| Owner Name: Shenyang Sunshine                 | P554      |
|-----------------------------------------------|-----------|
|                                          |      |
| Project Name: Clean-room Installation Project | 2009-2-10 |

| Serial | Description                    | Specification  | Circuit Cap. | Qty.   | Circuit No. | Brand        |
|--------|--------------------------------|----------------|--------------|--------|-------------|--------------|
|   | Lighting Distribution Box      |           | Ampere(A)    |   |        |         |
| 1      | 11MX(1st Floor)  | XSAII-18       |         |   |        | High Quality |
|   | Circuit Breaker                | C65H-63/C20/3P | 20           | 1      | D-11MX      | Schneider    |
|   | Circuit Breaker                | C65H-63/C10/1P | 10           | 8      | MX11-1~8    | Schneider    |
|   | Circuit Breaker                | C65H-63/C16/1P | 16           | 2      | MX11-9~10   | Schneider    |
| 2      | 12MX(1st Floor)  | XSAII-24       |         |   |        | High Quality |
|   | Circuit Breaker                | C65H-63/C20/3P | 20           | 1      | D-12MX      | Schneider    |
|   | Circuit Breaker                | C65H-63/C10/1P | 10           | 12     | MX12-1~12   | Schneider    |
|   | Circuit Breaker                | C65H-63/C16/1P | 16           | 2      | MX12-13~14  | Schneider    |
| 3      | 13MX(1st Floor)  | XSAII-24       |         |   |        | High Quality |
|   | Circuit Breaker                | C65H-63/C32/3P | 32           | 1      | D-13MX      | Schneider    |
|   | Circuit Breaker                | C65H-63/C10/1P | 10           | 15     | MX13-1~15   | Schneider    |
|   | Circuit Breaker                | C65H-63/C16/1P | 16           | 2      | MX13-16~17  | Schneider    |
| 4      | 14MX(1st Floor)  | XSAII-24       |         |   |        | High Quality |
|   | Circuit Breaker                | C65H-63/C32/3P | 32           | 1      | D-14MX      | Schneider    |
|   | Circuit Breaker                | C65H-63/C10/1P | 10           | 15     | MX14-1~15   | Schneider    |
|   | Circuit Breaker                | C65H-63/C16/1P | 16           | 2      | MX14-16~17  | Schneider    |
| 5      | 15MX(1st Floor)  | XSAII-18       |         |   |        | High Quality |
|   | Circuit Breaker                | C65H-63/C20/3P | 20           | 1      | D-15MX      | Schneider    |
|   | Circuit Breaker                | C65H-63/C10/1P | 10           | 8      | MX15-1~8    | Schneider    |
|   | Circuit Breaker                | C65H-63/C16/1P | 16           | 2      | MX15-9~10   | Schneider    |
| 6      | 16MX(Half Floor) | XSAII-24       |         |   |        | High Quality |
|   | Circuit Breaker                | C65H-63/C20/3P | 20           | 1      | D-16MX      | Schneider    |
|   | Circuit Breaker                | C65H-63/C10/1P | 10           | 14     | MX16-1~14   | Schneider    |

| SUNTEC | Page 1 of 8 |    |
|--------|-------------|--------------|

----

| Owner Name: Shenyang Sunshine                 | P554      |
|-----------------------------------------------|-----------|
|                                          |      |
| Project Name: Clean-room Installation Project | 2009-2-10 |

