Skip directly to site content Skip directly to search


Español  Other Languages


Centers for Disease Control and Prevention. CDC twenty four seven. Saving Lives, Protecting People
 Search
		×
			NIOSH
			NIOSH
				All CDC
				Submit
			For a full list of topics:A-Z Index
			Advanced Search
		Advanced Search


The National Institute for Occupational Safety and Health (NIOSH)


Section Navigation
			
			CDC Home








Preventing Electrocutions During Work with Scaffolds Near Overhead Power Lines						Print
																Related Pages
										August 1991
DHHS (NIOSH) Publication Number 91-110
cover image of NIOSH Alert 91-110
**WARNING!** Workers may be electrocuted when erecting, moving, or working from metal or conductive scaffolds near overhead power lines.
The National Institute for Occupational Safety and Health (NIOSH) requests assistance in preventing electrocutions of workers who contact overhead power lines when erecting or moving scaffolds, or when using conductive tools or materials from scaffolds. Recent NIOSH investigations conducted under the Fatal Accident Circumstances and Epidemiology (FACE) Program suggest that many employers, contractors, and workers may be unaware of the hazards of working with scaffolds near uninsulated overhead power lines.
This Alert describes 13 deaths that occurred in six separate incidents when workers erected or moved scaffolds that came into contact with energized, overhead power lines, or when they contacted overhead power lines while using conductive tools or materials from scaffolds. To prevent such electrocutions, the recommendations in this Alert should be followed by every employer, manager, supervisor, and worker where scaffolds and conductive tools or materials are used near overhead power lines. Editors of appropriate trade journals, safety and health officials, and other persons (especially those in the building trades) are requested to bring this Alert to the attention of employers, contractors, and workers.
BACKGROUND
When scaffolds, conductive tools, or other materials contact overhead power lines (see Figure 1), workers receive serious and often fatal injuries. Data from the NIOSH National Traumatic Occupational Fatalities (NTOF) data base indicate that nearly 6,500 traumatic work-related deaths occur each year in the United States; an estimated 7% of these fatalities are electrocutions [NIOSH 1991]. The NTOF data base also shows that from 1980 through 1986, at least 25 deaths resulted when workers contacted overhead power lines while erecting or moving scaffolds or while using conductive tool on scaffolds.
figure 1 image of Metal scaffold contacting an overhead power lineFigure 1. *Metal scaffold contacting an overhead power line.*
A review of the NTOF data has revealed that many occupational groups (e.g., brickmasons, carpenters, painters, construction laborers, and plasterers) are at risk of electrocution because their jobs involve working from scaffolds near overhead power lines [NIOSH 1991]. Through the FACE program, NIOSH investigated 13 scaffold-related electrocutions occurring over a 39-month period (June 1986 through September 1989). Because the FACE program is active in only 11 states, these fatalities represent only a small proportion of the scaffold-related electrocutions that occur each year in the United States.
Current OSHA Regulations
Current Occupational Safety and Health Administration (OSHA) regulations for the construction industry require employers to do the following:
Instruct each worker to recognize and avoid unsafe conditions [29 CFR* 1926.21(b)(2)]
Provide prompt medical attention in case of serious injury [29 CFR 1926.50]
Advise workers exposed to electrical hazards and protect against electric shock by de-energizing the circuit or by guarding it effectively with insulation or other means [29 CFR 1926.416(a)(1) and (a)(3)]
Lock panels (scaffold sections or tiers) together vertically with pins or other equivalent means where uplift (separation of panels) may occur [29 CFR 1926.451(d)(6)]OSHA has proposed revisions to the current safety regulations to prevent workers from placing scaffolds where they might contact overhead power lines or other energized circuits [51 Fed. Reg. 42706 (1986)]. These proposed regulations require that the following minimum clearances be maintained between scaffolds and exposed, energized power lines:
2 feet for insulated power lines of less than 300 volts
10 feet for insulated power lines of 300 volts or more and for all uninsulated power linesCase Reports
As part of the FACE Program, NIOSH investigated 13 electrocutions in six incidents that occurred between June 1986 and September 1989. Each incident involved electrical contact with conductive tools or materials used by workers on scaffolds, or workers who erected or moved scaffolds near overhead power lines.
Case No. 1–Two Fatalities
On June 17, 1986, a 28-year-old painter and a 33-year-old carpenter were painting church windows from a tubular, welded-frame scaffold approximately 25 feet high and mounted on rubber casters. After the workers had completed one side of the church, they attempted to move the scaffold to another location to continue painting. The workers passed the scaffold under a 12,000-volt power line that was approximately 30 feet above ground level. They then changed direction and tried to pass the scaffold under the same power line at a point that was only 24 feet above ground level. The scaffold contacted one phase of the power line, providing a path to the ground for the electric current. The two workers grasping the scaffold were electrocuted [NIOSH 1986e].
Case No. 2–One Fatality
On August 27, 1986, a company owner and six workers were painting a concrete silo. A 5- by 7-foot tubular, welded-frame scaffold was erected to reach the top of the silo approximately 6 feet across from a 7,200-volt power line. Workers were using 8-foot aluminum poles with rollers to paint the side of the silo. A 19-year-old laborer who was painting from the scaffold pulled the aluminum pole back onto the scaffold to load more paint onto the roller. In doing so, he contacted the power line with the aluminum pole and was electrocuted [NIOSH 1986g].
Case No. 3–Four Fatalities
