| Description                 | Value                          |        |
|-----------------------------|--------------------------------|--------|
| Product Name:               | NBG 125-100-160/161 A-F-A BAQE |
| Product No:                 | 95105171                       |
| EAN No:                     | 5700836546714                  |
|                        |                           |
| Technology:                 |                           |
| Pump speed data             | 2950 rpm                       |
| Real calculated flow rate   | 279 m3/H                       |
| pump lift                   | 26.4 m                         |
| Real blade diameter         | 169mm                          |
| Shaft seal                  | BAQE                           |
| Shaft diameter              | 32mm                           |
| Curve tolerance             | ISO 9906 Annex A               |
| Edition of pump             | A                              |
|                        |                           |
| Material                    |                           |
| pump body                   | cast iron                      |
|                        | EN-GJL-250 DIN W. – Nr.  |
|                        | A48-40 B ASTM                  |
| blade                       | Cast iron                      |
|                        | EN-GJL-250 DIN W. – Nr.  |
|                        | A48-30 B ASTM                  |
| Material Code               | A                              |
|                        |                           |
| Install                     |                           |
| Max Environment temperature | 40°C                      |
| Max Operation Pressure      | 16                             |
| Flange Standard             | EN1092-2                       |
| Connection Code             | F                              |
| Pump inlet                  | DN 125                         |
| Pump outlet                 | DN 100                         |
| Pressure Level              | PN 16                          |
| occipital ring              | occipital ring                 |
|                        |                           |
| Liquid                      |                           |
| Temperature of Liquid       | 0...120°C             |   |

----

| Electric Data:                    |                        |
|-----------------------------------|-----------------------------|
| Motor type                        | MMG200L                     |
| Number of Motor Poles             | 2                           |
| Rated Power – P2            | 30kw                        |
| Frequency of Power                | 50Hz                        |
| Rated voltage                     | 3 x 380-415 D / 660-690 Y V |
| Rated current                     | 53.3 / 31A                  |
| Start-up current                  | 720%                        |
| Cos phi-power factor              | 0, 88                       |
| Rated speed                       | 2950 rpm                    |
| efficiency of mortar in Full load | 91,4%                       |
| efficiency of mortar in 3/4 load  | 92,1%                       |
| efficiency of mortar in 1/2 load  | 91,3%                       |
| Encapsulation grade (IEC 34-5)    | IP55                        |
| Insulation grade (IEC 85)         | F                           |
| Motor protection                  | PTC                         |
| Motor No                          | 83315432                    |
| Motor series                      | Domestic                    |
|                              |                        |
| Other                             |                        |
| Net Weight                        | 335kg                       |
| Gross Weight                      | 353kg                       |
| Transport volume                  | 0.725m3                     |

----