----

| 39CBFI Series Modular Air-Conditioning Unit                     |   |
|-----------------------------------------------------------------|--------|
| Mark Method of Unit Type                                        | 1      |
| Air Amount scope                                                | 1      |
| Characteristics of Unit                                         | 2      |
| Introduction of software                                        | 4      |
| Control Illusion of Unit                                        | 5      |
| Control                                                         | 6      |
| Swift Model Selection                                           | 7      |
| Sketch Map of Function Section                                  | 8      |
| Adjustment of air valve                                         | 9      |
| Cold amount and heat amount of unit and pipe coil configuration | 10     |
| Weight of Pipe Coil                                             | 12     |
| Connection dimension of pipe coil installation                  | 13     |
| Fan section                                                     | 16     |
| Humidifier Option                                               | 19     |
| Silencer                                                        | 20     |
| Filter                                                          | 21     |
| Specification and number of Filter                              | 22     |
| Filtering grade of purification needed                          | 23     |
| Electrical heating section                                      | 24     |
| Case Weight                                                     | 24     |
|                                                            |   |
| 39CBF Series Modular Air-Conditioning Unit                      |   |
| Mark Method of 39CBF                                            | 25     |
| Air Amount Scope of 39CBF                                       | 25     |
| Characteristics of Unit 39CBF                                   | 26     |
| Swift Model Selection of 39CBF                                  | 28     |
| Other Specification                                             | 29     |

----

----

| l | Pipe coil employs Carrier’s latest ripple fins to install on copper pipe by mechanic expansion pipe method, which has excellent heat transfer efficiency. Customers can select hydrophilic aluminum foil to more excellent reach heat transfer performance. |
|---|-------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| l | When face velocity is more than 2.5m/s, water-dam can be added behind pipe coil, which can effectively separate water from air. |
|---|---------------------------------------------------------------------------------------------------------------------------------|

----

| l | Provide all-level filters, ranging from preliminary filter (board-structure, efficiency can reach G4 level), to medium filter (bag-structure, efficiency can reach F8 level), and high efficiency filter (H13). And provide active carbon filter, filter cartridge filter, antistatic filter and other special filters. |
|---|-------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

----

----

|   | Control of AC Unit                     |   |                                                                                                                                                                                                                                                                                                                                                                                                                                       |
|--------|----------------------------------------|--------|--------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|
|   |                                   |   |                                                                                                                                                                                                                                                                                                                                                                                                                                       |
|   | Monitor Equipment                      |   | Monitor Contents                                                                                                                                                                                                                                                                                                                                                                                                                           |
|   |                                   |   |                                                                                                                                                                                                                                                                                                                                                                                                                                       |
|   | AC Unit                                |   | Fan Start stop control; Fan Operation Status, Fault Alarm, Handle and auto status; , Filter silting Alarm; (pipe coil freeze protection Alarm) Cold Water Valve regulation, Hot Water Valve Regulation; Fresh-air Damper Adjustment; recirculation door Adjustment; Himidifier Switch; Supply Temperature; Supply Temperature; recirculation humidity level; indoor temperature and humidity level; outdoor temperature and humidity level |
|   |                                   |   |                                                                                                                                                                                                                                                                                                                                                                                                                                       |
|   | Schematic diagram of AC unit (Example) |

| 1  humility of return air             | 2  Temperature of Return air   | 3  Damper adjustment of Return air | 4   Fresh-air damper adjust | 5  Screen silting Alarm |
|-------------------------------------------------|------------------------------------------|----------------------------------------------|--------------------------------------------|-----------------------------------|
| 6  Hot Water Valve Adjust   | 7  Cold Water Valve adjustment | 8  humidifier Switch               | 9   Fan Operation Status    | 10 Fan Handle or auto Status      |
| 11 Fan Fault                                    | 12 Fan Stop Control                      | 13 Temperature of Supply Air                 |                                       |                              |

|   | AC Unit Fresh-Air Control                     |
|--------|-----------------------------------------------|
|   |                                          |   |   |
|   | Monitor equipment                             |   | monitor content |
|   |                                          |   |   |
|   | Fresh-air Unit                                |   | Fan Start Stop Control; Fan Operational Status, Fault Alarm, Handle and auto status, filter silt alarm; (pipe coil freeze protection Alarm) Cold Water Valve Adjustment, hot water Valve Adjustment, Fresh-air damper adjustment; temperature of supply air, indoor temperature and humidity, outdoor temperature and humidity |
|   |                                          |   |   |
|   | Schematic diagram of Fresh-air unit (Example) |

| 1   Fresh-air Damper openness | 2   Screen Silting Alarm | 3   Valve Adjustment          | 4   Fan Operation       | 5   handle – Auto Status |
|----------------------------------------------|-----------------------------------------|----------------------------------------------|----------------------------------------|-----------------------------------------------|
| 6   Fan Fault Alarm           | 7   Fan Start-stop       | 8   temperature of Supply air | 9   Outdoor Temperature |                                          |

----

|   | ● | aim to all kinds of AC unit and terminals, provide all-level control system solution |
|--------|---------|--------------------------------------------------------------------------------------|

|   | ● | Through communication signal line, assemble temperature, humility, valve and damper’s signals on AC unit and terminals, send alarms through internal logical procedure, control valve, damper openness, monitor fan, screen status, auto alarm. |
|--------|---------|-------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

|   | ● | Equip special system monitor interface, realizing system control of simple AC Unit. |
|--------|---------|-------------------------------------------------------------------------------------|

----

| Unit Specification                        |   | Pipe coil in the wind |   | Outline Diamension |    | Air    |   | Full Pressure of |
|-------------------------------------------|--------|-----------------------|--------|--------------------|---------|--------|--------|------------------|
|                                      |   |                  |   |               |    |   | Flow   |             | External unit |
| 39CFI                                     |   | Area (m2)             |   | Height H*          | Width W |   |   |             |   |   |   |   |   |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 0609                                      |   | 0.24                  |   | 700                | 1000    |   | 2008   |             | 2209 |   | 2430 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 0610                                      |   | 0.34                  |   | 700                | 1100    |   | 2755   |             | 3058 |   | 3364 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 0712                                      |   | 0.49                  |   | 800                | 1300    |   | 3979   |             | 4417 |   | 4859 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 0813                                      |   | 0.70                  |   | 900                | 1400    |   | 5663   |             | 6286 |   | 6915 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 0914                                      |   | 0.81                  |   | 1000               | 1500    |   | 6582   |             | 7306 |   | 8037 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 1015                                      |   | 1.05                  |   | 1100               | 1600    |   | 8495   |             | 9429    |   | 10372 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 1016                                      |   | 1.15                  |   | 1100               | 1700    |   | 9337   |             | 10364 |   | 11400 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 1117                                      |   | 1.44                  |   | 1200               | 1800    |   | 11632  |             | 12912 |   | 14703 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 1317                                      |   | 1.68                  |   | 1400               | 1800    |   | 13623  |             | 15121 |   | 16633 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 1518                                      |   | 2.07                  |   | 1600               | 1900    |   | 16837  |             | 18689 |   | 20558 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 1522                                      |   | 2.36                  |   | 1600               | 2300    |   | 19133  |             | 21238 |   | 23362 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 1622                                      |   | 2.55                  |   | 1700               | 2300    |   | 20664  |             | 22937 |   | 25231 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 1822                                      |   | 2.93                  |   | 1900               | 2300    |   | 23725  |             | 26335 |   | 28968 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 1824                                      |   | 3.30                  |   | 1900               | 2500    |   | 26786  |             | 29733 |   | 32706 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 1825                                      |   | 3.59                  |   | 1900               | 2600    |   | 29082  |             | 32281 |   | 35509 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 2025                                      |   | 3.96                  |   | 2100               | 2600    |   | 30143  |             | 35679 |   | 39247 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 2226                                      |   | 4.63                  |   | 2300               | 2700    |   | 37501  |             | 41626 |   | 45789 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| 2330                                      |   | 5.48                  |   | 2400               | 3100    |   | 44388  |             | 49271 |   | 54198 |   | 200~800 |
|                                      |   |                  |   |               |    |   |   |             |   |   |   |   |   |
| Unit height, not inclusive of base, 100mm | 400    | 3500                  |   | 52041              |    | 57766  |   | 63543            |   |   |

----

| Serial No. |   | Description                             |   | Simple Graph |   |                                                                    |   | Note                                                                                                              |
|------------|--------|-----------------------------------------|--------|--------------|--------|-------------------------------------------------------------------------|--------|-------------------------------------------------------------------------------------------------------------------|
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 1          |   | Combined Section                   |   |              |   | (0609~0813) 5M0914~1317) 6M(1518~1622) 8M(1822~2025) 9M(2226~2334) 11M  |   |                                                                                                              |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 2          |   | Bag Filter Section                      |   |              |   | 6M                                                                      |   | The function section is recommended to set repair section                                                    |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 3          |   | Comprehensive Filter Section            |   |              |   | 6M                                                                      |   | The function section is recommended to set repair section                                                    |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 4          |   | Surface Cold Section                    |   |              |   | 6M                                                                      |   | Include water-dam                                                                                                 |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 5          |   | Hot Water pipe coil section             |   |              |   | 3M                                                                      |   | When surface cold section did not include wet film humidifier and water-dam, can be installed with cold water pan |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 6          |   | Steam pipe coil section                 |   |              |   | 3M                                                                      |   |                                                                                                              |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 7          |   | Electricity Heat Section                |   |              |   | 3M                                                                      |   |                                                                                                              |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 8          |   | Steam Humidifier Section           |   |              |   | 6M                                                                      |   |                                                                                                              |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 9          |   | Wet Film Humidifying Section            |   |              |   | 3M                                                                      |   | Can directly install with pipe coil, water pan, no space Demand                                                   |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 10         |   | High Pressure Spray humidifying Section |   |              |   | 6M                                                                      |   | Can be neighbor with surface cold machine, use water-dam                                                          |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 11         |   | Fan Section                             |   |              |   |                                                                    |   | Fan has four air-out directions                                                                                   |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 12         |   | Fresh-air return air section            |   |              |   | (0609~0813) 10M(0914~1825) 12M(2025~2334) 18M                           |   |                                                                                                              |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 13         |   | Silencing Section                       |   |              |   | 6M, 12M                                                                 |   | The function section is recommended to set repair section                                                         |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 14         |   | Air Outlet Section                      |   |              |   | (0609~0813) 5M(0914~1317) 6M(1518~1622) 8M(1822~2025) 9M(2226~2334) 11M |   | The outlet can be on the side or on the top                                                                       |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 15         |   | Empty Section                           |   |              |   | 3M, 6M                                                                  |   |                                                                                                              |
|       |   |                                    |   |         |   |                                                                    |   |                                                                                                              |
| 16         |   | High Efficient filter section           |   |              |   | 9M                                                                      |   |                                                                                                              |

