Skip directly to site content Skip directly to page options Skip directly to A-Z link


Centers for Disease Control and Prevention. CDC twenty four seven. Saving Lives, Protecting People
															Search
		×
			NIOSH
			NIOSH
				All CDC
				Submit
			For a full list of topics:A-Z Index
			Advanced Search
		Advanced Search


The National Institute for Occupational Safety and Health (NIOSH)


Section Navigation
			
			CDC Home


Facebook
        Twitter
        LinkedIn
        Syndicate





Controlling Formaldehyde Exposures During Embalming										Related Pages
										1998
DHHS (NIOSH) Publication Number 98-149
Hazard
Embalmers are exposed to formaldehyde at concentrations averaging up to 9 parts per million (ppm) during embalming. Short-term exposures to this strong-smelling gas cause eye, nose, and throat irritation at levels up to 5 ppm. At levels from 10 to 20 ppm, it causes cough, chest tightness, and unusual heart beat; and from 50 to 100 ppm, fluid on the lungs, followed by death. Exposure to formaldehyde over a long time may also cause cancer.
Controls
NIOSH engineers designed and evaluated a local exhaust ventilation [LEV] system that effectively reduces embalmer’s exposure to formaldehyde below the OSHA permissible limit of 0.75 ppm, as an 8-hr time-weighted average exposure.
Local Exhaust Ventilation
The LEV system consists of a pair of 6-ft-long slot hoods placed on each side of the embalming table. These slot hoods capture formaldehyde by means of an exhaust fan placed outside the embalming room. The exhaust fan maintains an optimum airflow of 700 cubic feet per minute. For a slot width of 1 inch, the slot velocity is 720 feet per minute. Embalming equipment manufacturers and distributors can provide LEV systems for existing tables, or a sheet metal contractor can custom build the LEV system [see Figure 1.].
General room (dilution) ventilation is another way to exhaust formaldehyde from the embalming room. Depending on how well the air in a room is mixed, 4 to 13 times more exhaust air is needed to achieve the same control as from the LEV system. Make-up air costs for heating or cooling are considerably less for the LEV system than for dilution ventilation. Therefore, NIOSH recommends that the primary control be the LEV system.
Figure 1. Diagram of local exhaust ventilation slot hood.Figure 1. Diagram of local exhaust ventilation slot hood.
Acknowledgments
The principal contributors to this publication are Michael G. Gressel, Anne Votaw, Rosmarie T. Hagedorn, and Jerome P. Flesch. Drawing by Dick Carlson.
This document is in the public domain and may be freely copied or reprinted. NIOSH encourages all readers of this HAZARD CONTROLS to make it available to all interested employers and workers.
Controlling Formaldehyde Exposures During Embalming pdf icon[PDF – 157 KB]
							
					
						Page last reviewed:  June 6, 2014					Content source: 	National Institute for Occupational Safety and Health homeNIOSH Publications & Products
NIOSH-Issued Publications
Search NIOSHTIC-2 Research Database
Docket
Documents for Public Review
Peer Review Agenda
Databases
eNews
Federal Register Noticesplus icon
FRN Archive 2007-2010
FRN Archive 2005-2006
FRN Archive 2001-2004
FRN Archive 1996-2000
Press Releases and Updatesplus icon
Press Release Archives 2010-2013
Press Release Archives 2006-2009
Press Release Archives 2001-2005
Press Release Archives 1998-2000
Press Release Archives 1992-1997
Regulations
Regulatory Agenda
Science Blog
Software
Video Follow NIOSH Facebook
Pinterest
Twitter
YouTube
 NIOSH Homepage NIOSH A-Z
Workplace Safety & Health Topics
Publications and Products
Programs
Contact NIOSH


About CDC
					Contact Us
					800-232-4636
 Facebook Twitter Instagram LinkedIn Youtube Pinterest Snapchat
 CONTACT CDC
				Contact Us
							Call 800-232-4636
							Email Us
			ABOUT CDC
				About CDC
							Jobs
							Funding
			POLICIES
				Accessibility
							External Links
							Privacy
							Policies
							No Fear Act
							FOIA
							OIG
							Nondiscrimination
							Vulnerability Disclosure Policy
			CONNECT WITH US
				Facebook
								Twitter
								Instagram
								LinkedIn
							Youtube
								Pinterest
								Snapchat
								Email
			LANGUAGES
				Español
							繁體中文
							Tiếng Việt
							한국어
							Tagalog
							Русский
							العربية
							Kreyòl Ayisyen
							Français
							Polski
							Português
							Italiano
							Deutsch
							日本語
							فارسی
							English


U.S. Department of Health & Human Services
			Accessibility
			External Links
			Privacy
			Policies
			No Fear Act
			FOIA
			Nondiscrimination
			OIG
			Vulnerability Disclosure Policy
			USA.gov


Exit Notification / Disclaimer Policy Close
 Links with this icon  indicate that you are leaving the CDC website. The Centers for Disease Control and Prevention (CDC) cannot attest to the accuracy of a non-federal website.
				Linking to a non-federal website does not constitute an endorsement by CDC or any of its employees of the sponsors or the information and products presented on the website.
				You will be subject to the destination website's privacy policy when you follow the link.
				CDC is not responsible for Section 508 compliance (accessibility) on other federal or private website. Website Disclaimers
 Cancel Continue