Skip directly to site content Skip directly to page options Skip directly to A-Z link


Centers for Disease Control and Prevention. CDC twenty four seven. Saving Lives, Protecting People
															Search
		×
			NIOSH
			NIOSH
				All CDC
				Submit
			For a full list of topics:A-Z Index
			Advanced Search
		Advanced Search


The National Institute for Occupational Safety and Health (NIOSH)


Facebook
        Twitter
        LinkedIn
        Syndicate





Preventing Electrocutions Due to Damaged Receptacles and ConnectorsEspañol (Spanish)										Related Pages
										October 1986
DHHS (NIOSH) Publication Number 87-100
**WARNING!** Persons using electrical equipment are cautioned that the use of damaged receptacles and connectors can be extremely dangerous.
Summary
The National Institute for Occupational Safety and Health (NIOSH) is requesting assistance in preventing the electrocution of workers due to the use of damaged electrical receptacles and connectors. Two recent incidents are described. Results of the investigations indicate that *periodic inspection, recognition of hazards,* and *proper use of receptacles and connectors,* and *prompt repair of damaged connectors and receptacles,* could prevent such incidents. Editors of appropriate trade journals, safety and health officials, and especially those who work with electrical equipment, are requested to bring these recommendations to the attention of owners, managers, and workers.
Background
Occupational electrocutions continue to be a serious problem throughout the United States. Data obtained from the Bureau of Labor Statistics’ Annual Survey indicate that approximately 10% of all occupational fatalities are due to electrocutions. Those data, as well as other information collected by the National Institute for Occupational Safety and Health (NIOSH), demonstrate that fatalities due to electrocutions occur in a variety of ways. For example, previous NIOSH Alerts have described cases in which workers have been electrocuted as a result of contacting improperly grounded equipment, or when cranes or grain augers have contacted overhead power lines [1,2]. This Alert presents information on two fatal electrocutions that occurred as a result of using damaged receptacles and connectors.
Two investigations by NIOSH found evidence to suggest that the victims were unaware of hazards associated with the use of damaged connectors. In both cases, it was assumed that because a connector fit into a receptacle, the connection was proper and no hazard existed. The prevalence of this particular hazard is not clear. However, the cases described below point out the insidious nature of this hazard. The presence of receptacles and connectors in all workplaces, and the repetitive nature of their use (which in certain workplaces increases the possibility of damage) suggests that the potential hazard is widespread. These investigations also demonstrate that careful routine inspection and aggressive maintenance might well prevent such fatalities.
Case Reports of Fatal Incidents
Case #1–ONE FATALITY
On July 23, 1985, a 24-year-old employee of a textile mill was electrocuted when he *touched a loom frame* while performing his routine duties at the loom. The loom had become energized when an electrical, three-prong connector from a thread feeder machine was inserted into a damaged receptacle mounted on the loom. The damage to the receptacle permitted the ground prong of the plug to be improperly inserted into one of the phase terminals (90 degrees clockwise away from the appropriate ground terminal). This resulted in energizing the ground prong and the frame of the loom. When the worker touched the energized loom, he was electrocuted. It appeared, upon subsequent inspection, that the receptacle had been damaged because of a lack of adequate strain relief for the electrical cord from the thread feeder.
Case #2–ONE FATALITY
On July 29, 1985, a 29-year-old welder was electrocuted when he inserted the “male” end of an electrical plug on a portable arc welder into a broken “female” connector of an extension cord. As in the previous case, the victim inserted the ground prong of the welder cord 90 degrees clockwise away from the appropriate ground terminal of the extension cord, and the metal casing of the welder connector became energized. It appeared that the connector on the extension cord had been damaged by everyday use or abuse (being thrown down on and dragged across concrete floors, being run over by industrial equipment, etc.).
Regulatory Status
Although, in these investigations the receptacles and connectors in these investigations were listed by a nationally recognized testing laboratory, the damaged state of the receptacles negated their conformance to these listings,* to the manufacturers’ specifications, and to the safety features inherent in their design. NIOSH strongly urges periodic inspection and maintenance of electrical systems to assure compliance with applicable sections of the National Electric Code, OSHA standards, and other listing requirements. Electrical components should be used only in accordance with the manufacturers’ specifications, and should be tested and approved by a nationally recognized laboratory (such as Underwriters Laboratory, Factory Mutual, etc.).
Conclusion
The investigations by NIOSH indicate that damaged receptacles may physically permit improper electrical connections to be made, negating the intended safeguards designed into them. Furthermore, workers may not recognize a hazard of electrocution associated with the use of worn or damaged receptacles and connectors. Electrical hazards of this sort are of particular concern because of the large number of users of electrical equipment in all kinds of workplaces. Investigations of such incidents suggest failures in the areas of *PROPER UTILIZATION OF ELECTRICAL COMPONENTS, HAZARD RECOGNITION*, and *PERIODIC INSPECTION AND MAINTENANCE OF ELECTRICAL SYSTEMS*. These basic safety activities are potentially lifesaving in preventing such incidents.
Caution should be used around **ALL** electrical circuits and equipment. The potential for electric shock should never be underestimated. Employers and other groups should regularly emphasize the safe use of electricity in the workplace. Continuous efforts must be made to prevent electrical injuries and deaths due to damaged receptacles and connectors.
Recommendations
NIOSH makes the following recommendations in these areas:
1. Proper Utilization of Electrical Systems
All receptacles and connectors should be used only in accordance with the manufacturers’ specifications, and the specific listing for the item as set forth by nationally recognized testing laboratories. Users should be advised of the importance of using receptacles and connectors only for applications for which they have been designed. When a component is selected for use, it should be evaluated to determine if it can tolerate the environment to which it will be exposed. Physical abuse and stress on these components should be minimized by the selection of a safe location and by the use of stress/strain relief devices.
2. Awareness and Recognition of Hazards
Policies that address the proper use of receptacles and connectors should be developed and implemented by qualified safety personnel. Safety training should emphasize awareness and recognition of electrical hazards associated with receptacles and connectors (i.e., broken receptacles and connectors, improper electrical connections, damaged cords, the importance of grounding, etc.). Immediate corrective action should be taken when damaged components or safety hazards are encountered. When safety policies and procedures are developed, they should be enforced.
3. Periodic Inspection and Maintenance of Electrical Systems
Periodic inspections should be conducted for all electrical system equipment and components in order to identify all electrical hazards present. Records should be kept of any electrical hazards identified, and appropriate corrective action should be taken immediately. These periodic inspections should be supplemented with daily inspections by the personnel using this equipment.
We urge safety and trade associations interested in job site safety to bring these recommendations to the attention of employers.
Requests for additional information, and comments or questions concerning this announcement, should be directed to Mr. John Moran, Director, Division of Safety Research, National Institute for Occupational Safety and Health, 944 Chestnut Ridge Road, Morgantown, West Virginia 26505, Telephone (304) 291-4595.
We greatly appreciate your assistance.
[signature]
J. Donald Millar, M.D., D.T.P.H. (Lond.)
Assistant Surgeon General
Director, National Institute for Occupational Safety and Health
Centers for Disease Control
Note
* A listing means that the piece of equipment has met the safety criteria established by the testing laboratory. [Return to main text]
References
NIOSH Alert: Request for Assistance in Preventing Electrocution from Contact between Cranes and Power Lines. DHHS (NIOSH) Publication No. 85-111, National Institute for Occupational Safety and Health, 6 pages (1985).
NIOSH Alert: Request for Assistance in Preventing Grain Auger Electrocutions. DHHS (NIOSH) Publication No. 86-119, National Institute for Occupational Safety and Health, 4 pages (1986).
							
