----

|   |    |  Carrier China Carrier is affiliated to United Technologies. United Technologies ranks 126 in world’s 500 tops (2006), its business extends to architectural industry and aerospace industry around the world. In 1902, Professor Carrier invented first set of scientific air-conditioning system. Since then, carrier’s complete series products and system resolution have become first choice of many world-renowned buildings. In 2007, carrier’s sales revenue reaches 14.6 billion US dollars, leading in the whole industry. Its distributors’ network covers over 170 countries. Carrier is now world’s biggest HVAC manufacturer. Carrier China has 11 companies, 40 sales service offices and 2,500 employees. As the world-class factory, Carrier Yileng has several advanced production lines of units and compressors, covering main units of commercial and residential central air-conditioning systems and air terminal products. The various products can meet diversifying demands from different customers. |
|--------|--------------|---------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| Index                                     |   |   |
|-------------------------------------------|--------|--------|
|                                      |   |   |
| Type Explanation                          |   | 1      |
| Specification                             |   | 1      |
| Cooling Capacity                          |   | 1      |
|                                      |   |   |
| Characteristics of units                  |   | 2      |
|                                      |   |   |
| Performance Table                         |   | 4      |
|                                      |   |   |
| Outline Dimensions                        |   | 8      |
|                                      |   |   |
| Unit Hoisting                             |   | 12     |
| Foundation Dimensions                     |   | 12     |
|                                      |   |   |
| Ice Storage Application Performance Table |   | 13     |
| Option Explanation                        |   | 13     |
| On-site Wiring Diagram                    |   | 13     |

----

|                                           |   |                                |   |    |   |   |   |   |
|------------------------------------------------|--------|-------------------------------------|--------|---------|--------|--------|--------|--------|
|                                      |   |                                |   |    |   | 30HXY  |   | 30HXC  |
| Type                                           |   | 110B                                |   | 130B    |   | 165B   |   | 200B   |   | 250B |   | 300B |   | 350B |   | 400B |
| Nominal Cooling Capacity                       |   | kW                                  |   | 329     |   | 455    |   | 574    |   | 686 |   | 875 |   | 1027 |   | 1204 |   | 1366 |
| Cold Amount Regulation Number                  |   | 104kcal/h                           |   | 30      |   | 40     |   | 50     |   | 60 |   | 75 |   | 90 |   | 105 |   | 120 |
|                                           |   |                                |   |    |   | 3      |   | 6      |   | 6 |   | 6 |   | 8 |   | 8 |   | 10 |   | 10 |
| Minimum Cold Amount                            |   | %                                   |   | 40      |   | 19     |   | 19     |   | 21 |   | 14 |   | 14 |   | 10 |   | 10 |
| Compressor                                     |   | Loop A                              |   | No      |   | 1      |   | 2      |   | 2 |   | 2 |   | 2 |   | 2 |   | 2 |   | 2 |
|                                           |   | Loop B                              |   | No      |   | -      |   | -      |   | - |   | - |   | 1 |   | 1 |   | 2 |   | 2 |
|                                           |   | In/out Water Temperature            |   | °C |   |   |   |   |   |   |   | 12/7 |   |   |   |   |   |   |
| Evaporatorr                                    |   | Flow Rate                           |   | m3/h    |   | 57     |   | 78     |   | 99 |   | 118 |   | 150 |   | 177 |   | 207 |   | 235 |
|                                           |   | Water Pressure Drop                 |   | kPa     |   | 65     |   | 45     |   | 50 |   | 66 |   | 66 |   | 73 |   | 74 |   | 75 |
|                                           |   | In/out Diameter                     |   | Dg      |   | 100    |   | 125    |   | 125 |   | 125 |   | 150 |   | 150 |   | 200 |   | 200 |
|                                           |   | In/out Water Temperature            |   | °C |   |   |   |   |   |   |   | 30/35 |   |   |   |   |   |   |
| Condenser                                      |   | Flow Rate                           |   | m3/h    |   | 69     |   | 95     |   | 120 |   | 143 |   | 182 |   | 214 |   | 251 |   | 284 |
|                                           |   | Water Pressure Drop                 |   | kPa     |   | 63     |   | 83     |   | 77 |   | 69 |   | 68 |   | 59 |   | 68 |   | 69 |
|                                           |   | In/out Diameter                     |   | Dg      |   | 125    |   | 125    |   | 125 |   | 125 |   | 200 |   | 200 |   | 200 |   | 200 |
|                                           |   | Power Supply                        |   |    |   |   |   |   |   |   |   | 380V-3Ph-50Hz |   |   |   |   |   |   |
| Motor                                          |   | Input Power Rated operational       |   | kW      |   | 71     |   | 98     |   | 122 |   | 144 |   | 186 |   | 217 |   | 256 |   | 288 |
|                                           |   | power                               |   | A       |   | 134    |   | 172    |   | 214 |   | 253 |   | 218/108 |   | 254/127 |   | 225/225 |   | 253/253 |
|                                           |   | (Star /Triangle ) Max |   |    |   |   |   |   |   |   |   |   |   |   |   |   |   |   |   |   |
|                                           |   | Current for Start Up                |   | A       |   | 328    |   | 314    |   | 374 |   | 465 |   | 443/288 |   | 510/351 |   | 443/443 |   | 510/510 |
| HFC-134a                                       |   | Loop A                              |   | kg      |   | 78     |   | 90     |   | 102 |   | 130 |   | 107 |   | 120 |   | 90 |   | 110 |
| Filling Amount                                 |   | Loop B                              |   | kg      |   | -      |   | -      |   | - |   | - |   | 75 |   | 80 |   | 109 |   | 137 |
| Unit Weight(Include Refrigerant) |   | kg                                  |   | 1929    |   | 2446   |   | 2520   |   | 2957 |   | 4258 |   | 4378 |   | 5055 |   | 5223 |
| Operational Weight                             |   | kg                                  |   | 2089    |   | 2589   |   | 2685   |   | 3153 |   | 4618 |   | 4738 |   | 5518 |   | 5686 |
| Outline Dimensions                             |   | Length                              |   | mm      |   | 2556   |   | 2988   |   | 2988 |   | 2988 |   | 3512 |   | 3512 |   | 4021 |   | 4021 |
|                                           |   | Width                               |   | mm      |   | 980    |   | 980    |   | 980 |   | 980 |   | 1015 |   | 1015 |   | 1015 |   | 1015 |
|                                           |   | Height                              |   | mm      |   | 1910   |   | 1816   |   | 1816 |   | 1921 |   | 2060 |   | 2060 |   | 2112 |   | 2112 |