----

| Direction of unit:  | favorable current direction, pipe coil in/out water pipe those the access door on the left are left side door, and verse vise. |
|--------------------------|--------------------------------------------------------------------------------------------------------------------------------|

|      | 39CBFI               |
|-----------|----------------------|
| Unit Spec | L × H           | Weight |
| 39CBFI    | mm                   | kg |
| 0609      | 848.0 × 420.5   | 19.7 |
| 0610      | 948.0 × 420.5   | 20.9 |
| 0712      | 1148.0 × 420.5  | 23.8 |
| 0813      | 1248.0 × 420.5  | 25.3 |
| 0914      | 1348.0 × 578.0  | 36.7 |
| 1015      | 1448.0 × 578.0  | 38.5 |
| 1016      | 1548.0 × 578.0  | 40.0 |
| 1117      | 1648.0 × 578.0  | 42.7 |
| 1317      | 1648.0 × 578.0  | 42.7 |
| 1518      | 1748.0 × 735.0  | 46.0 |
| 1522      | 2148.0 × 735.5  | 62.4 |
| 1622      | 2148.0 × 735.5  | 62.4 |
| 1822      | 2148.0 × 893.0  | 72.0 |
| 1824      | 2348.0 × 893.0  | 76.8 |
| 1825      | 2448.0 × 893.0  | 79.5 |
| 2025      | 2448.0 × 893.0  | 79.5 |
| 2226      | 2548.0 × 1050.5 | 89.7 |
| 2330      | 2948.0 × 1050.5 | 100.7 |
| 2334      | 3348.0 × 1050.5 | 111.0 |

----

|           |            | 4 Row      | 6 Row   |
|----------------|-----------------|-----------------|--------------|
| Unit Spec | air volume | Total cold | A. cold | Air .resist. | Water Flow | Water Resis | Loop | Total C | A. cold | Air Resist |
| 39CBFI         | (CMH)           | (kW)            | (kW)         | (Pa) | (L/s) | (kPa) |   | (kW) | (kW) | (Pa) |
| 0609           | 2209            | 12.1            | 9.12         | 128 | 0.58 | 7.9 | HF | 17.16 | 11.75 | 196 |
| 0610           | 3058            | 16.58           | 11.90        | 124 | 0.79 | 12.4 | HF | 24.69 | 16.65 | 188 |
| 0712           | 4417            | 23.92           | 17.11        | 126 | 1.1 | 17.1 | HF | 36.07 | 24.24 | 192 |
| 0813           | 6286            | 35.39           | 25.27        | 126 | 1.7 | 34.6 | HF | 48.28 | 33.18 | 191 |
| 0914           | 7306            | 40.83           | 29.04        | 128 | 1.96 | 39.5 | HF | 55.62 | 38.37 | 192 |
| 1015           | 9429            | 53.41           | 38.08        | 127 | 2.6 | 46.9 | HF | 72.84 | 49.96 | 191 |
| 1016           | 10364           | 59.51           | 42.16        | 128 | 2.85 | 55.8 | HF | 81.18 | 55.39 | 191 |
| 1117           | 12912           | 79.53           | 58.65        | 125 | 3.8 | 17.8 | FL | 103.39 | 69.97 | 191 |
| 1317           | 15121           | 93.44           | 68.79        | 126 | 4.5 | 20.8 | FL | 121.26 | 82.01 | 192 |
| 1518           | 18689           | 116.43          | 85.41        | 127 | 5.6 | 26.7 | FL | 150.61 | 101.68 | 193 |
| 1522           | 21238           | 135.61          | 98.38        | 127 | 6.5 | 25.2 | FL | 173.71 | 116.64 | 192 |
| 1622           | 22937           | 145.83          | 105.99       | 127 | 7 | 27.7 | FL | 187.1 | 125.76 | 192 |
| 1822           | 26335           | 167.58          | 121.76       | 127 | 8 | 28.1 | FL | 214.93 | 144.44 | 192 |
| 1824           | 29733           | 193.22          | 139.09       | 128 | 9.2 | 35.6 | FL | 245.77 | 164.41 | 193 |
| 1825           | 32281           | 212.52          | 152.13       | 128 | 10.2 | 45 | FL | 257.06 | 174.31 | 191 |
| 2025           | 35679           | 234.3           | 167.90       | 128 | 11.2 | 44.8 | FL | 283.45 | 192.37 | 191 |
| 2226           | 41628           | 275.39          | 196.72       | 129 | 13.2 | 51.8 | FL | 332.93 | 225.39 | 191 |
| 2330           | 49271           | 331.15          | 234.96       | 129 | 15.8 | 69.5 | FL | 399.05 | 268.91 | 192 |
| 2334           | 57766           | *371.14         | *268.51      | *129 | *14.1 | *68.9 | FL | *450.89 | *308.05 | *193 |

|           |   | 6 Row  | 8 row       |
|----------------|--------|-------------|------------------|
|           | Air    |        |             |   |   |   |   |   |   |   |
| Unit Spec | volume | W Flow | Water Resis | Loop | Total Cold | A. Cold | Air Resistant | Water Fl | Water Resis | Loop |
| 39CBFI         | (CMH)  | (L/s)       | (kPa)            |   | (kW) | (kW) | (Pa) | (L/s) | (kPa) |   |
| 0609           | 2209   | 0.8         | 16.1             | HF | 19.7 | 12.91 | 264 | 0.9 | 26.6 | HF |
| 0610           | 3058   | 1.2         | 40.2             | HF | 27.73 | 18.07 | 253 | 1.3 | 64.2 | HF |
| 0712           | 4417   | 1.7         | 43.58            | HF | 37.96 | 25.18 | 254 | 1.8 | 14.8 | FL |
| 0813           | 6286   | 2.3         | 19.1             | FL | 55.05 | 36.28 | 257 | 2.6 | 29.2 | FL |
| 0914           | 7306   | 2.7         | 19.6             | FL | 63.8 | 42.09 | 258 | 3.1 | 29.5 | FL |
| 1015           | 9429   | 3.5         | 18.6             | FL | 83.77 | 54.95 | 256 | 4 | 29.5 | FL |
| 1016           | 10364  | 3.9         | 24.1             | FL | 92.6 | 60.76 | 257 | 4.4 | 38 | FL |
| 1117           | 12912  | 4.9         | 37.7             | FL | 116.72 | 76.14 | 256 | 5.6 | 57.8 | FL |
| 1317           | 15121  | 5.8         | 43.1             | FL | 136.75 | 89.19 | 257 | 6.5 | 64.6 | FL |
| 1518           | 18689  | 7.2         | 41.8             | FL | 169.37 | 110.39 | 259 | 8.1 | 65.2 | FL |
| 1522           | 21238  | 8.3         | 54.1             | FL | 182.96 | 121.25 | 256 | 8.7 | 22.6 | DB |
| 1622           | 22937  | 8.9         | 58.1             | FL | 196.83 | 130.62 | 256 | 9.4 | 23.8 | DB |
| 1822           | 26335  | 10.3        | 59.5             | FL | 226.3 | 150.1 | 256 | 10.8 | 18.8 | DB |
| 1824           | 29733  | 11.8        | 75.8             | FL | 258.44 | 170.76 | 257 | 12.4 | 25.8 | DB |
| 1825           | 32281  | 12.3        | 36.6             | DB | 282.03 | 186.02 | 258 | 13.5 | 31.4 | DB |
| 2025           | 35679  | 13.6        | 37.8             | DB | 311.39 | 205.46 | 258 | 14.9 | 33.5 | DB |
| 2226           | 41628  | 15.9        | 43.7             | DB | 364.32 | 240.16 | 258 | 17.4 | 38.5 | DB |
| 2330           | 49271  | 19.1        | 57.7             | DB | 433.94 | 285.45 | 259 | 20.8 | 49.8 | DB |
| 2334           | 57766  | 18          | 56.8             | DB | 521.38 | 340.26 | 259 | 24.9 | 76.1 | DB |

