exv4wau





Exhibit (au)









	 	 	 	 	 
	DATE:

	 	25th June, 2009	 	 
	 
	COMPANY:

	 	Plummers Industries Pty Ltd	 	 
	 
	ATTENTION:

	 	 	 	FAX NO: +61 24320 4777
	 
	FROM

	 	 	 	FAX NO: +675 986 5744
	 
	SUBJECT:	 	LGL Million Ounce Plant Upgrade (MOPU) Project
	 	 	MOPU-1101 Low Voltage MCC’s and Switchrooms







	 	 	 	 	 
	Total number of pages herewith - 9 - including this page.






Disclaimer: The contents of the facsimile and any attachments are private and confidential. If
you are not an authorised recipient, copying, distributing, reading or acting on this information
is strictly prohibited, and may render you liable to prosecution.




LETTER OF AWARD



LGL is pleased to hereby advise that your Company’s Tender for supply of Low Voltage MCC’s and
Switchrooms (Tender Package MOPU-1101) has been accepted subject to the provisions set out in this
Letter Of Award.





	1.	 	CONTRACT DOCUMENT
	 
	 	 	The Contract shall be entered into by Plummers Industries Pty Ltd ACN 008 907 784 (“PI”) and
Lihir Gold Limited ARBN 069 803 998 (“LGL”), and the agreement between the Parties is
evidenced by this Letter of Award.
	 
	 	 	The documents forming the Agreement shall be:






	 	a)	 	Terms & Conditions described within LGL Tender Documentation:






	 	§	 	MOPU-1101 Tender Invitation Letter Dated 11/11/08
	 
	 	§	 	Tender Package MOPU-1101 — Sections I, II, III & IV (including data sheets)






	 	b)	 	Plummers Industries Pty Ltd Tender submission documentation including:






	 	(i)	 	Section IV, Quotation dated 24/2/09 and revised on 23/4/09, 26/5/09 and 27/5/09
	 
	 	(ii)	 	Completed Data Sheets received 9/1/09, 12/1/09, 19/1/09, 30/1/09 and 24/2/09
	 
	 	(iii)	 	Response to Technical Enquiry MOPU-1101-# 1 received 9/1/09
	 
	 	(iv)	 	Response to Technical Enquiry MOPU-1101-# 2 received 30/1/09
	 
	 	(v)	 	Response to Technical Enquiry MOPU-1101-# 4 received 2/3/09






	 	c)	 	Post Tender correspondence between LGL and Plummers Industries Pty Ltd (refer Attachment
“A”)
	 
	 	d)	 	Post tender re-negotiated commercial conditions herein referred to as “Special
Conditions of Contract” (refer Attachment “B”).




For expediting and shipping purposes, a Purchase Order will be prepared and issued for the items
detailed in Item 3 (Pricing Schedule).





	2.	 	LGL REPRESENTATIVE





	 	 	 	 	 
	 

	 	 	 	Lihir Island, New Ireland Province
	Lihir Gold Limited

	 	Phone: +675 986 4014
	 	Papua New Guinea
	Incorporated in Papua New Guinea

	 	Fax: +675 986 4018
	 	PO Box 789 Port Moresby NCD 121
	ARBN 069 803 998

	 	Website: www.LGLGold.com
	 	Papua New Guinea











 









 











Page 2





	 	 	Your Company is hereby advised that LGL’s Representative’s is:




Name:

Telephone:

E-Mail:





	 	 	All communications should be addressed in the first instance to LGL’s Company Representative.
	 
	 	 	All correspondence is to be transmitted by e-mail and numbered sequentially using the
following protocol;






	 	i)	 	The e-mail Subject line shall include MOPU-1101 -C-XXX, followed by the subject
title, where XXX is your Company’s sequential correspondence counter. Similarly, LGL
correspondence will be labelled with MOPU-1101-L-XXX.
	 
	 	ii)	 	The Cc field of all e-mail correspondence shall include mopu@lqlgold.com.






	3.	 	PRICING SCHEDULE





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	Total
	 	 	 	 	 	 	 	 	 	 	Unit Amount	 	Amount
	Item	 	Description	 	Qty	 	AUD	 	AUD
	 	1	 	 	Motor Control Cubicles
	 	LOT	 	 	 	 	 	 	 	 
	 	2	 	 	Switchrooms
	 	LOT	 	 	 	 	 	 	 	 
	 	3	 	 	Distribution Boards
	 	LOT	 	 	 	 	 	 	 	 
	 	4	 	 	Uninterruptible Power Supplies
	 	LOT	 	 	 	 	 	 	 	 
	 	5	 	 	Control Panel (Installation only)
	 	LOT	 	 	 	 	 	 	 	 
	 	6	 	 	Battery Charger Systems
	 	LOT	 	 	 	 	 	 	 	 
	 	7	 	 	High Voltage Switchboards (Installation only)
	 	LOT	 	 	 	 	 	 	 	 
	 	8	 	 	High Voltage Remote Switching Panels (Installation only)
	 	LOT	 	 	 	 	 	 	 	 
	 	9	 	 	Variable Speed Drives (Installation only)
	 	LOT	 	 	 	 	 	 	 	 
	 	10	 	 	Local Control Stations
	 	LOT	 	 	 	 	 	 	 	 
	 	 	 	 	Options
	 	 	 	 	 	 	 	 	 	 	 	 
	 	11	 	 	Lifting Spreader Bars
	 	 	2	 	 	 	 	 	 	 	 	 
	 	12	 	 	Rubber Matting
	 	LOT	 	 	 	 	 	 	 	 
	 	13	 	 	Drawings and Documentation
	 	LOT	 	 	 	 	 	 	 	 
	 	14	 	 	Packaging
	 	LOT	 	 	 	 	 	 	 	 
	 	 	 	 	Total Cost AUD Excluding GST
	 	 	 	 	 	 	 	 	 	 	 	 







	 	 	The above pricing is based upon delivery Ex Works Brisbane Incoterms 2000.






	4.	 	SUPPLY SCHEDULE





	 	 	 
	 	 	Duration
	Activity	 	(After Award)
	Preliminary Engineering Drawings for Approval

	 	6 weeks
	Final Certified Engineering Drawings

	 	2 weeks from approval
	Final Certified Drawings

	 	At Completion
	Total Delivery Ex Works Brisbane

	 	36 weeks











 









 











Page 3.





	5.	 	CLAIMS FOR PAYMENT
	 
	 	 	Claims for payment shall be made in accordance with the following milestones:-






	 	•	 	upon Submission of Issue For Approval drawings
	 
	 	•	 	upon Purchase of Components.
	 
	 	•	 	Upon Manufacture of Sheet Metal
	 
	 	•	 	Upon Completion of Factory Acceptance Testing
	 
	 	•	 	Upon delivery ex works






	 	 	Invoices for payment shall be made to:-






	 	 	Lihir Gold Limited

ARBN 069 803 998

Lihir Island New Ireland Province

PO Box 789

Port Moresby NCD 121

Papua New Guinea






	 	 	Invoices shall include reference to Tender No. MOPU-1101 and be forwarded to the LGL
Representative nominated in this Letter of Award.
	 
	6.	 	TAGGING & PACKAGING TAGGING REQUIREMENTS
	 
	 	 	Tagging and Packaging of the Merchandise shall be in accordance with Section I — Part B
Purchase order Terms and Conditions — “C. Preparing Orders For Shipment”.
	 
	7.	 	INSURANCES
	 
	 	 	Pursuant to Clause 15 Section 1 Part B (Purchase Order Terms and Conditions) you will be
required to lodge evidence of insurances effected by you for the purposes of the contract
within 14 days of the this letter of award issue.
	 
	8.	 	SECURITY
	 
	 	 	Pursuant to Clause 5 Section 1 Part B (Purchase Order Terms and Conditions) you will be
required to lodge, as Security, an unconditional Bank Guarantee (in format as per Attachment
“C” — “Approved Form of Bank Guarantee”) to the sum of of the contract Value within 28 Days
of this Letter of Award issue date.
	 
	9.	 	RETENTION
	 
	 	 	Pursuant to Clause 5 Section 1 Part B (Purchase Order Terms and Conditions), LGL will withhold
of each invoice until such time as the earlier of merchandise is inspected on site or until
completion of equipment commissioning, for a period not to exceed 180 days from the delivery
completion date at the nominated delivery place or shipping point.
	 
	10.	 	CONTRACT NUMBER
	 
	 	 	The Contract No MOPU-1101 and Purchase Order No (TBA) must be referenced in all
correspondence and invoices.
	 
	11.	 	ACKNOWLEDGMENT & ACCEPTANCE
	 
	 	 	Please acknowledge receipt and acceptance of this Letter of Award by having a duly authorised
representative of your Company sign the acknowledgment below and return promptly by facsimile
(or a scan by e-mail) to LGL’s Representative.





Yours faithfully




MOPU Project Manager

Lihir Gold Limited





 









 








Page 4.



ACKNOWLEDGEMENT BY VENDOR 



Acknowledgement and acceptance of Letter Of Award by successful Vendor:




	 	 	 	 	 
	Contract No:

	 	MOPU-1101 — Supply of MCC’s and Switchrooms
 

	 	 
	 
	 	 	 	 
	Vendor:

	 	Plummers Industries Pty Ltd.
 

	 	 
	 
	 	 	 	 
	Name:
	 	 	 	 
	 

	 	 

	 	 
	Position:
	 	 	 	 
	 

	 	 

	 	 
	Signature:
	 	 	 	 
	 

	 	 

	 	 
	Date:
	 	 	 	 
	 

	 	 

	 	 











 









 
















Date: 11th November 2008




Plummer Industries

75 Wolston Road

Sumner Park QLD 4075




Attn:

Phone:

Fax:

E-mail:





			
	Re:	 	Million Ounce Plant Upgrade Project (MOPU)

Tender Package MOPU-1101

Low Voltage MCC’s and Switchrooms





Dear Sir:



Your company is invited to submit a Tender for the Low Voltage MCC’s and Switchrooms as specified
in the accompanying documents for the MOPU Project, Lihir Island, PNG.




1.0 Tender Documents



The documents forming this Tender Package are as follows:




Section I — Instructions to Tenderers (made up of Parts A, B, and C)

Section II — Site Conditions and Equipment and Material Standards

Section III — Detailed Specifications

Section IV — Form of Tender




2.0 Submission of Tenders



The following items shall be submitted by the Tenderer as part of its submission to Lihir Gold
Limited (“LGL”):



2.1 Acknowledgement of Receipt of Tender



The recipient is asked to confirm that this document has been received and to state whether it
intends to bid on the equipment supply within 48 hours of receipt.



2.2 Form of Quotation



The Tenderer shall complete all details on the Form of Tender as per Section I, Section II, Section
III and Section IV.




	 	 	 	 	 
	 

	 	 	 	Lihir Island, New Ireland Province
	Lihir Gold Limited

	 	Phone: +675 986 4014
	 	Papua New Guinea
	Incorporated in Papua New Guinea

	 	Fax: +675 986 4018
	 	PO Box 789 Port Moresby NCD 121
	ARBN 069 803 998

	 	Website: www.LGLGold.com
	 	Papua New Guinea











 









 











Page 2



2.3 Departures from Specification and Tender Documents



The Tenderer shall submit a tender price strictly in accordance with the Tender Documents, however,
should the Tenderer, in addition to its conforming tender, wish to submit alternative offers based
on departures from the Specifications or Tender Documents, it shall list the departures and the
associated variation to the conforming tender price for each departure.



2.4 Lodgement of Tenders



Two (2) hard copies of the Tender shall be submitted, enclosed in a sealed envelope and marked with
the name of the equipment being Tendered for and the specification number as shown in the
Invitation to Tender and shall be sent by prepaid post or courier and delivered to the following
address:




MOPU PROJECT

LGL

Level 9

500 Queen Street

Brisbane QLD 4001

Australia

Attention: Project Purchasing Manager



Facsimile or electronic copies of the entire Tender (including all parts, sections and annexures)
will be accepted by LGL provided that the Tenderer indicates on the transmission when the hard copy
of the Tender will arrive at LGL’s office, which must be no later than 2 days for Australia- based
tenderers and 5 days for overseas tenderers.



The tender envelope (or fax cover sheet) shall clearly identify:





	A)	 	Tender Closing Date;
	 
	B)	 	Description of Work; and
	 
	C)	 	Work Package being tendered for.





3. Closure of Tenders



Tenders will close at 3:00 PM Brisbane time, 2nd December 2008. No late tenders will be
accepted. Late tenders will be returned unopened to the Tenderer on receipt. LGL reserves the right
to accept or reject any Tender received after the Closing Time




4. Special Instructions to Tenderers



The Tenderer shall take special note of the following requirements stipulated in the Terms of
Payment in Section I “Instructions to Tenderers”:



4.1 Retention



LGL will withhold a percentage of each invoice (totalling of the total Purchase Order value) until
materials have been received and inspected on site, or, in the case of equipment, until successful
completion of equipment commissioning, for a period not to exceed 180 days from the date of
delivery at the nominated delivery place or shipping point.









 









 











Page 3



4.2 Bank Guarantee



An unconditional bank guarantee for of the total Purchase Order value shall be lodged by the Seller
with LGL within 30 days of Award. This bank guarantee shall be held by LGL for the full duration of
the defects liability period, which shall be 12 months from the successful commissioning of the
equipment.



Tenderers shall submit Tenders that fully comply with these requirements as their base Tender.
Should a Tenderer wish to offer an alternative Tender, this will be in addition to the base Tender.




5.0 Tender Enquiries



All enquires regarding this Request for Tender shall only be accepted in writing and directed to:




	 	 	 
	Attention:

	 	Roland Dober
	Fax:

	 	07-3318-9203
	E-Mail:

	 	mopu@lglgold.com and roland.dober@lglgold.com.au





We look forward to receiving your Tender submission.




Yours truly,




Lihir Gold Limited









 









 











Page 4





	ACKNOWLEDGEMENT OF INVITATION TO TENDER




Receipt of Invitation to Tender Reference MOPU-1101 hereby acknowledged.





	o	 	We intend to submit our Tender on or before the Closing Time and accept that
the supply of information will be communicated by way of e-mail or webpage.
	 
	o	 	We do not intend to submit a Tender and acknowledge that we will not receive
any further communication respecting this Tender opportunity.





	 	 	 	 	 	 	 
	 

	 	Name:	 	 	 	 
	 

	 	 	 	 

	 	 
	 

	 	Company:	 	 	 	 
	 

	 	 	 	 

	 	 
	 

	 	Tel:	 	 	 	 
	 

	 	 	 	 

	 	 
	 

	 	Fax:	 	 	 	 
	 

	 	 	 	 

	 	 
	 

	 	E-mail:	 	 	 	 
	 

	 	 	 	 

	 	 











 









 











Page 5.




ATTACHMENT “A”



POST TENDER CORRESPONDENCE



	 	 	 	 	 
	From	 	Subject	 	Sent
	To Vendor

	 

	 	MOPU-1101-L Invitation to Tender — Low Voltage MCC’s and Switchrooms
	 	Tue 11/11/2008 4:37 PM
	 

	 	MOPU-1101-L Low Voltage MCC’s and Switchrooms — Notice to tenderer’s
#1 (Plummers)
	 	Wed 19/11/2008 3:52 PM
	 

	 	MOPU-1101-L Low Voltage MCC’s and Switchrooms — Notice To Tenderers #2
	 	Thu 20/11/2008 12:16 PM
	 

	 	MOPU-1101-L Low Voltage MCC’s and Switchrooms — Notice To Tenderers #3
	 	Tue 25/11/2008 1:55 PM
	 

	 	MOPU-1101-L Low Voltage MCC’s and Switchrooms — Notice To Tenderers #4
	 	Tue 25/11/2008 2:03 PM
	 

	 	MOPU-1101-L Low Voltage MCC’s and Switchrooms — Notice To Tenderers #5
	 	Tue 25/11/2008 2:19 PM
	 

	 	MOPU-1101-L Low Voltage MCC’s and Switchrooms — Notice To Tenderers #6
	 	Thu 27/11/2008 7:39 AM
	 

	 	MOPU-1101-L Low Voltage MCC’s and Switchrooms — Notice to tenderer’s #7
	 	Thu 27/11/2008 9:37 AM
	 

	 	MOPU-1101-L Post Tender Technical Query
	 	Thu 22/01/2009 9:32 AM
	 

	 	MOPU-1101-L Notice To Tenderers
	 	Thu 29/01/2009 7:59 AM
	 

	 	MOPU-1101-L Revised Pricing
	 	Mon 2/02/2009 10:56 AM
	 

	 	MOPU-1101-I Minutes of MOPU-1101 Tender Meeting
	 	Thu 5/02/2009 8:26 AM
	 

	 	FW: MOPU-1101-I Deflection limits
	 	Thu 5/02/2009 10:02 AM
	 

	 	MOPU-1101-L LV MCCs and Switchroom — Post Tender Technical Query
	 	Fri 27/02/2009 1:27 PM
	 

	 	MOPU-1101-L MCCs and Switchrooms — Post Tender Technical Query #3
	 	Fri 17/04/2009 9:33 AM
	 

	 	MOPU-1101-L-MCC’s and Switchroom Section IV
	 	Mon 25/05/2009 3:39 PM
	 
	 	 	 	 
	From Vendor

	 

	 	RE: MOPU-1101-L Invitation to Tender- Low Voltage MCC’s and Switchrooms
	 	Wed 12/11/2008 10:43 AM
	 

	 	RE: MOPU-1101-L Invitation to Tender — Low Voltage MCC’s and Switchrooms
	 	Thu 13/11/2008 12:25 PM
	 

	 	RE: MOPU-1101-L Post Tender Query #1
	 	Fri 9/1/2009 8:00 AM
	 

	 	RE: MOPU-1101-L Post Tender Query #1
	 	Mon 12/01/2009 12:56 PM
	 

	 	RE: MOPU-1101-L Post Tender Query #1
	 	Mon 19/01/2009 12:12 PM
	 

	 	RE: MOPU-1101-L Post Tender Query #1
	 	Mon 19/01/2009 4:44 PM
	 

	 	RE: MOPU-1101-L Notice To Tenderers
	 	Thu 29/01/2009 3:07 PM
	 

	 	RE: MOPU-1101-L Post Tender Technical Query
	 	Fri 30/01/2009 8:30 AM
	 

	 	RE: MOPU-1101-L Revised Pricing
	 	Mon 2/02/2009 11:02 AM
	 

	 	RE: MOPU-1101-I Minutes of MOPU-1101 Tender Meeting
	 	Thu 5/02/2009 1:31 PM
	 

	 	RE: MOPU-1101-l Minutes of MOPU-1101 Tender Meeting
	 	Thu 5/02/2009 1:36 PM
	 

	 	RE: MOPU-1101-L Revised Pricing
	 	Tue 24/02/2009 2:53 PM
	 

	 	RE: MOPU-1101-L LV MCCs and Switchroom — Post Tender Technical Query
	 	Mon 2/03/2009 2:47 PM
	 

	 	FW: MOPU-1101-L LV MCCs and Switchroom — Post Tender Technical Query
	 	Mon 2/03/2009 2:52 PM






 









 






Page 6.




	 	 	 	 	 
	From	 	Subject	 	Sent
	 

	 	FW: MOPU-1101-I MCCs and Switchrooms — Post Tender Technical Query #3
	 	Thu 23/04/2009 3:13 PM
	 

	 	RE: MOPU-1101-L-MCC and Switchrooms
	 	Mon 25/05/2009 1:27 PM
	 

	 	RE: MOPU-1101-L-MCC’s and Switchroom Section IV
	 	Mon 25/05/2009 3:45 PM
	 

	 	RE: MOPU-1101-L-MCC’s and Switchroom Section IV
	 	Tue 26/05/2009 9:57 AM
	 

	 	RE: MOPU-1101-L-MCC and Switchrooms
	 	Wed 27/05/2009 9:17 AM
	 

	 	Lihir Revised cover letter
	 	Thu 25/06/2009 10:49 AM







 









 








Page 7.




ATTACHMENT “B”



SPECIAL CONDITIONS OF CONTRACT



MOPU-1101 Supply of MCC’s and Switchrooms


Amendments to Section 1 Part B “Purchase Order terms and Conditions” 





			
	SC1	 	Clause 5 Security and Retention (page 14)


Clause 5 first sentence delete 14 days and replace with “28 days”






			
	SC2	 	Clause 15.3 Professional Indemnity (page 20)


Delete Clause 5 in its entirety.






 









 








Page 8.




ATTACHMENT “C”



APPROVED FORM OF BANK GUARANTEE

(To be typed on Bank Letterhead)




			
	TO:	 	Lihir Gold Limited (incorporated in PNG), ARBN 069 803 998





Dear Sirs,



At the request of {insert company name} (ABN: {insert company ABN} ) of {Insert company address}
(hereinafter called “the Supplier”) and in consideration of you accepting this Guarantee in
relation to the Contract (defined below), {Insert bank name} (“ {insert bank name abbreviation}”)
unconditionally undertakes to pay on demand any sum or sums which may from time to time be demanded
in accordance with this Guarantee by you to a maximum aggregate sum of USD (#####) (the “Guaranteed
Amount”).



This Guarantee is to continue until the first to occur of:





	 	1.	 	4pm (local time in the place of the Office) on the ####### (the “Expiry Date”);
	 
	 	2.	 	your delivery of a notice to {Insert abbreviated bank name} that the Guarantee is no longer
required;
	 
	 	3.	 	the date this Guarantee is returned to {insert abbreviated bank name} at its office
at ######## (the “Office”);
	 
	 	 	 	or
	 
	 	4.	 	the date of payment to you by {insert abbreviated bank name} of the whole of the Guaranteed
amount (or such lesser sum as you may require).




If you wish to make a demand or issue any notice under this Guarantee then the notice or demand you
deliver to {insert abbreviated bank name} must:





	 	a)	 	be in writing;
	 
	 	b)	 	be or purport to be signed by you or for you and on your behalf;
	 
	 	c)	 	state that the notice or demand is made pursuant to this Guarantee; and
	 
	 	d)	 	if a demand, state the amount required to be paid under this Guarantee.




You may make multiple demands under this Guarantee, and upon payment by {insert abbreviated bank
name}, the Guaranteed Amount will automatically reduce by the amount paid.



If a demand is made in accordance with the above provisions, {insert abbreviated bank name} will
make such payment or payments to you or at your direction and notwithstanding any notice given by
the Supplier to {insert abbreviated bank name} not to make the payment.



Despite anything else in this Guarantee, {insert abbreviated bank name} may terminate it at any
time by paying you the Guaranteed Amount at that time or any lesser amount you agree.









 









 











Page 9.



Payments under this Guarantee by {insert abbreviated bank name} may be by:





	 	a)	 	Bank cheque;
	 
	 	b)	 	by telegraphic transfer to any account you nominate in writing for this purpose; or
	 
	 	c)	 	by such other method which {insert abbreviated bank name} agrees with you.




You cannot assign or transfer your rights under this Guarantee.



This Guarantee is governed by the law of Queensland.



This undertaking is effective from ######## and expires ####### at 4pm on ########.



Definitions



Contract means in respect of ####### for your Job #



You means the person or other entity described as the beneficiary in this Guarantee, and where
there is more than one, it includes any one or more of you.



Your has the corresponding meaning. It also includes your executor, administrator and your successor.



Dated at ##### this ### day of ###### 2008.




Yours faithfully,



Dated at:       
                  
                 this  
                 
   day of              
       2___



Signed by:      
                
                 
                
               
           )




(Bank Stamp)



In the presence of:
                                        
                    )





 









 








Page 4.



ACKNOWLEDGEMENT BY VENDOR



Acknowledgement and acceptance Letter Of Award by successful Vendor:




	 	 	 	 	 
	Contract No:

	 	MOPU-1101 — Supply of MCC’s and Switchrooms
 

	 	 
	 
	 	 	 	 
	Vendor:

	 	Plummers Industries Pty Ltd.
 

	 	 
	 
	 	 	 	 
	Name:
	 	 	 	 
	 

	 	 

	 	 
	Position:
	 	 	 	 
	 

	 	 

	 	 
	Signature:
	 	 	 	 
	 

	 	 

	 	 
	Date:
	 	 	 	 
	 

	 	 

	 	 







 









 













MILLION OUNCE PLANT UPGRADE PROJECT



LV MCCS AND SWITCHROOMS



MOPU-1101



SECTION I — INSTRUCTIONS TO TENDERERS



	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Approved	 	 
	Revision	 	Date	 	Author	 	By	 	Comments
	00
	 	22-5-08
	 	AB
	 	AB
	 	Original Issue






			
	 	 	 
	Section I — Part A Instructions to Tenderers
	 	1







 









 








LGL




Million Ounce Plant Upgrade (MOPU)



Equipment Supply Tender

section i Part A instructions to tenderers



index



	 	 	 	 	 	 	 
	1.

	 	Tenderers’ Understanding 
	 	 	1	 
	2.

	 	Tender Submissions 
	 	 	2	 
	3.

	 	Acceptance of Tender 
	 	 	3	 
	4.

	 	Tendered Prices 
	 	 	4	 
	5.

	 	Contract and Terms of Payment 
	 	 	5	 
	6.

	 	Weights and Dimensions 
	 	 	5	 
	7.

	 	Contractual Delivery Schedule 
	 	 	5	 
	8.

	 	Warranties/Guarantees 
	 	 	6	 
	9.

	 	Alternative Proposals 
	 	 	6	 
	10.

	 	Priority 
	 	 	6	 
	11.

	 	Quality Assurance/Quality Control 
	 	 	7	 
	12.

	 	Tests 
	 	 	7	 
	13.

	 	Erection or Start-Up 
	 	 	7	 
	14.

	 	Spare Parts 
	 	 	7	 
	15.

	 	Health, Safety, Environmental and Human Rights Compliance 
	 	 	7	 






			
	 	 	 
	Section I — Part A Instructions to Tenderers
	 	2











 









 











LGL EQUIPMENT SUPPLY TENDER




Section I Part A

Instructions to Tenderers





	1.	 	Tenderer’s Understanding






	 	1.1.	 	It is understood and agreed that the Tenderer shall read these instructions and
submit its Tender in conformity with the following documents:






	 	 	 	SECTION I: Instructions to Tenderer’s (Inclusive of Appendixes)

SECTION II: Site Conditions and Equipment and Material Standards)

SECTION III: Detailed Specifications)

SECTION IV: Form of Tender






	 	1.2.	 	The following definitions apply to terms used throughout Sections I, II, III and IV.





	 	 	 
	Term	 	Meaning
	LGL

	 	Lihir Gold Limited (Incorporated in Papua New Guinea) ARBN 069 803 998 with
an operation on Lihir Island, New Ireland Province, Papua New Guinea
	 
	 	 
	Closing Time

	 	The deadline for receipt by LGL of Tender submissions
	 
	 	 
	Equipment, 

Merchandise or Goods

	 	The equipment or goods described in Section III that is the subject of
the Invitation to Tender
	 
	 	 
	Invitation to Tender

	 	A letter of invitation from LGL to inviting offers to supply Merchandise
	 
	 	 
	Owner

	 	LGL
	 
	 	 
	Project

	 	LGL’s Million Ounce Plant Upgrade (MOPU)
	 
	 	 
	Purchase Order

	 	A formal document issued to a supplier for the supply of specific
Merchandise in accordance with standard terms and conditions as stated
in the document. A Purchase Order is a contract between LGL and the
Seller.
	 
	 	 
	Seller /Supplier

	 	(may also be referred to as the Manufacturer, Vendor, or Supplier) is
the Company whose Tender has been accepted by LGL, and to whom a
Purchase Order for the Merchandise described herein is awarded.
	 
	 	 
	Site

	 	LGL Operation on Lihir Island, New Ireland Province, Papua New Guinea
	 
	 	 
	Sub-Contractor or Sub-Supplier

	 	A contractor that has been engaged by the Seller to perform part of the
supply of the equipment or goods which are to be supplied by the Seller
in accordance with the Purchase Order.
	 
	 	 
	Tender or Proposal

	 	An offer to perform work or to supply Merchandise.
	 
	 	 
	Tenderer

	 	The company named on the Invitation to Tender







	 	1.3.	 	The Tender documents are the property of LGL and are delivered only for the purpose
of enabling each potential Tenderer to prepare and submit a Tender in response. All
information provided to the Tenderer during the tender process, including information
contained or referred to in the Tender Documents, is confidential and must not be
disclosed or released for any use or purpose.
	 
	 	1.4.	 	Unsuccessful Tenderers are required to return the Tender documents to LGL on receipt
of notice of award of tender to the successful Tenderer.





			
	 	 	 
	Section I — Part A Instructions to Tenderers
	 	1











 









 











LGL EQUIPMENT SUPPLY TENDER





	2.	 	Tender Submissions






	 	2.1.	 	Two (2) hard copies of the Tender for the supply of equipment, materials, and service
as detailed on the attached specification sheets must be submitted, enclosed in a sealed
envelope and marked with the name of the equipment being tendered for and the specification
number as shown in the Invitation to Tender and shall be sent by prepaid post or courier
and delivered to the following address:






	 	 	 	MILLION OUNCE PLANT UPGRADE

LGL Gold

Level 9

500 Queen Street

Brisbane QLD 4001

Australia

Attention: Projects Purchasing






	 	 	 	by the date and time for closing of Tenders nominated in the Invitation to Tender. In
the event that there is a request for the tender to be submitted electronically, this
request shall be extra to the hard copy requirements.
	 
	 	2.2.	 	Verbal Tenders and/or quotes will not be accepted.
	 
	 	2.3.	 	A Tender shall contain two (2) complete sets of manufacturer’s specifications on the
design and materials of construction and general arrangement drawings.
	 
	 	2.4.	 	The heading on a Tender shall show the name of the equipment and the tender number as
shown on the Invitation to Tender.
	 
	 	2.5.	 	In accordance with the tender documents, complete Tenders are required to be submitted.
Tenderers who feel it will be advantageous to tender on only some items of Merchandise
should obtain prior written consent from the Project Purchasing Manager.
	 
	 	2.6.	 	Tenderers requiring clarification of technical aspects of the Tender document shall
submit their questions in writing to the Project Purchasing Manager as early as possible
during the Tender period. LGL will issue clarifications or addenda (if required) to all
Tenderers.
	 
	 	2.7.	 	All equipment and materials must conform with the laws and regulations of the
Independent State of Papua New Guinea.
	 
	 	2.8.	 	Tenderers shall strictly adhere to the Closing Time, which will be as shown on the
Invitation to Tender. An extension of Tender time requires prior written approval and will
be at the sole discretion of LGL.
	 
	 	2.9.	 	Tender submissions shall be construed as an irrevocable, firm and fixed offer that is
open for acceptance for a period of sixty (60) days following the Closing Time.
	 
	 	2.10.	 	On receipt of a request in writing, and at the discretion of LGL, a Tender may be
withdrawn or revised, provided the withdrawal or revision is received on or before the
Closing Time.
	 
	 	2.11.	 	The Tenderer must submit a completed Form of Tender as outlined in Section IV.
Alterations, qualifications or omissions to the Form of Tender by the Tenderer may be
considered cause to reject a Tender.
	 
	 	2.12.	 	If any special tools are required for installation, operation, and maintenance, the
Tenderer shall provide a list of the type and quantity together with pricing of these tools
as separate





			
	 	 	 
	Section I — Part A Instructions to Tenderers
	 	2











 









 











LGL EQUIPMENT SUPPLY TENDER





	 	 	 	items delivered FCA or FOB (Incoterms 2000) in accordance with clause 4.
	 
	 	2.13.	 	A Tenderer who submits a Tender in strict accordance with the Tender documents may
also submit an alternative proposal as set out in clause 11.
	 
	 	2.14.	 	The Tenderer’s submission shall be construed as representation and warranty that it
has complied with and agrees to be bound by the terms and conditions of the tender
package.
	 
	 	2.15.	 	If the Tenderer is dependent on one or more Sub-Sellers or Sub-Contractors, the
Tenderer must identify those Sub-Sellers or Sub-Contractors in the proposal.
	 
	 	2.16.	 	LGL may require the Tenderer to provide evidence of its ability to carry out the
requirements within the required timeline, and the financial ability to complete the
requirements of the Contract.
	 
	 	2.17.	 	LGL reserves the right to seek further information or clarification to any Tender
submitted after the Closing Time, and the right to negotiate with any Tenderer after
Closing Time.
	 
	 	2.18.	 	LGL is not liable for any of the Tenderer’s costs incurred in responding to the
Invitation to Tender.






	3.	 	Acceptance of Tender






	 	3.1.	 	The acceptance of any Tender shall be based on an evaluation of Tenderers’ proposals
by LGL, through consideration of evaluation criteria determined solely at the discretion
of LGL. LGL is not obliged to inform Tenderers of any particular evaluation criteria or
the relative weight to be given to any particular evaluation criteria.
	 
	 	3.2.	 	LGL reserves the right to award a Contract in respect of all or only a portion of the
Equipment referred to in this RFQ or to award multiple Contracts to different Tenderers.
	 
	 	3.3.	 	LGL reserves the right to reject any or all Tenders received in response to this
Invitation to Tender without giving any notice or reasons. LGL also reserves the right to
accept any Tender, notwithstanding informalities or irregularities or other failures to
comply with the terms and conditions of this Invitation to Tender, contained in such
Tender.
	 
	 	3.4.	 	The Tender containing the lowest price or any Tender will not necessarily be
accepted. LGL reserves the right, without restriction, to exercise its sole discretion in
determining the best value and whether or not any Tender received provides the necessary
level of value to LGL to result in the acceptance of a tender.
	 
	 	3.5.	 	LGL reserves the right after the closing time, in its sole discretion, to seek
further information from or clarification of any Tender submitted by any Tenderer, and to
negotiate with any Tenderer, or with more than one Tenderer concurrently, the terms and
conditions of Tenders. LGL is not required to offer any modified terms and conditions to
any other Tenderer and LGL incurs no liability to any Tenderer in exercising its
discretion under this clause.
	 
	 	3.6.	 	LGL may, prior to accepting a Tender, require further evidence that a Tenderer has:






	 	(a)	 	the necessary experience and is prepared to use the necessary
personnel and equipment to fulfil the requirements of the Tender Documents
satisfactorily and within the required time; and





			
	 	 	 
	Section I — Part A Instructions to Tenderers
	 	3











 









 











LGL EQUIPMENT SUPPLY TENDER





	 	(b)	 	the financial ability to complete the requirements of the Tender
Documents.






	 	3.7.	 	By submitting a Tender, the Tenderer gives LGL permission to contact any organisation
for whom the Tenderer has supplied equipment, materials and/or services in order to obtain
information pertaining to timely completion, quality, methods and other matters relating to
work performed or being performed by the Tenderer.
	 
	 	3.8.	 	The submission of a Tender is representation and warranty by the Tenderer that it has
complied with and agrees to be bound by the terms and conditions of the Tender Documents.
No adjustment to any price or prices contained in the Tender nor any other compensation
will be allowed on account of any failure by the Tenderer to comply with the Tender
Documents.
	 
	 	3.9.	 	No Tender will be deemed accepted by LGL until a written notice of acceptance has been
issued to the successful Tenderer. Following notice of award, the successful Tenderer is
required to execute a formal Purchase Order in the form set out in the Tender Documents
(including the documents listed therein i.e. Purchase Order terms and conditions,
schedules, specification, etc.).
	 
	 	3.10.	 	The issue of the written notice of acceptance of a Tender shall constitute a binding
agreement between LGL and the Tenderer and LGL and the Tenderer shall enter into a Purchase
Order as defined in clause 1.2 above.






	4.	 	Tendered Prices






	 	4.1.	 	All Tendered Prices shall be presented consistently with the taxes clause contained in
clause 6 of the LGL Equipment Supply Purchase Order Terms and Conditions in Section 1 Part
B. Goods and Services Tax or other value added taxes are specifically excluded.
	 
	 	4.2.	 	Australian Manufactured Goods — Tendered Prices shall be in Australian dollars with
goods delivered FCA (Incoterms 2000) loaded conveyance at the location nominated in Section
III. The cost of inland freight from the factory to the nominated place of delivery and the
cost of any duty on imported components shall be included in the overall tendered price but
itemised separately. The successful Tenderer will be required to document any duty paid on
imported components to allow LGL to submit a claim for duty drawback (if applicable). The
Tenderer shall submit, as part of its Tender submission, the Tenderer’s ABN.
	 
	 	4.3.	 	North American Manufactured Goods — Tendered Prices shall be in United States of
America Dollars, with goods FOB (Incoterms 2000) vessel at the nearest major seaport. The
cost of inland freight (country of origin) to the nearest major seaport (Tenderer to
nominate) shall be included in the overall tendered price but to be itemised separately.
	 
	 	4.4.	 	All Other Countries’ Manufactured Goods — Tendered Prices shall be in United States of
America Dollars, with goods delivered FOB (Incoterms 2000) vessel at the nearest major
seaport. The cost of inland freight (country of origin) to the nearest major seaport
(Tenderer to nominate) shall be included in the overall tendered price but to be itemised
separately. The Tenderer shall bear all foreign currency risk and shall allow for the
purchase of forward cover in the overall tendered price but to be itemised separately. It
remains the Tenderers responsibility to purchase such cover on award of the Purchase Order
and all foreign currency risk shall reside with the Tenderer or Seller.
	 
	 	4.5.	 	Export packing (kiln dried timber) must be quoted as a separate item where applicable.
Any costs associated with fumigating containerised cargo as required by Australian Customs
or Papua New Guinea Customs to meet quarantine restrictions applicable to imports into





			
	 	 	 
	Section I — Part A Instructions to Tenderers
	 	4











 









 











LGL EQUIPMENT SUPPLY TENDER





	 	 	 	Australia and/or Papua New Guinea, must be included in this cost. Fumigation must be
carried out by a recognised licensed fumigator who issues a certificate of fumigation,
which accompanies the shipping documents.
	 
	 	4.6.	 	The Tendered Price shall be a lump sum fixed price in accordance with the relevant
Incoterms 2000 classification. The Tenderer is to refer to Incoterms 2000 for complete
details with regards to risks and liabilities when providing pricing.
	 
	 	4.7.	 	All Hazardous or Dangerous goods are to be priced DDP (Incoterms 2000) and are to be
delivered and discharged at the Site (or other defined control location).






	5.	 	Contract and Terms of Payment






	 	5.1.	 	LGL’s Purchase Order terms and conditions as detailed in Section I Part B, together
with any Special Conditions detailed in the formal Purchase Order, shall be the only terms
and conditions applicable to any Purchase Order placed.
	 
	 	5.2.	 	The Tenderer shall detail its terms of payment including cash discounts, package deal
discounts, progress payments with defined milestones or deliverables, etc.






	6.	 	Weights and Dimensions






	 	6.1.	 	The Tenderer shall detail the total shipping weight, the number of pieces and the
dimensions and weight of all pieces over five tonnes.
	 
	 	6.2.	 	The Tenderer shall also detail the total shipping weight, the number of pieces and the
dimensions and weight of all pieces over five tonnes for spare parts.
	 
	 	6.3.	 	The Tenderer shall detail the total shipping weight and the dimensions of the largest
and heaviest pieces to be handled during installation and maintenance.






	7.	 	Contractual Delivery Schedule






	 	7.1.	 	The Tenderer shall state the guaranteed shipping date ex factory and state location of
the factory for all components.
	 
	 	7.2.	 	If equipment is to be manufactured in more than one factory, the Tenderer must state
all locations including a list of sub-suppliers and place of manufacture.
	 
	 	7.3.	 	The Tenderer shall state the Delivery Completion Date of all components in accordance
with the relevant Incoterms 2000 classification. These dates will form part of the Purchase
Order and will be stated on the Purchase Order (as the “Shipping Date”).
	 
	 	7.4.	 	When determining delivery dates for individual components, the Tenderer shall allow two
(2) weeks from the time of submission of preliminary drawings for LGL’s approval and return
of drawings (as required in the Detailed Specifications). As part of the Tender submission,
the Tenderer shall detail the following:






	 	i)	 	Days required from the date the Purchase Order is issued to delivery of
preliminary drawings and manuals for review by LGL.
	 
	 	ii)	 	Days required from the date the reviewed preliminary drawings and manuals are





			
	 	 	 
	Section I — Part A Instructions to Tenderers
	 	5











 









 











LGL EQUIPMENT SUPPLY TENDER





	 	 	 	returned to the delivery of complete certified drawings.
	 
	 	iii)	 	Days required from date of Purchase Order to guaranteed date for delivery of
Final Certified Drawings.






	 	7.5.	 	When determining delivery dates for individual components, the Tenderer shall allow two
(2) weeks from the closing date of the Tender prior to award.
	 
	 	7.6.	 	The Tenderer shall submit a detailed manufacturing and delivery schedule including all
sub- supplier items in a similar format to the example in Section IV.
	 
	 	7.7.	 	The Tenderer shall include in its manufacturing and delivery schedule the requirement
to supply any drawings, operation manuals, maintenance manuals, and parts manuals (Data)
required as set out in Section III.






	8.	 	Warranties/Guarantees






	 	8.1.	 	Tenderers shall provide details of all warranties and guarantees. The warranty period
must be for a period of twelve (12) months following commissioning and acceptance by the
LGL or eighteen (18) months following delivery, whichever period is shorter.
	 
	 	8.2.	 	Tenderers shall indicate extended warranties as a separate item and the costs of any
such extended warranty shall be detailed.
	 
	 	8.3.	 	Tenderers must ensure LGL is able to receive the benefit of any longer warranties
provided by sub-suppliers where to do so is at no additional cost to the Seller.






	9.	 	Alternative Proposals






	 	9.1.	 	The Tenderer shall submit a Tender strictly in accordance with the Tender Documents,
however, should the Tenderer, in addition to its conforming Tender, wish to submit
alternative offers based on departures from the Tender Documents, it shall list the
departures and the associated variation to the conforming Tender Price for each departure.
	 
	 	9.2.	 	Any alternative proposal shall conform to the requirements set out in the Tender
Documents, except to the extent that it describes how the alternative proposal departs from
the specific requirements. Departures shall be itemised under separate headings titled 1.
Technical Departures; 2. Commercial Departures; and 3. Optional Equipment and/or Materials.
	 
	 	9.3.	 	Alternative Tenders are encouraged where the Tenderer considers the alternative to be
an improvement or more economical, but still meets or exceeds the requirements of the
Tender Documents.
	 
	 	9.4.	 	LGL is not bound to accept any such alternative proposal submitted by a Tenderer






	10.	 	Priority






	 	10.1.	 	Where the Detailed Specifications (Section III) vary from the general conditions, site
conditions, ore characteristics and equipment standards (Section II), the Detailed
Specifications shall be considered as correct.





			
	 	 	 
	Section I — Part A Instructions to Tenderers
	 	6











 









 











LGL EQUIPMENT SUPPLY TENDER





	11.	 	Quality Assurance/Quality Control






	 	11.1.	 	All goods shall meet or exceed internationally recognised standards and
specifications to the extent not specified in the Tender documents.
	 
	 	11.2.	 	Tenderers shall detail their standards and specifications for the goods and how they
will ensure that these are met.
	 
	 	11.3.	 	Tenderers shall describe their quality assurance and control program including any
standards and certifications attained.






	12.	 	Tests






	 	12.1.	 	The Tenderer shall develop and submit for review by LGL an Inspection and Test Plan,
which will detail the timing of any tests required as the equipment or materials are being
produced.
	 
	 	12.2.	 	Where applicable, the Tenderer shall state the extra costs, if any, for witnessed and
verified performance tests.
	 
	 	12.3.	 	If the Tenderer does not have adequate facilities for performance testing, it will
state this in its Tender.






	13.	 	Erection or Start-up






	 	13.1.	 	When the Tenderer considers erection supervision, specialists, or start-up personnel
to be necessary for warranty purposes, or when LGL requires these personnel, the costs will
be shown as separate items but will be included in the Tender package and itemised as
follows (refer to Section I Part C “Technical On-Site Personnel Terms” for details of what
is to be included in each of the following):






	 	§	 	Reimbursable Sum
	 
	 	§	 	Daily Rates for each class of technical on-Site personnel
	 
	 	§	 	The location of representation
	 
	 	§	 	Number of technical on-Site personnel
	 
	 	§	 	Number and frequency of visits for inspection, testing, installation, and
commissioning






	14.	 	Spare Parts






	 	14.1.	 	The Tenderer shall supply, as part of its Tender, a detailed list of recommended spare
parts for one year’s continuous operation showing part numbers and prices.
	 
	 	14.2.	 	The Tenderer shall also state the location of the nearest service depot and/or
distributor along with a list of spare parts that are carried showing costs and weights.






	15.	 	Health, Safety, Environmental and Human Rights Compliance






	 	15.1.	 	The Tenderer shall provide a brief description of all relevant health, safety,
environmental and human rights compliance programs.
	 
	 	15.2.	 	The Tenderer shall include a copy of its environmental policy with the Tender
submission and shall state if all applicable environmental guidelines and regulations are
being met in





			
	 	 	 
	Section I — Part A Instructions to Tenderers
	 	7











 









 











LGL EQUIPMENT SUPPLY TENDER





	 	 	 	relation to the goods.
	 
	 	15.3.	 	The Tenderer shall list any violations, infractions, ongoing investigations or
penalties associated with health, safety, the environment, or human rights that relate to
the Tenderer or any of its subcontractors.





			
	 	 	 
	Section I — Part A Instructions to Tenderers
	 	8











 









 











LGL EQUIPMENT SUPPLY TENDER




LGL




Million Ounce Plant Upgrade (MOPU)



Equipment Supply Tender



SECTION I PART B

PURCHASE ORDER TERMS AND CONDITIONS



	 	 	 	 	 	 	 
	A.

	 	Definitions
	 	 	10	 
	B.

	 	General Terms and Conditions
	 	 	13	 
	C.

	 	Preparing Orders for Shipment
	 	 	26	 






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	9











 









 











LGL EQUIPMENT SUPPLY TENDER





	A)	 	Definitions






	 	 	The definition of terms used, interpretation of this agreement, and the rights of all
parties hereunder shall be construed under and governed by the laws of Queensland and
the Commonwealth of Australia in effect at the date of the Invitation to Tender. Should
a legislative requirement come into effect after the date of the Invitation to Tender
but could not be reasonably then have been anticipated by a competent Seller and which
causes the Seller to incur more or less cost than otherwise would have been incurred,
the difference shall be assessed by LGL and added to or deducted as a Purchase Order
Amendment.






	 	 	The following words used in this document shall, where the contents so permit, have the
following meanings:





	 	 	 	 	 	 	 
	Term	 	Meaning
	Applicable Law	 	all laws, by-laws, Acts, Regulations, codes, conditions or
requirements of any authority having jurisdiction over the Seller,
Merchandise, Purchase Order or the performance of the Purchase Order
	 
	 	 	 	 	 	 
	Confidential
Information	 	in relation to any party to this Contract, information relating to a
party’s business, computer systems or affairs and includes any:
	 
	 	 	1	 	trade secrets, know-how, scientific and technical information;
	 
	 	 	2	 	product, customer, marketing or pricing information;
	 
	 	 	3	 	information in relation to this Contract; and
	 
	 	 	4	 	any other information which a party notifies the other is
confidential, or which the other party knows or ought to know is
confidential
	 
	 	 	 	 	 	 
	Delay Event	 	1	 	an LGL-caused Delay;
	 
	 	 	2	 	a variation that is the subject of a variation order other than a
Variation requested by the Seller;
	 
	 	 	3	 	a change of law;
	 
	 	 	4	 	an industrial dispute which results in a labour stoppage that:
	 
	 
	 	 	 	•	 	has not arisen by reason of, or in connection with, events in any
way connected with the Purchase Order or the Seller; and
	 
	 
	 	 	 	•	 	could not have been foreseen by an internationally recognised
seller of the Merchandise in the jurisdiction in which the Purchase
Order is being performed having carried out all necessary
investigations; and
	 
	 	 	5	 	a Force Majeure Event;
	 
	 	 	but excluding any events in items 1 to 5 which would not have
occurred but for:
	 
	 	 	6	 	a breach of this Purchase Order by, or the negligence or
recklessness of, the Seller or its Subcontractors;
	 
	 	 	7	 	the lack of legal capacity, or corporate powers, of the Seller; or
	 
	 	 	8	 	LGL acting in accordance with this Purchase Order including any
termination of the Contract in accordance with its terms.






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	10











 









 











LGL EQUIPMENT SUPPLY TENDER




	 	 	 	 	 
	Term	 	Meaning
	Delivery
Completion Date	 	the date of delivery (expressed as a number of weeks from the
Commencement Date) of all items of Merchandise in accordance with the
relevant Incoterms 2000 classification as detailed in the Purchase
Order.
	 
	 	 	 	 
	Force Majeure Event	 	means (and is limited to) the following specific events or circumstances:
	 
	 
	 	1	 	earthquake, flood or other natural catastrophe;
	 
	 
	 	2	 	strike or lockout;
	 
	 
	 	3	 	civil disturbance, riot or armed conflict;
	 
	 
	 	4	 	rebellion or sabotage;
	 
	 
	 	5	 	curtailment, rationing or allocation of normal sources of supply of
labour, materials, transportation, energy or utilities;
	 
	 
	 	6	 	sufferance of or voluntary compliance with act of government and
government regulations (whether or not valid);
	 
	 
	 	7	 	fire or explosion, including radioactive or toxic explosion; and
	 
	 
	 	8	 	war, insurrection, riot or acts of terrorism;
	 
	 	 	but only where those events or circumstances:
	 
	 
	 	9	 	are not reasonably foreseeable by the Seller;
	 
	 
	 	10	 	are beyond the reasonable control of the Seller; and
	 
	 
	 	11	 	are such that, even with the exercise of good engineering and
procurement practices, the Seller would not be able to prevent or
overcome.
	 
	 	 	 	 
	Merchandise	 	includes all goods, chattels, plant, equipment, machinery, stores, data
and other property of any kind described on the Purchase Order.
	 
	 	 	 	 
	LGL-Caused Delay
	 	1	 	delay or disruption caused by LGL but does not include any delay or
disruption cause by LGL acting in accordance with this Purchase Order;
	 
	 
	 	2	 	an act of prevention of LGL including a breach by LGL of any of its
obligations under this Contract, but does not include any delay or
disruption caused by the LGL acting in accordance with this Purchase
Order.
	 
	 	 	 	 
	Purchase Order	 	a formal document issued to a supplier for the supply of specific goods
in accordance with these standard terms and conditions The Purchase
Order is a contract between LGL and the Seller.
	 
	 	 	 	 
	Purchase Order
Amendment	 	a written direction from LGL identified as such directing the Seller to
carry out a Variation
	 
	 	 	 	 
	Purchase Order Value	 	The total value to be paid by LGL in consideration of the Seller
supplying and delivering the Merchandise.
	 
	 	 	 	 
	Seller	 	the person, firm or corporation from whom the Merchandise is being
purchased pursuant to this Purchase Order
	 
	 	 	 	 
	Shipping Date	 	The guaranteed date stated in the formal Purchase Order for the






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	11







 









 








LGL EQUIPMENT SUPPLY TENDER




	 	 	 	 	 
	Term	 	Meaning
	 	 	shipment of individual items of Merchandise in accordance with
the relevant Incoterms 2000 classification, or for the Delivery
Completion Date for all components in accordance with the
relevant Incoterms 2000 classification.
	 
	 	 	 	 
	Site	 	Lihir Mine Site, Putput, Lihir Island, New Ireland Province,
Papua New Guinea
	 
	 	 	 	 
	Standards	 	the standards specified to which the Merchandise is to meet or
exceed the requirements of; where no standards are specified,
the relevant Papua New Guinean (PNG) Standard shall apply. Where
there is no relevant PNG Standard, then the relevant Australian
Standard shall apply.
	 
	 	 	 	 
	Tax	 	any tax, levy, royalty, rate, duty, fee, impost, or other charge
imposed by any governmental, semi-governmental, or other body
authorised by law whether in PNG, Australia or other country to
impose such Tax. Without limiting the generality of the
foregoing, Tax includes any withholding tax (including foreign
contractor withholding tax), goods and services tax, value added
tax, petroleum resource rent tax, any tax respecting
environmental effects including a carbon tax.
	 
	 	 	 	 
	Variation	 	any one or more of the following:
	 
	 
	 	1	 	an increase, decrease or omission of any part of the Works;
	 
	 
	 	2	 	any change in the character or quality of any Merchandise or
any part of the Works; or
	 
	 
	 	3	 	any change in the method, sequence or timing of the Works,
	 
	 	 	but does not include a direction by LGL to perform the Works in
accordance with this Contract






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	12







 











 





LGL EQUIPMENT SUPPLY TENDER




B) General Terms and Conditions



The Seller must supply the Merchandise to LGL in accordance with the terms and conditions of the
Purchase Order.





	 	1)	 	COMPLETE AGREEMENT
	 
	 	 	 	This Purchase Order, which term shall include these terms and conditions and any
technical documents incorporated and/or attached hereto (Purchase Order Documents),
constitutes the sole and entire agreement between the parties.
	 
	 	 	 	The Purchase Order documents comprise the following with the order of precedence as
shown:






	 	a)	 	The formal, signed, computer generated Purchase Order detailing
specifically what is being ordered, the Purchase Order Value, any Special
Conditions or additional technical information
	 
	 	b)	 	Applicable correspondence detailed in the Purchase Order
	 
	 	c)	 	Tender Document Section I Part B: Purchase Order Terms and Conditions
	 
	 	d)	 	Tenderer’s Completed Tender Document Section IV
	 
	 	e)	 	Tender Document Section III
	 
	 	f)	 	Tender Document Sections I Part A and Section II
	 
	 	g)	 	Invitation to Tender Letter






	 	 	 	The Seller’s quotation is incorporated in and made a part of this Purchase Order only
to the extent of specifying the nature and description of the Merchandise ordered and
then only to the extent that such items are consistent with the other terms of this
Purchase Order. No other terms or conditions shall be binding upon LGL unless accepted
by it in writing.
	 
	 	2)	 	DELIVERY
	 
	 	 	 	The Seller shall deliver the Merchandise in accordance with the Delivery Completion
Date detailed in the Purchase Order, and any delivery milestones detailed in the
Seller’s schedule incorporated into the Purchase Documents.
	 
	 	3)	 	QUANTITY, QUALITY, AND VARIATIONS
	 
	 	 	 	Neither the quantity nor the quality of Merchandise delivered shall differ from that
specified in this Purchase Order unless the changed quantity or quality is ordered by
LGL on a Purchase Order Amendment specifically referring to this Purchase Order. LGL
shall not be required to pay for excess quantities of Merchandise and may return excess
quantities or Merchandise to Seller at Seller’s expense.
	 
	 	 	 	The Seller warrants that all Merchandise sold hereunder, shall have been produced, sold,
delivered and furnished in strict compliance with all Applicable Law and applicable
Standards, to which the Merchandise are subject. Seller shall execute and deliver such
documents as may be required to effect or to evidence compliance. All Applicable Law
required to be incorporated in agreements of this character are hereby incorporated
herein by this reference.
	 
	 	 	 	The Seller shall prepare an Inspection and Test Plan (ITP) in accordance with the
Seller’s standard practice within 2 weeks of award of the Purchase Order. The ITP will
be submitted for review and acceptance by LGL.
	 
	 	 	 	The Seller shall ensure that the Merchandise meets the consistent quality in accordance
with its quality assurance and control program.







			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	13






 









 





LGL EQUIPMENT SUPPLY TENDER





	 	 	 	LGL may issue a request for a quotation for a proposed Variation (Variation Quotation)
and, subject to this clause, the Seller must carry out a Variation which is the subject
of a Purchase Order Amendment.
	 
	 	 	 	Before a Purchase Order Amendment is issued, the Seller must provide a quotation for a
proposed Variation before LGL discusses with the Seller whether the work is to proceed
and the Seller must provide the quotation as soon as practicable after receipt of the
request. A Purchase Order Amendment must incorporate the terms of the Variation
Quotation.
	 
	 	 	 	The Seller’s Variation Quotation for the proposed Variation must include particulars of:






	 	•	 	its fixed price for carrying out the proposed Variation;
	 
	 	•	 	the effect (if any) of the proposed Variation on:






	 	o	 	the achievement of Delivery Completion;
	 
	 	o	 	any warranties with respect to the Equipment; and
	 
	 	o	 	the Seller’s ability to comply with any of its obligations under this Contract.






	 	•	 	any other relevant information related to carrying out the proposed Variation






	 	4)	 	PROGRESS REPORTS AND SCHEDULE
	 
	 	 	 	Commencing the first Monday after the date of issue of the Purchase Order, and
continuing thereafter every Monday until all equipment has been delivered in accordance
with the applicable Incoterms 2000 classification (including short-shipped items, if
any) the Seller shall submit a detailed procurement, manufacturing, assembly and
testing schedule and progress report.
	 
	 	 	 	Should any incident or occurrence arise which may delay the manufacturing, delivery
schedule, or Delivery Completion Date, the Seller shall immediately notify LGL in
writing.
	 
	 	5)	 	SECURITY AND RETENTION
	 
	 	 	 	If required by the Purchase Order, the Seller shall lodge an unconditional Bank
Guarantee in the amount detailed within 14 days of the Purchase Order issue. This
security will be held by LGL until the expiry of the Defects Liability Period. LGL may
recover all debts due and owing from the Seller to LGL from the security if not
otherwise paid by or recovered from the Seller.
	 
