Document Headings

                    Document headings vary by document type but may contain                    the following:                  
                -                       the agency or agencies that issued and signed a document                    
                -                       the number of the CFR title and the number of each part                      the document amends, proposes to amend, or is directly                      related to                    
                -                       the agency docket number / agency internal file number                    
                -                       the RIN which identifies each regulatory action listed in                      the Unified Agenda of Federal Regulatory and Deregulatory                      Actions                    

                    See the                                          Document Drafting Handbook                                        for more details.                  

###### Nuclear Regulatory Commission

          - [Docket No. 50-395] 

## 1.0 Background 

The South Carolina Electric & Gas Company (SCE&G, the licensee) is the holder of the Renewed Facility Operating License No. NPF-12 which authorizes operation of the Virgil C. Summer Nuclear Station (VSNS). The license provides, among other things, that the facility is subject to all rules, regulations, and orders of the Nuclear Regulatory Commission (NRC or the Commission) now or hereafter in effect. 

The facility consists of a pressurized-water reactor located in Fairfield County in South Carolina. 

## 2.0 Request/Action 

Title 10 of the Code of Federal Regulations (10 CFR), part 50, section 50.44 specifies requirements for the control of hydrogen gas generated after a postulated loss-of-coolant accident (LOCA) for reactors fueled with zirconium cladding. Acceptance criteria contained in 10 CFR 50.46 are for emergency core cooling systems (ECCSs) for reactors fueled with zircaloy or ZIRLOTM                     cladding. In addition, Appendix K to 10 CFR part 50 requires that the Baker-Just equation be used to predict the rates of energy release, hydrogen concentration, and cladding oxidation from the metal-water reaction.                 

                    In summary, the exemption request relates solely to the specific types of cladding material specified in these regulations. As written, the regulations presume the use of zircaloy or ZIRLOTM                     fuel rod cladding. Thus, an exemption from the requirements of 10 CFR 50.44, 10 CFR 50.46, and Appendix K to 10 CFR part 50 is needed to irradiate lead test assemblies (LTAs) consisting of developmental clad alloys at VSNS.                           ( print page 5225)    

## 3.0 Discussion 

### 3.1 Fuel Mechanical Design 

####                     Optimized ZIRLOTM

                    Optimized ZIRLOTM                     has a lower tin content than the licensed ZIRLOTM                    . Tin is a solid solution strengthener and α-phase stabilizer present entirely in the base α-phase zirconium crystalline structure. Potential impacts of a reduced tin content on material properties include (1) a reduced tensile strength, (2) an increased thermal creep rate, (3) an increased irradiation growth rate, (4) a reduced α→α+                    β                     phase transition temperature, and (5) an improved corrosion resistance. The slight reduction in tin content will not effect the size, shape, or distribution of any second phase or inter-metallic precipitates, nor the overall microstructure of this developmental zirconium alloy. With a consistent microstructure, low tin ZIRLOTM                     will exhibit many similar material characteristics as the licensed ZIRLOTM                    . Further, the final annealing of Optimized ZIRLOTM                     has been designed to improve mechanical performance.                 

In the exemption request, SCE&G provides details of the planned post-irradiation examinations (PIEs) of the LTAs. Examinations include rod profilometry, rod growth, rod oxidation, and visual inspection. In response to a request for additional information, the licensee stated that PIE data, as well as data from other Westinghouse LTA programs, will be used to ensure existing design models remain valid. 

As a result of the PIEs, any negative aspects of the low tin alloy's performance, including the potential impacts of a reduced tin content identified above, will be identified and resolved. Furthermore, significant deviations from model predictions will be reconciled. 

                    The fuel rod burnup and fuel duty experienced by the LTAs in VSNS will remain well within the operating experience base and applicable licensed limits for ZIRLOTM                    .                 

Utilizing currently approved fuel performance and fuel mechanical design models and methods, SCE&G and Westinghouse will perform cycle-specific reload evaluations to ensure that the LTAs satisfy existing design criteria. 