----

| Unit Cold |        |
|-----------|-------------|
| Amount    | Fresh-air   |
|      | Operational |
|      | Condition   |

| Unit spec | Air volume | 4 Row      | 6 Row   |
|-----------|------------|------------|---------|
| 39CBFI    | (CMH)      | Total Cold | A. Cold | Air Resist | Water Res | Water Flow | Loop | T Cold | A Cold | Air Consist |
|      |       | (kW)       | (kW)    | (Pa) | (L/s) | (kPa) |   | (kW) | (kW) | (Pa) |
| 0609      | 2209       | 31.55      | 13.66   | 134 | 1.5 | 27 | HF | 39.51 | 16.75 | 201 |
| 0610      | 3058       | 45.81      | 19.63   | 128 | 2.2 | 59.4 | HF | 51.03 | 21.75 | 193 |
| 0712      | 4417       | 59.83      | 26.18   | 130 | 2.9 | 15.1 | FL | 76.05 | 32.32 | 195 |
| 0813      | 6286       | 87.31      | 38.01   | 131 | 4.2 | 28 | FL | 109.86 | 46.64 | 197 |
| 0914      | 7306       | 102.48     | 44.53   | 132 | 4.9 | 49.2 | FL | 128.37 | 54.48 | 198 |
| 1015      | 9429       | 133.99     | 58.08   | 130 | 6.4 | 52.5 | FL | 160.2 | 68.89 | 195 |
| 1016      | 10364      | *149.59    | 64.66   | 131 | 7.2 | 59.0 | FL | 177.02 | 76.12 | 196 |
| 1117      | 12912      | *183.57    | *79.32  | *131 | *7.3 | *60.1 | FL | *214.73 | *92.33 | *196 |
| 1317      | 15121      | *215.15    | *92.94  | *132 | *8.6 | *70.3 | FL | *253.28 | 108.91 | *197 |
| 1518      | 18689      | *261.47    | *113.29 | *132 | *9.6 | *62 | FL | *314.54 | *135.25 | *197 |
| 1522      | 21238      | *296.3     | *128.45 | *131 | *10.1 | *63.6 | FL | *348.73 | *149.95 | *196 |
| 1622      | 22937      | *318.64    | *138.24 | *132 | *10.9 | *62.9 | FL | *379.61 | *163.23 | *196 |
| 1822      | 26335      | *366.3     | *158.88 | *132 | *12.5 | *65.3 | FL | *435.05 | *187.07 | *196 |
| 1824      | 29733      | *412.33    | *178.94 | *133 | *13.1 | *57.4 | FL | *490.59 | *210.96 | *197 |
| 1825      | 32281      | *443.04    | *192.65 | *133 | *313.2 | *61.6 | FL | *531.97 | *226.88 | *197 |
| 2025      | 35679      | *488.74    | *212.6  | *133 | *14.6 | *68 | FL | *585.95 | *250 | *197 |
| 2226      | 41628      | *561.78    | *245.1  | *134 | *15.8 | *69.8 | FL | *675.37 | *288.55 | *198 |
| 2330      | 49271      |       |    |   |   |   |   | *795.42 | *340.05 | *198 |
| 2334      | 57766      |       |    |   |   |   |   | *916.95 | *392.85 | *198 |

|      |   | 6 Row  | 8 Row       |
|-----------|--------|--------|-------------|
| Unit Spec | Air    |   |        |   |   |   |   |   |   |   |
| 39CBFI    | Volume | W Flow | Flow Resist | Loop | T. Cold | A. Cold | Air Resis | W Flow | Water Resi | Loop |
|      | (CMH)  | (L/s)  | (kPa)       |   | (kW) | (kW) | (Pa) | (L/s) | (kPa) |   |
| 0609      | 2209   | 1.9    | 63          | HF | 41.12 | 17.41 | 268 | 2 | 12.7 | FL |
| 0610      | 3058   | 2.4    | 18.8        | FL | 57.83 | 24.48 | 257 | 2.8 | 20.6 | FL |
| 0712      | 4417   | 3.6    | 31.6        | FL | 85.25 | 36.09 | 260 | 4.1 | 40.3 | FL |
| 0813      | 6286   | 5.3    | 52.6        | FL | 119.37 | 50.14 | 267 | 5.7 | 28.47 | DB |
| 0914      | 7306   | 6.1    | 64.9        | FL | 138.16 | 58.03 | 268 | 6.6 | 31.08 | DB |
| 1015      | 9429   | 7.7    | 36.15       | DB | 177.27 | 75.45 | 266 | 8.5 | 34.2 | DB |
| 1016      | 10364  | 8.5    | 38.88       | DB | 192.67 | 80.92 | 267 | 9.2 | 34.88 | DB |
| 1117      | 12912  | *8.5   | *40.12      | DB | *241.20 | *101.30 | *266 | *9.6 | *37.91 | DB |
| 1317      | 15121  | *10.1  | *38.93      | DB | *283.07 | *118.89 | *267 | *11.3 | *38.25 | DB |
| 1518      | 18689  | *11.6  | *41.76      | DB | *349.11 | *146.63 | *269 | *12.8 | *38.88 | DB |
| 1522      | 21238  | *11.9  | *51.7       | DB | *389.59 | *165.04 | *268 | *13.3 | *41.3 | DB |
| 1622      | 22937  | *13    | *53.9       | DB | *418.82 | *177.46 | *267 | *14.3 | *50 | DB |
| 1822      | 26335  | *14.8  | *52.36      | DB | *481.33 | *203.93 | *267 | *16.4 | *52.8 | DB |
| 1824      | 29733  | *15.6  | *57.6       | DB | *542.69 | *229.64 | *268 | *17.3 | *48 | DB |
| 1825      | 32281  | *15.9  | *58.7       | DB | *584.99 | *247.94 | *268 | *17.5 | *50.9 | DB |
| 2025      | 35679  | *17.5  | *60.6       | DB | *645.87 | *273.76 | *269 | *19.3 | *54.5 | DB |
| 2226      | 41628  | *19    | *60.4       | DB | *745.61 | *316.21 | *269 | *21 | *54.5 | DB |
| 2330      | 49271  | *21.9  | *69.2       | DB | *879.19 | *372.94 | *269 | *23.4 | *61.9 | DB |
| 2334      | 57766  | *21.9  | *76.7       | DB | *1016.91 | *431.73 | *269 | *24.3 | *72 | DB |

----

|      | Inlet temperature of hot water |
|-----------|--------------------------------|
| Unit Spec | 60 °C                     | 70 °C | 80°C |
| 39CBFI    | Heat                           | air resist | w resist | w Flow | Heat | air resist | w resist | w Flow | Heat | air resist | w resist | w Flow |
|      | (kW)                           | (Pa) | (kPa) | (L/s) | (kW) | (Pa) | (kPa) | (L/s) | (kW) | (Pa) | (kPa) | (L/s) |
| 0609      | 12.79                          | 55 | 1.0 | 0.3 | 20.22 | 56 | 2.2 | 0.5 | 22.92 | 57 | 2.8 | 0.5 |
| 0610      | 20.42                          | 56 | 2.8 | 0.5 | 78.58 | 60 | 4.8 | 0.7 | 32.38 | 54 | 6.4 | 0.8 |
| 0712      | 32.34                          | 58 | 4.2 | 0.8 | 41.72 | 58 | 6.6 | 1.0 | 47.19 | 55 | 8.6 | 1.1 |
| 0813      | 43.34                          | 54 | 7.0 | 1.0 | 60.47 | 57 | 8.7 | 1.3 | 72.16 | 62 | 10.1 | 1.4 |
| 0914      | 54.38                          | 61 | 7.5 | 1.2 | 69.91 | 58 | 11.8 | 1.6 | 83.63 | 62 | 12.8 | 1.7 |
| 1015      | 70.73                          | 60 | 10.4 | 1.6 | 90.73 | 61 | 16.4 | 2.1 | 108.46 | 61 | 17.7 | 2.2 |
| 1016      | 78.40                          | 55 | 13.2 | 1.8 | 92.25 | 60 | 17.8 | 2.1 | 119.29 | 61 | 18.8 | 2.2 |
| 1117      | 91.03                          | 55 | 17.4 | 2.1 | 115.38 | 56 | 24.1 | 2.5 | 137.06 | 55 | 24.6 | 2.5 |
| 1317      | 114.81                         | 61 | 21.3 | 2.5 | 134.37 | 55 | 26.9 | 2.8 | 160.37 | 55 | 28.7 | 3.0 |
| 1518      | 141.54                         | 62 | 25.5 | 3.0 | 166.57 | 62 | 34.5 | 3.5 | 198.72 | 56 | 36.9 | 3.7 |
| 1522      | 151.63                         | 58 | 16.0 | 3.2 | 196.27 | 59 | 26.0 | 4.1 | 235.90 | 61 | 29.5 | 4.3 |
| 1622      | 162.63                         | 58 | 17.4 | 3.4 | 211.41 | 59 | 29.2 | 4.4 | 258.37 | 61 | 36.4 | 5.2 |
| 1822      | 186.85                         | 55 | 22.1 | 3.9 | 242.87 | 60 | 37.3 | 5.1 | 291.96 | 61 | 42.4 | 5.4 |
| 1824      | 214.15                         | 59 | 29.2 | 4.5 | 276.48 | 58 | 47.2 | 5.7 | 333.27 | 55 | 50.9 | 6.1 |
| 1825      | 233.49                         | 61 | 33.7 | 4.8 | 302.41 | 60 | 56.8 | 6.2 | 363.08 | 61 | 64.7 | 6.6 |
| 2025      | 257.75                         | 57 | 40.1 | 5.3 | 333.67 | 58 | 67.4 | 6.8 | 398.91 | 61 | 70.7 | 7.1 |
| 2226      | 320.56                         | 58 | 55.7 | 6.6 | 374.32 | 57 | 70.5 | 7.5 | 445.08 | 55 | 72.8 | 7.6 |
| 2330      | 348.95                         | 60 | 58.4 | 7.0 | 461.95 | 60 | 71.1 | 9.0 | 530.27 | 55 | 75.8 | 11.5 |
| 2334      | 446.20                         | 58 | 66.2 | 9.7 | 553.49 | 58 | 74.4 | 11.3 | 660.44 | 61 | 79.8 | 11.7 |

| Unit Number | Pipe Coil Number |
|-------------|------------------|
| 39CBFI      | 2 Row            | 4 Row | 6 Row | 8 Row |
| 0609        | 35.30            | 73.16 | 77.70 | 83.92 |
| 0610        | 40.30            | 78.42 | 84.62 | 92.77 |
| 0712        | 42.60            | 89.86 | 98.80 | 104.68 |
| 0813        | 47.36            | 97.27 | 108.26 | 122.00 |
| 0914        | 51.30            | 103.46 | 115.90 | 131.38 |
| 1015        | 54.00            | 114.76 | 131.21 | 151.08 |
| 1016        | 56.36            | 119.38 | 137.55 | 159.12 |
| 1117        | 64.01            | 131.26 | 153.89 | 180.26 |
| 1317        | 69.90            | 142.88 | 169.35 | 187.94 |
| 1518        | 75.53            | 160.33 | 193.00 | 230.45 |
| 1522        | 111.54           | 178.95 | 217.85 | 256.74 |
| 1622        | 116.32           | 187.78 | 228.89 | 271.11 |
| 1822        | 124.14           | 204.02 | 252.26 | 300.51 |
| 1824        | 128.02           | 226.15 | 273.16 | 327.49 |
| 1825        | 129.86           | 228.14 | 288.05 | 347.01 |
| 2025        | 136.98           | 254.93 | 319.51 | 384.74 |
| 2226        | 166.16           | 284.69 | 359.83 | 435.83 |
| 2330        | 188.06           | 323.33 | 412.93 | 504.93 |
| 2334        | 206.11           | 363.44 | 468.24 | 576.24 |