	 	 	 	In addition, LGL will withhold a percentage of each invoice (totalling of the Purchase
Order Value) until such time as the earlier of Merchandise is inspected on Site or until
completion of equipment commissioning, for a period not to exceed 180 days from the
Delivery Completion Date at the nominated delivery place or shipping point.
	 
	 	6)	 	TAX






	 	6.1	 	Liability for Tax
	 
	 	 	 	The Seller shall reimburse LGL for the amount of LGL’s liability for any Tax
(excluding income tax) levied by the Australian or PNG government in respect of any
supply made by the Seller under this Contract but only to the extent that such Tax
is incurred or arises before delivery of the Merchandise in accordance with the
relevant Incoterms 2000 classification. Any Tax that is incurred or arises after
delivery of the Merchandise in accordance with the relevant Incoterms 2000
classification is to be borne by LGL and is not subject to reimbursement by the
Seller.
	 
	 	 	 	Any consideration to be paid or provided for a supply made under or in connection
with the Contract is expressed inclusive of all Tax, other than GST, in force at the
Completion Date.







			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	14






 









 





LGL EQUIPMENT SUPPLY TENDER





	 	 	 	Should LGL be required to withhold any amounts on account of any Tax (excluding
Income Tax) levied by the Australian or PNG government, the corresponding withheld
amount will be taken as a reduction in the consideration to be paid or provided.
	 
	 	6.2	 	GST
	 
	 	 	 	For the purposes of Clause 6:
	 
	 	 	 	“Adjustment Note” means an adjustment note as that term is defined in the GST Law or
a credit or debit note as those terms are defined in the PNG GST Act, as applicable;
	 
	 	 	 	“Consideration” has the meaning given by the GST Law;
	 
	 	 	 	“Goods” has the meaning given to that term by the GST Law or the PNG GST Act, as
applicable;
	 
	 	 	 	“GST” means GST as that term is defined by the GST Law or the goods and services tax
referred to in sections 6 and 8 of the PNG GST Act, as applicable;
	 
	 	 	 	“GST Amount” means, in relation to a Taxable Supply, the amount of GST payable in
respect of that Taxable Supply;
	 
	 	 	 	“GST Group” has the meaning given by the GST Law;
	 
	 	 	 	“GST Law” has the meaning given by the A New Tax System (Goods and Services Tax) Act
1999 (Cth);
	 
	 	 	 	“Input Tax Credit” means an input tax credit as that term is defined in the GST Law
or a credit for input tax as that term is defined in the PNG GST Act, as applicable
and a reference to an Input Tax Credit entitlement of a Party includes, as
applicable:






	 	•	 	An input tax credit for an acquisition made by that Party but to
which another member of the same GST Group is entitled; or
	 
	 	•	 	A credit for input tax for a supply which is made to that Party
but which is deemed by the PNG GST Act to be made to the representative member
or a group of companies;






	 	 	 	“PNG GST Act” means the Goods and Services Tax Act 2003 (PNG);
	 
	 	 	 	“Recipient” has the meaning given to that term by the GST Law or the PNG GST Act, as
applicable;
	 
	 	 	 	“Tax Invoice” has the meaning given by the GST Law or the PNG GST Act, as
applicable;
	 
	 	 	 	“Taxable Supply” means a taxable supply as that term is defined in the GST Law
(excluding the reference to section 84-5 of the A New Tax System (Goods and Services
Act 1999 (Cth)) or a supply upon which goods and services tax is imposed by the PNG
GST Act, as applicable.
	 
	 	6.3	 	Tax Exclusive Consideration
	 
	 	 	 	Any consideration to be paid or provided for a supply made under or in connection
with the Contract, unless specifically described in the Contract as “GST inclusive”,
does not include an amount on account of GST.
	 
	 	 	 	The Seller will make all reasonable endeavours to ensure the supply of the
Merchandise is GST-free under GST Law. In this regard, the Seller warrants that it
will export the Merchandise within 60 days of the earlier of receiving any
consideration for the supply or issuing an invoice for the supply and that it will
hold sufficient documentary evidence to substantiate the export of the Merchandise
within the 60 day timeframe.







			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	15







 









 








LGL EQUIPMENT SUPPLY TENDER





	 	 	 	Despite any other provision in the Contract, if a party (“Seller”) makes a supply
under or in connection with the Contract on which GST is imposed to any extent (not
being a supply the consideration for which is specifically described in the Contract
as “GST inclusive”):






	 	•	 	The consideration payable or to be provided for that supply under
the Contract is increased by, and the recipient of the supply (“Recipient”) must
also pay to the Seller, an amount equal to the GST payable by the Seller on that
supply;
	 
	 	•	 	The amount by which the GST exclusive consideration is increased
must be paid to the Seller by the Recipient at the same time as the GST
exclusive consideration is payable or to be provided; and
	 
	 	•	 	Notwithstanding any other provision of the Contract, the
Recipient is not required to pay any amount unless it has received a valid tax
invoice (or valid adjustment note) for that taxable supply.






	 	 	 	Notwithstanding the above provisions, the Buyer is only required to gross up a
payment under Clause 6.3 if and to the extent that the Buyer is entitled to claim a
corresponding Input Tax Credit.
	 
	 	6.4	 	Reimbursements
	 
	 	 	 	If a payment to a party under the Contract is a reimbursement or indemnification,
calculated by reference to a loss, cost or expense incurred by that party, then the
payment must be reduced by the amount of any input tax credit to which that party is
entitled for that loss, cost or expense. That party is assumed to be entitled to a
full input tax credit unless it proves, before the date on which the payment must be
made, that its entitlement is otherwise.
	 
	 	6.5	 	Adjustment Events
	 
	 	 	 	If, at any time, an adjustment event arises in respect of any supply made by a party
under the Contract, a corresponding adjustment must be made between the parties.
Payments to give effect to the adjustment must be made between the parties and the
Seller must issue a valid adjustment note in relation to the adjustment event.
	 
	 	6.6	 	Survival
	 
	 	 	 	This clause 6 shall survive on completion or termination of the Contract.






	 	7)	 	INSPECTION IN PROGRESS
	 
	 	 	 	Seller agrees that LGL or its designated agent shall have the right of inspection of all
Merchandise furnished hereunder while in any stage of engineering or manufacture upon
presentation of twenty-four (24) hours notice and Seller shall carry out any tests as
required by LGL to establish if the Merchandise conforms to this Purchase Order. Seller
shall make this a condition of any subcontract work and provide all relevant information
concerning its Subcontractors to LGL. The Seller and/or Subcontractors shall ensure that
LGL or its designated agent has access to drawings and the like to verify the goods
being manufactured. LGL or its designated agent shall have the power to reject any
Merchandise that does not conform to this Purchase Order, whereupon this rejected
Merchandise shall be re-supplied at no additional cost to LGL. Any such inspection or
any lack of such inspection shall not relieve Seller of any obligation contained in the
Purchase Order Documents.
	 
	 	8)	 	DRAWINGS, OPERATION MANUALS, MAINTENANCE MANUALS, AND PARTS LISTS
	 
	 	 	 	The Seller shall supply all drawings, manuals, etc, (Data) as required by the Purchase
Order, by pre-paid courier service at no additional cost. In addition to any other Data
required, the Seller shall submit:






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	16







 









 








LGL EQUIPMENT SUPPLY TENDER





	 	•	 	Mechanical: Five (5) sets of preliminary drawings for review.
	 
	 	•	 	Electrical: Two (2) sets of preliminary drawings on paper for review of design.
	 
	 	•	 	All Drawings: Two (2) sets on paper, one (1) electronic
“Certified for Construction” or “As Built”; as applicable, signed and dated.
	 
	 	•	 	Installation, Operation and Maintenance Manuals (Operator’s
Manuals): Two (2) preliminary copies. Manuals are to be in binders and tagged
with the Seller’s name, the Purchase Order number, model and equipment numbers.
	 
	 	•	 	Approved Operator’s Manuals: Four (4) SETS. (If the 2 preliminary
manuals are approved without comment by LGL, then only two (2) additional copies
are required.)
	 
	 	•	 	Parts Manuals: Four (4) sets including bearings, seals, and
filter conversions for mechanical equipment (Parts Manuals may be combined with
the Operator’s Manuals)






	 	 	 	LGL will review and return the Data to the Seller with one of the following comments:






	 	i)	 	“No Exception Taken” — the Seller will proceed with the
supply of Merchandise indicated on that submission in accordance with the
Purchase Order.
	 
	 	ii)	 	“Exception as Noted” — the Seller shall make the changes
noted and proceed with the supply of Merchandise in accordance with the
Purchase Order. The revised data will be resubmitted for LGL further
review.
	 
	 	iii)	 	“Revise as Noted and Resubmit” — the Seller shall revise
the data and resubmit for review prior to proceeding with supply of the
Merchandise unless written instructions are received to the contrary from
LGL.






	 	 	 	Drawings must be folded to A4 size.
	 
	 	 	 	All documents produced for the MOPU Project will contain the following information:




Purchaser: LGL

Project: MOPU

Location: Lihir Island Papua New Guinea

Equipment Title:

Equipment No.:

P.O. No.:

Date:

Revision No.:





	 	 	 	Within five (5) days after receipt of the Purchase Order, the Seller shall submit a
drawing schedule that will include drawing numbers, drawing descriptions, revision
numbers and submittal dates which will be in accordance with the dates detailed in the
Seller’s completed Tender Section IV “Technical Data Schedule”.
	 
	 	9)	 	SHIPPING
	 
	 	 	 	The Seller shall prepare the Merchandise for shipping in accordance with Part C of the
Purchase Order terms and conditions.
	 
	 	10)	 	PAYMENTS
	 
	 	 	 	In consideration of the payment by LGL to the Seller of the Purchase Order Value, the
Seller shall supply the Merchandise and otherwise perform its obligations in accordance
with the Purchase Order.






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	17







 









 








LGL EQUIPMENT SUPPLY TENDER





	 	 	 	Subject to the Seller properly performing its obligations under the Purchase Order, LGL
shall pay the Seller the Purchase Order Value.
	 
	 	 	 	Progress claim payments will be made by LGL in accordance with the milestones and
currency detailed in the formal Purchase Order. Payments will be made at the end of the
month following receipt of correct invoices. The time for payment of invoices, or for
accepting any discounts offered, shall run only from the date correct invoices are
furnished to LGL.
	 
	 	 	 	Progress claims shall include evidence that a milestone has been reached. Evidence of
achieving a milestone date will include: unpriced purchase orders to sub-suppliers
together with the sub-supplier’s written acceptance of the order; delivery dockets for
goods to be incorporated into the Merchandise; test certificates; and proof of delivery
of the component in accordance with the applicable Incoterms 2000 classification.
	 
	 	 	 	Progress claim invoices shall be sent to the address detailed for LGL in clause 33.
	 
	 	 	 	Progress claim invoice payments will be made by electronic funds transfer.
	 
	 	 	 	LGL may set off any amounts due and payable by the Seller to LGL against any payments
due and payable from LGL to the Seller either under this Purchase Order or otherwise.
	 
	 	11)	 	CANCELLATION
	 
	 	 	 	LGL may, at its option, cancel any Purchase Order for Merchandise (in whole or in part)
not then delivered or in transit by written notice which shall be effective immediately.
Provided the Seller is not in default, LGL shall pay to Seller the cost incurred by
Seller in connection with this Purchase Order prior to the date of such cancellation but
excluding unrecovered overheads or profits, provided that the amount payable by LGL in
respect of such cost, when added to all previous payments made or becoming payable
hereunder shall not exceed the total price stated in the Purchase Order. Upon such
payment, title to and property in any Merchandise forming part of or incomplete
Merchandise shall pass to LGL. If required by LGL, the Seller will novate any
subcontracts to LGL.
	 
	 	12)	 	TERMINATION FOR DEFAULT
	 
	 	 	 	In the event of any breach by Seller of any of the terms of this Purchase Order
including Seller’s warranties, LGL may at its option, and without prejudice to any of
its other rights, by notice in writing, cancel the Purchase Order in respect of any
undelivered Merchandise or non performed Service. In the case of a fundamental breach by
the Seller, termination shall be immediate, whereas for other breaches, termination will
be effective if the breach is not rectified within 30 calendar days of notice in writing
by LGL. The Delivery Completion Date stipulated for delivery of the Merchandise shall be
the fundamental term of the Purchase Order.
	 
	 	 	 	On issuing notice in writing of a breach (other than fundamental breach), LGL may
suspend payments to the Seller until the date on which the Seller remedies the breach.
	 
	 	 	 	LGL must immediately lift any suspension of payments if the Seller remedies the breach
or overcomes the effects of the breach.
	 
	 	 	 	Upon termination in accordance with this clause 12, LGL shall be entitled to, at its
election, to receive title to the Merchandise (in its then current state) and make no
further payment under this Contract or receive a full refund of all amounts paid under
this contract to the date of cancellation.






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	18







 









 








LGL EQUIPMENT SUPPLY TENDER





	 	13)	 	WARRANTIES — GUARANTEES
	 
	 	 	 	Seller warrants to LGL that the Merchandise shall be of the quality specified or of the
best of their respective kinds if no quality is specified, and shall conform to the
specifications, drawings, samples, and other descriptions set out in the Purchase Order
Documents. Seller guarantees and warrants the Merchandise against any and all defects in
workmanship and materials during the defects liability period which shall be the earlier
of eighteen months from the Delivery Completion Date of the equipment or twelve (12)
months following commissioning the equipment. In the absence of a specified standard,
the Merchandise shall be in accordance with PNG Standards, and if no applicable PNG
Standard exists, to Australian Standards.
	 
	 	 	 	The Seller warrants that the Merchandise will meet or exceed any availability or
performance guarantees specified in the Purchase Order. If those guarantees are not met
or exceeded (in the opinion of LGL) then the Seller shall pay as a debt due and payable
an amount to LGL as compensation for LGL’s genuine pre-estimate of its loss. This amount
shall be detailed in the Purchase Order.
	 
	 	 	 	During the defects liability period, defective Merchandise shall be replaced or repaired
by the Seller free of charge, or alternatively defective Merchandise may be replaced or
repaired by LGL at the Seller’s cost (such amounts to be a debt due and payable by the
Seller to LGL).
	 
	 	 	 	The Merchandise is ordered by LGL in reliance on each and all of the warranties and
guarantees specified herein, or implied by law or usage or trade, and unless otherwise
expressly stated herein, said warranties and guarantees shall apply. If the Seller is
not the manufacturer of some or all of the Merchandise covered by the Purchase Order,
Seller shall, in addition to the warranties and guarantees set out in the preceding
paragraph, or in the alternative to the said warranties and guarantees, make necessary
arrangements whereby the manufacturers involved will extend the same warranties and
guarantees to LGL directly.
	 
	 	14)	 	SELLER’S INDEMNITY
	 
	 	 	 	Insofar as this clause applies to property, it applies to property other than the
equipment or goods.
	 
	 	 	 	The Seller indemnifies LGL against:






	 	(i)	 	loss of or damage to LGL’s property;
	 
	 	(ii)	 	claims by third parties arising out of or as a consequence of the Seller’s performance of the
Purchase Order;
	 
	 	(iii)	 	claims in respect of personal injury or death or loss or damage to any other property arising
out of or as a consequence of the Seller’s performance of the Purchase Order; and
	 
	 	(iv)	 	the Seller’s breach of this contract,






	 	 	 	but the indemnity shall be reduced proportionally to the extent that the act or omission
of LGL or its consultants, agents or other contractors (not being employed by the
Seller) may have contributed to the injury, death, loss or damage.
	 
	 	 	 	The clause shall not apply to the extent that the Seller’s liability is limited by
another provision of the Purchase Order.
	 
	 	15)	 	INSURANCE TO BE ARRANGED BY SELLER






	 	15.1	 	Insurance of Merchandise: The Seller shall, at its own cost, insure
the Merchandise for its replacement value against loss or damage from the date of the
Purchase Order until






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	19







 









 





LGL EQUIPMENT SUPPLY TENDER





	 	 	 	the Merchandise is delivered in accordance with the relevant Incoterms 2000
classification.
	 
	 	 	 	The policy or policies effected under this subclause shall note the interests of LGL.
	 
	 	15.2	 	Public and Product Liability: Seller shall, at its own cost, maintain
and pay for public and product liability until expiry of the Defects Liability Period
with a limit of not less than Seller shall ensure each Sub-Contractor carries
equivalent comprehensive public and product liability insurance.
	 
	 	 	 	Policies shall note the interests of LGL and cover the parties’ respective liability
to each other for loss or damage to property (other than property required to be
covered under subclause 15.1 and the death of or injury to any person (other than
liability which the law requires to be covered under a workers compensation insurance
policy.
	 
	 	15.3	 	Professional Indemnity: Seller shall, at its own cost, maintain and pay
for professional indemnity insurance with a limit of not less than inclusive for any
one claim and in the aggregate or such greater amount as may be required by any
applicable professional organization or licensing authority. Such insurance shall be
continued in place for at least six (6) years following completion of the Works.
	 
	 	15.3	 	Worker’s Compensation: Seller shall insure its liability, including its
legal liability, as required under any applicable Worker’s Compensation statute or
regulation to its employees engaged in doing anything for the purpose of executing
Seller’s rights or obligations under the Purchase Order. Such Insurance shall be
endorsed, where possible, to indemnify LGL and its consultants, affiliates, employees
and agents against any liability which they may incur under any applicable Worker’s
Compensation statute or regulation thereunder, in relation to the said employees
engaged as aforesaid. Seller shall also ensure that each of its Sub-Contractors insures
their liability, including their legal liability, as required under any applicable
Worker’s Compensation statute or regulation thereunder to their employees engaged in
doing anything for the purpose of executing Seller’s rights or obligations under the
Purchase Order and such insurance by each Sub-Contractor shall be endorsed, where
possible, to indemnify Seller, LGL and their respective consultants, affiliates,
employees and agents against any liability which they may incur under any applicable
Worker’s Compensation statute or regulation thereunder, in relation to the said
employees engaged as aforesaid.
	 
	 	 	 	Seller shall pay all assessments due under relevant Worker’s Compensation
legislation.
	 
	 	 	 	Seller shall provide LGL with satisfactory evidence that Seller is in good standing
with applicable Worker’s Compensation authorities from time to time as may be
requested by LGL.






	 	16)	 	GENERAL INSURANCE PROVISIONS






	 	16.1	 	Insurance shall be effected by Seller before the commencement of the risks to
which the insurance relates with insurers approved by LGL whose approval shall not be
unreasonably withheld.
	 
	 	16.2	 	Seller shall show proof of the above cover prior to performing this Purchase
Order. Seller shall provide LGL with certificates of insurance of each policy requested
by LGL together with evidence of payment of premiums. If Seller fails to provide
satisfactory evidence of insurance to LGL, LGL may, but shall not be obligated to,
place such insurance as LGL may consider necessary and the cost of such coverage shall
be paid by Seller on demand.






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	20







 









 








LGL EQUIPMENT SUPPLY TENDER





	 	16.3	 	The effecting and keeping in force of insurance as required herein shall in no
way limit the responsibilities, obligations and liabilities of Seller under other
provisions of the Purchase Order.
	 
	 	16.4	 	Seller is responsible for all additional Insurance that it deems necessary and
it shall indemnify and hold harmless LGL and its consultants, affiliates, employees and
agents against any claims by it or any third party in the event of a loss or damage.
	 
	 	16.5	 	The policies for the insurance to be provided by Seller shall contain
provisions acceptable to LGL which:






	 	•	 	requires the insurer to inform both parties, whenever the insurer
gives a party or a subcontractor a notice in connection with the policy;
	 
	 	•	 	provides that a notice of claim given to the insurer by either
party or a subcontractor shall be accepted by the insurer as a notice of claim
given by both parties and the subcontractor; and
	 
	 	•	 	requires the insurer, whenever the Seller fails to maintain the
policy, promptly to give written notice thereof to both parties and prior to
cancellation of the policy.






	 	17)	 	PRICE
	 
	 	 	 	The price stated on this Purchase Order is a lump sum fixed price in accordance with the
relevant Incoterms 2000 classification and not subject to escalation. The price stated
on this Purchase Order includes all risks expressly and impliedly contemplated by the
agreement.
	 
	 	18)	 	SPARE PARTS
	 
	 	 	 	The Seller shall be obligated to supply spare parts at the prices detailed in its
completed Tender Section IV for purchases made by LGL up to the end of the Warranty
period.
	 
	 	 	 	The successful Tenderer shall be required to supply all cross reference part numbers on
non-original equipment manufacturer or sub-supplier parts
	 
	 	19)	 	PATENTS, TRADEMARKS AND COPYRIGHTS
	 
	 	 	 	Seller warrants to LGL and its successors in title, that the manufacture, sale or use of
the Merchandise will not infringe or contribute to the infringement of any intellectual
property rights including patents, trademarks, designs or copyrights in Australia or in
any other country. Seller indemnifies LGL and its successors in title against any loss
or damage (including legal fees and costs) arising from breach of this warranty or
prevention or hindrance of use of the Merchandise. The Intellectual Property in the
Merchandise and documents shall remain with the Seller, and the Seller provides an
irrevocable, royalty-free, perpetual licence to LGL to use the Intellectual Property.
	 
	 	20)	 	TITLE AND RISK IN THE MERCHANDISE
	 
	 	 	 	Risk in the Merchandise shall pass to LGL on delivery to the place specified in the
Purchase Order in accordance with the relevant Incoterms 2000 classification but subject
to LGL’s right to reject any Merchandise.
	 
	 	 	 	Title in the Merchandise passes to LGL upon payment to the Seller of the final milestone
payment.







			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	21







 









 








LGL EQUIPMENT SUPPLY TENDER





	 	21)	 	TRANSPORTATION
	 
	 	 	 	Immediately Seller despatches the Merchandise, Seller shall notify LGL of the date and
time of dispatch, the number of the Purchase Order, the kind and amount of Merchandise
dispatched and the route and method by which the Merchandise will be transported. All
Merchandise shall be packed, marked and transported as specified in this Purchase
Order, but if not specified, then in a proper and suitable manner and in all cases in
accordance with the proper requirements for carrier.
	 
	 	22)	 	INSPECTION OF MERCHANDISE
	 
	 	 	 	Notwithstanding any prior payment, all Merchandise is subject to inspection and testing,
which may be carried out after installation or incorporation and under operating
conditions. If upon or after any such inspection or test any Merchandise is found to be
unsatisfactory, defective, of inferior quality or workmanship or fails to meet the
specifications or any other requirements of this Purchase Order, LGL, without prejudice
to any other rights or remedies it might have, may return the Merchandise to Seller at
Seller’s expense. Upon return of any unsatisfactory or defective Merchandise, Seller
shall either resupply new Merchandise as a replacement of the returned Merchandise or
reimburse LGL for any amounts paid by LGL on account of the purchase price of returned
Merchandise and any other cost, expense, or damage incurred or suffered by LGL in
connection with the failure of the Seller to comply with the terms of this Purchase
Order, including such costs, expense or damage associated with the delivery,
installation or return of the Merchandise.
	 
	 	23)	 	CONFIDENTIAL INFORMATION
	 
	 	 	 	Any Confidential Information provided by the Seller or LGL shall not be disclosed by the
other party to any third person without prior written consent of the fist party. The
exceptions to his clause are if the information is in the public domain or the
information is required to be disclosed by law or the rules of a stock exchange on which
the party’s securities are listed.
	 
	 	 	 	Unless otherwise provided in this Purchase Order, all plans, drawings and specifications
prepared or supplied by or on behalf of LGL and any copies made therefrom shall be and
remain the property of LGL, and shall be used by Seller only in performance of this
Purchase Order, and shall be returned by Seller on completion of this Purchase Order.
	 
	 	24)	 	LICENCES
	 
	 	 	 	Unless otherwise specified in this Purchase Order, Seller at its cost shall obtain all
required licences, permits and authorities required in performance of this Purchase
Order and shall comply with all Applicable Law and Standards in relation to the
Merchandise.
	 
	 	25)	 	STANDARD CONDITIONS FOR ON-SITE WORK
	 
	 	 	 	If LGL requires the Seller to undertake on-Site work, the Seller will be required to
enter into a separate purchase order which will require the Seller to comply with the
terms detailed in Section 1 Part C -Technical On-site Personnel Terms.
	 
	 	26)	 	DELAYS AND LIQUIDATED DAMAGES
	 
	 	 	 	The Seller acknowledges that delivery of Merchandise must be made by the dates
specified. If the Seller fails to meet the dates stipulated in the Purchase Order, the
Seller shall pay to LGL of the Purchase Order Value for each day the shipment or
performance date is delayed up to a maximum of the Purchase Order Value by way of
Liquidated Damages. The Purchase Order shall specify if liquidated damages apply and if
so, the applicable percentages. Should the liquidated damages clause be found to be
unenforceable, then LGL will be entitled to claim damages on other grounds.






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	22







 









 








LGL EQUIPMENT SUPPLY TENDER





	 	 	 	Notwithstanding the foregoing, the Seller shall not be liable for delays due to causes
(not including financial causes) beyond its reasonable control and covered under a Delay
Event. If under these circumstances, LGL decides that it will not be unduly prejudiced
by any such Delay Event, the Delivery Completion Date or performance shall be extended
for the period equal to the time actually lost by reason of such Delay Event at no
additional cost to LGL.
	 
	 	 	 	The Seller shall immediately notify LGL in writing within ten (10) days if an incident
or occurrence arises which may delay the manufacturing, delivery schedule or Delivery
Completion Date. Failure to do so will constitute a waiver of any claim the Seller may
have had for an extension of time.
	 
	 	 	 	LGL will withhold progress payments or apply liquidated damages pending receipt of
final certified drawings within the time specified by the Seller in the Completed
Tender Section IV “Form of Tender
	 
	 	27)	 	LIMITATION OF LIABILITY
	 
	 	 	 	The total liability of each party arising out of or in connection with the Contract
including a claim in tort, under statute, for rectification or frustration or like claim
available under the law governing the Contract is limited to the Purchase Order Value.
	 
	 	 	 	The limitation shall continue to apply notwithstanding fundamental breach, breach of a
fundamental term, rescission, repudiation or termination for any reason or frustration,
whether unintentional or by operation of law.
	 
	 	 	 	The limitation of liability under this clause 27 shall not apply to:






	 	a)	 	Liability to pay the value of the Purchase Order as
adjusted pursuant to the Purchase Order Terms and Conditions;
	 
	 	b)	 	Loss arising through fraud, negligence or wilful misconduct by a party;
	 
	 	c)	 	Liability for infringement of any third party intellectual property rights;
	 
	 	d)	 	The extent that liability is otherwise limited by another
provision of the Contract; and
	 
	 	e)	 	Liability out of which by law the party liable cannot contract.






	 	28)	 	PROGRESS REPORTS
	 
	 	 	 	Commencing the first Monday after date of issue of the Purchase Order, and continuing
thereafter every Monday, until all equipment has been shipped (including short-shipped
items, if any), the Seller shall submit a detailed procurement, manufacturing, assembly
and testing schedule and progress report.
	 
	 	 	 	Should any incident or occurrence arise which may delay the manufacturing or delivery
schedule, the Seller shall immediately notify LGL in writing.
	 
	 	29)	 	SUSPENSION
	 
	 	 	 	LGL may direct the Seller to suspend supply or delivery of the whole or part of the
equipment or goods for such time as LGL thinks fit, if LGL is of the opinion that it is
necessary because of an act, default or omission on the part of LGL or the Seller; for
the protection or safety of any person or property; or to comply with a court order.
	 
	 	 	 	If the Seller wishes to suspend supply or delivery of the whole or part of the equipment
or goods the Seller shall obtain LGL’s prior written approval. LGL may approve the
suspension and may impose conditions of approval.






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	23







 









 








LGL EQUIPMENT SUPPLY TENDER





	 	 	 	As soon as LGL becomes aware that the reason for any suspension no longer exists, LGL
shall direct the Seller to recommence the suspended supply or delivery as soon as
reasonably practicable.
	 
	 	 	 	The Seller shall bear the cost of suspension pursuant to this clause unless the
suspension was necessary due to an act or omission of LGL or if they were not
responsible for the necessity of the protection, safety or court order. If the
suspension was caused by LGL, LGL shall only be liable to the Seller for a maximum of
per day for each day of the suspension up to a maximum aggregate liability of.
	 
	 	30)	 	NON-WAIVER
	 
	 	 	 	Failure of LGL to insist upon strict performance of any of the terms and conditions of
the Purchase Order, or failure or delay to exercise any rights or remedies provided
herein or by law or to properly notify Seller in the event of breach, or the approval,
acceptance of, or payment for, any Merchandise hereunder, shall not release the Seller of
any of the warranties, guarantees or obligations of this Purchase Order and shall not be
deemed a waiver of any right of LGL to insist upon strict performance hereof or of any of
its rights or remedies as to any such Merchandise or Service.
	 
	 	31)	 	NO ASSIGNMENT
	 
	 	 	 	Any assignment, mortgage, charge or other encumbrance of this Purchase Order by the
Seller, or of any rights hereunder or thereof in any manner, in whole or in part, by
operation of law or otherwise, without the prior written consent of LGL, shall be void.
	 
	 	 	 	LGL can assign and novate this Purchase Order without the consent of the Seller.
	 
	 	32)	 	DISPUTES
	 
	 	 	 	In case any dispute of difference shall arise between LGL and the Seller, either during
the performance of the Purchase Order requirements or after termination, abandonment or
breach of the Purchase Order, as to the construction of the Purchase Order or as to any
matter or thing whatsoever arising thereunder or in connection therewith, then the
aggrieved party shall give to the other, notice in writing setting out in full the
detailed particulars of the dispute or difference. Upon receipt or issue of the notice,
LGL shall give written notice to the Seller appointing a date, time and venue for a
conciliation meeting to be held to discuss in detail the dispute or difference and may
appoint such further time as may be necessary for the continuation thereof. The parties
shall not be legally represented at the conciliation meeting but shall present in their
own manner, with the assistance of witnesses and documentary evidence, the details of
their respective cases. If at the conclusion of the conciliation meeting the parties
fail to resolve the dispute or difference, either party may give to the other within
fourteen (14) days, a notice stating that at the expiration of thirty (30) days, it will
proceed to have the dispute or difference referred to a court of competent jurisdiction
and at the expiration thereof, but not before, may so proceed.
	 
	 	33)	 	NOTICES
	 
	 	 	 	Any notice or other communication in relation to this Purchase Order including any
request, demand, consent or approval, to or by a party to this Purchase Order must be in
legible writing and in English and addressed as follows:






	 	•	 	if to LGL addressed to: The MOPU Project Manager, Level 7,
Pacific Place, Cnr of Champion Parade and Musgrave Street, (PO Box 789), Port
Moresby, Papua New Guinea; facsimile +617-3318-9203
	 
	 	•	 	if to the Seller, as set out in the Purchase Order;







			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	24






 









 











LGL EQUIPMENT SUPPLY TENDER





	 	 	 	or a substitute address notified by a party to the other party;
	 
	 	 	 	The notice must be signed by:






	 	•	 	where the sender is the Seller, must be signed by an officer of the Seller;
	 
	 	•	 	where the sender is LGL, it must be signed by the Project Manager;
	 
	 	•	 	in the case of notice by email, the notice must be accompanied by a digital signature;






	 	 	 	The notice will be deemed to be given or made:






	 	•	 	if posted from an address other than in Australia or Papua New
Guinea to an address in Papua New Guinea, 10 Business Days after posting;
	 
	 	•	 	if posted from an address in Australia or Papua New Guinea, 7
Business Days after posting;
	 
	 	•	 	if delivered by hand, on delivery;
	 
	 	•	 	if faxed, on receipt of a transmission report confirming
successful transmission unless the addressee telephones the sender within 24
hours after transmission is received or regarded as received and informs the
sender it is not legible; and
	 
	 	•	 	if sent by email is regarded as given and received when sent to
the sender unless: the sender receives a report of delivery failure or delivery
delay; the sender receives an “Out of Office” reply or similar response; or the
addressee informs the sender that the notice is illegible, incomplete or
corrupted, within 24 hours of the notice being transmitted,






	 	 	 	but if delivery or receipt is on a day which is not a Business Day or is after 5.00 P.M.
at the place of delivery or receipt, it is taken as given at 9:00 a.m. on the
next Business Day; and






	 	•	 	can be relied on by the addressee and the addressee is not liable
to any other person for any consequences of that reliance if the addressee
believes it to be genuine, correct and authorised by the sender.






	 	 	 	In this clause 33 a reference to an addressee includes a reference to an addressee’s
agents or employees.






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	25







 









 





LGL EQUIPMENT SUPPLY TENDER




C) Preparing Orders for Shipment





	1.	 	General
	 
	 	 	The terms of shipment shall be as identified in the Project specification.
	 
	 	 	All Merchandise shall be prepared and packed to withstand transport from the point of origin to
Lihir Island in Papua New Guinea including periods of unprotected storage. The instructions
described herein shall be considered as minimum requirements and if additional measures for the
protection of the goods are needed according to the experience of the Seller, they shall be
provided.
	 
	 	 	Failure to comply with these instructions may result in delays in unloading and issuance of
payment.
	 
	 	 	Costs incurred by LGL as a consequence of insecure or unsuitable packaging will be backcharged
to the Seller.
	 
	 	 	In addition to the requirements detailed herein, further shipping instructions may be issued to
the Seller with the Purchase Order.
	 
	 	 	The Seller shall not show the declared value on shipping documents.






	 	1.1	 	Consignments
	 
	 	 	 	Unless otherwise agreed to in writing by LGL:






	 	•	 	Merchandise for fulfilment of a Purchase Order shall be
prepared for shipment in one single consignment; and
	 
	 	•	 	Merchandise for different Purchase Orders shall not be packed together.






	 	 	 	Actual contents of packages shall be subject to quantity check against the Seller’s
packing documents upon receipt at the project Site. Any discrepancies found at Site
shall be rectified by the Seller at no charge to LGL unless proof of correct supply can
be substantiated.
	 
	 	1.2	 	Merchandise Release
	 
	 	 	 	No Merchandise shall be packed for shipment until all requirements of the approved
Project Inspection and Test Plan have been met and a preliminary copy of the bill
of lading and other shipping documentation has been emailed to LGL.
	 
	 	 	 	Notwithstanding the above, all Merchandise may also be subject to final inspection by
LGL or LGL’s nominated representative immediately prior to packing. Merchandise
identified for final inspection shall not be packed without prior written approval from
LGL’s nominated representative.
	 
	 	1.3	 	Packaging Dimensions and Weight
	 
	 	 	 	Wherever possible, Sellers shall ensure that items are packaged to comply with normal
truck loading dimensions as follows:





	 	 	 
	Maximum Length

	 	12.5 metres
	Maximum Width

	 	2.5 metres
	Maximum Height

	 	2.85 metres
	Maximum Weight

	 	24 tonnes gross







			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	26







 









 








LGL EQUIPMENT SUPPLY TENDER





	 	 	 	If goods exceed any one of these dimensions then the Seller must provide details to
LGL’s nominated Shipping Agent not less than eight calendar weeks prior to packing. In
the case of oversize and/or awkwardly shaped goods, the Seller shall also submit
drawings showing the proposed method of dunnage, supports, centre of gravity, location
of lifting lugs, transport orientation, position of any skids and saddles, recommended
lifting arrangements, etc.
	 
	 	1.4	 	Grouping of Merchandise
	 
	 	 	 	Merchandise shall be grouped to facilitate easy identification and separation of
materials / items as per the following:






	 	•	 	Construction priority items (cast-in items, priority
steelwork, etc) shall be packed separately from other materials on the
Purchase Order and clearly labelled: “PRIORITY ITEMS”.
	 
	 	•	 	Commissioning and start up spares shall be packed
separately to all other Merchandise on the Purchase Order and clearly
labelled: “COMMISSIONING AND START-UP SPARES”.
	 
	 	•	 	As much as practical, palletised or containerised
equipment shall be packed so that equipment with similar equipment numbers
are grouped together.
	 
	 	•	 	Dangerous Goods may be packaged together as long as they are compatible.






	 	1.5	 	Hazardous Materials
	 
	 	 	 	The Seller shall give a minimum of three calendar weeks prior warning to LGL’s nominated
Shipping Agent if any consignment includes goods that fall into the category of
HAZARDOUS as defined in the “Australian Dangerous Goods Code”, or goods that have
inherent transport risks: eg subject to mechanical derangement, subject to magnetic
interference, etc. Prior to shipment, the Seller must advise LGL of any Dangerous Goods
and fax a copy of all required paperwork for the shipment of Dangerous Goods.
	 
	 	 	 	The Seller shall provide suitable containers and/or packaging for the transport of
hazardous goods, and all containers / packaging shall be suitable for transport via any of
road, rail, sea or air. All containers and packaging, and markings on the outside of the
containers and packaging, shall be in accordance with the “Australian Dangerous Goods
Code”.
	 
	 	 	 	All Dangerous Goods must be packaged separately from other merchandise. All packages must
be labelled with the proper hazard label, per procedures identified by the “Australian
Code for the Transport of Dangerous Goods by Road and Rail” Edition in effect at time of
shipment. Purchase Orders intended for shipment by airfreight must also be packaged in
accordance with “IATA Dangerous Goods Regulation” Edition in effect at time of shipment
by Passenger or Cargo aircraft.
	 
	 	 	 	It is the responsibility of the Seller to complete a Hazardous Goods declaration and
supply a Material safety Data Sheet (MSDS) and Emergency Procedure Guide (EPG).
	 
	 	 	 	Any dangerous goods shall also be declared on the Shippers Letter of Instruction (SLI),
and the SLI shall be accompanied with a properly completed Australian Maritime Safety
Authority (AMSA) Multimodal Dangerous Goods Form (MO41). This is a requirement of the
Federal Department of Transportation and if documentation is not adequately completed it
may result in the goods being unable to be transported and associated costs being
backcharged to the Seller.
	 
	 	1.6	 	Fumigation Certificates













			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	27






 









 











LGL EQUIPMENT SUPPLY TENDER





	 	 	 	Where required, a certificate of fumigation is to be supplied in accordance with
Australian and Papua New Guinea Quarantine Inspection Services requirements relative to
the country of supply.






	2.	 	Packaging Documentation






	 	2.1	 	Shippers Letter of Instruction
	 
	 	 	 	A Shippers Letter of Instruction (SLI) or carrier consignment note shall be fully and
comprehensively completed in the format required by LGL’s nominated Shipping Agent, and
forwarded to the Shipping Agent by email prior to delivery pickup. The receiver of the
goods identified on the SLI or consignment note shall be Lihir Gold Limited (PNG).
	 
	 	 	 	Where a consignment contains hazardous goods, they shall be declared on the SLI or
consignment note as required by Section 1.4.
	 
	 	2.2	 	Packing Lists
	 
	 	 	 	All shipments must be accompanied by a packing slip, which must show type of package,
gross weight and dimensions of each package. The packing slip must also describe the
Merchandise, the quantities shipped, whether or not there is a short shipment, LGL’s
Purchase Order number, the equipment number and the date shipped.
	 
	 	 	 	The original invoice / packing list shall be placed inside the package, and a copy of
the same documentation shall be placed inside a sealed waterproof document envelope
securely fixed to the outside of the packaging. Wherever possible, values shall be
identified against each line item on the invoice / packing list.
	 
	 	 	 	Where goods are classified as hazardous, a copy of the relevant MSDS and EPG shall be
included with each copy of the packing documentation.
	 
	 	 	 	When shipment is effected in wooden boxes, the packing slip shall be placed in a
suitable waterproof plastic envelope attached to the outside of the box by means of
heavy duty adhesive tape or other transit durable method of fastening.
	 
	 	 	 	When the Merchandise is shipped loose or on skids, the packing slip, again protected by
a suitable waterproof plastic envelope, shall be fixed at a location not likely to be
subject to the packing slip being torn off in transit.
	 
	 	 	 	In the case of multiple items covered by one packing slip, the case or piece to which
the packing slip is attached shall be clearly identified and all others must have
affixed a label indicating the case or piece number that has the packing slip. Items on
the packing slip must correspond in sequence to the items on the Purchase Order.
	 
	 	2.3	 	Bills of Lading (B.O.L.)
	 
	 	 	 	The applicable Purchase Order number must appear on all B.O.L.






	3.	 	Packaging Standards






	 	3.1	 	General
	 
	 	 	 	Packaging and packing shall be of such design that damage will not occur to the packed
goods during transport and handling from any effects of tilting, swinging, vibrating,
lifting, or stacking compression.
	 
	 	 	 	Where necessary, the packed goods shall be secured within the packaging in such a way
that they can withstand these loads without any damage. Such securing can be effected by






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	28







 









 








LGL EQUIPMENT SUPPLY TENDER





	 	 	 	fixing to skids or a base frame, cushioning between the goods and packaging wall, etc.
Nylok nuts shall be used on all securing bolts.
	 
	 	 	 	The types and extent of packing shall be compatible with the weight and characteristics
of the goods being packed. The use of cardboard cartons as outside protection is not
acceptable except where these are further contained in waterproof packing.
	 
	 	 	 	Electrical components or goods likely to suffer deterioration by moisture penetration or
entrapped water vapour shall be packed in completely weather- and dust-proofed packaging
and further protected by the provision of an absorbent desiccant (i.e. Silica Gel)
within the weatherproof barrier. The desiccant shall be contained in new, dry,
vapour-permeable bags, which shall clearly identify the nature and purpose of the
contents.
	 
	 	 	 	Rotors, electric motors, and rotating elements fitted with anti-friction bearings shall
be protected from internal damage by clearly visible external clamps that prevent
movement during transport and handling.
	 
	 	 	 	Other items of equipment or instrumentation that are free to move, vibrate or chafe
during shipping shall be adequately secured or blocked. Clearly visible warning notices
shall be provided to ensure on-site removal of securing devices and blocking prior to
operation.
	 
	 	 	 	If accessories are removed from any item of equipment or equipment is split into
components, then suitable blank shipping plates must be installed.
	 
	 	 	 	Prepared metal surfaces likely to rust or corrode shall be treated with a suitable
preservative (Shell Ensis SDC or equivalent) or otherwise protected by suitable
packaging. Care should be taken to ensure working surfaces are not impaired by the
application of any preservative.
	 
	 	 	 	All exposed flanges and machined faces shall be protected by plyboard covers with a
minimum thickness of 8 mm and a minimum over-cover of 30 mm. Plugs or cover plates shall
be provided on all inlets and outlets, and wherever else necessary to prevent ingress of
dirt.
	 
	 	 	 	Protective finishes to steelwork, piping, and equipment shall be protected from rubbing
and wearing during transport and handling by provision of suitable blocking and/or
padding (eg carpet).
	 
	 	 	 	Biodegradable packaging and packing shall be utilised wherever possible to facilitate
disposal of waste materials within the limited waste disposal facilities available on
Lihir Island.
	 
	 	3.2	 	Cardboard Cartons
	 
	 	 	 	Cardboard cartons shall be of good quality to withstand transport and handling, with a
net content of manageable weight for lifting by hand. All cartons shall be securely
taped crossways, top and bottom.
	 
	 	 	 	Fragile or sensitive items that cannot be manageably packed or adequately protected in
cardboard cartons must be packed in appropriate wooden crates or cases.
	 
	 	3.3	 	Wooden Crates and Boxes
	 
	 	 	 	Wooden crates and boxes shall be good quality pine timber with hardwood bases and steel
strengthening bands. Bearing timbers at the base of crates shall be spaced no more than
700mm apart.





	 	 	 
	Gross Weight	 	Timber Dimensions / Nominal Steel Strapping Requirements
	To 200kg

	 	Minimum 25mm thickness timber
throughout, 2 x 25mm steel straps
	 
	 	 
	200-400kg

	 	Minimum 25mm thickness timber throughout, at least 2 x 25mm
steel straps (or more if commensurate with weight) to body of crate
	 
	 	 
	400-600kg

	 	100x50mm framing, minimum 25mm thickness timber elsewhere,
at least 2 x 25mm steel straps (or more if commensurate with
weight) to body of crate, 2 x 25mm steel straps to corners.






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	29







 









 





LGL EQUIPMENT SUPPLY TENDER





	 	 	 	For gross weights greater than 600kg, crates shall be extreme duty wooden pallet crates
commensurate with the weight of the contents and the safe handling and protection of
the cargo.
	 
	 	3.4	 	Wooden Cases
	 
	 	 	 	Closed wooden cases (as opposed to open crates) shall be used for sea freight of all
sensitive equipment. They shall be of strong, solid, close jointed, export quality and
designed in accordance with AS2400.7-1990.
	 
	 	 	 	Cases shall be constructed from good quality pine timber with hardwood bases. Sheathing
boards shall be of a minimum thickness of I9mm. Plywood material must be glued marine
grade plywood. All joints and top screw/nail holes shall be sealed with Silicon Sealant
	 
	 	 	 	Skid-type bases shall have runners with a minimum cross sectional dimension not less
than the following:





	 	 	 
	 	 	Minimum Size of
	Mass of Shipment	 	Timber
	(kg)	 	(mm
x mm)
	Up to 1,000

	 	50 x 100
	1,000-3,000

	 	100x100
	3,000-7,500

	 	100x125
	7,500-12,500

	 	125x125
	>12,500

	 	As required







	 	 	 	The contents of each case shall be completely weather and dust-proofed by the use of
non-permeable film, of suitable strength such as “Polythene” sheet, tar paper or
approved equivalent, to form a sealed moisture barrier.
	 
	 	3.5	 	Steel Drums
	 
	 	 	 	Steel drums shall be of export quality and shall be non-returnable.
	 
	 	3.6	 	Bundling of Loose Items
	 
	 	 	 	Items such as steel pipe, steel sections, and timber shall be segregated by length and
size and bundled in packs not exceeding 2,000 kg in weight. Each pack shall be of one
product type and shall be strapped with 25mm wide heavy-duty steel strapping spaced at
a maximum of 1500mm intervals. A minimum of three lengths of timber with a minimum
cross section of 100mm x 50mm shall be incorporated with the bundle to form an integral
base and facilitate handling by forklift.
	 
	 	3.7	 	Internal Packing
	 
	 	 	 	All internal packing must be biodegradable (i.e. cardboard or paper rather than
polystyrene or bubble wrap) to facilitate disposal on Lihir island. Any
non-biodegradable packing may be returned to the Seller, with all associated freight
costs back-charged against the Seller’s account.





4. Marking and Tagging of Merchandise





	 	4.1	 	General
	 
	 	 	 	All cases and fabricated pieces shall have the following marking stencilled on with
black paint using letters no smaller than five (5) cm high (in case of small electric
motors,






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	30







 









 





LGL EQUIPMENT SUPPLY TENDER





	 	 	 	reducers or pumps shipped open on skids, this last requirement may be relaxed):




LIHIR GOLD LTD

MOPU PROJECT

LIHIR ISLAND,

PAPUA NEW GUINEA

PURCHASE ORDER No. :                     

PACKAGE No. :                      OF
                    

GROSS WEIGHT:                     kg

DIMENSIONS:                     L
                    W
                    H (cms)





	 	 	 	When more than one package is being shipped under the same Purchase Order number, each
package shall be separately numbered and show the total number being consigned, e.g.
PACKAGE 1 of 5, PACKAGE 2 of 5, etc.
	 
	 	 	 	Shipping marks shall be written in capital letters with letter height of not less than
20 mm and shall be applied using either paint or indelible ink. Wherever possible,
marks shall be displayed at three different points of each shipping package.
	 
	 	 	 	All uncrated items shall be tagged as per the above shipping marks. Tagging shall be
done by means of an aluminium label (minimum size 7.5 cm x 5 cm) punched with
information and attached with corrosion resistant wire. Plastic waterproof laminated
tagging attached with corrosion resistant wire or locked plastic bands will be accepted
as an alternative. Note: The use of a “tag” may not be practical for all items, in
which case an alternate method of identification is by stencilling or painting
(fabricated items) and if this is not practical or good practice (shafts, pulleys,
machined parts, etc) then the identification shall be by label with sunlight resistant
indelible waterproof black ink letters. The label shall be affixed with heavy-duty
adhesive tape.
	 
	 	 	 	When Merchandise is being shipped disassembled, all parts must be tagged with EQUIPMENT
NUMBER                     . In addition, each part must be numbered, i.e. Item No.
                     of
                     (total number of
parts for that assembly). Each part must be identified with the ITEM NUMBER, which is
detailed on the Seller’s Certified Drawing.






	5.	 	Packing & Shipping






	 	5.1	 	All Suppliers
	 
	 	 	 	The Seller must:






	 	•	 	Place the Merchandise at the disposal of LGL at the time
as provided in the Purchase Order, at the point of delivery named or which
is usual for the delivery of such merchandise and for their loading on the
conveyance to be provided by LGL.
	 
	 	•	 	Provide suitable packaging of the Merchandise so that
all items will arrive at the destination in an undamaged condition. And
without restricting the generality of the foregoing, the Seller shall pay
particular attention to Merchandise susceptible to damage from moisture when
stored for a period of time in a tropical climate. All crates must be skid
mounted, and all Merchandise weighing more than five (5) tonnes must have
lifting points and the centre of gravity clearly marked.
	 
	 	•	 	Give LGL reasonable notice as to when the Merchandise will be at its disposal.
	 
	 	•	 	Markings specified on the Purchase Order shall be
stencilled with waterproof ink on at least two sides of the package. The
case number shall identify the






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	31







 









 





LGL EQUIPMENT SUPPLY TENDER





	 	 	 	individual package and also indicate total number of packages in the shipment
such as package 1 of 7, or 3 of 5, etc.
	 
	 	•	 	No advertising or mark that indicates contents may appear on the package.






	 	5.2	 	Overseas Suppliers Only
	 
	 	 	 	In addition to the above, the Seller must:






	 	•	 	Provide suitable packaging for Ocean Freight so that all
items will arrive at the destination in an undamaged condition.
	 
	 	•	 	Render LGL every assistance in obtaining any documents
which are issued in the country of delivery and/or origin which LGL may
require for the purpose of exportation and/or importation.






	6.	 	Spare Parts
	 
	 	 	All spare parts, in addition to the requirements for marking and tagging, shall be packed
separately and clearly identified as spares.
	 
	 	 	Spare parts shall be packed in separate boxes/crates or containers and clearly marked with an
additional 75 mm white strip painted around the entire circumference of all boxes/crates or
containers. Spare parts must not be packed with the original equipment. Failure to comply will
result in delays in clearing the shipment ultimately affecting prompt payment of invoice.
	 
	7.	 	Palletising of Goods
	 
	 	 	Pallets shall be of export quality and non-returnable. Pallet dimensions shall be no greater
than 1150mm x 1150mm in plan area, and they shall be of suitable construction to withstand
2000kg horizontal breaking force.
	 
	 	 	Cardboard cartons packed on pallets must be shrink-wrapped with a 6mm thick sheet of plywood
placed on top of the cartons prior to shrink-wrapping.
	 
	 	 	Tins and plastic pails packed on pallets shall have a 6mm thick sheet of plywood placed between
each layer, a 6mm thick top sheet of plywood, and be shrink-wrapped. Palletised packing shall
be limited to the following:






	 	 	 	For 4 litre tins or pails: no more than 5 layers.
	 
	 	 	 	For 10 litre tins or pails: no more than 3 layers.
	 
	 	 	 	For 20 litre tins or pails: no more than 3 layers.
	 
	 	 	 	For tins or pails of greater than 20 litres capacity: single layer only.






	 	 	Steel drums packed on pallets are to be strapped together with steel strapping.
	 
	8.	 	Special Requirements For Air freight
	 
	 	 	Goods identified on the Purchase Order as requiring airfreight shall be packed in heavy-duty
export quality ‘triwall’ cardboard cartons with a gross weight that must not exceed 30kg.
Wherever possible, the cartons should not be larger than 300mm x 300mm x 300mm, and under no
circumstances shall they be larger than 750mm x 750mm x 750mm. If either the weight or size
exceeds the above limits, the Seller shall contact LGL for instructions.
	 
	 	 	In addition to the markings identified in Section 4, the words “AIRFREIGHT ORDER” must be
clearly marked in bold print next to the order number.
	 
	 	 	Airfreight consignments shall meet all other requirements for shipment, packaging and
documentation identified elsewhere in this specification.






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	32







 









 





LGL EQUIPMENT SUPPLY TENDER





	9.	 	Sub-Sellers
	 
	 	 	Sub-Sellers are required to conform to all requirements and the Purchase Order Number assigned
by LGL is the number to be used by sub-suppliers where reference is made to a Purchase Order.
	 
	10.	 	Additional Information
	 
	 	 	Any assistance or additional information required concerning marking and tagging of equipment
may be requested by e-mail: mopu@lglgold.com.






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	33







 









 





LGL EQUIPMENT SUPPLY TENDER




LGL




Million ounce Plant Upgrade (MOPU)



EQUIPMENT SUPPLY TENDER



Section I Part C




Technical On-site Personnel Terms (Separate Purchase Order)



INDEX




	 	 	 	 	 
	1. Service Order Terms and Conditions
	 	 	35	 
	2. Site
	 	 	35	 
	3. Employee Replacement
	 	 	35	 
	4. Transport
	 	 	35	 
	5. Accommodation and Messing
	 	 	35	 
	6. On-Site Facilities
	 	 	35	 
	7. First Aid
	 	 	35	 
	8. Reimbursable Sum
	 	 	36	 
	9. Per Diem Rate (Working Time)
	 	 	36	 
	10. Daywork Sheets
	 	 	36	 
	11. Field Breaks
	 	 	36	 
	12. Back Charges
	 	 	37	 






			
	 	 	 
	Section I — Part C Technical On-Site Personnel Terms
	 	34







 









 





LGL EQUIPMENT SUPPLY TENDER





	1.	 	Service Order Terms and Conditions






	 	1.1	 	The Seller shall provide technical on-Site personnel
(erection supervision, specialists, or start-up personnel including any
Sub-Contractors) in accordance with LGL’s Service Order terms
and conditions (which are appended hereto) to assist with the
installation, inspection, testing, and commissioning of the
Merchandise purchased from the Seller under a
Merchandise Supply Purchase Order. The following terms and
conditions are in addition to those set out in LGL’s Service
Order terms and conditions.






	2.	 	Site






	 	2.1	 	The Site is defined as Lihir Gold Limited’s operation on Lihir
Island, New Ireland Province, Papua New Guinea.






	3.	 	Employee Replacement






	 	3.1	 	Seller must replace at its own expense unsuitable
technical on-Site personnel upon reasonable and duly
substantiated written request of LGL, including those dismissed from the Site
for cause or who terminate before the completion of the
assignment without the  prior approval of the Seller and LGL.






	4.	 	Transport






	 	4.1	 	Seller’s technical on-Site personnel must obtain approval from the
designated LGL representative, prior to travelling to
Site. A travel request form and travel itinerary is
required for such approval.






	 	4.2	 	Seller is responsible for all transportation of technical
on-Site personnel to and from their home base to Cairns,
Australia. LGL will arrange transportation from Cairns to the
Site.






	 	4.3	 	If Seller’s technical on-Site personnel arrive at the Site
during working hours, they are expected to work that day.






	5.	 	Accommodation and Messing






	 	5.1	 	LGL will supply accommodation and meals free of
charge for Seller’s technical on-Site personnel while they are
on Site.






	6.	 	On-Site Facilities






	 	6.1	 	LGL will provide necessary Site facilities including
temporary offices, site ablutions, and limited telephone
access.






	 	6.2	 	Seller must provide, at its cost, any necessary tools or
special equipment required by the technical on-Site personnel.






	7.	 	First Aid






	 	7.1	 	A First Aid Centre is located on the Site
and will be made available to Seller’s technical on-
Site personnel who, while engaged in the execution of the
Works, become ill or sustain injury.





Section I – Part C Technical On-Site Personnel Terms 


35


 








 





LGL EQUIPMENT SUPPLY TENDER





	 	7.2	 	Should a medical situation require an evacuation from Site, LGL will make the
appropriate arrangements for the evacuation on behalf of Seller to Cairns, Australia.
The costs of any such evacuation will be the responsibility of Seller.






	8.	 	Reimbursable Sum






	 	8.1	 	LGL will pay the Seller the Reimbursable Sum detailed in the Purchase Order at the
beginning and at the end of the Seller’s on-Site technical personnel assignment at the
Site. The Reimbursable Sum includes:






	9.	 	Per Diem Rate (Working Time)






	 	9.1	 	The quoted Per Diem Rate of hire shall only be applicable to days actually worked on
the Site (and pro-rata hours where the technical on-Site personnel are not available for
work).
	 
	 	9.2	 	The daily rate is inclusive of 10 hours per day, 7 days per week including Saturdays,
Sundays and Public Holidays. Hours worked in excess of 10 hours per day shall be prorated
at the Per Diem Rate. Sick time hours will be the responsibility of Seller.
	 
	 	9.3	 	The day of arrival and departure are deemed included in the Reimbursable Sum, per
above.






	10.	 	Daywork Sheets






	 	10.1	 	LGL will pay the daily rate for the Seller’s technical on-Site personnel at the daily
rates detailed in the Purchase Order for days actually worked at site, or on a pro-rata
basis if the on-Site personnel are not available for work for part or all of a day or work
more than 10 hours per day at LGL’s request.
	 