| Serial | Description                       | Specification                           | Circuit Cap. | Qty.   | Circuit No. | Brand        |
|--------|-----------------------------------|-----------------------------------------|--------------|--------|-------------|--------------|
|   | Circuit Breaker                   | C65H-63/C16/1P                          | 16           | 2      | MX16-15~16  | Schneider    |
| 7      | 21MX(2nd Floor)     | XSAII-24                                |         |   |        | High Quality |
|   | Circuit Breaker                   | C65H-63/C40/3P                          | 40           | 1      | D-21MX      | Schneider    |
|   | Circuit Breaker                   | C65H-63/C10/1P                          | 10           | 10     | MX21-1~10   | Schneider    |
|   | Circuit Breaker                   | C65H-63/C16/1P                          | 16           | 5      | MX21-11~15  | Schneider    |
| 8      | 22MX(2nd Floor)     | XSAII-24                                |         |   |        | High Quality |
|   | Circuit Breaker                   | C65H-63/C40/3P                          | 40           | 1      | D-22MX      | Schneider    |
|   | Circuit Breaker                   | C65H-63/C10/1P                          | 10           | 3      | MX22-1~3    | Schneider    |
|   | Circuit Breaker                   | C65H-63/C16/1P                          | 16           | 10     | MX22-4~13   | Schneider    |
| 9      | 23MX(2nd Floor)     | XSAII-24                                |         |   |        | High Quality |
|   | Circuit Breaker                   | C65H-63/C25/3P                          | 25           | 1      | D-23MX      | Schneider    |
|   | Circuit Breaker                   | C65H-63/C10/1P                          | 10           | 14     | MX23-1~14   | Schneider    |
|   | Circuit Breaker                   | C65H-63/C16/1P                          | 16           | 2      | MX23-15~16  | Schneider    |
| 10     | 11MHX (1st Floor Evacuation)      | XSAII-72                                |         |   |        | High Quality |
|   | Circuit Breaker                   | C65H-63/C25/3P                          | 25           | 1      | D-11MHX     | Schneider    |
|   | Circuit Breaker                   | C65H-63/C10/1P                          | 10           | 17     | MHX11-1~17  | Schneider    |
| 11     | 21MHX(2nd FloorEvacuation) | XSAII-72                                |         |   |        | High Quality |
|   | Circuit Breaker                   | C65H-63/C25/3P                          | 25           | 1      | D-21MHX     | Schneider    |
|   | Circuit Breaker                   | C65H-63/C10/1P                          | 10           | 10     | MHX21-1~10  | Schneider    |
|   | Power Supply Box                  |                                    |         |   |        |         |
| 1      | 11DX(1st Floor)            | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker                   | C65H-63/C32/3P                          | 32           | 1      | D-11DX      | Schneider    |
|   | Leakage Protection Breaker        | DPNVigiC20                              | 20+30mA      | 5      | 11DX-1~5    | Schneider    |

| SUNTEC | Page 2 of 8 |    |
|--------|------------------|--------------|

----

| Owner Name: Shenyang Sunshine                 | P554      |
|-----------------------------------------------|-----------|
|                                          |      |
| Project Name: Clean-room Installation Project | 2009-2-10 |

| Serial | Description                | Specification                           | Circuit Cap. | Qty.   | Circuit No. | Brand        |
|--------|----------------------------|-----------------------------------------|--------------|--------|-------------|--------------|
|   | Leakage Protection Breaker | DPNVigiC32                              | 32+30mA      | 1      | 11DX-6      | Schneider    |
| 2      | 12DX(1st Floor)     | XSAII-36(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C32/3P                          | 32           | 1      | D-12DX      | Schneider    |
|   | Leakage Protection Breaker | DPNVigiC20                              | 20+30mA      | 5      | 12DX-1~5    | Schneider    |
| 3      | 13DX(1st Floor)     | XSAII-24(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C25/3P                          | 25           | 1      | D-13DX      | Schneider    |
|   | Leakage Protection Breaker | DPNVigiC20                              | 20+30mA      | 5      | 13DX-1~5    | Schneider    |
| 4      | 14DX(1st Floor)     | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C40/3P                          | 40           | 1      | D-14DX      | Schneider    |
|   | Leakage Protection Breaker | DPNVigiC20                              | 20+30mA      | 5      | 14DX-1~5    | Schneider    |
|   | Circuit Breaker            | C65H-63/C20/1P                          | 20           | 1      | 14DX-6      | Schneider    |
|   | Circuit Breaker            | C65H-63/C10/1P                          | 10           | 1      | 14DX-7      | Schneider    |
| 5      | 15DX(1st Floor)     | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C32/3P                          | 32           | 1      | D-15DX      | Schneider    |
|   | Leakage Protection Breaker | DPNVigiC20                              | 20+30mA      | 6      | 15DX-1~6    | Schneider    |
| 6      | 16DX(1st Floor)     | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C32/3P                          | 32           | 1      | D-16DX      | Schneider    |
|   | Leakage Protection Breaker | DPNVigiC20                              | 20+30mA      | 5      | 16DX-1~5    | Schneider    |
|   | Circuit Breaker            | C65H-63/C10/1P                          | 10           | 4      | 16DX-6~9    | Schneider    |
| 7      | 17DX(1st Floor)     | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C40/3P                          | 32           | 1      | D-17DX      | Schneider    |
|   | Leakage Protection Breaker | DPNVigiC20                              | 20+30mA      | 5      | 16DX-1~5    | Schneider    |
|   | Circuit Breaker            | C65H-63/C10/1P                          | 10           | 2      | 16DX-6~7    | Schneider    |
| 8      | 18DX(1st Floor)     | XSAII-24(Concealed Installation) |         |   |        | High Quality |

| SUNTEC | Page 3 of 8 |    |
|--------|------------------|--------------|

----

| Owner Name: Shenyang Sunshine                 | P554      |
|-----------------------------------------------|-----------|
|                                          |      |
| Project Name: Clean-room Installation Project | 2009-2-10 |