----

| 39CBFI | A      | B      | øC                     | F      |
|--------|--------|--------|-----------------------------|--------|
| 0609   | 800    | 357    | 1—  ′′ | 233    |
|   |   |   | 1/2 MPT                     |   |
| 0610   | 800    | 421    | 1—  ′′ | 233    |
|   |   |   | 1/2 MPT                     |   |
| 0712   | 900    | 484    | 1—  ′′ | 233    |
|   |   |   | 1/2 MPT                     |   |
| 0813   | 1000   | 611    | 1—  ′′ | 233    |
| 0914   | 1100   | 675    | 1/2 MPT                     | 233    |
| 1015   | 1200   | 802    | 1—  ′′ | 233    |
|   |   |   | 1/2 MPT                     |   |
| 1016   | 1200   | 802    | 1—  ′′ | 233    |
|   |   |   | 1/2 MPT                     |   |
| 1117   | 1300   | 917    | 1—  ′′ | 240    |
|   |   |   | 1/2 MPT                     |   |
| 1317   | 1500   | 1107   | 1—  ′′ | 240    |
|   |   |   | 1/2 MPT                     |   |
| 1518   | 1700   | 1298   |                        | 240    |

| 39CBFI                                       | D  | E   | øC                  |
|----------------------------------------------|----|-----|--------------------------|
| 2 排   热水 | 55 | 138 | 1-1/2′′             |
| 4 排                                   | 91 | 173 |                     |
| 6 排                                   | 63 | 201 | 见上表 |
| 8 排                                   | 88 | 226 |                     |

| 39CBFI | A    | B    | øC      | F   |
|--------|------|------|--------------|-----|
| 1522   | 1700 | 1298 | 2′′ MPT | 240 |
| 1622   | 1800 | 1361 | 2′′ MPT | 240 |
| 1822   | 2000 | 1523 | 3′′ MPT | 254 |
| 1824   | 2000 | 1523 | 3′′ MPT | 254 |
| 1825   | 2000 | 1523 | 3′′ MPT | 254 |

| 39CBFI                                     | D   | E   | øC      |
|--------------------------------------------|-----|-----|--------------|
| 2 row hot water                            | 55  | 138 | 1-1/2′′ |
| 4 row(diameter 2′′ MPT) | 116 | 198 | Refer to     |
| 4 row(diameter 3′′ MPT) | 88  | 226 | above chart  |
| 6 row、8 row                         | 88  | 226 |         |

----

| 39CBFI | A    | B    | øC      | øF      |
|--------|------|------|--------------|--------------|
| 2025   | 2200 | 982  | 2′′ MPT | 3′′ MPT |
| 2226   | 2400 | 1173 | 2′′ MPT | 3′′ MPT |
| 2330   | 2500 | 1300 | 2′′ MPT | 3′′ MPT |
| 2334   | 2500 | 1300 | 2′′ MPT | 3′′ MPT |

| 39CBFI      | D1  | D2  | E1               | E2  | øC        |
|-------------|-----|-----|------------------|-----|----------------|
| 2 row hot   | 55  | 138 | 1-1/2” MPT |
| 4 row       | 116 | 88  | 198              | 226 | Refer to above |
| 6 row 8 Row | 88  | 226 | chart avove      |

| Unit Spec | Pipe Coil             | Steam         | Weight |
|-----------|-----------------------|---------------|--------|
| 39CBFI    | Type                  | Pressure(MPa) | kg     |
| 0609      | (GL-2R-09-06)× 1 | 28.3          | 32.6   | 36.2 | 45 |
| 0610      | (GL-2R-09-07)× 1 | 38.2          | 44.2   | 49.1 | 48 |
| 0712      | (GL-2R-11-09)× 1 | 53.9          | 62.3   | 69.1 | 57 |
| 0813      | (GL-2R-15-10)× 1 | 76.4          | 88.3   | 97.9 | 80 |
| 0914      | (GL-2R-17-11)× 1 | 92.1          | 106.5  | 118.1 | 98 |
| 1015      | (GL-2R-19-12)× 1 | 115.9         | 136.7  | 151.5 | 107 |
| 1016      | (GL-2R-19-13)× 1 | 129.6         | 149.9  | 166.2 | 114 |
| 1117      | (GL-2R-22-14)× 1 | 161.1         | 186.4  | 206.7 | 126 |
| 1317      | (GL-2R-13-14)× 2 | 188.5         | 217.9  | 241.6 | 167 |
| 1518      | (GL-2R-15-15)× 2 | 234.9         | 271.6  | 301.3 | 212 |
| 1522      | (GL-2R-15-19)× 2 | 271.4         | 313.8  | 348.1 | 243 |
| 1622      | (GL-2R-17-19)× 2 | 298.9         | 345.7  | 382.8 | 269 |
| 1822      | (GL-2R-19-19)× 2 | 345.6         | 399.4  | 442.7 | 286 |
| 1824      | (GL-2R-19-21)× 2 | 387.4         | 448.1  | 496.3 | 303 |
| 1825      | (GL-2R-19-22)× 2 | 416.6         | 481.7  | 533.0 | 320 |
| 2025      | (GL-2R-22-22)× 2 | 464.8         | 537.8  | 595.5 | 354 |
| 2226      | (GL-2R-22-23)× 2 | 525.6         | 607.3  | 672.5 | 374 |
| 2330      | (GL-2R-22-27)× 2 | 620.7         | 717.4  | 795.9 | 413 |
| 2334      | (GL-2R-22-31)× 2 | 724.0         | 835.8  | 927.9 | 471 |

| 注: Inlet Day-bulb temperature is 7oC .the weight on the chart only refers to the weight of pipe coil, exclusive of weight of box. |
|-----------------------------------------------------------------------------------------------------------------------------------------------------------|

----

| 39CBFI | A    | B   | øC      | F   |
|--------|------|-----|--------------|-----|
| 0609   | 800  | 287 | 2′′ MPT | 278 |
| 0610   | 800  | 287 | 2′′ MPT | 278 |
| 0712   | 900  | 358 | 2′′ MPT | 278 |
| 0813   | 1000 | 500 | 2′′ MPT | 278 |
| 0914   | 1100 | 571 | 2′′ MPT | 278 |
| 1015   | 1200 | 678 | 2′′ MPT | 278 |
| 1016   | 1200 | 678 | 2′′ MPT | 278 |
| 1117   | 1300 | 784 | 2′′ MPT | 278 |

| 39CBFI     | D  | E   |
|------------|----|-----|
| 2 排 | 80 | 154 |

| 39CBFI | A    | B   | øC      | F   |
|--------|------|-----|--------------|-----|
| 1317   | 1500 | 429 | 2′′ MPT | 278 |
| 1518   | 1700 | 500 | 2′′ MPT | 278 |
| 1522   | 1700 | 500 | 2′′ MPT | 278 |
| 1622   | 1800 | 571 | 2′′ MPT | 278 |
| 1822   | 2000 | 678 | 2′′ MPT | 278 |
| 1824   | 2000 | 678 | 2′′ MPT | 278 |
| 1825   | 2000 | 678 | 2′′ MPT | 278 |
| 2025   | 2200 | 784 | 2′′ MPT | 278 |
| 2226   | 2400 | 784 | 2′′ MPT | 478 |
| 2330   | 2500 | 784 | 2′′ MPT | 478 |
| 2334   | 2500 | 784 | 2′′ MPT | 478 |

