| Bill of Power Consumption in Production Workshop |
|--------------------------------------------------------------------------------|

| Serial No. | Description                                | Unit(KW) | Calculating Power(KW) | Calculating Current after Compensation | Cable Type               | Remarks                      |
|------------|--------------------------------------------|------------------------|------------------------------|----------------------------------------|--------------------------|------------------------------|
| A          | Gross Installed Capacity of Workshop Power | 1831                   | 999                          | 1597.75                                | ZR-YJV22-1.0,3x300+1x150 | Compliance with Actual Needs |
| 1          | Power Supply Box11DX                       | 15                     | 11                           | 20.89                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 2          | Power Supply Box12DX                       | 18                     | 13                           | 24.69                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 3          | Power Supply Box13DX                       | 13                     | 9                            | 17.09                                  | ZR-YJV22-1.0,5x4         | Compliance with Actual Needs |
| 4          | Maintanence Box21,22JX                     | 20                     | 17                           | 32.29                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 5          | Power Supply Box15DX                       | 15                     | 11                           | 20.89                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 6          | Power Supply Box16DX                       | 18                     | 13                           | 24.69                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 7          | Maintanence Box23,24JX                     | 20                     | 16                           | 30.39                                  | ZR-YJV22-1.0,5x16        | Compliance with Actual Needs |
| 8          | Power Supply Box18DX                       | 13                     | 9                            | 17.09                                  | ZR-YJV22-1.0,5x4         | Compliance with Actual Needs |
| 9          | Power Supply Box19DX                       | 28                     | 21                           | 39.88                                  | ZR-YJV22-1.0,5x10        | Compliance with Actual Needs |
| 10         | Power Supply Box110DX                      | 7                      | 7                            | 13.29                                  | ZR-YJV22-1.0,5x4         | Compliance with Actual Needs |
| 11         | Power Supply Box111DX                      | 20                     | 15                           | 28.49                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 12         | Power Supply Box112DX                      | 12                     | 10                           | 18.99                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 13         | Power Supply Box113DX                      | 77                     | 49                           | 93.06                                  | ZR-YJV22-1.0,3x35+2x16   | Compliance with Actual Needs |
| 14         | Power Supply Box114DX                      | 20                     | 15                           | 28.49                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 15         | Power Supply Box116DX                      | 54                     | 19                           | 36.09                                  | ZR-YJV22-1.0,5x16        | Compliance with Actual Needs |
| 16         | Power Supply Box117DX                      | 14                     | 11                           | 20.89                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 17         | Power Supply Box21DX                       | 20                     | 15                           | 28.49                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 18         | Power Supply Box22DX                       | 18                     | 14                           | 26.59                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 19         | Power Supply Box23DX                       | 22                     | 12                           | 22.79                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 20         | Power Cabinet11LX                          | 38                     | 32                           | 60.78                                  | ZR-YJV22-1.0,3x25+2x16   | Compliance with Actual Needs |
| 21         | Power Cabinet12LX                          | 115                    | 97                           | 184.23                                 | ZR-YJV22-1.0,3x95+2x50   | Compliance with Actual Needs |
| 22         | Power Cabinet13LX                          | 35                     | 26                           | 49.38                                  | ZR-YJV22-1.0,5x16        | Compliance with Actual Needs |
| 23         | Power Cabinet21LX                          | 103                    | 87                           | 165.23                                 | ZR-YJV22-1.0,3x95+2x50   | Compliance with Actual Needs |
| 24         | Maintanence Box25,26JX                     | 20                     | 17                           | 32.29                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 25         | CIP Washing Unit                           | 28.5                   | 28.5                         | 54.13                                  | ZR-YJV22-1.0,3x25+2x16   | Compliance with Actual Needs |
| 26         | CIP Washing Unit                           | 15.5                   | 15.5                         | 29.44                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 27         | Cleaning Machine of Instruments            | 10.65                  | 10.65                        | 20.23                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 28         | Sterilizing Cabinet                        | 9                      | 8                            | 15.19                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 29         | Sterilizing Cabinet                        | 9                      | 8                            | 15.19                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 30         | Cleaning Machine                           | 10.65                  | 15.5                         | 29.44                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 31         | Cleaning Machine                           | 10.65                  | 15.5                         | 29.44                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 32         | Sterilizing Cabinet                        | 11.5                   | 10.35                        | 19.66                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 33         | Drying Box                                 | 20                     | 18                           | 34.19                                  | ZR-YJV22-1.0,5x10        | Compliance with Actual Needs |
| 34         | Elevator                                   | 7.5                    | 7.5                          | 14.24                                  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |

