Skip directly to site content Skip directly to page options Skip directly to A-Z link


Centers for Disease Control and Prevention. CDC twenty four seven. Saving Lives, Protecting People
															Search
		×
			NIOSH
			NIOSH
				All CDC
				Submit
			For a full list of topics:A-Z Index
			Advanced Search
		Advanced Search


The National Institute for Occupational Safety and Health (NIOSH)


Section Navigation
			
			CDC Home


Facebook
        Twitter
        LinkedIn
        Syndicate





Hazard ID 7 - Fire Fighting Hazards During Propane Tank FiresEspañol (Spanish)										Related Pages
										June 1999
DHHS (NIOSH) Publication Number 99-129
cover page - Hazard ID 7-Fire Fighting Hazards During Propane Tank Fires
Description of Hazard
On April 15, 1998, the National Institute for Occupational Safety and Health (NIOSH) investigated the line-of-duty deaths of two volunteer firefighters (Report No. 98F14). The investigation was part of the NIOSH Fire Fighter Fatality Investigation and Prevention Program. Both firefighters were part of a volunteer fire department that responded to an 18,000-gallon bulk propane tank fire.
The fire started after unprotected external piping from the tank was struck by an all-terrain vehicle and the propane vapors were ignited by a pilot flame from a nearby vaporizer. Upon arrival at the fire scene, the firefighters watered down the buildings adjacent to the propane tank and allowed the tank to burn itself out, since the tank was venting. About 8 minutes after the fire fighters arrived, the tank exploded, separated into four parts, and flew in four directions. The two firefighters (who were approximately 105 feet from the tank) were struck by a piece of the exploding tank and killed instantly. Six other firefighters and a deputy sheriff were injured as a result of the explosion. Such explosions may occur whenever flames contact propane tanks.
18,000-gallon propane tank
An 18,000-gallon propane tank with protective fencing to reduce the risk of physical damage to the exterior piping system.
Recommendations for Prevention
During propane tank fires, the potential always exists for an explosion known as boiling liquid expanding vapor explosion (BLEVE). To reduce this risk, fire departments, fire fighters, and propane tank owners and users should follow the recommendations below. They are based on emergency response procedures in the 1996 North American Emergency Response Guidebook (NAERG96), which were developed jointly by Transport Canada, the U.S. Department of Transportation, and the Secretariat of Communications and Transportation of Mexico.
Fire fighters should do the following:
Fight fire from the maximum distance possible, or use unmanned hose holders or monitor nozzles.
Cool containers by flooding them with large quantities of water until well after fire is out.
Do not direct water at the source of leak or at safety devices; icing may occur.
Leave the area immediately if you hear a rising sound from venting safety devices or see discoloration of the tank.
For massive fires, use unmanned hose holders or monitor nozzles; if this is impossible, leave the area and let the fire burn.
Be aware that when a BLEVE occurs, sections of the tank can fly in any direction. Just avoiding the ends of the tank should not be considered a safe operating procedure.Fire departments should do the following:
Follow the OSHA regulations [29 CFR*1910.120 (q)]Emergency response to hazardous substance releases]. These regulations should be incorporated into fire department standard operating procedures (SOPs), which should be strictly enforced.
Train first responders to be aware of the hazards associated with propane tank fires, including BLEVE.*CFR = Code of Federal Regulations
Ensure that fire department code enforcement personnel adhere to the guidelines specified by the National Fire Protection Association (NFPA) and NAERG96 for the evaluation and certification of propane tanks.
For more information about safe fire fighting procedures for propane tank fires, see NAERG96 or contact the NFPA, the National Propane Gas Association (NPGA), or the International Fire Service Training Association (IFSTA).Propane tank owners and users should do the following:
Protect above ground external piping from physical damage with fencing or other protection Equip propane tank piping with excess-flow valves and emergency shutoff valves in accordance with the NFPA 58, LP-Gas Code.The Fire Fighter Fatality Investigation and Prevention Program is conducted by NIOSH. The purpose of the program is to determine factors that cause or contribute to fire fighter deaths suffered in the line of duty and to develop strategies for preventing similar incidents in the future.
Acknowledgments
The principal contributors to this publication were Richard W. Braddee and Frank C. Washenitz II. Jerome P. Flesch provided technical review, and Kristina Wasmund and Vanessa Becks provided desktop publishing.
Hazard ID 7 – Fire Fighting Hazards During Propane Tank Firespdf icon [PDF – 96 KB]
							
					
						Page last reviewed:  June 6, 2014					Content source: 	National Institute for Occupational Safety and Health homeNIOSH Publications & Products
NIOSH-Issued Publications
Search NIOSHTIC-2 Research Database
Docket
Documents for Public Review
Peer Review Agenda
Databases
eNews
Federal Register Noticesplus icon
FRN Archive 2007-2010
FRN Archive 2005-2006
FRN Archive 2001-2004
FRN Archive 1996-2000
Press Releases and Updatesplus icon
Press Release Archives 2010-2013
Press Release Archives 2006-2009
Press Release Archives 2001-2005
Press Release Archives 1998-2000
Press Release Archives 1992-1997
Regulations
Regulatory Agenda
Science Blog
Software
Video Follow NIOSH Facebook
Pinterest
Twitter
YouTube
 NIOSH Homepage NIOSH A-Z
Workplace Safety & Health Topics
Publications and Products
Programs
Contact NIOSH


About CDC
					Contact Us
					800-232-4636
 Facebook Twitter Instagram LinkedIn Youtube Pinterest Snapchat
 CONTACT CDC
				Contact Us
							Call 800-232-4636
							Email Us
			ABOUT CDC
				About CDC
							Jobs
							Funding
			POLICIES
				Accessibility
							External Links
							Privacy
							Policies
							No Fear Act
							FOIA
							OIG
							Nondiscrimination
							Vulnerability Disclosure Policy
			CONNECT WITH US
				Facebook
								Twitter
								Instagram
								LinkedIn
							Youtube
								Pinterest
								Snapchat
								Email
			LANGUAGES
				Español
							繁體中文
							Tiếng Việt
							한국어
							Tagalog
							Русский
							العربية
							Kreyòl Ayisyen
							Français
							Polski
							Português
							Italiano
							Deutsch
							日本語
							فارسی
							English


U.S. Department of Health & Human Services
			Accessibility
			External Links
			Privacy
			Policies
			No Fear Act
			FOIA
			Nondiscrimination
			OIG
			Vulnerability Disclosure Policy
			USA.gov


Exit Notification / Disclaimer Policy Close
 Links with this icon  indicate that you are leaving the CDC website. The Centers for Disease Control and Prevention (CDC) cannot attest to the accuracy of a non-federal website.
				Linking to a non-federal website does not constitute an endorsement by CDC or any of its employees of the sponsors or the information and products presented on the website.
				You will be subject to the destination website's privacy policy when you follow the link.
				CDC is not responsible for Section 508 compliance (accessibility) on other federal or private website. Website Disclaimers
 Cancel Continue