| Serial | Description                | Specification                           | Circuit Cap. | Qty.   | Circuit No. | Brand        |
|--------|----------------------------|-----------------------------------------|--------------|--------|-------------|--------------|
|   | Circuit Breaker            | C65H-63/C25/3P                          | 25           | 1      | D-18DX      | Schneider    |
|   | Leakage Protection Breaker | DPNVigiC20                              | 20+30mA      | 3      | 16DX-1~3    | Schneider    |
|   | Circuit Breaker            | C65H-63/C10/1P                          | 10           | 2      | 16DX-4~5    | Schneider    |
| 8      | 19DX(1st Floor)     | XSAII-24(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C50/3P                          | 50           | 1      | D-18DX      | Schneider    |
|   | Leakage Protection Breaker | DPNVigiC20                              | 20+30mA      | 5      | 18DX-1~5    | Schneider    |
|   | Circuit Breaker            | C65H-63/C10/1P                          | 10           | 3      | 18DX-6~8    | Schneider    |
| 9      | 110DX(1st Floor)    | XSAII-12(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C25/3P                          | 25           | 1      | D-110DX     | Schneider    |
|   | Leakage Protection Breaker | DPNVigiC16                              | 16+30mA      | 3      | 110DX-1~3   | Schneider    |
|   | Circuit Breaker            | C65H-63/C10/1P                          | 10           | 3      | 110DX-4~6   | Schneider    |
| 10     | 111DX(1st Floor)    | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C40/3P                          | 40           | 1      | D-111DX     | Schneider    |
|   | Leakage Protection Breaker | DPNVigiC20                              | 20+30mA      | 4      | 111DX-1~4   | Schneider    |
|   | Circuit Breaker            | C65H-63/C10/1P                          | 10           | 3      | 111DX-5~7   | Schneider    |
| 11     | 112DX(1st Floor)    | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C32/3P                          | 32           | 1      | D-112DX     | Schneider    |
|   | Leakage Protection Breaker | DPNVigiC20                              | 20+30mA      | 5      | 112DX-1~5   | Schneider    |
|   | Circuit Breaker            | C65H-63/C10/1P                          | 10           | 1      | 112DX-6     | Schneider    |
| 12     | 113DX(1st Floor)    | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C32/3P                          | 32           | 1      | D-113DX     | Schneider    |
|   | Leakage Protection Breaker | DPNVigiC20                              | 20+30mA      | 5      | 113DX-1~5   | Schneider    |
|   | Circuit Breaker            | C65H-63/C10/1P                          | 10           | 4      | 113DX-6~9   | Schneider    |
| 14     | 114DX(1st Floor)    | XSAII-18(Concealed Installation) |         |   |        | High Quality |

| SUNTEC | Page 4 of 8 |    |
|--------|------------------|--------------|

----

| Owner Name: Shenyang Sunshine                 | P554      |
|-----------------------------------------------|-----------|
|                                          |      |
| Project Name: Clean-room Installation Project | 2009-2-10 |

| Serial | Description                   | Specification                           | Circuit Cap. | Qty.   | Circuit No. | Brand        |
|--------|-------------------------------|-----------------------------------------|--------------|--------|-------------|--------------|
|   | Circuit Breaker               | C65H-63/C40/3P                          | 40           | 1      | D-114DX     | Schneider    |
|   | Leakage Protection Breaker    | DPNVigiC20                              | 20+30mA      | 1      | 114DX-1     | Schneider    |
|   | Circuit Breaker               | C65H-63/C10/1P                          | 10           | 4      | 114DX-2~5   | Schneider    |
| 15     | 115DX(1st Floor)       | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker               | C65H-63/C40/3P                          | 40           | 1      | D-115DX     | Schneider    |
|   | Leakage Protection Breaker    | DPNVigiC20                              | 20+30mA      | 7      | 115DX-1~7   | Schneider    |
| 16     | 116DX(1st Floor)       | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker               | C65H-63/C63/3P                          | 63           | 1      | D-116DX     | Schneider    |
|   | Leakage Protection Breaker    | DPNVigiC32                              | 32+30mA      | 3      | 116DX-1~3   | Schneider    |
|   | Circuit Breaker               | C65H-63/C63/1P                          | 63           | 2      | 116DX-4~5   | Schneider    |
| 17     | 117DX(1st Floor)       | XSAII-24(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker               | C65H-63/C32/3P                          | 32           | 1      | D-117DX     | Schneider    |
|   | Leakage Protection Breaker    | DPNVigiC20                              | 20-+30mA     | 3      | 117DX-1~3   | Schneider    |
|   | Circuit Breaker               | C65H-63/C10/1P                          | 10           | 2      | 117DX-4~5   | Schneider    |
| 18     | 21DX(2nd Floor)        | XSAII-24(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker               | C65H-63/C40/3P                          | 40           | 1      | D-21DX      | Schneider    |
|   | Leakage Protection Breaker    | DPNVigiC20                              | 20-+30mA     | 6      | 21DX-1~6    | Schneider    |
|   | Circuit Breaker               | C65H-63/C10/1P                          | 10           | 2      | 21DX-7~8    | Schneider    |
| 19     | 22DX(2nd Floor) | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker               | C65H-63/C40/3P                          | 40           | 1      | D-22DX      | Schneider    |
|   | Leakage Protection Breaker    | DPNVigiC20                              | 20-+30mA     | 6      | 22DX-1~6    | Schneider    |
| 20     | 23DX(2nd Floor) | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker               | C65H-63/C32/3P                          | 32           | 1      | D-23DX      | Schneider    |
|   | Leakage Protection Breaker    | DPNVigiC20                              | 20-+30mA     | 6      | 23DX-1~5    | Schneider    |

