|                                                                          | 开利空调销售服务(上海)有限公司 |
|-------------------------------------------------------------------------------|--------------------------------------------------------------------------------------------------------------------|
| Carrier Air Conditioning Sales & Services  (Shanghai) Co., Ltd. |
|                                                                          |

| 型号Type                                                                                      | 30HXC                                                                       | 130B                   |
|-----------------------------------------------------------------------------------------------------------|-----------------------------------------------------------------------------|------------------------|
| 名义制冷量Nominal Refrigerating Capacity                                    | KW                                                                          | 455                    |
| 输入功率Input Power                                                               | KW                                                                          | 98                     |
| 蒸发器Evaporator                                                                        | 进、出水温度In/Out Water Temperature    | oC                | 12/7 |
| 流量Flow Rate                                                                                 | m3/h                                                                        | 78                     |
| 水压降Water Pressure Drop                                                               | kPa                                                                         | 45                     |
| 进出口径In/Out Diameter                                                           | Dg                                                                          | 125                    |
| 冷凝器Condensor                                                                         | 进、出水温度In/Out Water Temperature    | oC                | 30/35 |
| 流量Flow Rate                                                                                 | m3/h                                                                        | 95                     |
| 水压降Water Pressure Drop                                                               | kPa                                                                         | 83                     |
| 进出口径In/Out Diameter                                                           | Dg                                                                          | 125                    |
| 冷量调节档数Cold Amount Regulation Number                             |                                                                        | 6                      |
| 最小冷量Minimum Cold Amount                                                       | %                                                                           | 19                     |
| 压缩机Compressor                                                                        | 回路ALoop A                                                     | 数量Number | 2 |
| 回路BLoop B                                                                                   | 数量Number                                                      |                   |
|                                                                                                      | 电源Power Supply                                                | V-Ph-Hz                | 380-3-50 |
| 电                                                                                                  | 额定工况电流Rated Current for Operation | A                      | 172 |
| 机                                                                                                  | 最大启动电流Max Current for Start-up    | A                      | 314 |
| Motor                                                                                                     | (星-三角)(Star-Triangle)                    |
| HFC-134a                                                                                                  | 回路ALoop A                                                     | Kg                     | 90 |
| 充注量Filling Amount                                                                    | 回路BLoop B                                                     | Kg                     |   |
| 外形尺寸Outline Dimension                                                         | 长Length                                                              | mm                     | 2988 |
| 宽Width                                                                                             | mm                                                                          | 980                    |
| 高Hight                                                                                             | mm                                                                          | 1816                   |
| 机组重量(含冷媒)Unit Weight (Include Refrigerant) | Kg                                                                          | 2446                   |
| 运行重量(Operational Weight)                                                      | Kg                                                                          | 2589                   |

| 注:1、以上技术规格基于蒸发器及冷凝器水侧污垢系数0.086Note: 1.The above-mentioned specification is based on dirt coeffcient of evaporator and condensor on water side, which is 0.086. |
|----------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|
| 2、机组水侧标准设计压力为1.0MPa2. Standard design pressure of unit on water side is 1.0Mpa.                                                                                                                                                                    |

----

|                                                                          | 开利空调销售服务(上海)有限公司 |
|-------------------------------------------------------------------------------|--------------------------------------------------------------------------------------------------------------------|
| Carrier Air Conditioning Sales & Services  (Shanghai) Co., Ltd. |
|                                                                          |

| 型号Type                                                                                      | 30HXC                                                                       | 250B             |
|-----------------------------------------------------------------------------------------------------------|-----------------------------------------------------------------------------|------------------|
| 名义制冷量Nominal Refrigerating Capacity                                    | KW                                                                          | 875              |
| 输入功率Input Power                                                               | KW                                                                          | 186              |
| 蒸发器Evaporator                                                                        | 进、出水温度In/Out Water Temperature    | oC          | 12/7 |
| 流量Flow Rate                                                                                 | m3/h                                                                        | 150              |
| 水压降Water Pressure Drop                                                               | kPa                                                                         | 66               |
| 进出口径In/Out Diameter                                                           | Dg                                                                          | 150              |
| 冷凝器Condensor                                                                         | 进、出水温度In/Out Water Temperature    | oC          | 30/35 |
| 流量Flow Rate                                                                                 | m3/h                                                                        | 182              |
| 水压降Water Pressure Drop                                                               | kPa                                                                         | 68               |
| 进出口径In/Out Diameter                                                           | Dg                                                                          | 200              |
| 冷量调节档数Cold Amount Regulation Number                             |                                                                        | 8                |
| 最小冷量Min Cold Amount                                                           | %                                                                           | 14               |
| 压缩机Compressor                                                                        | 回路ALoop A                                                     | 数量 | 2 |
| 回路BLoop B                                                                                   | 数量                                                            | 1                |
|                                                                                                      | 电源Power Supply                                                | V-Ph-Hz          | 380-3-50 |
| 电                                                                                                  | 额定工况电流Rated Current for Operation | A                | 218/108 |
| 机                                                                                                  | 最大启动电流Max Current for Start-up    | A                | 443/288 |
| Motor                                                                                                     | (星-三角)(Star-Triangle)                    |
| HFC-134a                                                                                                  | 回路ALoop A                                                     | Kg               | 107 |
| 充注量Filling Amount                                                                    | 回路BLoop B                                                     | Kg               | 75 |
| 外形尺寸Outline Dimensions                                                        | 长Length                                                              | mm               | 3512 |
| 宽Width                                                                                             | mm                                                                          | 1015             |
| 高Hight                                                                                             | mm                                                                          | 2060             |
| 机组重量(含冷媒)Nuit Weight (Include Refrigerant) | Kg                                                                          | 4258             |
| 运行重量Operation Weight                                                          | Kg                                                                          | 4618             |

| 注:1、以上技术规格基于蒸发器及冷凝器水侧污垢系数0.086Note: 1.The above-mentioned specification is based on dirt coeffcient of evaporator and condensor on water side, which is 0.086. |
|----------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|
| 2、机组水侧标准设计压力为1.0MPa2.Standard design pressure of unit on water side is 1.0Mpa.                                                                                                                                                                     |

----