	 	10.2	 	It is the responsibility of Seller’s technical on-Site personnel to obtain an LGL
Daywork sheet on arrival at the Site.
	 
	 	10.3	 	Daywork sheets must be completed by the Seller’s technical on-Site personnel daily for
days (or hours) worked in accordance with clause 10.1 and be signed by the designated LGL
representative. The original signed Daywork sheets must accompany the Seller’s invoice to
enable LGL to make payment.






	11.	 	Field Breaks






	 	11.1	 	Seller will be expected to rotate technical on-Site personnel on a work roster, if
required. The standard LGL roster is 28 days on Site, followed by 14 days field break. No
guarantee for duration on Site of technical on-Site personnel is given. Pro-rata
entitlements do not apply and work assignments of less than 28 days are not subject to
field break provision.
	 
	 	11.2	 	Field break flights will be provided by LGL in economy/excursion class. No payment will be






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	36







 









 








LGL EQUIPMENT SUPPLY TENDER





	 	 	 	made for travelling time for field breaks.
	 
	 	11.3	 	If Seller’s technical on-Site personnel who are entitled to field breaks, elect to take
their field break in a location other than the point of origin, LGL will reimburse, upon
presentation and approval of an expense report supported by original receipts for travel
and hotel accommodation, up to the value of an economy/excursion airfare to and from their
place of origin.






	12.	 	Back Charges






	 	12.1	 	Seller must give its technical on-Site personnel the authority to accept backcharges
for remedial works carried out to the Merchandise supplied under a separate Merchandise
Supply Purchase Order.






			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	37







 









 





LGL EQUIPMENT SUPPLY TENDER




     Appendix A Service Order Terms and Conditions



1. General



1.1. The Contractor shall supply the Services starting on the Commencement Date in accordance with
these general conditions and any written or verbal directions given by the Principal from time to
time.



1.2. By supplying Services to the Principal in response to a Purchase Order, the Contractor agrees
to be bound by these general conditions.



1.3. The Principal shall pay the Contractor the Purchase Order Price for Services delivered by the
Contractor in accordance with these general conditions.




2. Contractor’s Obligations



2.1. The Contractor must perform the Services:





(a) using a high degree of skill, care and diligence and in a good workmanlike manner in
conformity with industry standards and practices current from time to time;




(b) in accordance with the Principal’s requirements and schedule for completing the Services
provided by the Principal;




(c) in compliance with plant operating schedules in order that the Contractor must at all times
seek to minimise disruption to the Principal’s operations;




(d) in accordance with all acts, laws, regulations, rules, orders, by-laws, orders, licences,
codes, permits and other statutory instruments that apply to the performance of the Services at
the Location and with the requirements, instructions or directions of any authorised person
exercising a right pursuant to the mining legislation, conditions of the mining tenements or
permits applicable at the Location;




(e) in accordance with all relevant guidelines or policies of the Principal as notified from time
to time, including those on workplace health and safety, camp rules, environment and community
relations, training and localisation and security (copies of which are available upon request;




(f) using suitably qualified, experienced, appropriately licensed and authorised personnel;




(g) in accordance with the Specification; and




(h) by the Due Date.


2.2. If the Principal (or someone authorised on behalf of the Principal) reasonably requests, the
Contractor must demonstrate compliance with clause 2.1. This includes providing evidence of
measures taken to achieve compliance.



2.3. The Contractor must supply such Documents as are reasonably required by the Principal. The
Principal’s review, approval of, or comment on, any part of the Services, including any Documents,
does not affect the Contractor’s obligations or absolve the Contractor from its sole responsibility
for performance of the Services in accordance with this agreement.



2.4. The Contractor shall be deemed to have examined all information relevant to the risks,
contingencies and relevant
physical conditions in relation to the Services. The Principal accepts no responsibility for
latent conditions.




3. Equipment



3.1. Unless previously agreed in writing with the Principal, the Contractor must supply all
equipment necessary to perform the Services. Any vehicles or machinery supplied by the Contractor
must be properly registered with the appropriate government authority, roadworthy and regularly
inspected for mechanical safety.



3.2. Where the Services involve the supply and installation of equipment, any such equipment
becomes the property of the Principal upon the earlier of incorporation into any of the Principal’s
existing plant or equipment or payment of the Contractor’s invoice that itemises the equipment in
question.




4. Representatives



4.1. Each party shall appoint a representative and may replace the representative by giving written
notice to the other party. The parties acknowledge that the representative of each party is
authorised to act on that party’s behalf.




5. Defects



5.1. The Contractor shall re-perform at its cost any part of the Services (or re-supply any
equipment) that is not in accordance with the requirements of these general conditions or the
Specification if directed to do so by the Principal within a period of 6 months following
completion of the Services.




6. Variations



6.1. The Principal may at any time, issue a direction to the Contractor which:





(a) increases, decreases or deletes any part of the Services;




(b) changes the character, quality or quantity of any part of the
Services; or




(c) requires the Contractor to supply additional Services.


6.2. If the Principal issues a direction under 6.1, the Contractor must carry out the Services as
varied by such direction.



6.3. If the Contractor becomes aware that a service is required which is additional to the
Services, or that there is a need to vary the Services, the Contractor must immediately notify the
Principal in writing giving details of the nature and extent of the
variation.



6.4. The Principal and the Contractor must agree in writing the scope and extent of the variation
to the Services plus any adjustment to the Purchase Order Price before the Contractor carries out
the varied Services.



6.5. if the parties are unable to agree the adjustment to the Purchase Order Price, a variation
directed or approved by the Principal must be valued by the Principal’s Representative:





(a) in accordance with the rates in the Service Order Instructions Page to the extent the
Principal’s Representative determines it is reasonable to use them; or




(b) if clause 6.5.1 does not apply, using reasonable rates or prices.




			
	 	 	 
	Section I — Part C Technical On-Site Personnel Terms
	 	38







 









 





LGL EQUIPMENT SUPPLY TENDER




7. Payments



7.1. The Contractor shall render invoices to the Principal’s Representative at regular monthly
intervals for work completed from the date of the preceding payment claim (except in respect of the
first payment claim which is to be for work completed from the commencement of the Services) and in
the manner and format specified by the Principal’s Representative.



7.2. The Principal shall pay:





(a) the Purchase Order Price; and




(b) the Reimbursable Items.


7.3. The Purchase Order Price will be inclusive of all costs associated with the supply of the
Services including Taxes (but excluding GST), sick leave, annual leave, superannuation, long
service leave, consumables, fuel, tools and all other operating expenses.



7.4. The Principal may deduct from payments to be made to the Contractor any debt or other moneys
due from the Contractor to the Principal, or the amount of any claim which the Principal may make
against the Contractor.



7.5. The Principal may reject all or any portion of an invoice (provided it acts reasonably) and
the Contractor may refer that dispute for resolution under clause 15. While the dispute is being
resolved, the Principal is not obliged to pay the disputed amount and the Contractor is not
entitled to suspend performance of its obligations under this
agreement.



7.6. Subject to clauses 7.4,7.5 and the receipt of a correct tax invoice (including but not limited
to showing quantities of Services provided, acceptance of those services by the Principal,
correctly calculated prices and accurate payee details), by the end of the month following the
month of receipt of an invoice, the Principal shall pay the Contractor, provided that the sum of
all invoices is not to exceed the Purchase Order Price. Payment will be made in the currency shown
on the Purchase Order.



7.7. Unless the Purchase Order specifically provides otherwise, the Purchase Order Price shall be
fixed and not subject to any adjustment for fluctuations in exchange rates or variations in costs
(direct or indirect) of labour, materials, equipment or freight.



7.8. Subject to clause 7.9, where the Contractor informs the Principal that payments to be made by
the Principal to the Contractor under these general conditions are not liable to taxation in Papua
New Guinea and requests that no foreign contractors withholding tax be deducted from payments under
this agreement, if the Principal complies with that request, Contractor indemnifies and keeps
indemnified the Principal for any costs and any liability to the PNG taxation authorities.



7.9. The Principal is not obliged to comply with a request by the Contractor not to deduct any
withholding amounts unless it has been provided with sufficient evidence (in its absolute
discretion) that such with hoidings are not in fact required based on written evidence from the PNG
government.




8. Regular meetings



8.1. Each week, or as otherwise directed by the Principal’s Representative, the Principal’s
Representative and Contractor’s Representative will meet (at a location, time and date to be
advised by the Principal’s Representative) to review the progress of the Services.




9. Training and Localisation



9.1. The Principal is committed to a policy which maximises the
employment of qualified Papua New Guinea citizens and promotes the transfer of skills through
training.



9.2. The Contractor shall comply with the Principal’s training and localisation policy by using
local Lihirian labour whenever possible and economically justified.



9.3. The Principal reserves the right to audit and monitor the Contractor at any time for
compliance with this clause 9.




10. Intellectual Property



10.1. The Contractor hereby assigns the Intellectual Property Rights conceived or produced by the
Contractor during performance of or in relation to the Services to the Principal.




11. Insurance



11.1. The Contractor must maintain the following insurance coverage:





(a) Public Liability Insurance covering all legal liability to pay damages or compensation arising
out of any injury to or death of any person or any loss of or damage to any property (including,
but not limited to, property of the Principal) for an amount of not less than in respect of any
one occurrence and in the aggregate;




(b) Workers’ Compensation Insurance which shall comply with the laws for the time being in force
in Papua New Guinea and any other place outside Papua New Guinea where the Contractor forms
contracts with its employees, contractors and agents engaged in the provision of the Services.
Such insurance shall indemnify and keep indemnified the Principal as principal in respect of any
claim made under any relevant workers or accident compensation legislation or at common law in
Papua New Guinea and will include where non Papua New Guinea domiciled employees, contractors and
agents are engaged in the provision of the Services in Papua New Guinea an additional WETHA Policy
Extension;




(c) Insurance which is compulsory under the laws for the time being in force in Papua New Guinea
governing the use of motor vehicles; and




(d) Third Party Property Damage insurance covering all mechanicallypropelled vehicles used in
connection with the Services with a limit of liability for damage to third parties of not less
than in respect of any one accident or series of accidents arising out of one event;


11.2. Insurances must be with a reputable insurer and be acceptable to the Principal (acting
reasonably).



11.3. The
interests of the Principal must be noted on all policies, where practicable.



11.4. Prior to the commencement of the Services, and at each anniversary of the commencement, the
Contractor must provide to the Principal certificates of currency for the insurances listed in
clause 11.1.



11.5. All insurances must be maintained in full force and effect for the duration of the provision
of the Services and for a 6 month period following completion of the Services.



11.6. The effecting of insurance as required under this clause shall not in any way limit the
obligations or responsibilities of the Contractor.




12. Indemnity





			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	39







 









 





LGL EQUIPMENT SUPPLY TENDER



12.1. The Contractor shall indemnify the Principal against any loss or damage and against
all claims, demands, proceedings, costs, charges and expenses whatsoever, arising out of:





(a) any claim made by a third party against the Principal or Contractor; and




(b) loss of or damage to any property (including property of the principal) or injury to or death
of any person, arising out of or in connection with the Services, except to the extent that such
loss or damage was caused or contributed to by the acts or omissions of the Principal.



13. Taxation



13.1. Liability For Tax



13.1.1. The Contractor shall reimburse the Principal for the amount of the Principal’s liability
for any Tax (excluding Income Tax) levied in respect of any supply made by the Contractor under
these general conditions.



13.1.2. Any consideration to be paid or provided for a supply made under or in connection with
these general conditions is expressed inclusive of all Tax, other than value added tax/goods and
services tax referred to in clause 13.2 (hereafter referred to as “GST”).



13.1.3. Should the Principal be required to withhold any amounts on account of any Tax (excluding
Income Tax), the corresponding withheld amount will be taken as a reduction in the consideration to
be paid or provided.



13.2. Value Added Tax/Goods and Services Tax



13.2.1. Words or expressions used in this clause which are defined in the A New Tax System (Goods
and Services Tax) Act 1999 (Cth) (“GST Law”) or the Goods and Services Tax Act 2003 (PNG) (“PNG GST
Act”) and related imposition Acts have the same meaning in this clause, as applicable.



13.2.2. “Adjustment Note” means an adjustment note as that term is defined in the GST Law or a
credit or debit note as those terms are defined in the PNG GST Act, as applicable;



13.2.3. “Input Tax Credit” means an input tax credit as that term is defined in the GST Law or a
credit for input tax as that term is defined in the PNG GST Act, as applicable and a reference to
an Input Tax Credit entitlement of a Party includes, as applicable:





(a) an input tax credit for an acquisition made by that Party but to which another member of the
same GST Group is entitled; or




(b) a credit for input tax for a supply which is made to that Party but which is deemed by the PNG
GST Act to be made to the representative member of a group of companies.


13.2.4. Any consideration to be paid or provided for a supply made under or in connection with
these general conditions, unless specifically described as “GST inclusive”, does not include an
amount on account of GST (“GST exclusive consideration”).



13.2.5. Any consideration to be paid or provided for a supply made under or in connection with the
Agreement will be made on the basis that the supply is Zero-Rated, unless the PNG GST Act requires
that the supply be made on a basis taxable at some other rate in which case unless specifically
described in the Agreement as “GST inclusive”, does not include an amount on account of GST.



13.2.6. Despite any other provision, if a party (“Supplier”) makes a supply under or in connection
with these general conditions on which GST is imposed at any other rate than zero percent (not
being a supply the consideration for which is specifically described as “GST inclusive”):





(a) The consideration payable or to be provided for that supply is increased by, and the recipient
of the supply (“Recipient”) must also pay to the Supplier, an amount equal to the GST payable by
the Supplier on that supply;




(b) The amount by which the GST exclusive consideration is increased must be paid to the Supplier
by the Recipient at the same time as the GST exclusive consideration is payable or to be provided;
and




(c) Notwithstanding any other provision, the Recipient is not required to pay any amount unless it
has received a valid tax invoice (or valid adjustment note) for that taxable supply.


13.2.7. Notwithstanding the above provisions, the Principal is only required to gross up a payment
if and to the extent that the Principal is entitled to claim a corresponding credit, refund or
rebate in respect of the grossed up amount.



13.2.8. No GST under the PNG GST Act on GST taxed inputs is claimable against the Principal on any
Reimbursable Items or otherwise pursuant to any provision of this agreement.



13.3. If a payment to a party under these general conditions is a reimbursement or indemnification,
calculated by reference to a loss, cost or expense incurred by that party, then the payment must be
reduced by the amount of any input tax credit to which that party is entitled for that loss, cost
or expense. That party is assumed to be entitled to a full input tax credit unless it proves,
before the date on which the payment must be made, that its entitlement is otherwise.



13.4. If, at any time, an adjustment event arises in respect of any supply made by a party under
these general conditions, a corresponding adjustment must be made between the parties. Payments to
give effect to the adjustment must be made between the parties and the Supplier must issue a valid
adjustment note in relation to the adjustment event.



13.5. This clause does not merge on completion or termination.




14. Termination



14.1. If the Contractor fails to provide any part of the Services in accordance with the
requirements of this agreement or in the opinion of the Principal, the Services are of an
unsatisfactory quality, then in addition to any other rights and remedies which may be available to
the Principal under these general conditions, the Principal may, in its discretion by notice in
writing, direct the Contractor to remedy the deficiency and defect. In default of compliance with
any notice given, the Principal may remedy the deficiency or defect and recover from the Contractor
all costs, loss and damages incurred as a result of the Contractor’s non compliance.



14.2. If
at any time:





(a) the Contractor fails to carry out the Services with due diligence and in a competent manner to
the reasonable satisfaction of the Principal; or




(b) the Contractor otherwise breaches a term of this agreement; or




(c) the Contractor refuses or fails to carry out any instruction or direction lawfully given by
the Principal; or




			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	40







 









 





LGL EQUIPMENT SUPPLY TENDER





(d) the standard of the Contractor’s equipment or materials, or activities of any personnel
are considered by the Principal to be detrimental to the performance of the Services, or hazardous
to the Contractor’s or Principal’s employees or reputation; or




then the Principal may give the Contractor notice in writing specifying the default and (where the
default is capable of being remedied) requiring the Contractor to remedy the same at the
Contractor’s expense within a reasonable period of time, being no less than 5 Business Days and no
more than 20 Business Days (“a Default Notice”).


14.3. If, following the expiration of the time period to remedy stated in a Default Notice, the
Contractor fails to remedy the default, then the Principal (without prejudice to any other rights
that it may have under these general conditions or otherwise) may exercise all or any of the
following powers:





(a) suspend payment until the default has been remedied;




(b) remedy the deficiency or defect and recover from the Contractor all costs, loss and damages
incurred as a result of the Contractor’s non compliance; or




(c) terminate this agreement.


14.4. The provision of the Services may be terminated with immediate effect by written notice if,
the Contractor suffers an Insolvency Event or in the opinion of the Principal:





(a) the Contractor fails to comply with any safety obligation which is of a significant nature to
justify termination;




(b) the Contractor causes or contributes to serious environmental harm;




(c) the Contractor has failed to comply with any legislative obligation that is fundamental to the
performance of the Services; or




(d) the Contractor commits a serious or persistent breach of any of the terms of these general
conditions which is incapable of being remedied to the reasonable
satisfaction of the Principal.


14.5. Termination for Convenience



14.5.1. The provision of the Services may be terminated upon the Principal giving 21 days written
notice to the Contractor that it no longer requires the Contractor’s services.



14.5.2. Upon providing this notice, the Contractor shall be entitled to payment for all Services
provided up to and including the date of termination subject to the requirement that Services
provided following receipt of a notice in clause 14.5.1 must be approved by the Principal in
writing.



14.6. Unless otherwise agreed, the Contractor shall not be entitled to any other compensation for
termination in accordance with clause 14.5, including for any loss or profits, loss of opportunity,
loss of business or anticipated earnings.



14.7. In the event of termination for any reason, the Contractor shall:





(a) deliver to the Principal all data, specifications, information, drawings, reports, accounts
and all other documents and materials prepared by the Contractor or its subcontractors in
connection with the Services as at the date of the Principal’s notice and all approvals, consents,
authorisations and the like obtained from all relevant authorities;




(b) if required by the Principal, novate to the Principal any
subcontracts or other agreements in relation to the Services;




(c) remove any of its materials and other things on or in the vicinity of the Location or the
Principal’s premises as directed by the Principal; and




(d) ensure the Location is left in a safe, clean and tidy condition.



15. Dispute Resolution



15.1. Either party may provide written notice to the other of any dispute arising in relation to
the Services or these general conditions. This notice must contain particulars of the alleged
dispute and be in writing.



15.2. Within 14 days of receiving a notification of dispute under clause 15.1, representatives of
the parties shall meet together and use their reasonable endeavours to settle the dispute.



15.3. If after a period of 28 days after the notice under clause 15.1 was delivered, the
representatives have been unable to resolve the dispute, the dispute will be referred to a senior
manager of each party who shall use their reasonable endeavours to settle the dispute. If the
dispute is not resolved by senior managers within 42 days after the notice under clause 15.1 was
delivered, then either party may issue proceedings to have the
dispute determined.



15.4. Despite the existence of a dispute, the parties must continue to perform their respective
obligations under these general conditions.



15.5. No
party may commence proceedings in court in relation to a dispute unless:





(a) a notice has been delivered in relation to that dispute under
clause 15.1; and




(b) the party commencing proceedings has complied with its obligations under clauses 15.2 and 15.3
(to the extent reasonably possible).




(c) or the only relief sought is urgent injunctive or urgent declaratory relief.



16. Force Majeure



16.1. Where either party’s ability to carry out its obligations under the Purchase Order (not
including payment obligations) is prevented, impeded, restricted or delayed by any cause outside
its reasonable control, then the party whose ability is so impeded, restricted or affected shall
have the right, by giving written notice to the other party, to suspend performance of its
obligations until such time that the party giving the notice is able to continue the performance of
Its obligations under this agreement.




17. Confidentiality



17.1. The Contractor shall keep secret and confidential and shall not disclose to any third party
without the prior consent of the Principal any information, data, specifications, drawings,
reports, accounts or other documents and things supplied by the Principal or made available by the
Principal or brought into existence by the Contractor in supplying the Services and shall take or
cause to be taken, such reasonable precautions as necessary to maintain secrecy and confidentiality
and prevent disclosure.




18. No Assignment or Subcontracting




			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	41







 









 





LGL EQUIPMENT SUPPLY TENDER



18.1. The Contractor shall not assign this agreement, in whole or in part, without the prior
written consent of the Principal.



18.2. No part of the Services may be subcontracted out without the Principal’s prior written
consent.




19. General



19.1. Relationship



Nothing expressed or implied in this agreement and no act by a party may be treated as creating an
employer and employee relationship, a partnership, a joint venture, the relationship of principal
and agent or a fiduciary relationship between the parties. The Contractor shall not bind or commit
or purport to bind or commit the Principal in any way or pledge the credit of the Principal for any
purpose.



19.2. Waiver of Rights



Failure by the Principal to insist upon strict performance of any term or condition hereof shall
not be deemed to be a waiver of any of the Principal’s rights or remedies hereunder nor of any
rights arising out of any subsequent breach by or default of the Contractor.



19.3. Governing Law



The Purchase Order is subject to and to be construed in accordance with the laws for the time being
in force in Papua New Guinea. Each party irrevocably submits to the non exclusive jurisdiction of
courts exercising jurisdiction in Papua New Guinea and courts of appeal from them in respect of any
proceedings arising out of or in connection with this agreement.



19.4. Entire agreement



This agreement states all the express terms of this agreement between the parties in respect of its
subject matter. It supersedes all prior discussions and negotiations, in respect of its subject
matter.



19.5. Order of Precedence



The documents listed below together form the agreement between the Principal and the
Contractor:





(a) the Service Order Instruction Page (if any);




(b) the Purchase Order;




(c) any Specification(s); and




(d) these general conditions. If there is any ambiguity, discrepancy or inconsistency between the
documents comprising the agreement, the documents shall rank in the order of precedence listed
above.



20. Notices



20.1. Any notice, request or other communication under this Purchase Order (“Notice”) must be in
writing and addressed to the other party at the address shown in the Service Order Instructions
Page.



20.2. Each Notice may be delivered personally or by facsimile transmission or pre-paid mail and
shall be treated as having been duly received:





(a) when delivered (in the case of its being personally delivered);




(b) on the day of the facsimile transmission if a Business Day, otherwise on the next following
Business Day (in the case of its being transmitted by facsimile to the facsimile number of the
recipient and a correct and complete transmission report for that transmission being received by
the sender); and




(c) on the third Business Day after posting (in the case of its
being sent by pre-paid mail).



21. Definitions and Interpretation



21.1. In the Purchase Order:





(a) The
Principal is Lihir Gold Limited (a company incorporated in PNG, ARBN 069 803 998).




(b) The
Contractor is the organisation or person providing the Services;




(c) “Business Day” means a day on which banks are open for business in Port Moresby excluding a
Saturday, Sunday or public holiday in that city;




(d) “Claim” means any claim, action, suit, demand, proceeding, notice, litigation, investigation
or judgement whether based in contract, tort, under statute or otherwise;




(e) “Commencement Date” means the date for commencement of the Services as specified in the
Purchase Order;




(f) “Due Date” means the date for completion of the Services specified in a Purchase Order;




(g) “Documents” means any document, item or material to be provided by the Contractor including
any drawings, manuals and documents required to effect customs clearance and any other documents
which the Principal reasonably requires;




(h) “including” (and any variation) is to be read as if followed by “(without limitation)”;




(i) “Income Tax” means any tax of general application imposed on net income;




(j) “Insolvency Event” means, in relation to any party, that any of the following events or
circumstances have occurred:




(i) the affected party becomes insolvent or bankrupt or is unable to pay its debts when they
fall due or commits an act of bankruptcy or is declared insolvent; or




(ii) proceedings are commenced to appoint a liquidator or provisional liquidator to the affected
party (not being for the purposes of amalgamation or reconstruction of the affected party); or




(iii) the
affected party is placed under official management or administration; or




(iv) any trustee, receiver or receiver and manager is appointed in respect of any material part
of the affected party’s assets; or




(v) anything analogous, or having substantially similar effect, to the occurrence of these
events in relation to the affected party;




(k) “Intellectual Property Right” means any intellectual and industrial property rights, including
trade marks, copyright (including future copyright), inventions, patents, designs, circuits and
other eligible layouts, database rights, and other intellectual property rights, including any
application or right to apply for registration of any of these rights;





			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	42







 









 





LGL EQUIPMENT SUPPLY TENDER





(l) “Location” is the location specified in the Purchase Order or such other sites as directed
by the Principal;




(m) “Purchase Order” means the purchase order issued by the Principal for the supply of the
Services at the Location for the Purchase Order Price;




(n) “Purchase Order Price” means the price specified in the Purchase Order or, if no price is
specified in the Purchase Order, calculated by reference to the hourly rates specified in the
Service Order Instructions Page;




(o) “Reimbursable Items” are those items specified in the Service Order Instructions Page or the
Purchase Order as being Reimbursable Items;




(p) “Services” means those Services identified in the Purchase Order, to be provided by
the Contractor in accordance with these general conditions;




(q) “Service Order Instructions Page” means the document identified as such which, when completed
and signed by the Principal and the Contractor, forms part of this agreement;




(r) “Specification” means any specification provided by or approved by the Principal (including
any modifications or variations, provided they are approved by the Principal);




(s) “Tax” means any tax, levy, royalty, rate, duty, fee, impost, customs or other charge imposed
by any governmental, semi-governmental, or other body authorised by law whether in the Supplier’s
country of origin, Australia, PNG or elsewhere to impose such Tax. Without limiting the
generality of the foregoing, Tax includes any withholding tax (including foreign contractor
withholding tax), goods and services tax, value added tax, a petroleum resource rent tax or any
taxrespecting environmental effects including a carbon tax.


Version 2A as at 15 May 2008





			
	 	 	 
	Section I — Part B Purchase Order Terms and Conditions
	 	43







 









 





LGL EQUIPMENT SUPPLY TENDER




     Appendix B Service Order Instructions



CONTRACTOR’S
NAME: [To be specified](“The
Contractor”)




ABN/COMPANY NUMBER: [To be specified]|


ADDRESS: [To be specified]


FACSIMILE: [To be specified]




PRINCIPAL’S NAME: Lihir Gold Limited (“The Principal”)


ABN/COMPANY NUMBER: a company incorporated in Papua New Guinea (ARBN 069 803 998)


ADDRESS: Level 7, Pacific Place Cnr of Champion Parade and Musgrave Street, Port Moresby


FACSIMILE: (+675) 986 4018



SERVICES: As specified in the Purchase Order and any additional instructions or Specifications
provided by the Principal to the Contractor.



COMMENCEMENT DATE: The date specified in the Purchase Order or such other date as notified in
writing by the Principal.



DUE DATE: The date specified in the Purchase Order or such other date as notified in writing by the
Principal.



FEES: The Purchase Order Price is to be as set out in the Purchase Order or, if no price is
specified in the Purchase Order, calculated by reference to the hourly rates specified below.



Reimbursable Sum: [To be specified]



Per Diem Rate (Working Time) [To be specified]



Equipment Hire Rates: [To be specified]



Accommodation Required       Yes/No                     
Number of Rooms                     



REIMBURSABLE ITEMS: any reasonable costs properly incurred by the Contractor with the Principal’s
prior written consent but excluding additional labour, fuel, tools and other general operating
expenses. Items purchased from the Principal’s Lihir Island supply warehouse will be charged to the
Contractor at cost plus a admin fee.




Principal’s Representative: [To be specified]


Position Title: [To be specified]




Contractor’s Representative: [To be specified]


Position Title: [To be specified]




Accepted by the Principal:




	 	 	 
	Name:
                                        


	 	Title:
                                        

	 
	Signature:
                                        


	 	Date:
                                        

	 
	 	 
	Accepted by the Contractor:
	 	 
	 
	 	 
	Name:
                                        


	 	Title:
                                        

	 
	Signature:
                                        


	 	Date:
                                        







			
	 	 	 
	Section I — Part C Technical On-Site Personnel Terms
	 	44







 











 










LIHIR OPERATIONS — LIHIR ISLAND




STANDARD SPECIFICATION

SITE CONDITIONS AND STANDARDS FOR

SUPPLY OF GOODS AND EQUIPMENT

SECTION II



	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Approved	 	 
	Revision	 	Date	 	Author	 	By	 	Comments
	 
	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 
	01

	 	06-8-08
	 	AB
	 	AB
	 	Buyer supplied motors added
	00

	 	01-5-08
	 	AB
	 	AB
	 	Draft





LGL-000-01-S
Equipment Purchase Specification Section II Page 1 of 10




 









 













	 	 	 	 	 
	1 SCOPE
	 	 	3	 
	1.1 General
	 	 	3	 
	2 SITE CONDITIONS
	 	 	3	 
	2.1 Location
	 	 	3	 
	2.2 Climate
	 	 	3	 
	3 BUYER SUPPLIED MOTORS
	 	 	3	 
	3.1 Motor Supply
	 	 	3	 
	3.2 Motor Type
	 	 	3	 
	3.3 Mounting and Drive
	 	 	3	 
	3.4 Required Motor Data
	 	 	4	 
	3.5 Installation
	 	 	4	 
	4 STANDARDS, CODES AND REGULATIONS
	 	 	4	 
	4.1 Statutory
	 	 	4	 
	4.2 Technical Specifications
	 	 	5	 
	4.3 Drawing Conventions
	 	 	5	 
	4.3.1 Relevant Specifications
	 	 	5	 
	4.3.2 Drawing Structure
	 	 	5	 
	4.3.3 Project Titleblock
	 	 	5	 
	4.3.4 Electronic Filenames
	 	 	5	 
	4.3.5 Electronic Formats
	 	 	6	 
	4.4 Labeling Conventions
	 	 	6	 
	4.4.1 Relevant Specifications
	 	 	6	 
	4.4.2 Equipment Numbering
	 	 	6	 
	4.4.3 Loop Numbering
	 	 	6	 
	4.4.4 Pipe Labeling
	 	 	7	 
	4.5 Project Documentation
	 	 	7	 
	4.6 Correspondence
	 	 	7	 
	4.6.1 General
	 	 	7	 
	4.6.2 Formal Transmittal of Information
	 	 	8	 
	5 APPENDIX A — LIST OF STANDARD SPECIFICATIONS
	 	 	9	 






LGL-000-01-S
Equipment Purchase Specification Section II Page 2 of 10




 









 















	1	 	SCOPE
	 
	1.1	 	General
	 
	 	 	This document provides information relating to site conditions, climate, and standards
that are relevant to the supply of goods and equipment for use on the Lihir site.
	 
	2	 	SITE CONDITIONS
	 
	2.1	 	Location
	 
	 	 	The Lihir plant is located on Lihir Island which in the New Ireland province of Papua New
Guinea and is approximately 3 degrees south of the equator.
	 
	2.2	 	Climate
	 
	 	 	The Lihir plant site is located in a coastal, tropical environment with temperatures
ranging from a minimum of 19.5°C to a maximum of 34.0°C, and annual rainfall ranging
from a minimum of 2600mm to a peak of 8400mm over 20 years of record. The plant site and
associated infrastructure lie within 80m of sea level.
	 
	 	 	There is no strong seasonal pattern to the climate, with temperature and monthly
rainfall remaining relatively uniform throughout the year. Temperature averages 27.0°C
while average annual rainfall is in the order of 3900-4000 mm/year.
	 
	 	 	Low rainfall conditions appear to be driven by Pacific El Nino events, with the worst
periods of drought generally recorded in August-November for site conditions.
	 
	3	 	BUYER SUPPLIED MOTORS
	 
	3.1	 	Motor Supply
	 
	 	 	When specified in Section III “Detailed Specifications” herein, motors will be supplied
by the Buyer.
	 
	3.2	 	Motor Type
	 
	 	 	Buyer supplied motors will be 415 volt, 3 phase, 50 Hz, 1.0 S.F., TEFC, cast iron
Australian metric frame as per Australian Standards 1359 and 1360, standard shaft
suitable for belt drive (even for direct drive applications, in order to limit spares),
with standard Australian metric frame assignments, for ratings up to 185 kW.
	 
	3.3	 	Mounting and Drive
	 
	 	 	The Tenderer shall provide all necessary drive and mounting facilities for Buyer supplied
motors including: base mounting holes, brackets, bases, sheaves, belts, couplings,
guards, and similar to match the nominated motor.
	 
	 	 	All sheaves shall be of the taperlock type.




LGL-000-01-S
Equipment Purchase Specification Section II Page 3 of 10




 









 














	 	 	If standard slide bases are required with Buyer supplied motors, they shall be so
specified by the Tenderer.
	 
	3.4	 	Required Motor Data
	 
	 	 	Tenderers shall provide the following information with their Tenders:-






	 	•	 	Normal drive brake kW;
	 
	 	•	 	Maximum drive brake kW (state conditions);
	 
	 	•	 	Recommended motor, kW;
	 
	 	•	 	Motor rpm;
	 
	 	•	 	Frame size;
	 
	 	•	 	Conduit box location (if non-standard);
	 
	 	•	 	Drive details (direct coupled, V-belt, mounted horizontally or vertically, etc);
	 
	 	•	 	Starting torque requirements (if other than standard NEMA Design B);
	 
	 	•	 	Shaft details if non-standard; and
	 
	 	•	 	Flange details, if applicable.
	 
	 	•	 	Mounting Code as per AS 1359.






	3.5	 	Installation
	 
	 	 	The Tenderer shall include in its Tender the cost of receiving and installing the Buyer
supplied motors at its shop or factory. Where the Buyer elects to field install motors,
the Tenderer shall do all things necessary (including the drilling of mounting holes) to
facilitate such installation with an absolute minimum of field work
	 
	4	 	STANDARDS, CODES AND REGULATIONS
	 
	 	 	The Tenderer is not required to depart from its standard design or specification, but
significant non-fundamental differences between its product and the requirements of the
Tender Documents must be explained in its Tender. Where no differences are explained,
the Tenderer undertakes to supply equipment and/or materials in accordance with the
standards and specifications referenced in the Tender Documents.
	 
	4.1	 	Statutory
	 
	 	 	Equipment and installation shall conform to the current requirements, rules and
regulations of the relevant PNG authorities having jurisdiction over the Project site.
	 
	 	 	Where conflict arises between specifications and the applicable standards, the standards
shall prevail unless this specification requires a higher or more rigorous standard to
be applied.
	 
	 	 	All pertinent standards including those for detail components shall be applicable even
if omitted from the specifications or drawings.




LGL-000-01-S
Equipment Purchase Specification Section II Page 4 of 10




 









 














	4.2	 	Technical Specifications
	 
	 	 	All design and construction shall comply with the relevant standard specifications
listed in Appendix A — List of Standard Specifications.
	 
	4.3	 	Drawing Conventions
	 
	4.3.1	 	Relevant Specifications
	 
	 	 	To ensure consistency with existing site documentation all project drawings shall comply
with the Standard Specification for AutoCAD Drawings (Specification A002). Key
requirements are outlined in Sections 4.3.2 to 4.3.5 below.
	 
	4.3.2	 	Drawing Structure
	 
	 	 	All drawings shall be generated using the LGL standard drawing sheet and drawing
attributes provided. These attributes must not be altered without the prior written
approval of LGL, although Vendors / Consultants may add their own drawing number in a
separate title block. Except as otherwise indicated by Specification A002 (for
Electrical drawings), project drawing numbers shall be of the form ‘AAAA-B-CCCC where
AAAA is a three or four digit facility number defining the appropriate element of the
process plant, B is a single character discipline code identifying the engineering
discipline associated with the drawing, and CCCC is a four digit, sequential sheet
number by facility and discipline.
	 
	 	 	The relevant discipline codes for the MOPU project are identified in Specification A002.
Sheet numbers shall be progressively allocated by the Vendor from a batch of sequential
numbers issued by LGL. Unless otherwise advised, all sheet numbers for the MOPU project
shall be 4 digits long and commence with the number ‘2’.
	 
	4.3.3	 	Project Titleblock
	 
	 	 	Each drawing title shall comprise 3 to 4 lines as follows:






	 	•	 	Line 1 (Folio Title): “LGL Process Plant — Lihir Island” or “LGL
Geothermal Power Supply — Lihir Island” as appropriate.
	 
	 	•	 	Line 2 (Facility Name): Relevant facility name as defined by Appendix A.
	 
	 	•	 	Lines 3/4 (Drawing Description): Relevant drawing description to clearly
describe drawing content and distinguish each drawing from other
drawings in the project set.






	 	 	Until such time as a drawing is revised to ‘As Constructed’ the Project ID Code (MOPU)
shall be included in the drawing number box on the titleblock as a ‘work-in-progress’
flag. This flag shall be removed from each and every drawing upon completion of ‘As
Constructed’ revisions.
	 
	4.3.4	 	Electronic Filenames
	 
	 	 	Electronic drawing filenames shall be of the form ‘MOPU-AAAABCCCC_D.dwg’ where
‘AAAABCCCC’ represents a contraction of the drawing number defined by Section 4.3.2 and
‘D’ represents the current drawing revision number, as per the following:




LGL-000-01-S
Equipment Purchase Specification Section II Page 5 of 10





 









 













	 	 	 	 	 
	 

	 	Drawing Number
	 	Electronic Filename
	 
	 	 	 	 
	 

	 	1341-C-2046 Rev 2
	 	MOPU-1341c2046_2.dwg







	 	 	As in Section 4.3.3 the Project ID Code (‘MOPU-’) shall be removed from each and every
filename upon completion of ‘As Constructed’ revisions.
	 
	4.3.5	 	Electronic Formats
	 
	 	 	All AutoCAD drawing files shall be formatted for full compatibility with AutoCAD Lite
2004 and AutoCAD 200.
	 
	 	 	Issue of drawings for review or comment shall be done as pdf documents formatted to A3
size to facilitate ready distribution and printing. Drawings supplied in pdf format
shall be fully compatible with Adobe Reader 8.0 and Adobe Acrobat Professional 6.0.
	 
	 	 	Transmittal of AutoCAD drawing files shall be complete with all XRef files referenced by
the drawings, included with the drawing or the drawing package. All plot style tables &
pen assignments utilised by the Consultant, shall be supplied with the transmittal, so
that correct printing of the AutoCAD files can be undertaken by LGL.
	 
	4.4	 	Labeling Conventions
	 
	4.4.1	 	Relevant Specifications
	 
	 	 	Equipment, cabling and piping shall be labeled in accordance with the Standard
Specification for Vendor Documentation (Specification A003), Standard Specification for
Piping Information (Specification A005) and Standard Specification for Process
Instrument Loop Numbering (Specification A007). Key requirements are outlined in
Sections 4.4.2 to 4.4.4 below.
	 
	4.4.2	 	Equipment Numbering
	 
	 	 	Each new item of equipment shall be identified by a unique ID number of the form AABBBB
where ‘AA’ is a two character equipment code and ‘BBBB’ is a four digit numeric counter
commencing with the number ‘2’ or ‘3’ to identify the MOPU project. Each equipment
sub-assembly with a separate electrical drive shall be allocated its own unique
equipment number of the form AABBBBC where ‘AABBBB’ is the equipment number identified
for the unit as a whole, and ‘C’ is a sequential, alphabetic suffix to identify
individual sub-assembly elements.
	 
	 	 	The principal equipment numbers for the project are identified in the Project Equipment
List. Any additional equipment numbers shall be allocated by the Vendor / Consultant
from a batch of counter numbers provided by LGL. The allocation of numbers shall be
carried out in such a way that equipment items grouped together physically in the final
plant and/or grouped together on the P&ID drawings, shall have similar or closely
sequenced numbers.
	 
	4.4.3	 	Loop Numbering
	 
	 	 	Instrumentation shall be identified in accordance with the conventions shown on standard
Drawing 130-FP-002. Loop numbers shall be of the form AABBBB where AA is the instrument
code as per Drawing 130-FP-002 and




LGL-000-01-S
Equipment Purchase Specification Section II Page 6 of 10




 









 














	 	 	BBBB is a 4 digit sequential counter that is unique compared to both other loop
numbers and equipment numbers.






	 	 	An initial loop number database for the project is identified in the Loop Number
Register. Any additional loop numbering shall be labeled by the Vendor / Consultant from
a batch of sequential counter numbers provided by LGL. Loop numbering shall be carried
out in such a way that instrument items grouped together physically in the final plant
and/or grouped together on the P&ID drawings, shall have closely sequenced numbers.






	4.4.4	 	Pipe Labeling
	 
	 	 	All new pipes and pipe branches shall be identified by an ID label of the form
AAA-BB-CCCC-DDDD-EE where AAA is the nominal pipe diameter in mm, BB is a code
describing the fluid carried by the pipe, CCCC is the four digit facility number, DDDD
is a unique 4 digit sequential counter, and EE is a code representing the pipe material
specification. Relevant fluid description and pipe specification codes are identified in
Specification A005.
	 
	 	 	The principal piping elements for the project are identified in the Project Line List.
Any additional pipes shall be labelled by the Vendor / Consultant from a batch of
sequential counter numbers provided by LGL. The allocation of counter numbers shall be
carried out in such a way that pipes grouped together physically in the final plant
and/or grouped together on the P&ID drawings, shall have similar or closely sequenced
numbers.
	 
	4.5	 	Project Documentation
	 
	 	 	All project documentation including reports, datasheets, databases, drawing lists,
purchase information, IOM documentation, etc shall comply with the Project Instructions,
Standard Specification for Vendor Documentation (Specification A003) and Standard
Specification for Piping Information (Specification A005).
	 
	 	 	In particular:






	 	•	 	Information shall be collated in the identified formats to facilitate ready
incorporation into other project databases.
	 
	 	•	 	Each document shall be cross referenced against all relevant equipment
items to enable database searching by equipment number.
	 
	 	•	 	All pdf documents of greater than 10 pages length shall include
interactive bookmarks to allow ready navigation to each item in the
document table of contents.






	4.6	 	Correspondence
	 
	4.6.1	 	General
	 
	 	 	For ease and currency of communication, project correspondence will be handled by email
wherever possible. Without exception, every email shall be structured as follows:






	 	•	 	The email shall be addressed to both the project email
address
(‘MOPU@lglgold.com’) and the intended recipient of the email.




LGL-000-01-S
Equipment Purchase Specification Section II Page 7 of 10




 









 














	 	•	 	The caption in the email subject line shall be of the form AAAA-BBBB-C-
DDD-EEEE, where AAAA is the Project ID Code, BBBB is the relevant
four character work package number (eg Contract Number or Purchase
Order number), C is single character code identifying the email originator
(as identified below), DDD is a sequential correspondence counter for the
particular Contract, and EEEE is a descriptive title (of as many characters
as required) to clearly identify and distinguish the email subject.






	 	 	Emails from LGL shall have the originator code “L”, emails from the Design Coordinator
shall have the originator code “D” and emails from all other Consultants, Contractors or
Vendors shall have the originator code “C”. Each organisation assigned to the project
shall maintain their own separate correspondence counter.
	 
	4.6.2	 	Formal Transmittal of Information
	 
	 	 	Consultants / Vendors shall ensure that all formal transmittal of drawings and
documentation to LGL, whether by email, disk or hardcopy, is accompanied by an
electronic transmittal form in Microsoft EXCEL that identifies the following:






	 	•	 	A sequential transmittal number.
	 
	 	•	 	The electronic filename and a description of each drawing /
document being transmitted. Suitable descriptions would include the last two lines of
a drawing titleblock or a brief summation of document purpose or content.






	 	 	Any covering email shall also include the word Transmittal’ in the descriptive title
component of the subject line.
	 
	 	 	The purpose of these requirements is to enable ready collation of information from
varied sources into a comprehensive project database. Transfers of drawings and
documentation which do not meet these criteria will be treated as issue for information
purposes only and the relevant drawings / documents will not be registered in the
project database.
	 
	 	 	In the absence of any other agreed format for the transmittal form, the Standard LGL
Transmittal (Specification A008) shall be utilised.




LGL-000-01-S
Equipment Purchase Specification Section II Page 8 of 10




 









 













5 APPENDIX A — LIST OF STANDARD SPECIFICATIONS




Administrative Specifications




	 	 	 
	Spec. Number	 	Title
	A001

	 	Project Instructions
	A002

	 	Specification for AutoCAD Drawings
	A003

	 	Specification for Vendor Documentation
	A004

	 	Register Project Information 
	A005

	 	 Specification for Piping Information
	A006

	 	Standard Format for Piping Information
	A007

	 	Specification for Loop Numbering
	A008

	 	Standard Transmittal Form






Technical Specifications — Design




	 	 	 
	Spec. Number	 	Title
	E100

	 	General Electrical Specification
	E101

	 	DCS and Control System Specificatio
	D002

	 	Civil & Structural Design Criteria
	D003

	 	Mechanical Design Criteria
	D004

	 	Piping Design Criteria






Technical Specifications — Construction




General




	 	 	 
	Spec. Number	 	Title
	G001

	 	Specification for Packaging and Shipping






Electrical




	 	 	 
	Spec. Number	 	Title
	E001

	 	Specification for Low Voltage Motor Control Centres
	E002

	 	Specification for HV Switchgear
	Eoo3

	 	Specification for Transportable Switchrooms
	E004

	 	Specification for Transformers
	E005

	 	Specification for Motors
	E006

	 	Instruments and Field Devices
	E007

	 	LV Cable
	E008

	 	HV Cable
	E009

	 	Variable Speed Drives and Soft Starters






Civil and Structural




	 	 	 
	Spec. Number	 	Title
	S001

	 	Specification for Bulk Earthworks
	S002

	 	Specification for Piling
	S003

	 	Specification for General Civil Works
	S004

	 	Specification for Concrete





LGL-000-01-S
Equipment Purchase Specification Section II Page 9 of 10




 









 













Civil and Structural (Contd)




	 	 	 
	Spec. Number	 	Title	;
	S005

	 	Specification for Concrete Masonry
	S006

	 	Specification for Structural Steelwork
	S007

	 	Specification for Cladding






Mechanical and Piping




	 	 	 
	Spec. Number	 	Title
	M001

	 	Specification for Agitators
	M002

	 	Specification for Cranes, Monorails and Hoists
	M003

	 	Specification for Compressed Air Services
	M004

	 	Specification for Conveyor Equipment
	M005

	 	Specification for Fans and Blowers
	M006

	 	Specification for Instrumentation
	M007

	 	Specification for Piping
	M008

	 	Specification for Protective Coatings
	M009

	 	Specification for Pumps
	M010

	 	Specification for Signage
	M011

	 	Specification for Specialty Piping Items
	M012

	 	Specification for Tanks
	M013

	 	Specification for Valving 
	M100

	 	Specification for Installation of Mechanical Plant





LGL-000-01-S
Equipment Purchase Specification Section II Page 10 of 10




 









 













MILLION OUNCE PLANT UPGRADE PROJECT




LOW VOLTAGE MCCS AND SWITCHROOMS



MOPU-1101



SECTION III — DETAILED SPECIFICATION



	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Approved	 	 
	Revision	 	Date	 	Author	 	By	 	Comments
	 
	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 
	00

	 	04-11-08
	 	CJH
	 	 	 	Issued for Tender
	A

	 	03-09-08
	 	CJH
	 	 	 	Issued for Client Review






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 2






INDEX




	 	 	 	 	 
	1 SCOPE
	 	 	3	 
	 
	 	 	 	 
	2 ITEMS NOT INCLUDED
	 	 	3	 
	 
	 	 	 	 
	3 CODES AND STANDARDS
	 	 	3	 
	 
	 	 	 	 
	4 OPERATION AND DUTY
	 	 	4	 
	 
	 	 	 	 
	5 DESIGN DATA
	 	 	4	 
	 
	 	 	 	 
	6 INFORMATION TO BE PROVIDED BY TENDERER
	 	 	4	 
	 
	 	 	 	 
	7 INFORMATION TO BE PROVIDED BY SUCCESSFUL TENDERER
	 	 	5	 
	 
	 	 	 	 
	8 TESTING
	 	 	7	 
	 
	 	 	 	 
	9 SPARE PARTS
	 	 	7	 
	 
	 	 	 	 
	10 SPECIAL TOOLS
	 	 	7	 
	 
	 	 	 	 
	11 SHIPPING
	 	 	7	 
	 
	 	 	 	 
	12 DRAWINGS
	 	 	8	 
	 
	 	 	 	 
	13 SCOPE OF SUPPLY
	 	 	19	 
	 
	 	 	 	 
	14 REQUIRED DELIVERY DATES
	 	 	26	 
	 
	 	 	 	 
	15 PREFERRED EQUIPMENT SUPPLIERS
	 	 	27	 
	 
	 	 	 	 
	16 EQUIPMENT SUPPLIERS CONTACT DETAILS
	 	 	29	 
	 
	 	 	 	 
	17 BATTERY LIMITS
	 	 	30	 
	 
	 	 	 	 
	18 APPENDIX A — TECHNICAL DATASHEETS
	 	 	31	 
	 
	 	 	 	 
	19 APPENDIX B — DRAWINGS
	 	 	32	 
	 
	 	 	 	 
	20 APPENDIX C — SPECIFICATIONS
	 	 	33	 






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 3







	1	 	SCOPE






This
specification covers the provision of all labour, materials, equipment and services for the
design, fabrication, supply, testing, delivery and guarantee of Low Voltage MCCs, Switchrooms and
associated equipment for the Lihir Gold MOPU Project.




It is not intended that manufacturers depart from their standard design. However, any deviations
from these specifications shall be listed and explained in the Bidder’s proposal. The lack of
such a listing shall indicate that no such deviations exist.




The successful Tenderer will also be required to install Owner’s equipment into the switchrooms,
including HV switchboards, DCS panels, etc. These items will be free-issued to the successful
Tenderer. The Owner will arrange delivery of these items by truck to the Tenderer’s premises. The
Tenderer will be responsible for unloading the equipment.




The successful Tenderer will also be required to arrange delivery and unloading of low
voltage Variable Speed Drives and Soft Starters as required from the Owner’s preferred
supplier and to install the drives into MCC’s and switchrooms to meet the schedule.




	2	 	ITEMS NOT INCLUDED






Ø    Shipping and delivery to site.




Ø    Offloading at nominated site.




Ø    Installation labour at nominated site.




Ø    Concrete foundations.




Ø    External cabling outside battery limits.




Ø    Hold-down or mounting bolts, nuts and washers at concrete foundations / structural
steel.




Ø    Supply of low voltage Soft Starters and associated equipment to be installed within
MCCs.




Ø    Supply of low voltage VSDs, filters, reactors and remote keypads to be installed
within MCCs.




Ø    Supply of low voltage VSDs in enclosures to be installed within switchrooms.




Ø    Supply of DCS Panels.




Ø    Supply of preformed cables for connection between pairs of DCS Panels.




Ø    Supply of HV Switchboards.




Ø    Supply of Remote Switching Panels.




Ø    Supply of CO2 Fire Extinguishers.




	3	 	CODES AND STANDARDS






Lihir Standard Specification (Appendix C) — E001 — Low Voltage Motor Control Centres.

Lihir Standard Specification (Appendix C) — E003 — Transportable Switchrooms.

Lihir Standard Specification (Appendix C) — E009 — Variable Speed Drives & Soft Starters.





All applicable Codes and Standards, and in particular: -



	 	 	 
	AS 1170 / PNGS

	 	Minimum design loads on structures






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 4






	 	 	 
	1001
	 	 
	 
	 	 
	AS 1319

	 	Rules for the Design and Use of Safety Signs for the
Occupational Environment
	 
	 	 
	AS 1680

	 	Interior lighting — General principles and recommendations
	 
	 	 
	AS 1930

	 	Circuit Breakers up to 1000 V
	 
	 	 
	AS 2179

	 	Metal rainwater goods — specification
	 
	 	 
	AS 2293

	 	Emergency evacuation and lighting in buildings
	 
	 	 
	AS 2768

	 	Electrical insulating materials — Evaluation and
classification based on thermal endurance
	 
	 	 
	AS 2904

	 	Damp-proof courses and flashings
	 
	 	 
	AS/NZS 3000

	 	SAA Wiring Rules
	 
	 	 
	AS 3116

	 	Approval and test specification — Electric cables -
Elastomer insulated — For working voltages up to and
including 0.6/1 kV
	 
	 	 
	AS 3439.1 2002

	 	Low-voltage switchgear and control gear assemblies -
Type-tested and partially type-tested assemblies
	 
	 	 
	AS 3500

	 	Plumbing and Drainage Code
	 
	 	 
	AS 3947

	 	Low Voltage Switchgear and Control gear
	 
	 	 
	AS
4100 / PNGS 1003

	 	Steel Structures
	 
	 	 
	AS 4600

	 	Cold Formed Steel Structures
	 
	 	 
	AS/NZS 5000.1

	 	Electric cables — Polymeric insulated — For working voltages
up to and including 0.6/1 kV
	 
	 	 
	AS 60038

	 	Standard voltages
	 
	 	 
	AS 60044.1

	 	Instrument Transformers — Current Transformers
	 
	 	 
	AS 60044.2

	 	Voltage Transformers for Measurement and Protection
	 
	 	 
	AS 60529

	 	Degrees of protection provided by enclosures (IP Code)
	 
	 	 
	AS 60947.8

	 	Low-voltage switchgear and controlgear — Control units for
built-in thermal protection (PTC) for rotating electrical
machines
	 
	 	 
	AS 61000

	 	EMC Compatability







	4	 	OPERATION AND DUTY






All MCCs shall be designed for continuous duty on an 415V, ±10% 50 Hz, 63kA fault capacity
busbars fed from the Owner’s transformers.




	5	 	DESIGN DATA





As per the Data Sheet in Appendix A.




	6	 	INFORMATION TO BE PROVIDED BY TENDERER






Refer to Section I of these documents. In addition to the requirements of Section I, the
Tenderer shall provide the following information with his proposal:




	 	Ø	 	A price for all the materials, equipment and services included in this Specification.





			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 5







	 	Ø 	 	Where Tenderers have tendered based on currency exchange rate variations, the exact rates upon which the proposal is based, the basis for claiming a variation from
the quoted rates, and the exact amounts in each currency which are affected by such a variation must be given.
	 
	 	Ø 	 	Completed Data Sheets as shown in Appendix A.
	 
	 	Ø 	 	Dimensioned arrangement drawings for the MCC’s and switchrooms.
	 
	 	Ø 	 	Descriptive literature of all components.
	 
	 	Ø 	 	List of routine tests to be carried out on all equipment.
	 
	 	Ø 	 	A design, manufacture and delivery schedule ex-works showing the shortest
possible times obtainable after receipt of order.






	7	 	INFORMATION TO BE PROVIDED BY SUCCESSFUL TENDERER






Within one week from date of acceptance of purchase order, the supplier shall prepare and submit
a complete list of drawings and documents that he will be providing.




All drawings and manuals shall be submitted for the Owner’s review as detailed in Section I
Appendix B. The Tenderer shall have responsibility for the detailed design and correctness of all
designs and drawings, material lists, schedules, engineering and other like things. The Owner
reserves the right to also review all such things, prior to manufacture and assemble, but his
review does not limit the Tenderers overall responsibility for the complete design and manufacture
of the entire system. Following written approval by the Owner, drawings and manuals shall be
submitted as final certified documents, suitable for equipment assembly on site, commissioning and
operation.




The following drawings and information shall be submitted for approval:




	 	Ø 	 	MCC General Arrangement drawings
	 
	 	Ø 	 	MCC Plan and Cable Gland Plate Layout drawings
	 
	 	Ø 	 	MCC Cell Door and Internal Layout drawings
	 
	 	Ø 	 	MCC Labeling drawings
	 
	 	Ø 	 	MCC Bill of Materials for each cell
	 
	 	Ø 	 	  Switchroom General Arrangement drawings
	 
	 	Ø 	 	 Switchroom Equipment Layout & Dimensions drawings
	 
	 	Ø 	 	 Switchroom Structural Layout drawings (Base Frame / Walls / Roof)
	 
	 	Ø 	 	 Switchroom Stairs and Landing Layout & Details drawings
	 
	 	Ø 	 	 Switchroom Support Columns & Bracing drawings
	 
	 	Ø 	 	 Switchroom Cable Ladder drawings
	 
	 	Ø 	 	 Switchroom Cable Glanding Boxes drawings
	 
	 	Ø 	 	 Switchroom Hold-down Bolt Arrangement & Details drawings
	 
	 	Ø 	 	 Switchroom Elevation Sections drawings
	 
	 	Ø 	 	 Switchroom Electrical Light & Power Layout drawings
	 
	 	Ø 	 	 Switchroom Fire Services drawings
	 
	 	Ø 	 	 Switchroom Lifting Instructions drawings
	 
	 	Ø 	 	 Local Control Station drawings
	 
	 	Ø 	 	 Battery Charger drawings





			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 6







	 	Ø 	 	 Uninterruptible Power Supply drawings
	 
	 	Ø 	 	 Distribution Board drawings





     If as a result of heat loading calculations ducted air-conditioning is required, the following
drawings shall be provided:




	 	Ø 	 	 Ducted Air-Conditioning System Layout drawings
	 
	 	Ø 	 	 Concrete Foundation Layout drawings
	 
	 	Ø 	 	 Switchroom Internal Duct Arrangement drawings






In addition to the supply and installation of the equipment, the supplier shall provide the
following design services:




	 	Ø 	 	 program the Motor Protection Relays with the required control functionality
following consultation with the purchaser
	 
	 	Ø 	 	 test all the MCCs for their functionality, including testing of incomer circuit breakers
for correct protection function operation (protection settings will be provided by the
Owner)
	 
	 	Ø 	 	 test all battery chargers for their functionality
	 
	 	Ø 	 	 test all UPS’s for their functionality
	 
	 	Ø 	 	 provide a copy of the programming software for the MPRs which will enable the
purchaser to update the settings and download into the protection relay
	 
	 	Ø 	 	 provide heat loading calculations on the equipment within the scope of supply
	 
	 	Ø 	 	 provide air conditioning calculations for each switchroom
	 
	 	Ø 	 	 provide certified calculations for switchroom structures for site seismic conditions






Note that documentation provided by the Successful Tenderer shall apply specifically to the MOPU
project. Standard generalized documentation is acceptable only if it accurately depicts the MOPU
installation. Where modifications to standard equipment are made, documentation shall be clearly,
legibly and permanently modified to show the changes or new documents shall be produced.