----

| 1. | Powerful Pro-Dialog control system, direct-viewing display, and simple operation |
|----|----------------------------------------------------------------------------------|

| 2. | Full-liquid evaporator with reinforced heat-transfer pipes, featuring high heat transfer efficiency |
|----|-----------------------------------------------------------------------------------------------------|

| 3. | Electronic expansion valve is agilely controllable. |
|----|-----------------------------------------------------|

| 4. | Stop valve equipped with refrigerants is easy for maintenance. |
|----|----------------------------------------------------------------|

| 5. | External second-stage oil separator conceal installed inside evaporator by Carrier’s patent technology has high efficiency of separation |
|----|------------------------------------------------------------------------------------------------------------------------------------------------|

| 6. | When releasing from factory, evaporator and condenser are fitted with connection pipes and clamps, which are easy for installation. |
|----|-------------------------------------------------------------------------------------------------------------------------------------|

| 1. | The compressor can be repaired on-site and Carrier designs dual-screw compressor for HFC-134a |
|----|-----------------------------------------------------------------------------------------------|

| 2. | Semi-closed motor is parallel with compressor, which gears up the system, so that compact structure can be realized. |
|----|----------------------------------------------------------------------------------------------------------------------|

| 3. | Use aerospace gear AGMA12 (the highest grade of American Gear Manufacturer's Association), which runs quietly and is sturdy and durable. |
|----|------------------------------------------------------------------------------------------------------------------------------------------|

| 4. | Employing computer optimization design to produce completely ne w concept tooth of rotor, machining precision of major components can reach micro-size, as a result, compressor is efficient and leakage rate is tiny. |
|----|------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| 5. | Use refrigerants to cool motor, and motor can work reliably under low temperature. |
|----|------------------------------------------------------------------------------------|

| 6. | Plunger type unloading device, simple and reliable structure, no internal loss |
|----|--------------------------------------------------------------------------------|

| 7. | Unique design internal silencer reduces gas pulsation of exhaust gas efficiently |
|----|----------------------------------------------------------------------------------|

| l | Compact structure, less space demand, save machine room’s space |
|---|-----------------------------------------------------------------------|

| l | The maximum width of units is only 1015mm, which can easily pass through door frame |
|---|-------------------------------------------------------------------------------------|

| l | Whole set of units releases from factory, and the cooling medium has been filled inside |
|---|-----------------------------------------------------------------------------------------|

| l | When installing, only need connect water pipe and power supply of evaporator and condenser |
|---|--------------------------------------------------------------------------------------------|

| l | The unit is driven by several sets of compressor, wide adjustment scope of refrigerating capacity, high efficient partial loading |
|---|-----------------------------------------------------------------------------------------------------------------------------------|

| l | The units adopts double-loop design, stable and low maintenance cost |
|---|----------------------------------------------------------------------|

----

| l | Colorful user panel, provide LED digital display of operation and control parameters, direct-viewing |
|---|------------------------------------------------------------------------------------------------------|

| l | The unit flow chart clearly displays on user panel, providing immediate access to major operation parameters such as suction/exhaust gas, temperature, running hours of compressor |
|---|------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| l | Quick access to and modify all operation and control parameters by menu operations |
|---|------------------------------------------------------------------------------------|

| l | Provide local, remote and CCN network to control units start or stop. |
|---|-----------------------------------------------------------------------|

| l | Advanced EXV electronic expansion valve is driven by 1500-stage stepper motor, which matches screw compressor and full-liquid evaporator, ensuring stable and efficient operation under full or partial loading. |
|---|------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| l | Automatically control each refrigeration loops, and start stop of each compressor in each loop, as well as up/down load, in order to balance the operation time of each loop and compressor. |
|---|----------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| l | Realize interlock control between units and cold water and chilled water to assure units run under efficient and secure conditions. |
|---|-------------------------------------------------------------------------------------------------------------------------------------|

| l | Provide “requirement limitation” function that limits the maximum refrigerating capacity of units through power control. The function can be used for energy management of multi-units, realizing the optimization of whole system operation efficiency by limiting the cold amount of individual unit. |
|---|---------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| l | When unit starts up, it will reduce flow rate to control water temperature within adjustable scope (0.1-1.1/min), in order to avoid energy loss caused by low temperature water. It will promote energy efficiency ratio of unit, prolong unit’s lifetime. |
|---|------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| l | It offers “Energy save Restoration” function, which will settle a negative correction of cold capacity in accordance with variation tendency of outdoor temperature or return water temperature (provide users with temperature signals), so that unnecessary energy waste can avoid. And it immediately matches the external reducing fluctuation tendency to raise the operation efficiency of units. |
|---|---------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| l | Before starting up the unit, the function will quickly confirm every switch, sensor, voltage and compressor by analog inspection. |
|---|-----------------------------------------------------------------------------------------------------------------------------------|

| l | During its operation, human-computer interface will display a variety of setting points and real operation parameters, monitoring units’ operation. When it is necessary, the system will alarm. |
|---|--------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| l | The unit may provide more than 140 display and alarm information. The operator can resort to relevant solution to remove faults by alarm information. |
|---|-------------------------------------------------------------------------------------------------------------------------------------------------------|

| l | The system provides functions such as temperature of cold water is too low, oil pressure is low, pressure of refrigerating fluid is too high, leak current, motor overload, voltage too high or too low, open-phase protection and many others. |
|---|-------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