On October 31, 1986, a crew of four painters (aged 56, 37, 37, and 31) completed painting one side of a three-story structure. The crew was using a five-tier, tubular, welded-frame scaffold mounted on 5-inch, rubber-clad aluminum wheels. The painters and the crew chief attempted to move the 28.5-foot scaffold to the other side of the structure. The scaffold contacted one phase of a 12,000-volt power line that was approximately 27.5 feet above the ground. The contact created a path to the ground for the electric current. The four painters were electrocuted and the crew chief was severely burned [NIOSH 1986a].
Case No. 4–One Fatality
On November 24, 1986, seven employees of a masonry company were erecting a brick wall from a tubular, welded-frame scaffold approximately 24 feet high. The scaffold had been constructed approximately 21 inches across from a 7,620-volt power line. A laborer carried a piece of wire reinforcement (10 feet long by 8 inches wide) along the top section of the scaffold and contacted the power line with it. The laborer, who was wearing leather gloves, received an electric shock and dropped the wire reinforcement, which fell across the power line and simultaneously contacted the metal rail of the scaffold, energizing the entire scaffold. A 20-year-old bricklayer standing on the work platform in contact with the main scaffold was electrocuted [NIOSH 1986f].
Case No. 5–Two Fatalities
On June 5, 1987, a seven-tier, tubular, welded-frame scaffold (31 feet high) was erected to paint a 33-foot-high sign at the entrance of a new shopping mall. After the sign had been partially painted, the scaffold was moved to allow concrete to be placed in the area around the sign. The scaffold was positioned approximately 10 feet horizontally from a 13,750-volt overhead power line. Several days later, the crew of seven workers (carpenters, laborers, and painters) were instructed to replace the scaffold and finish painting the sign. The crew positioned themselves around the scaffold and attempted to lift it approximately 5 inches onto the newly constructed concrete pad. As they were lifting the scaffold, the top section partially separated from the adjoining section, toppled over, and contacted the power line. A 28-year-old carpenter and a 31-year-old laborer were electrocuted. The other five workers were hospitalized with electrical burns [NIOSH 1987b].
Case No. 6–Three Fatalities
On September 25, 1989, six workers were using a mobile, elevated work platform to install aluminum siding on a warehouse under construction. The platform measured 25.5 feet from ground level to the top guardrail. Approximately 3 days before the incident, the crew had passed the platform under a 69,000-volt overhead power line located 34 feet above the ground. On the day of the incident, the crew tried to pass the platform under the same power line at a different location where the power line was only 27 feet above ground level. In addition, fill dirt brought into this location for landscaping caused the ground level to slope upward approximately 1.5 feet. As the crew passed the platform under the power line, the top guardrail contacted the bottom phase of the power line. Three crew members (a 30-year-old laborer and two steel workers aged 34 and 38) were electrocuted; three others were seriously burned [NIOSH 1990b].
Conclusions
Many employers, contractors, and workers may be unaware of the hazards of working with scaffolds near overhead power lines. If the current and the proposed OSHA regulations had been followed, particularly with regard to minimum clearances, the electrocutions reported here could have been prevented.
Recommendations
The following precautions should be taken to prevent electrocutions and injuries resulting from contact between overhead power lines and conductive tools, materials, or scaffolds:
Employers, contractors, and workers should comply with the current OSHA regulations for working with scaffolds near energized power lines [29 CFR 1926.21(b)(2), 1926.50, 1926.416(a)(1), 1926.416(a)(3), 1926.451(d)(6)].
In accordance with the proposed OSHA regulations [51 Fed. Reg 42706 (1986)], scaffolds should not be used or moved within the following minimum clearance distances from exposed, energized power lines:–2 feet for insulated power lines of less than 300 volts
–10 feet for insulated power lines of 300 volts or more and for all uninsulated power lines
Employers should review existing safety programs and revise them where needed to address work with scaffolds around power lines.
Employers should develop and implement safety programs where none exist. Comprehensive safety programs should include, but not be limited to, safety training in the hazards of scaffolds and power lines, with special emphasis on avoiding inadvertent contact.
Managers and workers should conduct initial and daily surveys at the worksite before beginning any job; managers should then implement appropriate control measures and training to address hazards identified at the site.
Employers should inform workers about the hazards of erecting, moving, or working from scaffolds near overhead power lines or other energized circuits. These instructions should emphasize that most overhead, high-voltage power lines are not insulated and that workers should assume that such lines are not insulated if there is any doubt.
Employers should notify the utility company when scaffolds must be erected or moved in areas with overhead power lines where the required clearances cannot be maintained. In such situations, utility companies should de-energize the power lines or cover them with insulating hoses or blankets before any work is initiated.
Before a scaffold is erected or moved, employers should ensure that workers consider the following factors:–Distance from overhead power lines
–Vertical clearance between the ground and any sagging power lines
–Scaffold height and weight
–Wheel condition
–Obstacles
–Ground slope or changes in elevation that may alter clearance distance
–Other ground or floor conditions
Clearance between the power lines and scaffold should be monitored. If a scaffold is to be moved in the vicinity of overhead power lines, a competent worker should be assigned to observe the clearance and warn others if the minimum distance is not maintained.
Electrically conductive tools or materials should not be used where they may contact overhead power lines. Nonconductive tools or materials should be substituted.