Commencing two weeks after date of issue of each purchase order, and continuing thereafter
at fortnightly intervals, until all equipment has been shipped (including short-shipped
items, if any), the Vendor shall submit a detailed procurement, manufacturing, assembly and
testing schedule and progress report to the Owner.




The Successful Bidder shall submit two preliminary copies of his operating and maintenance
instruction manual for approval eight weeks after date of acceptance of tender. This issue of
preliminary manuals is not required to include test results or final certified drawings,
instruction manuals shall be presented in sets, logically broken down (where appropriate) into
separate binders for different equipment.




All manuals shall be provided with detailed indices to facilitate locating information. Manuals
shall contain additional copies (reduced sizes as appropriate) of all final certified drawings
including schematics and wiring diagrams.




Statutory and other approvals, licenses and certifications are to be provided.



			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 7







All items of equipment supplied under this specification shall be identified with the
switchboard number, the purchase order number and the item number.




All documentation shall be in the English language.




	8	 	TESTING






Standard commercial production tests including mechanical and electrical operation tests shall be
performed on all equipment supplied under the Specification.




Complete operational tests shall be carried out including the following free issued
equipment:




	 	Ø 	 	 Supplier to install, wire and test as far as possible free issued HV Switchboards
and remote switching panels within the switchrooms
	 
	 	Ø 	 	 Supplier to install and wire free issued IP20 VSDs (up to and including 22kW), soft
starters and associated equipment within the MCC
	 
	 	Ø 	 	 Supplier to install, wire and test as far as possible free issued IP54 VSD cabinets
(rated 30kW and above) within the switchrooms






Bidder shall provide complete details of their routine tests.




	9	 	SPARE PARTS






Tenderers are to submit a priced spare parts list, including consumable spares,
commissioning spares and insurance spares.




	10	 	SPECIAL TOOLS






Tenderers are to submit a priced list for special tools required for installation and
maintenance of the equipment supplied.




Supplier shall provide all lifting lugs, transportation cradles, lifting spiders / frames / beams
and spreaders for the loading and unloading of the equipment onto and off transport and for
installation.




All miscellaneous material and minor components such as, fasteners, washers, packing, touch up
paint, connectors, covers, supports etc., necessary for the site assembly and installation of the
equipment are to be supplied.




	11	 	SHIPPING






Suitable packing and temporary support for transport is to be included in price. In addition,
taking delivery, unpacking and installation into the switchrooms of free issue items shall be
accounted for.



			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 8







	12	 	DRAWINGS




The list of drawings attached to the tender (Appendix B) is detailed below.




	 	 	 	 	 
	Drawing Number	 	Revision	 	Description
	MOPU-0000-E80-0005

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter
	 

	 	 	 	0.37kW to 30kW
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0006

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Reversing
	 

	 	 	 	0.37kW to 30kW
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0007

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC VSD Starter
	 

	 	 	 	0.37kW to 22kW
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0008

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter
	 

	 	 	 	37kW to 45kW
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0009

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Reversing
	 

	 	 	 	37kW to 45kW
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0010

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC VSD Starter
	 

	 	 	 	30kW to 45kW
	 

	 	 	 	Schematic Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0011

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC VSD Starter
	 

	 	 	 	30kW to 45kW
	 

	 	 	 	Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0012

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter
	 

	 	 	 	55kW to 110kW
	 

	 	 	 	Schematic and Termination Diagram






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 9






	 	 	 	 	 
	Drawing Number	 	Revision	 	Description
	MOPU-0000-E80-0013

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter- Reversing
	 

	 	 	 	55kW to 110kW
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0014

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC VSD Starter
	 

	 	 	 	55kW to 110kW
	 

	 	 	 	Schematic Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0015

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC VSD Starter
	 

	 	 	 	55kW to 110kW
	 

	 	 	 	Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0016

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter
	 

	 	 	 	132kW to 150kW
	 

	 	 	 	Schematic Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0017

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter
	 

	 	 	 	132kW to 150kW
	 

	 	 	 	Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0018

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Reversing
	 

	 	 	 	132kW to 150kW
	 

	 	 	 	Schematic Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0019

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Reversing
	 

	 	 	 	132kW to 150kW
	 

	 	 	 	Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0020

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC VSD Starter
	 

	 	 	 	132kW to 150kW
	 

	 	 	 	Schematic Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0021

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC VSD Starter
	 

	 	 	 	132kW to 150kW
	 

	 	 	 	Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0022

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 10






	 	 	 	 	 
	Drawing Number	 	Revision	 	Description
	 

	 	 	 	185kW to 630kW
	 

	 	 	 	Schematic Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0023

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter
	 

	 	 	 	185kW to 630kW
	 

	 	 	 	Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0024

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Reversing
	 

	 	 	 	185kW to 630kW
	 

	 	 	 	Schematic Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0025

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Reversing
	 

	 	 	 	185kW to 630kW
	 

	 	 	 	Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0026

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC VSD Starter
	 

	 	 	 	185kW to 630kW
	 

	 	 	 	Schematic Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0027

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC VSD Starter
	 

	 	 	 	185kW to 630kW
	 

	 	 	 	Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0028

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC Incomer
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0029

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC Feeder
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0030

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC Feeder/Contactor
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0031

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Sump Pump
	 

	 	 	 	0.37kW to 30kW
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0032

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Conveyor
	 

	 	 	 	0.37kW to 30kW






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 11






	 	 	 	 	 
	Drawing Number	 	Revision	 	Description
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0033

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Conveyor
	 

	 	 	 	37kW to 45kW
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0034

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Conveyor


55kW to 110kW
	 

	 	 	 	Schematic and Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0035

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Conveyor
	 

	 	 	 	132kW to 150kW
	 

	 	 	 	Schematic Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0036

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Conveyor
	 

	 	 	 	132kW to 150kW
	 

	 	 	 	Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0037

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter — Conveyor
	 

	 	 	 	185kW to 630kW
	 

	 	 	 	Schematic Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0038

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC DOL Starter —  Conveyor
	 

	 	 	 	185kW to 630kW
	 

	 	 	 	Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0039

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC MCC
	 

	 	 	 	24V DC, 48V DC and 110V AC Power
Supplies
	 

	 	 	 	Schematic Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0040

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC MCC
	 

	 	 	 	24V DC, 48V DC and 110V AC Power
Supplies
	 

	 	 	 	Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0041

	 	B
	 	Standard Drawing
	 

	 	 	 	415V AC Soft Starter
	 

	 	 	 	185kW to 630kW
	 

	 	 	 	Schematic Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0042

	 	B
	 	Standard Drawing






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 12






	 	 	 	 	 
	Drawing Number	 	Revision	 	Description
	 

	 	 	 	415V AC Soft Starter
	 

	 	 	 	185kW to 630kW
	 

	 	 	 	Termination Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0080

	 	A
	 	Standard Drawing
	 

	 	 	 	240V AC UPS
	 

	 	 	 	Distribution Board
	 

	 	 	 	Single Line Diagram
	 
	 	 	 	 
	MOPU-0000-E80-0081

	 	A
	 	Standard Drawing
	 

	 	 	 	415V AC Light and Small Power
	 

	 	 	 	Distribution Board
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-0000-E80-0082

	 	A
	 	Standard Drawing
	 

	 	 	 	415V AC Light and Small Power
	 

	 	 	 	Distribution Board
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-0000-E80-0100

	 	A
	 	Standard Drawing
	 

	 	 	 	Electrical Installation Details
Local Control Stations — 0.37kW to 55kW
	 

	 	 	 	General Arrangement
	 
	 	 	 	 
	MOPU-0000-E80-0101

	 	A
	 	Standard Drawing
	 

	 	 	 	Electrical Installation Details
	 

	 	 	 	Local Control Stations — 75kW to 185kW
	 

	 	 	 	General Arrangement
	 
	 	 	 	 
	MOPU-0000-E80-0800

	 	A
	 	Standard Drawing
	 

	 	 	 	Electrical Installation Details
	 

	 	 	 	MCC Cable Glanding Box
	 

	 	 	 	General Arrangement
	 
	 	 	 	 
	MOPU-1314-E22-MC2001A-01

	 	A
	 	Processing Plant
	 

	 	 	 	Primary Crushing
	 

	 	 	 	415V AC MCC 1314-MC2001A
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1314-E22-MC2001A-02

	 	A
	 	Processing Plant
	 

	 	 	 	Primary Crushing
	 

	 	 	 	415V AC MCC 1314-MC2001A
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1314-E22-MC2001B-01

	 	A
	 	Processing Plant
	 

	 	 	 	Primary Crushing
	 

	 	 	 	415V AC MCC 1314-MC2001B






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 13






	 	 	 	 	 
	Drawing Number	 	Revision	 	Description
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1314-E22-MC2001B-02

	 	A
	 	Processing Plant
	 

	 	 	 	Primary Crushing
	 

	 	 	 	415V AC MCC 1314-MC2001B
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1315-E22-MC2051-01

	 	A
	 	Processing Plant
	 

	 	 	 	Primary Conveying
	 

	 	 	 	415V AC MCC 1315-MC2051
	 

	 	 	 	Single Line Diagram
	 
	 	 	 	 
	MOPU-1316-E22-MC2101-01

	 	A
	 	Processing Plant
	 

	 	 	 	Ore Stockpile
	 

	 	 	 	415V AC MCC 1316-MC2101
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1316-E22-MC2101-02

	 	A
	 	Processing Plant
	 

	 	 	 	Ore Stockpile
	 

	 	 	 	415V AC MCC 1316-MC2101
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1316-E22-MC2101-03

	 	A
	 	Processing Plant
	 

	 	 	 	Ore Stockpile
	 

	 	 	 	415V AC MCC 1316-MC2101
	 

	 	 	 	Single Line Diagram (Sheet 3)
	 
	 	 	 	 
	MOPU-1316-E22-MC2101-04

	 	A
	 	Processing Plant
	 

	 	 	 	Ore Stockpile
	 

	 	 	 	415V AC MCC 1316-MC2101
	 

	 	 	 	Single Line Diagram (Sheet 4)
	 
	 	 	 	 
	MOPU-1326-E22-MC2201A-01

	 	A
	 	Processing Plant
	 

	 	 	 	Grinding & Classification — High Grade Ore
	 

	 	 	 	415V AC MCC 1326-MC2201A
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1326-E22-MC2201A-02

	 	A
	 	Processing Plant
	 

	 	 	 	Grinding & Classification — High Grade Ore
	 

	 	 	 	415V AC MCC 1326-MC2201A
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1326-E22-MC2201A-03

	 	A
	 	Processing Plant
	 

	 	 	 	Grinding & Classification — High Grade Ore
	 

	 	 	 	415V AC MCC 1326-MC2201A
	 

	 	 	 	Single Line Diagram (Sheet 3)
	 
	 	 	 	 
	MOPU-1326-E22-MC2201B-01

	 	A
	 	Processing Plant






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 14






	 	 	 	 	 
	Drawing Number	 	Revision	 	Description
	 

	 	 	 	Grinding & Classification — High Grade Ore
	 

	 	 	 	415V AC MCC 1326-MC2201B
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1326-E22-MC2201B-02

	 	A
	 	Processing Plant
	 

	 	 	 	Grinding & Classification — High Grade Ore
	 

	 	 	 	415V AC MCC 1326-MC2201B
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1326-E22-MC2201B-03

	 	A
	 	Processing Plant
	 

	 	 	 	Grinding & Classification — High Grade Ore
	 

	 	 	 	415V AC MCC 1326-MC2201A
	 

	 	 	 	Single Line Diagram (Sheet 3)
	 
	 	 	 	 
	MOPU-1341-E22-MC2741-01

	 	A
	 	Processing Plant
	 

	 	 	 	Grinding Thickener
	 

	 	 	 	415V AC MCC 1341-MC2741
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1341-E22-MC2741-02

	 	A
	 	Processing Plant
	 

	 	 	 	Grinding Thickener
	 

	 	 	 	415V AC MCC 1341-MC2741
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1343-E22-MC2401A-01

	 	A
	 	Processing Plant
	 

	 	 	 	Pressure Oxidation
	 

	 	 	 	415V AC MCC 1343-MC2401A
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1343-E22-MC2401A-02

	 	A
	 	Processing Plant
	 

	 	 	 	Pressure Oxidation
	 

	 	 	 	415V AC MCC 1343-MC2401A
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1343-E22-MC2401B-01

	 	A
	 	Processing Plant
	 

	 	 	 	Pressure Oxidation
	 

	 	 	 	415V AC MCC 1343-MC2401B
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1343-E22-MC2401B-02

	 	A
	 	Processing Plant
	 

	 	 	 	Pressure Oxidation
	 

	 	 	 	415V AC MCC 1343-MC2401B
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1343-E22-MC2401C-01

	 	A
	 	Processing Plant
	 

	 	 	 	Pressure Oxidation
	 

	 	 	 	415V AC MCC 1343-MC2401C






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 15






	 	 	 	 	 
	Drawing Number	 	Revision	 	Description
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1343-E22-MC2401C-02

	 	A
	 	Processing Plant
	 

	 	 	 	Pressure Oxidation
	 

	 	 	 	415V AC MCC 1343-MC2401C
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1343-E22-MC2401D-01

	 	A
	 	Processing Plant
	 

	 	 	 	Pressure Oxidation
	 

	 	 	 	415V AC MCC 1343-MC2401D
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1343-E22-MC2401D-02

	 	A
	 	Processing Plant
	 

	 	 	 	Pressure Oxidation
	 

	 	 	 	415V AC MCC 1343-MC2401D
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1351-E22-MC2551A-01

	 	A
	 	Processing Plant
	 

	 	 	 	Cyanidation & Adsorption
	 

	 	 	 	415V AC MCC 1351-MC2551A
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1351-E22-MC2551A-02

	 	A
	 	Processing Plant
	 

	 	 	 	Cyanidation & Adsorption
	 

	 	 	 	415V AC MCC 1351-MC2551A
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1351-E22-MC2551A-03

	 	A
	 	Processing Plant
	 

	 	 	 	Cyanidation & Adsorption
	 

	 	 	 	415V AC MCC 1351-MC2551A
	 

	 	 	 	Single Line Diagram (Sheet 3)
	 
	 	 	 	 
	MOPU-1351-E22-MC2551A-04

	 	A
	 	Processing Plant
	 

	 	 	 	Cyanidation & Adsorption
	 

	 	 	 	415V AC MCC 1351-MC2551A
	 

	 	 	 	Single Line Diagram (Sheet 4)
	 
	 	 	 	 
	MOPU-1351-E22-MC2551B-01

	 	A
	 	Processing Plant
	 

	 	 	 	Cyanidation & Adsorption
	 

	 	 	 	415V AC MCC 1351-MC2551B
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1351-E22-MC2551B-02

	 	A
	 	Processing Plant
	 

	 	 	 	Cyanidation & Adsorption
	 

	 	 	 	415V AC MCC 1351-MC2551B
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1351-E22-MC2551B-03

	 	A
	 	Processing Plant






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 16






	 	 	 	 	 
	Drawing Number	 	Revision	 	Description
	 

	 	 	 	Cyanidation & Adsorption
	 

	 	 	 	415V AC MCC 1351-MC2551B
	 

	 	 	 	Single Line Diagram (Sheet 3)
	 
	 	 	 	 
	MOPU-1351-E22-MC2551B-04

	 	A
	 	Processing Plant
	 

	 	 	 	Cyanidation & Adsorption
	 

	 	 	 	415V AC MCC 1351-MC2551B
	 

	 	 	 	Single Line Diagram (Sheet 4)
	 
	 	 	 	 
	MOPU-1351-E22-MC2551B-05

	 	A
	 	Processing Plant
	 

	 	 	 	Cyanidation & Adsorption
	 

	 	 	 	415V AC MCC 1351-MC2551B
	 

	 	 	 	Single Line Diagram (Sheet 5)
	 
	 	 	 	 
	MOPU-1560-E22-MC2561-01

	 	A
	 	Processing Plant
	 

	 	 	 	New Oxygen Plant
	 

	 	 	 	415V AC MCC 1560-MC2561
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1560-E22-MC2561-02

	 	A
	 	Processing Plant
	 

	 	 	 	New Oxygen Plant
	 

	 	 	 	415V AC MCC 1560-MC2561
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1560-E22-MC2561-03

	 	A
	 	Processing Plant
	 

	 	 	 	New Oxygen Plant
	 

	 	 	 	415V AC MCC 1560-MC2561
	 

	 	 	 	Single Line Diagram (Sheet 3)
	 
	 	 	 	 
	MOPU-1560-E22-MC2561-04

	 	A
	 	Processing Plant
	 

	 	 	 	New Oxygen Plant
	 

	 	 	 	415V AC MCC 1560-MC2561
	 

	 	 	 	Single Line Diagram (Sheet 4)
	 
	 	 	 	 
	MOPU-1560-E22-MC2561-05

	 	A
	 	Processing Plant
	 

	 	 	 	New Oxygen Plant
	 

	 	 	 	415V AC MCC 1560-MC2561
	 

	 	 	 	Single Line Diagram (Sheet 5)
	 
	 	 	 	 
	MOPU-1825-E22-MC2160-01

	 	A
	 	Processing Plant
	 

	 	 	 	Wurtol Weir and Pump Station
	 

	 	 	 	415V AC MCC 1825-MC2160
	 

	 	 	 	Single Line Diagram
	 
	 	 	 	 
	MOPU-1830-E22-MC2850-01

	 	A
	 	Processing Plant
	 

	 	 	 	Process Sea Water
	 

	 	 	 	415V AC MCC 1830-MC2850






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 17






	 	 	 	 	 
	Drawing Number	 	Revision	 	Description
	 

	 	 	 	Single Line Diagram
	 
	 	 	 	 
	MOPU-1780-E22-MC2931-01

	 	A
	 	Electrical Distribution
	 

	 	 	 	Power Transmission to Site
	 

	 	 	 	415V AC MCC 1780-MC2931
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1780-E22-MC2931-02

	 	A
	 	Electrical Distribution
	 

	 	 	 	Power Transmission to Site
	 

	 	 	 	415V AC MCC 1780-MC2931
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1780-E22-MC2932-01

	 	A
	 	Electrical Distribution
	 

	 	 	 	Power Transmission to Site
	 

	 	 	 	415V AC MCC 1780-MC2932
	 

	 	 	 	Single Line Diagram (Sheet 1)
	 
	 	 	 	 
	MOPU-1780-E22-MC2932-02

	 	A
	 	Electrical Distribution
	 

	 	 	 	Power Transmission to Site
	 

	 	 	 	415V AC MCC 1780-MC2932
	 

	 	 	 	Single Line Diagram (Sheet 2)
	 
	 	 	 	 
	MOPU-1314-E56-SS2001-01

	 	B
	 	Processing Plant
	 

	 	 	 	Primary Crushing
	 

	 	 	 	SS2001 Substation
	 

	 	 	 	Equipment Layout
	 
	 	 	 	 
	MOPU-1315-E56-SS2051-01

	 	B
	 	Processing Plant
	 

	 	 	 	Primary Conveying
	 

	 	 	 	SS2251 Substation
	 

	 	 	 	Equipment Layout
	 
	 	 	 	 
	MOPU-1316-E56-SS2101-01

	 	B
	 	Processing Plant
	 

	 	 	 	Ore Stockpile
	 

	 	 	 	SS2101 Substation
	 

	 	 	 	Equipment Layout
	 
	 	 	 	 
	MOPU-1326-E56-SS2200-01

	 	C
	 	Processing Plant
	 

	 	 	 	Grinding & Classification — High Grade Ore
	 

	 	 	 	SS2200 Substation
	 

	 	 	 	Equipment Layout
	 
	 	 	 	 
	MOPU-1341-E56-SS2741-01

	 	B
	 	Processing Plant
	 

	 	 	 	Grinding Thickener
	 

	 	 	 	SS2741 Substation
	 

	 	 	 	Equipment Layout
	 
	 	 	 	 
	MOPU-1343-E56-SS2400-01

	 	B
	 	Processing Plant






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 






			
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 18






	 	 	 	 	 
	Drawing Number	 	Revision	 	Description
	 

	 	 	 	Pressure Oxidation
	 

	 	 	 	SS2400 Substation
	 

	 	 	 	Equipment Layout
	 
	 	 	 	 
	MOPU-1351-E56-SS2551-01

	 	B
	 	Processing Plant
	 

	 	 	 	Cyanidation & Adsorption
	 

	 	 	 	SS2551 Substation
	 

	 	 	 	Equipment Layout
	 
	 	 	 	 
	MOPU-1560-E56-SS2560-01

	 	B
	 	Processing Plant
	 

	 	 	 	New Oxygen Plant
	 

	 	 	 	SS2560 Substation
	 

	 	 	 	Equipment Layout
	 
	 	 	 	 
	MOPU-1825-E56-SS2160-01

	 	B
	 	Processing Plant
	 

	 	 	 	Wurtol Weir and Pump Station
	 

	 	 	 	SS2160 Substation
	 

	 	 	 	Equipment Layout
	 
	 	 	 	 
	MOPU-1830-E56-SS2850-01

	 	B
	 	Processing Plant
	 

	 	 	 	Process Seawater
	 

	 	 	 	SS2850 Substation
	 

	 	 	 	Equipment Layout
	 
	 	 	 	 
	MOPU-1780-E56-SS2931-01

	 	B
	 	Electrical Distribution
	 

	 	 	 	Power Transmission to Site
	 

	 	 	 	SS2931 Substation
	 

	 	 	 	Equipment Layout
	 
	 	 	 	 
	MOPU-1780-E56-SS2931-02

	 	B
	 	Electrical Distribution
	 

	 	 	 	Power Transmission to Site
	 

	 	 	 	SS2931 Substation
	 

	 	 	 	Section A
	 
	 	 	 	 
	MOPU-1780-E56-SS2932-01

	 	B
	 	Electrical Distribution
	 

	 	 	 	Power Transmission to Site
	 

	 	 	 	SS2932 Substation
	 

	 	 	 	Equipment Layout
	 
	 	 	 	 
	MOPU-1780-E56-SS2932-02

	 	B
	 	Electrical Distribution
	 

	 	 	 	Power Transmission to Site
	 

	 	 	 	SS2932 Substation
	 

	 	 	 	Section A






			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008







 











 





			
	 	 	 
	MOPU-1101	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS	 	PAGE 19





13 SCOPE OF SUPPLY


The successful Tenderer will be required to supply each transportable switchroom
(including necessary lifting equipment) and install all equipment within the switchroom. The list
of equipment below indicates the scope required for each major item (i.e. supply, install, both or
excluded).


The successful Tenderer will be required to install cable ladder beneath the switchroom within
the confines of the sub-floor beams and install cabling between items of equipment which are
installed within the switchroom. In addition the Tenderer shall supply and install cable glanding
boxes to be mounted below each MCC (see standard installation drawing) in the sub-floor area.



	 	 	 	 	 
	Equipment	 	 	 	 
	Number	 	Description	 	Scope
	 
	 	LV MOTOR CONTROL CENTRES	 	 
	MC2001A
	 	Primary Crushing MCC A	 	Supply + Install
	MC2001B
	 	Primary Crushing MCC B	 	Supply + Install
	MC2051
	 	Primary Conveyor MCC	 	Supply + Install
	MC2101
	 	Ore Stockpile MCC	 	Supply + Install
	MC2160
	 	Wurtol Weir and Pump Station MCC	 	Supply + Install
	MC2201A
	 	Grinding & Classification MCC A	 	Supply + Install
	MC2201B
	 	Grinding & Classification MCC B	 	Supply + Install
	MC2401A
	 	Pressure Oxidation MCC A	 	Supply + Install
	MC2401B
	 	Pressure Oxidation MCC B	 	Supply + Install
	MC2401C
	 	Pressure Oxidation MCC C	 	Supply + Install
	MC2401D
	 	Pressure Oxidation MCC D	 	Supply + Install
	MC2551A
	 	Cyanidation & Adsorption MCC A	 	Supply + Install
	MC2551B
	 	Cyanidation & Adsorption MCC B	 	Supply + Install
	MC2561A
	 	Oxygen Plant MCC A	 	Supply + Install
	MC2561B
	 	Oxygen Plant MCC B	 	Supply + Install
	MC2741
	 	Grinding Thickeners MCC	 	Supply + Install
	MC2850
	 	Process Seawater MCC	 	Supply + Install
	MC2931
	 	Bus E Auxilliary MCC	 	Supply + Install
	MC2932
	 	Bus F Auxilliary MCC	 	Supply + Install
	 
	 	SWITCHROOMS	 	 
	SS2001A
	 	Primary Crushing LV Switchroom	 	Supply Only
	SS2001B
	 	Primary Crushing HV Switchroom	 	Supply Only
	SS2051
	 	Primary Conveying LV Switchroom	 	Supply Only
	SS2101
	 	Primary Conveying & Ore Stockpile LV Switchroom	 	Supply Only





			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms	 	      28/07/2008




 







 





			
	 	 	 
	MOPU-1101	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS	 	PAGE 20





	 	 	 	 	 
	Equipment	 	 	 	 
	Number	 	Description	 	Scope
	SS2160
	 	Wurtol Weir and Pump Station LV Switchroom	 	Supply Only
	SS2200A
	 	Grinding Area LV Switchroom	 	Supply Only
	SS2200B
	 	Grinding Area HV Switchroom	 	Supply Only
	SS2400A
	 	Pressure Oxidation LV Switchroom	 	Supply Only
	SS2400B
	 	Pressure Oxidation HV Switchroom	 	Supply Only
	SS2551A
	 	Cyanidation & Adsorption LV Switchroom	 	Supply Only
	SS2551 B
	 	Cyanidation & Adsorption HV Switchroom	 	Supply Only
	SS2560A
	 	Oxygen Plant LV Switchroom	 	Supply Only
	SS2560B
	 	Oxygen Plant HV Switchroom	 	Supply Only
	SS2741
	 	Grinding Thickeners LV Switchroom	 	Supply Only
	SS2850
	 	Process Seawater LV Switchroom	 	Supply Only
	SS2931A
	 	Bus C3, C4 & E LV Switchroom	 	Supply Only
	SS2931B
	 	Bus C3, C4 HV Switchroom	 	Supply Only
	SS2931C
	 	Bus E HV Switchroom	 	Supply Only
	SS2932A
	 	Bus F LV Switchroom	 	Supply Only
	SS2932B
	 	Bus F HV Switchroom	 	Supply Only
	 
	 	DISTRIBUTION BOARDS	 	 
	DB2001A
	 	Primary Crushing LV Switchroom Light &
Power Distribution Board 36 pole, 415V, 250A,
20kA/0.2s, IP42	 	Supply + Install
	DB2001B
	 	Primary Crushing HV Switchroom Light &
Power Distribution Board 36 pole, 415V, 250A,
20kA/0.2s, IP42	 	Supply + Install
	DB2001C
	 	Primary Crushing UPS Distribution Board 24 pole, 240V,
160A, 20kA/0.2s, IP42	 	Supply + Install
	DB2001D
	 	Primary Crushing Area Distribution Board 72 pole, 415V,
250A, 20kA/0.2s, IP42 with Lighting Control Section	 	Supply + Install
	DB2051A
	 	Primary Conveying LV Switchroom Light &
Power Distribution Board 36 pole, 415V, 250A,
20kA/0.2s, IP42	 	Supply + Install
	DB2051B
	 	Primary Conveying UPS Distribution Board 24 pole, 240V,
160A, 20kA/0.2s, IP42	 	Supply + Install
	DB2051C
	 	Primary Conveying Area Distribution Board 72
pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting
Control Section	 	Supply + Install
	DB2101A
	 	Ore Stockpile LV Switchroom Light & Power Distribution
Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	Supply + Install
	DB2101B
	 	Ore Stockpile UPS Distribution Board 24 pole, 240V,
160A, 20kA/0.2s, IP42	 	Supply + Install
	DB2101C
	 	Ore Stockpile Area Distribution Board 72 pole, 415V,
250A, 20kA/0.2s, IP42 with Lighting Control Section	 	Supply + Install
	DB2160A
	 	Wurtol Pumping Station LV Switchroom Light & Power
Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	Supply + Install
	DB2160B
	 	Wurtol Pumping Station UPS Distribution Board 24 pole,	 	Supply + Install





			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms	 	28/07/2008 




 







 





			
	 	 	 
	MOPU-1101	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS	 	PAGE 21





	 	 	 	 	 
	Equipment	 	 	 	 
	Number	 	Description	 	Scope
	 
	 	240V, 160A, 20kA/0.2s, IP42	 	 
	DB2160C
	 	Wurtol Pumping Station Area Distribution Board 72 pole,
415V, 250A, 20kA/0.2s, IP42 with Lighting Control
Section	 	Supply + Install
	DB2201A
	 	Grinding LV Switchroom Light & Power Distribution Board
72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control
Section	 	Supply + Install
	DB2201B
	 	Grinding HV Switchroom Light & Power Distribution Board
72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting
Control Section	 	Supply + Install
	DB2201C
	 	Grinding UPS Distribution Board 24 pole, 240V, 160A,
20kA/0.2s, IP42	 	Supply + Install
	DB2201D
	 	Grinding Area Light & Power Distribution Board 72 pole,
415V, 250A, 20kA/0.2s, IP42 with Lighting Control
Section	 	Supply + Install
	DB2401A
	 	Pressure Oxidation LV Switchroom Light &
Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s,
IP42	 	Supply + Install
	DB2401B
	 	Pressure Oxidation HV Switchroom Light & Power
Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	Supply + Install
	DB2401C
	 	Pressure Oxidation UPS Distribution Board 24 pole,
240V, 160A, 20kA/0.2s, IP42	 	Supply + Install
	DB2401D
	 	Pressure Oxidation Area Distribution Board 72 pole,
415V, 250A, 20kA/0.2s, IP42 with Lighting Control
Section	 	Supply + Install
	DB2551A
	 	Cyanidation & Adsorption LV Switchroom Light & Power
Distribution Board 36 pole, 415V, 250A, 20kA/0.2s	 	Supply + Install
	DB2551B
	 	Cyanidation & Adsorption HV Switchroom Light & Power
Distribution Board 36 pole, 415V, 250A, 20kA/0.2s	 	Supply + Install
	DB2551C
	 	Cyanidation & Adsorption UPS Distribution Board 24 pole,
240V, 160A, 20kA/0.2s, IP42	 	Supply + Install
	DB2551D
	 	Cyanidation & Adsorption Area Distribution Board 72 pole, 415V,
250A, 20kA/0.2s, IP42 with Lighting Control Section	 	Supply + Install
	DB2561A
	 	Oxygen Plant LV Switchroom Light & Power Distribution
Board 36 pole, 415V, 250A, 20kA/0.2s	 	Supply + Install
	DB2561B
	 	Oxygen Plant HV Switchroom Light & Power Distribution
Board 36 pole, 415V, 250A, 20kA/0.2s	 	Supply + Install
	DB2561C
	 	Oxygen Plant UPS Distribution Board 24 pole, 240V, 160A,
20kA/0.2s, IP42	 	Supply + Install
	DB2561D
	 	Oxygen Plant Area Distribution Board 72 pole, 415V, 250A,
20kA/0.2s, IP42 with Lighting Control Section	 	Supply + Install
	DB2741A
	 	Grinding Thickeners LV Switchroom Light & Power
Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	Supply + Install
	DB2741B
	 	Grinding Thickeners UPS Distribution Board 24 pole,
240V, 160A, 20kA/0.2s, IP42	 	Supply + Install
	DB2741C
	 	Grinding Thickeners Area Distribution Board 72 pole,	 	Supply + Install





			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms	 	28/07/2008 




 







 





			
	 	 	 
	MOPU-1101	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS	 	PAGE 22





	 	 	 	 	 
	Equipment	 	 	 	 
	Number	 	Description	 	Scope
	 
	 	415V, 250A, 20kA/0.2s, IP42 with Lighting
Control Section	 	 
	DB2850A
	 	Process Seawater LV Switchroom Light &
Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s,
IP42	 	Supply + Install
	DB2850B
	 	Process Seawater Area Distribution Board 72 pole,
415V, 250A, 20kA/0.2s, IP42 with Lighting Control
Section	 	Supply + Install
	DB2931A
	 	Bus C3, C4 & E Switchroom Light & Power
Distribution Board 72 pole, 415V, 250A, 20kA/0.2s,
IP42	 	Supply + Install
	DB2931B
	 	Bus C3, C4 & E UPS Distribution Board 24 pole,
240V, 160A, 20kA/0.2s, IP42	 	Supply + Install
	DB2932A
	 	Bus F Switchroom Light & Power Distribution Board
72 pole, 415V, 250A, 20kA/0.2s, IP42	 	Supply + Install
	DB2932B
	 	Bus F UPS Distribution Board 24 pole, 240V,
160A, 20kA/0.2s, IP42	 	Supply + Install
	 
	 	UNINTERRUPTIBLE POWER SUPPLIES	 	 
	UP2001
	 	Primary Crushing LV Switchroom UPS 12kVA, 415V
three phase in, 240V single phase out	 	Supply + install
	UP2051
	 	Primary Conveying LV Switchroom UPS 8kVA, 415V
three phase in, 240V single phase out	 	Supply + Install
	UP2101
	 	Ore Stockpile LV Switchroom UPS 8kVA, 415V three
phase in, 240V single phase out	 	Supply + Install
	UP2160
	 	Wurtol Pumping Station LV Switchroom UPS 8kVA,
415V three phase in, 240V single phase out	 	Supply + Install
	UP2201
	 	Grinding Area LV Switchroom UPS 12kVA, 415V three
phase in, 240V single phase out	 	Supply + Install
	UP2401
	 	Pressure Oxidation LV Switchroom UPS 12kVA, 415V
three phase in, 240V single phase out	 	Supply + Install
	UP2551
	 	Cyanidation & Adsorption LV Switchroom UPS 12kVA,
415V three phase in, 240V single phase out	 	Supply + Install
	P520
	 	Oxygen Plant LV Switchroom UPS 12kVA, 415V three
phase in, 240V single phase out	 	Supply + Install
	UP2741
	 	Grinding Thickeners LV Switchroom UPS 8kVA, 415V
three phase in, 240V single phase out	 	Supply + Install
	UP2931
	 	33kV Bus E Switchroom UPS 8kVA, 415V three phase
in, 240V single phase out	 	Supply + Install
	UP2932
	 	33kV Bus F Switchroom UPS 8kVA, 415V three phase
in, 240V single phase out	 	Supply + Install
	 
	 	CONTROL PANELS	 	 
	CP2001A
	 	Primary Crushing LV Switchroom DCS Panel A	 	Install Only (Free Issue)
	CP2001B
	 	Primary Crushing LV Switchroom DCS Panel B	 	Install Only (Free Issue)
	CP2051
	 	Primary Conveying LV Switchroom DCS Panel	 	Install Only (Free Issue)





			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms	 	28/07/2008 




 







 





			
	 	 	 
	MOPU-1101
LOW VOLTAGE MCCS AND SWITCHROOMS	 	SECTION III — DETAILED SPECIFICATION

PAGE 23





	 	 	 	 	 
	Equipment	 	 	 	 
	Number	 	Description	 	Scope
	CP2101
	 	Ore Stockpile LV Switchroom DCS Panel	 	Install Only (Free Issue)
	CP2401A
	 	Pressure Oxidation LV Switchroom DCS Panel A	 	Install Only (Free Issue)
	CP2401B
	 	Pressure Oxidation LV Switchroom DCS Panel B	 	Install Only (Free Issue)
	CP2551A
	 	Cyanidation & Adsorption LV Switchroom DCS Panel A	 	Install Only (Free Issue)
	CP2551B
	 	Cyanidation & Adsorption LV Switchroom DCS Panel B	 	Install Only (Free Issue)
	CP2560A
	 	Oxygen Plant LV Switchroom DCS Panel A	 	Install Only (Free Issue)
	CP2560B
	 	Oxygen Plant LV Switchroom DCS Panel B	 	Install Only (Free Issue)
	CP2741
	 	Grinding Thickeners LV Switchroom DCS Panel	 	Install Only (Free Issue)
	Lot
	 	DCS Panels Marshalling	 	Supply + Install
	CP2160
	 	Wurtol Pumping Station LV Switchroom PLC Panel	 	Install Only (Free Issue)
	CP2850
	 	 Process Seawater LV Switchroom Control Panel	 	Install Only (Free Issue)
	CP2603
	 	Oxygen Plant Hardwired Emergency Trip Panel	 	Install Only (Free Issue)
	CP2900A
	 	SW2900 Tariff Metering Panel	 	Install Only (Free Issue)
	CP2931A
	 	Bus C3, C4 & E Switchroom PLC Panel	 	Install Only (Free Issue)
	CP2932A
	 	Bus F Switchroom PLC Panel	 	Install Only (Free Issue)
	Lot
	 	19” Rack Mounted Fibre Optic Breakout Panels	 	Install Only (Free Issue)
	 
	 	BATTERY CHARGERS	 	 
	BC2000
	 	Primary Crushing HV Switchroom 48VDC, 70Ahr	 	Supply + Install
	BC2200
	 	Grinding Area HV Switchroom 48VDC, 70Ahr	 	Supply + Install
	BC2400
	 	Pressure Oxidation HV Switchroom 48VDC, 70Ahr	 	Supply + Install
	BC2550
	 	Cyanidation & Adsorption HV Switchroom 48VDC, 70Ahr	 	Supply + Install
	BC2560
	 	Oxygen Plant HV Switchroom 48VDC, 160Ahr	 	Supply + Install
	BC2900
	 	Bus C3 & C4 HV Switchroom 48VDC, 160Ahr	 	Supply + Install
	BC2931
	 	Bus E HV Switchroom 48VDC, 230Ahr	 	Supply + Install
	BC2932
	 	Bus F HV Switchroom 48VDC, 230Ahr	 	Supply + Install
	 
	 	HV SWITCHBOARDS	 	 
	SW2000
	 	Primary Crushing 11kV Switchboard	 	Install Only (Free Issue)





			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms	 	28/07/2008 




 







 





			
	 	 	 
	MOPU-1101	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS	 	PAGE 24





	 	 	 	 	 
	Equipment	 	 	 	 
	Number	 	Description	 	Scope
	SW2001
	 	HGO Crusher 3.3kV Switchboard	 	Install Only (Free Issue)
	SW2200
	 	Grinding 11kV Switchboard	 	Install Only (Free Issue)
	SW2400
	 	Pressure Oxidation 11kV Switchboard	 	Install Only (Free Issue)
	SW2550
	 	Cyanidation & Adsorption 11kV Switch board	 	Install Only (Free Issue)
	SW2560
	 	Oxygen Plant 11kV Switchboard	 	Install Only (Free Issue)
	SW2900
	 	Bus C3 & C4 11kV Switchboard	 	Install Only (Free Issue)
	SW2931
	 	Bus E 33kV Switchboard	 	Install Only (Free Issue)
	SW2932
	 	Bus F 33kV Switchboard	 	Install Only (Free Issue)
	 
	 	REMOTE SWITCHING PANELS	 	 
	CP2000
	 	Primary Crushing 3.3 & 11kV Remote Switching Panel	 	Install Only (Free Issue)
	CP2200
	 	Grinding 11kV Remote Switching Panel	 	Install Only (Free Issue)
	CP2400
	 	Pressure Oxidation 11kV Remote Switching Panel	 	Install Only (Free Issue)
	CP2550
	 	Cyanidation & Adsorption 11kV Remote Switching Panel	 	Install Only (Free Issue)
	CP2560
	 	Oxygen Plant 11kV Remote Switching Panel	 	Install Only (Free Issue)
	CP2900
	 	Bus C3 & C4 11kV Remote Switching Panel	 	Install Only (Free Issue)
	CP2931
	 	Bus E 33kV Remote Switching Panel	 	Install Only (Free Issue)
	CP2932
	 	Bus F 33kV Remote Switching Panel	 	Install Only (Free Issue)
	 
	 	VARIABLE SPEED DRIVES	 	 
	Lot
	 	Variable Speed Drives (as per attached schedule)	 	Install Only (Free Issue)
	 
	 	LOCAL CONTROL STATIONS	 	 
	Lot
	 	Local Control Stations (as per attached schedule)	 	Supply Only





			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms	 	28/07/2008





 








 





			
	 	 	 
	MOPU-1101	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS	 	PAGE 26





14 REQUIRED DELIVERY DATES


The successful Tenderer will be required to supply the equipment to meet the following
required ex-works delivery dates.



	 	 	 	 	 
	Equipment	 	 	 	 
	Number	 	Description	 	Delivery Date
	 
	 	COMPLETE SWITCHROOMS INC. EQUIPMENT+LCS	 	 
	SS2001A
	 	Primary Crushing LV Switchroom	 	16th September 2009
	SS2001B
	 	Primary Crushing HV Switchroom	 	16th September 2009
	SS2051
	 	Primary Conveying LV Switchroom	 	15th September 2009
	SS2101
	 	Ore Stockpile LV Switchroom	 	15th September 2009
	SS2160
	 	Wurtol Weir and Pump Station LV Switchroom	 	14th July 2009
	SS2200A
	 	Grinding Area LV Switchroom	 	15th September 2009
	SS2200B
	 	Grinding Area HV Switchroom	 	15th September 2009
	SS2400A
	 	Pressure Oxidation LV Switchroom	 	13th October 2009
	SS2400B
	 	Pressure Oxidation HV Switchroom	 	13th October 2009
	SS2551A
	 	Cyanidation & Adsorption LV Switchroom	 	29th July 2009
	SS2551B
	 	Cyanidation & Adsorption HV Switchroom	 	29th July 2009
	SS2560A
	 	Oxygen Plant LV Switchroom	 	20th October 2009
	SS2560B
	 	Oxygen Plant HV Switchroom	 	20th October 2009
	SS2741
	 	Grinding Thickener LV Switchroom	 	9th June 2009
	SS2850
	 	Process Seawater LV Switchroom	 	13th October 2009
	SS2931A
	 	Bus C3, C4 & E LV Switchroom	 	12th August 2009
	SS2931B
	 	Bus C3, C4 HV Switchroom	 	12th August 2009
	SS2931C
	 	Bus E HV Switchroom	 	12th August 2009
	SS2932A
	 	Bus F LV Switchroom	 	23rd July 2009
	SS2932B
	 	Bus F HV Switchroom	 	23rd July 2009





			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms	 	28/07/2008




 







 





			
	 	 	 
	MOPU-1101	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS	 	PAGE 27





15 PREFERRED EQUIPMENT SUPPLIERS


The Successful Tenderer will be required to supply equipment conforming to the list below.


Tenderers may also provide pricing for an alternative equipment type in addition to pricing
for the preferred equipment. Any deviations from this list shall be listed and explained in the
Bidder’s proposal.


Tenderers must provide pricing for switchrooms manufactured by both of the preferred
suppliers. Contact details for these suppliers are listed in Section 16.



	 	 	 	 	 
	Equipment Type	 	Supplier	 	Range/ Part No.
	MCCs
	 	 	 	 
	Motor Protection Relays ≤110kW
	 	 	 	S+S CEP-7C3
	Motor Protection Relays ≥132kW
	 	 	 	Multilin MM300
	Contactors
	 	 	 	 
	Circuit Breakers for MCC Motor Protection
	 	 	 	NZMH2-M40
NZMH2-M63
	 
	 	 	 	NZMH2-M100
	 
	 	 	 	NZMH2-M160
	 
	 	 	 	NZMH3-ME220
	 
	 	 	 	NZMH3-ME350
	 
	 	 	 	NZMH3-ME450
	 
	 	 	 	NZMH4-ME550
	 
	 	 	 	NZMH4-ME1400
	Circuit Breakers for MCC Feeder Protection
	 	 	 	NZMH2-A40

NZMH2-A63
	 
	 	 	 	NZMH2-A100
	 
	 	 	 	NZMH2-A160
	 
	 	 	 	NZMH3-AE200
	 
	 	 	 	NZMH3-AE250
	 
	 	 	 	NZMH3-AE400
	 
	 	 	 	NZMH4-AE630
	 
	 	 	 	NZMH4-AE1250
	LV Control Circuit Breakers
	 	 	 	 
	LV Control Fuses
	 	 	 	RS32 series
	Incomer Protection
	 	 	 	Terasaki AR-S Series
	Incomer Metering
	 	 	 	Integra 520 Series
	Earth Leakage Relays
	 	 	 	ELR-2M
	I/O Modules
	 	 	 	1794-IA8 and 1794-OA8





			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchroom	 	28/07/2008 




 







 





			
	 	 	 
	MOPU-1101

LOW VOLTAGE MCCS AND SWITCHROOMS	 	SECTION III — DETAILED SPECIFICATION

PAGE 28





	 	 	 	 	 
	Equipment Type	 	Supplier	 	Range/ Part No.
	I/O Adaptors
	 	 	 	1794-ADN
	RTD Monitors
	 	 	 	XM-361 and XM-441
	Control Relays
	 	 	 	LY Series
	Switched Mode Power Supplies
	 	 	 	QUINT Power Series
	Indicators
	 	 	 	S+S D7 Series (LED)
	Pushbuttons
	 	 	 	S+S D7 Series (Flush)
	Selector Switches
	 	 	 	CA10 Series
	Terminals
	 	 	 	WDU Series
	Switchrooms
	 	 	 	 
	Transportable Rooms
	 	 	 	 
	Smoke Detection Systems
	 	 	 	Laser Plus
	Air Conditioners
	 	 	 	Split System
	Lighting (Interior)
	 	 	 	Project Batten PB/CE Range
	Lighting (Exterior)
	 	 	 	Stradalux STR Range
	Distribution Boards
	 	 	 	 
	Boards
	 	 	 	Concept Plus Range
	Circuit Breakers
	 	 	 	Terasaki
	Uninterruptible Power Supplies
	 	 	 	 
	UPS Units
	 	 	 	9155
	Surge Reduction Filters
	 	 	 	Critec TSG-SRF (Wall Mount)
	Battery Charger Systems
	 	 	 	 
	Battery Chargers
	 	 	 	MCR-II
	Batteries
	 	 	 	VRLA
	Local Control Stations
	 	 	 	 
	Isolators	 	 	 	Socomec 32BR (Side Operated)
	Indicators	 	 	 	C-H E34 Series (LED)
	Pushbuttons	 	 	 	C-H E34 Series (Flush Booted)
	Terminals	 	 	 	WDU Series





			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms	 	28/07/2008




 







 





			
	 	 	 
	MOPU-1101	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS	 	PAGE 29




16 EQUIPMENT SUPPLIERS CONTACT DETAILS


The contact details for the preferred switchroom manufacturers are as follows:



			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms	 	28/07/2008




 








 





			
	 	 	 
	MOPU-1101
	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS
	 	PAGE 30






17 BATTERY LIMITS



The Contract Battery Limits for the Scope of Work are as follows:





	 	Ø	 	 Incoming and outgoing power terminals of the wall mounted VSDs.
	 
	 	Ø	 	Outgoing power terminals of each feeder and Motor Starter within the MCCs.
	 
	 	Ø	 	Field control and instrument marshalling terminals in the DCS Panels.
	 
	 	Ø	 	Incoming power terminals of the MCC main incomers.
	 
	 	Ø	 	 Structural steel supports for mounting on concrete foundations.





			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms
	 	28/07/2008






 









 





			
	 	 	 
	MOPU-1101	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS	 	PAGE 31





18 APPENDIX A — TECHNICAL DATASHEETS



			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms	 	28/07/2008




 







 





			
	 	 	 
	MOPU-1101	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS	 	PAGE 32





19 APPENDIX B — DRAWINGS



			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms	 	28/07/2008




 







 





			
	 	 	 
	MOPU-1101	 	SECTION III — DETAILED SPECIFICATION
	LOW VOLTAGE MCCS AND SWITCHROOMS	 	PAGE 33





20 APPENDIX C — SPECIFICATIONS



			
	 	 	 
	Section III MOPU-1101-00-S LV MCCs and Switchrooms	 	28/07/2008




 







 




LGL


MILLION OUNCE PLANT UPGRADE (MOPU) PROJECT
EQUIPMENT SUPPLY TENDER


MOPU-1101
LOW VOLTAGE MCCs & SWITCH ROOMS


SECTION IV

FORM OF TENDER



	 	 	 
	Date:
	 	5/01/2009
	Name of Tenderer:
	 	PLUMMERS INDUSTRIES PTY LTD
	Proposal Number:
	 	Q 4929
	Validity of Proposal:
	 	90 DAYS
	Equipment:
	 	MCCS AND SWITCHROOMS
	Make:
	 	PI 2000 (MCC’s)
	Model:
	 	 
	Type:
	 	 
	Manufacturer:
	 	PLUMMERS INDUSTRIES PTY LTD
	Dealer distributor in Country:
	 	PLUMMERS INDUSTRIES PTY LTD QLD




 







 




PRICING SUMMARY

MOPU-1101 -Low Voltage MCCs & Switchrooms

Tenderer’s Name: PLUMMERS INDUSTRIES PTY


All prices to be in Australian or US currency (refer clause 4 of Section I Part A)



			
	 	 	 
	Currency of Manufacturer’s Quotation	 	 
	Location of Seller’s Premises
	 	BRISBANE AUSTRALIA





	 	 	 	 	 	 	 	 	 
	Table 1.1 Cost Breakdown	 	UOM	 	QTY	 	Unit Cost	 	Extended
	Refer Attached Pricing Schedules
	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 
	Equipment Options
	 	EA	 	 	 	 	 	 
	Special Tools
	 	EA	 	 	 	 	 	 
	Extended Warranty Costs (if applicable)
	 	EA	 	 	 	 	 	 
	Discount (if any)
	 	EA	 	 	 	 	 	 
	Export Packing
	 	EA	 	 	 	 	 	 
	Loading to Transport
	 	EA	 	 	 	 	 	 
	Forward Cover Foreign Currency Risk (if any)
	 	EA	 	 	 	 	 	 
	Subtotal FCA (Incoterms 2000) Point of Manufacture





	 	 	 	 	 	 	 	 	 
	Freight/Logistics Cost Breakdown	 	UOM	 	QTY	 	Unit Cost	 	Extended
	Freight to nearest Seaport (Nomiate)
	 	EA	 	 	 	 	 	 
	Customs/Port Terminal Charges (if any)
	 	EA	 	 	 	 	 	 
	Forward Cover Foreign Currency Risk
(if any)
	 	EA	 	 	 	 	 	 
	Subtotal FOB (Incoterms 2000) Seaport
	 	 	 	 
	 
	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	TOTAL FOB COST	 	 




 







 




COMMERCIAL DETAILS


Equipment Tender # and Description

Tenderer’s Name: PLUMMERS INDUSTRIES PTY LTD


Tenderer’s Proposed Terms of Payment (Include details)

See cover letter


Cancellation Charges (Include details such as schedule and values)


As per progress items claims


Point(s) of Manufacture

Specify City and State (if applicable) for each point(s) of supply

BRISBANE QUEENSLAND


Shipment Location

75 Wolston Road Sumner Park (Using James Eng)


Sub-Suppliers

Provide list of all major/critical components from sub-supplier. State sub-supplier name and location of
component manufacture.


SWITCHROOMS — JAMES ENGINEERING BRISBANE


Progress Reports and Schedule


(Detailed design, procurement, manufacturing, assembly, testing, delivery schedule and progress report)



			
	 	 	 
	Number of weeks from date of Purchase Order	 	6 of weeks
	Frequency of updates	 	4 of weeks





Liquidated Damages — Manufacturer’s Proposal, Subject to Assessment by LGL (Include details)



				
	 	 	 
	Per Diem Rate	 	(%)
	Maximum Amount	 	(%)





Warranties/Guarantees



			
	 	 	 
	From date of equipment startup-commissioning (Number of months)	 	12 of months
	From date of final component shipment (Number of months)	 	18 of months




Extended Warranty


List all extended warranties for the Equipment and components

None available


Extended Warranty Cost (if applicable)


Other Details (Add information if required)



	 	 	 	 	 
	Does the Seller accept the Warranty Terms and Conditions?
	 	Yes	 	þ
	 
	 	No	 	o




 







 




COMMERCIAL DETAILS



Drawings, Operators Manuals and Parts Manuals (Where applicable)

Preliminary Engineering Drawings for approval

Number of days from date of Purchase Order

From 6 weeks for first drawing set.



Final Certified Engineering Drawings


			
	 	 	 
	Number of days from date of approved preliminary drawings
	 	14 days





Final Certified (Where preliminary drawings are not required for approval)

Number of days from date of Purchase Order


At completion


Operators Manuals (Installation, Operation, Maintenance and Training)

Operator Manuals in addition to requirements outlined in Section I

Additional sets (Indicate cost if applicable)

Electronic sets – CD-R (Indicate cost if applicable)


Parts Manuals (Including Bearings, Seals, and Filter Conversions)

Parts Manuals in addition to requirements outlined in Section I

Additional sets (Indicate cost if applicable)

Electronic sets – CD-R (Indicate cost if applicable)


Quality Assurance/Quality Control (Include details)

Attached


Health, Safety, Environmental & Human Rights Compliance (Include details)


Tools (Special tools required for installation, operation and maintenance of Equipment)


	 	 	 	 	 
	 	 	Description	Amount
	None Required
	 	 	 	 
	 
	 	 	 	 
	 
	 	Total





Contract Local/Overseas Content



	 	 	 	 	 
	 	 	Description	Amount
	Plummers Industries is 100% Australian owned and operated
	 	 	 	 
	 
	 	 	 	 
	 
	 	Total Contract Value





 








 




COMMERCIAL DETAILS


Additional Items/Details (if required)


 







 





ALTERNATIVE TENDER

Tenderer’s Proposed Departures From the Tender Documents




Equipment Tender # and Description

Tenderer’s Name: PLUMMERS INDUSTRIES




All prices to be in Australian or US currency (refer clause 4 of Section I Part A)




			
	Currency of Manufacturer’s Quotation
	 	AUSTRALIA





Tenderer to detail the additional or reduced cost associated with each departure itemised.
Tenderer to add additional line items and clarification below if required.




	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Table 1.2 Technical Departures	 	UOM	 	QTY	 	Unit Cost	 	Extended
	See cover letter
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	[List item]
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	Forward Cover Foreign Currency Risk (if any)
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	Subtotal FOB (Incoterms 2000) Seaport
	 	 	+/-	 	 	 	 






	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Table 1.3 Commercial Departures	 	UOM	 	QTY	 	Unit Cost	 	Extended
	[List Item]
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	See cover letter
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	Forward Cover Foreign Currency Risk (if any)
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	Subtotal FOB (Incoterms 2000) Seaport
	 	 	+/-	 	 	 	 	 






	 	 	 	 	 	 	 	 	 
	Table 1.4 Optional Equipment and/or Materials	 	UOM	 	QTY	 	Unit Cost	 	Extended
	Tenderer to indicate if the following design features are considered Standard or Non-Standard equipment items. For all
non-standard items, Tenderer to provide cost. Unless otherwise specified it is understood the equipment options below
will meet or exceed all technical requirements in Section III. Tenderer to add additional line items and clarification
below, if required.
	 	 
