Skip directly to site content Skip directly to search


Español  Other Languages


Centers for Disease Control and Prevention. CDC twenty four seven. Saving Lives, Protecting People
 Search
		×
			NIOSH
			NIOSH
				All CDC
				Submit
			For a full list of topics:A-Z Index
			Advanced Search
		Advanced Search


The National Institute for Occupational Safety and Health (NIOSH)








Preventing Electrocutions of Workers in Fast Food Restaurants						Español (Spanish)							Print
																Related Pages
										December 1984
DHHS (NIOSH) Publication Number 85-104
Background
On June 30, 1984, an 18-year-old male worker in a fast food restaurant died by electrocution on the job. The worker, who had 15 months’ work experience at this restaurant, was electrocuted while kneeling to insert the plug of a portable electric toaster into a 110-12OV/20 amp outlet on a floor which had recently been damp-mopped. The victim was found convulsing. He had one hand on the plug, and the other on the receptacle box. Another worker who attempted to “take the pulse” of the victim received an electrical shock but was not injured.
When the assistant manager saw what was happening, he went to the breaker box to shut off the current but was unable to locate the appropriate breaker. The emergency rescue squad was called, and before they arrived, the proper circuit breaker was located and thrown. By that time, the victim had been in contact with the electricity for three to eight minutes. Attempts at cardiopulmonary resuscitation (CPR) by fellow workers and members of the emergency rescue squad were unsuccessful; the victim was pronounced dead on arrival at a nearby hospital.
The specific events that resulted in this electrocution could not be defined with absolute precision. However, investigators from NIOSH concluded that while the victim was inserting the plug of the toaster into the receptacle with his right hand and holding open the grounded metal receptacle cover with his left hand, the index finger of his right hand touched an energized prong of the plug and he received an electrical shock across the chest.
Recommendations By NIOSH
Because one-tenth (0.1) amp of electricity flowing through the human body for two seconds can cause death, any active electrical circuit can pose a potentially lethal hazard.
Electrical hazards in the kitchens of commercial restaurants are particular concern because of the variety of electrical appliances in use. However, safeguards and safe work practices can eliminate most of these hazards NIOSH recommends that:
Ground fault circuit interrupters (GFCIs) of the breaker or receptacle type be installed in situations where electricity and wetness coexist. GFCIs will interrupt the electrical circuit before current sufficient to cause death or serious injury has passed through a body. GFCIs are inexpensive ($50.00-$85.00 for breaker type, $25.00-$45.00 for receptacle type) and a qualified electrician can install them in existing electrical circuits with relative ease;
Exposed receptacle boxes be made of nonconductive material so that contact with the box will not constitute “a ground”;
Plugs and receptacles be designed to prevent energization until insertion is complete;
All circuit breaker or fuse boxes bear a label for each circuit breaker or fuse which clearly identifies its corresponding outlets and fixtures. Also, breaker switches should not be used for on-off switches;
All workers, when hired, be made aware of electrical hazards and of safe work practices by which to avoid these hazards. Workers should be informed that, in the event of an electrical injury, no contact should be made with the victim or the electrical apparatus causing the injury until the current has been shut off; and that
Workers in the restaurant be encouraged to train in CPR.We are requesting that editors of appropriate trade journals, health officials, and especially food service inspectors institute and bring these recommendations to the attention of restaurant managers and owners and potential victims. Suggestions, requests for additional information on control practices, or questions related to this announcement should be directed to Mr. John Moran, Director, Division of Safety Research, National Institute for Occupational Safety and Health, 944 Chestnut Ridge Road, Morgantown, West Virginia 26505, Telephone (304) 291-4595.
We greatly appreciate your assistance.
[signature]
J. Donald Millar, M.D., D.T.P.H. (Lond.)
Assistant Surgeon General
Director, National Institute for Occupational Safety and Health
Centers for Disease Control
Image of hands manipulating a electrical switch boxPreventing Electrocutions of Workers in Fast Food Restaurants
							
					
							Last Reviewed:  June 6, 2014						Source: 	National Institute for Occupational Safety and Health
					Facebook
        Twitter
        LinkedIn
        Syndicate homeNIOSH Publications & Products
NIOSH-Issued Publications
Search NIOSHTIC-2 Research Database
Docket
Documents for Public Review
Peer Review Agenda
Databases
eNews
Federal Register Noticesplus icon
FRN Archive 2007-2010
FRN Archive 2005-2006
FRN Archive 2001-2004
FRN Archive 1996-2000
Press Releases and Updatesplus icon
Press Release Archives 2010-2013
Press Release Archives 2006-2009
Press Release Archives 2001-2005
Press Release Archives 1998-2000
Press Release Archives 1992-1997
Regulations
Regulatory Agenda
Science Blog
Software
Video Follow NIOSH Facebook
Pinterest
Twitter
YouTube
 NIOSH Homepage NIOSH A-Z
Workplace Safety & Health Topics
Publications and Products
Programs
Contact NIOSH


About CDC
					Contact Us
					800-232-4636
 Facebook Twitter Instagram LinkedIn Youtube Pinterest Snapchat
 CONTACT CDC
				Contact Us
							Call 800-232-4636
							Email Us
			ABOUT CDC
				About CDC
							Jobs
							Funding
			POLICIES
				Accessibility
							External Links
							Privacy
							Policies
							No Fear Act
							FOIA
							OIG
							Nondiscrimination
							Vulnerability Disclosure Policy
			CONNECT WITH US
				Facebook
								Twitter
								Instagram
								LinkedIn
							Youtube
								Pinterest
								Snapchat
								Email
			LANGUAGES
				Español
							繁體中文
							Tiếng Việt
							한국어
							Tagalog
							Русский
							العربية
							Kreyòl Ayisyen
							Français
							Polski
							Português
							Italiano
							Deutsch
							日本語
							فارسی
							English


U.S. Department of Health & Human Services
			Accessibility
			External Links
			Privacy
			Policies
			No Fear Act
			FOIA
			Nondiscrimination
			OIG
			Vulnerability Disclosure Policy
			USA.gov


Exit Notification / Disclaimer Policy Close
 Links with this icon  indicate that you are leaving the CDC website. The Centers for Disease Control and Prevention (CDC) cannot attest to the accuracy of a non-federal website.
				Linking to a non-federal website does not constitute an endorsement by CDC or any of its employees of the sponsors or the information and products presented on the website.
				You will be subject to the destination website's privacy policy when you follow the link.
				CDC is not responsible for Section 508 compliance (accessibility) on other federal or private website. Website Disclaimers
 Cancel Continue