Manufacturers should consider developing scaffolds made of nonconductive materials.
Employers should establish procedures to be followed in emergencies (for example, if a scaffold contacts an electric power line, keep all unauthorized personnel away from the area).
All employers and workers should be trained in cardiopulmonary resuscitation (CPR) [NIOSH 1986c, 1989a, 1989b, 1990a].
Manufacturers or purchasers of scaffolds should affix conspicuous decals to each scaffold section warning about the hazards of contacting overhead power lines.NIOSH urges safety and trade associations, electric utility companies, product manufacturers, and OSHA State consultative services to bring these recommendations to the attention of all employers and workers using scaffolds.
Acknowledgments
Richard W. Braddee, Division of Safety Research, NIOSH, was the principal author of this Alert.
Comments or questions about this document should be directed to Thomas R. Bender, M.D., Director, Division of Safety Research, National Institute for Occupational Safety and Health, 944 Chestnut Ridge Road, Morgantown, West Virginia 26505-2888; telephone (304) 291-4595.
Further information about electrical hazards is available in seven previously published NIOSH Alerts [NIOSH 1984, 1985, 1986b, 1986c, 1987a, 1989a].
[signature]
J. Donald Millar, M.D., D.T.P.H. (Lond.)
Assistant Surgeon General
Director, National Institute for Occupational Safety and Health
Centers for Disease Control
Note
* Code of Federal Regulations. See CFR in references. [Return to main text]
References
29 CFR 1926.21(b)(2). Code of Federal regulations. Washington, DC: U.S. Government Printing Office, Office of the Federal Register.
29 CFR 1926.50. Code of Federal regulations. Washington, DC: U.S. Government Printing Office, Office of the Federal Register.
29 CFR 1926.416(a)(1), (3). Code of Federal regulations. Washington, DC: U.S. Government Printing Office, Office of the Federal Register.
29 CFR 1926.451(d)(6). Code of Federal regulations. Washington, DC: U.S. Government Printing Office, Office of the Federal Register.
51 Fed. Reg. 42706 [1986]. Occupational Safety and Health Administration: safety standards for scaffolds used in the construction industry; proposed rulemaking.
NIOSH [1984]. NIOSH Alert: request for assistance in preventing electrocutions of workers in fast food restaurants. Cincinnati, OH: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, DHHS (NIOSH) Publication No. 85-104.
NIOSH [1985]. NIOSH Alert: request for assistance in preventing electrocutions from contact between cranes and power lines. Cincinnati, OH: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, DHHS (NIOSH) Publication No. 85-111.
NIOSH [1986a]. Four members of a maintenance crew electrocuted in California at a major naval installation. Morgantown, WV: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, Division of Safety Research, Fatal Accident Circumstances and Epidemiology (FACE) Report 87-2-II.
NIOSH [1986b]. NIOSH Alert: request for assistance in preventing electrocutions due to damaged receptacles and connectors. Cincinnati, OH: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, DHHS (NIOSH) Publication No. 87-100.
NIOSH [1986c]. NIOSH Alert: request for assistance in preventing fatalities of workers who contact electrical energy. Cincinnati, OH: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, DHHS (NIOSH) Publication No. 87-103.
NIOSH [1986d]. NIOSH Alert: request for assistance in preventing grain auger electrocutions. Cincinnati, OH: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, DHHS (NIOSH) Publication No. 86-119.
NIOSH [1986e]. Two workers electrocuted in Tennessee. Morgantown, WV: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, Division of Safety Research, Fatal Accident Circumstances and Epidemiology (FACE) Report 86-39-II.
NIOSH [1986f]. 20-Year-old bricklayer electrocuted in Maryland. Morgantown, WV: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, Division of Safety Research, Fatal Accident Circumstances and Epidemiology (FACE) Report 87-19-II.
NIOSH [1986g]. 19-Year-old laborer electrocuted in Kentucky. Morgantown, WV: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, Division of Safety Research, Fatal Accident Circumstances and Epidemiology (FACE) Report 87-15-II.
NIOSH [1987a]. NIOSH Alert: request for assistance in preventing electrocutions by undetected feedback electrical energy present in power lines. Cincinnati, OH: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, DHHS (NIOSH) Publication No. 88-104.
NIOSH [1987b]. Two workers (a carpenter and a laborer) electrocuted in South Carolina. Morgantown, WV: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, Division of Safety Research, Fatal Accident Circumstances and Epidemiology (FACE) Report 87-48-II.
NIOSH [1989a]. NIOSH Alert: request for assistance in preventing electrocutions of workers using portable metal ladders near overhead power lines. Cincinnati, OH: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, DHHS (NIOSH) Publication No. 89-110.
NIOSH [1989b]. NIOSH testimony to the U.S. Department of Labor: statement of the National Institute for Occupational Safety and Health. Presented at the OSHA informal public hearing on the proposed rule for electric power generation, transmission, and distribution; electrical protective equipment, November 28, 1989. NIOSH policy statements. Cincinnati, OH: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health.
NIOSH [1990a]. NIOSH comments to the U.S. Department of Labor: statement of the National Institute for Occupational Safety and Health. Submitted after the hearing on the Occupational Safety and Health Administration’s proposed rule on permit required confined spaces, May 18, 1990. NIOSH policy statements. Cincinnati, OH: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Health.
NIOSH [1990b]. One laborer and two steel workers electrocuted when an elevated work platform contacts 69,000-volt power line in Ohio. Morgantown, WV: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, Division of Safety Research, Fatal Accident Circumstances and Epidemiology (FACE) Report 90-01.
NIOSH [1991]. National Traumatic Occupational Fatality (NTOF) database. Morgantown, WV: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, Division of Safety Research.
91-110sum.pdf (Worker/Employer Summary Sheet Only) [PDF – 207 KB]
							