| 39CBFI     | D  | E   |
|------------|----|-----|
| 2 排 | 80 | 154 |

----

| Unit Spec 39CBFI | Fitting Fan | Max Power ofFan(kW) | Max seat of Fan | Length of Fan Section(mm)HorizontaVertical | Weight(kg) |
|------------------|-------------|---------------------|-----------------|--------------------------------------------|------------|
| 0609             | ADZ180      | 1.5                 | Y90             | 600                                        | 900        | 20.55 |
| 0610             | ADZ180      | 2.2                 | Y100            | 600                                        | 900        | 20.55 |
| ADZ200           | 700         | 900                 | 23.21           |
| 0712             | ADZ225      | 3.7                 | Y112            | 700                                        | 900        | 32.98 |
| ADZ/RDZ250       | 700         | 900                 | 34.98/37.08     |
| 0813             | ADZ/RDZ280  | 5.5                 | Y132            | 800                                        | 900        | 41.44/43.64 |
| ADZ/RDZ315       | 800         | 900                 | 46.44/47.64     |
| 0914             | ADZ/RDZ315  | 5.5                 | Y132            | 800                                        | 900        | 46.44/47.64 |
| ADZ/RDZ355       | 900         | 900                 | 60.41/64.41     |
| 1015             | ADZ/RDZ355  | 7.5                 | Y132            | 900                                        | 900        | 60.41/64.41 |
| ADZ/RDZ400       | 900         | 900                 | 73.48/76.48     |
| 1016             | ADZ/RDZ355  | 7.5                 | Y132            | 900                                        | 900        | 64.21/68.21 |
| ADZ/RDZ400       | 900         | 900                 | 77.21/80.21     |
| 1117             | ADZ/RDZ400  | 11                  | Y160            | 900                                        | 900        | 79.02/82.02 |
| ADZ/RDZ450       | 1100        | 1100                | 88.02/97.52     |
| 1317             | ADZ/RDZ400  | 15                  | Y160            | 900                                        | 900        | 79.02/82.02 |
| ADZ/RDZ450       | 1100        | 1100                | 88.02/97.52     |
| 1518             | ADZ/RDZ450  | 15                  | Y160            | 1100                                       | 1100       | 88.02/97.52 |
| ADZ/RDZ500       | 1100        | 1100                | 97.16/108.16    |
| 1522             | ADZ/RDZ500  | 18.5                | Y180            | 1100                                       | 1100       | 97.16/108.16 |
| ADZ/RDZ560       | 1300        | 1300                | 186.0/195.0     |
| 1622             | ADZ/RDZ560  | 18.5                | Y180            | 1300                                       | 1300       | 186.0/195.0 |
| ADZ/RDZ630       | 1400        | 1400                | 250.0/253.0     |
| 1822             | ADZ/RDZ560  | 18.5                | Y180            | 1300                                       |       | 186.0/195.0 |
| ADZ/RDZ630       | 1400        |                | 250.0/253.0     |
| 1824             | ADZ/RDZ560  | 22                  | Y180            | 1300                                       |       | 186.0/195.0 |
| ADZ/RDZ630       | 1400        |                | 250.0/253.0     |
| 1825             | ADZ/RDZ630  | 30                  | Y200            | 1400                                       |       | 250.0/253.0 |
| ADZ/RDZ710       | 1500        |                | 281.0/323.0     |
| 2025             | ADZ/RDZ630  | 30                  | Y200            | 1400                                       |       | 250.0/253.0 |
| ADZ/RDZ710       | 1500        |                | 281.0/323.0     |
| 2226             | ADZ/RDZ710  | 30                  | Y200            | 1500                                       |       | 281.0/323.0 |
| ADZ/RDZ800       | 1700        |                | 370.0/405.0     |
| 2330             | ADZ/RDZ800  | 37                  | Y225            | 1700                                       |       | 370.0/405.0 |
| ADZ/RDZ900       | 1900        |                | 442.0/490.0     |
| 2334             | ADZ/RDZ800  | 45                  | Y225            | 1700                                       |       | 370.0/405.0 |
| ADZ/RDZ900       | 1900        |                | 442.0/490.0     |

----

| Unit Spec39CBFI | Fitting Fan | A      | D     | E     |
|----------------------|------------------|--------|-------|-------|
| THF                  | BHF              | UBF    | UBR   |
| 0609                 | ADZ180           | 289.5  | 229   | 290.5 | 193.5 | 125 | 222 |
| 0610                 | ADZ180           | 314.5  | 229   | 290.5 | 193.5 | 125 | 222 |
| ADZ200               | 312.5            | 256    | 298.5 | 192.5 | 125 | 231 |
| 0712                 | ADZ/RDZ225       | 411.5  | 288   | 312.5 | 192.5 | 125 | 268 |
| ADZ/RDZ250           | 411.5            | 322    | 324.0 | 192.0 | 125 | 257 |
| 0813                 | ADZ/RDZ280       | 392.5  | 361   | 340.5 | 193.5 | 125 | 306 |
| ADZ/RDZ315           | 349.5            | 404    | 359.5 | 191.5 | 125 | 293 |
| 0914                 | ADZ/RDZ315       | 399.5  | 404   | 359.5 | 191.5 | 125 | 293 |
| ADZ/RDZ355           | 391.5            | 453    | 384.5 | 194.5 | 125 | 315 |
| 1015                 | ADZ/RDZ355       | 441.5  | 453   | 384.5 | 194.5 | 125 | 315 |
| ADZ/RDZ400           | 391.5            | 507    | 413.0 | 193.0 | 125 | 345 |
| 1016                 | ADZ/RDZ355       | 491.5  | 453   | 384.5 | 194.5 | 125 | 315 |
| ADZ/RDZ400           | 491.5            | 507    | 413.0 | 193.0 | 125 | 345 |
| 1117                 | ADZ/RDZ400       | 541.5  | 507   | 413.0 | 193.0 | 125 | 345 |
| ADZ/RDZ450           | 424.5            | 569    | 441.5 | 193.5 | 125 | 373 |
| 1317                 | ADZ/RDZ400       | 541.5  | 507   | 413.0 | 193.0 | 125 | 345 |
| ADZ/RDZ450           | 379.5            | 569    | 441.5 | 193.5 | 125 | 373 |
| 1518                 | ADZ/RDZ450       | 429.5  | 569   | 441.5 | 193.5 | 125 | 373 |
| ADZ/RDZ500           | 410.5            | 638    | 463.5 | 193.5 | 125 | 395 |
| 1522                 | ADZ/RDZ500       | 610.5  | 638   | 463.5 | 193.5 | 125 | 395 |
| ADZ/RDZ560           | 617.5            | 715    | 554.5 | 253.5 | 125 | 426 |
| 1622                 | ADZ/RDZ560       | 617.5  | 715   | 554.5 | 253.5 | 125 | 426 |
| ADZ/RDZ630           | 531.5            | 801    | 596.5 | 252.5 | 125 | 469 |
| 1822                 | ADZ/RDZ560       | 617.5  | 715   | 554.5 | 253.5 | 125 | 426 |
| ADZ/RDZ630           | 531.5            | 801    | 596.5 | 252.5 | 125 | 469 |
| 1824                 | ADZ/RDZ560       | 717.5  | 715   | 554.5 | 253.5 | 125 | 426 |
| ADZ/RDZ630           | 691.5            | 801    | 596.5 | 252.5 | 125 | 469 |
| 1825                 | ADZ/RDZ630       | 741.5  | 801   | 596.5 | 252.5 | 125 | 469 |
| ADZ/RDZ710           | 629.5            | 898    | 644.5 | 253.5 | 125 | 516 |
| 2025                 | ADZ/RDZ630       | 741.5  | 801   | 596.5 | 252.5 | 125 | 469 |
| ADZ/RDZ710           | 629.5            | 898    | 644.5 | 253.5 | 125 | 516 |
| 2226                 | ADZ/RDZ710       | 679.5  | 898   | 644.5 | 253.5 | 125 | 516 |
| ADZ/RDZ800           | 620.0            | 1007   | 713.5 | 266.5 | 125 | 572 |
| 2330                 | ADZ/RDZ800       | 820.0  | 1007  | 713.5 | 266.5 | 125 | 572 |
| ADZ/RDZ900           | 792.0            | 1130   | 770.5 | 266.5 | 125 | 629 |
| 2334                 | ADZ/RDZ800       | 1020.0 | 1007  | 713.5 | 266.5 | 125 | 572 |
| ADZ/RDZ900           | 1167.0           | 1130   | 770.5 | 266.5 | 125 | 629 |

----

| Unit Spec39CBFI | Fitting Fan | A     | D      | E      |
|----------------------|------------------|-------|--------|--------|
| THF                  | BHF              | UBF   | UBR    |
| 0609                 | ADZ180           | 289.5 | 229    | 940.5  | 843.5 | 125 | 222 |
| 0610                 | ADZ180           | 339.5 | 229    | 940.5  | 843.5 | 125 | 222 |
| ADZ200               | 312.5            | 256   | 948.5  | 842.5  | 125 | 231 |
| 0712                 | ADZ/RDZ225       | 411.5 | 288    | 1062.5 | 842.5 | 125 | 268 |
| ADZ/RDZ250           | 411.5            | 322   | 1074.0 | 942.0  | 125 | 257 |
| 0813                 | ADZ/RDZ280       | 392.5 | 361    | 1190.5 | 1043.5 | 125 | 306 |
| ADZ/RDZ315           | 349.5            | 404   | 1209.5 | 1041.5 | 125 | 293 |
| 0914                 | ADZ/RDZ315       | 399.5 | 404    | 1309.5 | 1141.5 | 125 | 293 |
| ADZ/RDZ355           | 391.5            | 453   | 1334.5 | 1144.5 | 125 | 315 |
| 1015                 | ADZ/RDZ355       | 441.5 | 453    | 1434.5 | 1244.5 | 125 | 315 |
| ADZ/RDZ400           | 391.5            | 507   | 1463.0 | 1243.0 | 125 | 345 |
| 1016                 | ADZ/RDZ355       | 491.5 | 453    | 1434.5 | 1244.5 | 125 | 315 |
| ADZ/RDZ400           | 491.5            | 507   | 1463.0 | 1243.0 | 125 | 345 |
| 1117                 | ADZ/RDZ400       | 541.5 | 507    | 1563.0 | 1343.0 | 125 | 345 |
| ADZ/RDZ450           | 424.5            | 569   | 1591.5 | 1343.5 | 125 | 373 |
| 1317                 | ADZ/RDZ400       | 541.5 | 507    | 1763.0 | 1543.0 | 125 | 345 |
| ADZ/RDZ450           | 379.5            | 569   | 1791.5 | 1543.5 | 125 | 373 |
| 1518                 | ADZ/RDZ450       | 429.5 | 569    | 1991.5 | 1743.5 | 125 | 373 |
| ADZ/RDZ500           | 410.5            | 638   | 2013.5 | 1743.5 | 125 | 395 |
| 1522                 | ADZ/RDZ500       | 610.5 | 638    | 2013.5 | 1743.5 | 125 | 395 |
| ADZ/RDZ560           | 617.5            | 715   | 2104.5 | 1803.5 | 125 | 426 |
| 1622                 | ADZ/RDZ460       | 617.5 | 715    | 2204.5 | 1903.5 | 125 | 426 |
| ADZ/RDZ5630          | 531.5            | 801   | 2246.5 | 1902.5 | 125 | 469 |