	[List Item]

	 	EA	 	 	 	 	 	 
	 

	 	EA	 	 	 	 	 	 
	 

	 	EA	 	 	 	 	 	 
	 

	 	EA	 	 	 	 	 	 
	 

	 	EA	 	 	 	 	 	 
	Forward Cover Foreign Currency Risk (if any)

	 	EA	 	 	 	 	 	 
	Subtotal FOB (Incoterms 2000) Seaport

	 	+/-	 	 
	 	 
	 

	 	 	 	 	 	TOTAL FOB COST	 	 






 









 





COMMERCIAL DETAILS




	 	 	 
	Equipment Tender # and Description:
	 	 
	Tenderer’s Name:

	 	PLUMMERS INDUSTRIES






Table 2.1 Schedule of Key Dates




	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	Available For	 	 	 	 
	 	 	 	 	 	 	Place of	 	Start	 	Inspection	 	Dispatch	 	Delivery
	Item	 	Tag	 	 	Manufacture	 	Manufacture	 	Or Testing	 	Ex Works	 	Site
	 	 	 	 	 	 	 	 	(Weeks After Order)
	 
	To be discussed at kick off meeting depending on
site and client scheduling

	 	 	 	 	 	 
	 	 
	 	 
	 	 
	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Table 2.2 Contractual Delivery Schedule	 	 	 	 	 	 	 	 
	State delivery in number of weeks from date of Purchase Order for the following:	 	 	 	 	 	 
	Manufacture and Supply

	 	 	36	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	 	 	 	 	 	 	 	 
	Delivery Completion Date

	 	Oct-09
	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	 	 	 	 	 	 	 	 





Table 2.3 Witnessed and Verified Performance Tests



List the Tests that need to be witnessed and verified and detail if the cost of these tests is
included in the Tendered Price




	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Component and Test	 	Cost Included?	 	 	 	 	 	 	 	 	 	 	Cost	 
	All final testing and inspections need to be witnessed and verified prior to release.	 	Yes	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	See attached ITP
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	Total Cost:	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 





 









 





COMMERCIAL DETAILS




	 	 	 
	Equipment Tender # and Description 
	 	 
	Tenderer’s Name:

	 	PLUMMERS INDUSTRIES






Table 2.3 Equipment Weights and Dimensions




	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	Weight	 	 	Shipping Dimensions	 
	Item	 	Description	 	Tag	 	 	(kg)	 	 	(mm)	 
	1.	 	SS2850
	 	 	 	 	 	 	14000	 	 	 	8.2X 3.8	 
	2.	 	SS2051
	 	 	 	 	 	 	14000	 	 	 	8.2X 3.8	 
	3.	 	SS2101
	 	 	 	 	 	 	18000	 	 	 	12.2 X 5.7	 
	4.	 	SS2741
	 	 	 	 	 	 	18000	 	 	 	12.2 X 6.0	 
	5.	 	SS2160
	 	 	 	 	 	 	16000	 	 	 	15.2 X 5.7	 
	6.	 	SS2551
	 	 	 	 	 	 	2 X 20000	 	 	 	28.2 X 3.2	 
	7.	 	 
	 	 	 	 	 	 	12000	 	 	 	6.7 X 6.0	 
	8.	 	SS2932
	 	 	 	 	 	 	1X24T,1X12T	 	 	 	20.2 X 6.0, 10.2 X 6.0	 
	9.	 	SS2560
	 	 	 	 	 	 	26000	 	 	 	17.2X6.4	 
	10.	 	 
	 	 	 	 	 	 	16000	 	 	 	13.2X6.4	 
	11.	 	SS2000
	 	 	 	 	 	 	28000	 	 	 	14.7X6.4	 
	12.	 	 
	 	 	 	 	 	 	12000	 	 	 	8.2 X 6.4	 
	13.	 	SS2931
	 	 	 	 	 	 	1X20T, 1X12T	 	 	 	15.5 X 10.4	 
	14.	 	 
	 	 	 	 	 	 	28000	 	 	 	22.8X6.0	 
	15	 	SS2200
	 	 	 	 	 	 	2 X 16000	 	 	 	16.2 X 4.7, 16.2 X 4.7	 
	16	 	 
	 	 	 	 	 	 	22000	 	 	 	16.2 X 6.6	 
	17	 	SS2400
	 	 	 	 	 	 	2 X 22000	 	 	 	14.2 X 6.0	 
	18	 	 
	 	 	 	 	 	 	14000	 	 	 	8.2X6.0	 
	19	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	20	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	21	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	22	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	Total Equipment Weight	 	 	 	 	 	 	238000	 	 	 	 	 
	Total Cubic Measure	 	 	 	 	 	 	 	 	 	 	0	 
	Total Number of Pieces	 	 	 	 	 	 	 	 	 	 	 	 






Table 2.4 Spare Parts




	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	Weight	 	 	Shipping Dimensions	 
	Item	 	Description	 	Tag	 	 	(kg)	 	 	(mm)	 
	1.	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	2.	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	3.	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	4.	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	5.	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	6.	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	Total Spare Parts Weight	 	 	 	 	 	 	0	 	 	 	 	 
	Total Cubic Measure	 	 	 	 	 	 	 	 	 	 	0	 
	Total Number of Pieces	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Total shipping weight or cubic measure “Revenue Tonne”	 	 	 	 	 	 	 	 
	(Revenue Tonne = greater of tonnage or cubic meter)	 	 	 	 	 	 	 	 






 









 





SPARE PARTS




Equipment Tender # and Description:

Tenderer’s Name: PLUMMERS INDUSTRIES




Spare Parts



Recommended spare parts for one (1) year of Operation



(Tenderer to provide separate list of spare parts in Excel format)



To be advised once MCC design has been completed



Commissioning spare parts



(Tenderer to provide separate list of commissioning parts in Excel format)



Spare Components



(Tenderer to provide pricing for spare components)




	 	 	 	 	 	 	 
	Export/Domestic Packing
	 	 	 	 	 	 
	Freight (to nearest Port of Exit)
	 	 	 	 	 	 
	Ocean Freight to Port of Entry
	 	 	 	 	 	 
	Customs/Port Terminal Charges (if any)
	 	 	 	 	 	 
	Inland Freight to Project Site
	 	 	 	 	 	 
	 

	 	TOTAL COST	 	 	 	 
	 

	 	 	 	 	%	 





Parts Discount (This parts discount would apply for all initial spare parts
purchased)



Nearest Service Depot and/or Distributor (State name and address)



Other locations for spare parts support (State name and address)



Approximate value for Equipment spare parts carried at named locations



Recommended major components as consignment stock at Work Site without cost to Buyer



(Tenderer to provide separate list of major components or modules in Excel format)



Recommended list and pricing for all high turnover consumables



(Tenderer to provide separate list of consumables in Excel
format)




 









 





SPARES




	 	 	 
	Equipment Tender # and Description
	 	 
	Tenderer’s Name:

	 	PLUMMERS INDUSTRIES






Table 3.1 Commissioning Spares




	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	Unit Price If	 	 	Unit Price If	 
	 	 	 	 	 	 	Recommended	 	 	Purchased With	 	 	Supplied At Later	 
	Item	 	 	Description	 	Quantity	 	 	Main Order	 	 	Date	 
	 	 	 	 	To be advised once MCC design has been completed
	 	 	 	 	 	 	 	 	 	 






Table 3.2 Capital Spares




	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	Unit Price If	 	 	Unit Price If	 
	 	 	 	 	 	 	 	 	Recommended	 	 	Purchased With	 	 	Supplied At Later	 
	Item	 	 	Description	 	 	Quantity	 	 	Main Order	 	 	Date	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 





 









 





AVAILABILITY GUARANTEES




Equipment Tender # and Description

Tenderer’s Name: PLUMMERS INDUSTRIES




	 	 	 
	Equipment Availability Guarantees (NHP Equipment)

	 	 
	Year 1
	 	 
	Year 2
	 	 
	Year 3
	 	 
	Year 4
	 	 
	Year 5
	 	 






Compensation for availability guarantee(s) not being met:



NIL



Conditions of availability guarantees(s):



None




 









 





SERVICE & SUPPORT




Equipment Tender # and Description

Tenderer’s Name: PLUMMERS INDUSTRIES




Technical On-Site Personnel (if Applicable)



Reimbursable Sum per Person from X to Cairns or return (detail point
of origin)



Not Applicable



Daily Rates for technical on-Site personnel — detail skills/trades



Not Applicable



Equipment (List required equipment)



Not Applicable



Location of Representation Not Applicable



Number of Representatives Not Applicable



Estimated length of stay Not Applicable



Number/Frequency of visits Not Applicable



Additional Items/Details



Number of Technical On-Site Personnel days available at no cost to Buyer



Nil



Emergency Contact for Technical On-Site requirements (Provide details)



Sub-Contractors



Provide the company names of sub-contractors that would be considered for technical on-Site
personnel supply and state their involvement



None



Discounted Labour Rate (In the event of additional work outside the scope of work)




 









 





SERVICE & SUPPORT



Product Support (Technical Service and Training)



Outline recommendations for Operator and Maintenance Training Personnel (Provide details)



Not Required



Outline the period Service Personnel will be provided without cost to Buyer. Assume this is an
advice/troubleshooting role.



Warranty Period



Outline the period Training Personnel will be provided without cost to Buyer.



Not Required



Cost of Service Personnel (Hourly rate)



Cost of Training Personnel (Hourly rate)



Name and address of Manufacturer’s Representative



          - 75 Wolston Road Sumner Park



Identify from which location of Service and Training Personnel will be
provided
Brisbane or Perth



Identify the preferred location for Component Exchange/Rebuilds (Identify preferred
locations) Brisbane



Identify any major components or modules that Tenderer recommends and is prepared to locate in the
LGL warehouse as consignment stock at no cost to Buyer



None




Other Details (Add information if required)




 









 





TECHNICAL DATA SCHEDULE




Equipment Tender # and Description

Tenderer’s Name: PLUMMERS INDUSTRIES




Table 4.1 Technical Data Schedule




	 	 	 	 	 	 	 
	 	 	Weeks After	 	Vendor Agreement	 
	Item	 	Award	 	(Y/N)	 
	DATA WITH TENDER
	 	 	 	 	 	 
	Preliminary general arrangement drawing
	 	6+	 	 	 	 
	Proposed manufacturing Schedule
	 	6	 	 	 	 
	Recommended commissioning & capital spares
	 	12	 	 	 	 
	 	 
	DATA AFTER AWARD
	 	 	 	 	 	 
	Detailed and dimensioned general arrangement drawing including:
	 	12 weeks+	 	 	 	 
	• Lifting details
	 	 	 	 	 	 
	• Operating and maintenance tolerances
	 	 	 	 	 	 
	• Piping and electrical interface details
	 	 	 	 	 	 
	• Itemised list of components
	 	 	 	 	 	 
	Fixed and firm manufacturing schedule
	 	10.0	 	 	 	 
	Inspection and test plan
	 	6.0	 	 	 	 
	Operating and maintenance manuals:
	 	delivery -2	 	 	 	 
	• Preliminary
	 	 	 	 	 	 
	• Final
	 	 	 	 	 	 
	As-built drawings
	 	delivery	 	 	 	 







 











 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	 	 	 	 	 	 	MOTOR CONTROL CENTRES (includes installation of free issued VSD/Soft Str)	 	 	 	 	 	 	 	 
	1314	 	MC2001A	 	SS2001	 	Primary Crushing MCC A
	 	1	 	 	 	 	 	 	 	 	 	 
	1314	 	MC2001B	 	SS2001	 	Primary Crushing MCC B
	 	1	 	 	 	 	 	 	 	 	 	 
	1315	 	MC2051	 	SS2051	 	Primary Conveyor MCC
	 	1	 	 	 	 	 	 	 	 	 	 
	1316	 	MC2101	 	SS2101	 	Ore Stockpile MCC
	 	1	 	 	 	 	 	 	 	 	 	 
	1825	 	MC2160	 	SS2160	 	Wurtol Pumping Station MCC
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	MC2201A	 	SS2200	 	Grinding & Classification MCC A
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	MC2201B	 	SS2200	 	Grinding & Classification MCC B
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	MC2401A	 	SS2400	 	Pressure Oxidation MCC A
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	MC2401B	 	SS2400	 	Pressure Oxidation MCC B
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	MC2401C	 	SS2400	 	Pressure Oxidation MCC C
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	MC2401D	 	SS2400	 	Pressure Oxidation MCC D
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	MC2551A	 	SS2551	 	Cyanidation & Adsorption MCC A
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	MC2551B	 	SS2551	 	Cyanidation & Adsorption MCC B
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	MC2561A	 	SS2560	 	Oxygen Plant MCC A
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	MC2561B	 	SS2560	 	Oxygen Plant MCC B
	 	1	 	 	 	 	 	 	 	 	 	 
	1341	 	MC2741	 	SS2741	 	Grinding Thickeners MCC
	 	1	 	 	 	 	 	 	 	 	 	 
	1830	 	MC2850	 	SS2850	 	Process Seawater MCC
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	MC2931	 	SS2931	 	Bus E Auxilliary MCC
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	MC2932	 	SS2932	 	Bus F Auxilliary MCC
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price MCCs
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	SWITCHROOMS (James Engineering)
	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	SS2001A	 	SS2001	 	Primary Crushing LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1314	 	SS2001B	 	SS2001	 	Primary Crushing HV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1315	 	SS2051	 	SS2051	 	Primary Conveying LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1316	 	SS2101	 	SS2101	 	Ore Stockpile LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1825	 	SS2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1326	 	SS2200A	 	SS2200	 	Grinding Area LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1326	 	SS2200B	 	SS2200	 	Grinding Area HV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1343	 	SS2400A	 	SS2400	 	Pressure Oxidation LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1343	 	SS2400B	 	SS2400	 	Pressure Oxidation HV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1351	 	SS2551A	 	SS2551	 	Cyanidation & Adsorption LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1351	 	SS2551B	 	SS2551	 	Cyanidation & Adsorption HV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1560	 	SS2560A	 	SS2560	 	Oxygen Plant LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1560	 	SS2560B	 	SS2560	 	Oxygen Plant HV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1341	 	SS2741	 	SS2741	 	Grinding Thickeners LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1830	 	SS2850	 	SS2850	 	Process Seawater LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1780	 	SS2931A	 	SS2931	 	Bus C3, C4 & E LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1780	 	SS2931B	 	SS2931	 	Bus C3 & C4 HV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1780	 	SS2931C	 	SS2931	 	Bus E HV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 






 









 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1780	 	SS2932A	 	SS2932	 	Bus F LV Switchroom
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2932B	 	SS2932	 	Bus F HV Switchroom
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	VESDA Systems
	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	SS2001A	 	SS2001	 	Primary Crushing LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1314	 	SS2001B	 	SS2001	 	Primary Crushing HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1315	 	SS2051	 	SS2051	 	Primary Conveying LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1316	 	SS2101	 	SS2101	 	Ore Stockpile LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1825	 	SS2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	SS2200A	 	SS2200	 	Grinding Area LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	SS2200B	 	SS2200	 	Grinding Area HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	SS2400A	 	SS2400	 	Pressure Oxidation LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	SS2400B	 	SS2400	 	Pressure Oxidation HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	SS2551A	 	SS2551	 	Cyanidation & Adsorption LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	SS2551B	 	SS2551	 	Cyanidation & Adsorption HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	SS2560A	 	SS2560	 	Oxygen Plant LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	SS2560B	 	SS2560	 	Oxygen Plant HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1341	 	SS2741	 	SS2741	 	Grinding Thickeners LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1830	 	SS2850	 	SS2850	 	Process Seawater LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2931A	 	SS2931	 	Bus C3, C4 & E LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2931B	 	SS2931	 	Bus C3 & C4 HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2931C	 	SS2931	 	Bus E HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2932A	 	SS2932	 	Bus F LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2932B	 	SS2932	 	Bus F HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price Switchrooms from James Engineering
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	SWITCHROOMS (Brice Engineers)
	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	SS2001A	 	SS2001	 	Primary Crushing LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1314	 	SS2001B	 	SS2001	 	Primary Crushing HV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1315	 	SS2051	 	SS2051	 	Primary Conveying LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1316	 	SS2101	 	SS2101	 	Ore Stockpile LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1825	 	SS2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1326	 	SS2200A	 	SS2200	 	Grinding Area LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1326	 	SS2200B	 	SS2200	 	Grinding Area HV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1343	 	SS2400A	 	SS2400	 	Pressure Oxidation LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1343	 	SS2400B	 	SS2400	 	Pressure Oxidation HV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1351	 	SS2551A	 	SS2551	 	Cyanidation & Adsorption LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1351	 	SS2551B	 	SS2551	 	Cyanidation & Adsorption HV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1560	 	SS2560A	 	SS2560	 	Oxygen Plant LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1560	 	SS2560B	 	SS2560	 	Oxygen Plant HV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1341	 	SS2741	 	SS2741	 	Grinding Thickeners LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 
	1830	 	SS2850	 	SS2850	 	Process Seawater LV Switchroom
	 	1	 	 	 	 	 	N/A	 	N/A	 	 






 









 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1780	 	SS2931A	 	SS2931	 	Bus C3, C4 & E LV Switchroom
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2931B	 	SS2931	 	Bus C3 & C4 HV Switchroom
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2931C	 	SS2931	 	Bus E HV Switchroom
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2932A	 	SS2932	 	Bus F LV Switchroom
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2932B	 	SS2932	 	Bus F HV Switchroom
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	VESDA Systems
	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	SS2001A	 	SS2001	 	Primary Crushing LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1314	 	SS2001B	 	SS2001	 	Primary Crushing HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1315	 	SS2051	 	SS2051	 	Primary Conveying LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1316	 	SS2101	 	SS2101	 	Ore Stockpile LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1825	 	SS2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	SS2200A	 	SS2200	 	Grinding Area LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	SS2200B	 	SS2200	 	Grinding Area HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	SS2400A	 	SS2400	 	Pressure Oxidation LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	SS2400B	 	SS2400	 	Pressure Oxidation HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	SS2551A	 	SS2551	 	Cyanidation & Adsorption LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	SS2551B	 	SS2551	 	Cyanidation & Adsorption HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	SS2560A	 	SS2560	 	Oxygen Plant LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	SS2560B	 	SS2560	 	Oxygen Plant HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1341	 	SS2741	 	SS2741	 	Grinding Thickeners LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1830	 	SS2850	 	SS2850	 	Process Seawater LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2931A	 	SS2931	 	Bus C3, C4 & E LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2931B	 	SS2931	 	Bus C3 & C4 HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2931C	 	SS2931	 	Bus E HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2932A	 	SS2932	 	Bus F LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SS2932B	 	SS2932	 	Bus F HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price Switchrooms from Brice Engineers
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	DISTRIBUTION BOARDS (Chassis and Panel Only)
	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	DB2001A	 	SS2001	 	Primary Crushing LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1314	 	DB2001B	 	SS2001	 	Primary Crushing HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1314	 	DB2001C	 	SS2001	 	Primary Crushing UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1314	 	DB2001D	 	SS2001	 	Primary Crushing Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 	 	 	 	 	 	 	 	 
	1315	 	DB2051A	 	SS2051	 	Primary Conveying LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1315	 	DB2051B	 	SS2051	 	Primary Conveying UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 






 









 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1315	 	DB2051C	 	SS2051	 	Primary Conveying Area Distribution Board 72 pole. 415V, 250A. 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 	 	 	 	 	 	 	 	 
	1316	 	DB2101A	 	SS2101	 	Ore Stockpile LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1316	 	DB2101B	 	SS2101	 	Ore Stockpile UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1316	 	DB2101C	 	SS2101	 	Ore Stockpile Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 	 	 	 	 	 	 	 	 
	1825	 	DB2160A	 	SS2160	 	Wurtol Pumping Station LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1825	 	DB2160B	 	SS2160	 	Wurtol Pumping Station UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1825	 	DB2160C	 	SS2160	 	Wurtol Pumping Station Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	DB2201A	 	SS2201	 	Grinding LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	DB2201B	 	SS2201	 	Grinding HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	DB2201C	 	SS2201	 	Grinding Area UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s., IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	DB2201D	 	SS2201	 	Grinding Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	DB2401A	 	SS2401	 	Pressure Oxidation LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	DB2401B	 	SS2401	 	Pressure Oxidation HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	DB2401C	 	SS2401	 	Pressure Oxidation UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	DB2401D	 	SS2401	 	Pressure Oxidation Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	DB2551A	 	SS2551	 	Cyanidation & Adsorption LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	DB2551B	 	SS2551	 	Cyanidation & Adsorption HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	DB2551C	 	SS2551	 	Cyanidation & Adsorption UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	DB2551D	 	SS2551	 	Cyanidation & Adsorption Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	DB2561A	 	SS2560	 	Oxygen Plant LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s
	 	1	 	 	 	 	 	 	 	 	 	 




 








 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1560	 	DB2561B	 	SS2560	 	Oxygen Plant HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	DB2561C	 	SS2560	 	Oxygen Plant UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	DB2561D	 	SS2560	 	Oxygen Plant Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 	 	 	 	 	 	 	 	 
	1341	 	DB2741A	 	SS2741	 	Grinding Thickeners LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1341	 	DB2741B	 	SS2741	 	Grinding Thickeners UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1341	 	DB2741C	 	SS2741	 	Grinding Thickeners Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 	 	 	 	 	 	 	 	 
	1830	 	DB2850A	 	SS2850	 	Process Seawater LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1830	 	DB2850B	 	SS2850	 	Process Seawater Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	DB2931A	 	SS2931	 	Bus C3, C4 & E Light & Power Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	DB2931B	 	SS2931	 	Bus C3, C4 & E UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	DB2932A	 	SS2932	 	Bus F Light & Power Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	DB2932B	 	SS2932	 	Bus F UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	PC Sum for Fitout of DB’s with Circuit Breakers
	 	PC	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	UNINTERRUPTIBLE POWER SUPPLIES
	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	UP2001	 	SS2001	 	Primary Crushing LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1315	 	UP2051	 	SS2051	 	Primary Conveying LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1316	 	UP2101	 	SS2101	 	Ore Stockpile LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1825	 	UP2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	UP2201	 	SS2200	 	Grinding Area LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	UP2401	 	SS2400	 	Pressure Oxidation LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 






 









 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1351	 	UP2551	 	SS2551	 	Cyanidation & Absorption LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	UP2561	 	SS2560	 	Oxygen Plant LV Switchroom UPS 12KVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1341	 	UP2741	 	SS2741	 	Grinding Thickeners LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	UP2931	 	SS2931	 	Bus C3, C4 & E LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	UP2932	 	SS2932	 	Bus F LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price UPS
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Control Panels
	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	CP2001A	 	SS2001	 	Primary Crushing LV Switchroom DCS Panel A
	 	1	 	 	 	 	 	 	 	 	 	 
	1314	 	CP2001B	 	SS2001	 	Primary Crushing LV Switchroom DCS Panel B
	 	1	 	 	 	 	 	 	 	 	 	 
	1315	 	CP2051	 	SS2051	 	Primary Conveying LV Switchroom DCS Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1316	 	CP2101	 	SS2101	 	Ore Stockpile LV Switchroom DCS Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	CP2201A	 	SS2200	 	Grinding Area LV Switchroom DCS Panel A
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	CP2201B	 	SS2200	 	Grinding Area LV Switchroom DCS Panel B
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	CP2401A	 	SS2400	 	Pressure Oxidation LV Switchroom DCS Panel A
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	CP2401B	 	SS2400	 	Pressure Oxidation LV Switchroom DCS Panel B
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	CP2551A	 	SS2551	 	Cyanidation & Absorption LV Switchroom DCS Panel A
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	CP2551B	 	SS2551	 	Cyanidation & Absorption LV Switchroom DCS Panel B
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	CP2560A	 	SS2560	 	Oxygen Plant LV Switchroom DCS Panel A
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	CP2560B	 	SS2560	 	Oxygen Plant LV Switchroom DCS Panel B
	 	1	 	 	 	 	 	 	 	 	 	 
	1341	 	CP2741	 	SS2741	 	Grinding Thickeners LV Switchroom DCS Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1825	 	CP2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom PLC Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	CP2931A	 	SS2931	 	Bus C3, C4 & E HV Switchroom PLC Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	CP2932A	 	SS2932	 	Bus F HV Switchroom PLC Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	CP2603	 	SS2560	 	PC Sum for Installation of Oxygen Plant Hardwired Emergency
	 	PC	 	 	 	 	 	 	 	 	 	 
	1830	 	CP2850	 	SS2850	 	PC Sum for Installation of Process Seawater LV Switchroom C
	 	PC	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	PC Sum for Internal Marshalling of 13 DCS Panels
	 	PC	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	PC Sum for Cabling of 18 Panels Within Switchrooms
	 	PC	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	PC Sum for Installation of 19” RM FOBOTs in LV Switchroom
	 	PC	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price Control Panels
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	BATTERY CHARGER SYSTEMS
	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	BC2000	 	SS2001	 	Primary Crushing HV Switchroom 48VDC, 70Ahr
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	BC2200	 	SS2200	 	Grinding Area HV Switchroom 48VDC, 70Ahr
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	BC2400	 	SS2400	 	Pressure Oxidation HV Switchroom 48VDC, 70Ahr
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	BC2550	 	SS2551	 	Cyanidation & Absorption HV Switchroom 48VDC, 70Ahr
	 	1	 	 	 	 	 	 	 	 	 	 




 







 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1560	 	BC2560	 	SS2560	 	Oxygen Plant HV Switchroom 48VDC, 160Ahr
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	BC2900	 	SS2931	 	Bus C3 & C4 HV Switchroom 48VDC, 160Ahr
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	BC2931	 	SS2931	 	Bus E HV Switchroom 48VDC, 230Ahr
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	BC2932	 	SS2932	 	Bus F HV Switchroom 48VDC, 230Ahr
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price Battery Charger Systems
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	HV SWITCHBOARDS
	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	SW2000	 	SS2001	 	Primary Crushing 11kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 
	1314	 	SW2001	 	SS2001	 	HGO Crusher 3.3kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	SW2200	 	SS2200	 	Grinding Area 11kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	SW2400	 	SS2400	 	Pressure Oxidation 11kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	SW2550	 	SS2551	 	Cyanidation & Absorption 11kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	SW2560	 	SS2560	 	Oxygen Plant 11kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SW2900	 	SS2931	 	Bus C3 & C4 11kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SW2931	 	SS2931	 	Bus E 33kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	SW2932	 	SS2932	 	Bus F 33kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price HV Switchboards
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	HV REMOTE SWITCHING PANELS
	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	CP2000	 	SS2001	 	Primary Crushing 11kV & 3.3kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	CP2200	 	SS2200	 	Grinding Area 11kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	CP2400	 	SS2400	 	Pressure Oxidation 11kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	CP2550	 	SS2551	 	Cyanidation & Absorption 11kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	CP2560	 	SS2560	 	Oxygen Plant 11kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	CP2900	 	SS2931	 	Bus C3 & C4 11kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	CP2900A	 	SS2931	 	Bus C3 & C4 11kV Tariff Metering Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	CP2931	 	SS2931	 	Bus E 33kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1780	 	CP2932	 	SS2932	 	Bus F 33kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	PC Sum for Cabling of 9 Panels Within Switchrooms
	 	PC	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price HV Remote Switching Panels
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	FLOOR MOUNTED VSDs
	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	FD2001	 	SS2001	 	Primary Apron Feeder VSD 315kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1315	 	FD2003	 	SS2101	 	HGO Apron Feeder No.1 VSD 55kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1315	 	FD2004	 	SS2101	 	HGO Apron Feeder No.2 VSD 55kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1315	 	FD2005	 	SS2101	 	HGO Emergency Apron Feeder VSD 55kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1825	 	PU2161	 	SS2160	 	Wurtol Raw Water Pump No.1 VSD 600kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1825	 	PU2162	 	SS2160	 	Wurtol Raw Water Pump No.2 VSD 600kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1825	 	PU2163	 	SS2160	 	Wurtol Raw Water Pump No.3 VSD 600kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2030	 	SS2200	 	Pre-oxidation Feed Pump No.1 VSD 185kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2031	 	SS2200	 	Pre-oxidation Feed Pump No.2 VSD 185kW
	 	1	 	 	 	 	 	 	 	 	 	 




 







 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1326	 	PU2040	 	SS2200	 	Cyclone Overflow Transfer Pump No.1 VSD 400kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2041	 	SS2200	 	Cyclone Overflow Transfer Pump No.2 VSD 400kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2042	 	SS2200	 	Cyclone Overflow Transfer Pump No.3 VSD 400kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2043	 	SS2200	 	Cyclone Overflow Transfer Pump No.4 VSD 400kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2021	 	SS2200	 	Cyclone Feed Pump No.1 VSD 525kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2022	 	SS2200	 	Cyclone Feed Pump No.2 VSD 525kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	PU2741	 	SS2400	 	Autoclave Feed Booster Pump VSD 185kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	AG2245	 	SS2400	 	Autoclave No.4 Compartments 3-6 Agitator VSD 200kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	PU2123	 	SS2400	 	Flashed Slurry Forwarding Pump No.1 VSD 200kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	PU2124	 	SS2400	 	Flashed Slurry Forwarding Pump No.2 VSD 200kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	PU2125	 	S2400	 	Flashed Slurry Forwarding Pump No.3 VSD 200kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	AG2241	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	AG2242	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	AG2243	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	AG2244	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	PU2033	 	SS2400	 	Autoclave Feed Pump No.1 VSD 600kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1343	 	PU2034	 	SS2400	 	Autoclave Feed Pump No.2 VSD 600kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	PU2105	 	SS2551	 	Lime Recirculation Pump VSD 30kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	PU2058	 	SS2551	 	Leach Trash Screen Feed Pump VSD 110kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	PU2212	 	SS2551	 	CIL Tails Pump No.1 VSD 315kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1351	 	PU2213	 	SS2551	 	CIL Tails Pump No.2 VSD 315kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	P440A	 	SS2560	 	LOX Process Pump A VSD 150kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1560	 	P440B	 	SS2560	 	LOX Process Pump B VSD 150kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1341	 	PU2026	 	SS2741	 	Grinding Thickener No.1 U/F Pump No.1 VSD 75kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1341	 	PU2027	 	SS2741	 	Grinding Thickener No.1 U/F Pump No.2 VSD 75kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1341	 	PU2028	 	SS2741	 	Grinding Thickener No.2 U/F Pump No.1 VSD 525kW
	 	1	 	 	 	 	 	 	 	 	 	 
	1341	 	PU2029	 	SS2741	 	Grinding Thickener No.2 U/F Pump No.2 VSD 525kW
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price VSDs
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	LOCAL CONTROL STATIONS (Supply price for each even if quantity is 0)
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-01	 	 	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors ≤30kW)
	 	174	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-02	 	 	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors ≤ 55kW)
	 	5	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-03	 	 	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors ≤90kW)
	 	14	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-04	 	 	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors ≤185kW)
	 	13	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-05	 	 	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors ≤30kW)
	 	6	 	 	 	 	 	 	 	 	 	 






 









 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	 	 	LCS-06	 	 	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors  ≤ 55kW)
	 	7	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-07	 	 	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors ≤90kW)
	 	2	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-08	 	 	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors ≤185kW)
	 	7	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-09	 	 	 	Local control station with start pushbutton, emergency stop button and labels (no isolator)
	 	21	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-10	 	 	 	Local control station with start pushbutton, stop pushbutton, emergency stop button and labels (no isolator)
	 	25	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-11	 	 	 	Local control station with forward pushbutton, reverse pushbutton, emergency stop button and labels (no isolator)
	 	2	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-12	 	 	 	80 amp, 3 pole isolator only
	 	19	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-13	 	 	 	125 amp, 3 pole isolator only
	 	2	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-14	 	 	 	200 amp, 3 pole isolator only
	 	0	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-15	 	 	 	400 amp, 3 pole isolator only
	 	0	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-16	 	 	 	80 amp, 6 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors ≤30kW)
	 	0	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-17	 	 	 	80 amp, 6 pole isolator, reverse, lock-off emergency stop, start pushbutton and labels (DOL motors ≤30kW)
	 	0	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-18	 	 	 	Local control station with 32 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)
	 	7	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-19	 	 	 	Local control station with 63 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)
	 	34	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-20	 	 	 	Local control station with 125 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)
	 	3	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-21	 	 	 	Local control station with 200 amp decontactor, 4 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)
	 	2	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-CONV	 	 	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton, larger box, extra terminals and labels
	 	3	 	 	 	 	 	 	 	 	 	 






 









 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	 	 	LCS-SLEW	 	 	 	80 amp, 3 pole isolator, reverse, lock-off emergency stop, start pushbutton and labels (DOL motors ≤30kW)
	 	0	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-ES	 	 	 	Lock-off emergency stop pushbutton only
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price Local Control Stations
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Drawings and Documentation
	 	Lot	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Packaging
	 	Lot	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Lifting Equipment
	 	Lot	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Inland Freight to Port
	 	Lot	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Drawings / Packaging / Transport
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total MCC & Switchrooms (without Options)
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	RECOMMENDED OPTIONS
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total MCC & Switchrooms (with Options)
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Installation Cost for Brice Eng.
	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Delivery of Plummers supplied equipment
	 	1	 	 	 	 	 	 	 	 	 	 







 











 




LIHIR MOPU Project
MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule


SCHEDULE OF PRICES
VARIATIONS FOR ADDITIONS AND DELETIONS for MCC DOL STARTERS


	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	Price
	1.1
	 	0.37kW DOL	 	1 x 0.37kW DOL Starter	 	1	 	 
	1.2
	 	0.55kW DOL	 	1 x 0.55kW DOL Starter	 	1	 	 
	1.3
	 	1.1kW DOL	 	1 x 1.1kW DOL Starter	 	1	 	 
	1.4
	 	1.5kW DOL	 	1 x 1.5kW DOL Starter	 	1	 	 
	1.5
	 	2.2kW DOL	 	1 x 2.2kW DOL Starter	 	1	 	 
	1.6
	 	3kW DOL	 	1 x 3kW DOL Starter	 	1	 	 
	1.7
	 	4kW DOL	 	1 x 4kW DOL Starter	 	1	 	 
	1.8
	 	5.5kW DOL	 	1 x 5.5kW DOL Starter	 	1	 	 
	1.9
	 	7.5kW DOL	 	1 x 7.5kW DOL Starter	 	1	 	 
	1.10
	 	11kW DOL	 	1 x 11kW DOL Starter	 	1	 	 
	1.11
	 	15kW DOL	 	1 x 15kW DOL Starter	 	1	 	 
	1.12
	 	18.5kW DOL	 	1 x 18.5kW DOL Starter	 	1	 	 
	1.13
	 	22kW DOL	 	1 x 22kW DOL Starter	 	1	 	 
	1.14
	 	30kW DOL	 	1 x 30kW DOL Starter	 	1	 	 
	1.15
	 	37kW DOL	 	1 x 37kW DOL Starter	 	1	 	 
	1.16
	 	45kW DOL	 	1 x 45kW DOL Starter	 	1	 	 
	1.17
	 	55kW DOL	 	1 x 55kW DOL Starter	 	1	 	 
	1.18
	 	75kW DOL	 	1 x 75kW DOL Starter	 	1	 	 
	1.19
	 	90kW DOL	 	1 x 90kW DOL Starter	 	1	 	 
	1.20
	 	110kW DOL	 	1 x 110kW DOL Starter	 	1	 	 
	1.21
	 	132kW DOL	 	1 x 132kW DOL Starter	 	1	 	 
	1.22
	 	150kW DOL	 	1 x 150kW DOL Starter	 	1	 	 
	1.23
	 	185kW DOL	 	1 x 185kW DOL Starter	 	1	 	 
	1.24
	 	200kW DOL	 	1 x 200kW DOL Starter	 	1	 	 
	1.25
	 	220kW DOL	 	1 x 220kW DOL Starter	 	1	 	 
	1.26
	 	250kW DOL	 	1 x 250kW DOL Starter	 	1	 	 
	1.27
	 	280kW DOL	 	1 x 280kW DOL Starter	 	1	 	 
	1.28
	 	315kW DOL	 	1 x 315kW DOL Starter	 	1	 	 
	1.29
	 	355kW DOL	 	1 x 355kW DOL Starter	 	1	 	 
	1.30
	 	400kW DOL	 	1 x 400kW DOL Starter	 	1	 	 
	1.31
	 	450kW DOL	 	1 x 450kW DOL Starter	 	1	 	 
	1.32
	 	500kW DOL	 	1 x 500kW DOL Starter	 	1	 	 
	1.33
	 	560kW DOL	 	1 x 560kW DOL Starter	 	1	 	 
	1.34
	 	630kW DOL	 	1 x 630kW DOL Starter	 	1	 	 




VARIATIONS FOR ADDITIONS AND DELETIONS for MCC VSD MODULES
Installation Only. All VSDs are free issued.


	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	 
	2.1
	 	0.55kW VSD	 	1 x 0.55kW VSD Starter	 	1	 	 
	2.2
	 	1.1kW VSD	 	1 x 1.1kW VSD Starter	 	1	 	 
	2.3
	 	1.5kW VSD	 	1 x 1.5kW VSD Starter	 	1	 	 
	2.4
	 	2.2kW VSD	 	1 x 2.2kW VSD Starter	 	1	 	 
	2.5
	 	3.7kW VSD	 	1 x 3.7kW VSD Starter	 	1	 	 
	2.6
	 	5.5kW VSD	 	1 x 5.5kW VSD Starter	 	1	 	 
	2.7
	 	7.5kW VSD	 	1 x 7.5kW VSD Starter	 	1	 	 
	2.8
	 	11kW VSD	 	1 x 11kW VSD Starter	 	1	 	 
	2.9
	 	15kW VSD	 	1 x 15kW VSD Starter	 	1	 	 
	2.10
	 	18.5kW VSD	 	1 x 18.5kW VSD Starter	 	1	 	 
	2.11
	 	22kW VSD	 	1 x 22kW VSD Starter	 	1	 	 
	2.12
	 	30kW VSD	 	1 x 30kW VSD Starter	 	1	 	 
	2.13
	 	37kW VSD	 	1 x 37kW VSD Starter	 	1	 	 
	2.14
	 	45kW VSD	 	1 x 45kW VSD Starter	 	1	 	 
	2.15
	 	55kW VSD	 	1 x 55kW VSD Starter	 	1	 	 




Variations Pricing_Rev 00
Revised 230209 Q 4929 - NHP - MOPU-1101_Pricing Schedules


                                             Page 11 of 17 Pages


 







 




LIHIR MOPU Project
MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule



	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	Price
	2.16
	 	75kW VSD	 	1 x 75kW VSD Starter	 	1	 	 
	2.17
	 	90kW VSD	 	1 x 90kW VSD Starter	 	1	 	 
	2.18
	 	110kW VSD	 	1 x 110kW VSD Starter	 	1	 	 
	2.19
	 	132kW VSD	 	1 x 132kW VSD Starter	 	1	 	 
	2.20
	 	150kW VSD	 	1 x 150kW VSD Starter	 	1	 	 
	2.21
	 	185kW VSD	 	1 x 185kW VSD Starter	 	1	 	 
	2.22
	 	220kW VSD	 	1 x 220kW VSD Starter	 	1	 	 
	2.23
	 	280kW VSD	 	1 x 280kW VSD Starter	 	1	 	 
	2.24
	 	315kW VSD	 	1 x 315kW VSD Starter	 	1	 	 
	2.25
	 	355kW VSD	 	1 x 355kW VSD Starter	 	1	 	 
	2.26
	 	400kW VSD	 	1 x 400kW VSD Starter	 	1	 	 
	2.27
	 	450kW VSD	 	1 x 450kW VSD Starter	 	1	 	 
	2.28
	 	500kW VSD	 	1 x 500kW VSD Starter	 	1	 	 
	2.29
	 	630kW VSD	 	1 x 630kW VSD Starter	 	1	 	 




VARIATIONS FOR ADDITIONS AND DELETIONS for MCC SOFT STARTER MODULES
Installation Only. All soft starters are free issued.


	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	 
	3.1
	 	132kW SSD	 	1 x 132kW Soft Starter	 	1	 	 
	3.2
	 	150kW SSD	 	1 x 150kW Soft Starter	 	1	 	 
	3.3
	 	160kW SSD	 	1 x 160kW Soft Starter	 	1	 	 
	3.4
	 	185kW SSD	 	1 x 185kW Soft Starter	 	1	 	 
	3.5
	 	220kW SSD	 	1 x 220kW Soft Starter	 	1	 	 
	3.6
	 	250kW SSD	 	1 x 250kW Soft Starter	 	1	 	 
	3.7
	 	280kW SSD	 	1 x 280kW Soft Starter	 	1	 	 
	3.8
	 	315kW SSD	 	1 x 315kW Soft Starter	 	1	 	 
	3.9
	 	355kW SSD	 	1 x 355kW Soft Starter	 	1	 	 
	3.10
	 	400kW SSD	 	1 x 400kW Soft Starter	 	1	 	 
	3.11
	 	450kW SSD	 	1 x 450kW Soft Starter	 	1	 	 
	3.12
	 	500kW SSD	 	1 x 500kW Soft Starter	 	1	 	 
	3.13
	 	630kW SSD	 	1 x 630kW Soft Starter	 	1	 	 





VARIATIONS FOR ADDITIONS AND DELETIONS for MCC FEEDER/INCOMER MODULES


	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	 
	4.1
	 	40 F	 	1 x 40 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.2
	 	63 F	 	1 x 63 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.3
	 	100 F	 	1 x 100 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.4
	 	160 F	 	1 x 160 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.5
	 	200 F	 	1 x 200 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.6
	 	250 F	 	1 x 250 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.7
	 	400 F	 	1 x 400 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.8
	 	630 F	 	1 x 630 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.9
	 	1250 F	 	1 x 1250 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.10
	 	40 F/C	 	1 x 40 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.11
	 	63 F/C	 	1 x 63 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.12
	 	100 F/C	 	1 x 100 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.13
	 	160 F/C	 	1 x 160 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.14
	 	200 F/C	 	1 x 200 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.15
	 	250 F/C	 	1 x 250 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.16
	 	400 F/C	 	1 x 400 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.17
	 	630 F/C	 	1 x 630 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.18
	 	1250 F/C	 	1 x 1250 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.15
	 	800 IC	 	1 x 800 Amp Air Circuit Breaker Incomer	 	1	 	 
	4.16
	 	1600 IC	 	1 x 1600 Amp Air Circuit Breaker Incomer	 	1	 	 
	4.17
	 	3200 IC	 	1 x 3200 Amp Air Circuit Breaker Incomer	 	1	 	 
	4.18
	 	4000 IC	 	1 x 4000 Amp Air Circuit Breaker Incomer	 	1	 	 




Variations Pricing_Rev 00
Revised 230209 Q 4929 - NHP - MOPU-1101_Pricing Schedules


                                             Page 12 of 17 Pages


 







 




LIHIR MOPU Project
MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule


VARIATIONS FOR ADDITIONS AND DELETIONS for LCS TYPES



	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	LCS Type	 	Description	 	Qty	 	Price
	5.1
	 	LCS-1	 	80 amp, 3 pole isolator, lock-off emergency
stop, start pushbutton and labels (DOL motors
£30kW)	 	 	1	 	 	 
	5.2
	 	LCS-2	 	125 amp, 3 pole isolator, lock-off emergency
stop, start pushbutton and labels (DOL motors
£55kW)	 	 	1	 	 	 
	5.3
	 	LCS-3	 	200 amp, 3 pole isolator, lock-off emergency
stop, start pushbutton and labels (DOL motors
£90kW)	 	 	1	 	 	 
	5.4
	 	LCS-4	 	400 amp, 3 pole isolator, lock-off emergency
stop, start pushbutton and labels (DOL motors
£185kW)	 	 	1	 	 	 
	5.5
	 	LCS-5	 	80 amp, 3 pole isolator, lock-off emergency
stop, start pushbutton, stop pushbutton and
labels (VSD motors £30kW)	 	 	1	 	 	 
	5.6
	 	LCS-6	 	125 amp, 3 pole isolator, lock-off emergency
stop, start pushbutton, stop pushbutton and
labels (VSD motors £55kW)	 	 	1	 	 	 
	5.7
	 	LCS-7	 	200 amp, 3 pole isolator, lock-off emergency
stop, start pushbutton, stop pushbutton and
labels (VSD motors £90kW)	 	 	1	 	 	 
	5.8
	 	LCS-8	 	400 amp, 3 pole isolator, lock-off emergency
stop, start pushbutton, stop pushbutton and
labels (VSD motors £185kW)	 	 	1	 	 	 
	5.9
	 	LCS-9	 	Local control station with start pushbutton,
emergency stop button and labels (no
isolator)	 	 	1	 	 	 
	5.10
	 	LCS-10	 	Local control station with start pushbutton,
stop pushbutton, emergency stop button and
labels (no isolator)	 	 	1	 	 	 
	5.11
	 	LCS-11	 	Local control station with forward
pushbutton, reverse pushbutton, emergency stop
button and labels (no isolator)	 	 	1	 	 	 
	5.12
	 	LCS-12	 	80 amp, 3 pole isolator only	 	 	1	 	 	 
	5.13
	 	LCS-13	 	125 amp, 3 pole isolator only	 	 	1	 	 	 
	5.14
	 	LCS-14	 	200 amp, 3 pole isolator only	 	 	1	 	 	 
	5.15
	 	LCS-15	 	400 amp, 3 pole isolator only	 	 	1	 	 	 
	5.16
	 	LCS-16	 	80 amp, 6 pole isolator, lock-off emergency
stop, start pushbutton and labels (DOL motors
£30kW)	 	 	1	 	 	 
	5.17
	 	LCS-17	 	80 amp, 6 pole isolator, reverse, lock-off
emergency stop, start pushbutton and labels (DOL
motors £30kW)	 	 	1	 	 	 
	5.18
	 	LCS-18	 	Local control station with 32 amp
decontactor, 2 pilot pins, start pushbutton,
emergency stop button and labels (include male
decontactor)	 	 	1	 	 	 
	5.19
	 	LCS-19	 	Local control station with 63 amp
decontactor, 2 pilot pins, start pushbutton,
emergency stop button and labels (include male
decontactor)	 	 	1	 	 	 
	5.20
	 	LCS-20	 	Local control station with 125 amp
decontactor, 2 pilot pins, start pushbutton,
emergency stop button and labels (include male
decontactor)	 	 	1	 	 	 
	5.21
	 	LCS-21	 	Local control station with 200 amp decontactor, 4
pilot pins, start pushbutton, emergency stop
button and labels (include male decontactor)	 	 	1	 	 	 
	5.22
	 	LCS-CONV	 	200 amp, 3 pole isolator, lock-off emergency
stop, start pushbutton, stop pushbutton, larger
box, extra terminals and labels	 	 	1	 	 	 
	5.23
	 	LCS-SLEW	 	80 amp, 3 pole isolator, reverse, lock-off
emergency stop, start pushbutton and labels (DOL
motors £30kW)	 	 	1	 	 	 
	5.24
	 	LCS-ES	 	Lock-off emergency stop pushbutton only	 	 	1	 	 	 




Variations Pricing_Rev 00
Revised 230209 Q 4929 - NHP - MOPU-1101_Pricing Schedules


                                             Page 13 of 17 Pages


 







 




LIHIR MOPU Project
MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule


VARIATIONS FOR DISTRIBUTION BOARDS



	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	 	 	Description	 	Qty	 	Price
	6,1
	 	 	 	Distribution Board 72 pole, 415V, 250A, 20kA/0.2s,
IP42 with Lighting Control Section	 	 	1	 	 	 
	6.2
	 	 	 	Distribution Board 72 pole, 415V, 250A, 20kA/0.2s,
IP42	 	 	1	 	 	 
	6.3
	 	 	 	Distribution Board 36 pole, 415V, 250A, 20kA/0.2s,
IP42	 	 	1	 	 	 
	6.4
	 	 	 	Distribution Board 36 pole, 415V, 250A, 20kA/0.2s,
IP42, with Lighting Control Section	 	 	1	 	 	 
	6.5
	 	 	 	Distribution Board 24 pole, 240V, 160A, 20kA/0.2s,
IP42	 	 	1	 	 	 
	6.6
	 	 	 	Install one single pole, 10 amp circuit breaker	 	 	1	 	 	 
	6.7
	 	 	 	Install one single pole, 16 amp circuit breaker	 	 	1	 	 	 
	6.8
	 	 	 	Install one single pole, 10 amp circuit breaker
with 30mA earth leakage	 	 	1	 	 	 
	6.9
	 	 	 	Install one single pole, 16 amp circuit breaker with
30mA earth
leakage	 	 	1	 	 	 
	6.10
	 	 	 	Install one single pole, 10 amp circuit breaker
with 100mA earth leakage	 	 	1	 	 	 
	6.11
	 	 	 	Install one single pole, 16 amp circuit breaker
with 100mA earth leakage	 	 	1	 	 	 
	6.12
	 	 	 	Install one three pole, 16 amp circuit breaker	 	 	1	 	 	 
	6.13
	 	 	 	Install one three pole, 16 amp circuit breaker with
30mA earth leakage	 	 	1	 	 	 
	6.14
	 	 	 	Install one three pole, 16 amp circuit breaker with
300mA earth leakage	 	 	1	 	 	 
	6.15
	 	 	 	Install one three pole, 20 amp circuit breaker	 	 	1	 	 	 
	6.16
	 	 	 	Install one three pole, 20 amp circuit breaker with
30mA earth leakage	 	 	 	 	 	 
	6.17
	 	 	 	Install one three pole, 20 amp circuit breaker with
100mA earth leakage	 	 	 	 	 	 
	6.18
	 	 	 	Install one three pole, 32 amp circuit breaker	 	 	 	 	 	 
	6.19
	 	 	 	Install one three pole, 32 amp circuit breaker with
30mA earth leakage	 	 	 	 	 	 
	6.20
	 	 	 	Install one three pole, 32 amp circuit breaker with
100mA earth leakage	 	 	 	 	 	 
	6.21
	 	 	 	Install one three pole, 63 amp circuit breaker	 	 	 	 	 	 
	6.22
	 	 	 	Install one three pole, 63 amp circuit breaker with
30mA earth leakage	 	 	 	 	 	 
	6.23
	 	 	 	Install one three pole, 63 amp circuit breaker with
100mA earth leakage	 	 	 	 	 	 





OPTIONAL PRICING FOR SWITCHROOM GAS SUPPRESSION SYSTEM



	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	 
	7.1
	 	James
Engineering	 	Gas Suppression System, Primary Crushing LV Switchroom	 	 	1	 	 	 
	7.2
	 	James
Engineering	 	Gas Suppression System, Primary Crushing HV Switchroom	 	 	1	 	 	 
	7.3
	 	James
Engineering	 	Gas Suppression System, Primary Conveying LV
Switchroom	 	 	1	 	 	 
	7.4
	 	James
Engineering	 	Gas Suppression System, Ore Stockpile LV
Switchroom	 	 	1	 	 	 
	7.5
	 	James
Engineering	 	Gas Suppression System, Wurtol Pumping Station LV
Switchroom	 	 	1	 	 	 




Variations Pricing_Rev 00
Revised 230209 Q 4929 - NHP - MOPU-1101_Pricing Schedules


                                             Page 14 of 17 Pages

 







 




LIHIR MOPU Project
 MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule



	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	Price
	7.6
	 	James Engineering	 	Gas Suppression System, Grinding LV Switchroom	 	 	1	 	 	 
	7.7
	 	James Engineering	 	Gas Suppression System, Grinding HV Switchroom	 	 	1	 	 	 
	7.8
	 	James Engineering	 	Gas Suppression System, Pressure Oxidation LV
Switchroom	 	 	1	 	 	 
	7.9
	 	James Engineering	 	Gas Suppression System, Pressure Oxidation HV
Switchroom	 	 	1	 	 	 
	7.10
	 	James Engineering	 	Gas Suppression System, Cyanidation & Adsorption
LV Switchroom	 	 	1	 	 	 
	7.11
	 	James Engineering	 	Gas Suppression System, Cyanidation & Adsorption
HV Switchroom	 	 	1	 	 	 
	7.12
	 	James Engineering	 	Gas Suppression System, Oxygen Plant LV
Switchroom	 	 	1	 	 	 
	7.13
	 	James Engineering	 	Gas Suppression System, Oxygen Plant HV
Switchroom	 	 	1	 	 	 
	7.14
	 	James Engineering	 	Gas Suppression System, Grinding Thickeners LV
Switchroom	 	 	1	 	 	 
	7.15
	 	James Engineering	 	Gas Suppression System, Process Seawater LV
Switchroom	 	 	1	 	 	 
	7.16
	 	James Engineering	 	Gas Suppression System, Bus C3, C4 & E LV
Switchroom	 	 	1	 	 	 
	7.17
	 	James Engineering	 	Gas Suppression System, Bus C3 & C4 HV
Switchroom	 	 	1	 	 	 
	7.18
	 	James Engineering	 	Gas Suppression System, Bus E HV Switchroom	 	 	1	 	 	 
	7.19
	 	James Engineering	 	Gas Suppression System, Bus F LV Switchroom	 	 	1	 	 	 
	7.20
	 	James Engineering	 	Gas Suppression System, Bus F HV Switchroom	 	 	1	 	 	 
	7.21
	 	Brice Engineers	 	Gas Suppression System, Primary Crushing LV
Switchroom	 	 	1	 	 	 
	7.22
	 	Brice Engineers	 	Gas Suppression System, Primary Crushing HV
Switchroom	 	 	1	 	 	 
	7.23
	 	Brice Engineers	 	Gas Suppression System, Primary Conveying LV
Switchroom	 	 	1	 	 	 
	7.24
	 	Brice Engineers	 	Gas Suppression System, Ore Stockpile LV
Switchroom	 	 	1	 	 	 
	7.25
	 	Brice Engineers	 	Gas Suppression System, Wurtol Pumping Station LV
Switchroom	 	 	1	 	 	 
	7.26
	 	Brice Engineers	 	Gas Suppression System, Grinding LV Switchroom	 	 	1	 	 	 
	7.27
	 	Brice Engineers	 	Gas Suppression System, Grinding HV Switchroom	 	 	1	 	 	 
	7.28
	 	Brice Engineers	 	Gas Suppression System, Pressure Oxidation LV
Switchroom	 	 	1	 	 	 
	7.29
	 	Brice Engineers	 	Gas Suppression System, Pressure Oxidation HV
Switchroom	 	 	1	 	 	 
	7.30
	 	Brice Engineers	 	Gas Suppression System, Cyanidation & Adsorption
LV Switchroom	 	 	1	 	 	 
	731
	 	Brice Engineers	 	Gas Suppression System, Cyanidation & Adsorption
HV Switchroom	 	 	1	 	 	 
	7.32
	 	Brice Engineers	 	Gas Suppression System, Oxygen Plant LV
Switchroom	 	 	1	 	 	 
	7.33
	 	Brice Engineers	 	Gas Suppression System, Oxygen Plant HV
Switchroom	 	 	1	 	 	 
	7.34
	 	Brice Engineers	 	Gas Suppression System, Grinding Thickeners LV
Switchroom	 	 	1	 	 	 
	7.35
	 	Brice Engineers	 	Gas Suppression System, Process Seawater LV
Switchroom	 	 	1	 	 	 
	7.36
	 	Brice Engineers	 	Gas Suppression System, Bus C3, C4 & E LV
Switchroom	 	 	1	 	 	 
	7.37
	 	Brice Engineers	 	Gas Suppression System, Bus C3 & C4 HV Switchroom	 	 	1	 	 	 




Variations Pricing_Rev 00
Revised 230209 Q 4929 - NHP - MOPU-1101_Pricing Schedules


                                             Page 15 of 17 Pages

 







 




LIHIR MOPU Project
MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule



	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	Price
	7.38
	 	Brice Engineers	 	Gas Suppression System, Bus E HV Switchroom	 	 	1	 	 	 
	7.39
	 	Brice Engineers	 	Gas Suppression System, Bus F LV Switchroom	 	 	1	 	 	 
	7.40
	 	Brice Engineers	 	Gas Suppression System, Bus F HV Switchroom	 	 	1	 	 	 





OPTIONAL PRICING FOR 2 HOUR FIRE RATING OF SWITCHROOM WALLS

For Wall Adjacent to (or Floor Above) Transformers.