                    Based upon LTA irradiation experience of similar low tin versions of ZIRLOTM                    , expected performance due to similar material properties, and an LTA PIE program aimed at qualifying model predictions, the staff finds the LTA mechanical design acceptable for VSNS.                 

### 3.2 Core Physics and Non-LOCA Safety Analysis 

The SCE&G exemption request relates solely to the specific types of cladding material specified in the regulations. No new or altered design limits for purposes of 10 CFR part 50, Appendix A, General Design Criterion 10, “Reactor Design,” need to be applied or are required for this program. 

####                     Optimized ZIRLOTM

                    Due to similar material properties, any impact of low tin ZIRLOTM                     on the safety analysis models and methods is expected to be minimal. Utilizing currently approved core physics, core thermal-hydraulics, and non-LOCA safety analysis models and methods, SCE&G and Westinghouse will perform cycle-specific reload evaluations to ensure that the LTAs satisfy design criteria.                 

Nuclear design evaluations will ensure that LTAs be placed in nonlimiting core locations. As such, additional thermal margin to design limits will be maintained between LTA fuel rods and the hot rod evaluated in safety analyses. Thermal-hydraulic and non-LOCA evaluations will confirm that the LTAs are bounded by the current analysis of record. 

Based upon the use of approved models and methods, expected material performance, and the placement of LTAs in nonlimiting core locations, the staff finds that the irradiation of up to four LTAs in VSNS will not result in unsafe operation nor violation of Specified Acceptable Fuel Design Limits. Furthermore, in the event of a Design Basis Accident, these LTAs will not promote consequences beyond those currently analyzed. 

### 3.3 Regulatory Evaluation 

Pursuant to 10 CFR 50.12, the Commission may, upon application by any interested person or upon its own initiative, grant exemptions from the requirements of 10 CFR part 50 if, (1) the exemptions are authorized by law, will not present an undue risk to public health or safety, and are consistent with the common defense and security; and (2) special circumstances are present. 

#### 3.3.1 10 CFR 50.44

                    The underlying purpose of 10 CFR 50.44 is to ensure that means are provided for the control of hydrogen gas that may be generated following a LOCA. The licensee has provided means for controlling hydrogen gas and has previously considered the potential for hydrogen gas generation stemming from a metal-water reaction. The LTA rods containing a low tin version of ZIRLOTM                     cladding are similar in chemical composition to zircaloy cladding. Metal-water reaction tests performed by Westinghouse on low tin versions of ZIRLOTM                     (documented in Appendix B of Addendum 1 to WCAP-12610-P-A) demonstrate comparable reaction rates. Accordingly, the previous calculations of hydrogen production resulting from a metal-water reaction will not be significantly changed. As such, application of 10 CFR 50.44 is not necessary for the licensee to achieve its underlying purpose in these circumstances.                 

#### 3.3.2 10 CFR 50.46

                    The underlying purpose of 10 CFR 50.46 is to establish acceptance criteria for ECCS performance. The applicability of these ECCS acceptance criteria has been demonstrated by Westinghouse. Ring compression tests performed by Westinghouse on low tin versions of ZIRLOTM                     (documented in Appendix B of Addendum 1 to WCAP-12610-P-A) demonstrate an acceptable retention of post-LOCA ductility up to 10 CFR 50.46 limits of 2200 °F and 17 percent Equivalent Cladding Reacted. Utilizing currently approved LOCA models and methods, Westinghouse will perform cycle-specific reload evaluations prior to use to ensure that the LTAs satisfy 10 CFR 50.46 acceptance criteria. Therefore, the exemption to expand the application of 10 CFR 50.46 to include Optimized ZIRLOTM                     is acceptable.                 