----

| Unit Spec 39CBFI | Humidifying amount of  day steam kg/h | High Pressure spray amount高压喷雾量 kg/h |
|------------------|-------------------------------------------------|-------------------------------------------------------------------------|
| 0609             | 6.3~20                                          | 5~15                                                                    |
| 0610             | 10~40                                           | 5~15                                                                    |
| 0712             | 25~63                                           | 11~25                                                                   |
| 0813             | 20~80                                           | 15~35                                                                   |
| 0914             | 32~80                                           | 26~45                                                                   |
| 1015             | 40~80                                           | 36~65                                                                   |
| 1016             | 63~125                                          | 36~65                                                                   |
| 1117             | 80~160                                          | 46~80                                                                   |
| 1317             | 125~200                                         | 46~80                                                                   |
| 1518             | 125~200                                         | 66~110                                                                  |
| 1522             | 160~200                                         | 81~130                                                                  |
| 1622             | 160~200                                         | 81~130                                                                  |
| 1822             | 160~200                                         | 81~130                                                                  |
| 1824             | 200~315                                         | 111~140                                                                 |
| 1825             | 200~315                                         | 111~140                                                                 |
| 2025             | 315~400                                         | 141~180                                                                 |
| 2226             | 315~500                                         | 141~180                                                                 |
| 2330             | 315~630                                         | 150~220                                                                 |
| 2334             | 315~630                                         | 150~220                                                                 |

| Unit Spec39CBFI | Humidifying amount of wet film(kg / h) |
|-----------------|----------------------------------------|
| Efficient40%    | efficient 60%                          | efficient 75% | efficient 85% |
| 0609            | 5.8                                    | 8.6 | 10.8 | 11.5 |
| 0610            | 8.0                                    | 11.9 | 14.9 | 15.9 |
| 0712            | 11.5                                   | 17.2 | 21.5 | 23.0 |
| 0813            | 16.4                                   | 24.5 | 30.7 | 32.7 |
| 0914            | 19.0                                   | 28.5 | 35.6 | 38.0 |
| 1015            | 24.5                                   | 36.8 | 46.0 | 49.0 |
| 1016            | 27.0                                   | 40.4 | 50.0 | 53.9 |
| 1117            | 33.6                                   | 50.4 | 63.0 | 67.2 |
| 1317            | 39.3                                   | 59.0 | 73.8 | 78.7 |
| 1518            | 48.6                                   | 72.9 | 91.2 | 97.3 |
| 1522            | 55.3                                   | 82.9 | 103.6 | 110.5 |
| 1622            | 59.7                                   | 89.5 | 111.9 | 119.3 |
| 1822            | 68.5                                   | 102.8 | 128.5 | 137.0 |
| 1824            | 77.4                                   | 116.0 | 145.0 | 154.7 |
| 1825            | 84.0                                   | 126.0 | 157.5 | 168.0 |
| 2025            | 92.8                                   | 139.2 | 174.0 | 185.6 |
| 2226            | 108.3                                  | 162.4 | 203.0 | 216.6 |
| 2330            | 128.2                                  | 192.3 | 240.3 | 256.4 |
| 2334            | 150.3                                  | 225.4 | 281.8 | 300.6 |

----

| Unit Spec | First Grade Silencing(6M) | Weight |
|-----------|---------------------------|--------|
| 39CBFI    | 6M-I                      | 7M-I   | 8M-I | 9M-I | 10M-I | 11M-I | 12M-I | 6M-II | 7M-II | 8M-II | 9M-II | 10M-II | 11M-II | 12M-II | kg |
| 0609      | 2                         |   |   |   |   |   |   | 2 |   |   |   |   |   |   | 30 |
| 0610      | 2                         |   |   |   |   |   |   | 2 |   |   |   |   |   |   | 30 |
| 0712      |                      | 3      |   |   |   |   |   |   | 2 |   |   |   |   |   | 44 |
| 0813      |                      |   | 3 |   |   |   |   |   |   | 2 |   |   |   |   | 50 |
| 0914      |                      |   |   | 5 |   |   |   |   |   |   |   |   |   |   | 65 |
| 1015      |                      |   |   |   | 4 |   |   |   |   |   |   | 2 |   |   | 74 |
| 1016      |                      |   |   |   | 4 |   |   |   |   |   |   | 2 |   |   | 74 |
| 1117      |                      |   |   |   |   | 6 |   |   |   |   |   |   |   |   | 90 |
| 1317      | 6                         | 6      |   |   |   |   |   |   |   |   |   |   |   |   | 114 |
| 1518      |                      | 5      | 5 |   |   |   |   |   | 2 | 2 |   |   |   |   | 136 |
| 1522      |                      | 6      | 6 |   |   |   |   |   | 2 | 2 |   |   |   |   | 158 |
| 1622      |                      |   | 12 |   |   |   |   |   |   | 4 |   |   |   |   | 170 |
| 1822      |                      |   |   | 12 |   |   |   |   |   |   | 4 |   |   |   | 190 |
| 1824      |                      |   |   | 14 |   |   |   |   |   |   | 4 |   |   |   | 216 |
| 1825      |                      |   |   | 14 |   |   |   |   |   |   | 4 |   |   |   | 216 |
| 2025      |                      |   |   |   | 14 |   |   |   |   |   |   | 4 |   |   | 228 |
| 2226      |                      |   |   |   |   | 14 |   |   |   |   |   |   |   |   | 210 |
| 2330      |                      |   |   |   |   | 9 | 9 |   |   |   |   |   | 2 | 2 | 325 |
| 2334      |                      |   |   |   |   | 10 | 10 |   |   |   |   |   | 2 | 2 | 356 |

| Unit Spec | Second Silencing (12M) | Weight |
|-----------|------------------------|--------|
| 39CBFI    | 6M-I                   | 7M-I   | 8M-I | 9M-I | 10M-I | 11M-I | 12M-I | 6M-II | 7M-II | 8M-II | 9M-II | 10M-II | 11M-II | 12M-II | kg |
| 0609      | 4                      |   |   |   |   |   |   | 4 |   |   |   |   |   |   | 60 |
| 0610      | 4                      |   |   |   |   |   |   | 4 |   |   |   |   |   |   | 60 |
| 0712      |                   | 6      |   |   |   |   |   |   | 4 |   |   |   |   |   | 88 |
| 0813      |                   |   | 6 |   |   |   |   |   |   | 4 |   |   |   |   | 100 |
| 0914      |                   |   |   | 10 |   |   |   |   |   |   |   |   |   |   | 130 |
| 1015      |                   |   |   |   | 8 |   |   |   |   |   |   | 4 |   |   | 148 |
| 1016      |                   |   |   |   | 8 |   |   |   |   |   |   | 4 |   |   | 148 |
| 1117      |                   |   |   |   |   | 12 |   |   |   |   |   |   |   |   | 180 |
| 1317      | 12                     | 12     |   |   |   |   |   |   |   |   |   |   |   |   | 228 |
| 1518      |                   | 10     | 10 |   |   |   |   |   | 4 | 4 |   |   |   |   | 272 |
| 1522      |                   | 12     | 12 |   |   |   |   |   | 4 | 4 |   |   |   |   | 316 |
| 1622      |                   |   | 24 |   |   |   |   |   |   | 8 |   |   |   |   | 340 |
| 1822      |                   |   |   | 24 |   |   |   |   |   |   | 8 |   |   |   | 380 |
| 1824      |                   |   |   | 28 |   |   |   |   |   |   | 8 |   |   |   | 432 |
| 1825      |                   |   |   | 28 |   |   |   |   |   |   | 8 |   |   |   | 432 |
| 2025      |                   |   |   |   | 28 |   |   |   |   |   |   | 8 |   |   | 456 |
| 2226      |                   |   |   |   |   | 28 |   |   |   |   |   |   |   |   | 420 |
| 2330      |                   |   |   |   |   | 18 | 18 |   |   |   |   |   | 4 | 4 | 650 |
| 2334      |                   |   |   |   |   | 20 | 20 |   |   |   |   |   | 4 | 4 | 712 |

----

| Filter                                                                                    |   |                                        |
|-------------------------------------------------------------------------------------------|--------|---------------------------------------------|
| In accordance with demand of functions, there are several filters can be selected  : |
| 1” thk external pump speedy filter                                                  |   | 2” thk external pump low speed filter |
| 1” thk internal pump speedy filter                                                  |   | 2” thk internal pump low speed filter |
| Internal preliminary bag filter                                                           |   | internal sub-efficiency bag filter          |
| Preliminary and medial filter performance                                                 |   |                                        |
| filter efficiency: Board- preliminary G3 Grade, bag medium F5 Grade                       |   |                                        |

----

| Unit Spec | Board Filter External Specification η=G3 | weightkg       |
|-----------|-----------------------------------------------|----------------|
| 39CBFI    | 392 × 395                                | 492 × 395 | 592 × 395 | 692 × 395 | 392 × 495 | 492 × 495 | 592 × 495 | thk 1” | thk 2” |
| 0609      | 2                                             |           |   |   |   |   |   | 2.6 | 3.1 |
| 0610      | 2                                             |           |   |   |   |   |   | 2.6 | 3.1 |
| 0712      |                                          |           |   |   |   | 2 |   | 3.2 | 3.8 |
| 0813      |                                          |           | 3 |   |   |   |   | 4.8 | 5.8 |
| 0914      |                                          |           |   | 3 |   |   |   | 5.1 | 6.1 |
| 1015      | 4                                             |           |   |   | 2 |   |   | 8.2 | 9.8 |
| 1016      | 2                                             |           |   |   | 4 |   |   | 8.6 | 10.3 |
| 1117      |                                          |           |   |   | 3 | 3 |   | 9.3 | 11.2 |
| 1317      |                                          |           |   |   |   | 3 | 3 | 10.2 | 12.2 |
| 1518      | 8                                             | 4              |   |   |   |   |   | 16.4 | 19.7 |
| 1522      |                                          |           |   |   | 8 | 4 |   | 18.4 | 22.1 |
| 1622      |                                          |           |   |   | 4 | 8 |   | 18.8 | 22.6 |
| 1822      |                                          |           |   |   | 4 |   | 8 | 20.4 | 24.5 |
| 1824      | 3                                             |           | 6 |   | 2 |   | 4 | 23.7 | 28.4 |
| 1825      | 2                                             |           | 4 |   | 3 |   | 6 | 24.3 | 29.2 |
| 2025      | 4                                             | 4              |   |   | 6 | 6 |   | 29.8 | 35.8 |
| 2226      |                                          | 4              |   |   |   | 16 |   | 31.6 | 37.9 |
| 2330      |                                          | 6              | 2 |   |   | 12 | 4 | 38.6 | 46.3 |
| 2334      |                                          | 9              | 3 |   |   | 12 | 4 | 44.7 | 53.6 |