	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	 
	8.1
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Primary Crushing LV Switchroom	 	 	1	 	 	 
	8.2
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Primary Crushing HV Switchroom	 	 	1	 	 	 
	8.3
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Primary
Conveying LV Switchroom	 	 	1	 	 	 
	8.4
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Ore Stockpile LV Switchroom	 	 	1	 	 	 
	8.5
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Wurtol Pumping Station LV Switchroom	 	 	1	 	 	 
	8.6
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Grinding LV Switchroom	 	 	1	 	 	 
	8.7
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Grinding HV Switchroom	 	 	1	 	 	 
	8.8
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Pressure Oxidation LV Switchroom	 	 	1	 	 	 
	8.9
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Pressure Oxidation HV Switchroom	 	 	1	 	 	 
	8.10
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Cyanidation & Adsorption LV Switchroom	 	 	1	 	 	 
	8.11
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Cyanidation & Adsorption HV Switchroom	 	 	1	 	 	 
	8.12
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Oxygen Plant LV Switchroom	 	 	1	 	 	 
	8.13
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Oxygen Plant HV Switchroom	 	 	1	 	 	 
	8.14
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Grinding Thickener LV Switchroom	 	 	1	 	 	 
	8.15
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Process Seawater LV Switchroom	 	 	1	 	 	 
	8.16
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Bus C3, C4 & E LV Switchroom	 	 	1	 	 	 
	8.17
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Bus C3 & C4 HV Switchroom	 	 	1	 	 	 
	8.18
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Bus E HV Switchroom	 	 	1	 	 	 
	8.19
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Bus F LV Switchroom	 	 	1	 	 	 
	8.20
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls,
Bus F HV Switchroom	 	 	1	 	 	 
	8.21
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls,
Primary Crushing LV Switchroom	 	 	1	 	 	 
	8.22
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls,
Primary Crushing HV Switchroom	 	 	1	 	 	 
	8.23
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls,
Primary Conveying LV Switchroom	 	 	1	 	 	 
	8.24
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls,
Primary Conveying & Ore Stockpile LV Switchroom	 	 	1	 	 	 
	8.25
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls,
Wurtol Pumping Station LV Switchroom	 	 	1	 	 	 




Variations Pricing_Rev 00
Revised 230209 Q 4929 - NHP - MOPU-1101_Pricing Schedules

                                             Page 16 of 17 Pages


 







 




LIHIR MOPU Project
MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule



	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	Price
	8.26
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Grinding LV
Switchroom
	 	 	1	 	 	 
	8.27
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Grinding HV
Switchroom
	 	 	1	 	 	 
	8.28
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Pressure Oxidation
LV Switchroom
	 	 	1	 	 	 
	8.29
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Pressure Oxidation
HV Switchroom
	 	 	1	 	 	 
	8.30
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Cyanidation &
Adsorption LV
Switchroom
	 	 	1	 	 	 
	8.31
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Cyanidation &
Adsorption HV
Switchroom
	 	 	1	 	 	 
	8.32
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Oxygen Plant LV
Switchroom
	 	 	1	 	 	 
	8.33
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Oxygen Plant HV
Switchroom
	 	 	1	 	 	 
	8.34
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Grinding Thickeners
LV Switchroom
	 	 	1	 	 	 
	8.35
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Process Seawater LV
Switchroom
	 	 	1	 	 	 
	8.36
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Bus C3, C4 & E LV
Switchroom
	 	 	1	 	 	 
	8.37
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Bus C3 & C4 HV
Switchroom
	 	 	1	 	 	 
	8.38
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Bus E HV
Switchroom
	 	 	1	 	 	 
	8.39
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Bus F LV
Switchroom
	 	 	1	 	 	 
	8.40
	 	Brice Engineers
	 	Two (2) hour
fire rating of
Switchroom Walls,
Bus F HV
Switchroom
	 	 	1	 	 	 




Variations Pricing_Rev 00
Revised 230209 Q 4929 - NHP - MOPU-1101_Pricing Schedules


                                             Page 17 of 17 Pages


 







 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	 
	 	 	 	 	 	MOTOR CONTROL CENTRES (includes installation of free issued VSD/Soft Str)	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	MC2001A	 	SS2001	 	Primary Crushing MCC A	 	1 	 	 	 	 	 	 	 	 	 	 
	1314
	 	MC2001B	 	SS2001	 	Primary Crushing MCC B	 	1 	 	 	 	 	 	 	 	 	 	 
	1315
	 	MC2051	 	SS2051	 	Primary Conveyor MCC	 	1 	 	 	 	 	 	 	 	 	 	 
	1316
	 	MC2101	 	SS2101	 	Ore Stockpile MCC	 	1 	 	 	 	 	 	 	 	 	 	 
	1825
	 	MC2160	 	SS2160	 	Wurtol Pumping Station MCC	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	MC2201A	 	SS2200	 	Grinding & Classification MCC A	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	MC2201B	 	SS2200	 	Grinding & Classification MCC B	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	MC2401A	 	SS2400	 	Pressure Oxidation MCC A	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	MC2401B	 	SS2400	 	Pressure Oxidation MCC B	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	MC2401C	 	SS2400	 	Pressure Oxidation MCC C	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	MC2401D	 	SS2400	 	Pressure Oxidation MCC D	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	MC2551A	 	SS2551	 	Cyanidation & Adsorption MCC A	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	MC2551B	 	SS2551	 	Cyanidation & Adsorption MCC B	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	MC2561A	 	SS2560	 	Oxygen Plant MCC A	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	MC2561B	 	SS2560	 	Oxygen Plant MCC B	 	1 	 	 	 	 	 	 	 	 	 	 
	1341
	 	MC2741	 	SS2741	 	Grinding Thickeners MCC	 	1 	 	 	 	 	 	 	 	 	 	 
	1830
	 	MC2850	 	SS2850	 	Process Seawater MCC	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	MC2931	 	SS2931	 	Bus E Auxilliary MCC	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	MC2932	 	SS2932	 	Bus F Auxilliary MCC	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price MCCs	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	SWITCHROOMS (James Engineering)	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	SS2001A	 	SS2001	 	Primary Crushing LV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1314
	 	SS2001B	 	SS2001	 	Primary Crushing HV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1315
	 	SS2051	 	SS2051	 	Primary Conveying LV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1316
	 	SS2101	 	SS2101	 	Ore Stockpile LV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1825
	 	SS2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	SS2200A	 	SS2200	 	Grinding Area LV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	SS2200B	 	SS2200	 	Grinding Area HV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	SS2400A	 	SS2400	 	Pressure Oxidation LV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	SS2400B	 	SS2400	 	Pressure Oxidation HV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	SS2551A	 	SS2551	 	Cyanidation & Adsorption LV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	SS2551B	 	SS2551	 	Cyanidation & Adsorption HV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	SS2560A	 	SS2560	 	Oxygen Plant LV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	SS2560B	 	SS2560	 	Oxygen Plant HV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1341
	 	SS2741	 	SS2741	 	Grinding Thickeners LV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1830
	 	SS2850	 	SS2850	 	Process Seawater LV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2931A	 	SS2931	 	Bus C3, C4 & E LV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2931B	 	SS2931	 	Bus C3 & C4 HV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2931C	 	SS2931	 	Bus EHV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2932A	 	SS2932	 	Bus FLV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2932B	 	SS2932	 	Bus FHV Switchroom	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	VESDA Systems	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	SS2001A	 	SS2001	 	Primary Crushing LV Switchroom VESDA System	 	1 	 	 	 	 	 	 	 	 	 	 
	1314
	 	SS2001B	 	SS2001	 	Primary Crushing HV Switchroom VESDA System	 	1 	 	 	 	 	 	 	 	 	 	 
	1315
	 	SS2051	 	SS2051	 	Primary Conveying LV Switchroom VESDA System	 	1 	 	 	 	 	 	 	 	 	 	 





 








 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1316

	 	SS2101
	 	SS2101
	 	Ore Stockpile LV Switchroom VESDA System
	 	1 
	 	 
	 	 
	 	 
	 	 
	 	 
	1825

	 	SS2160
	 	SS2160
	 	Wurtol Pumping Station LV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1326

	 	SS2200A
	 	SS2200
	 	Grinding Area LV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1326

	 	SS2200B
	 	SS2200
	 	Grinding Area HV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1343

	 	SS2400A
	 	SS2400
	 	Pressure Oxidation LV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1343

	 	SS2400B
	 	SS2400
	 	Pressure Oxidation HV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1351

	 	SS2551A
	 	SS2551
	 	Cyanidation & Adsorption LV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1351

	 	SS2551B
	 	SS2551
	 	Cyanidation & Adsorption HV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1560

	 	SS2560A
	 	SS2560
	 	Oxygen Plant LV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1560

	 	SS2560B
	 	SS2560
	 	Oxygen Plant HV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1341

	 	SS2741
	 	SS2741
	 	Grinding Thickeners LV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1830

	 	SS2850
	 	SS2850
	 	Process Seawater LV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931A
	 	SS2931
	 	Bus C3, C4 & E LV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931B
	 	SS2931
	 	Bus C3 & C4 HV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931C
	 	SS2931
	 	Bus E HV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2932A
	 	SS2932
	 	Bus F LV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2932B
	 	SS2932
	 	Bus F HV Switchroom VESDA System
	 	1 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Total Price Switchrooms from James Engineering	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	SWITCHROOMS (Brice Engineers)	 	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	SS2001A
	 	SS2001
	 	Primary Crushing LV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	SS2001B
	 	SS2001
	 	Primary Crushing HV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1315

	 	SS2051
	 	SS2051
	 	Primary Conveying LV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1316

	 	SS2101
	 	SS2101
	 	Ore Stockpile LV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1825

	 	SS2160
	 	SS2160
	 	Wurtol Pumping Station LV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1326

	 	SS2200A
	 	SS2200
	 	Grinding Area LV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1326

	 	SS2200B
	 	SS2200
	 	Grinding Area HV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	SS2400A
	 	SS2400
	 	Pressure Oxidation LV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	SS2400B
	 	SS2400
	 	Pressure Oxidation HV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	SS2551A
	 	SS2551
	 	Cyanidation & Adsorption LV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	SS2551B
	 	SS2551
	 	Cyanidation & Adsorption HV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	SS2560A
	 	SS2560
	 	Oxygen Plant LV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	SS2560B
	 	SS2560
	 	Oxygen Plant HV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1341

	 	SS2741
	 	SS2741
	 	Grinding Thickeners LV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1830

	 	SS2850
	 	SS2850
	 	Process Seawater LV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931A
	 	SS2931
	 	Bus C3, C4 & E LV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931B
	 	SS2931
	 	Bus C3 & C4 HV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931C
	 	SS2931
	 	Bus E HV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2932A
	 	SS2932
	 	Bus F LV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2932B
	 	SS2932
	 	Bus F HV Switchroom	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	VESDA Systems	 	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	SS2001A
	 	SS2001
	 	Primary Crushing LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	SS2001B
	 	SS2001
	 	Primary Crushing HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1315

	 	SS2051
	 	SS2051
	 	Primary Conveying LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1316

	 	SS2101
	 	SS2101
	 	Ore Stockpile LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1825

	 	SS2160
	 	SS2160
	 	Wurtol Pumping Station LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1326

	 	SS2200A
	 	SS2200
	 	Grinding Area LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 






 









 






	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1326

	 	SS2200B
	 	SS2200
	 	Grinding Area HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	SS2400A
	 	SS2400
	 	Pressure Oxidation LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	SS2400B
	 	SS2400
	 	Pressure Oxidation HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	SS2551A
	 	SS2551
	 	Cyanidation & Adsorption LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	SS2551B
	 	SS2551
	 	Cyanidation & Adsorption HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	SS2560A
	 	SS2560
	 	Oxygen Plant LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	SS2560B
	 	SS2560
	 	Oxygen Plant HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1341

	 	SS2741
	 	SS2741
	 	Grinding Thickeners LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1830

	 	SS2850
	 	SS2850
	 	Process Seawater LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931A
	 	SS2931
	 	Bus C3, C4 & E LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931B
	 	SS2931
	 	Bus C3 & C4 HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931C
	 	SS2931
	 	Bus E HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2932A
	 	SS2932
	 	Bus F LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2932B
	 	SS2932
	 	Bus F HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Total Price Switchrooms from Brice Engineers	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	DISTRIBUTION BOARDS (Chassis and Panel Only)	 	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	DB2001A
	 	SS2001
	 	Primary Crushing LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1 
	 	 
	 	 
	 	 
	 	 
	 	 
	1314

	 	DB2001B
	 	SS2001
	 	Primary Crushing HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1314

	 	DB2001C
	 	SS2001
	 	Primary Crushing UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1314

	 	DB2001D
	 	SS2001
	 	Primary Crushing Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1 	 	 	 	 	 	 	 	 	 	 
	1315

	 	DB2051A
	 	SS2051
	 	Primary Conveying LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1315

	 	DB2051B
	 	SS2051
	 	Primary Conveying UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1315

	 	DB2051C
	 	SS2051
	 	Primary Conveying Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1 	 	 	 	 	 	 	 	 	 	 
	1316

	 	DB2101A
	 	SS2101
	 	Ore Stockpile LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1316

	 	DB2101B
	 	SS2101
	 	Ore Stockpile UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1316

	 	DB2101C
	 	SS2101
	 	Ore Stockpile Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1 	 	 	 	 	 	 	 	 	 	 
	1825

	 	DB2160A
	 	SS2160
	 	Wurtol Pumping Station LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A. 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1825

	 	DB2160B
	 	SS2160
	 	Wurtol Pumping Station UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1825

	 	DB2160C
	 	SS2160
	 	Wurtol Pumping Station Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1 	 	 	 	 	 	 	 	 	 	 
	1326

	 	DB2201A
	 	SS2201
	 	Grinding LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1326

	 	DB2201B
	 	SS2201
	 	Grinding HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1326

	 	DB2201C
	 	SS2201
	 	Grinding Area UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1326

	 	DB2201D
	 	SS2201
	 	Grinding Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1 	 	 	 	 	 	 	 	 	 	 






 









 






	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1343

	 	DB2401A
	 	SS2401
	 	Pressure Oxidation LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1 
	 	 
	 	 
	 	 
	 	 
	 	 
	1343

	 	DB2401B
	 	SS2401
	 	Pressure Oxidation HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1343

	 	DB2401C
	 	SS2401
	 	Pressure Oxidation UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1343

	 	DB2401D
	 	SS2401
	 	Pressure Oxidation Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1 	 	 	 	 	 	 	 	 	 	 
	1351

	 	DB2551A
	 	SS2551
	 	Cyanidation & Adsorption LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s
	 	1 	 	 	 	 	 	 	 	 	 	 
	1351

	 	DB2551B
	 	SS2551
	 	Cyanidation & Adsorption HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s
	 	1 	 	 	 	 	 	 	 	 	 	 
	1351

	 	DB2551C
	 	SS2551
	 	Cyanidation & Adsorption UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1351

	 	DB2551D
	 	SS2551
	 	Cyanidation & Adsorption Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1 	 	 	 	 	 	 	 	 	 	 
	1560

	 	DB2561A
	 	SS2560
	 	Oxygen Plant LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s
	 	1 	 	 	 	 	 	 	 	 	 	 
	1560

	 	DB2561B
	 	SS2560
	 	Oxygen Plant HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s
	 	1 	 	 	 	 	 	 	 	 	 	 
	1560

	 	DB2561C
	 	SS2560
	 	Oxygen Plant UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1560

	 	DB2561D
	 	SS2560
	 	Oxygen Plant Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1 	 	 	 	 	 	 	 	 	 	 
	1341

	 	DB2741A
	 	SS2741
	 	Grinding Thickeners LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1341

	 	DB2741B
	 	SS2741
	 	Grinding Thickeners UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1341

	 	DB2741C
	 	SS2741
	 	Grinding Thickeners Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1 	 	 	 	 	 	 	 	 	 	 
	1830

	 	DB2850A
	 	SS2850
	 	Process Seawater LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1830

	 	DB2850B
	 	SS2850
	 	Process Seawater Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1 	 	 	 	 	 	 	 	 	 	 
	1780

	 	DB2931A
	 	SS2931
	 	Bus C3, C4 & E Light & Power Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1 	 	 	 	 	 	 	 	 	 	 
	1780

	 	DB2931B
	 	SS2931
	 	Bus C3, C4 & E UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	1780

	 	DB2932A
	 	SS2932
	 	Bus F Light & Power Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1 	 	 	 	 	 	 	 	 	 	 
	1780

	 	DB2932B
	 	SS2932
	 	Bus F UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	PC Sum for Fitout of DB’s with Circuit Breakers
	 	PC 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Total Price Distribution Boards	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	UNINTERRUPTIBLE POWER SUPPLIES	 	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	UP2001
	 	SS2001
	 	Primary Crushing LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out
	 	1 	 	 	 	 	 	 	 	 	 	 
	1315

	 	UP2051
	 	SS2051
	 	Primary Conveying LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out
	 	1 	 	 	 	 	 	 	 	 	 	 






 









 






	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1316
	 	UP2101	 	SS2101	 	Ore Stockpile LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out	 	1 	 	 	 	 	 	 	 	 	 	 
	1825
	 	UP2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	UP2201	 	SS2200	 	Grinding Area LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	UP2401	 	SS2400	 	Pressure Oxidation LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	UP2551	 	SS2551	 	Cyanidation & Absorption LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	UP2561	 	SS2560	 	Oxygen Plant LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out	 	1 	 	 	 	 	 	 	 	 	 	 
	1341
	 	UP2741	 	SS2741	 	Grinding Thickeners LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	UP2931	 	SS2931	 	Bus C3, C4 & E LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	UP2932	 	SS2932	 	Bus F LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price UPS	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Control Panels	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	CP2001A	 	SS2001	 	Primary Crushing LV Switchroom DCS Panel A	 	1 	 	 	 	 	 	 	 	 	 	 
	1314
	 	CP2001B	 	SS2001	 	Primary Crushing LV Switchroom DCS Panel B	 	1 	 	 	 	 	 	 	 	 	 	 
	1315
	 	CP2051	 	SS2051	 	Primary Conveying LV Switchroom DCS Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1316
	 	CP2101	 	SS2101	 	Ore Stockpile LV Switchroom DCS Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	CP2201A	 	SS2200	 	Grinding Area LV Switchroom DCS Panel A	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	CP2201B	 	SS2200	 	Grinding Area LV Switchroom DCS Panel B	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	CP2401A	 	SS2400	 	Pressure Oxidation LV Switchroom DCS Panel A	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	CP2401B	 	SS2400	 	Pressure Oxidation LV Switchroom DCS Panel B	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	CP2551A	 	SS2551	 	Cyanidation & Absorption LV Switchroom DCS Panel A	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	CP2551B	 	SS2551	 	Cyanidation & Absorption LV Switchroom DCS Panel B	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	CP2560A	 	SS2560	 	Oxvgen Plant LV Switchroom DCS Panel A	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	CP2560B	 	SS2560	 	Oxygen Plant LV Switchroom DCS Panel B	 	1 	 	 	 	 	 	 	 	 	 	 
	1341
	 	CP2741	 	SS2741	 	Grinding Thickeners LV Switchroom DCS Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1825
	 	CP2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom PLC Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	CP2931A	 	SS2931	 	Bus C3, C4 & E HV Switchroom PLC Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	CP2932A	 	SS2932	 	Bus F HV Switchroom PLC Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	CP2603	 	SS2560	 	PC Sum for Installation of Oxygen Plant Hardwired Emergency Trip Panel	 	PC 	 	 	 	 	 	 	 	 	 	 
	1830
	 	CP2850	 	SS2850	 	PC Sum for Installation of Process Seawater LV Switchroom Control Panel	 	PC 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	PC Sum for Internal Marshalling of 13 DCS Panels	 	PC 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	PC Sum for Cabling of 18 Panels Within Switchrooms	 	PC 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	PC Sum for Installation of 19” RM FOBOTs in LV Switchrooms	 	PC 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price Control Panels	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	BATTERY CHARGER SYSTEMS	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	BC2000	 	SS2001	 	Primary Crushing HV Switchroom 48VDC, 70Ahr	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	BC2200	 	SS2200	 	Grinding Area HV Switchroom 48VDC, 70Ahr	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	BC2400	 	SS2400	 	Pressure Oxidation HV Switchroom 48VDC, 70Ahr	 	1 	 	 	 	 	 	 	 	 	 	 





 








 






	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1351
	 	BC2550	 	SS2551	 	Cyanidation & Absorption HV Switchroom 48VDC, 70Ahr	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	BC2560	 	SS2560	 	Oxygen Plant HV Switchroom 48VDC, 160Ahr	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	BC2900	 	SS2931	 	Bus C3 & C4 HV Switchroom 48VDC, 160Ahr	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	BC2931	 	SS2931	 	Bus E HV Switchroom 48VDC, 230Ahr	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	BC2932	 	SS2932	 	Bus F HV Switchroom 48VDC. 230Ahr	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price Battery Charger Systems	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	HV SWITCHBOARDS	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	SW2000	 	SS2001	 	Primary Crushing 11 kV Switchboard	 	1 	 	 	 	 	 	 	 	 	 	 
	1314
	 	SW2001	 	SS2001	 	HGO Crusher 3.3kV Switchboard	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	SW2200	 	SS2200	 	Grinding Area 11 kV Switchboard	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	SW2400	 	SS2400	 	Pressure Oxidation 11 kV Switchboard	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	SW2550	 	SS2551	 	Cyanidation & Absorption 11 kV Switchboard	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	SW2560	 	SS2560	 	Oxygen Plant 11 kV Switchboard	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SW2900	 	SS2931	 	Bus C3 & C4 11 kV Switchboard	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SW2931	 	SS2931	 	Bus E 33kV Switchboard	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SW2932	 	SS2932	 	Bus F 33kV Switchboard	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price HV Switchboards	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	HV REMOTE SWITCHING PANELS	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	CP2000	 	SS2001	 	Primary Crushing 11kV & 3.3kV Remote Switching Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	CP2200	 	SS2200	 	Grinding Area 11kV Remote Switching Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	CP2400	 	SS2400	 	Pressure Oxidation 11kV Remote Switching Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	CP2550	 	SS2551	 	Cyanidation & Absorption 11kV Remote Switching Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	CP2560	 	SS2560	 	Oxygen Plant 11kV Remote Switching Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	CP2900	 	SS2931	 	Bus C3 & C4 11kV Remote Switching Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	CP2900A	 	SS2931	 	Bus C3 & C4 11kV Tariff Metering Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	CP2931	 	SS2931	 	Bus E 33kV Remote Switching Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	1780
	 	CP2932	 	SS2932	 	Bus F 33kV Remote Switching Panel	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	PC Sum for Cabling of 9 Panels Within Switchrooms	 	PC 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price HV Remote Switching Panels	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	FLOOR MOUNTED VSDs	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	FD2001	 	SS2001	 	Primary Apron Feeder VSD 315kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1315
	 	FD2003	 	SS2101	 	HGO Apron Feeder No.1 VSD 55kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1315
	 	FD2004	 	SS2101	 	HGO Apron Feeder No.2 VSD 55kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1315
	 	FD2005	 	SS2101	 	HGO Emergency Apron Feeder VSD 55kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1825
	 	PU2161	 	SS2160	 	Wurtol Raw Water Pump No.1 VSD 600kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1825
	 	PU2162	 	SS2160	 	Wurtol Raw Water Pump No.2 VSD 600kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1825
	 	PU2163	 	SS2160	 	Wurtol Raw Water Pump No.3 VSD 600kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2030	 	SS2200	 	Pre-oxidation Feed Pump No.1 VSD 185kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2031	 	SS2200	 	Pre-oxidation Feed Pump No.2 VSD 185kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2040	 	SS2200	 	Cyclone Overflow Transfer Pump No.1 VSD 400kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2041	 	SS2200	 	Cyclone Overflow Transfer Pump No.2 VSD 400kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2042	 	SS2200	 	Cyclone Overflow Transfer Pump No.3 VSD 400kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2043	 	SS2200	 	Cyclone Overflow Transfer Pump No.4 VSD 400kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2021	 	SS2200	 	Cyclone Feed Pump No.1 VSD 525kW	 	1 	 	 	 	 	 	 	 	 	 	 





 








 






	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1326
	 	PU2022	 	SS2200	 	Cyclone Feed Pump No.2 VSD 525kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	PU2741	 	SS2400	 	Autoclave Feed Booster Pump VSD 185kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	AG2245	 	SS2400	 	Autoclave No.4 Compartments 3-6 Agitator VSD 200kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	PU2123	 	SS2400	 	Flashed Slurry Forwarding Pump No.1 VSD 200kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	PU2124	 	SS2400	 	Flashed Slurry Forwarding Pump No.2 VSD 200kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	PU2125	 	SS2400	 	Flashed Slurry Forwarding Pump No.3 VSD 200kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	AG2241	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	AG2242	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	AG2243	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	AG2244	 	SS2400	 	Autoclave No.4 Compartments 1 A-1 C Agitator VSD 400kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	PU2033	 	SS2400	 	Autoclave Feed Pump No.1 VSD 600kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1343
	 	PU2034	 	SS2400	 	Autoclave Feed Pump No.2 VSD 600kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	PU2105	 	SS2551	 	Lime Recirculation Pump VSD 30kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	PU2058	 	SS2551	 	Leach Trash Screen Feed Pump VSD 110kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	PU2212	 	SS2551	 	CIL Tails Pump No.1 VSD 315kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1351
	 	PU2213	 	SS2551	 	CIL Tails Pump No.2 VSD 315kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	P440A	 	SS2560	 	LOX Process Pump A VSD 150kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1560
	 	P440B	 	SS2560	 	LOX Process Pump B VSD 150kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1341
	 	PU2026	 	SS2741	 	Grinding Thickener No.1 U/F Pump No.1 VSD 75kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1341
	 	PU2027	 	SS2741	 	Grinding Thickener No.1 U/F Pump No.2 VSD 75kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1341
	 	PU2028	 	SS2741	 	Grinding Thickener No.2 U/F Pump No.1 VSD 525kW	 	1 	 	 	 	 	 	 	 	 	 	 
	1341
	 	PU2029	 	SS2741	 	Grinding Thickener No.2 U/F Pump No.2 VSD 525kW	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price VSDs	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	LOCAL CONTROL STATIONS (Supply price for each even if quantity is 0)	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-01	 	 	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <30kW)	 	174 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-02	 	 	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <55kW)	 	5 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-03	 	 	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <90kW)	 	14 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-04	 	 	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <185kW)	 	13 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-05	 	 	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors <30kW)	 	6 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-06	 	 	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors <55kW)	 	7 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-07	 	 	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors <90kW)	 	2 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-08	 	 	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors <l85kW)	 	7 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-09	 	 	 	Local control station with start pushbutton, emergency stop button and labels (no isolator)	 	21 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-10	 	 	 	Local control station with start pushbutton, stop pushbutton, emergency stop button and labels (no isolator)	 	25 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-11	 	 	 	Local control station with forward pushbutton, reverse pushbutton, emergency stop button and labels (no isolator)	 	2 	 	 	 	 	 	 	 	 	 	 





 








 






	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	 
	 	LCS-12	 	 	 	80 amp, 3 pole isolator only	 	19 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-13	 	 	 	125 amp, 3 pole isolator only	 	2 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-14	 	 	 	200 amp, 3 pole isolator only	 	0 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-15	 	 	 	400 amp, 3 pole isolator only	 	0 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-16	 	 	 	Lock-off emergency stop pushbutton only	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-17	 	 	 	80 amp, 6 pole isolator, reverse, forward pushbutton, lock-off emergency stop and labels (DRD/slew motors <30kW)	 	7 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-18	 	 	 	Local control station with 63 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)	 	34 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-19	 	 	 	Local control station with 63 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button, multitrode level relay and labels (include male decontactor)	 	3 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-20	 	 	 	Local control station with 125 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button, multitrode level relay and labels (include male decontactor)	 	2 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-21	 	 	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton, larger box, extra terminals and labels (conveyors <30kW)	 	3 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-22	 	 	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton, larger box, extra terminals and labels (conveyors <55kW)	 	0 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-23	 	 	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton, larger box, extra terminals and labels (conveyors <90kW)	 	0 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-24	 	 	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton, larger box, extra terminals and labels (conveyors <185kW)	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price Local Control Stations	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Drawings and Documentation	 	Lot	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Packaging	 	Lot	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Lifting Equipment	 	Lot	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Inland Freight to Port	 	Lot	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Drawings / Packaging / Transport	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total MCC & Switchrooms (without Options)	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	RECOMMENDED OPTIONS	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	1 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total MCC & Switchrooms (with Options)	 	 	 	 	 	 	 	 	 	 	 	 





 








 




LIHIR MOPU Project
MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule



	 	 	 	 	 	 	 	 	 	 	 
	SCHEDULE OF PRICES	 	 	 	 
	VARIATIONS FOR ADDITIONS AND DELETIONS for MCC DOL STARTERS	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	Price
	1.1
	 	0.37kW DOL	 	1 x 0.37kW DOL Starter	 	 	1	 	 	 
	1.2
	 	0.55kW DOL	 	1 x 0.55kW DOL Starter	 	 	1	 	 	 
	1.3
	 	1.1kW DOL	 	1 x 1.1kW DOL Starter	 	 	1	 	 	 
	1.4
	 	1.5kW DOL	 	1 x 1.5kW DOL Starter	 	 	1	 	 	 
	1.5
	 	2.2kW DOL	 	1 x 2.2kW DOL Starter	 	 	1	 	 	 
	1.6
	 	3kW DOL	 	1 x 3kW DOL Starter	 	 	1	 	 	 
	1.7
	 	4kW DOL	 	1 x 4kW DOL Starter	 	 	1	 	 	 
	1.8
	 	5.5kW DOL	 	1 x 5.5kW DOL Starter	 	 	1	 	 	 
	1.9
	 	7.5kW DOL	 	1 x 7.5kW DOL Starter	 	 	1	 	 	 
	1.10
	 	11kW DOL	 	1 x 11kW DOL Starter	 	 	1	 	 	 
	1.11
	 	15kW DOL	 	1 x 15kW DOL Starter	 	 	1	 	 	 
	1.12
	 	18.5kW DOL	 	1 x 18.5kW DOL Starter	 	 	1	 	 	 
	1.13
	 	22kW DOL	 	1 x 22kW DOL Starter	 	 	1	 	 	 
	1.14
	 	30kW DOL	 	1 x 30kW DOL Starter	 	 	1	 	 	 
	1.15
	 	37kW DOL	 	1 x 37kW DOL Starter	 	 	1	 	 	 
	1.16
	 	45kW DOL	 	1 x 45kW DOL Starter	 	 	1	 	 	 
	1.17
	 	55kW DOL	 	1 x 55kW DOL Starter	 	 	1	 	 	 
	1.18
	 	75kW DOL	 	1 x 75kW DOL Starter	 	 	1	 	 	 
	1.19
	 	90kW DOL	 	1 x 90kW DOL Starter	 	 	1	 	 	 
	1.20
	 	110kW DOL	 	1 x 110kW DOL Starter	 	 	1	 	 	 
	1.21
	 	132kW DOL	 	1 x 132kW DOL Starter	 	 	1	 	 	 
	1.22
	 	150kW DOL	 	1 x 150kW DOL Starter	 	 	1	 	 	 
	1.23
	 	185kW DOL	 	1 x 185kW DOL Starter	 	 	1	 	 	 
	1.24
	 	200kW DOL	 	1 x 200kW DOL Starter	 	 	1	 	 	 
	1.25
	 	220kW DOL	 	1 x 220kW DOL Starter	 	 	1	 	 	 
	1.26
	 	250kW DOL	 	1 x 250kW DOL Starter	 	 	1	 	 	 
	1.27
	 	280kW DOL	 	1 x 280kW DOL Starter	 	 	1	 	 	 
	1.28
	 	315kW DOL	 	1 x 315kW DOL Starter	 	 	1	 	 	 
	1.29
	 	355kW DOL	 	1 x 355kW DOL Starter	 	 	1	 	 	 
	1.30
	 	400kW DOL	 	1 x 400kW DOL Starter	 	 	1	 	 	 
	1.31
	 	450kW DOL	 	1 x 450kW DOL Starter	 	 	1	 	 	 
	1.32
	 	500kW DOL	 	1 x 500kW DOL Starter	 	 	1	 	 	 
	1.33
	 	560kW DOL	 	1 x 560kW DOL Starter	 	 	1	 	 	 
	1.34
	 	630kW DOL	 	1 x 630kW DOL Starter	 	 	1	 	 	 
	 
	VARIATIONS FOR ADDITIONS AND DELETIONS for MCC VSD MODULES

Installation Only. All VSDs are free issued.
	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	 
	2.1
	 	0.55kW VSD	 	1 x 0.55kW VSD Starter	 	 	1	 	 	 
	2.2
	 	1.1kW VSD	 	1 x 1.1kW VSD Starter	 	 	1	 	 	 
	2.3
	 	1.5kW VSD	 	1 x 1.5kW VSD Starter	 	 	1	 	 	 
	2.4
	 	2.2kW VSD	 	1 x 2.2kW VSD Starter	 	 	1	 	 	 
	2.5
	 	3.7kW VSD	 	1 x 3.7kW VSD Starter	 	 	1	 	 	 
	2.6
	 	5.5kW VSD	 	1 x 5.5kW VSD Starter	 	 	1	 	 	 
	2.7
	 	7.5kW VSD	 	1 x 7.5kW VSD Starter	 	 	1	 	 	 
	2.8
	 	11kW VSD	 	1 x 11kW VSD Starter	 	 	1	 	 	 
	2.9
	 	15kW VSD	 	1 x 15kW VSD Starter	 	 	1	 	 	 
	2.10
	 	18.5kW VSD	 	1 x 18.5kW VSD Starter	 	 	1	 	 	 
	2.11
	 	22kW VSD	 	1 x 22kW VSD Starter	 	 	1	 	 	 
	2.12
	 	30kW VSD	 	1 x 30kW VSD Starter	 	 	1	 	 	 
	2.13
	 	37kW VSD	 	1 x 37kW VSD Starter	 	 	1	 	 	 
	2.14
	 	45kW VSD	 	1 x 45kW VSD Starter	 	 	1	 	 	 
	2.15
	 	55kW \/SD	 	1 x 55kW \/SD Starter	 	 	1	 	 	 




Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 9 of 15 Pages


 







 




LIHIR MOPU Project
MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule



	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	Price
	2.16
	 	75kW VSD	 	1 x 75kW VSD Starter	 	 	1	 	 	 
	2.17
	 	90kW VSD	 	1 x 90kW VSD Starter	 	 	1	 	 	 
	2.18
	 	110kW VSD	 	1 x 110kW VSD Starter	 	 	1	 	 	 
	2.19
	 	132KW VSD	 	1 x 132kW VSD Starter	 	 	1	 	 	 
	2.20
	 	150kW VSD	 	1 x 150kW VSD Starter	 	 	1	 	 	 
	2.21
	 	185kW VSD	 	1 x 185kW VSD Starter	 	 	1	 	 	 
	2.22
	 	220kW VSD	 	1 x 220kW VSD Starter	 	 	1	 	 	 
	2.23
	 	280kW VSD	 	1 x 280kW VSD Starter	 	 	1	 	 	 
	2.24
	 	315kW VSD	 	1 x 315kW VSD Starter	 	 	1	 	 	 
	2.25
	 	355kW VSD	 	1 x 355kW VSD Starter	 	 	1	 	 	 
	2.26
	 	400kW VSD	 	1 x 400kW VSD Starter	 	 	1	 	 	 
	2.27
	 	450kW VSD	 	1 x 450kW VSD Starter	 	 	1	 	 	 
	2.28
	 	500kW VSD	 	1 x 500kW VSD Starter	 	 	1	 	 	 
	2.29
	 	630kW VSD	 	1 x 630kW VSD Starter	 	 	1	 	 	 
	 
	VARIATIONS FOR ADDITIONS AND DELETIONS for MCC SOFT STARTER MODULES

Installation Only. All soft starters are free issued.
	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	 
	3.1
	 	132kW SSD	 	1 x 132kW Soft Starter	 	 	1	 	 	 
	3.2
	 	150kW SSD	 	1 x 150kW Soft Starter	 	 	1	 	 	 
	3.3
	 	160kW SSD	 	1 x 160kW Soft Starter	 	 	1	 	 	 
	3.4
	 	185kW SSD	 	1 x 185kW Soft Starter	 	 	1	 	 	 
	3.5
	 	220kW SSD	 	1 x 220kW Soft Starter	 	 	1	 	 	 
	3.6
	 	250kW SSD	 	1 x 250kW Soft Starter	 	 	1	 	 	 
	3.7
	 	280kW SSD	 	1 x 280kW Soft Starter	 	 	1	 	 	 
	3.8
	 	315kW SSD	 	1 x 315kW Soft Starter	 	 	1	 	 	 
	3.9
	 	355kW SSD	 	1 x 355kW Soft Starter	 	 	1	 	 	 
	3.10
	 	400kW SSD	 	1 x 400kW Soft Starter	 	 	1	 	 	 
	3.11
	 	450kW SSD	 	1 x 450kW Soft Starter	 	 	1	 	 	 
	3.12
	 	500kW SSD	 	1 x 500kW Soft Starter	 	 	1	 	 	 
	3.13
	 	630kW SSD	 	1 x 630kW Soft Starter	 	 	1	 	 	 
	 
	VARIATIONS FOR ADDITIONS AND DELETIONS for MCC FEEDER/INCOMER MODULES
	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	 
	4.1
	 	40 F	 	1 x 40 Amp Circuit Breaker Feeder Module	 	 	1	 	 	 
	4.2
	 	63 F	 	1 x 63 Amp Circuit Breaker Feeder Module	 	 	1	 	 	 
	4.3
	 	100 F	 	1 x 100 Amp Circuit Breaker Feeder Module	 	 	1	 	 	 
	4.4
	 	160 F	 	1 x 160 Amp Circuit Breaker Feeder Module	 	 	1	 	 	 
	4.5
	 	200 F	 	1 x 200 Amp Circuit Breaker Feeder Module	 	 	1	 	 	 
	4.6
	 	250 F	 	1 x 250 Amp Circuit Breaker Feeder Module	 	 	1	 	 	 
	4.7
	 	400 F	 	1 x 400 Amp Circuit Breaker Feeder Module	 	 	1	 	 	 
	4.8
	 	630 F	 	1 x 630 Amp Circuit Breaker Feeder Module	 	 	1	 	 	 
	4.9
	 	1250 F	 	1 x 1250 Amp Circuit Breaker Feeder Module	 	 	1	 	 	 
	4.10
	 	40 F/C	 	1 x 40 Amp Circuit Breaker Feeder/Contactor Module	 	 	1	 	 	 
	4.11
	 	63 F/C	 	1 x 63 Amp Circuit Breaker Feeder/Contactor Module	 	 	1	 	 	 
	4.12
	 	100 F/C	 	1 x 100 Amp Circuit Breaker Feeder/Contactor Module	 	 	1	 	 	 
	4.13
	 	160 F/C	 	1 x 160 Amp Circuit Breaker Feeder/Contactor Module	 	 	1	 	 	 
	4.14
	 	200 F/C	 	1 x 200 Amp Circuit Breaker Feeder/Contactor Module	 	 	1	 	 	 
	4.15
	 	250 F/C	 	1 x 250 Amp Circuit Breaker Feeder/Contactor Module	 	 	1	 	 	 
	4.16
	 	400 F/C	 	1 x 400 Amp Circuit Breaker Feeder/Contactor Module	 	 	1	 	 	 
	4.17
	 	630 F/C	 	1 x 630 Amp Circuit Breaker Feeder/Contactor Module	 	 	1	 	 	 
	4.18
	 	1250 F/C	 	1 x 1250 Amp Circuit Breaker Feeder/Contactor Module	 	 	1	 	 	 
	4.15
	 	800 IC	 	1 x 800 Amp Air Circuit Breaker Incomer	 	 	1	 	 	 
	4.16
	 	1600 IC	 	1 x 1600 Amp Air Circuit Breaker Incomer	 	 	1	 	 	 
	4.17
	 	3200 IC	 	1 x 3200 Amp Air Circuit Breaker Incomer	 	 	1	 	 	 
	4.18
	 	4000 IC	 	1 x 4000 Amp Air Circuit Breaker Incomer	 	 	1	 	 	 




Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 10 of 15 Pages


 







 




LIHIR MOPU Project
MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule



	 	 	 	 	 	 	 	 	 	 	 
	VARIATIONS FOR ADDITIONS AND DELETIONS for LCS TYPES	 	 
	 
	Item No.	 	LCS Type	 	Description	 	Qty	 	Price
	5.1
	 	LCS-1
	 	80 amp, 3 pole isolator, lock-off
emergency stop, start pushbutton and
labels (DOL motors £30kW)
	 	 	1	 	 	 
	5.2
	 	LCS-2
	 	125 amp, 3 pole isolator, lock-off
emergency stop, start pushbutton and
labels (DOL motors £55kW)
	 	 	1	 	 	 
	5.3
	 	LCS-3
	 	200 amp, 3 pole isolator, lock-off
emergency stop, start pushbutton and
labels (DOL motors £90kW)
	 	 	1	 	 	 
	5.4
	 	LCS-4
	 	400 amp, 3 pole isolator, lock-off
emergency stop, start pushbutton and
labels (DOL motors £185kW)
	 	 	1	 	 	 
	5.5
	 	LCS-5
	 	80 amp, 3 pole isolator, lock-off
emergency stop, start pushbutton, stop
pushbutton and labels (VSD motors £30kW)
	 	 	1	 	 	 
	5.6
	 	LCS-6
	 	125 amp, 3 pole isolator, lock-off
emergency stop, start pushbutton, stop
pushbutton and labels (VSD motors £55kW)
	 	 	1	 	 	 
	5.7
	 	LCS-7
	 	200 amp, 3 pole isolator, lock-off
emergency stop, start pushbutton, stop
pushbutton and labels (VSD motors £90kW)
	 	 	1	 	 	 
	5.8
	 	LCS-8
	 	400 amp, 3 pole isolator, lock-off
emergency stop, start pushbutton, stop
pushbutton and labels (VSD motors £185kW)
	 	 	1	 	 	 
	5.9
	 	LCS-9
	 	Local control station with start
pushbutton, emergency stop button and
labels (no isolator)
	 	 	1	 	 	 
	5.10
	 	LCS-10
	 	Local control station with start
pushbutton, stop pushbutton, emergency
stop button and labels (no isolator)
	 	 	1	 	 	 
	5.11
	 	LCS-11
	 	Local control station with forward
pushbutton, reverse pushbutton, emergency
stop button and labels (no isolator)
	 	 	1	 	 	 
	5.12
	 	LCS-12
	 	80 amp 3 pole isolator only
	 	 	1	 	 	 
	5.13
	 	LCS-13
	 	125 amp, 3 pole isolator only
	 	 	1	 	 	 
	5.14
	 	LCS-14
	 	200 amp, 3 pole isolator only
	 	 	1	 	 	 
	5.15
	 	LCS-15
	 	400 amp, 3 pole isolator only
	 	 	1	 	 	 
	5.16
	 	LCS-16
	 	80 amp, 6 pole isolator, lock-off
emergency stop, start pushbutton and
labels (DOL motors £30kW)
	 	 	1	 	 	 
	5.17
	 	LCS-17
	 	80 amp, 6 pole isolator, reverse,
lock-off emergency stop, start pushbutton
and labels (DOL motors £30kW)
	 	 	1	 	 	 
	5.18
	 	LCS-18
	 	Local control station with 32 amp
decontactor, 2 pilot pins, start
pushbutton, emergency stop button and
labels (include male decontactor)
	 	 	1	 	 	 
	5.19
	 	LCS-19
	 	Local control station with 63 amp
decontactor, 2 pilot pins, start
pushbutton, emergency stop button and
labels (include male decontactor)
	 	 	1	 	 	 
	5.20
	 	LCS-20
	 	Local control station with 125 amp
decontactor, 2 pilot pins, start
pushbutton, emergency stop button and
labels (include male decontactor)
	 	 	1	 	 	 
	5.21
	 	LCS-21
	 	Local control station with 200 amp
decontactor, 4 pilot pins, start
pushbutton, emergency stop button and
labels (include male decontactor)
	 	 	1	 	 	 
	5.22
	 	LCS-CONV
	 	200 amp, 3 pole isolator, lock-off
emergency stop, start pushbutton, stop
pushbutton, larger box, extra terminals
and labels
	 	 	1	 	 	 
	5.23
	 	LCS-SLEW
	 	80 amp, 3 pole isolator, reverse,
lock-off emergency stop, start pushbutton
and labels (DOL motors £30kW)
	 	 	1	 	 	 
	5.24 
	 	LCS-ES                 	 	Lock-off emergency stop pushbutton only	 	 	1	 	 	 




Variations Pricing_Rev 00

Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 11 of 15 Pages


 







 




LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule


VARIATIONS FOR DISTRIBUTION BOARDS



	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	 	 	Description	 	Qty	 	Price
	6.1
	 	 	 	Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting
Control Section	 	 	1	 	 	 
	6.2
	 	 	 	Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42	 	 	1	 	 	 
	6.3
	 	 	 	Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	 	1	 	 	 
	6.4
	 	 	 	Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42,
with Lighting Control Section	 	 	1	 	 	 
	6.5
	 	 	 	Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42	 	 	1	 	 	 
	6.6
	 	 	 	Install one single pole, 10 amp circuit breaker	 	 	1	 	 	 
	6.7
	 	 	 	Install one single pole, 16 amp circuit breaker	 	 	1	 	 	 
	6.8
	 	 	 	Install one single pole, 10 amp circuit breaker with 30mA earth leakage	 	 	1	 	 	 
	6.9
	 	 	 	Install one single pole, 16 amp circuit breaker with 30mA earth leakage	 	 	1	 	 	 
	6.10
	 	 	 	Install one single pole, 10 amp circuit breaker with 100mA earth leakage	 	 	1	 	 	 
	6.11
	 	 	 	Install one single pole, 16 amp circuit breaker with 100mA earth leakage	 	 	1	 	 	 
	6.12
	 	 	 	Install one three pole, 16 amp circuit breaker	 	 	1	 	 	 
	6.13
	 	 	 	Install one three pole, 16 amp circuit breaker with 30mA earth leakage	 	 	1	 	 	 
	6.14
	 	 	 	Install one three pole, 16 amp circuit breaker with 300mA earth leakage	 	 	1	 	 	 
	6.15
	 	 	 	Install one three pole, 20 amp circuit breaker	 	 	1	 	 	 
	6.16
	 	 	 	Install one three pole, 20 amp circuit breaker with 30mA earth leakage	 	 	 	 	 	 
	6.17
	 	 	 	Install one three pole, 20 amp circuit breaker with 100mA earth leakage	 	 	 	 	 	 
	6.18
	 	 	 	Install one three pole, 32 amp circuit breaker	 	 	 	 	 	 
	6.19
	 	 	 	Install one three pole, 32 amp circuit breaker with 30mA earth leakage	 	 	 	 	 	 
	6.20
	 	 	 	Install one three pole, 32 amp circuit breaker with 100mA earth leakage	 	 	 	 	 	 
	6.21
	 	 	 	Install one three pole, 63 amp circuit breaker	 	 	 	 	 	 
	6.22
	 	 	 	Install one three pole, 63 amp circuit breaker with 30mA earth leakage	 	 	 	 	 	 
	6.23
	 	 	 	Install one three pole, 63 amp circuit breaker with 100mA earth leakage	 	 	 	 	 	 
	 
	OPTIONAL PRICING FOR SWITCHROOM GAS SUPPRESSION SYSTEM
	 
	Item No.	 	Supplier	 	Description	 	Qty	 	 
	7.1
	 	James Engineering	 	Gas Suppression System, Primary Crushing LV Switchroom	 	 	1	 	 	 
	7.2
	 	James Engineering	 	Gas Suppression System, Primary Crushing HV Switchroom	 	 	1	 	 	 
	7.3
	 	James Engineering	 	Gas Suppression System, Primary Conveying LV Switchroom	 	 	1	 	 	 
	7.4
	 	James Engineering	 	Gas Suppression System, Ore Stockpile LV Switchroom	 	 	1	 	 	 
	7.5
	 	James Engineering	 	Gas Suppression System, Wurtol Pumping Station LV Switchroom	 	 	1	 	 	 




Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 12 of 15 Pages


 







 




LIHIR MOPU Project
MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule



	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	Price
	7.6
	 	James Engineering	 	Gas Suppression System, Grinding LV Switchroom	 	 	1	 	 	 
	7.7
	 	James Engineering	 	Gas Suppression System, Grinding HV Switchroom	 	 	1	 	 	 
	7.8
	 	James Engineering	 	Gas Suppression System, Pressure Oxidation LV Switchroom	 	 	1	 	 	 
	7.9
	 	James Engineering	 	Gas Suppression System, Pressure Oxidation HV Switchroom	 	 	1	 	 	 
	7.10
	 	James Engineering	 	Gas Suppression System, Cyanidation & Adsorption LV Switchroom	 	 	1	 	 	 
	7.11
	 	James Engineering	 	Gas Suppression System, Cyanidation & Adsorption HV Switchroom	 	 	1	 	 	 
	7.12
	 	James Engineering	 	Gas Suppression System, Oxygen Plant LV Switchroom	 	 	1	 	 	 
	7.13
	 	James Engineering	 	Gas Suppression System, Oxygen Plant HV Switchroom	 	 	1	 	 	 
	7.14
	 	James Engineering	 	Gas Suppression System, Grinding Thickeners LV Switchroom	 	 	1	 	 	 
	7.15
	 	James Engineering	 	Gas Suppression System, Process Seawater LV Switchroom	 	 	1	 	 	 
	7.16
	 	James Engineering	 	Gas Suppression System, Bus C3, C4 & E LV Switchroom	 	 	1	 	 	 
	7.17
	 	James Engineering	 	Gas Suppression System, Bus C3 & C4 HV Switchroom	 	 	1	 	 	 
	7.18
	 	James Engineering	 	Gas Suppression System, Bus E HV Switchroom	 	 	1	 	 	 
	7.19
	 	James Engineering	 	Gas Suppression System, Bus F LV Switchroom	 	 	1	 	 	 
	7.20
	 	James Engineering	 	Gas Suppression System, Bus F HV Switchroom	 	 	1	 	 	 
	7.21
	 	Brice Engineers	 	Gas Suppression System, Primary Crushing LV Switchroom	 	 	1	 	 	 
	7.22
	 	Brice Engineers	 	Gas Suppression System, Primary Crushing HV Switchroom	 	 	1	 	 	 
	7.23
	 	Brice Engineers	 	Gas Suppression System, Primary Conveying LV Switchroom	 	 	1	 	 	 
	7.24
	 	Brice Engineers	 	Gas Suppression System, Ore Stockpile LV Switchroom	 	 	1	 	 	 
	7.25
	 	Brice Engineers	 	Gas Suppression System, Wurtol Pumping Station LV Switchroom	 	 	1	 	 	 
	7.26
	 	Brice Engineers	 	Gas Suppression System, Grinding LV Switchroom	 	 	1	 	 	 
	7.27
	 	Brice Engineers	 	Gas Suppression System, Grinding HV Switchroom	 	 	1	 	 	 
	7.28
	 	Brice Engineers	 	Gas Suppression System, Pressure Oxidation LV Switchroom	 	 	1	 	 	 
	7.29
	 	Brice Engineers	 	Gas Suppression System, Pressure Oxidation HV Switchroom	 	 	1	 	 	 
	7.30
	 	Brice Engineers	 	Gas Suppression System, Cyanidation & Adsorption LV Switchroom	 	 	1	 	 	 
	7.31
	 	Brice Engineers	 	Gas Suppression System, Cyanidation & Adsorption HV Switchroom	 	 	1	 	 	 
	7.32
	 	Brice Engineers	 	Gas Suppression System, Oxygen Plant LV Switchroom	 	 	1	 	 	 
	7.33
	 	Brice Engineers	 	Gas Suppression System, Oxygen Plant HV Switchroom	 	 	1	 	 	 
	7.34
	 	Brice Engineers	 	Gas Suppression System, Grinding Thickeners LV Switchroom	 	 	1	 	 	 
	7.35
	 	Brice Engineers	 	Gas Suppression System, Process Seawater LV Switchroom	 	 	1	 	 	 
	7.36
	 	Brice Engineers	 	Gas Suppression System, Bus C3, C4 & E LV Switchroom	 	 	1	 	 	 
	7.37
	 	Brice Engineers	 	Gas Suppression System, Bus C3 & C4 HV Switchroom	 	 	1	 	 	 




Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 13 of 15 Pages


 







 




LIHIR MOPU Project
MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule



	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	Price
	7.38
	 	Brice Engineers	 	Gas Suppression System, Bus E HV Switchroom	 		1	 	 	 
	7.39
	 	Brice Engineers	 	Gas Suppression System, Bus F LV Switchroom	 		1	 	 	 
	7.40
	 	Brice Engineers	 	Gas Suppression System, Bus F HV Switchroom	 		1	 	 	 
	 
	OPTIONAL PRICING FOR 2 HOUR FIRE RATING OF SWITCHROOM WALLS
For Wall Adjacent to (or Floor Above) Transformers.
	 
