titan bl ow- o f f drain valve can increase the time between cleanings .

The above data represents common market and service applications. No representation or guarantee, expressed or implied, is given due to the numerous 

variations of concentrations, temperatures and flow conditions that may occur during actual service.

TECHNICAL T

MODELS: YS 55-BZ 

 (threaded ends - bro nze )

YS 56-BZ 

 ( s o lder ends - bro nze )

1" YS 56-BZ

1" YS 55-BZ
TITAN FLOW CONTROL, Inc.

290 Corporate Drive E-mail: titan@titanfci.com

Lumberton, NC 28358 Web: www.titanfci.com

Tel: 910.735.0000 Fax: 910.738.3848

YS5556-0315

®

TITAN

BILL OF MATERIALS (1)

No. PART YS 55/56 - BZ

1 Body Bronze (C84400)

ASTM B584

2 Cap Bronze (C84400)

ASTM B584

3 Straining Element (2) Stainless Steel

4 Gasket (2) Teflon

5 NPT Plug (Blow-off) Bronze (C84400)

ASTM B584

1. Bill of Materials represents standard materials. Equivalent or better 

materials may be substituted at the manufacturer's discretion. 

2. Denotes recommended spare parts.

Titan FCI makes every effort to ensure the information presented on our literature accurately reflects exact product specifications. However, as product changes occur, there may be short-term differences between actual product 

specifications and the information contained within our literature. Titan FCI reserves the right to make design and specification changes to improve our products without prior notification. When required, request certified drawings.

"Y" (WYE) STRAINER 

YS 55-BZ - (Threaded)

YS 56-BZ - (Solder)

Threaded or Solder Ends • ANSI Class 125 • Bronze

ANSI Class

125

STANDARD SCREEN SELECTIONS

Size Liquid Open Area Steam Open Area

1/4" ~ 2" 20 mesh 51.8% 30 mesh 44.8%

2 1/2" ~ 3" 1/16 (.0625) 41% 3/64 (.045) 36%

1

2

4

3

5

1.	 Dimensions and weights are for reference only. When required,request certified drawings.

2. Face to face values have a tolerance of ±0.06 in (±2.0 mm).

DIMENSIONS AND PERFORMANCE DATA (1)

SIZE

in 1/4 3/8 1/2 3/4 1 1 1/4 1 1/2 2 2 1/2 3

mm 8 10 15 20 25 32 40 50 65 80

A DIMENSION

FACE TO FACE (YS 55) (2)

in C/F 2.38 2.80 3.18 3.70 4.41 4.93 5.91 C/F 10.60

mm C/F 61 71 81 94 112 125 150 C/F 269

A DIMENSION

FACE TO FACE (YS 56) (2)

in C/F C/F 2.75 3.36 3.80 4.58 5.33 6.11 C/F 11.40

mm C/F C/F 70 86 97 116 136 155 C/F 290

B DIMENSION

CENTER LINE TO BOTTOM (YS 55)

in C/F 1.39 1.60 1.86 2.13 2.50 2.92 3.60 C/F 5.50

mm C/F 36 41 48 54 64 74 92 C/F 140

B DIMENSION

CENTER LINE TO BOTTOM (YS 56)

in C/F C/F 1.60 1.86 2.13 2.50 2.92 3.60 C/F 7.0

mm C/F C/F 41 48 54 64 74 92 C/F 140

C DIMENSION SCREEN REMOVAL

in C/F 3.75 4.0 4.25 4.75 6.0 7.0 8.0 C/F 10.0

mm C/F 95 102 108 121 152 178 203 C/F 254

D NPT Plug BLOW-OFF

in C/F 1/4" 1/4" 1/4" 1/2" 1/2" 3/4" 1" C/F 1"

mm C/F 8 8 8 15 15 20 25 C/F 25

ASSEMBLED WEIGHT

YS 55- THREADED (APPROXIMATE)

lb C/F 0.35 0.45 0.85 1.30 2.00 2.65 4.30 C/F 12.90

kg C/F 0.16 0.21 0.39 0.6 0.91 1.21 1.95 C/F 5.85

ASSEMBLED WEIGHT

YS 56 - SOLDER (APPROXIMATE)

lb C/F C/F 0.35 0.55 0.85 1.60 1.65 2.80 C/F 16.20

kg C/F C/F 0.16 0.25 0.39 0.73 0.75 1.27 C/F 7.35

Flow Coefficient Cv 0.7 2 8 15 22 38 42 70 110 160

PRESSURE - TEMPERATURE RATINGS (1)

0

50

100

150

200

250

-20 100 200 300 400

Pressure (PSI)

Temperature (°F)

SOURCE: ASME/ANSI B16.15

Bronze (C84400) - ASTM B584 

ANSI 125

Threaded Ends - YS 55

1. The pressure-temperature ratings given are ONLY for the YS 55-BZ (Threaded) per ASME B16.15. 

The internal working pressure rating for a solder joint strainer is dependent, not only on the 

strainer, but also on the composition of the solder used for the joint. The working pressure 

ratings shown for model YS 56-BZ (Solder) are representative of using an alloy Sb5 95-5 

tin-antimony solder. For other solder joints, please consult factory.

A

B

C

D

Illustrations are representative of YS 55-BZ (Threaded-end 

connections) only. Materials, as listed to the left, and Dimensions 

and Performance Data, as listed below, include both the YS 55-

BZ and the YS 56-BZ (Solder-end connections). Please ask for 

certified drawings when required.

1.5" YS 55-BZ

Threaded Ends

REFERENCED STANDARDS & CODES

CODE DESCRIPTION

ASME/ANSI B16.15 Cast Bronze Threaded Fittings

ASME/ANSI B16.18 Cast Copper Alloy Solder Joint Pressure Fittings

ASME/ANSI B16.50 Copper Alloy Braze-Joint Pressure Fittings

PRESSURE - TEMPERATURE RATING - YS 55-BZ (Threaded)

(1/4" - 3")

WOG (Non-shock): 200 PSI @ 150 °F

PRESSURE - TEMPERATURE RATING - YS 56-BZ (Solder) (1)

(1/4" - 1 1/2") (2" - 3")

WOG (Non-shock): 400 PSI @ 100 °F 315 PSI @ 100 °F