| Unit Spec | Board Internal Filter Specification=G3 | Weightkg       |
|-----------|----------------------------------------|----------------|
| 39CBFI    | 290 × 595                         | 390 × 493 | 390 × 595 | 595 × 595 | thk 1” | thk 2” |
| 0609      |                                   | 2              |   |   | 2.8 | 3.4 |
| 0610      |                                   | 2              |   |   | 2.8 | 3.4 |
| 0712      | 3                                      |           |   |   | 3.5 | 4.2 |
| 0813      |                                   |           |   | 2 | 5.4 | 6.5 |
| 0914      | 2                                      |           | 2 |   | 6.0 | 7.2 |
| 1015      | 2                                      |           |   | 2 | 6.4 | 7.7 |
| 1016      | 3                                      |           |   | 2 | 7.6 | 9.1 |
| 1117      |                                   |           | 3 | 2 | 8.2 | 9.8 |
| 1317      | 2                                      |           |   | 4 | 11.0 | 13.2 |
| 1518      |                                   |           | 2 | 4 | 11.0 | 13.2 |
| 1522      | 2                                      |           |   | 6 | 14.4 | 17.3 |
| 1622      | 5                                      |           |   | 6 | 18.0 | 21.6 |
| 1822      | 5                                      |           |   | 6 | 18.9 | 22.7 |
| 1824      | 2                                      |           | 3 | 6 | 19.5 | 23.4 |
| 1825      | 4                                      |           |   | 8 | 22.0 | 26.4 |
| 2025      |                                   |           |   | 12 | 24.0 | 28.8 |
| 2226      | 4                                      |           |   | 12 | 28.8 | 34.6 |
| 2330      | 7                                      |           |   | 12 | 34.5 | 41.4 |
| 2334      | 8                                      |           |   | 15 | 39.6 | 47.5 |

----

| Unit Spec | Bag internal filter Specification η=F5 | weight  |
|-----------|---------------------------------------------|---------|
| kg        |
| 39CBFI    | 290X595                                     | 390X493 | 390X595 | 595X595 | 590X290 | 590X390 | thk 1” | thk 2” |
| 0609      |                                        | 2       |   |   |   |   | 2.2 | 2.6 |
| 0610      |                                        | 2       |   |   |   |   | 2.2 | 2.6 |
| 0712      | 3                                           |    |   |   |   |   | 2.6 | 3.1 |
| 0813      |                                        |    |   | 2 |   |   | 5.0 | 6.0 |
| 0914      |                                        |    |   |   | 2 | 2 | 5.2 | 6.2 |
| 1015      |                                        |    |   | 2 | 2 |   | 5.2 | 6.2 |
| 1016      | 1                                           |    |   | 2 | 2 |   | 5.9 | 7.1 |
| 1117      |                                        |    | 1 | 2 |   | 2 | 6.5 | 7.8 |
| 1317      | 2                                           |    |   | 4 |   |   | 8.0 | 9.6 |
| 1518      |                                        |    | 2 | 4 |   |   | 8.0 | 9.6 |
| 1522      | 2                                           |    |   | 6 |   |   | 10.6 | 12.7 |
| 1622      | 2                                           |    |   | 6 | 3 |   | 14.2 | 17.0 |
| 1822      | 2                                           |    |   | 6 | 3 |   | 14.5 | 17.4 |
| 1824      | 2                                           |    |   | 6 |   | 3 | 14.7 | 17.6 |
| 1825      |                                        |    |   | 8 | 4 |   | 16.4 | 19.7 |
| 2025      |                                        |    |   | 12 |   |   | 16.8 | 20.2 |
| 2226      |                                        |    |   | 12 | 4 |   | 21.6 | 25.9 |
| 2330      | 3                                           |    |   | 12 | 4 |   | 25.6 | 30.7 |
| 2334      | 3                                           |    |   | 15 | 5 |   | 30.3 | 36.4 |

| 机组规格 | Box Efficient filter Specification η=H11 | weight |
|----------------------------------|-----------------------------------------------|--------|
| kg                               |
| 39CBFI                           | 290X595                                       | 390X   | 493 | 390X595 | 595X595 | thk 12” |
| 0609                             |                                          | 2      |   |   |   | 29.0 |
| 0610                             |                                          | 2      |   |   |   | 29.0 |
| 0712                             | 3                                             |   |   |   |   | 39.0 |
| 0813                             |                                          |   |   |   | 2 | 44.0 |
| 0914                             | 2                                             |   |   | 2 |   | 61.0 |
| 1015                             | 2                                             |   |   |   | 2 | 70.0 |
| 1016                             | 3                                             |   |   |   | 2 | 83.0 |
| 1117                             |                                          |   |   | 3 | 2 | 96.5 |
| 1317                             | 2                                             |   |   |   | 4 | 114.0 |
| 1518                             |                                          |   |   | 2 | 4 | 123.0 |
| 1522                             | 2                                             |   |   |   | 6 | 158.0 |
| 1622                             | 5                                             |   |   |   | 6 | 197.0 |
| 1822                             | 5                                             |   |   |   | 6 | 197.0 |
| 1824                             | 2                                             |   |   | 3 | 6 | 210.5 |
| 1825                             | 4                                             |   |   |   | 8 | 228.0 |
| 2025                             |                                          |   |   |   | 12 | 264.0 |
| 2226                             | 4                                             |   |   |   | 12 | 316.0 |
| 2330                             | 7                                             |   |   |   | 12 | 355.0 |
| 2334                             | 8                                             |   |   |   | 15 | 434.0 |

| Purification level                                      |         |              |   |   |         |   |   |      |   |   |
|---------------------------------------------------------|--------------|-------------------|--------|--------|--------------|--------|--------|-----------|--------|--------|
| US Fed. Std. 209D                                       | 100,000      |              | 10,000 | 1,000  | 100          |   | 10     | 1         |   | 0.1    |
| US Fed. Std. 209E                                       | M6.5         |              | M5.5   | M4.5   | M3.5         |   | M2.5   | M1.5      |   | M0.5   |
| Purification Level VDI 2083                             | 6            |              | 5      | 4      | 3            |   | 2      | 1         |   | 0      |
| Flow form                                               | Tangled Flow | Transitional Flow |   |   | horizon Flow |   |   |
| filterFilingRtae(%)                                     | 5~10         |              | 10~20  | 30~70  | >80       |   |   | >90    |   |   |
| First gradefilteringlevel                               |         | G4                |   |   | F5           |   |   |      | F6     |   |
| Second Gradefiltering levelDIN EN 779DIN 24 183/EN 1822 |         |              | F7     |   |         | F9H10  |   | H10H12H13 |   | H13    |
| Third GradeFitering Level                               |         | H12H13            |   | H13    | H14          |   | H15    | H16       |   | H17    |

----

| Model selection regulation of Electrical heating pipe coil |
|------------------------------------------------------------|
| Unit Type                                                  | V Area | Single row electrical | weight | Second row electrical | Third row electrical Wgt. |
| 39CBFI                                                     | 单根最大功率(W) | (m2) | Heating (kW) | kg | Heating | weight | Heating |   |
| 0609                                                       | 810 | 0.26 | < 5 | 17 | 5~10 | 21.0 | 10~14 | 25.0 |
| 0610                                                       | 960 | 0.30 | < 6 | 18 | 6~12 | 22.0 | 12~18 | 26.0 |
| 0712                                                       | 1260 | 0.48 | < 8 | 27.5 | 8~16 | 32.5 | 16~22 | 37.5 |
| 0813                                                       | 1410 | 0.63 | < 13 | 30.5 | 13~26 | 39.5 | 26~38 | 48.5 |
| 0914                                                       | 1560 | 0.80 | < 14.5 | 35 | 14.5~29 | 44.5 | 29~43 | 54.0 |
| 1015                                                       | 1710 | 1.00 | < 20.5 | 42 | 20.5~41 | 55.5 | 41~60 | 69.0 |
| 1016                                                       | 1860 | 1.08 | < 22.5 | 43.7 | 22.5~45 | 58.2 | 45~65 | 72.7 |
| 1117                                                       | 2010 | 1.31 | < 24 | 47.6 | 24~48 | 63.2 | 48~70 | 78.6 |
| 1317                                                       | 2010 | 1.58 | < 30 | 56.5 | 30~60 | 76.0 | 60~85 | 95.5 |
| 1518                                                       | 2360 | 2.00 | < 36 | 63 | 36~72 | 84.0 | 72~105 | 105.0 |
| 1522                                                       | 2960 | 2.53 | < 44 | 70 | 44~88 | 96.0 | 88~130 | 122.0 |
| 1622                                                       | 2960 | 2.72 | < 46 | 74 | 46~92 | 100.0 | 92~135 | 126.0 |
| 1822                                                       | 2960 | 3.10 | < 53 | 73 | 53~106 | 114.0 | 106~155 | 145.0 |
| 1824                                                       | 3260 | 3.42 | < 59 | 95.5 | 59~118 | 130.5 | 118~175 | 165.5 |
| 1825                                                       | 3410 | 3.59 | < 61 | 97.2 | 61~122 | 133.2 | 122~180 | 169.2 |
| 2025                                                       | 3410 | 4.02 | < 72 | 107 | 72~144 | 149.0 | 144~210 | 191.0 |
| 2226                                                       | 3560 | 4.66 | < 85 | 121.5 | 85~170 | 171.5 | 170~250 | 221.5 |
| 2330                                                       | 4160 | 5.74 | < 100 | 137 | 100~200 | 196.0 | 200~280 | 255.0 |
| 2334                                                       | 5360 | 6.61 | < 125 | 148.5 | 125~250 | 216.5 | 250~340 | 284.5 |