| SUNTEC | Page 5 of 8 |    |
|--------|------------------|--------------|

----

| Owner Name: Shenyang Sunshine                 | P554      |
|-----------------------------------------------|-----------|
|                                          |      |
| Project Name: Clean-room Installation Project | 2009-2-10 |

| Serial | Description                | Specification                           | Circuit Cap. | Qty.   | Circuit No. | Brand        |
|--------|----------------------------|-----------------------------------------|--------------|--------|-------------|--------------|
|   | Circuit Breaker            | C65H-63/C10/1P                          | 10           | 2      | 23DX-6~7    | Schneider    |
|   | Power Supply Box           |                                    |         |   |        |         |
| 1      | 11EX(1st Floor)     | XSAII-84(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C50/3P                          | 50           | 1      | D-11EX      | Schneider    |
|   | Leakage Protection Breaker | C65H/63/16/4+VigiC65ELE                 | 16+30mA      | 5      | 11EX-1~5    | Schneider    |
| 2      | 12EX(1st Floor)     | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C50/3P                          | 50           | 1      | D-12EX      | Schneider    |
|   | Leakage Protection Breaker | C65H/63/32/4+VigiC65ELE                 | 32+30mA      | 7      | 11EX-1~7    | Schneider    |
| 3      | 13EX(1st Floor)     | XSAII-24(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C63/3P                          | 63           | 1      | D-13EX      | Schneider    |
|   | Leakage Protection Breaker | C65H/63/32/4+VigiC65ELE                 | 32+30mA      | 9      | 11EX-1~9    | Schneider    |
| 4      | 14EX(1st Floor)     | XSAII-48(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C50/3P                          | 50           | 1      | D-14EX      | Schneider    |
|   | Leakage Protection Breaker | C65H/63/16/4+VigiC65ELE                 | 16+30mA      | 6      | 14EX-1~6    | Schneider    |
| 6      | 15EX(1st Floor)     | XSAII-18(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C50/3P                          | 50           | 1      | D-15EX      | Schneider    |
|   | Leakage Protection Breaker | C65H/63/32/4+VigiC65ELE                 | 32+30mA      | 7      | 15EX-1~7    | Schneider    |
| 7      | 16EX(1st Floor)     | XSAII-24(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C63/3P                          | 63           | 1      | D-16EX      | Schneider    |
|   | Leakage Protection Breaker | C65H/63/32/4+VigiC65ELE                 | 32+30mA      | 9      | 16EX-1~9    | Schneider    |
| 8      | 17EX(1st Floor)     | XSAII-24(Concealed Installation) |         |   |        | High Quality |
|   | Circuit Breaker            | C65H-63/C40/3P                          | 40           | 1      | D-17EX      | Schneider    |
|   | Leakage Protection Breaker | C65H/63/D10/3P                          | 10           | 7      | 17EX-1~7    | Schneider    |
| 9      | 21EX(2nd Floor)     | XSAII-24(Concealed Installation) |         |   |        | High Quality |

| SUNTEC | Page 6 of 8 |    |
|--------|------------------|--------------|

----

| Owner Name: Shenyang Sunshine                 | P554      |
|-----------------------------------------------|-----------|
|                                          |      |
| Project Name: Clean-room Installation Project | 2009-2-10 |