#### 3.3.3 10 CFR Part 50, Appendix K

                    Paragraph I.A.5 of Appendix K to 10 CFR part 50 states that the rates of energy, hydrogen concentration, and cladding oxidation from the metal-water reaction shall be calculated using the Baker-Just equation. Since the Baker-Just equation presumes the use of zircaloy clad fuel, strict application of the rule would not permit use of the equation for the LTA cladding for determining acceptable fuel performance. Metal-water reaction tests performed by Westinghouse on low tin versions of ZIRLOTM                     (documented in Appendix B of Addendum 1 to WCAP-12610-P-A) demonstrate conservative reaction rates relative to the Baker-Just equation. Thus, application of Appendix K, Paragraph I.A.5 is not necessary for the licensee to achieve its underlying purpose in these circumstances.                 

#### 3.3.4 Special Circumstances 

                    In summary, the staff reviewed the licensee's request of proposed exemption to allow up to four LTAs containing fuel rods, guide thimble tubes, and instrumentation tubes                           ( print page 5226)                        fabricated with Optimized ZIRLOTM                    . Based on the staff's evaluation, as set forth above, the staff considers that granting the proposed exemption will not defeat the underlying purpose of 10 CFR 50.44, 10 CFR 50.46, or Appendix K to 10 CFR part 50. Accordingly, special circumstances, are present pursuant to 10 CFR 50.12(a)(2)(ii).                 

#### 3.3.5. Other Standards in 10 CFR 50.12

                    The staff examined the rest of the licensee's rationale to support the exemption request, and concluded that the use of Optimized ZIRLOTM                     would satisfy 10 CFR 50.12(a) as follows:                 

(1) The requested exemption is authorized by law: 

No law precludes the activities covered by this exemption request. The Commission, based on technical reasons set forth in rulemaking records, specified the specific cladding materials identified in 10 CFR 50.44, 10 CFR 50.46, and 10 CFR part 50, Appendix K. Cladding materials are not specified by statute. 

(2) The requested exemption does not present an undue risk to the public health and safety as stated by the licensee: 

                        The LTA safety evaluation will ensure that these acceptance criteria [in the Commission's regulations] are met following the insertion of LTAs containing Optimized ZIRLOTM                         material. Fuel assemblies using Optimized ZIRLOTM                         cladding will be evaluated using NRC-approved analytical methods and plant specific models to address the changes in the cladding material properties. The safety analysis for VSNS is supported by the applicable technical specification. The VSNS reload cores containing Optimized ZIRLOTM                         cladding will continue to be operated in accordance with the operating limits specified in the technical specifications. LTAs utilizing Optimized ZIRLOTM                         cladding will be placed in non-limiting core locations. Thus, the granting of this exemption request will not pose an undue risk to public health and safety.                     

                    The NRC staff has evaluated these considerations as set forth in Section 3.1 of this exemption. For the reasons set forth in that section, the staff concludes that Optimized ZIRLOTM                     may be used as a cladding material for no more than four LTAs to be placed in nonlimiting core locations during VSNS's next refueling outage, and that an exemption from the requirements of 10 CFR 50.44, 10 CFR 50.46, and 10 CFR part 50, Appendix K does not pose an undue risk to the public health and safety.                 

## 4.0 Conclusion 

                    Accordingly, the Commission has determined that, pursuant to 10 CFR 50.12(a), the exemption is authorized by law, will not present an undue risk to the public health and safety, and is consistent with the common defense and security. Also, special circumstances are present. Therefore, the Commission hereby grants SCE&G exemptions from the requirements of 10 CFR 50.44, 10 CFR 50.46, and 10 CFR part 50, Appendix K, to allow four LTAs containing fuel rods with Optimized ZIRLOTM                     and several different developmental clad alloys.                 

Pursuant to 10 CFR 51.32, the Commission has determined that the granting of this exemption will not have a significant effect on the quality of the human environment (70 FR 1742). 

This exemption is effective upon issuance. 

Dated in Rockville, Maryland, this 14th day of January 2005. 

For the Nuclear Regulatory Commission. 

James E. Lyons, 

Deputy Director, Division of Licensing Project Management, Office of Nuclear Reactor Regulation. 

[FR Doc. 05-1772 Filed 1-31-05; 8:45 am] 

BILLING CODE 7590-01-P