----

|          |   |        |   |             |   |            |   |      |   |             |
|---------------|--------|-------------|--------|------------------|--------|-----------------|--------|-----------|--------|------------------|
| Ref. Capacity |   | Input Power |   | Evaporator       |   | Condenser       |
|          |   |        |   | Cold water       |   | Cold Water      |   | Flow Rate |   | Chill Water      |   | Chill Water |   | Chill Water |
| (kW)          |   | (kW)        |   | out Tep(°C) |   | in Tep(°C) |   | (m3 / h)  |   | Out Tep(°C) |   | In Tep(°C) |   | (m3 / h) |
| 316           |   | 64          |   |             |   |            |   | 54        |   | 31               |   | 26 |   | 65 |
| 312           |   | 67          |   | 5                |   | 10              |   | 54        |   | 33               |   | 28 |   | 65 |
| 308           |   | 70          |   |             |   |            |   | 53        |   | 35               |   | 30 |   | 65 |
| 305           |   | 74          |   |             |   |            |   | 52        |   | 37               |   | 32 |   | 65 |
| 326           |   | 64          |   |             |   |            |   | 56        |   | 31               |   | 26 |   | 67 |
| 322           |   | 67          |   |  6          |   | 11              |   | 55        |   | 33               |   | 28 |   | 67 |
| 319           |   | 70          |   |             |   |            |   | 55        |   | 35               |   | 30 |   | 67 |
| 315           |   | 74          |   |             |   |            |   | 54        |   | 37               |   | 32 |   | 67 |
| 336           |   | 65          |   |             |   |            |   | 58        |   | 31               |   | 26 |   | 69 |
| 333           |   | 68          |   | 7                |   | 12              |   | 57        |   | 33               |   | 29 |   | 69 |
| 329           |   | 71          |   |             |   |            |   | 57        |   | 35               |   | 30 |   | 69 |
| 325           |   | 74          |   |             |   |            |   | 56        |   | 37               |   | 32 |   | 69 |
| 347           |   | 65          |   |             |   |            |   | 60        |   | 31               |   | 26 |   | 71 |
| 343           |   | 68          |   | 8                |   | 13              |   | 59        |   | 33               |   | 28 |   | 71 |
| 339           |   | 71          |   |             |   |            |   | 58        |   | 35               |   | 30 |   | 70 |
| 335           |   | 75          |   |             |   |            |   | 58        |   | 37               |   | 32 |   | 70 |
| 357           |   | 65          |   |             |   |            |   | 61        |   | 31               |   | 26 |   | 73 |
| 353           |   | 68          |   | 9                |   | 14              |   | 61        |   | 33               |   | 28 |   | 73 |
| 349           |   | 72          |   |             |   |            |   | 60        |   | 35               |   | 30 |   | 72 |
| 345           |   | 75          |   |             |   |            |   | 59        |   | 37               |   | 32 |   | 72 |
| 367           |   | 65          |   |             |   |            |   | 63        |   | 31               |   | 26 |   | 74 |
| 363           |   | 68          |   | 10               |   | 15              |   | 62        |   | 33               |   | 28 |   | 74 |
| 360           |   | 72          |   |             |   |            |   | 62        |   | 38               |   | 30 |   | 74 |
| 355           |   | 75          |   |             |   |            |   | 61        |   | 37               |   | 32 |   | 74 |

|          |   |        |   |             |   |            |   |      |   |             |
|---------------|--------|-------------|--------|------------------|--------|-----------------|--------|-----------|--------|------------------|
| Ref. Capacity |   | Input Power |   | Evaporator       |   | Condenser       |
|          |   |        |   | Cold water       |   | Cold Water      |   | Flow Rate |   | Chill Water      |   | Chill Water |   | Chill Water |
| (kW)          |   | (kW)        |   | out Tep(°C) |   | in Tep(°C) |   | (m3 / h)  |   | Out Tep(°C) |   | In Tep(°C) |   | (m3 / h) |
| 439           |   | 89          |   |             |   |            |   | 76        |   | 31               |   | 26 |   | 91 |
| 431           |   | 93          |   | 5                |   | 10              |   | 74        |   | 33               |   | 28 |   | 90 |
| 424           |   | 98          |   |             |   |            |   | 73        |   | 35               |   | 30 |   | 90 |
| 416           |   | 102         |   |             |   |            |   | 72        |   | 37               |   | 32 |   | 89 |
| 456           |   | 89          |   |             |   |            |   | 78        |   | 31               |   | 26 |   | 94 |
| 448           |   | 93          |   | 6                |   | 11              |   | 77        |   | 33               |   | 28 |   | 93 |
| 439           |   | 98          |   |             |   |            |   | 76        |   | 35               |   | 30 |   | 92 |
| 430           |   | 103         |   |             |   |            |   | 74        |   | 37               |   | 32 |   | 92 |
| 473           |   | 90          |   |             |   |            |   | 81        |   | 31               |   | 26 |   | 97 |
| 464           |   | 94          |   | 7                |   | 12              |   | 80        |   | 33               |   | 28 |   | 96 |
| 455           |   | 98          |   |             |   |            |   | 78        |   | 35               |   | 30 |   | 95 |
| 447           |   | 103         |   |             |   |            |   | 77        |   | 37               |   | 32 |   | 95 |
| 488           |   | 90          |   |             |   |            |   | 84        |   | 31               |   | 26 |   | 99 |
| 480           |   | 94          |   | 8                |   | 13              |   | 82        |   | 33               |   | 28 |   | 99 |
| 472           |   | 99          |   |             |   |            |   | 81        |   | 35               |   | 30 |   | 98 |
| 462           |   | 103         |   |             |   |            |   | 79        |   | 37               |   | 32 |   | 97 |
| 505           |   | 90          |   |             |   |            |   | 87        |   | 31               |   | 26 |   | 102 |
| 495           |   | 95          |   | 9                |   | 14              |   | 85        |   | 33               |   | 28 |   | 101 |
| 486           |   | 99          |   |             |   |            |   | 84        |   | 35               |   | 30 |   | 101 |
| 478           |   | 104         |   |             |   |            |   | 82        |   | 37               |   | 32 |   | 100 |
| 521           |   | 91          |   |             |   |            |   | 90        |   | 31               |   | 6 |   | 105 |
| 512           |   | 95          |   | 10               |   | 15              |   | 88        |   | 33               |   | 28 |   | 104 |
| 503           |   | 99          |   |             |   |            |   | 87        |   | 35               |   | 30 |   | 104 |
| 493           |   | 104         |   |             |   |            |   | 85        |   | 37               |   | 32 |   | 103 |

