Skip directly to site content Skip directly to page options Skip directly to A-Z link


Centers for Disease Control and Prevention. CDC twenty four seven. Saving Lives, Protecting People
															Search
		×
			NIOSH
			NIOSH
				All CDC
				Submit
			For a full list of topics:A-Z Index
			Advanced Search
		Advanced Search


The National Institute for Occupational Safety and Health (NIOSH)


Facebook
        Twitter
        LinkedIn
        Syndicate





Controlling Chemical Hazards During the Application of Artificial FingernailsEspañol (Spanish)										Related Pages
										January 1999
DHHS (NIOSH) Publication Number 99-112
cover page - Hazard ID 5-Cercopithecine herpesvirus 1 (B Virus) Infection Resulting from Ocular Exposure
Hazard
Artificial fingernail products are made from many chemicals, but the main one in most of these products is ethyl methacrylate (EMA). In 1974 the U.S. Food and Drug Administration outlawed a similar chemical, methyl methacrylate (MMA), used in fingernail products. MMA was proven harmful to nail technicians and customers. However, both MMA and EMA can cause contact dermatitis, asthma, and allergies in the eyes and nose, all problems that nail technicians know about. Both can make the eyes, nose, and other mucous membranes sting, become red, and swell. Customers are at risk, too. Because it is often difficult to tell which chemical in a nail salon is causing a sensitivity or allergy, it is best to control your exposure before you become sensitized.
Controls
In the nail salon, to get rid of EMA in the air you breathe, you should apply artificial fingernails at a ventilated work table. It is also helpful to keep all bottles of fingernail liquid tightly capped. Finally, you should look at your work habits to see if they can be improved.
Ventilated Table
Researchers from the National Institute for Occupational Safety and Health (NIOSH) have found that a ventilation table protects the nail technician best against breathing EMA. The ventilated table is the most important engineering control for getting rid of EMA in the fingernail salon because the vented table places local exhaust ventilation close to the work area.
Place local exhaust ventilation as close to the EMA source as possible. Exhaust this air outdoors. Charcoal filters that allow the air to be used over again are not recommended because it is hard to know when the charcoal is full.
Build a ventilated table, or change a table you already own into a ventilated one (Figure 1). Ventilated table sizes will vary from nail salon to nail salon. Choose a wood for your ventilated table that will not soak up the chemicals. If the table acts like a sponge, it may actually expose you to the chemicals you want to avoid. A veneer-coated particle board works well for the table material.
Figure 1 - image of ventilated tableMake a hole in the table top for an air intake (called the downdraft face). This downdraft face should be placed on the technician’s side of the table. Cover the hole with a screen-like cover (or perforated plate) to prevent things from falling in.
The client’s side of the table should be a little higher than the technician’s side. This will allow the client’s hands to hang over the downdraft face and be as close as possible to the local exhaust ventilation (Figure 2).
Figure 2 - image of local exhaust diagramMake sure enough air blows through the table downdraft to get rid of the EMA. The amount of air exhausted depends on its speed as it moves through the downdraft face and on the size of the table opening. However, too much air rushing past the fingernails may cause the artificial nail product to crystallize.
An air speed of 620 feet per minute, directly above the 13- by 4-inch downdraft face works well. A 22-inch baffle should surround the downdraft face to pull the moving air closer to the client=s hands.
Different drying times are needed for different fingernail products and different application techniques. Although a stronger and larger airflow will collect more dust during filing and dry the color coat faster, a slower and lower airflow gives better results for the artificial fingernail product.
Choose an exhaust fan that can exhaust at least 250 cubic feet per minute of air and has 1/4-inch static pressure. A 1/8 horse power centrifugal fan should work well. To prevent fan noise from getting in the way of talk or client comfort, you can do one of three things: (1) buy a quiet fan, (2) put a cover over a noisier fan, or (3) buy an outdoor fan to be placed on an outside wall. The fan should have control settings. Use either a multi-speed or high-volume exhaust fan with a damper. You can find a fan supplier by looking in a directory called “Thomas Register of American Manufacturers.” Look under the headings of “fans” or “fans, centrifugal.” Your public library should have this directory. The fan supplier may be able to install your fan, as well as supply the duct work and other needed materials.
Provide enough makeup air to replace the exhausted air. If the makeup air is too weak, there will be negative pressure areas and perhaps drafts. The air intake, which pulls outdoor air inside, should not be placed near the building exhaust. If the exhaust and intake vents are too close, dirty air will be pulled back into the room.
Comfort fans should not blow directly on the downdraft face because the strong air movement can interfere with the exhaust airflow.
Keep Dispenser Bottles Closed
Use dispenser bottles that have small openings, only large enough for an application brush to enter. The bottle stoppers should be pressure sensitive. A dispenser bottle with a pressure-sensitive stopper and small opening will result in less evaporation of the fingernail liquid and, thus, will cut down on possible exposures to methacrylates (Figure 3).
Figure 3 - image of closed dispenser bottleKeep Dispenser Bottles Closed Change Your Work Habits
Nail technicians can also lower their exposures to these airborne chemicals by changing some of their work habits:
EMA-soaked gauze pads should be placed in a sealed bag before being thrown in the trash can.
Trash can liners should be changed daily.
No more than the needed amount of fingernail liquid should be poured into the closed dispenser bottle.
Nail technicians should wear personal protective clothing and glasses. When technicians remove artificial nails, chips of acrylic often fly off, creating a need for eye protection. In addition to safety glasses, technicians also should wear long sleeves and gloves to protect their skin from acrylic dust.
Technicians should wash their hands, arms, and face with mild soap and water several times throughout the day to remove potentially irritating dust.
Eating and drinking should not be allowed where artificial fingernails are applied or in other working areas. Methacrylates in nail dust can be carried accidently to the mouth or face on a cup or other food item, and this contact may cause a skin rash. Also, many other chemicals are used in a salon that could cause health problems if swallowed.
Smoking should be banned for the entire salon because many of the chemicals in a beauty shop, including nail products, catch fire easily.Acknowledgments
The principal contributors to this publication are Cheryl F. Estill, Amy B. Spencer, Jane B. McCammon, R. Leroy Mickelsen, Ova E. Johnston, Anne Votaw, and Jerome P. Flesch. The drawings are by Dick Carlson, Daniel Farwick, and Daniel Watkins. Desktop publishing was provided by Rosmarie T. Hagedorn and Susan Kaelin.
This document is in the public domain and may be freely copied or reprinted. NIOSH encourages all readers of this *HAZARD CONTROLS* to make it available to all interested employers and workers.
Controlling Chemical Hazards During the Application of Artificial Fingernailspdf icon [PDF – 175.18 KB]
							
