Organization Name:

Note: Representatives submitting on behalf of an organization must enter information below.

Requestor Representative:

Section 301 Investigation: China's Acts, Policies, and Practices Related to Technology 

Transfer, Intellectual Property, and Innovation - Form to Request Exclusion of Product

When submitting a product exclusion request using this form, enter the specified 

information in the following fields and explain the basis and rationale for your statements. 

By completing this form, you certify that the information provided is complete and 

correct to the best of your knowledge. 

1. Indicate whether the comment contains business confidential information (BCI), is a public

document, or is a public version of a BCI document.

3.

2. Please provide a complete and detailed description of the product of concern:

4.

5. Requestor's relationship to the product:

CONTINUED BELOW

*

10-digit HTSUS item number* for product you wish to address in this product exclusion request:

Use numerical characters only with no special characters (example: 1023456789). For help in finding 

the HTSUS item number associated with your product, see https://hts.usitc.gov/

1

7.

6. Does this submission in regulations.gov include additional attachments?

Please indicate whether any additional attachment contains business confidential

information (BCI), is a public document, or is a public version of a BCI document.

VERSION 1

Requestor Information

Requestor Name (Last, First):
END 2

8. Is this product, or a comparable product, available from sources in the United States?:

VERSION 1

11. Please provide information in support your request, taking account of the instructions

provided in Section B of the Federal Register notice (note: text entered below can extend

beyond the apparent size of this box).

9. Is this product, or a comparable product, available from sources in third countries?:

10. Please provide the value and quantity (with units) of the Chinese-origin product of concern

that you purchased for each calendar year specified. Limit this figure to the products

purchased by your firm (or by members of your trade association) alone. Please provide 

estimates if precise figures are unavailable.

2016 Value:

2015 Value:

2017 Value:

2016 Quantity:

2015 Quantity:

2017 Quantity:
3 Pole Contactor 50–120 FLA

HCD Series

3 pole contactors are typically used in commercial applications. 

These contactors utilize three wires to control electrical current 

direction. Our engineers and quality specialists provide services 

that meet or exceed customer requirements—all products 

undergo in-house testing and validation. We carry extensive 

domestic inventory to meet delivery schedules.

Features

• 3 Pole NO

• Silver Cadmium Oxide Contacts

• UL 508 File No. E227250

• CSA File No. 221260 (1456104)

• Multiple mounting and termination 

options available, contact us for 

more information.

CONTACTORS

Initial Dielectric Strength

Between Contacts & Coils: 2,200 VAC

Between Poles: 2,200 VAC

Between Open Contacts: 2,200 VAC

Arc Cover

Standard

Insulation System

130°C Class B

Temperature Range

-40°C to +65°C

-40°F to +150°F

Unit Weight

50–60 FLA 32 oz

75–120 FLA 64 oz

Power Pole Terminations

Aluminum box lug

Wire Size

50–60 FLA Box Lug 14-2

75–90 FLA Box Lug 14-1

Recommended Tightening Torque

Box lug: 50 in. lbs

Quick Connects

Coil terminals:

Dual: .250′′ QC or #6–32 screw/.250′′ QC

Power terminals:

Dual .250′′ QC

We can custom engineer a solution 

to meet any need. Just ask.

815.626.5170 | HartlandControls.com

Specifications

Dimensions (inches [mm])

50–60 FLA 75–120 FLA

2.56

[65.0]

2.11

[53.5]

1.54

[39.0]

3.19

[81.0]

3.64

[92.5]

.05

[1.3]

.24

[6.0]

3.386

[86.0]

2.874

[73.0]

2.50

[63.5]

5.118

[130.0]

4.437

[112.7]

4.626

[117.5]

.064

[1.62]

5.199

[132.06]

.394

[10.0]

4.12

[104.6]

3.72

[94.5]

3.27

[83.0]
CONTACTORS

Line Voltage

Full Load Amps

Resistive Amps 

@ 600 VAC

Locked Rotor Amps 

@ 240/277 VAC

Locked Rotor Amps 

@ 480 VAC

Locked Rotor Amps 

@ 600 VAC

3 Pole Contactors

50 65 300 250 200

60 75 360 300 240

75 90 450 375 300

90 120 540 450 360

120 150 720 600 480

Horsepower Rating

Full Load 

Amps

120 V 240 V 480 V 600 V

Single Phase Three Phase Single Phase Three Phase Single Phase Three Phase Single Phase Three Phase

3 Pole Contactors

50 3 – 10 15 – 30 – 30

60 5 – 10 25 – 30 – 30

75 5 – 15 25 – 40 – 40

90 7.5 – 20 30 – 50 – 50

120 7.5 – 20 30 – 50 – 50

Standard Fault Short Circuit Rating

Suitable for use on a circuit capable of delivering not more than 5k rms symmetrical amperes, 

600 Volts maximum at 400% of fuse and circuit breaker.

High Fault Short Circuit Rating

Suitable for use on a circuit capable of delivering not more than 100k rms symmetrical amperes as shown.

Maximum Circuit Breaker Maximum J Fuse

480 Volts Maximum Minimum Enclosure Volume 600 Volts Maximum Minimum Enclosure Volume

05 150 A 256 cu. in. 200 A 256 cu. in.

06 150 A 256 cu. in. 200 A 256 cu. in.

07 225 A 1008 cu. in. 200 A 1008 cu. in.

09 225 A 1008 cu. in. 200 A 1008 cu. in.

12 225 A 1008 cu. in. 200 A 1008 cu. in.

Note: for a circuit capable of delivering more than 5k rms symmetrical amperes, the equipment enclosure must have a minimum of four 

fastening points or a piano hinge and two fastening points.

3 Pole Contactor 50–120 FLA

HCD Series

©2017 Hartland Controls | Printed in USA | All rights reserved | PS0100610171000

Multiple mounting and termination options available, contact us for more information.