----

|          |   |        |   |             |   |            |
|---------------|--------|-------------|--------|------------------|--------|-----------------|
| Ref. Capacity |   | Input Power |   | evaporator       |   | Condenser       |
|          |   |        |   | Cold water       |   | Cold Water      |   | Flow Rate |   | Chill Water |   | Chill Water |   | Chill Water |
| (kW)          |   | (kW)        |   | out Tep(°C) |   | in Tep(°C) |   | (m3 / h) |   | Out Tep(°C) |   | In Tep(°C) |   | (m3 / h) |
| 554           |   | 110         |   |             |   |            |   | 95 |   | 31 |   | 26 |   | 114 |
| 544           |   | 115         |   | 5                |   | 10              |   | 94 |   | 33 |   | 28 |   | 113 |
| 533           |   | 122         |   |             |   |            |   | 92 |   | 35 |   | 30 |   | 113 |
| 524           |   | 127         |   |             |   |            |   | 90 |   | 37 |   | 32 |   | 112 |
| 575           |   | 111         |   |             |   |            |   | 99 |   | 31 |   | 26 |   | 118 |
| 564           |   | 117         |   | 6                |   | 11              |   | 97 |   | 33 |   | 28 |   | 117 |
| 554           |   | 122         |   |             |   |            |   | 95 |   | 35 |   | 30 |   | 116 |
| 543           |   | 128         |   |             |   |            |   | 93 |   | 37 |   | 32 |   | 115 |
| 595           |   | 111         |   |             |   |            |   | 102 |   | 31 |   | 26 |   | 121 |
| 586           |   | 117         |   | 7                |   | 12              |   | 101 |   | 33 |   | 28 |   | 121 |
| 574           |   | 122         |   |             |   |            |   | 99 |   | 35 |   | 30 |   | 120 |
| 563           |   | 128         |   |             |   |            |   | 97 |   | 37 |   | 32 |   | 119 |
| 617           |   | 111         |   |             |   |            |   | 106 |   | 31 |   | 29 |   | 125 |
| 606           |   | 117         |   | 8                |   | 13              |   | 104 |   | 33 |   | 28 |   | 124 |
| 594           |   | 123         |   |             |   |            |   | 102 |   | 35 |   | 30 |   | 123 |
| 584           |   | 128         |   |             |   |            |   | 100 |   | 37 |   | 32 |   | 122 |
| 637           |   | 111         |   |             |   |            |   | 110 |   | 31 |   | 26 |   | 129 |
| 626           |   | 117         |   | 9                |   | 14              |   | 108 |   | 33 |   | 28 |   | 128 |
| 615           |   | 123         |   |             |   |            |   | 106 |   | 35 |   | 30 |   | 127 |
| 604           |   | 129         |   |             |   |            |   | 104 |   | 34 |   | 32 |   | 126 |
| 658           |   | 112         |   |             |   |            |   | 113 |   | 31 |   | 26 |   | 132 |
| 646           |   | 118         |   | 10               |   | 15              |   | 111 |   | 33 |   | 28 |   | 131 |
| 635           |   | 123         |   |             |   |            |   | 109 |   | 35 |   | 30 |   | 130 |
| 622           |   | 129         |   |             |   |            |   | 107 |   | 37 |   | 32 |   | 129 |

|          |   |        |   |             |   |            |   |      |   |             |   |            |   |        |
|---------------|--------|-------------|--------|------------------|--------|-----------------|--------|-----------|--------|------------------|--------|-----------------|--------|-------------|
| Ref. Capacity |   | Input Power |   | evaporator       |   | Condenser       |
|          |   |        |   | Cold water       |   | Cold Water      |   | Flow Rate |   | Chill Water      |   | Chill Water     |   | Chill Water |
| (kW)          |   | (kW)        |   | out Tep(°C) |   | in Tep(°C) |   | (m3 / h)  |   | Out Tep(°C) |   | In Tep(°C) |   | (m3 / h)    |
| 658           |   | 129         |   |             |   |            |   | 113       |   | 31               |   | 26              |   | 135         |
| 651           |   | 137         |   | 5                |   | 10              |   | 112       |   | 33               |   | 28              |   | 135         |
| 644           |   | 143         |   |             |   |            |   | 111       |   | 35               |   | 30              |   | 135         |
| 636           |   | 150         |   |             |   |            |   | 109       |   | 37               |   | 32              |   | 135         |
| 680           |   | 130         |   |             |   |            |   | 117       |   | 31               |   | 26              |   | 139         |
| 672           |   | 137         |   | 6                |   | 11              |   | 116       |   | 33               |   | 28              |   | 139         |
| 664           |   | 143         |   |             |   |            |   | 114       |   | 35               |   | 30              |   | 139         |
| 657           |   | 151         |   |             |   |            |   | 113       |   | 37               |   | 32              |   | 139         |
| 701           |   | 130         |   |             |   |            |   | 121       |   | 31               |   | 26              |   | 143         |
| 694           |   | 138         |   | 7                |   | 12              |   | 119       |   | 33               |   | 28              |   | 143         |
| 686           |   | 144         |   |             |   |            |   | 118       |   | 35               |   | 30              |   | 143         |
| 678           |   | 151         |   |             |   |            |   | 117       |   | 37               |   | 32              |   | 143         |
| 723           |   | 131         |   |             |   |            |   | 124       |   | 31               |   | 26              |   | 147         |
| 715           |   | 138         |   | 8                |   | 13              |   | 123       |   | 33               |   | 28              |   | 147         |
| 708           |   | 144         |   |             |   |            |   | 122       |   | 35               |   | 30              |   | 146         |
| 699           |   | 152         |   |             |   |            |   | 120       |   | 37               |   | 32              |   | 146         |
| 744           |   | 131         |   |             |   |            |   | 128       |   | 31               |   | 26              |   | 151         |
| 737           |   | 139         |   | 9                |   | 14              |   | 127       |   | 33               |   | 28              |   | 151         |
| 728           |   | 145         |   |             |   |            |   | 125       |   | 35               |   | 30              |   | 150         |
| 720           |   | 152         |   |             |   |            |   | 124       |   | 37               |   | 32              |   | 150         |
| 766           |   | 134         |   |             |   |            |   | 64        |   | 31               |   | 26              |   | 155         |
| 758           |   | 139         |   | 10               |   | 15              |   | 64        |   | 33               |   | 28              |   | 154         |
| 750           |   | 145         |   |             |   |            |   | 63        |   | 35               |   | 30              |   | 154         |
| 741           |   | 153         |   |             |   |            |   | 62        |   | 37               |   | 32              |   | 154         |