| Unit Weight | 39CBFI | 39CBFI |
|-------------|--------|--------|
| 39CBFI      | 3M     | 6M     | 9M | 12M | head Face |
| 0609        | 56.7   | 81.3   | 105.6 | 130.7 | 8.4 |
| 0610        | 60.2   | 86.0   | 111.9 | 138.5 | 9.4 |
| 0712        | 70.5   | 100.3  | 129.2 | 159.4 | 13.5 |
| 0813        | 79.4   | 111.0  | 144.5 | 178.1 | 16.9 |
| 0914        | 84.1   | 119.3  | 155.0 | 190.5 | 20.8 |
| 1015        | 88.3   | 127.3  | 165.5 | 204.8 | 24.9 |
| 1016        | 92.1   | 132.2  | 171.3 | 211.5 | 26.6 |
| 1117        | 97.7   | 140.3  | 182.7 | 224.4 | 31.3 |
| 1317        | 102.1  | 146.9  | 191.7 | 235.8 | 37.0 |
| 1518        | 109.9  | 158.2  | 206.7 | 254.4 | 45.5 |
| 1522        | 143.4  | 198.9  | 253.0 | 307.8 | 55.9 |
| 1622        | 145.5  | 202.2  | 257.4 | 313.5 | 59.8 |
| 1822        | 148.8  | 207.8  | 265.3 | 323.7 | 71.4 |
| 1824        | 159.8  | 221.3  | 283.6 | 346.8 | 73.7 |
| 1825        | 164.3  | 226.9  | 290.5 | 262.8 | 76.9 |
| 2025        | 168.5  | 233.6  | 299.4 | 366.0 | 85.6 |
| 2226        | 177.1  | 245.8  | 315.2 | 385.3 | 98.4 |
| 2330        | 197.0  | 271.6  | 346.8 | 422.3 | 119.1 |
| 2334        | 214.0  | 293.2  | 373.4 | 453.6 | 135.3 |

----

----

|   | · | Modules design, parts have strong commonality, easy change |
|--------|--------|------------------------------------------------------------|

|   | · | Double panel structure, 50mm foam 50mm foam panel is light and rigid, and its thermal conductivity is less than 0.0199W/M.°C |
|--------|--------|-----------------------------------------------------------------------------------------------------------------------------------|

|    | · | The down drain method ensures all the condensed water discharged. 。 |
|--------------|--------|----------------------------------------------------------------------------|

|   | · | Using corrugated link mechanism adjustment, and air damper can open flexibly. Electric remote control device can be installed. |
|--------|--------|--------------------------------------------------------------------------------------------------------------------------------|

|   | · | Pipe coil header is steel header, and copper header is available if user has such requirement. The drain valve and air evacuation valve are installed on pipe coil header to ensure no air on loop, meanwhile empty standing water inside pipe coil to avoid frost crack. |
|--------|--------|---------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

|   | · | Preliminary  filter is board structure , and efficiency reaches G4 Grade |
|--------|--------|------------------------------------------------------------------------------------|

----

|   | · | The product is China’s first air conditioner to gain EUROVENT. The certificate ensures the real performance is not less than that of sample product. |
|--------|--------|------------------------------------------------------------------------------------------------------------------------------------------------------------|

|   | · | EUROVENT is the professional standard to modular air conditioner, which is widely accepted in the world. The standard is taken charge by France EUROVENT Institute, which is one of international authorized certification authority. |
|--------|--------|---------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

|   | · | EUROVENT includes EN1886 and EN13053 |
|--------|--------|--------------------------------------|

|   | · | EN1886 is for mechanical features of modular air conditioner, including mechanical strength of chassis, cold bridge factor, heat transfer coefficient, air leakage rate, by-pass rate of filter, sound insulation of chassis. EN13053 mainly aims at air conditioners that its whole performance precedes calculated value of model selection program. |
|--------|--------|--------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| ChassisGrade | Max Re. Deflect(mm.m-1) | Bear MaxAir Press |
|--------------|-----------------------------------|-----------------------------|
| 1            | 10                                | No                          |
| 1A           | 10                                | Yes                         |
| 2            | 4                                 | No                          |
| 2A           | 4                                 | Yes                         |

| Class TB1 | 0.75 < Kb ≤ 1                                                                                                                    |
|-----------|-----------------------------------------------------------------------------------------------------------------------------------------------|
| Class TB2 | 0.6 < Kb ≤ 0.75                                                                                                                  |
| Class TB3 | 0.45 < Kb ≤ 0.6                                                                                                                  |
| Class TB4 | 0.3 < Kb ≤ 0.45                                                                                                                  |
| Class TB5 | No Requirement                  无要求 |

| Leakage Class | Max Air Leak Rate l/sm2                  最大漏风率 l/sm2 |
|--------------------|---------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|
| 3A                 | 5.70                                                                                                                                                                                        |
| A                  | 1.90                                                                                                                                                                                        |
| B                  | 0.63                                                                                                                                                                                        |
| C                  | 0.21                                                                                                                                                                                        |

|   | · | Excellent air tightness: case of unit consists of panel, frame and gland strip.The panel adopts unique embedding method, so that connection points can be connected precisely. The new gland strip is applied between frame and panel, and each access door and pass-through of pipes has been meticulously designed to ensure air tightness of unit. It completely complies with or beyond the GB/T14294-93. |
|--------|--------|---------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

----

|      |          | Outline dimension |       |    |               |    |
|-----------|---------------|-------------------|------------|---------|--------------------|---------|
| Unit spec | Pipe coil ft. |              | Air Volume |    | excess pressure of |
| 39CBF     | area(m2)      | H*                | W          | 2.25m/s | 2.5m/s             | 2.75m/s | outlet |
|      |          |              |       |    |               |    | Pa |
|      |          |              |       |    |               |    |   |
| 0609      | 0.24          | 710               | 1010       | 2008    | 2209               | 2430    | 200~800 |
|      |          |              |       |    |               |    |   |
| 0610      | 0.34          | 710               | 1110       | 2755    | 3058               | 3364    | 200~800 |
|      |          |              |       |    |               |    |   |
| 0712      | 0.49          | 810               | 1310       | 3979    | 4417               | 4859    | 200~800 |
|      |          |              |       |    |               |    |   |
| 0813      | 0.70          | 910               | 1410       | 5663    | 6286               | 6915    | 200~800 |
|      |          |              |       |    |               |    |   |
| 0914      | 0.81          | 1010              | 1510       | 6582    | 7306               | 8037    | 200~800 |
|      |          |              |       |    |               |    |   |
| 1015      | 1.05          | 1110              | 1610       | 8495    | 9429               | 10372   | 200~800 |
|      |          |              |       |    |               |    |   |
| 1016      | 1.15          | 1110              | 1710       | 9337    | 10364              | 11400   | 200~800 |
|      |          |              |       |    |               |    |   |
| 1117      | 1.44          | 1210              | 1810       | 11632   | 12912              | 14703   | 200~800 |
|      |          |              |       |    |               |    |   |
| 1317      | 1.68          | 1410              | 1810       | 13623   | 15121              | 16633   | 200~800 |
|      |          |              |       |    |               |    |   |
| 1518      | 2.07          | 1610              | 1910       | 16837   | 18689              | 20558   | 200~800 |
|      |          |              |       |    |               |    |   |
| 1522      | 2.36          | 1610              | 2310       | 19133   | 21238              | 23362   | 200~800 |
|      |          |              |       |    |               |    |   |
| 1622      | 2.55          | 1710              | 2310       | 20664   | 22937              | 25231   | 200~800 |
|      |          |              |       |    |               |    |   |
| 1822      | 2.93          | 1910              | 2310       | 23725   | 26335              | 28968   | 200~800 |
|      |          |              |       |    |               |    |   |
| 1824      | 3.30          | 1910              | 2510       | 26786   | 29733              | 32706   | 200~800 |
|      |          |              |       |    |               |    |   |
| 1825      | 3.59          | 1910              | 2610       | 29082   | 32281              | 35509   | 200~800 |
|      |          |              |       |    |               |    |   |
| 2025      | 3.96          | 2110              | 2610       | 30143   | 35679              | 39247   | 200~800 |
|      |          |              |       |    |               |    |   |
| 2226      | 4.63          | 2310              | 2710       | 37501   | 41626              | 45789   | 200~800 |
|      |          |              |       |    |               |    |   |
| 2330      | 5.48          | 2410              | 3110       | 44388   | 49271              | 54198   | 200~800 |
|      |          |              |       |    |               |    |   |
| 2334      | 6.42          | 2410              | 3510       | 52041   | 57766              | 63543   | 200~800 |
|      |          |              |       |    |               |    |   |
| 2532      | 8.13          | 2610              | 3310       | 65853   | 73170              | 80487   | 200~800 |
|      |          |              |       |    |               |    |   |
| 2832      | 9.01          | 2910              | 3310       | 72973   | 81081              | 89198   | 200~800 |
|      |          |              |       |    |               |    |   |
| 3132      | 9.98          | 3210              | 3310       | 80838   | 89820              | 98802   | 200~800 |
|      |          |              |       |    |               |    |   |
| 3438      | 12.36         | 3510              | 3910       | 100116  | 111240             | 122364  | 200~800 |
|      |          |              |       |    |               |    |   |
| 3841      | 14.69         | 3910              | 4210       | 118989  | 132210             | 145431  | 200~800 |
|      |          |              |       |    |               |    |   |
| 4444      | 17.72         | 4510              | 4510       | 143532  | 159480             | 175428  | 200~800 |
|      |          |              |       |    |               |    |   |
| 4750      | 22.01         | 4810              | 5110       | 178281  | 198090             | 217899  | 200~800 |

----

----

----