	Item No.	 	Supplier	 	Description	 	Qty	 	 
	8.1
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Primary Crushing LV Switchroom	 	 	1	 	 	 
	8.2
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Primary Crushing HV Switchroom	 	 	1	 	 	 
	8.3
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Primary Conveying LV Switchroom	 	 	1	 	 	 
	8.4
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Ore Stockpile LV Switchroom	 	 	1	 	 	 
	8.5
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Wurtol Pumping Station LV Switchroom	 	 	1	 	 	 
	8.6
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Grinding LV Switchroom	 	 	1	 	 	 
	8.7
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Grinding HV Switchroom	 	 	1	 	 	 
	8.8
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Pressure Oxidation LV Switchroom	 	 	1	 	 	 
	8.9
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Pressure Oxidation HV Switchroom	 	 	1	 	 	 
	8.10
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Cyanidation & Adsorption LV Switchroom	 	 	1	 	 	 
	8.11
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Cyanidation & Adsorption HV Switchroom	 	 	1	 	 	 
	8.12
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Oxygen Plant LV Switchroom	 	 	1	 	 	 
	8.13
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Oxygen Plant HV Switchroom	 	 	1	 	 	 
	8.14
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Grinding Thickener LV Switchroom	 	 	1	 	 	 
	8.15
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Process Seawater LV Switchroom	 	 	1	 	 	 
	8.16
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Bus C3, C4 & E LV Switchroom	 	 	1	 	 	 
	8.17
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Bus C3 & C4 HV Switchroom	 	 	1	 	 	 
	8.18
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Bus E HV Switchroom	 	 	1	 	 	 
	8.19
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Bus F LV Switchroom	 	 	1	 	 	 
	8.20
	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Bus F HV Switchroom	 	 	1	 	 	 
	8.21
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Primary Crushing LV Switchroom	 	 	1	 	 	 
	8.22
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Primary Crushing HV Switchroom	 	 	1	 	 	 
	8.23
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Primary Conveying LV Switchroom	 	 	1	 	 	 
	8.24
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Primary Conveying & Ore Stockpile LV Switchroom	 	 	1	 	 	 
	8.25
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Wurtol Pumping Station LV Switchroom	 	 	1	 	 	 




Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 14 of 15 Pages


 







 




LIHIR MOPU Project
MOPU-1101 MCCs and Switchrooms
Variations Pricing Schedule



	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	Price
	8.26
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Grinding LV Switchroom	 	 	1	 	 	 
	8.27
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Grinding HV Switchroom	 	 	1	 	 	 
	8.28
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Pressure Oxidation LV
Switchroom	 	 	1	 	 	 
	8.29
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Pressure Oxidation HV
Switchroom	 	 	1	 	 	 
	8.30
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Cyanidation & Adsorption
LV Switchroom	 	 	1	 	 	 
	8.31
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Cyanidation & Adsorption
HV Switchroom	 	 	1	 	 	 
	8.32
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Oxygen Plant LV Switchroom	 	 	1	 	 	 
	8.33
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Oxygen Plant HV Switchroom	 	 	1	 	 	 
	8.34
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Grinding Thickeners LV
Switchroom	 	 	1	 	 	 
	8.35
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Process Seawater LV
Switchroom	 	 	1	 	 	 
	8.36
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus C3, C4 & E LV
Switchroom	 	 	1	 	 	 
	8.37
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus C3 & C4 HV Switchroom	 	 	1	 	 	 
	8.38
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus E HV Switchroom	 	 	1	 	 	 
	8.39
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus F LV Switchroom	 	 	1	 	 	 
	8.40
	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus F HV Switchroom	 	 	1	 	 	 




Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 15 of 15 Pages


 







 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	 	 	 	 	 	 	MOTOR CONTROL CENTRES (includes installation of

 free issued VSD/Soft Str)	 	 	 	 
	1314

	 	MC2001A	 	SS2001	 	Primary Crushing MCC A	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	MC2001B	 	SS2001	 	Primary Crushing MCC B	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1315

	 	MC2051	 	SS2051	 	Primary Conveyor MCC	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1316

	 	MC2101	 	SS2101	 	Ore Stockpile MCC	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1825

	 	MC2160	 	SS2160	 	Wurtol Pumping Station MCC	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326

	 	MC2201A	 	SS2200	 	Grinding & Classification MCC A	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326

	 	MC2201B	 	SS2200	 	Grinding & Classification MCC B	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	MC2401A	 	SS2400	 	Pressure Oxidation MCC A	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	MC2401B	 	SS2400	 	Pressure Oxidation MCC B	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	MC2401C	 	SS2400	 	Pressure Oxidation MCC C	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	MC2401D	 	SS2400	 	Pressure Oxidation MCC D	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	MC2551A	 	SS2551	 	Cyanidation & Adsorption MCC A	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	MC2551B	 	SS2551	 	Cyanidation & Adsorption MCC B	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	MC2561A	 	SS2560	 	Oxygen Plant MCC A	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	MC2561B	 	SS2560	 	Oxygen Plant MCC B	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1341

	 	MC2741	 	SS2741	 	Grinding Thickeners MCC	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1830

	 	MC2850	 	SS2850	 	Process Seawater MCC	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	MC2931	 	SS2931	 	Bus E Auxilliary MCC	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	MC2932	 	SS2932	 	Bus F Auxilliary MCC	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Total Price MCCs	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	SWITCHROOMS (James Engineering)	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	SS2001A	 	SS2001	 	Primary Crushing LV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	SS2001B	 	SS2001	 	Primary Crushing HV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1315

	 	SS2051	 	SS2051	 	Primary Conveying LV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1316

	 	SS2101	 	SS2101	 	Ore Stockpile LV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1825

	 	SS2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326

	 	SS2200A	 	SS2200	 	Grinding Area LV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326

	 	SS2200B	 	SS2200	 	Grinding Area HV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	SS2400A	 	SS2400	 	Pressure Oxidation LV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	SS2400B	 	SS2400	 	Pressure Oxidation HV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	SS2551A	 	SS2551	 	Cyanidation & Adsorption LV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	SS2551B	 	SS2551	 	Cyanidation & Adsorption HV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	SS2560A	 	SS2560	 	Oxygen Plant LV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	SS2560B	 	SS2560	 	Oxygen Plant HV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1341

	 	SS2741	 	SS2741	 	Grinding Thickeners LV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1830

	 	SS2850	 	SS2850	 	Process Seawater LV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931A	 	SS2931	 	Bus C3, C4 & E LV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931B	 	SS2931	 	Bus C3 & C4 HV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931C	 	SS2931	 	Bus E HV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2932A	 	SS2932	 	Bus F LV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2932B	 	SS2932	 	Bus F HV Switchroom	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	VESDA Systems	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	SS2001A	 	SS2001	 	Primary Crushing LV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	SS2001B	 	SS2001	 	Primary Crushing HV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1315

	 	SS2051	 	SS2051	 	Primary Conveying LV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1316

	 	SS2101	 	SS2101	 	Ore Stockpile LV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1825

	 	SS2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326

	 	SS2200A	 	SS2200	 	Grinding Area LV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 






 









 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	Location	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1326
	 	SS2200B	 	SS2200	 	Grinding Area HV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	SS2400A	 	SS2400	 	Pressure Oxidation LV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	SS2400B	 	SS2400	 	Pressure Oxidation HV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351
	 	SS2551A	 	SS2551	 	Cyanidation & Adsorption LV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351
	 	SS2551B	 	SS2551	 	Cyanidation & Adsorption HV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560
	 	SS2560A	 	SS2560	 	Oxygen Plant LV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560
	 	SS2560B	 	SS2560	 	Oxygen Plant HV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1341
	 	SS2741	 	SS2741	 	Grinding Thickeners LV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1830
	 	SS2850	 	SS2850	 	Process Seawater LV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2931A	 	SS2931	 	Bus C3, C4 & E LV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2931B	 	SS2931	 	Bus C3 & C4 HV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2931C	 	SS2931	 	Bus E HV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2932A	 	SS2932	 	Bus F LV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2932B	 	SS2932	 	Bus F HV Switchroom VESDA System	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price Switchrooms from James Engineering	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	SWITCHROOMS (Brice Engineers)	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	SS2001A	 	SS2001	 	Primary Crushing LV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1314
	 	SS2001B	 	SS2001	 	Primary Crushing HV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1315
	 	SS2051	 	SS2051	 	Primary Conveying LV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1316
	 	SS2101	 	SS2101	 	Ore Stockpile LV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1825
	 	SS2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1326
	 	SS2200A	 	SS2200	 	Grinding Area LV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1326
	 	SS2200B	 	SS2200	 	Grinding Area HV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1343
	 	SS2400A	 	SS2400	 	Pressure Oxidation LV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1343
	 	SS2400B	 	SS2400	 	Pressure Oxidation HV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1351
	 	SS2551A	 	SS2551	 	Cyanidation & Adsorption LV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1351
	 	SS2551B	 	SS2551	 	Cyanidation & Adsorption HV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1560
	 	SS2560A	 	SS2560	 	Oxygen Plant LV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1560
	 	SS2560B	 	SS2560	 	Oxygen Plant HV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1341
	 	SS2741	 	SS2741	 	Grinding Thickeners LV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1830
	 	SS2850	 	SS2850	 	Process Seawater LV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2931A	 	SS2931	 	Bus C3, C4 & E LV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2931B	 	SS2931	 	Bus C3 & C4 HV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2931C	 	SS2931	 	Bus E HV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2932A	 	SS2932	 	Bus F LV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2932B	 	SS2932	 	Bus F HV Switchroom	 	 		 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	VESDA Systems	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	SS2001A	 	SS2001	 	Primary Crushing LV Switchroom VESDA System	 	 		 	 	 	 	 	 	 	 	 	 	 
	1314
	 	SS2001B	 	SS2001	 	Primary Crushing HV Switchroom VESDA System	 	 		 	 	 	 	 	 	 	 	 	 	 
	1315
	 	SS2051	 	SS2051	 	Primary Conveying LV Switchroom VESDA System	 	 		 	 	 	 	 	 	 	 	 	 	 
	1316
	 	SS2101	 	SS2101	 	Ore Stockpile LV Switchroom VESDA System	 	 		 	 	 	 	 	 	 	 	 	 	 
	1825
	 	SS2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom VESDA System	 	 		 	 	 	 	 	 	 	 	 	 	 
	1326
	 	SS2200A	 	SS2200	 	Grinding Area LV Switchroom VESDA System	 	 		 	 	 	 	 	 	 	 	 	 	 




 







 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1326
	 	SS2200B	 	SS2200	 	Grinding Area HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	SS2400A	 	SS2400	 	Pressure Oxidation LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	SS2400B	 	SS2400	 	Pressure Oxidation HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1351
	 	SS2551A	 	SS2551	 	Cyanidation & Adsorption LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1351
	 	SS2551B	 	SS2551	 	Cyanidation & Adsorption HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1560
	 	SS2560A	 	SS2560	 	Oxygen Plant LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1560
	 	SS2560B	 	SS2560	 	Oxygen Plant HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1341
	 	SS2741	 	SS2741	 	Grinding Thickeners HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1830
	 	SS2850	 	SS2850	 	Process Seawater LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2931A	 	SS2931	 	Bus C3, C4 & E LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2931B	 	SS2931	 	Bus C3 & C4 HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2931C	 	SS2931	 	Bus E HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2932A	 	SS2932	 	Bus F LV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	SS2932B	 	SS2932	 	Bus F HV Switchroom VESDA System	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price Switchrooms from Brice Engineers	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 
	 	 	 	 	 	DISTRIBUTION BOARDS (Chassis and Panel Only)	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	DB2001A	 	SS2001	 	Primary Crushing LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	DB2001B	 	SS2001	 	Primary Crushing HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	DB2001C	 	SS2001	 	Primary Crushing UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	DB2001D	 	SS2001	 	Primary Crushing Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1315
	 	DB2051A	 	SS2051	 	Primary Conveying LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1315
	 	DB2051B	 	SS2051	 	Primary Conveying UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1315
	 	DB2051C	 	SS2051	 	Primary Conveying Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1316
	 	DB2101A	 	SS2101	 	Ore Stockpile LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1316
	 	DB2101B	 	SS2101	 	Ore Stockpile UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1316
	 	DB2101C	 	SS2101	 	Ore Stockpile Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1825
	 	DB2160A	 	SS2160	 	Wurtol Pumping Station LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1825
	 	DB2160B	 	SS2160	 	Wurtol Pumping Station UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1825
	 	DB2160C	 	SS2160	 	Wurtol Pumping Station Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326
	 	DB2201A	 	SS2201	 	Grinding LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326
	 	DB2201B	 	SS2201	 	Grinding HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326
	 	DB2201C	 	SS2201	 	Grinding Area UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326
	 	DB2201D	 	SS2201	 	Grinding Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section	 	 	1	 	 	 	 	 	 	 	 	 	 	 





 








 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1343

	 	DB2401A	 	SS2401	 	Pressure Oxidation LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	DB2401B	 	SS2401	 	Pressure Oxidation HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	DB2401C	 	SS2401	 	Pressure Oxidation UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	DB2401D	 	SS2401	 	Pressure Oxidation Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	DB2551A	 	SS2551	 	Cyanidation & Adsorption LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	DB2551B	 	SS2551	 	Cyanidation & Adsorption HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	DB2551C	 	SS2551	 	Cyanidation & Adsorption UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	DB2551D	 	SS2551	 	Cyanidation & Adsorption Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	DB2561A	 	SS2560	 	Oxygen Plant LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	DB2561B	 	SS2560	 	Oxygen Plant HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	DB2561C	 	SS2560	 	Oxygen Plant UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	DB2561D	 	SS2560	 	Oxygen Plant Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1341

	 	DB2741A	 	SS2741	 	Grinding Thickeners LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0 2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1341

	 	DB2741B	 	SS2741	 	Grinding Thickeners UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1341

	 	DB2741C	 	SS2741	 	Grinding Thickeners Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1830

	 	DB2850A	 	SS2850	 	Process Seawater LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s. IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1830

	 	DB2850B	 	SS2850	 	Process Seawater Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	DB2931A	 	SS2931	 	Bus C3, C4 & E Light & Power Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	DB2931B	 	SS2931	 	Bus C3, C4 & E UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	DB2932A	 	SS2932	 	Bus F Light & Power Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	DB2932B	 	SS2932	 	Bus F UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	PC Sum for Fitout of DB’s with Circuit Breakers	 	 	PC	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Total Price Distribution Boards	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	UNINTERRUPTIBLE POWER SUPPLIES	 	 		 	 	 	 	 	 	 	 	 	 	 
	1314

	 	UP2001	 	SS2001	 	Primary Crushing LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1315

	 	UP2051	 	SS2051	 	Primary Conveying LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out	 	 	1	 	 	 	 	 	 	 	 	 	 	 






 









 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1316
	 	UP2101	 	SS2101	 	0re Stockpile LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1825
	 	UP2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326
	 	UP2201	 	SS2200	 	Grinding Area LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	UP2401	 	SS2400	 	Pressure Oxidation LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351
	 	UP2551	 	SS2551	 	Cyanidation & Absorption LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560
	 	UP2561	 	SS2560	 	Oxygen Plant LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1341
	 	UP2741	 	SS2741	 	Grinding Thickeners LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	UP2931	 	SS2931	 	Bus C3, C4 & E LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	UP2932	 	SS2932	 	Bus F LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price UPS	 	 		 	 	 	 	 	 	 	 	 	 	 
	 
	 
	 	 	 	 	 	Control Panels	 	 		 	 	 	 	 	 	 	 	 	 	 
	1314
	 	CP2001A	 	SS2001	 	Primary Crushing LV Switchroom DCS Panel A	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	CP2001B	 	SS2001	 	Primary Crushing LV Switchroom DCS Panel B	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1315
	 	CP2051	 	SS2051	 	Primary Conveying LV Switchroom DCS Panel	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1316
	 	CP2101	 	SS2101	 	Ore Stockpile LV Switchroom DCS Panel	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326
	 	CP2201A	 	SS2200	 	Grinding Area LV Switchroom DCS Panel A	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326
	 	CP2201B	 	SS2200	 	Grinding Area LV Switchroom DCS Panel B	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	CP2401A	 	SS2400	 	Pressure Oxidation LV Switchroom DCS Panel A	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	CP2401B	 	SS2400	 	Pressure Oxidation LV Switchroom DCS Panel B	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351
	 	CP2551A	 	SS2551	 	Cyanidation & Absorption LV Switchroom DCS Panel A	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351
	 	CP2551B	 	SS2551	 	Cyanidation & Absorption LV Switchroom DCS Panel B	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560
	 	CP2560A	 	SS2560	 	Oxygen Plant LV Switchroom DCS Panel A	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560
	 	CP2560B	 	SS2560	 	Oxygen Plant LV Switchroom DCS Panel B	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1341
	 	CP2741	 	SS2741	 	Grinding Thickeners LV Switchroom DCS Panel	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1825
	 	CP2160	 	SS2160	 	Wurtol Pumping Station LV Switchroom PLC Panel	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	CP2931A	 	SS2931	 	Bus C3, C4 & E HV Switchroom PLC Panel	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780
	 	CP2932A	 	SS2932	 	Bus F HV Switchroom PLC Panel	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560
	 	CP2603	 	SS2560	 	PC Sum for Installation of Oxygen Plant Hardwired Emergency Trip Panel	 	 	PC	 	 	 	 	 	 	 	 	 	 	 
	1830
	 	CP2850	 	SS2850	 	PC Sum for Installation of Process Seawater LV Switchroom Control Panel	 	 	PC	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	PC Sum for Internal Marshalling of 13 DCS Panels	 	 	PC	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	PC Sum for Cabling of 18 Panels Within Switchrooms	 	 	PC	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	PC Sum for Installation of 19” RM FOBOTs in LV Switchrooms	 	 	PC	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price Control Panels	 	 		 	 	 	 	 	 	 	 	 	 	 
	 
	 
	 	 	 	 	 	BATTERY CHARGER SYSTEMS	 	 		 	 	 	 	 	 	 	 	 	 	 
	1314
	 	BC2000	 	SS2001	 	Primary Crushing HV Switchroom 48VDC, 70Ahr	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326
	 	BC2200	 	SS2200	 	Grinding Area HV Switchroom 48VDC, 70Ahr	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	BC2400	 	SS2400	 	Pressure Oxidation HV Switchroom 48VDC. 70Ahr	 	 	1	 	 	 	 	 	 	 	 	 	 	 






 










 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply 	 	Install (Unit)	 	Install	 	Total
	1351
	 	BC2550	 	SS2551	 	Cyanidation &
Absorption HV Switchroom 48VDC, 70Ahr	 	1	 	 	 	 	 	 	 	 	 	 
	1560
	 	BC2560	 	SS2560	 	Oxygen Plant HV Switchroom 48VDC, 160Ahr	 	1	 	 	 	 	 	 	 	 	 	 
	1780
	 	BC2900	 	SS2931	 	Bus C3 & C4 HV Switchroom 48VDC, 160Ahr	 	1	 	 	 	 	 	 	 	 	 	 
	1780
	 	BC2931	 	SS2931	 	Bus E HV Switchroom 48VDC, 230Ahr	 	1	 	 	 	 	 	 	 	 	 	 
	1780
	 	BC2932	 	SS2932	 	Bus F HV Switchroom 48VDC, 230Ahr	 	1	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price Battery Charger Systems	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	HV SWITCHBOARDS	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	SW2000	 	SS2001	 	Primary Crushing 11kV Switchboard	 	1	 	 	 	 	 	 	 	 	 	 
	1314
	 	SW2001	 	SS2001	 	HGO Crusher 3.3kV Switchboard	 	1	 	 	 	 	 	 	 	 	 	 
	1326
	 	SW2200	 	SS2200	 	Grinding Area 11kV Switchboard	 	1	 	 	 	 	 	 	 	 	 	 
	1343
	 	SW2400	 	SS2400	 	Pressure Oxidation 11kV Switchboard	 	1	 	 	 	 	 	 	 	 	 	 
	1351
	 	SW2550	 	SS2551	 	Cyanidation & Absorption 11kV Switchboard	 	1	 	 	 	 	 	 	 	 	 	 
	1560
	 	SW2560	 	SS2560	 	Oxygen Plant 11kV Switchboard	 	1	 	 	 	 	 	 	 	 	 	 
	1780
	 	SW2900	 	SS2931	 	Bus C3 & C4 11kV Switchboard	 	1	 	 	 	 	 	 	 	 	 	 
	1780
	 	SW2931	 	SS2931	 	Bus E 33kV Switchboard	 	1	 	 	 	 	 	 	 	 	 	 
	1780
	 	SW2932	 	SS2932	 	Bus F 33kV Switchboard	 	1	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price HV Switchboards	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	HV REMOTE SWITCHING PANELS	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	CP2000	 	SS2001	 	Primary Crushing 11kV & 3.3kV Remote Switching Panel	 	1	 	 	 	 	 	 	 	 	 	 
	1326
	 	CP2200	 	SS2200	 	Grinding Area 11kV Remote Switching Panel	 	1	 	 	 	 	 	 	 	 	 	 
	1343
	 	CP2400	 	SS2400	 	Pressure Oxidation 11kV Remote Switching Panel	 	1	 	 	 	 	 	 	 	 	 	 
	1351
	 	CP2550	 	SS2551	 	Cyanidation & Absorption 11kV
Remote Switching Panel	 	1	 	 	 	 	 	 	 	 	 	 
	1560
	 	CP2560	 	SS2560	 	Oxygen Plant 11kV Remote Switching Panel	 	1	 	 	 	 	 	 	 	 	 	 
	1780
	 	CP2900	 	SS2931	 	Bus C3 & C4 11kV Remote Switching Panel	 	1	 	 	 	 	 	 	 	 	 	 
	1780
	 	CP2900A	 	SS2931	 	Bus C3 & C4 11kV Tariff Metering Panel	 	1	 	 	 	 	 	 	 	 	 	 
	1780
	 	CP2931	 	SS2931	 	Bus E 33kV Remote Switching Panel	 	1	 	 	 	 	 	 	 	 	 	 
	1780
	 	CP2932	 	SS2932	 	Bus F 33kV Remote Switching Panel	 	1	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	PC Sum for Cabling of 9 Panels Within Switchrooms	 	PC	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price HV Remote Switching Panels	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	FLOOR MOUNTED VSDs	 	 	 	 	 	 	 	 	 	 	 	 
	1314
	 	FD2001	 	SS2001	 	Primary Apron Feeder VSD 315kW	 	1	 	 	 	 	 	 	 	 	 	 
	1315
	 	FD2003	 	SS2101	 	HGO Apron Feeder No.1 VSD 55kW	 	1	 	 	 	 	 	 	 	 	 	 
	1315
	 	FD2004	 	SS2101	 	HGO Apron Feeder No.2 VSD 55kW	 	1	 	 	 	 	 	 	 	 	 	 
	1315
	 	FD2005	 	SS2101	 	HGO Emergency Apron Feeder VSD 55kW	 	1	 	 	 	 	 	 	 	 	 	 
	1825
	 	PU2161	 	SS2160 	 	Wurtol Raw Water Pump No.1 VSD 600kW	 	1	 	 	 	 	 	 	 	 	 	 
	1825
	 	PU2162	 	SS2160	 	Wurtol Raw Water Pump No.2 VSD 600kW	 	1	 	 	 	 	 	 	 	 	 	 
	1825
	 	 PU2163	 	SS2160	 	Wurtol Raw Water Pump No.3 VSD 600kW	 	1	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2030	 	SS2200	 	Pre-oxidation Feed Pump No.1 VSD 185kW	 	1	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2031	 	SS2200	 	Pre-oxidation Feed Pump No.2 VSD 185kW	 	1	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2040	 	SS2200	 	Cyclone Overflow Transfer Pump No.1 VSD 400kW	 	1	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2041	 	SS2200	 	Cyclone Overflow Transfer Pump No.2 VSD 400kW	 	1	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2042	 	SS2200	 	Cyclone Overflow Transfer Pump No.3 VSD 400kW	 	1	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2043	 	SS2200	 	Cyclone Overflow Transfer Pump No.4 VSD 400kW	 	1	 	 	 	 	 	 	 	 	 	 
	1326
	 	PU2021	 	SS2200	 	Cyclone Feed Pump No.1 VSD 525kW 	 	1	 	 	 	 	 	 	 	 	 	 



















 








	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total	 
	1326
	 	PU2022	 	SS2200	 	Cyclone Feed Pump No.2 VSD 525kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	PU2741	 	SS2400	 	Autoclave Feed Booster Pump VSD185kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	AG2245	 	SS2400	 	Autoclave No.4 Compartments 3-6 Agitator VSD 200kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	PU2123	 	SS2400	 	Flashed Slurry Forwarding Pump No.1 VSD 200kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	PU2124	 	SS2400	 	Flashed Slurry Forwarding Pump No.2 VSD200kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	PU2125	 	SS2400	 	Flashed Slurry Forwarding Pump No.3 VSD 200kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	AG2241	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	AG2242	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	AG2243	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	AG2244	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	PU2033	 	SS2400	 	Autoclave Feed Pump No.1 VSD 600kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1343
	 	PU2034	 	SS2400	 	Autoclave Feed Pump No.2 VSD 600kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1351
	 	PU2105	 	SS2551	 	Lime Recirculation Pump VSD 30kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1351
	 	PU2058	 	SS2551	 	Leach Trash Screen Feed Pump VSD 110kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1351
	 	PU2212	 	SS2551	 	CIL Tails Pump No.1  VSD 315kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1351
	 	PU2213	 	SS2551	 	CIL Tails Pump No.2 VSD 315kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1560
	 	P440A	 	SS2560	 	LOX Process Pump A VSD 150kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1560
	 	P440B	 	SS2560	 	LOX Process Pump B VSD 150kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1341
	 	PU2026	 	SS2741	 	Grinding Thickener No.1 U/F Pump No.1 VSD 75kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1341
	 	PU2027	 	SS2741	 	Grinding Thickener No.1 U/F Pump No.2 VSD 75kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1341
	 	PU2028	 	SS2741	 	Grinding Thickener No.2 U/F Pump No.1 VSD 525kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	1341
	 	PU2029	 	SS2741	 	Grinding Thickener No.2 U/F Pump No.2 VSD 525kW	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Price VSDs	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 
	 	 	 	 	 	LOCAL CONTROL STATIONS (Supply price for each even if quantity is 0)	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-01	 	 	 	80 amp, 3 pole isolator, lock-off
emergency stop, start pushbutton and labels (DOL motors
£30kW)	 	174	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-02	 	 	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors£55kW)	 	5	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-03	 	 	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors£90kW)	 	14	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-04	 	 	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors£185kW)	 	13	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-05	 	 	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors£30kW)	 	6	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-06	 	 	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors£55kW)	 	7	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-07	 	 	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors£90kW)	 	2	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-08	 	 	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors£l85kW)	 	7	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-09	 	 	 	Local control station with start pushbutton, emergency stop button and labels (no isolator)	 	21	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-10	 	 	 	Local control station with start pushbutton, stop pushbutton, emergency stop button and labels (no isolator)	 	25	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	LCS-11	 	 	 	Local control station with forward pushbutton, reverse pushbutton, emergency stop button and labels (no isolator)	 	2	 	 	 	 	 	 	 	 	 	 	 	 




















 









	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	 

	 	LCS-12
	 	 	 	80 amp, 3 pole isolator only	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	LCS-13
	 	 	 	125 amp, 3 pole isolator only	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	LCS-14
	 	 	 	200 amp, 3 pole isolator only	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	LCS-15
	 	 	 	400 amp, 3 pole isolator only	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	LCS-16
	 	 	 	Lock-off emergency stop pushbutton only	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	LCS-17
	 	 	 	80 amp, 6 pole isolator, reverse, forward pushbutton, lock-off emergency stop and
labels (DRD/slew motors ≤30kW)	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	LCS-18
	 	 	 	Local control station with 63 amp decontactor, 2 pilot pins, start pushbutton, emergency
stop button and labels (include male decontactor)	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	LCS-19
	 	 	 	Local control station with 63 amp decontactor, 2 pilot pins, start pushbutton, emergency
stop button, multitrode level relay and labels (include male decontactor)	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	LCS-20
	 	 	 	Local control station with 125 amp decontactor, 2 pilot pins, start pushbutton,
emergency stop button, multitrode level relay and labels (include male decontactor)	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	LCS-21
	 	 	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton,
larger box, extra terminals and labels (conveyors ≤30kW)	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	LCS-22
	 	 	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton,
larger box, extra terminals and labels (conveyors ≤55kW)	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	LCS-23
	 	 	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton,
larger box, extra terminals and labels (conveyors ≤90kW)	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	LCS-24
	 	 	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton,
larger box, extra terminals and labels (conveyors ≤185kW)	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Total Price Local Control Stations	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Drawings and Documentation	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Packaging	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Lifting Equipment	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Inland Freight to Port	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Total Drawings / Packaging / Transport	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Total MCC & Switchrooms (without Options)	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	RECOMMENDED OPTIONS	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Supply of two spreader bars from James Engineering	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Supply of Rubber Matting	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Variation for 415 Volt Matting — per metre	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Variation for 11000 Volt Matting — per metre	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Variation for 33000 Volt Matting
— per metre	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Variation for supply of Cirlocks for MCBs QTY Unknown -	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Total MCC & Switchrooms (with Options)	 	 	 	 	 	 	 	 	 	 	 	 



















 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule




	 	 	 	 	 	 	 	 	 
	SCHEDULE OF PRICES	 	 	 	 	 	 
	VARIATIONS FOR ADDITIONS AND DELETIONS for MCC DOL STARTERS	 	 	 	 
	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	Price
	1.1
	 	0.37kW DOL	 	1 x 0.37kW DOL Starter	 	1	 	 
	1.2
	 	0.55kW DOL	 	1 x 0.55kW DOL Starter	 	1	 	 
	1.3
	 	1.1kW  DOL	 	1 x 1.1kW DOL Starter	 	1	 	 
	1.4
	 	1.5kW DOL	 	1 x 1.5kW DOL Starter	 	1	 	 
	1.5
	 	2.2kW DOL	 	1 x 2.2kW DOL Starter	 	1	 	 
	1.6
	 	3kW DOL	 	1 x 3kW DOL Starter	 	1	 	 
	1.7
	 	4kW DOL	 	1 x 4kW DOL Starter	 	1	 	 
	1.8
	 	5.5kW DOL	 	1 x 5.5kW DOL Starter	 	1	 	 
	1.9
	 	7.5kW DOL	 	1 x 7.5kW DOL Starter	 	1	 	 
	1.10
	 	11kW DOL	 	1 x 11kW DOL Starter	 	1	 	 
	1.11
	 	15kW DOL	 	1 x 15kW DOL Starter	 	1	 	 
	1.12
	 	18.5kW DOL	 	1 x 18.5kW DOL Starter	 	1	 	 
	1.13
	 	22kW DOL	 	1 x 22kW DOL Starter	 	1	 	 
	1.14
	 	30kW DOL	 	1 x 30kW DOL Starter	 	1	 	 
	1.15
	 	37kW DOL	 	1 x 37kW DOL Starter	 	1	 	 
	1.16
	 	45kW DOL	 	1 x 45kW DOL Starter	 	1	 	 
	1.17
	 	55kW DOL	 	1 x 55kW DOL Starter	 	1	 	 
	1.18
	 	75kW DOL	 	1 x 75kW DOL Starter	 	1	 	 
	1.19
	 	90kW DOL	 	1 x 90kW DOL Starter	 	1	 	 
	1.20
	 	110kW DOL	 	1 x 110kW DOL Starter	 	1	 	 
	1.21
	 	132kW DOL	 	1 x 132kW DOL Starter	 	1	 	 
	1.22
	 	150kW DOL	 	1 x 150kW DOL Starter	 	1	 	 
	1.23
	 	185kW DOL	 	1 x 185kW DOL Starter	 	1	 	 
	1.24
	 	200kW DOL	 	1 x 200kW DOL Starter	 	1	 	 
	1.25
	 	220kW DOL	 	1 x 220kW DOL Starter	 	1	 	 
	1.26
	 	250kW DOL	 	1 x 250kW DOL Starter	 	1	 	 
	1.27
	 	280kW DOL	 	1 x 280kW DOL Starter	 	1	 	 
	1.28
	 	315kW DOL	 	1 x 315kW DOL Starter	 	1	 	 
	1.29
	 	355kW DOL	 	1 x 355kW DOL Starter	 	1	 	 
	1.30
	 	400kW DOL	 	1 x 400kW DOL Starter	 	1	 	 
	1.31
	 	450kW DOL	 	1 x 450kW DOL Starter	 	1	 	 
	1.32
	 	500kW DOL	 	1 x 500kW DOL Starter	 	1	 	 
	1.33
	 	560kW DOL	 	1 x 560kW DOL Starter	 	1	 	 
	1.34
	 	630kW DOL	 	1 x 630kW DOL Starter	 	1	 	 
	 
	 	 	 	 	 	 	 	 





	 	 	 	 	 	 	 	 	 	 	 	 	 
	VARIATIONS FOR ADDITIONS AND DELETIONS for MCC VSD MODULES	 	 	 	 	 	 
	Installations Only. All VSDs are free issued.	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	 	 	 
	2.1

	 	0.55kW VSD
	 	1 x 0.55kW VSD Starter
	 	 	1	 	 	 	 	 
	2.2

	 	1.1kW VSD
	 	1 x 1.1kW VSD Starter
	 	 	1	 	 	 	 	 
	2.3

	 	1.5kW VSD
	 	1 x 1.5kW VSD Starter
	 	 	1	 	 	 	 	 
	2.4

	 	2.2kW VSD
	 	1 x 2.2kW VSD Starter
	 	 	1	 	 	 	 	 
	2.5

	 	3.7kW VSD
	 	1 x 3.7kW VSD Starter
	 	 	1	 	 	 	 	 
	2.6

	 	5.5kW VSD
	 	1 x 5.5kW VSD Starter
	 	 	1	 	 	 	 	 
	2.7

	 	7.5kW VSD
	 	1 x 7.5kW VSD Starter
	 	 	1	 	 	 	 	 
	2.8

	 	11kW VSD
	 	1 x 11kW VSD Starter
	 	 	1	 	 	 	 	 
	2.9

	 	15kW VSD
	 	1 x 15kW VSD Starter
	 	 	1	 	 	 	 	 
	2.10

	 	18.5kW VSD
	 	1 x 18.5kW VSD Starter
	 	 	1	 	 	 	 	 
	2.11

	 	22kW VSD
	 	1 x 22kW VSD Starter
	 	 	1	 	 	 	 	 
	2.12

	 	30kW VSD
	 	1 x 30kW VSD Starter
	 	 	1	 	 	 	 	 
	2.13

	 	37kW VSD
	 	1 x 37kW VSD Starter
	 	 	1	 	 	 	 	 
	2.14

	 	45kW VSD
	 	1 x 45kW VSD Starter
	 	 	1	 	 	 	 	 
	2.15

	 	55kW VSD
	 	1 x 55kW VSD Starter
	 	 	1	 	 	 	 	 





Variations Pricing_Rev
00


Page 9 of 15
Pages











 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule




	 	 	 	 	 	 	 	 	 
	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	Price
	2.16
	 	75kW VSD	 	1 x 75kW VSD Starter	 	1	 	 
	2.17
	 	90kW VSD	 	1 x 90kW VSD Starter	 	1	 	 
	2.18
	 	110kW VSD	 	1 x 110kW VSD Starter	 	1	 	 
	2.19
	 	132kW VSD	 	1 x 132kW VSD Starter	 	1	 	 
	2.20
	 	150kW VSD	 	1 x 150kW VSD Starter	 	1	 	 
	2.21
	 	185kW VSD	 	1 x 185kW VSD Starter	 	1	 	 
	2.22
	 	220kW VSD	 	1 x 220kW VSD Starter	 	1	 	 
	2.23
	 	280kW VSD	 	1 x 280kW VSD Starter	 	1	 	 
	2.24
	 	315kW VSD	 	1 x 315kW VSD Starter	 	1	 	 
	2.25
	 	355kW VSD	 	1 x 355kW VSD Starter	 	1	 	 
	2.26
	 	400kW VSD	 	1 x 400kW VSD Starter	 	1	 	 
	2.27
	 	450kW VSD	 	1 x 450kW VSD Starter	 	1	 	 
	2.28
	 	500kW VSD	 	1 x 500kW VSD Starter	 	1	 	 
	2.29
	 	630kW VSD	 	1 x 630kW VSD Starter	 	1	 	 






VARIATIONS FOR ADDITIONS AND DELETIONS for MCC SOFT STARTER MODULES

Installation Only. All soft starters are free issued.




	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	 
	3.1
	 	132kW SSD	 	1 x 132kW Soft Starter	 	1	 	 
	3.2
	 	150kW SSD	 	1 x 150kW Soft Starter	 	1	 	 
	3.3
	 	160kW SSD	 	1 x160kW Soft Starter	 	1	 	 
	3.4
	 	185kW SSD	 	1 x 185kW Soft Starter	 	1	 	 
	3.5
	 	220kW SSD	 	1 x 220kW Soft Starter	 	1	 	 
	3.6
	 	250kW SSD	 	1 x 250kW Soft Starter	 	1	 	 
	3.7
	 	280kW SSD	 	1 x 280kW Soft Starter	 	1	 	 
	3.8
	 	315kW SSD	 	1 x 315kW Soft Starter	 	1	 	 
	3.9
	 	355kW SSD	 	1 x 355kW Soft Starter	 	1	 	 
	3.10
	 	400kW SSD	 	1 x 400kW Soft Starter	 	1	 	 
	3.11
	 	450kW SSD	 	1 x 450kW Soft Starter	 	1	 	 
	3.12
	 	500kW SSD	 	1 x 500kW Soft Starter	 	1	 	 
	3.13
	 	630kW SSD	 	1 x 630kW Soft Starter	 	1	 	 






VARIATIONS FOR ADDITIONS AND DELETIONS for MCC FEEDER/INCOMER MODULES




	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	 
	4.1
	 	40 F	 	1 x 40 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.2
	 	63 F	 	1 x 63 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.3
	 	100 F	 	1 x 100 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.4
	 	160 F	 	1 x 160 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.5
	 	200 F	 	1 x 200 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.6
	 	250 F	 	1 x 250 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.7
	 	400 F	 	1 x 400 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.8
	 	630 F	 	1 x 630 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.9
	 	1250 F	 	1 x 1250 Amp Circuit Breaker Feeder Module	 	1	 	 
	4.10
	 	40 F/C	 	1 x 40 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.11
	 	63 F/C	 	1 x 63 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.12
	 	100 F/C	 	1 x 100 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.13
	 	160 F/C	 	1 x 160 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.14
	 	200 F/C	 	1 x 200 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.15
	 	250 F/C	 	1 x 250 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.16
	 	400 F/C	 	1 x 400 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.17
	 	630 F/C	 	1 x 630 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.18
	 	1250 F/C	 	1 x 1250 Amp Circuit Breaker Feeder/Contactor Module	 	1	 	 
	4.15
	 	800 IC	 	1 x 800 Amp Air Circuit Breaker Incomer	 	1	 	 
	4.16
	 	1600 IC	 	1 x 1600 Amp Air Circuit Breaker Incomer	 	1	 	 
	4.17
	 	3200 IC	 	1 x 3200 Amp Air Circuit Breaker Incomer	 	1	 	 
	4.18
	 	4000 IC	 	1 x 4000 Amp Air Circuit Breaker Incomer	 	1	 	 








Variations Pricing_Rev 00



Page 10 of 15 Pages












 




LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule





VARIATIONS FOR ADDITIONS AND DELETIONS for LCS TYPES




	  	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 
	Item No.	 	LCS Type	 	Description	 	Qty	 	Price
	5.1
	 	LCS-1	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors ≤30kW)	 	1	 	 	 	 
	5.2
	 	LCS-2	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors ≤55kW)	 	1	 	 	 	 
	5.3
	 	LCS-3	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors ≤90kW)	 	1	 	 	 	 
	5.4
	 	LCS-4	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors ≤l85kW)	 	1	 	 	 	 
	5.5
	 	LCS-5	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors ≤30kW)	 	1	 	 	 	 
	5.6
	 	LCS-6	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors ≤55kW)	 	1
	5.7
	 	LCS-7	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and
labels (VSD motors≤90kW)	 	1	 	 	 	 
	5.8
	 	LCS-8	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors ≤185kW)	 	1	 	 	 	 
	5.9
	 	LCS-9	 	Local control station with start pushbutton, emergency stop button and labels (no isolator)	 	1	 	 	 	 
	5.10
	 	LCS-10	 	Local control station with start pushbutton, stop pushbutton, emergency stop button
and labels (no isolator)	 	1	 	 	 	 
	5.11
	 	LCS-11	 	Local control station with forward pushbutton, reverse pushbutton, emergency stop button
and labels (no isolator)	 	1	 	 	 	 
	5.12
	 	LCS-12	 	80 amp, 3 pole isolator only	 	1	 	 	 	 
	5.13
	 	LCS-13	 	125 amp, 3 pole isolator only	 	1	 	 	 	 
	5.14
	 	LCS-14	 	200 amp, 3 pole isolator only	 	1	 	 	 	 
	5.15
	 	LCS-15	 	400 amp, 3 pole isolator only	 	1	 	 	 	 
	5.16
	 	LCS-16	 	80 amp, 6 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors ≤30kW)	 	1	 	 	 	 
	5.17
	 	LCS-17	 	80 amp, 6 pole isolator, reverse, lock-off emergency stop, start pushbutton and labels (DOL motors ≤30kW)	 	1	 	 	 	 
	5.18
	 	LCS-18	 	Local control station with 32 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)	 	1	 	 	 	 
	5.19
	 	LCS-19	 	Local control station with 63 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)	 	1	 	 	 	 
	5.20
	 	LCS-20	 	Local control station with 125 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)	 	1	 	 	 	 
	5.21
	 	LCS-21	 	Local control station with 200 amp decontactor, 4 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)	 	1	 	 	 	 
	5.22
	 	LCS-CONV	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton, larger box, extra terminals and labels	 	1	 	 	 	 
	5.23
	 	LCS-SLEW	 	80 amp, 3 pole isolator, reverse,
lock-off emergency stop, start pushbutton and labels (DOL motors ≤30kW)	 	1	 	 	 	 
	5.24	 	LCS-ES
	 	Lock-off emergency stop pushbutton only
	 	1	 	 	 	 









Variations
Pricing_Rev 00 




Page 11 of 15
Pages











 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule





VARIATIONS FOR DISTRIBUTION BOARDS






	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	 	 	Description	 	Qty	 	Price
	 	6.1	 	 	 	 	Distribution Board 72 pole, 415V, 250A,
20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 
	 	6.2	 	 	 	 	Distribution Board 72 pole, 415V, 250A,
20kA/0.2s, IP42

	 	1	 	 
	 	6.3	 	 	 	 	Distribution Board 36 pole, 415V, 250A,
20kA/0.2s, IP42

	 	1	 	 
	 	6.4	 	 	 	 	Distribution Board 36 pole, 415V, 250A,
20kA/0.2s, IP42, with Lighting Control Section

	 	1	 	 
	 	6.5	 	 	 	 	Distribution Board 24 pole, 240V, 160A,
20kA/0.2s, IP42

	 	1	 	 
	 	6.6	 	 	 	 	Install one single pole, 10 amp circuit breaker
	 	1	 	 
	 	6.7	 	 	 	 	Install one single pole, 16 amp circuit breaker

	 	1	 	 
	 	6.8	 	 	 	 	Install one single pole, 10 amp circuit breaker 

with 30mA earth leakage
	 	1	 	 
	 	6.9	 	 	 	 	Install one single pole, 16 amp circuit breaker 

with 30mA earth leakage

	 	1	 	 
	 	6.10	 	 	 	 	Install one single pole, 10 amp circuit breaker 

with 100mA earth leakage

	 	1	 	 
	 	6.11	 	 	 	 	Install one single pole, 16 amp circuit breaker 

with 100mA earth leakage

	 	1	 	 
	 	6.12	 	 	 	 	Install one three pole, 16 amp circuit breaker

	 	1	 	 
	 	6.13	 	 	 	 	Install one three pole, 16 amp circuit breaker 

with 30mA earth leakage

	 	1	 	 
	 	6.14	 	 	 	 	Install one three pole, 16 amp circuit breaker 

with 300mA earth leakage

	 	1	 	 
	 	6.15	 	 	 	 	Install one three pole, 20 amp circuit breaker
	 	1	 	 
	 	6.16	 	 	 	 	Install one three pole, 20 amp circuit breaker 

with 30mA earth leakage
	 	 	 	 
	 	6.17	 	 	 	 	Install one three pole, 20 amp circuit breaker 

with 100mA earth leakage
	 	 		 
	 	6.18	 	 	 	 	Install one three pole, 32 amp circuit breaker

	 	 	 	 
	 	6.19	 	 	 	 	Install one three pole, 32 amp circuit breaker 

with 30mA earth leakage

	 	 	 	 
	 	6.20	 	 	 	 	Install one three pole, 32 amp circuit breaker 

with 100mA earth leakage
	 	 	 	 
	 	6.21	 	 	 	 	Install one three pole, 63 amp circuit breaker

	 	 	 	 
	 	6.22	 	 	 	 	Install one three pole, 63 amp circuit breaker 

with 30mA earth leakage

	 	 	 	 
	 	6.23	 	 	 	 	Install one three pole, 63 amp circuit breaker 

with 100mA earth leakage

	 	 	 	 






OPTIONAL PRICING FOR SWITCHROOM GAS SUPPRESSION SYSTEM




	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	 
	 	7.1	 	 	James Engineering
	 	Gas Suppression System, Primary Crushing LV
Switchroom

	 	1	 	 
	 	7.2	 	 	James Engineering
	 	Gas Suppression System, Primary Crushing HV
Switchroom

	 	1	 	 
	 	7.3	 	 	James Engineering
	 	Gas Suppression System, Primary Conveying LV
Switchroom

	 	1	 	 
		7.4		 	James Engineering
	 	Gas Suppression System, Ore Stockpile LV
Switchroom

	 	1	 	 
	 	7.5	 	 	James Engineering
	 	Gas Suppression System, Wurtol Pumping Station LV
Switchroom

	 	1	 	 






Variations Pricing_Rev 00





Page 12 of 15
Pages











 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variation Pricing Schedule




	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	Price
	7.6
	 	James Engineering	 	Gas Suppression System, Grinding LV Switchroom	 	1	 	 
	7.7
	 	James Engineering	 	Gas Suppression System, Grinding HV Switchroom	 	1	 	 
	7.8
	 	James Engineering	 	Gas Suppression System, Pressure Oxidation LV Switchroom	 	1	 	 
	7.9
	 	James Engineering	 	Gas Suppression System, Pressure Oxidation HV Switchroom	 	1	 	 
	7.10
	 	James Engineering	 	Gas Suppression System, Cyanidation & Adsorption LV Switchroom	 	1	 	 
	7.11
	 	James Engineering	 	Gas Suppression System, Cyanidation & Adsorption HV Switchroom	 	1	 	 
	7.12
	 	James Engineering	 	Gas Suppression System, Oxygen Plant LV Switchroom	 	1	 	 
	7.13
	 	James Engineering	 	Gas Suppression System, Oxygen Plant HV Switchroom	 	1	 	 
	7.14
	 	James Engineering	 	Gas Suppression System, Grinding Thickeners LV Switchroom	 	1	 	 
	7.15
	 	James Engineering	 	Gas Suppression System, Process Seawater LV Switchroom	 	1	 	 
	7.16
	 	James Engineering	 	Gas Suppression System, Bus C3, C4 & E LV Switchroom	 	1	 	 
	7.17
	 	James Engineering	 	Gas Suppression System, Bus C3 & C4 HV Switchroom	 	1	 	 
	7.18
	 	James Engineering	 	Gas Suppression System, Bus E HV Switchroom	 	1	 	 
	7.19
	 	James Engineering	 	Gas Suppression System, Bus F LV Switchroom	 	1	 	 
	7.20
	 	James Engineering	 	Gas Suppression System, Bus F HV Switchroom	 	1	 	 
	7.21
	 	Brice Engineers	 	Gas Suppression System, Primary Crushing LV Switchroom	 	1	 	 
	7.22
	 	Brice Engineers	 	Gas Suppression System, Primary Crushing HV Switchroom	 	1	 	 
	7.23
	 	Brice Engineers	 	Gas Suppression System, Primary Conveying LV Switchroom	 	1	 	 
	7.24
	 	Brice Engineers	 	Gas Suppression System, Ore Stockpile LV Switchroom	 	1	 	 
	7.25
	 	Brice Engineers	 	Gas Suppression System, Wurtol Pumping Station LV Switchroom	 	1	 	 
	7.26
	 	Brice Engineers	 	Gas Suppression System, Grinding LV Switchroom	 	1	 	 
	7.27
	 	Brice Engineers	 	Gas Suppression System, Grinding HV Switchroom	 	1	 	 
	7.28
	 	Brice Engineers	 	Gas Suppression System, Pressure Oxidation LV Switchroom	 	1	 	 
	7.29
	 	Brice Engineers	 	Gas Suppression System, Pressure Oxidation HV Switchroom	 	1	 	 
	7.30
	 	Brice Engineers	 	Gas Suppression System, Cyanidation & Adsorption LV Switchroom	 	1	 	 
	7.31
	 	Brice Engineers	 	Gas Suppression System, Cyanidation & Adsorption HV Switchroom	 	1	 	 
	7.32
	 	Brice Engineers	 	Gas Suppression System, Oxygen Plant LV Switchroom	 	1	 	 
	7.33
	 	Brice Engineers	 	Gas Suppression System, Oxygen Plant HV Switchroom	 	1	 	 
	7.34
	 	Brice Engineers	 	Gas Suppression System, Grinding Thickeners LV Switchroom	 	1	 	 
	7.35
	 	Brice Engineers	 	Gas Suppression System, Process Seawater LV Switchroom	 	1	 	 
	7.36
	 	Brice Engineers	 	Gas Suppression System, Bus C3, C4 & E LV Switchroom	 	1	 	 
	7.37
	 	Brice Engineers	 	Gas Suppression System, Bus C3 & C4 HV Switchroom	 	1	 	 






Variations Pricing_Rev 00




Page 13 of 15 Pages












 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule




	 	 	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	Price
	 	7.38	 	 	Brice Engineers
	 	Gas Suppression System, Bus E HV Switchroom

	 	 	1	 	 	 
	 	7.39	 	 	Brice Engineers
	 	Gas Suppression System, Bus F LV Switchroom

	 	 	1	 	 	 
	 	7.40	 	 	Brice Engineers
	 	Gas Suppression System, Bus F HV Switchroom

	 	 	1	 	 	 






OPTIONAL PRICING FOR 2 HOUR FIRE RATING OF SWITCHROOM WALLS

For Wall Adjacent to (or Floor Above) Transformers.




	 	 	 	 	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	 
	 	8.1	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Primary
Crushing LV Switchroom

	 	 	1	 	 	 
	 	8.2	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Primary
Crushing HV Switchroom

	 	 	1	 	 	 
	 	8.3	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Primary
Conveying LV Switchroom

	 	 	1	 	 	 
	 	8.4	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Ore
Stockpile LV Switchroom

	 	 	1	 	 	 
	 	8.5	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Wurtol
Pumping Station LV Switchroom

	 	 	1	 	 	 
	 	8.6	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Grinding LV
Switchroom

	 	 	1	 	 	 
	 	8.7	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Grinding HV
Switchroom

	 	 	1	 	 	 
	 	8.8	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Pressure
Oxidation LV Switchroom

	 	 	1	 	 	 
	 	8.9	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Pressure
Oxidation HV Switchroom

	 	 	1	 	 	 
	 	8.10	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Cyanidation
& Adsorption LV Switchroom

	 	 	1	 	 	 
	 	8.11	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Cyanidation
& Adsorption HV Switchroom

	 	 	1	 	 	 
	 	8.12	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Oxygen
Plant LV Switchroom

	 	 	1	 	 	 
	 	8.13	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Oxygen
Plant HV Switchroom

	 	 	1	 	 	 
	 	8.14	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Grinding
Thickener LV Switchroom

	 	 	1	 	 	 
	 	8.15	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Process
Seawater LV Switchroom

	 	 	1	 	 	 
	 	8.16	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Bus C3, C4
& E LV Switchroom

	 	 	1	 	 	 
	 	8.17	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Bus C3 &
C4 HV Switchroom

	 	 	1	 	 	 
	 	8.18	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Bus E HV
Switchroom

	 	 	1	 	 	 
	 	8.19	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Bus F LV
Switchroom

	 	 	1	 	 	 
	 	8.20	 	 	James Engineering
	 	Two (2) hour fire rating of Switchroom Walls, Bus F HV
Switchroom

	 	 	1	 	 	 
	 	8.21	 	 	Brice Engineers
	 	Two (2) hour fire rating of Switchroom Walls, Primary
Crushing LV Switchroom

	 	 	1	 	 	 
	 	8.22	 	 	Brice Engineers
	 	Two (2) hour fire rating of Switchroom Walls, Primary
Crushing HV Switchroom

	 	 	1	 	 	 
	 	8.23	 	 	Brice Engineers
	 	Two (2) hour fire rating of Switchroom Walls, Primary
Conveying LV Switchroom

	 	 	1	 	 	 
	 	8.24	 	 	Brice Engineers
	 	Two (2) hour fire rating of Switchroom Walls, Primary
Conveying & Ore Stockpile LV Switchroom

	 	 	1	 	 	 
	 	8.25	 	 	Brice Engineers
	 	Two (2) hour fire rating of Switchroom Walls, Wurtol
Pumping Station LV Switchroom

	 	 	1	 	 	 










Variations
Pricing_Rev 00


Page 14 of 15 Pages











 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule




	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Item
NO. 	 	Supplier	 	Description	 	QTY	 	Price	 
	 	8.26	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Grinding LV Switchroom
	 	 	1	 	 	 	 	 
	 	8.27	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Grinding HV Switchroom
	 	 	1	 	 	 	 	 
	 	8.28	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Pressure Oxidation LV Switchroom
	 	 	1	 	 	 	 	 
	 	8.29	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Pressure Oxidation HV Switchroom
	 	 	1	 	 	 	 	 
	 	8.30	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Cyanidation & Adsorption LV Switchroom
	 	 	1	 	 	 	 	 
	 	8.31	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Cyanidation & Adsorption HV Switchroom
	 	 	1	 	 	 	 	 
	 	8.32	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Oxygen Plant LV Switchroom
	 	 	1	 	 	 	 	 
	 	8.33	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Oxygen Plant HV Switchroom
	 	 	1	 	 	 	 	 
	 	8.34	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Grinding Thickeners LV Switchroom
	 	 	1	 	 	 	 	 
	 	8.35	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Process Seawater LV Switchroom
	 	 	1	 	 	 	 	 
	 	8.36	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus C3, C4 & E LV Switchroom
	 	 	1	 	 	 	 	 
	 	8.37	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus C3 & C4 HV Switchroom
	 	 	1	 	 	 	 	 
	 	8.38	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus E HV Switchroom
	 	 	1	 	 	 	 	 
	 	8.39	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus F LV Switchroom
	 	 	1	 	 	 	 	 
	 	8.40	 	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus F HV Switchroom
	 	 	1	 	 	 	 	 






Variations Pricing_Rev 00




Page 15 of 15 Pages











 





LGL

MILLION OUNCE PLANT UPGRADE (MOPU) PROJECT

EQUIPMENT SUPPLY TENDER




MOPU-1101

LOW VOLTAGE MCCs & SWITCHROOMS



SECTION IV

FORM OF TENDER



	 	 	 
	Date:	 	5/01/2009
	Name of Tenderer:

	 	PLUMMERS INDUSTRIES PTY LTD
	Proposal Number:

	 	Q 4929
	Validity of Proposal:

	 	90 DAYS
	Equipment:

	 	MCCS AND SWITCHROOMS
	Make:

	 	PI 2000 (MCC’s)
	Model:
	 	 
	Type:
	 	 
	Manufacturer:

	 	PLUMMERS INDUSTRIES PTY LTD
	Dealer distributor in Country:

	 	PLUMMERS INDUSTRIES PTY LTD QLD



















 





PRICING
SUMMARY




MOPU—1101 — Low Voltage MCCs & Switchrooms




Tenderer’s Name: PLUMMERS INDUSTRIES PTY




All prices to be in Australian or US currency (refer clause 4 of Section I Part A)




	 	 	 	 	 	 	 
	Currency of Manufacturer’s Quotation
	 	 	 	 	 	 
	 

	 	 	 	 	 	 
	Location of Seller’s Premises

	 	 	 	BRISBANE AUSTRALIA	 	 






Table 1.1 Cost Breakdown




	 	 	 	 	 	 	 	 	 
	 	 	UOM	 	QTY	 	Unit Cost	 	Extended
	Refer Attached Pricing Schedules
	 	 	 	 	 	 	 	 
	 
	Equipment Options

	 	EA	 	 	 	 	 	 
	Special Tools

	 	EA	 	 	 	 	 	 
	Extended Warranty Costs (if applicable)

	 	EA	 	 	 	 	 	 
	Discount (if any)

	 	EA	 	 	 	 	 	 
	Export Packing

	 	EA	 	 	 	 	 	 
	Loading to Transport

	 	EA	 	 	 	 	 	 
	Forward Cover Foreign Currency Risk (if any)

	 	EA	 	 	 	 	 	 






Subtotal FCA (Incoterms 2000) Point of Manufacture




	 	 	 	 	 	 	 	 	 
	 	 	UOM	 	QTY	 	Unit Cost	 	Extended
	Freight/Logistics Cost Breakdown
	 	 	 	 	 	 	 	 
	Freight to nearest Seaport (Nomiate)

	 	EA	 	 	 	 	 	 
	Customs/Port Terminal Charges (if any)

	 	EA	 	 	 	 	 	 
	Forward Cover Foreign Currency Risk (if any)

	 	EA	 	 	 	 	 	 
	Subtotal FOB (Incoterms 2000) Seaport
	 	 	 	 	 	 
	 

	 	 	 	 	 
	 

	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	TOTAL FOB COST	 	 






 











 





COMMERCIAL DETAILS




Equipment Tender # and Description

Tenderer’s Name: PLUMMERS INDUSTRIES PTY LTD




Tenderer’s Proposed Terms of Payment (Include details)

See cover letter




Cancellation Charges (Include details such as schedule and values)




As
per progress items claims




Point(s)
of Manufacture

Specify City and State (if applicable) for each point(s) of supply

BRISBANE QUEENSLAND




Shipment
Location

75 Wolston Road Sumner Park (Using James Eng)




Sub-Suppliers

Provide list of all major/critical components from sub-supplier. State sub-supplier name and location of component manufacture.

SWITCHROOMS — JAMES ENGINEERING BRISBANE




	 	 	 	 	 
	Progress Reports and Schedule
	(Detailed design, procurement, manufacturing, assembly, testing, delivery schedule and
progress report)
	Number of weeks from date of Purchase Order
	 	6 of weeks
	Frequency of updates
	 	4 of weeks






Liquidated Damages — Manufacturer’s Proposal, Subject to Assessment by LGL (Include details)

Per Diem Rate (%)

Maximum Amount (%)




	 	 	 	 	 
	Warranties/Guarantees
	 	 	 	 
	From date of equipment startup-commissioning (Number of months)
	 	12 of months
	From date of final component shipment (Number of months)
	 	18 of months






Extended
Warranty

List all extended warranties for the Equipment and components
 None available




Extended Warranty Cost (if applicable)




Other Details (Add information if required)




	 	 	 
	Does the Seller accept the Warranty Terms and Conditions?

	 	Yes     þ
	 

	 	No       o






 









 






COMMERCIAL DETAILS




Drawings, Operators Manuals and Parts Manuals (Where applicable)

Preliminary Engineering Drawings for approval

Number of days from date of Purchase Order




From 6 weeks for first drawing set.



	 	 	 	 	 
	Final Certified Engineering Drawings
	 	 	 	 
	Number of days from date of approved preliminary drawings
	 	14 days






Final Certified (Where preliminary drawings are not required for approval)

Number of days from date of Purchase Order




At completion



Operators Manuals (Installation, Operation, Maintenance and Training)

Operator Manuals in addition to requirements outlined in Section I

Additional sets (Indicate cost if applicable)

Electronic sets — CD-R (Indicate cost if applicable)




Parts Manuals (Including Bearings, Seals, and Filter Conversions)

Parts Manuals in addition to requirements outlined in Section I

Additional sets (Indicate cost if applicable)

Electronic sets — CD-R (Indicate cost if applicable)




Quality Assurance/Quality Control (Include details)




Attached




Health, Safety, Environmental & Human Rights Compliance (Include details)




Tools (Special tools required for installation, operation and maintenance of Equipment)




	 	 	 	 	 
	Description	 	Amount	 
	None Required

	Total

	Contract Local/Overseas Content







	 	 	 	 	 
	Description	 	Amount	 
	Plummers Industries is 100% Australian owned and operated
	 	 	 	 
	Total Contract Value
	 	 	 	 






 









 






COMMERCIAL DETAILS



Additional
Items/Details  (if required)





 











 





ALTERNATIVE TENDER




Tenderer’s Proposed Departures From the Tender Documents



Equipment Tender # and Description

Tenderer’s Name: PLUMMERS INDUSTRIES




All prices to be in Australian or US currency (refer clause 4 of Section I Part A)




			
	Currency of Manufacturer’s Quotation
	 	AUSTRALIA





Tenderer to detail the additional or reduced cost associated with each departure itemised. Tenderer
to add additional line items and clarification below if required.




	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Table 1.2 Technical Departures	 	UOM	 	QTY	 	Unit Cost	 	Extended
	See cover letter
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	[List item]
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	Forward Cover Foreign Currency Risk (if any)
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 






                              Subtotal
FOB (Incoterms 2000) Seaport _____________________________ +/-



	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Table 1.3 Commercial Departures	 	UOM	 	QTY	 	Unit Cost	 	Extended
	[List Item]
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	See cover letter
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	Forward Cover Foreign Currency Risk (if any)
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 






                              Subtotal
FOB (Incoterms 2000) Seaport
_____________________________+/-




	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Table 1.4 Optional Equipment and/or Materials	 	UOM	 	QTY	 	Unit Cost	 	Extended	 




Tenderer to indicate if the following design features are considered Standard or Non-Standard
equipment items. For all non-standard items, Tenderer to provide cost. Unless otherwise specified
it is understood the equipment options below will meet or exceed all technical requirements in
Section III. Tenderer to add additional line items and
clarification below, if required.