----

|          |   |        |   |             |   |            |
|---------------|--------|-------------|--------|------------------|--------|-----------------|
| Ref. Capacity |   | Input Power |   | evaporator       |   | Condenser       |
|          |   |        |   | Cold water       |   | Cold Water      |   | Flow Rate |   | Chill Water |   | Chill Water |   | Chill Water |
| (kW)          |   | (kW)        |   | out Tep(°C) |   | in Tep(°C) |   | (m3 / h) |   | Out Tep(°C) |   | In Tep(°C) |   | (m3 / h) |
| 845           |   | 168         |   |             |   |            |   | 145 |   | 31 |   | 29 |   | 174 |
| 829           |   | 176         |   | 5                |   | 10              |   | 143 |   | 33 |   | 28 |   | 173 |
| 813           |   | 185         |   |             |   |            |   | 140 |   | 35 |   | 30 |   | 172 |
| 797           |   | 193         |   |             |   |            |   | 137 |   | 37 |   | 32 |   | 170 |
| 877           |   | 169         |   |             |   |            |   | 151 |   | 31 |   | 26 |   | 180 |
| 860           |   | 177         |   | 6                |   | 11              |   | 148 |   | 33 |   | 28 |   | 178 |
| 844           |   | 185         |   |             |   |            |   | 145 |   | 35 |   | 30 |   | 177 |
| 827           |   | 193         |   |             |   |            |   | 142 |   | 37 |   | 32 |   | 175 |
| 909           |   | 170         |   |             |   |            |   | 156 |   | 31 |   | 26 |   | 186 |
| 892           |   | 178         |   | 7                |   | 12              |   | 153 |   | 33 |   | 28 |   | 184 |
| 875           |   | 186         |   |             |   |            |   | 150 |   | 35 |   | 30 |   | 182 |
| 858           |   | 194         |   |             |   |            |   | 148 |   | 37 |   | 32 |   | 181 |
| 941           |   | 170         |   |             |   |            |   | 162 |   | 31 |   | 26 |   | 191 |
| 924           |   | 178         |   | 8                |   | 13              |   | 159 |   | 33 |   | 28 |   | 190 |
| 906           |   | 187         |   |             |   |            |   | 156 |   | 35 |   | 30 |   | 188 |
| 889           |   | 195         |   |             |   |            |   | 153 |   | 37 |   | 32 |   | 186 |
| 974           |   | 171         |   |             |   |            |   | 167 |   | 31 |   | 26 |   | 197 |
| 956           |   | 179         |   | 9                |   | 14              |   | 164 |   | 33 |   | 28 |   | 195 |
| 937           |   | 187         |   |             |   |            |   | 161 |   | 35 |   | 30 |   | 193 |
| 920           |   | 195         |   |             |   |            |   | 158 |   | 37 |   | 32 |   | 192 |
| 1005          |   | 172         |   |             |   |            |   | 173 |   | 31 |   | 26 |   | 202 |
| 988           |   | 180         |   | 10               |   | 15              |   | 170 |   | 33 |   | 28 |   | 201 |
| 969           |   | 188         |   |             |   |            |   | 167 |   | 35 |   | 30 |   | 199 |
| 950           |   | 196         |   |             |   |            |   | 163 |   | 37 |   | 32 |   | 197 |

|          |   |        |   |             |   |            |
|---------------|--------|-------------|--------|------------------|--------|-----------------|
| Ref. Capacity |   | Input Power |   | evaporator       |   | Condenser       |
|          |   |        |   | Cold water       |   | Cold Water      |   | Flow Rate |   | Chill Water |   | Chill Water |   | Chill Water |
| (kW)          |   | (kW)        |   | out Tep(°C) |   | in Tep(°C) |   | (m3 / h) |   | Out Tep(°C) |   | In Tep(°C) |   | (m3 / h) |
| 985           |   | 196         |   |             |   |            |   | 169 |   | 31 |   | 26 |   | 203 |
| 974           |   | 205         |   | 5                |   | 10              |   | 167 |   | 33 |   | 28 |   | 203 |
| 963           |   | 215         |   |             |   |            |   | 166 |   | 35 |   | 30 |   | 203 |
| 951           |   | 225         |   |             |   |            |   | 164 |   | 37 |   | 32 |   | 202 |
| 1017          |   | 197         |   |             |   |            |   | 175 |   | 31 |   | 26 |   | 209 |
| 1007          |   | 206         |   | 6                |   | 11              |   | 173 |   | 33 |   | 28 |   | 209 |
| 996           |   | 216         |   |             |   |            |   | 171 |   | 35 |   | 30 |   | 208 |
| 983           |   | 226         |   |             |   |            |   | 169 |   | 37 |   | 32 |   | 208 |
| 1051          |   | 198         |   |             |   |            |   | 181 |   | 31 |   | 26 |   | 215 |
| 1039          |   | 206         |   | 7                |   | 12              |   | 179 |   | 33 |   | 28 |   | 214 |
| 1027          |   | 217         |   |             |   |            |   | 177 |   | 35 |   | 30 |   | 214 |
| 1014          |   | 227         |   |             |   |            |   | 174 |   | 37 |   | 32 |   | 213 |
| 1082          |   | 199         |   |             |   |            |   | 186 |   | 31 |   | 26 |   | 220 |
| 1070          |   | 207         |   | 8                |   | 13              |   | 184 |   | 33 |   | 28 |   | 220 |
| 1058          |   | 218         |   |             |   |            |   | 182 |   | 35 |   | 30 |   | 220 |
| 1046          |   | 228         |   |             |   |            |   | 180 |   | 37 |   | 32 |   | 219 |
| 1115          |   | 200         |   |             |   |            |   | 192 |   | 31 |   | 26 |   | 226 |
| 1103          |   | 208         |   | 9                |   | 14              |   | 190 |   | 33 |   | 28 |   | 225 |
| 1091          |   | 218         |   |             |   |            |   | 188 |   | 35 |   | 30 |   | 225 |
| 1078          |   | 229         |   |             |   |            |   | 185 |   | 37 |   | 32 |   | 225 |
| 1148          |   | 200         |   |             |   |            |   | 197 |   | 31 |   | 26 |   | 232 |
| 1135          |   | 209         |   | 10               |   | 15              |   | 195 |   | 33 |   | 28 |   | 231 |
| 1122          |   | 219         |   |             |   |            |   | 193 |   | 35 |   | 30 |   | 231 |
| 1110          |   | 230         |   |             |   |            |   | 191 |   | 37 |   | 32 |   | 230 |