----

| 35 | Switching Cabinet11HX                               | 46  | 46     | 87.36  | ZR-YJV22-1.0,3x50+2x25   | Compliance with Actual Needs |
|----|-----------------------------------------------------|-----|--------|--------|--------------------------|------------------------------|
| 36 | Switching Cabinet21HX                               | 10  | 10     | 18.99  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 37 | Freezing Machine                                    | 189 | 189    | 358.96 | ZR-YJV22-1.0,3x240+2x120 | Compliance with Actual Needs |
| 38 | Freezing Machine                                    | 189 | 189    | 358.96 | ZR-YJV22-1.0,3x240+2x120 | Compliance with Actual Needs |
| 39 | Freezing Machine                                    | 98  | 98     | 186.12 | ZR-YJV22-1.0,3x150+2x70  | Compliance with Actual Needs |
| 40 | Process Second-Class Load                           | 442 |   |   |                     |                         |
| B  | Gross Capacity of Second-Class Load in Process      | 442 | 276    | 530.82 | ZR-YJV22-1.0,3x150+1x70  | Compliance with Actual Needs |
| 1  | Power Supply Box11EX                                | 24  | 18     | 34.18  | ZR-YJV22-1.0,5x10        | Compliance with Actual Needs |
| 2  | Power Supply Box12EX                                | 27  | 20     | 37.98  | ZR-YJV22-1.0,5x10        | Compliance with Actual Needs |
| 3  | Power Supply Box13EX                                | 33  | 25     | 47.48  | ZR-YJV22-1.0,5x16        | Compliance with Actual Needs |
| 4  | Power Supply Box14EX                                | 24  | 20     | 37.98  | ZR-YJV22-1.0,5x10        | Compliance with Actual Needs |
| 5  | Power Supply Box15EX                                | 27  | 20     | 37.98  | ZR-YJV22-1.0,5x10        | Compliance with Actual Needs |
| 6  | Power Supply Box16EX                                | 33  | 25     | 47.48  | ZR-YJV22-1.0,5x16        | Compliance with Actual Needs |
| 7  | Power Supply Box17EX                                | 16  | 14     | 26.59  | ZR-YJV22-1.0,5x10        | Compliance with Actual Needs |
| 8  | Power Supply Box21EX                                | 24  | 18     | 34.18  | ZR-YJV22-1.0,5x10        | Compliance with Actual Needs |
| 9  | Power Supply Box22EX                                | 33  | 25     | 47.48  | ZR-YJV22-1.0,5x16        | Compliance with Actual Needs |
| 10 | Power Supply Box23EX                                | 22  | 17     | 32.29  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 11 | Power Supply Box24EX                                | 12  | 12     | 22.79  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 12 | Power Cabinet11~13ELX                               | 21  | 17     | 32.29  | ZR-YJV22-1.0,5x16        | Compliance with Actual Needs |
| 13 | Power Cabinet21ELX                                  | 2   | 2      | 3.8    | ZR-YJV22-1.0,5x4         | Compliance with Actual Needs |
| 14 | Power Cabinet22ELX                                  | 23  | 23     | 43.68  | ZR-YJV22-1.0,5x16        | Compliance with Actual Needs |
| 15 | Tunnel Oven                                         | 33  | 33     | 62.67  | ZR-YJV22-1.0,3x35+2x16   | Compliance with Actual Needs |
| 16 | Capping Machine                                     | 10  | 10     | 18.99  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 17 | Power Supply Box14DX                                | 22  | 17     | 32.29  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 18 | Power Supply Box17DX                                | 22  | 17     | 32.29  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 19 | HPLC                                                | 17  | 17     | 32.29  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 20 | HPLC                                                | 17  | 17     | 32.29  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| C  | Gross Capacity of Air Conditioning Load in Workshop | 316 | 253    | 480.51 | ZR-YJV22-1.0,3x240+2x120 | Compliance with Actual Needs |
| 1  | Power Cabinet11KX                                   | 26  | 26     | 49.38  | ZR-YJV22-1.0,5x16        | Compliance with Actual Needs |
| 2  | Power Cabinet12KX                                   | 33  | 33     | 62.67  | ZR-YJV22-1.0,3x25+2x16   | Compliance with Actual Needs |
| 3  | Power Cabinet13KX                                   | 30  | 30     | 56.98  | ZR-YJV22-1.0,3x25+2x16   | Compliance with Actual Needs |
| 4  | Power Cabinet14KX                                   | 48  | 48     | 91.16  | ZR-YJV22-1.0,3x35+2x16   | Compliance with Actual Needs |
| 5  | Power Cabinet15KX                                   | 41  | 41     | 77.87  | ZR-YJV22-1.0,3x35+2x16   | Compliance with Actual Needs |
| 6  | Power Cabinet16KX                                   | 40  | 40     | 75.97  | ZR-YJV22-1.0,3x35+2x16   | Compliance with Actual Needs |
| 7  | Power Cabinet11KHX                                  | 30  | 30     | 56.98  | ZR-YJV22-1.0,3x25+2x16   | Compliance with Actual Needs |
| 8  | Power Cabinet12KHX                                  | 68  | 68     | 129.15 | ZR-YJV22-1.0,3x70+2x35   | Compliance with Actual Needs |