					
						Page last reviewed:  June 6, 2014					Content source: 	National Institute for Occupational Safety and Health homeNIOSH Publications & Products
NIOSH-Issued Publications
Search NIOSHTIC-2 Research Database
Docket
Documents for Public Review
Peer Review Agenda
Databases
eNews
Federal Register Noticesplus icon
FRN Archive 2007-2010
FRN Archive 2005-2006
FRN Archive 2001-2004
FRN Archive 1996-2000
Press Releases and Updatesplus icon
Press Release Archives 2010-2013
Press Release Archives 2006-2009
Press Release Archives 2001-2005
Press Release Archives 1998-2000
Press Release Archives 1992-1997
Regulations
Regulatory Agenda
Science Blog
Software
Video Follow NIOSH Facebook
Pinterest
Twitter
YouTube
 NIOSH Homepage NIOSH A-Z
Workplace Safety & Health Topics
Publications and Products
Programs
Contact NIOSH


About CDC
					Contact Us
					800-232-4636
 Facebook Twitter Instagram LinkedIn Youtube Pinterest Snapchat
 CONTACT CDC
				Contact Us
							Call 800-232-4636
							Email Us
			ABOUT CDC
				About CDC
							Jobs
							Funding
			POLICIES
				Accessibility
							External Links
							Privacy
							Policies
							No Fear Act
							FOIA
							OIG
							Nondiscrimination
							Vulnerability Disclosure Policy
			CONNECT WITH US
				Facebook
								Twitter
								Instagram
								LinkedIn
							Youtube
								Pinterest
								Snapchat
								Email
			LANGUAGES
				Español
							繁體中文
							Tiếng Việt
							한국어
							Tagalog
							Русский
							العربية
							Kreyòl Ayisyen
							Français
							Polski
							Português
							Italiano
							Deutsch
							日本語
							فارسی
							English


U.S. Department of Health & Human Services
			Accessibility
			External Links
			Privacy
			Policies
			No Fear Act
			FOIA
			Nondiscrimination
			OIG
			Vulnerability Disclosure Policy
			USA.gov


Exit Notification / Disclaimer Policy Close
 Links with this icon  indicate that you are leaving the CDC website. The Centers for Disease Control and Prevention (CDC) cannot attest to the accuracy of a non-federal website.
				Linking to a non-federal website does not constitute an endorsement by CDC or any of its employees of the sponsors or the information and products presented on the website.
				You will be subject to the destination website's privacy policy when you follow the link.
				CDC is not responsible for Section 508 compliance (accessibility) on other federal or private website. Website Disclaimers
 Cancel Continue