----

| 30HXC350B          |   |             |   |            |
|--------------------|--------|------------------|--------|-----------------|
|               |   |             |   |            |   |   |
|               |   |             |   | evaporator      |   | Condenser |
| Ref. Capacity |   | Input Power |   | Cold water |   | Cold Water |   | Flow Rate out |   | Chill Water |   | Chill Water |   | Chill Water |
| (kW)               |   | (kW)             |   | Tep( ̊C)    |   | in Tep( ̊C) |   | (m3 / h) |   | Out Tep( ̊C) |   | In Tep( ̊C) |   | (m3 / h) |
| 1161114011171095   |   | 231243254266     |   | 5               |   | 10 |   | 200196192188 |   | 31333537 |   | 26283032 |   | 239238236234 |
| 1206118411611138   |   | 232255255267     |   | 6               |   | 11 |   | 207200200196 |   | 31353537 |   | 26303032 |   | 247243243242 |
| 1250122712041180   |   | 233245256267     |   | 7               |   | 12 |   | 215211207203 |   | 31333537 |   | 26283032 |   | 255253251249 |
| 1295127012471223   |   | 234245257268     |   | 8               |   | 13 |   | 223218215210 |   | 313333537 |   | 26283032 |   | 263261259256 |
| 1339131512911265   |   | 235246258269     |   | 9               |   | 14 |   | 230226222218 |   | 31333537 |   | 26283032 |   | 271268266264 |
| 138235813331308    |   | 236247258270     |   | 10              |   | 15 |   | 238234229225 |   | 31333537 |   | 26283032 |   | 278276274271 |

| 30HXC400B          |   |             |   |            |
|--------------------|--------|------------------|--------|-----------------|
|               |   |             |   |            |   |   |
|               |   |             |   | evaporator      |   | Condenser |
| Ref. Capacity |   | Input Power |   | Cold water |   | Cold Water |   | Flow Rate out |   | Chill Water |   | Chill Water |   | Chill Water |
| (kW)               |   | (kW)             |   | Tep( ̊C)    |   | in Tep( ̊C) |   | (m3 / h) |   | Out Tep( ̊C) |   | In Tep( ̊C) |   | (m3 / h) |
| 1310129612821265   |   | 259273286299     |   | 5               |   | 10 |   | 225223220218 |   | 31333537 |   | 26283032 |   | 270270270269 |
| 1353133913241308   |   | 261274287301     |   | 6               |   | 11 |   | 233230228225 |   | 31333537 |   | 26283032 |   | 278277277277 |
| 1396138213661350   |   | 263276288303     |   | 7               |   | 12 |   | 240238235232 |   | 31333537 |   | 26273032 |   | 285285284284 |
| 1441142514081392   |   | 264277290305     |   | 8               |   | 13 |   | 248245242239 |   | 31333537 |   | 26283032 |   | 293293292292 |
| 1484146814511435   |   | 265278291306     |   | 9               |   | 14 |   | 255252250247 |   | 31333537 |   | 26283032 |   | 301300300299 |
| 1528151114951476   |   | 266379292307     |   | 10              |   | 15 |   | 263260257254 |   | 31333537 |   | 26283032 |   | 309308307307 |

----

| 1. | picture 1 is space for maintenance, 2 is space for drawn pipe (the drawn pipes on right side and left side can exchange) |
|----|--------------------------------------------------------------------------------------------------------------------------------------|

| 2. | Pi and Pi’ are two sets of holes for stone bolts, which can select one set to install |
|----|---------------------------------------------------------------------------------------------|

| 3. | On-site water pipe uses clamp connection, clamp and fitting connection pipes are provided randomly (blue section), and the length of connection pipe is 120mm. |
|----|----------------------------------------------------------------------------------------------------------------------------------------------------------------|

| Type      |   | A   |   |   | B   |   |   | C   |   |   | D   |   |   | E    |   | S     |   | R     |
|-----------|--------|-----|--------|--------|-----|--------|--------|-----|--------|--------|-----|--------|--------|------|--------|-------|--------|-------|
| 30HXY110B |   | 238 |   |   | 287 |   |   | 320 |   |   | 279 |   |   | 1910 |   | Dg100 |   | Dg125 |

| Loading Distribution(kg) |   |   |   |   |   |   |   |   |   |   |   |   |   |      |   |   |      |   |   |
|--------------------------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|-----------|--------|--------|-----------|--------|--------|
| Type                     |   | P1     |   |   | P2     |   |   | P3     |   |   | P4     |   |   | P1’ |   |   | P2’ |   |   | P3’ |   |   | P4’ |   |   | PT |   |
| 30HXY110B                |   | 601    |   |   | 451    |   |   | 590    |   |   | 447    |   |   | 619       |   |   | 473       |   |   | 568 |   |   | 429 |   |   | 2089 |   |