					
							Last Reviewed:  June 6, 2014						Source: 	National Institute for Occupational Safety and Health
					Facebook
        Twitter
        LinkedIn
        Syndicate homeNIOSH Publications & Products
NIOSH-Issued Publications
Search NIOSHTIC-2 Research Database
Docket
Documents for Public Review
Peer Review Agenda
Databases
eNews
Federal Register Noticesplus icon
FRN Archive 2007-2010
FRN Archive 2005-2006
FRN Archive 2001-2004
FRN Archive 1996-2000
Press Releases and Updatesplus icon
Press Release Archives 2010-2013
Press Release Archives 2006-2009
Press Release Archives 2001-2005
Press Release Archives 1998-2000
Press Release Archives 1992-1997
Regulations
Regulatory Agenda
Science Blog
Software
Video Follow NIOSH Facebook
Pinterest
Twitter
YouTube
 NIOSH Homepage NIOSH A-Z
Workplace Safety & Health Topics
Publications and Products
Programs
Contact NIOSH


About CDC
					Contact Us
					800-232-4636
 Facebook Twitter Instagram LinkedIn Youtube Pinterest Snapchat
 CONTACT CDC
				Contact Us
							Call 800-232-4636
							Email Us
			ABOUT CDC
				About CDC
							Jobs
							Funding
			POLICIES
				Accessibility
							External Links
							Privacy
							Policies
							No Fear Act
							FOIA
							OIG
							Nondiscrimination
							Vulnerability Disclosure Policy
			CONNECT WITH US
				Facebook
								Twitter
								Instagram
								LinkedIn
							Youtube
								Pinterest
								Snapchat
								Email
			LANGUAGES
				Español
							繁體中文
							Tiếng Việt
							한국어
							Tagalog
							Русский
							العربية
							Kreyòl Ayisyen
							Français
							Polski
							Português
							Italiano
							Deutsch
							日本語
							فارسی
							English


U.S. Department of Health & Human Services
			Accessibility
			External Links
			Privacy
			Policies
			No Fear Act
			FOIA
			Nondiscrimination
			OIG
			Vulnerability Disclosure Policy
			USA.gov


Exit Notification / Disclaimer Policy Close
 Links with this icon  indicate that you are leaving the CDC website. The Centers for Disease Control and Prevention (CDC) cannot attest to the accuracy of a non-federal website.
				Linking to a non-federal website does not constitute an endorsement by CDC or any of its employees of the sponsors or the information and products presented on the website.
				You will be subject to the destination website's privacy policy when you follow the link.
				CDC is not responsible for Section 508 compliance (accessibility) on other federal or private website. Website Disclaimers
 Cancel Continue