| Description                 | Value                         |  |
|-----------------------------|-------------------------------|--|
| Product Name:               | NBG 125-80-160/161 A-F-A BAQE |
| Product No:                 | 95105153                      |
| EAN No:                     | 5700836546530                 |
|                        |                          |
| Technology:                 |                          |
| Pump speed data             | 2940 rpm                      |
| Real calculated flow rate   | 147 m3/H                      |
| pump lift                   | 29.2 m                        |
| Real blade diameter         | 161mm                         |
| Shaft seal                  | BAQE                          |
| Shaft diameter              | 32mm                          |
| Curve tolerance             | ISO 9906 Annex A              |
| Edition of pump             | A                             |
|                        |                          |
| Material                    |                          |
| pump body                   | cast iron                     |
|                        | EN-GJL-250 DIN W. – Nr. |
|                        | A48-40 B ASTM                 |
| blade                       | Cast iron                     |
|                        | EN-GJL-250 DIN W. – Nr. |
|                        | A48-40 B ASTM                 |
| Material Code               | A                             |
|                        |                          |
| Install                     |                          |
| Max Environment temperature | 40°C                     |
| Max Operation Pressure      | 16                            |
| Flange Standard             | EN1092-2                      |
| Connection Code             | F                             |
| Pump inlet                  | DN 125                        |
| Pump outlet                 | DN 80                         |
| Pressure Level              | PN 16                         |
| occipital ring              | occipital ring                |
|                        |                          |
| Liquid                      |                          |
| Temperature of Liquid       | 0...120°C            |

----

| Electric Data:                    |                        |
|-----------------------------------|-----------------------------|
| Motor type                        | MMG160L                     |
| Number of Motor Poles             | 2                           |
| Rated Power – P2            | 18.5kw                      |
| Frequency of Power                | 50Hz                        |
| Rated voltage                     | 3 x 380-415 D / 660-690 Y V |
| Rated current                     | 33 / 19.2A                  |
| Start-up current                  | 720%                        |
| Cos phi-power factor              | 0, 90                       |
| Rated speed                       | 2940 rpm                    |
| efficiency of mortar in Full load | 90,0%                       |
| efficiency of mortar in 3/4 load  | 90,8%                       |
| efficiency of mortar in 1/2 load  | 90,1%                       |
| Encapsulation grade (IEC 34-5)    | IP55                        |
| Insulation grade (IEC 85)         | F                           |
| Motor protection                  | PTC                         |
| Motor No                          | 83315428                    |
| Motor series                      | Domestic                    |
|                              |                        |
| Other                             |                        |
| Net Weight                        | 215kg                       |
| Gross Weight                      | 228kg                       |
| Transport volume                  | 0.725m3                     |

----