| Serial | Description                                                      | Specification                           | Circuit Cap. | Qty.   | Circuit No.   | Brand        |
|--------|------------------------------------------------------------------|-----------------------------------------|--------------|--------|---------------|--------------|
|   | Circuit Breaker                                                  | C65H-63/C50/3P                          | 50           | 1      | D-21EX        | Schneider    |
|   | Leakage Protection Breaker                                       | DPNVigiC32                              | 32+30mA      | 7      | 21EX-1~7      | Schneider    |
| 10     | 22EX(2nd Floor)                                           | XSAII-36(Concealed Installation) |         |   |          | High Quality |
|   | Circuit Breaker                                                  | C65H-63/C63/3P                          | 63           | 1      | D-22EX        | Schneider    |
|   | Leakage Protection Breaker                                       | DPNVigiC20                              | 20+30mA      | 10     | 22EX-1~10     | Schneider    |
| 11     | 23EX(2nd Floor)                                           | XSAII-36(Concealed Installation) |         |   |          | High Quality |
|   | Circuit Breaker                                                  | C65H-63/C40/3P                          | 40           | 1      | D-23EX        | Schneider    |
|   | Leakage Protection Breaker                                       | DPNVigiC20                              | 20+30mA      | 8      | 23EX-1~8      | Schneider    |
| 12     | 24EX(2nd Floor)                                           | XSAII-36(Concealed Installation) |         |   |          | High Quality |
|   | Circuit Breaker                                                  | C65H-63/C32/3P                          | 32           | 1      | D-24EX        | Schneider    |
|   | Leakage Protection Breaker                                       | DPNVigiC20                              | 20+30mA      | 6      | 24EX-1~6      | Schneider    |
|   | Maintenance Power Box (1st Floor)                         |                                    |         |   |          |         |
| 1      | Maintenance Power Box                                            | Non-Standard                            |         | 4      |          | High Quality |
|   | 11JX、12JX、13JX、14JX                         |                                    |         |   |          |         |
|   | Circuit Breaker                                                  | C65H/63/D63/3P                          | 63           | 16     | Incoming Line | Schneider    |
|   | Leakage Protection Breaker                                       | C65H/63/32/4+VigiC65ELE                 | 32+30mA      | 16     |          | Schneider    |
|   | Leakage Protection Breaker                                       | DPNVigiC16                              | 16+30mA      | 48     |          | Schneider    |
| 1      | Maintenance Power Box (Trench)                                   | Non-Standard                            |         | 6      |          | High Quality |
|   | 01JX、02JX、03JX、04JX、05JX、06JX |                                    |         |   |          |         |
|   | Circuit Breaker                                                  | C65H/63/D63/3P                          | 63           | 16     | Incoming Line | Schneider    |
|   | Leakage Protection Breaker                                       | C65H/63/32/4+VigiC65ELE                 | 32+30mA      | 16     |          | Schneider    |
|   | Leakage Protection Breaker                                       | DPNVigiC16                              | 16+30mA      | 48     |          | Schneider    |

| SUNTEC | Page 7 of 8 |    |
|--------|------------------|--------------|

----

| Owner Name: Shenyang Sunshine                 | P554      |
|-----------------------------------------------|-----------|
|                                          |      |
| Project Name: Clean-room Installation Project | 2009-2-10 |

| Serial | Description                                                      | Specification           | Circuit Cap. | Qty.   | Circuit No.   | Brand        |
|--------|------------------------------------------------------------------|-------------------------|--------------|--------|---------------|--------------|
| 1      | Maintenance Power Box (Half Floor)                        | Non-Standard            |         | 6      |          | High Quality |
|   | 21JX、22JX、23JX、24JX、25JX、26JX |                    |         |   |          |         |
|   | Circuit Breaker                                                  | C65H/63/D63/3P          | 63           | 16     | Incoming Line | Schneider    |
|   | Leakage Protection Breaker                                       | C65H/63/32/4+VigiC65ELE | 32+30mA      | 16     |          | Schneider    |
|   | Leakage Protection Breaker                                       | DPNVigiC16              | 16+30mA      | 48     |          | Schneider    |
| 1      | Socket Box (Seed Proliferation)                                  | Non-Standard            |         | 8      |          |         |
|   | Socket                                                           |                    |         |   |          | Schneider    |
|   |                                                             |                    |         |   |          |         |
|   |                                                             |                    |         |   |          |         |
|   |                                                             |                    |         |   |          |         |
|   |                                                             |                    |         |   |          |         |
|   |                                                             |                    |         |   |          |         |
|   |                                                             |                    |         |   |          |         |
|   |                                                             |                    |         |   |          |         |
|   |                                                             |                    |         |   |          |         |

| SUNTEC | Page 8 of 8 |    |
|--------|------------------|--------------|

----