----

| 4. | picture 1 is space for maintenance, 2 is space for drawn pipe (the drawn pipes on right side and left side can exchange) |
|----|--------------------------------------------------------------------------------------------------------------------------------------|

| 5. | Pi and Pi’ are two sets of holes for stone bolts, which can select one set to install |
|----|---------------------------------------------------------------------------------------------|

| 6. | On-site water pipe uses clamp connection, clamp and fitting connection pipes are provided randomly (blue section), and the length of connection pipe is 120mm. |
|----|----------------------------------------------------------------------------------------------------------------------------------------------------------------|

| Type               |   | A   |   |   | B   |   |   | C   |   |   | D   |   |   | E    |   |   | S     |   |   | R     |   |
|--------------------|--------|-----|--------|--------|-----|--------|--------|-----|--------|--------|-----|--------|--------|------|--------|--------|-------|--------|--------|-------|--------|
| 30HXC130B30HXC165B |   | 210 |   |   | 302 |   |   | 320 |   |   | 235 |   |   | 1816 |   |   | Dg125 |   |   | Dg125 |   |
| 30HXC200B          |   | 272 |   |   | 297 |   |   | 320 |   |   | 235 |   |   | 1921 |   |   | Dg125 |   |   | Dg125 |   |

| Loading Distribution(kg) |   |   |   |   |   |   |   |   |   |   |   |   |   |      |   |   |
|--------------------------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|-----------|--------|--------|
| Type                     |   | P1     |   |   | P2     |   |   | P3     |   |   | P4     |   |   | P1’ |   |   | P2’ |   |   | P3’ |   |   | P4’ |   |   | PT |   |
| 30HXC130B                |   | 804    |   |   | 543    |   |   | 741    |   |   | 501    |   |   | 840       |   |   | 506 |   |   | 773 |   |   | 470 |   |   | 2589 |   |
| 30HXC165B                |   | 834    |   |   | 563    |   |   | 768    |   |   | 520    |   |   | 871       |   |   | 526 |   |   | 803 |   |   | 485 |   |   | 2685 |   |
| 30HXC200B                |   | 978    |   |   | 662    |   |   | 903    |   |   | 610    |   |   | 1021      |   |   | 618 |   |   | 942 |   |   | 572 |   |   | 3153 |   |

----

| 7. | picture 1 is space for maintenance, 2 is space for drawn pipe (the drawn pipes on right side and left side can exchange) |
|----|--------------------------------------------------------------------------------------------------------------------------------------|

| 8. | Pi and Pi’ are two sets of holes for stone bolts, which can select one set to install |
|----|---------------------------------------------------------------------------------------------|

| 9. | On-site water pipe uses clamp connection, clamp and fitting connection pipes are provided randomly (blue section), and the length of connection pipe is 120mm. |
|----|----------------------------------------------------------------------------------------------------------------------------------------------------------------|

| Type               |   | A   |   |   | B   |   |   | C     |   |   | D   |   |   | E    |   |   | S     |   |   | R     |   |
|--------------------|--------|-----|--------|--------|-----|--------|--------|-------|--------|--------|-----|--------|--------|------|--------|--------|-------|--------|--------|-------|--------|
| 30HXC250B30HXC300B |   | 306 |   |   | 340 |   |   | 357.5 |   |   | 284 |   |   | 2060 |   |   | Dg150 |   |   | Dg200 |   |

| Loading Distribution (kg) |   |   |   |   |   |   |   |   |   |   |   |   |   |      |   |   |
|---------------------------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|-----------|--------|--------|
| type                      |   | P1     |   |   | P2     |   |   | P3     |   |   | P4     |   |   | P1’ |   |   | P2’ |   |   | P3’ |   |   | P4’ |   |   | PT |   |
| 30HXC250B                 |   | 1350   |   |   | 960    |   |   | 1355   |   |   | 953    |   |   | 1403      |   |   | 911 |   |   | 1396 |   |   | 908 |   |   | 4618 |   |
| 30HXC300B                 |   | 1388   |   |   | 988    |   |   | 1380   |   |   | 982    |   |   | 1440      |   |   | 937 |   |   | 1431 |   |   | 930 |   |   | 4738 |   |

----

| 10. | picture 1 is space for maintenance, 2 is space for drawn pipe (the drawn pipes on right side and left side can exchange) |
|-----|--------------------------------------------------------------------------------------------------------------------------------------|

| 11. | Pi and Pi’ are two sets of holes for stone bolts, which can select one set to install |
|-----|---------------------------------------------------------------------------------------------|

| 12. | On-site water pipe uses clamp connection, clamp and fitting connection pipes are provided randomly (blue section), and the length of connection pipe is 120mm. |
|-----|----------------------------------------------------------------------------------------------------------------------------------------------------------------|

| type               |   | A   |   |   | B   |   |   | C   |   |   | D   |   |   | E    |   |   | S     |   |   | R     |   |
|--------------------|--------|-----|--------|--------|-----|--------|--------|-----|--------|--------|-----|--------|--------|------|--------|--------|-------|--------|--------|-------|--------|
| 30HXC350B30HXC400B |   | 290 |   |   | 379 |   |   | 340 |   |   | 309 |   |   | 2112 |   |   | Dg200 |   |   | Dg200 |   |

| Loading Distribution (kg) |   |   |   |   |   |   |   |   |   |   |   |   |   |
|---------------------------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|
| type                      |   | P1     |   |   | `P2    |   |   | P3     |   |   | P4     |   |   | P1’ |   |   | P2’ |   |   | P3’ |   |   | P4’ |   |   | PT |   |
| 30HXC350B                 |   | 1799   |   |   | 1313   |   |   | 1391   |   |   | 1015   |   |   | 1864 |   |   | 1249 |   |   | 1438 |   |   | 967 |   |   | 5518 |   |
| 30HXC400B                 |   | 1851   |   |   | 1360   |   |   | 1432   |   |   | 1043   |   |   | 1918 |   |   | 1287 |   |   | 1486 |   |   | 995 |   |   | 5686 |   |

----

|      |   |   |   |   |   |   |   |   |   |   |    |   |   |    |   |   | (mm)                        |   |
|-----------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|---------|--------|--------|---------|--------|--------|-----------------------------|--------|
| type      |   | X      |   |   | Y      |   |   | Z      |   |   | W (Min) |   |   | L (Min) |   |   | Operation Weight  (kg) |   |
| 30HXY110B |   | 1156   |   |   | 398    |   |   | 900    |   |   | 1200    |   |   | 1828    |   |   | 2089                        |   |
| 30HXC130B |   | 1299   |   |   | 405    |   |   | 892    |   |   | 1200    |   |   | 1828    |   |   | 2589                        |   |
| 30HXC165B |   | 2685   |   |
| 30HXC200B |   | 1299   |   |   | 400    |   |   | 870    |   |   | 1200    |   |   | 1828    |   |   | 3153                        |   |
| 30HXC250B |   | 1652   |   |   | 426    |   |   | 1031   |   |   | 1200    |   |   | 2515    |   |   | 4618                        |   |
| 30HXC300B |   | 4738   |   |
| 30HXC350B |   | 1888   |   |   | 432    |   |   | 1103   |   |   | 1200    |   |   | 3113    |   |   | 5518                        |   |
| 30HXC400B |   | 1877   |   |   | 438    |   |   | 1098   |   |   | 1200    |   |   | 3113    |   |   | 5686                        |   |