----

| D                                                                                | Gross Capacity of Lighting Load in Workshop     | 122    | 104    | 185.9  | ZR-YJV22-1.0,3x185+1x95  | Compliance with Actual Needs |
|----------------------------------------------------------------------------------|-------------------------------------------------|--------|--------|--------|--------------------------|------------------------------|
| 1                                                                                | Lighting Box11MHX                               | 9      | 9      | 16.09  | NH-VV-1.0,5x6            | Compliance with Actual Needs |
| 2                                                                                | Lighting Box21MHX                               | 6      | 6      | 10.73  | NH-VV-1.0,5x4            | Compliance with Actual Needs |
| 3                                                                                | Lighting BoxDGMX                                | 11     | 11     | 19.66  | ZR-VV-1.0,5x6            | Compliance with Actual Needs |
| 4                                                                                | Lighting Box11MX                                | 5      | 5      | 8.94   | ZR-VV-1.0,5x4            | Compliance with Actual Needs |
| 5                                                                                | Lighting Box12MX                                | 9      | 9      | 16.09  | ZR-VV-1.0,5x4            | Compliance with Actual Needs |
| 6                                                                                | Lighting Box13MX                                | 12     | 12     | 21.15  | ZR-VV-1.0,5x10           | Compliance with Actual Needs |
| 7                                                                                | Lighting Box14MX                                | 12     | 12     | 21.15  | ZR-VV-1.0,5x10           | Compliance with Actual Needs |
| 8                                                                                | Lighting Box15MX                                | 8      | 8      | 14.3   | ZR-VV-1.0,5x4            | Compliance with Actual Needs |
| 9                                                                                | Lighting Box16MX                                | 7      | 7      | 12.51  | ZR-VV-1.0,5x4            | Compliance with Actual Needs |
| 10                                                                               | Lighting Box21MX                                | 16     | 16     | 28.6   | ZR-VV-1.0,5x10           | Compliance with Actual Needs |
| 11                                                                               | Lighting Box22MX                                | 16     | 16     | 28.6   | ZR-VV-1.0,5x10           | Compliance with Actual Needs |
| 12                                                                               | Lighting Box23MX                                | 11     | 11     | 19.66  | ZR-VV-1.0,5x6            | Compliance with Actual Needs |
| E                                                                                | Gross Capacity of Second-Class Load in Workshop | 614    | 425    | 807.17 | ZR-YJV22-1.0,3x240+1x120 | Compliance with Actual Needs |
| 1                                                                                | Switching Cabinet11HX                           | 46     | 46     | 87.36  | ZR-YJV22-1.0,3x50+2x25   | Compliance with Actual Needs |
| 2                                                                                | Switching Cabinet21HX                           | 10     | 10     | 18.99  | ZR-YJV22-1.0,5x6         | Compliance with Actual Needs |
| 3                                                                                | Lighting Box11MHX                               | 9      | 9      | 16.09  | NH-VV-1.0,5x6            | Compliance with Actual Needs |
| 4                                                                                | Lighting Box21MHX                               | 6      | 6      | 10.73  | NH-VV-1.0,5x4            | Compliance with Actual Needs |
| 5                                                                                | Power Cabinet11KHX                              | 30     | 30     | 56.98  | ZR-YJV22-1.0,3x25+2x16   | Compliance with Actual Needs |
| 6                                                                                | Power Cabinet12KHX                              | 68     | 68     | 129.15 | ZR-YJV22-1.0,3x70+2x35   | Compliance with Actual Needs |
| 7                                                                                | Process Second-Class Load                       | 445    |   |   |                     |                         |
|                                                                             |                                            |   |   |   |                     |                         |
| Note: Gross Capacity of Whole Workshop =A+C+D+E-445=1831+316+122+614-445=2883 KW |
|                                                                             |                                            |   |   |   |                     |                         |
|                                                                             |                                            |   |   |   |                     |                         |
|                                                                             |                                            |   |   |   |                     |                         |
|                                                                             |                                            |   |   |   |                     |                         |

----