Skip directly to site content Skip directly to page options Skip directly to A-Z link Skip directly to A-Z link Skip directly to A-Z link


Centers for Disease Control and Prevention. CDC twenty four seven. Saving Lives, Protecting People
Search
            ×
                        Mining
                        Mining
                            NIOSH
                            All CDC
                    Submit
                For a full list of topics:A-Z Index
                Advanced Search
            Advanced Search


The National Institute for Occupational Safety and Health (NIOSH)





Mining Publication: Technical Bulletin Pager Phones: Circuit Protection
Keywords: Communications Lightning arresters Lightning protection Pager phones
This page is archived for historical purposes and is no longer being maintained or updated. Contact NIOSH Mining if you need an accessible version.
Original creation date: January 1975
Authors: Arthur D. Little, Inc.
Contract/MOA Report - January 1975
Download PDF Document (0.20 MB)
NIOSHTIC2 Number: 20031847
U.S. Department of the Interior, Bureau of Mines, Contract No. S0144082, 1975 Jan; :1-7
Wires leading to or from underground facilities can develop hazardous voltages because of lightning exposure. The locations of many mine portals are particularly susceptible to lightning effects. The application of protective devices to limit this potential danger is necessary. Requirement: The Code of Federal Regulations, Title 30, Mineral Resources, Part 75, paragraph 75.52 1 identifies the requirement for lightning arrestors to be used on ungrounded, exposed power conductors and telephone wires. "Each ungrounded, exposed power conductor and telephone wire that leads underground shall be equipped with suitable lightning arrestors of approved type within 100 feet of the point where the circuit enters the mine." For telephone circuits, a wide range of protective devices are available. The public service telephone companies and Rural Electrification Authority have considerable experience with the problem. The current recommendation by these organizations for such installations is to use gas-tube protectors, operating with a well-designed and constructed grounding circuit. Although pager phones are d-c systems, with signals in the audio range, many installations have coupled RF (Radio Frequency) signals on the same cable that is used for the pager system. The telephones themselves are constructed with isolating circuits, so as not to disturb RF transmission. Lightning arrestors and protective circuits must also provide this same isolation and circuit integrity for the RF signals. Capacitive protective elements cannot be used for lightning protection of such circuits, as they would short out the RF signals. Lightning strokes, either cloud-to-cloud or cloud-to-ground, release tremendous energy. The voltage associated with cloud-to-earth lightning stokes is about 5 to 20 million Volts, but the danger is in the large amounts of energy developed by the fields induced in exterior cabling. Arrestor Connection: In early telephone installations, carbon blocks of 3 mil (0.003") carbon were used as a protective breakdown device for phone circuits, but in the past ten years gas-tube devices have become more acceptable. When sufficient energy is developed between two circuits, such as a telephone line and ground reference, the protective device ionizes and provides a low-impedance path to ground, thus Arthur I3 Little, Inc keeping the hazardous voltage from reaching the remainder of the system. In a gas-tube this action takes place in a few microseconds (0.000001 second) by the ionization of gas at 1 50 to 500 Volts in a chamber, as shown below. Most installations provide a discharge path from each conductor to ground. This is the two-element system shown below. A limitation of this system is that it does not protect against energy levels that can build up between the line pair. Either of the two protective arrestors can fire on a random statistical basis with a high-energy signal applied to the line conductors. In the short time before the second arrestor operates, a large energy potential can be present between the line pair conductors. To offset this condition, the three-element system was developed. The first approach was to provide three separate arrestors as shown below. This scheme is somewhat successful, but retains the problem of significant time delays before all potential paths are closed to the buildup of energy to a danger level. A scheme to improve on this deficiency is to include all gaps within one enclosure so that when any gap is ionized the other two will benefit from a preionization and reduce the time to complete all circuits as the energy differential increases. Ground Wire: Title 30, Part 75, paragraph 75.701-4 identifies that grounding wires for the type of cable used in telephone systems (less than #6 AWG) shall be at least the same cross-sectional area as that of the conductor cable. Good installation practices dictate that the choice of ground cable for this application be at least #14 AWG solid copper. Steel or other conductor may be used if the equivalent conductivity is at least equal of # 14 AWG copper (2.5 ohms/ 1,000 feet). The protective circuit should be connected close to the point of entry into a building or below ground, and in any case not more than 100 feet from where the circuit enters the mine. Ground reference should be at a short distance from the protective circuit. Ground can be a good electromechanical bond by direct connection to a metallic water pipe leading underground, or to a buried metal stake. A 314-inch-diameter, 8-foot-long copper rod, buried vertically so that the top is 18 to 24 inches below the top surface, is normal practice to ensure a solid electrical ground reference.
Image of publication Technical Bulletin Pager Phones: Circuit ProtectionContract/MOA Report - January 1975
Download PDF Document (0.20 MB)
NIOSHTIC2 Number: 20031847
U.S. Department of the Interior, Bureau of Mines, Contract No. S0144082, 1975 Jan; :1-7
See Also
Development of a Visual Display and Control System
Experience with an Integrated, Computer-Controlled Communications and Monitoring System at the Robena Mine
Medium-Frequency Propagation in Coal Mines
Mine Communications and Tracking Glossary
Technical Bulletin Pager Phones: Installation
Theory on the Propagation of UHF Radio Waves in Coal Mine Tunnels
Through-The-Earth Wireless Real-Time Two-Way Voice Communications
U.S. Bureau of Mines New Developments in Mine Communications
Ultra-Low Frequency Through-the-Earth Communication Technology
Underground Mine Communications
Underground Mine Communications (in Four Parts): 2. Paging Systems
Page last reviewed: September 21, 2012
Page last updated: September 21, 2012
Content source: National Institute for Occupational Safety and Health, Mining Program
Facebook
        Twitter
        LinkedIn
        Syndicate Mining
        Site BrowserSafety and Health TopicsData & StatisticsMethodologyMine DisastersMSHA Data FilesMine & Mineworker ChartsTools & PublicationsTools You Can UsePublicationsNews & ArticlesResearch ProgramNORA Mining CouncilStrategic PlanMining Program, 2019-2023Miner Health Program, 2020-2030ProjectsContractsFunding OpportunitiesMining LinksAbout UsContact NIOSH MiningEmploymentFacilitiesHistoryVisitor Information NIOSH Homepage
 NIOSH A-Z
Workplace Safety & Health Topics
Publications and Products
Programs