| 1. | If unit uses first generation mute chassis, the foundation shall be made as whole, and its surface should be horizontal. The dimensions of foundation is according to the outline dimensions of unit, each side in the length direction shall add more than 250mm, each side in the width direction shall add more than 150mm. The dash dot line shows foundation dimension of unit, after installing mute chassis. |
|----|---------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| 2. | Four pieces of stone bolts, each one is M20X300 |
|----|-------------------------------------------------|

| 3. | The position for stone bolts can be 1 2 3 4 or 1' 2’ 3’ 4’ shown on the picture |
|----|---------------------------------------------------------------------------------------------------|

|                        |   |   |   |   |   |   |   |   |   |   |   |   |   |   |   |   | (mm) |   |
|-----------------------------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|--------|------|--------|
| Type                        |   | A      |   |   | B      |   |   | C      |   |   | P      |   |   | Q      |   |   | R    |   |
| 30HXY110B                   |   | 468    |   |   | 1600   |   |   | 2554   |   |   | 930    |   |   | 100    |   |   | 980  |   |
| 30HXC130B30HXC165B30HXC200B |   | 658    |   |   | 1546   |   |   | 2988   |   |   | 930    |   |   | 100    |   |   | 980  |   |
| 30HXC250B30HXC300B          |   | 650    |   |   | 2111   |   |   | 3512   |   |   | 965    |   |   | 100    |   |   | 1015 |   |
| 30HXC350B30HXC400B          |   | 710    |   |   | 2503   |   |   | 4021   |   |   | 965    |   |   | 100    |   |   | 1015 |   |

----

| type                                             |                                                     | 30HXY  |   |   | 30HXC  |   |
|--------------------------------------------------|----------------------------------------------------------|--------|--------|--------|--------|--------|
|                                             |                                                     |   |   | 110B   |   |   | 130B |   |   | 165B |   |   | 200B |   |   | 250B |   |   | 300B |   |   | 350B |   |   | 400B |   |
| 空调                                 | 制冷量                                 | kW     |   | 317    |   |   | 438 |   |   | 554 |   |   | 654 |   |   | 845 |   |   | 985 |   |   | 1161 |   |   | 1307 |   |
| 工况                                 | 输入功率                         | kW     |   | 71     |   |   | 98 |   |   | 122 |   |   | 144 |   |   | 185 |   |   | 215 |   |   | 254 |   |   | 287 |   |
| 蓄冰                                 | 制冷量                                 | kW     |   | 211    |   |   | 270 |   |   | 336 |   |   | 436 |   |   | 509 |   |   | 656 |   |   | 699 |   |   | 869 |   |
| 工况                                 | 输入功率                         | kW     |   | 69     |   |   | 94 |   |   | 119 |   |   | 140 |   |   | 179 |   |   | 207 |   |   | 246 |   |   | 277 |   |
| 额定工况电流 | A                                                        |   | 131    |   |   | 171    |   |   | 213 |   |   | 251 |   |   | 323 |   |   | 375 |   |   | 444 |   |   | 501 |   |
| 最大启动电流 | A                                                        |   | 328    |   |   | 314    |   |   | 374 |   |   | 465 |   |   | 575 |   |   | 650 |   |   | 745 |   |   | 840 |   |
| 蒸                                         | 流量                                         | m3/h   |   | 58     |   |   | 80 |   |   | 102 |   |   | 120 |   |   | 155 |   |   | 179 |   |   | 214 |   |   | 238 |   |
| 发                                         | 空调工况水压降 | kPa    |   | 80     |   |   | 54 |   |   | 64 |   |   | 80 |   |   | 81 |   |   | 89 |   |   | 91 |   |   | 92 |   |
| 器                                         | 蓄冰工况水压降 | kPa    |   | 139    |   |   | 96 |   |   | 109 |   |   | 126 |   |   | 76 |   |   | 84 |   |   | 104 |   |   | 88 |   |

| 1. | Work condition of air conditioner: cold water in/out temperature is 7/12°C, chilled water in/out temperature 30/35°C |
|----|--------------------------------------------------------------------------------------------------------------------------------|

| 2. | Work condition of ice storage: cold water outlet temperature is -6°C, chilled water inlet temperature is 30°C. |
|----|--------------------------------------------------------------------------------------------------------------------------|

| 3. | refrigerating medium shall be 25% |
|----|-----------------------------------|

| l | Interfaces of water room of evaporator and condenser can reverse respectively |
|---|-------------------------------------------------------------------------------|

| l | Water room of evaporator and condenser can provide 1.6Mpa/2.1Mpa high bearing pressure options |
|---|------------------------------------------------------------------------------------------------|

| l | Low temperature unit: |
|---|-----------------------|

| l | Mute Chassis |
|---|--------------|

| Type                                                                                                |   | Size(L x W x H) mm |   | Weight (kg) |   | Type      |   | Size(L x W x H) mm                     |   | Weight (kg) |
|-----------------------------------------------------------------------------------------------------|--------|--------------------|--------|-------------|--------|-----------|--------|----------------------------------------|--------|-------------|
| 30HXY110B                                                                                           |   | 2867 x 1192 x 2080 |   | 500         |   | 30HXY110B |   | When installing second generation |   | 130         |
| 30HXC130B~30HXC200B                                                                          |   | 3315 x 1192 x 2143 |   | 600         |   | 30HXC130B |   | Generation Mute chassis                |   | 130         |
| 30HXC250B~30HXC300B                                                                          |   | 3724 x 1221 x 2212 |   | 700         |   | 30HXC165B |   | Chassis, outline is same               |   | 130         |
| 30HXC350B~30HXC400B                                                                          |   | 4333 x 1221 x 2312 |   | 800         |   | 30HXC200B |   | to the original set.                   |   | 160         |
| 注:When ordering the equipment, user shall specific the detailed type on the contract. |

----

----