					
						Page last reviewed:  June 6, 2014					Content source: 	National Institute for Occupational Safety and Health homeNIOSH Publications & Products
NIOSH-Issued Publications
Search NIOSHTIC-2 Research Database
Docket
Documents for Public Review
Peer Review Agenda
Databases
eNews
Federal Register Noticesplus icon
FRN Archive 2007-2010
FRN Archive 2005-2006
FRN Archive 2001-2004
FRN Archive 1996-2000
Press Releases and Updatesplus icon
Press Release Archives 2010-2013
Press Release Archives 2006-2009
Press Release Archives 2001-2005
Press Release Archives 1998-2000
Press Release Archives 1992-1997
Regulations
Regulatory Agenda
Science Blog
Software
Video Follow NIOSH Facebook
Pinterest
Twitter
YouTube
 NIOSH Homepage NIOSH A-Z
Workplace Safety & Health Topics
Publications and Products
Programs
Contact NIOSH


About CDC
					Contact Us
					800-232-4636
 Facebook Twitter Instagram LinkedIn Youtube Pinterest Snapchat
 CONTACT CDC
				Contact Us
							Call 800-232-4636
							Email Us
			ABOUT CDC
				About CDC
							Jobs
							Funding
			POLICIES
				Accessibility
							External Links
							Privacy
							Policies
							No Fear Act
							FOIA
							OIG
							Nondiscrimination
							Vulnerability Disclosure Policy
			CONNECT WITH US
				Facebook
								Twitter
								Instagram
								LinkedIn
							Youtube
								Pinterest
								Snapchat
								Email
			LANGUAGES
				Español
							繁體中文
							Tiếng Việt
							한국어
							Tagalog
							Русский
							العربية
							Kreyòl Ayisyen
							Français
							Polski
							Português
							Italiano
							Deutsch
							日本語
							فارسی
							English


U.S. Department of Health & Human Services
			Accessibility
			External Links
			Privacy
			Policies
			No Fear Act
			FOIA
			Nondiscrimination
			OIG
			Vulnerability Disclosure Policy
			USA.gov


Exit Notification / Disclaimer Policy Close
 Links with this icon  indicate that you are leaving the CDC website. The Centers for Disease Control and Prevention (CDC) cannot attest to the accuracy of a non-federal website.
				Linking to a non-federal website does not constitute an endorsement by CDC or any of its employees of the sponsors or the information and products presented on the website.
				You will be subject to the destination website's privacy policy when you follow the link.
				CDC is not responsible for Section 508 compliance (accessibility) on other federal or private website. Website Disclaimers
 Cancel Continue