About CDC
					Contact Us
					800-232-4636
 Facebook Twitter Instagram LinkedIn Youtube Pinterest Snapchat
 CONTACT CDC
				Contact Us
							Call 800-232-4636
							Email Us
			ABOUT CDC
				About CDC
							Jobs
							Funding
			POLICIES
				Accessibility
							External Links
							Privacy
							Policies
							No Fear Act
							FOIA
							OIG
							Nondiscrimination
							Vulnerability Disclosure Policy
			CONNECT WITH US
				Facebook
								Twitter
								Instagram
								LinkedIn
							Youtube
								Pinterest
								Snapchat
								Email
			LANGUAGES
				Español
							繁體中文
							Tiếng Việt
							한국어
							Tagalog
							Русский
							العربية
							Kreyòl Ayisyen
							Français
							Polski
							Português
							Italiano
							Deutsch
							日本語
							فارسی
							English


U.S. Department of Health & Human Services
			Accessibility
			External Links
			Privacy
			Policies
			No Fear Act
			FOIA
			Nondiscrimination
			OIG
			Vulnerability Disclosure Policy
			USA.gov


Exit Notification / Disclaimer Policy Close
 Links with this icon  indicate that you are leaving the CDC website. The Centers for Disease Control and Prevention (CDC) cannot attest to the accuracy of a non-federal website.
				Linking to a non-federal website does not constitute an endorsement by CDC or any of its employees of the sponsors or the information and products presented on the website.
				You will be subject to the destination website's privacy policy when you follow the link.
				CDC is not responsible for Section 508 compliance (accessibility) on other federal or private website. Website Disclaimers
 Cancel Continue