	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	[List Item]
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 
	Forward Cover Foreign Currency Risk (if any)
	 	EA	 	 	 	 	 	 	 	 	 	 	 	 






                              Subtotal FOB (Incoterms 2000) Seaport _____________________________+/-



TOTAL FOB COST

















 





COMMERCIAL DETAILS




Equipment Tender # and Description:




Tenderer’s Name:  PLUMMERS INDUSTRIES




Table 2.1 Schedule of Key Dates




	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	Available For	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	Inspection Or	 	 	 	 	 	 	 
	Item	 	Tag	 	 	Place of Manufacture	 	 	Start Manufacture	 	 	Testing	 	 	Dispatch Ex Works	 	 	Delivery Site	 
	 	 	 	 	 	 	 	 	 	 	(Weeks After Order)	 
	To be discussed at kick off meeting depending on
site and client scheduling
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 






Table
2.2 Contractual Delivery Schedule

State delivery in number of weeks from date of Purchase Order for the following: 

Manufacture and Supply                            36 

Delivery Completion Date                    Oct-09




Table
2.3 Witnessed and Verified Performance Tests

List the Tests that need to be witnessed and verified and detail if the cost of these tests is included in the Tendered Price




	 	 	 	 	 	 	 	 	 	 	 	 	 
	Component and Test	 	Cost Included?	 	 	 	 	 	 	Cost	 
	All final testing and inspections need to be witnessed and verified prior to release.
	 	Yes	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 
	See attached ITP
	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	Total Cost:	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 



















 





COMMERCIAL DETAILS




	 	 	 
	Equipment Tender # and Description
	 	 
	Tenderer’s Name: PLUMMERS INDUSTRIES

	 	 






Table 2.3 Equipment Weights and Dimensions




	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Weight	 	Shipping Dimensions
	Item	 	Description	 	Tag	 	(kg)	 	(mm)
	1.
	 	SS2850	 	 	 	14000	 	8.2X 3.8
	2.
	 	SS2051	 	 	 	14000	 	8.2X 3.8
	3.
	 	SS2101	 	 	 	18000	 	12.2 X 5.7
	4.
	 	SS2741	 	 	 	18000	 	12.2 X 6.0
	5.
	 	SS2160	 	 	 	16000	 	15.2 X 5.7
	6.
	 	SS2551	 	 	 	2 X 20000	 	28.2 X 3.2
	7.
	 	 	 	 	 	12000	 	6.7 X 6.0
	8.
	 	SS2932	 	 	 	1X24T,1X12T	 	20.2 X 6.0,10.2 X 6.0
	9.
	 	SS2560	 	 	 	26000	 	17.2 X 6.4
	10.
	 	 	 	 	 	16000	 	13.2 X 6.4
	11.
	 	SS2000	 	 	 	28000	 	14.7 X 6.4
	12.
	 	 	 	 	 	12000	 	8.2 X 6.4
	13.
	 	SS2931	 	 	 	1X20T,1X12T	 	15.5 X 10.4
	14.
	 	 	 	 	 	28000	 	22.8 X 6.0
	15
	 	SS2200	 	 	 	2 X 16000	 	16.2 X 4.7, 16.2 X 4.7
	16
	 	 	 	 	 	22000	 	16.2 X 6.6
	17
	 	SS2400	 	 	 	2 X 22000	 	14.2 X 6.0
	18
	 	 	 	 	 	14000	 	8.2 X 6.0
	19
	 	 	 	 	 	 	 	 
	20
	 	 	 	 	 	 	 	 
	21
	 	 	 	 	 	 	 	 
	22
	 	 	 	 	 	 	 	 
	Total Equipment Weight	 	 	 	238000	 	 
	 	 	 	 	 
	Total Cubic Measure	 	 	 	 	 	0
	 	 	 	 	 
	Total Number of Pieces	 	 	 	 	 	 
	 	 	 	 	 





Table 2.4 Spare Parts




	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Weight	 	Shipping Dimensions
	Item	 	Description	 	Tag	 	(kg)	 	(mm)
	1.
	 	 	 	 	 	 	 	 
	2.
	 	 	 	 	 	 	 	 
	3.
	 	 	 	 	 	 	 	 
	4.
	 	 	 	 	 	 	 	 
	5.
	 	 	 	 	 	 	 	 
	6.
	 	 	 	 	 	 	 	 
	Total Spare Parts Weight	 	 	 	0	 	 
	 	 	 	 	 
	Total Cubic Measure	 	 	 	 	 	0
	 	 	 	 	 
	Total Number of Pieces	 	 	 	 	 	 
	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 
	Total shipping weight or cubic measure “Revenue Tonne”	 	 	 	 	 	 
	 	 	 	 	 	 	 
	(Revenue Tonne = greater of tonnage or cubic meter)	 	 	 	 	 	 






 









 






SPARE PARTS




Equipment Tender # and Description:

Tenderer’s Name: PLUMMERS INDUSTRIES




	 	 	 	 	 
	Spare Parts
	 	 	 	 
	Recommended spare parts for one (1) year of Operation
	 	 	 	 
	(Tenderer to provide separate list of spare parts in Excel format)
	 	 	 	 
	To be advised once MCC design has been completed
	 	 	 	 
	Commissioning spare parts
	 	 	 	 
	(Tenderer to provide separate list of commissioning parts in Excel format)
	 	 	 	 
	 
	 	 	 	 
	Spare Components
	 	 	 	 
	(Tenderer to provide pricing for spare components)
	 	 	 	 
	 
	 	 	 	 
	Export/Domestic Packing
	 	 	 	 
	Freight (to nearest Port of Exit)
	 	 	 	 
	Ocean Freight to Port of Entry
	 	 	 	 
	Customs/Port Terminal Charges (if any)
	 	 	 	 
	Inland Freight to Project Site
	 	 	 	 
	TOTAL COST
	 	 	 	 
	 
	 	 	 	 
	Parts Discount (This parts discount would apply for all initial spare parts purchased)
	 	 	%	 
	 
	 	 	 	 
	Nearest Service Depot and/or Distributor (State name and address)
	 	 	 	 
	 
	 	 	 	 
	Other locations for spare parts support (State name and address)
	 	 	 	 
	 
	 	 	 	 
	Approximate value for Equipment spare parts carried at named locations
	 	 	 	 
	 
	 	 	 	 
	Recommended major components as consignment stock at Work Site without cost to Buyer
	 	 	 	 
	(Tenderer to provide separate list of major components or modules in Excel format)
	 	 	 	 
	 
	 	 	 	 
	Recommended list and pricing for all high turnover consumables
	 	 	 	 
	(Tenderer to provide separate list of consumables in Excel format)
	 	 	 	 







 











 





SPARES




	 	 	 
	Equipment Tender # and Description
	 	 
	Tenderer’s Name: PLUMMERS INDUSTRIES








Table 3.1 Commissioning Spares




	 	 	 	 	 	 	 	 	 
		 		 		 	Unit Price If	 	Unit Price If
	 	 	 	 	Recommended	 	Purchased With Main	 	Supplied At Later
	Item	 	Description	 	Quantity	 	Order	 	Date
	 
	 	To be advised once MCC design has been completed
 	 	 	 	 
	 	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 






Table 3.2 Capital Spares




	 	 	 	 	 	 	 	 	 
		 		 		 	Unit Price If	 	Unit Price If
	 	 	 	 	Recommended	 	Purchased With Main	 	Supplied At Later
	Item	 	Description	 	Quantity	 	Order	 	Date
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 
	

	 	 	 	 	 	 	 	 






 









 





AVAILABILITY GUARANTEES




Equipment Tender # and Description



Tenderer’s Name: PLUMMERS INDUSTRIES




	 
	Equipment Availability Guarantees (NHP Equipment) 


	Year 1

	Year 2

	Year 3

	Year 4

	Year 5

	 

	Compensation for availability guarantee(s) not being met:

	NIL

	 

	Conditions of availability guarantees(s):

	None







 









 






SERVICE & SUPPORT




Equipment Tender # and Description

Tenderer’s Name: PLUMMERS INDUSTRIES




	 	 
	Technical On-Site Personnel (if Applicable)
	 
	Reimbursable Sum per Person from X to Cairns or return (detail point of origin)
	 
	Not Applicable
	 
	 
	 
	Daily Rates for technical on-Site personnel — detail skills/trades
	 
	Not Applicable
	 
	 
	 
	Equipment (List required equipment)
	 
	Not Applicable
	 
	 
	 
	Location of Representation Not Applicable
	 
	Number of Representatives Not Applicable
	 
	Estimated length of stay Not Applicable
	 
	Number/Frequency of visits Not Applicable
	 
	Additional Items/Details
	 
	Number of Technical On-Site Personnel days available at no cost to Buyer
	 
	Nil
	 
	Emergency Contact for Technical On-Site requirements (Provide details)
	 
	 
	 
	Sub-Contractors
	 
	Provide the company names of sub-contractors that would be considered for technical on-Site personnel supply and state their involvement
	 
	 
	 
	None
	 
	 
	 
	Discounted Labour Rate (In the event of additional work outside the scope of work)
	 






 









 






SERVICE & SUPPORT




Product Support (Technical Service and Training)




	 	 
	Outline recommendations for Operator and Maintenance Training Personnel (Provide details)
	 
	Not Required
	 
	Outline the period Service Personnel will be provided without cost to Buyer. Assume this is an advice/troubleshooting role.
	 
	Warranty Period
	 
	Outline the period Training Personnel will be provided without cost to Buyer.
	 
	Not Required
	 
	Cost of Service Personnel (Hourly rate)
	 
	Cost of Training Personnel (Hourly rate)
	 
	 
	 
	Name and address of Manufacturer’s Representative
	 
	           — 75 Wolston Road Sumner Park
	 
	Identify from which location of Service and Training Personnel will be provided Brisbane or Perth
	 
	Identify the preferred location for Component Exchange/Rebuilds (Identify preferred locations) Brisbane
	 
	Identify any major components or modules that Tenderer recommends and is prepared to locate in the LGL warehouse as consignment stock at no cost to Buyer
	 
	 
	 
	None
	 
	

	 
	Other Details (Add information if required)
	 







 











 





TECHNICAL DATA SCHEDULE




Equipment Tender # and Description

Tenderer’s Name: PLUMMERS INDUSTRIES




Table 4.1 Technical Data Schedule




	 	 	 	 	 	 	 
	 	 	Weeks After	 	Vendor Agreement	 
	Item	 	Award	 	(Y/N)	 
	DATA WITH TENDER
	 	 	 	 	 	 
	Preliminary general arrangement drawing
	 	6+	 	 	 	 
	Proposed manufacturing Schedule
	 	6	 	 	 	 
	Recommended commissioning & capital spares
	 	12	 	 	 	 
	 
	 	 	 	 	 	 
	DATA AFTER AWARD
	 	 	 	 	 	 
	Detailed and dimensioned general arrangement drawing including:
	 	12 weeks+	 	 	 	 
	• Lifting details
	 	 	 	 	 	 
	• Operating and maintenance tolerances
	 	 	 	 	 	 
	• Piping and electrical interface details
	 	 	 	 	 	 
	• Itemised list of components
	 	 	 	 	 	 
	Fixed and firm manufacturing schedule
	 	10.0	 	 	 	 
	Inspection and test plan
	 	6.0	 	 	 	 
	Operating and maintenance manuals:
	 	delivery -2	 	 	 	 
	• Preliminary
	 	 	 	 	 	 
	• Final
	 	 	 	 	 	 
	As-built drawings
	 	delivery	 	 	 	 



















 




 





	 	 	 
	From:
	 	 
	Sent:

	 	Friday, 9 January 2009 8:59 AM
	To:

	 	MOPU_11
	Subject:

	 	FW: MOPU-1101-I Post Tender Query #1
	Attachments:

	 	Completed Battery Charger Datasheet.xls; Q 4929 — NHP — MOPU-1101_Pricing
	 

	 	Schedules.xls; Q 4929 -Moeller — MOPU-1101_Pricing Schedules.xls; Q 4929 -
	 

	 	MOPU-1101_Distribution Board Datasheet.xls





I’ve saved these in w drive.



Regards,




Administrative Assistant — Purchasing

Lihir Services Australia Pty Ltd

GPO Box 905, Brisbane QLD 4001

Level 9, 500 Queen St, Brisbane QLD 4000




CONFIDENTIALITY CAUTION AND DISCLAIMER



This message is intended only for the use of the Individual or entity to which it is addressed and
contains information that is privileged and confidential. If the reader of this message is not the
intended recipient, or the employee or agent responsible for delivering the message to the intended
recipient, you are hereby notified that any dissemination, distribution or copying of this
communication is strictly prohibited. If you have received this communication in error, please
notify us immediately at (61-7) 3318 3300 and delete the original message. If you are the intended
recipient of this message, we remind you that electronic mail on the Internet may not be secure and
that this message was not and future messages will not be encrypted or otherwise protected, unless
specifically requested, in which case, special arrangements will be made.



 





From:

Sent: Friday, 9 January 2009 8:00 AM

To:

Cc:

Subject: RE: MOPU-1101-L Post Tender Query #1



Hi



Please find attached D/B data sheets.



I have also attached Battery Charger data sheet, the sheets that were sent with the tender are
completed but filled out in the wrong column.



Also attached is the pricing schedule.



As yet I have not received any data sheets for the rooms from either supplier and I have been
advised I should see the sheets next Tuesday.



I am sorry if this causes any inconveniences.



Best Regards



 





From:

Sent: 08 Jnanuary, 2009 3:41 PM




1









 





To:

Cc:

Subject: MOPU-1101-L Post Tender Query #1



Dear Sir,



To assist us in accessing your tender, could you please provide us with the following files in
native (Excel) format.




Switchroom Datasheets (Brice and James Engineering)

Distribution Board Datasheets

Completed Battery Charger Datasheets

Pricing Schedule



We appreciate your attention to this matter at your earliest
convenience.



Regards,




Administrative Assistant — Purchasing

Lihir Services Australia Pty Ltd

GPO Box 905, Brisbane QLD 4001

Level 9, 500 Queen St, Brisbane QLD 4000




T:

E:




CONFIDENTIALITY CAUTION AND DISCLAIMER



This
message is intended only for the use of the individual or entity to
which it is addressed and contains information that is privileged and confidential. If the reader of this message is not the
intended recipient, or the employee or agent responsible for delivering the message to the intended
recipient, you are hereby notified that any dissemination, distribution or copying of this
communication is strictly prohibited. If you have received this communication in error, please
notify us immediately at (61-7) 3318 3300 and delete the original message. If you are the intended
recipient of this message, we remind you that electronic mail on the Internet may not be secure and
that this message was not and future messages will not be encrypted or otherwise protected, unless
specifically requested, in which case, special arrangements will be made.





2












 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply
(Unit)	 	Supply	 	Install
(Unit)	 	Install	 	Total
	 	 	 	 	 	 	 	 	MOTOR CONTROL CENTRES

 (includes installation of free

 issued VSD/Soft Str)
	 	 	 	 	 	 	 	 	 	 	 	 
	 	1314	 	 	MC2001A
	 	SS2001
	 	Primary Crushing MCC A

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1314	 	 	MC2001B
	 	SS2001
	 	Primary Crushing MCC B

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1315	 	 	MC2051
	 	SS2051
	 	Primary Conveyor MCC

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1316	 	 	MC2101
	 	SS2101
	 	Ore Stockpile MCC

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1825	 	 	MC2160
	 	SS2160
	 	wurtol Pumping Station MCC

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1326	 	 	MC2201A
	 	SS2200
	 	Grinding & Classification MCC A

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1326	 	 	MC2201B
	 	SS2200
	 	Grinding & Classification MCC B

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	MC2401A
	 	SS2400
	 	Pressure Oxidation MCC A

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	MC2401B
	 	SS2400
	 	Pressure Oxidation MCC B

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	MC2401C
	 	SS2400
	 	Pressure Oxidation MCC C

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	MC2401D
	 	SS2400
	 	Pressure Oxidation MCC D

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1351	 	 	MC2551A
	 	SS2551
	 	Cyanidation & Adsorption MCC A

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1351	 	 	MC2551B
	 	 SS2551
	 	Cyanidation & Adsorption MCC B

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1560	 	 	MC2561A
	 	SS2560
	 	Oxygen Plant MCC A

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1560	 	 	MC2561B
	 	SS2560
	 	Oxygen Plant MCC B

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1341	 	 	MC2741
	 	SS2741
	 	Grinding Thickeners MCC

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1830	 	 	MC2850
	 	SS2850
	 	Process Seawater MCC

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	MC2931
	 	SS2931
	 	Bus E Auxilliary MCC

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	MC2932
	 	SS2932
	 	Bus F Auxilliary MCC

	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	Total Price MCCs
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	SWITCHROOMS (James Engineering)
	 	 	 	 	 	 	 	 	 	 	 	 
	 	1314	 	 	SS2001A
	 	 SS2001
	 	Primary Crushing LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1314	 	 	SS2001B
	 	SS2001
	 	Primary Crushing HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1315	 	 	SS2051
	 	SS2051
	 	Primary Conveying LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1316	 	 	SS2101
	 	SS2101
	 	Ore Stockpile LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1825	 	 	SS2160
	 	SS2160
	 	Wurtol Pumping Station LV Switchroom
	 	1	 	 	 	 	 	 	 	 	 	 
	 	1326	 	 	SS2200A
	 	SS2200
	 	Grinding Area LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1326	 	 	SS2200B
	 	 SS2200
	 	Grinding Area HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	SS2400A
	 	 SS2400
	 	Pressure Oxidation LV Switchroom
	 	1	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	SS2400B
	 	SS2400
	 	Pressure Oxidation HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1351	 	 	SS2551A
	 	SS2551
	 	Cyanidation & Adsorption LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1351	 	 	SS2551B
	 	SS2551
	 	Cyanidation & Adsorption HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1560	 	 	SS2560A
	 	SS2560
	 	Oxygen Plant LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1560	 	 	SS2560B
	 	SS2560
	 	Oxygen Plant HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1341	 	 	SS2741
	 	SS2741
	 	Grinding Thickeners LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1830	 	 	SS2850
	 	SS2850
	 	Process Seawater LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2931A
	 	SS2931
	 	Bus C3, C4 & E LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2931B
	 	SS2931
	 	Bus C3 & C4 HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2931C
	 	 SS2931
	 	Bus E HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2932A
	 	SS2932
	 	Bus F LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2932B
	 	SS2932
	 	Bus F HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	VESDA Systems
	 	 	 	 	 	 	 	 	 	 	 	 
	 	1314	 	 	SS2001A
	 	SS2001
	 	Primary Crushing LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1314	 	 	SS2001B
	 	SS2001
	 	Primary Crushing HV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1315	 	 	SS2051
	 	SS2051
	 	Primary Conveying LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 






 









 






	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	 	1316	 	 	SS2101
	 	SS2101
	 	Ore Stockpile LV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1825	 	 	SS2160
	 	SS2160
	 	Wurtol Pumping Station LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1326	 	 	SS2200A
	 	SS2200
	 	Grinding Area LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1326	 	 	SS2200B
	 	SS2200
	 	Grinding Area HV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	SS2400A
	 	SS2400
	 	Pressure Oxidation LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	SS2400B
	 	SS2400
	 	Pressure Oxidation HV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1351	 	 	SS2551A
	 	SS2551
	 	Cyanidation & Adsorption LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1351	 	 	SS2551B
	 	SS2551
	 	Cyanidation & Adsorption HV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1560	 	 	SS2560A
	 	SS2560
	 	Oxygen Plant LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1560	 	 	SS2560B
	 	SS2560
	 	Oxygen Plant HV Switchroom VESDA System
	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1341	 	 	SS2741
	 	SS2741
	 	Grinding Thickeners LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1830	 	 	SS2850
	 	SS2850
	 	Process Seawater LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2931A
	 	SS2931
	 	Bus C3, C4 & E LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2931B
	 	SS2931
	 	Bus C3 & C4 HV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2931C
	 	SS2931
	 	Bus E HV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2932A
	 	SS2932
	 	Bus F LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2932B
	 	SS2932
	 	Bus F HV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	Total Price Switchrooms from James Engineering
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	SWITCHROOMS (Brice Engineers)
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	1314	 	 	SS2001A
	 	SS2001
	 	Primary Crushing LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1314	 	 	SS2001B
	 	SS2001
	 	Primary Crushing HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1315	 	 	SS2051
	 	SS2051
	 	Primary Conveying LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1316	 	 	SS2101
	 	SS2101
	 	Ore Stockpile LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1825	 	 	SS2160
	 	SS2160
	 	Wurtol Pumping Station LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1326	 	 	SS2200A
	 	SS2200
	 	Grinding Area LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1326	 	 	SS2200B
	 	SS2200
	 	Grinding Area HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	SS2400A
	 	SS2400
	 	Pressure Oxidation LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	SS2400B
	 	SS2400
	 	Pressure Oxidation HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1351	 	 	SS2551A
	 	SS2551
	 	Cyanidation & Adsorption LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1351	 	 	SS2551B
	 	SS2551
	 	Cyanidation & Adsorption HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1560	 	 	SS2560A
	 	SS2560
	 	Oxygen Plant LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1560	 	 	SS2560B
	 	SS2560
	 	Oxygen Plant HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1341	 	 	SS2741
	 	SS2741
	 	Grinding Thickeners LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1830	 	 	SS2850
	 	SS2850
	 	Process Seawater LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2931A
	 	SS2931
	 	Bus C3, C4 & E LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2931B
	 	SS2931
	 	Bus C3 & C4 HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2931C
	 	SS2931
	 	Bus E HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2932A
	 	SS2932
	 	Bus F LV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	SS2932B
	 	SS2932
	 	Bus F HV Switchroom

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	VESDA Systems
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	1314	 	 	SS2001A
	 	SS2001
	 	Primary Crushing LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1314	 	 	SS2001B
	 	SS2001
	 	Primary Crushing HV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1315	 	 	SS2051
	 	SS2051
	 	Primary Conveying LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1316	 	 	SS2101
	 	SS2101
	 	Ore Stockpile LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1825	 	 	SS2160
	 	SS2160
	 	Wurtol Pumping Station LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 
	 	1326	 	 	SS2200A
	 	SS2200
	 	Grinding Ara LV Switchroom VESDA System

	 	1	 	 	 	 	 	 	 	 	 	 	 	 







 











 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1326

	 	SS2200B
	 	SS2200
	 	Grinding Area HV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	SS2400A
	 	SS2400
	 	Pressure Oxidation LV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1343

	 	SS2400B
	 	SS2400
	 	Pressure Oxidation HV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	SS2551A
	 	SS2551
	 	Cyanidation & Adsorption LV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1351

	 	SS2551B
	 	SS2551
	 	Cyanidation & Adsorption HV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	SS2560A
	 	SS2560
	 	Oxygen Plant LV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1560

	 	SS2560B
	 	SS2560
	 	Oxygen Plant HV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1341

	 	SS2741
	 	SS2741
	 	Grinding Thickeners LV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1830

	 	SS2850
	 	SS2850
	 	Process Seawater LV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931A
	 	SS2931
	 	Bus C3, C4 & E LV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931B
	 	SS2931
	 	Bus C3 & C4 HV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2931C
	 	SS2931
	 	Bus E HV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2932A
	 	SS2932
	 	Bus F LV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1780

	 	SS2932B
	 	SS2932
	 	Bus F HV Switchroom VESDA System
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Total Price Switchrooms from
Brice Engineers	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	DISTRIBUTION BOARDS (Chassis and
Panel Only)	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	DB2001A
	 	SS2001
	 	Primary Crushing LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A,
20kA/0.2s, IP42
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	DB2001B
	 	SS2001
	 	Primary Crushing HV Switchroom Light & Power Distribution Board 36 pole, 415V,
250A, 20kA/0.2s, IP42
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	DB2001C
	 	SS200l
	 	Primary Crushing UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	DB2001D
	 	SS2001
	 	Primary Crushing Area Distribution Board 72pole, 415V, 250A, 20kA/0.2s, IP42 with
Lighting Control Section
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1315

	 	DB2051A
	 	SS2051
	 	Primary Conveying LV Switchroom Light & Power Distribution Board 36 pole, 415V,
250A, 20kA/0.2s, IP42
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1315

	 	DB2051B
	 	SS2051
	 	Primary Conveying UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1315

	 	DB2051C
	 	SS2051
	 	Primary Conveying Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with
Lighting Control Section
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1316

	 	DB2101A
	 	SS2101
	 	Ore Stockpile LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A,
20kA/0.2s, IP42
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1316

	 	DB2101B
	 	SS2101
	 	Ore Stockpile UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s IP42
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1316

	 	DB2101C
	 	SS2101
	 	Ore Stockpile Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with
Lighting Control Section
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1825

	 	DB2160A
	 	SS2160
	 	Wurtol Pumping Station LV Switchroom Light & Power Distribution Board 36 pole,
415V, 250A, 20kA/0.2s, IP42
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1825

	 	DB2160B
	 	SS2160
	 	Wurtol Pumping Station UPS
Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1825

	 	DB2160C
	 	SS2160
	 	Wurtol Pumping Station Area
Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42
with Lighting Control Section
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326

	 	DB2201A
	 	SS2201
	 	Grinding LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A,
20kA/0.2s, IP42
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326

	 	DB2201B
	 	SS2201
	 	Grinding HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A,
20kA/0.2s, IP42
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326

	 	DB2201C
	 	SS2201
	 	Grinding Area UPS Distribution
Board 24 pole 240V, 160A, 20kA/0.2s, IP42
	 	 	1	 	 	 	 	 	 	 	 	 	 	 
	1326

	 	DB2201D
	 	SS2201
	 	Grinding Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting
Control Section
	 	 	1	 	 	 	 	 	 	 	 	 	 	 



















 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	 	1343	 	 	DB2401A
	 	SS2401
	 	Pressure Oxidation LV Switchroom Light & Power Distribution Board 36 pole, 415V,250A, 20kA/0.2s, IP42

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	DB2401B
	 	SS2401
	 	Pressure Oxidation HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	DB2401C
	 	SS2401
	 	Pressure Oxidation UPS Distribution Board 24 pole, 240V,160A, 20kA/0.2s,IP42

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1343	 	 	DB2401D
	 	SS2401
	 	Pressure Oxidation Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1351	 	 	DB2551A
	 	SS2551
	 	Cyanidation & Adsorption LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1351	 	 	DB2551B
	 	SS2551
	 	Cyanidation & Adsorption HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s

	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	1351	 	 	DB2551C
	 	SS2551
	 	Cyanidation & Adsorption UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1351	 	 	DB2551D
	 	SS2551
	 	Cyanidation & Adsorption Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1560	 	 	DB2561A
	 	SS2560
	 	Oxygen Plant LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1560	 	 	DB2561B
	 	SS2560
	 	Oxygen Plant HV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1560	 	 	DB2561C
	 	SS2560
	 	Oxygen Plant UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1560	 	 	DB2561D
	 	SS2560
	 	Oxygen Plant Area Distribution Board 72 pole,415v,250A,
20kA/0.2s, IP42 with Lighting Control Section

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1341	 	 	DB2741A
	 	SS2741
	 	Grinding Thickeners LV Switchroom Light & Power Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1341	 	 	DB2741B
	 	SS2741
	 	Grinding Thickeners UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1341	 	 	DB2741C
	 	SS2741
	 	Grinding Thickeners Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1830	 	 	DB2850A
	 	SS2850
	 	Process Seawater LV Switchroom Light & Power Distribution Board 36 pole, 415V,250A, 20kA/0.2s, IP42

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1830	 	 	DB2850B
	 	SS2850
	 	Process Seawater Area Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	DB2931A
	 	SS2931
	 	Bus C3, C4 & E Light & Power Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	DB2931B
	 	SS2931
	 	Bus C3, C4 & E UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	DB2932A
	 	SS2932
	 	Bus F Light & Power Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1780	 	 	DB2932B
	 	SS2932
	 	Bus F UPS Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42

	 	1	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	PC Sum for Fitout of DB’s with Circuit Breakers

	 	PC
	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	Total Price Distribution Boards
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	UNINTERRUPTIBLE POWER SUPPLIES
	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	1314	 	 	UP2001
	 	SS2001
	 	Primary Crushing LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out

	 	1	 	 	 	 	 	 	 	 	 	 
	 	1315	 	 	UP2051
	 	SS2051
	 	Primary Conveying LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out

	 	1	 	 	 	 	 	 	 	 	 	 




















 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	Supply	 	Install (Unit)	 	Install	 	Total
	1316

	 	UP2101
	 	SS2101
	 	Ore Stockpile LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1825

	 	UP2160
	 	SS2160
	 	Wurtol Pumping Station LV
Switchroom UPS 8kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1326

	 	UP2201
	 	SS2200
	 	Grinding Area LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1343

	 	UP2401
	 	SS2400
	 	Pressure Oxidation LV Switchroom
UPS 12kVA, 415V three phase in,240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1351

	 	UP2551
	 	SS2551
	 	Cyanidation & Absorption LV
Switchroom UPS 12kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1560

	 	UP2561
	 	SS2560
	 	Oxygen Plant LV Switchroom UPS 12kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1341

	 	UP2741
	 	SS2741
	 	Grinding Thickeners LV Switchroom
UPS 8kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1780

	 	UP2931
	 	SS2931
	 	Bus
C3, C4 & E LV Switchroom UPS 8kVA, 415V three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	1780

	 	UP2932
	 	SS2932
	 	Bus F LV Switchroom UPS 8kVA 415V
three phase in, 240V single phase out
	 	1	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Total Price UPS	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Control Panels	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	CP2001A
	 	SS2001
	 	Primary Crushing LV Switchroom DCS Panel A
	 	1	 	 	 	 	 	 	 	 	 	 
	1314

	 	CP2001B
	 	SS2001
	 	Primary Crushing LV Switchroom DCS Panel B
	 	1	 	 	 	 	 	 	 	 	 	 
	1315

	 	CP2051
	 	SS2051
	 	Primary Conveying LV Switchroom DCS Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1316

	 	CP2101
	 	SS2101
	 	Ore Stockpile LV Switchroom DCS Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1326

	 	CP2201A
	 	SS2200
	 	Grinding Area LV Switchroom DCS Panel A
	 	1	 	 	 	 	 	 	 	 	 	 
	1326

	 	CP2201B
	 	SS2200
	 	Grinding Area LV Switchroom DCS Panel B
	 	1	 	 	 	 	 	 	 	 	 	 
	1343

	 	CP2401A
	 	SS2400
	 	Pressure Oxidation LV Switchroom DCS Panel A
	 	1	 	 	 	 	 	 	 	 	 	 
	1343

	 	CP2401B
	 	SS2400
	 	Pressure Oxidation LV Switchroom DCS Panel B
	 	1	 	 	 	 	 	 	 	 	 	 
	1351

	 	CP2551A
	 	SS2551
	 	Cyanidation & Absorption LV Switchroom DCS Panel A
	 	1	 	 	 	 	 	 	 	 	 	 
	1351

	 	CP2551B
	 	SS2551
	 	Cyanidation & Absorption LV Switchroom DCS Panel B
	 	1	 	 	 	 	 	 	 	 	 	 
	1560

	 	CP2560A
	 	SS2560
	 	Oxygen plant LV Switchroom DCS Panel A
	 	1	 	 	 	 	 	 	 	 	 	 
	1560

	 	CP2560B
	 	SS2560
	 	Oxygen Plant LV Switchroom DCS Panel B
	 	1	 	 	 	 	 	 	 	 	 	 
	1341

	 	CP2741
	 	SS2741
	 	Grinding Thickeners LV Switchroom DCS Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1825

	 	CP2160
	 	SS2160
	 	Wurtol Pumping Station LV Switchroom PLC Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1780

	 	CP2931A
	 	SS2931
	 	Bus C3, C4 & E HV Switchroom PLC Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1780

	 	CP2932A
	 	SS2932
	 	Bus F HV Switchroom PLC Panel
	 	1	 	 	 	 	 	 	 	 	 	 
	1560

	 	CP2603
	 	SS2560
	 	PC Sum for Installation of Oxygen Plant Hardwired Emergency Trip Panel
	 	PC
	 	 	 	 	 	 	 	 	 	 
	1830

	 	CP2850
	 	SS2850
	 	PC Sum for Installation of Process Seawater LV Switchroom Control Panel
	 	PC
	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	PC Sum for Internal Marshalling of 13 DCS Panels
	 	PC
	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	PC Sum for Cabling of 18 Panels Within Switchrooms
	 	PC
	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	PC Sum for Installation of 19” RM FOBOTs in LV Switchrooms
	 	PC
	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	Total Price Control Panels	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 

	 	 	 	 	 	BATTERY CHARGER SYSTEMS	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1314

	 	BC2000
	 	SS2001
	 	Primary Crushing HV Switchroom 48VDC, 70Ahr
	 	1	 	 	 	 	 	 	 	 	 	 
	1326

	 	BC2200
	 	SS2200
	 	Grinding Area HV Switchroom 48VDC, 70Ahr
	 	1	 	 	 	 	 	 	 	 	 	 
	1343

	 	BC2400
	 	SS2400
	 	Pressure Oxidation HV Switchroom 48VDC, 70Ahr
	 	1	 	 	 	 	 	 	 	 	 	 




















 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	Supply (Unit)	 	 	Supply	 	 	Install (Unit)	 	 	Install	 	 	Total	 
	1351	 	BC2550	 	SS2551	 	Cyanidation & Absorption HV Switchroom 48VDC, 70Ahr
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1560	 	BC2560	 	SS2560	 	Oxygen Plant HV Switchroom 48VDC, 160Ahr
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780	 	BC2900	 	SS2931	 	Bus C3 & C4 HV Switchroom 48VDC, 160Ahr
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780	 	BC2931	 	SS2931	 	Bus E HV Switchroom 48VDC, 230Ahr
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780	 	BC2932	 	SS2932	 	Bus F HV Switchroom 48VDC, 230Ahr
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price Battery Charger Systems
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	HV SWITCHBOARDS
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	SW2000	 	SS2001	 	Primary Crushing 11kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	SW2001	 	SS2001	 	HGO Crusher 3.3kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1326	 	SW2200	 	SS2200	 	Grinding Area 11kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	SW2400	 	SS2400	 	Pressure Oxidation 11kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1351	 	SW2550	 	SS2551	 	Cyanidation & Absorption 11kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1560	 	SW2560	 	SS2560	 	Oxygen Plant 11kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780	 	SW2900	 	SS2931	 	Bus C3 & C4 11kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780	 	SW2931	 	SS2931	 	Bus E 33kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780	 	SW2932	 	SS2932	 	Bus F 33kV Switchboard
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price HV Switchboards
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	HV REMOTE SWITCHING PANELS
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	CP2000	 	SS2001	 	Primary Crushing 11kV & 3.3kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1326	 	CP2200	 	SS2200	 	Grinding Area 11kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	CP2400	 	SS2400	 	Pressure Oxidation 11kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1351	 	CP2550	 	SS2551	 	Cyanidation & Absorption 11kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1560	 	CP2560	 	SS2560	 	Oxygen Plant 11kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780	 	CP2900	 	SS2931	 	Bus C3 & C4 11kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780	 	CP2900A	 	SS2931	 	Bus C3 & C4 11kV Tariff Metering Panel
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780	 	CP2931	 	SS2931	 	Bus E 33kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1780	 	CP2932	 	SS2932	 	Bus F 33kV Remote Switching Panel
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	PC Sum for Cabling of 9 Panels Within Switchrooms
	 	PC	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price HV Remote Switching Panels
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	FLOOR MOUNTED VSDs
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1314	 	FD2001	 	SS2001	 	Primary Apron Feeder VSD 315kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1315	 	FD2003	 	SS2101	 	HGO Apron Feeder No.1 VSD 55kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1315	 	FD2004	 	SS2101	 	HGO Apron Feeder No.2 VSD 55kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1315	 	FD2005	 	SS2101	 	HGO Emergency Apron Feeder VSD 55kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1825	 	PU2161	 	SS2160	 	Wurtol Raw Water Pump No.1 VSD 600kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1825	 	PU2162	 	SS2160	 	Wurtol Raw Water Pump No.2 VSD 600kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1825	 	PU2163	 	SS2160	 	Wurtol Raw Water Pump No.3 VSD 600kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2030	 	SS2200	 	Pre-oxidation Feed Pump No.1 VSD 185kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2031	 	SS2200	 	Pre-oxidation Feed Pump No.2 VSD 185kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2040	 	SS2200	 	Cyclone Overflow Transfer Pump No.1 VSD 400kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2041	 	SS2200	 	Cyclone Overflow Transfer Pump No.2 VSD 400kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2042	 	SS2200	 	Cyclone Overflow Transfer Pump No.3 VSD 400kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2043	 	SS2200	 	Cyclone Overflow Transfer Pump No.4 VSD 400kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1326	 	PU2021	 	SS2200	 	Cyclone Feed Pump No.1 VSD 525kW
	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 






 









 






	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	 	Supply (Unit)	 	 	Supply	 	 	Install (Unit)	 	 	Install	 	 	Total	 
	1326	 	PU2022	 	SS2200	 	Cyclone Feed Pump No.2 VSD 525kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	PU2741	 	SS2400	 	Autoclave Feed Booster Pump VSD 185KW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	AG2245	 	SS2400	 	Autoclave No.4 Compartments 3-6 Agitator VSD 200kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	PU2123	 	SS2400	 	Flashed Slurry Forwarding Pump No.1 VSD 200kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	PU2124	 	SS2400	 	Flashed Slurry Forwarding Pump No.2 VSD 200kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	PU2125	 	SS2400	 	Flashed Slurry Forwarding Pump No.3 VSD 200kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	AG2241	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400KW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	AG2242	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400KW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	AG2243	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400KW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	AG2244	 	SS2400	 	Autoclave No.4 Compartments 1A-1C Agitator VSD 400KW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	PU2033	 	SS2400	 	Autoclave Feed Pump No.1 VSD 600kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1343	 	PU2034	 	SS2400	 	Autoclave Feed Pump No.2 VSD 600kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1351	 	PU2105	 	SS2551	 	Lime Recirculation Pump VSD 30kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1351	 	PU2058	 	SS2551	 	Leach Trash Screen Feed Pump VSD 110kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1351	 	PU2212	 	SS2551	 	CIL Tails Pump No.1 VSD 315kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1351	 	PU2213	 	SS2551	 	CIL Tails Pump No.2 VSD 315kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1560	 	P440A	 	SS2560	 	LOX Process Pump A VSD 150kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1560	 	P440B	 	SS2560	 	LOX Process Pump B VSD 150kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1341	 	PU2026	 	SS2741	 	Grinding Thickener No.1 U/F Pump No.1 VSD 75kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1341	 	PU2027	 	SS2741	 	Grinding Thickener No.1 U/F Pump No.2 VSD 75kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1341	 	PU2028	 	SS2741	 	Grinding Thickener No.2 U/F Pump No.1 VSD 525kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	1341	 	PU2029	 	SS2741	 	Grinding Thickener No.2 U/F Pump No.2 VSD 525kW
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price VSDs
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	LOCAL CONTROL STATIONS (Supply price for each even if quantity is 0)
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-01	 	 	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <30kW)
	 	 	174	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-02	 	 	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <55kW)
	 	 	5	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-03	 	 	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <90kW)
	 	 	14	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-04	 	 	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <185kW)
	 	 	13	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-05	 	 	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors <30kW)
	 	 	6	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-06	 	 	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors <55kW)
	 	 	7	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-07	 	 	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors <90kW)
	 	 	2	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-08	 	 	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors <185kW)
	 	 	7	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-09	 	 	 	Local control station with start pushbutton, emergency stop button and labels (no isolator)
	 	 	21	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-10	 	 	 	Local control station with start pushbutton, stop pushbutton, emergency stop button and labels (no isolator)
	 	 	25	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-11	 	 	 	Local control station with forward pushbutton, reverse pushbutton, emergency stop button and labels (no isolator)
	 	 	2	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 






 









 





	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	Area	 	Tag No.	 	Location	 	Description	 	Quantity	 	 	Supply (Unit)	 	 	Supply	 	 	Install (Unit)	 	 	Install	 	 	Total	 
	 	 	LCS-12	 	 	 	80 amp, 3 pole isolator only
	 	 	19	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-13	 	 	 	125 amp, 3 pole isolator only
	 	 	2	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-14	 	 	 	200 amp, 3 pole isolator only
	 	 	0	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-15	 	 	 	400 amp, 3 pole isolator only
	 	 	0	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-16	 	 	 	80 amp, 6 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <30kW)
	 	 	0	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-17	 	 	 	80 amp, 6 pole isolator, reverse, lock-off emergency stop, start pushbutton and labels (DOL motors <30kW)
	 	 	0	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-18	 	 	 	Local control station with 32 amp decontactor, 2 pilot pins, start pushbutton, emergency slop button and labels (include male decontactor)
	 	 	7	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-19	 	 	 	Local control station with 63 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)
	 	 	34	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-20	 	 	 	Local control station with 125 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)
	 	 	3	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-21	 	 	 	Local control station with 200 amp decontactor, 4 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)
	 	 	2	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-CONV	 	 	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton, larger box, extra terminals and labels
	 	 	3	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-SLEW	 	 	 	80 amp, 3 pole isolator, reverse, lock-off emergency stop, start pushbutton and labels (DOL motors <30kW)
	 	 	0	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	LCS-ES	 	 	 	Lock-off emergency stop pushbutton only
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Price Local Control Stations
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Drawings and Documentation
	 	Lot	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Packaging
	 	Lot	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Lifting Equipment
	 	Lot	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Inland Freight to Port
	 	Lot	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total Drawings / Packaging / Transport
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total MCC & Switchrooms (without Options)
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	RECOMMENDED OPTIONS
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	1	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	 
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	 	 	 	 	Total MCC & Switchrooms (with Options)
	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 






 









 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule




SCHEDULE OF PRICES

VARIATIONS FOR ADDITIONS AND DELETIONS for MCC DOL STARTERS




	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	Price
	1.1	 	0.37kW DOL	 	1 x 0.37kW DOL Starter
	 	1	 	 
	1.2	 	0.55kW DOL	 	1 x 0.55kW DOL Starter
	 	1	 	 
	1.3	 	1.1kWDOL	 	1 x 1.1kW DOL Starter
	 	1	 	 
	1.4	 	1.5kW DOL	 	1 x1.5kW DOL Starter
	 	1	 	 
	1.5	 	2.2kW DOL	 	1 x 2.2kW DOL Starter
	 	1	 	 
	1.6	 	3kW DOL	 	1 x 3kW DOL Starter
	 	1	 	 
	1.7	 	4kW DOL	 	1 x 4kW DOL Starter
	 	1	 	 
	1.8	 	5.5kW DOL	 	1 x 5.5kW DOL Starter
	 	1	 	 
	1.9	 	7.5kW DOL	 	1 x 7.5kW DOL Starter
	 	1	 	 
	1.10	 	11kW DOL	 	1 x 11kW DOL Starter
	 	1	 	 
	1,11	 	15kW DOL	 	1 x 15kW DOL Starter
	 	1	 	 
	1.12	 	18.5kW DOL	 	1 x 18.5kW DOL Starter
	 	1	 	 
	1.13	 	22kW DOL	 	1 x 22kW DOL Starter
	 	1	 	 
	1.14	 	30kW DOL	 	1 x 30kW DOL Starter
	 	1	 	 
	1.15	 	37kW DOL	 	1 x 37kW DOL Starter
	 	1	 	 
	1.16	 	45kW DOL	 	1 x 45kW DOL Starter
	 	1	 	 
	1.17	 	55kW DOL	 	1 x 55kW DOL Starter
	 	1	 	 
	1.18	 	75kW DOL	 	1 x 75kW DOL Starter
	 	1	 	 
	1.19	 	90kW DOL	 	1 x 90kW DOL Starter
	 	1	 	 
	1.20	 	110kW DOL	 	1 x 110kW DOL Starter
	 	1	 	 
	1.21	 	132kW DOL	 	1 x 132kW DOL Starter
	 	1	 	 
	1.22	 	150kW DOL	 	1 x 150kW DOL Starter
	 	1	 	 
	1.23	 	185kW DOL	 	1 x 185kW DOL Starter
	 	1	 	 
	1.24	 	200kW DOL	 	1 x 200kW DOL Starter
	 	1	 	 
	1.25	 	220kW DOL	 	1 x 220kW DOL Starter
	 	1	 	 
	1.26	 	250kW DOL	 	1 x 250kW DOL Starter
	 	1	 	 
	1.27	 	280kW DOL	 	1 x 280kW DOL Starter
	 	1	 	 
	1.28	 	315kW DOL	 	1 x 315kW DOL Starter
	 	1	 	 
	1.29	 	355kW DOL	 	1 x 355kW DOL Starter
	 	1	 	 
	1.30	 	400kW DOL	 	1 x 400kW DOL Starter
	 	1	 	 
	1.31	 	450kW DOL	 	1 x 450kW DOL Starter
	 	1	 	 
	1.32	 	500kW DOL	 	1 x 500kW DOL Starter
	 	1	 	 
	1.33	 	560kW DOL	 	1 x 560kW DOL Starter
	 	1	 	 
	1.34	 	630kW DOL	 	1 x 630kW DOL Starter
	 	1	 	 






VARIATIONS FOR ADDITIONS AND DELETIONS for MCC VSD MODULES

Installation Only. All VSDs are free issued.




	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	 
	2.1	 	0.55kW VSD	 	1 x 0.55kW VSD Starter
	 	1	 	 
	2.2	 	1.1kW VSD	 	1 x 1.1kW VSD Starter
	 	1	 	 
	2.3	 	1.5kW VSD	 	1 x 1.5kW VSD Starter
	 	1	 	 
	2.4	 	2.2kW VSD	 	1 x 2.2kW VSD Starter
	 	1	 	 
	2.5	 	3.7kW VSD	 	1 x 3.7kW VSD Starter
	 	1	 	 
	2.6	 	5.5kW VSD	 	1 x 5.5kW VSD Starter
	 	1	 	 
	2.7	 	7.5kW VSD	 	1 x 7.5kW VSD Starter
	 	1	 	 
	2.8	 	11kW VSD	 	1 x 11kW VSD Starter
	 	1	 	 
	2.9	 	15kW VSD	 	1 x15kW VSD Starter
	 	1	 	 
	2.10	 	18.5kW VSD	 	1 x 18.5kW VSD Starter
	 	1	 	 
	2.11	 	22kW VSD	 	1 x 22kW VSD Starter
	 	1	 	 
	2.12	 	30kW VSD	 	1 x 30kW VSD Starter
	 	1	 	 
	2.13	 	37kW VSD	 	1 x 37kW VSD Starter
	 	1	 	 
	2.14	 	45kW VSD	 	1 x 45kW VSD Starter
	 	1	 	 
	2.15	 	55kW VSD	 	1 x 55kW VSD Starter
	 	1	 	 




Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 9 of 15 Pages


 









 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule




	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	Price
	2.16	 	75kW VSD	 	1 x 75kW VSD Starter
	 	1	 	 
	2.17	 	90kW VSD	 	1 x 90kW VSD Starter
	 	1	 	 
	2.18	 	110kW VSD	 	1 x 110kW VSD Starter
	 	1	 	 
	2.19	 	132kW VSD	 	1 x 132kW VSD Starter
	 	1	 	 
	2.20	 	150kW VSD	 	1 x150kW VSD Starter
	 	1	 	 
	2.21	 	185kW VSD	 	1 x 185kW VSD Starter
	 	1	 	 
	2.22	 	220kW VSD	 	1 x 220kW VSD Starter
	 	1	 	 
	2.23	 	280kW VSD	 	1 x 280kW VSD Starter
	 	1	 	 
	2.24	 	315kW VSD	 	1 x 315kW VSD Starter
	 	1	 	 
	2.25	 	355kW VSD	 	1 x 355kW VSD Starter
	 	1	 	 
	2.26	 	400kW VSD	 	1 x 400kW VSD Starter
	 	1	 	 
	2.27	 	450kW VSD	 	1 x 450kW VSD Starter
	 	1	 	 
	2.28	 	500kW VSD	 	1 x 500kW VSD Starter
	 	1	 	 
	2.29	 	630kW VSD	 	1 x 630kW VSD Starter
	 	1	 	 






VARIATIONS FOR ADDITIONS AND DELETIONS for MCC SOFT STARTER MODULES

Installation Only. All soft starters are free issued.




	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	 
	3.1	 	132kW SSD	 	1 x 132kW Soft Starter
	 	1	 	 
	3.2	 	150kW SSD	 	1 x 150kW Soft Starter
	 	1	 	 
	3.3	 	160kW SSD	 	1 x 160kW Soft Starter
	 	1	 	 
	3.4	 	185kW SSD	 	1 x 185kW Soft Starter
	 	1	 	 
	3.5	 	220kW SSD	 	1 x 220kW Soft Starter
	 	1	 	 
	3.6	 	250kW SSD	 	1 x 250kW Soft Starter
	 	1	 	 
	3.7	 	280kW SSD	 	1 x 280kW Soft Starter
	 	1	 	 
	3.8	 	315kW SSD	 	1 x 315kW Soft Starter
	 	1	 	 
	3.9	 	355kW SSD	 	1 x 355kW Soft Starter
	 	1	 	 
	3.10	 	400kW SSD	 	1 x 400kW Soft Starter
	 	1	 	 
	3.11	 	450kW SSD	 	1 x 450kW Soft Starter
	 	1	 	 
	3.12	 	500kW SSD	 	1 x 500kW Soft Starter
	 	1	 	 
	3.13	 	630kW SSD	 	1 x 630kW Soft Starter
	 	1	 	 






VARIATIONS FOR ADDITIONS AND DELETIONS for MCC FEEDER/INCOMER MODULES




	 	 	 	 	 	 	 	 	 
	Item No.	 	Module Type	 	Module Description	 	Qty	 	 
	4,1	 	40 F	 	1 x 40 Amp Circuit Breaker Feeder Module
	 	1	 	 
	4.2	 	63 F	 	1 x 63 Amp Circuit Breaker Feeder Module
	 	1	 	 
	4.3	 	100 F	 	1 x 100 Amp Circuit Breaker Feeder Module
	 	1	 	 
	4.4	 	160 F	 	1 x 160 Amp Circuit Breaker Feeder Module
	 	L	 	 
	4.5	 	200 F	 	1 x 200 Amp Circuit Breaker Feeder Module
	 	1	 	 
	4.6	 	250 F	 	1 x 250 Amp Circuit Breaker Feeder Module
	 	1	 	 
	4.7	 	400 F	 	1 x 400 Amp Circuit Breaker Feeder Module
	 	1	 	 
	4.8	 	630 F	 	1 x 630 Amp Circuit Breaker Feeder Module
	 	1	 	 
	4.9	 	1250 F	 	1 x 1250 Amp Circuit Breaker Feeder Module
	 	1	 	 
	4.10	 	40 F/C	 	1 x 40 Amp Circuit Breaker Feeder/Contactor Module
	 	1	 	 
	4.11	 	63 F/C	 	1 x 63 Amp Circuit Breaker Feeder/Contactor Module
	 	1	 	 
	4.12	 	100 F/C	 	1 x 100 Amp Circuit Breaker Feeder/Contactor Module
	 	1	 	 
	4.13	 	160 F/C	 	1 x 160 Amp Circuit Breaker Feeder/Contactor Module
	 	1	 	 
	4.14	 	200 F/C	 	1 x 200 Amp Circuit Breaker Feeder/Contactor Module
	 	1	 	 
	4.15	 	250 F/C	 	1 x 250 Amp Circuit Breaker Feeder/Contactor Module
	 	1	 	 
	4.16	 	400 F/C	 	1 x 400 Amp Circuit Breaker Feeder/Contactor Module
	 	1	 	 
	4.17	 	630 F/C	 	1 x 630 Amp Circuit Breaker Feeder/Contactor Module
	 	1	 	 
	4.18	 	1250 F/C	 	1 x 1250 Amp Circuit Breaker Feeder/Contactor Module
	 	1	 	 
	4.15	 	800 IC	 	1 x 800 Amp Air Circuit Breaker Incomer
	 	1	 	 
	4.16	 	1600 IC	 	1 x 1600 Amp Air Circuit Breaker Incomer
	 	1	 	 
	4.17	 	3200 IC	 	1 x 3200 Amp Air Circuit Breaker Incomer
	 	1	 	 
	4.18	 	4000 IC	 	1 x 4000 Amp Air Circuit Breaker Incomer
	 	1	 	 




Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 10 of 15 Pages


 









 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule




VARIATIONS FOR ADDITIONS AND DELETIONS for LCS TYPES




	 	 	 	 	 	 	 	 	 
	Item No.	 	LCS Type	 	Description	 	Qty	 	Price
	5.1	 	LCS-1	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <30kW)
	 	1	 	 
	5.2	 	LCS-2	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <55kW)
	 	1	 	 
	5.3	 	LCS-3	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <90kW)
	 	1	 	 
	5.4	 	LCS-4	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <185kW)
	 	1	 	 
	5.5	 	LCS-5	 	80 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors <30kW)
	 	1	 	 
	5.6	 	LCS-6	 	125 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors <55kW)
	 	1	 	 
	5.7	 	LCS-7	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors <90kW)
	 	1	 	 
	5.8	 	LCS-8	 	400 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton and labels (VSD motors <185kW)
	 	1	 	 
	5.9	 	LCS-9	 	Local control station with start pushbutton, emergency stop button and labels (no isolator)
	 	1	 	 
	5.10	 	LCS-10	 	Local control station with start pushbutton, stop pushbutton, emergency stop button and labels (no isolator)
	 	1	 	 
	5.11	 	LCS-11	 	Local control station with forward pushbutton, reverse pushbutton, emergency stop button and labels (no isolator)
	 	1	 	 
	5.12	 	LCS-12	 	80 amp, 3 pole isolator only
	 	1	 	 
	5.13	 	LCS-13	 	125 amp, 3 pole isolator only
	 	1	 	 
	5.14	 	LCS-14	 	200 amp, 3 pole isolator only
	 	1	 	 
	5.15	 	LCS-15	 	400 amp, 3 pole isolator only
	 	1	 	 
	5.16	 	LCS-16	 	80 amp, 6 pole isolator, lock-off emergency stop, start pushbutton and labels (DOL motors <30kW)
	 	1	 	 
	5.17	 	LCS-17	 	80 amp, 6 pole isolator, reverse, lock-off emergency stop, start pushbutton and labels (DOL motors <30kW)
	 	1	 	 
	5.18	 	LCS-18	 	Local control station with 32 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)
	 	1	 	 
	5.19	 	LCS-19	 	Local control station with 63 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)
	 	1	 	 
	5.20	 	LCS-20	 	Local control station with 125 amp decontactor, 2 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)
	 	1	 	 
	5,21	 	LCS-21	 	Local control station with 200 amp decontactor, 4 pilot pins, start pushbutton, emergency stop button and labels (include male decontactor)
	 	1	 	 
	5.22	 	LCS-CONV	 	200 amp, 3 pole isolator, lock-off emergency stop, start pushbutton, stop pushbutton, larger box, extra terminals and labels
	 	1	 	 
	5.23	 	LCS-SLEW	 	80 amp, 3 pole isolator, reverse, lock-off emergency stop, start pushbutton and labels (DOL motors <30kW)
	 	1	 	 
	5.24	 	LCS-ES	 	Lock-off emergency stop pushbutton only
	 	1	 	 





 Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 11 of 15 Pages

 









 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule




VARIATIONS FOR DISTRIBUTION BOARDS




	 	 	 	 	 	 	 	 	 
	Item No.	 	 	 	Description	 	Qty	 	Price
	6.1	 	 	 	Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42 with Lighting Control Section
	 	1	 	 
	6.2	 	 	 	Distribution Board 72 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 
	6.3	 	 	 	Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42
	 	1	 	 
	6.4	 	 	 	Distribution Board 36 pole, 415V, 250A, 20kA/0.2s, IP42, with Lighting Control Section
	 	1	 	 
	6.5	 	 	 	Distribution Board 24 pole, 240V, 160A, 20kA/0.2s, IP42
	 	1	 	 
	6.6	 	 	 	Install one single pole, 10 amp circuit breaker
	 	1	 	 
	6.7	 	 	 	Install one single pole, 16 amp circuit breaker
	 	1	 	 
	6.8	 	 	 	Install one single pole, 10 amp circuit breaker with 30mA earth leakage
	 	1	 	 
	6.9	 	 	 	Install one single pole, 16 amp circuit breaker with 30mA earth leakage
	 	1	 	 
	6.10	 	 	 	Install one single pole, 10 amp circuit breaker with 100mA earth leakage
	 	1	 	 
	6.11	 	 	 	Install one single pole, 16 amp circuit breaker with 100mA earth leakage
	 	1	 	 
	6.12	 	 	 	Install one three pole, 16 amp circuit breaker
	 	1	 	 
	6.13	 	 	 	Install one three pole, 16 amp circuit breaker with 30mA earth leakage
	 	1	 	 
	6.14	 	 	 	Install one three pole, 16 amp circuit breaker with 300mA earth leakage
	 	1	 	 
	6.15	 	 	 	Install one three pole, 20 amp circuit breaker
	 	1	 	 
	6.16	 	 	 	Install one three pole, 20 amp circuit breaker with 30mA earth leakage
	 	 	 	 
	6.17	 	 	 	Install one three pole, 20 amp circuit breaker with 100mA earth leakage
	 	 	 	 
	6.18	 	 	 	Install one three pole, 32 amp circuit breaker
	 	 	 	 
	6.19	 	 	 	Install one three pole, 32 amp circuit breaker with 30mA earth leakage
	 	 	 	 
	6.20	 	 	 	Install one three pole, 32 amp circuit breaker with 100mA earth leakage
	 	 	 	 
	6.21	 	 	 	Install one three pole, 63 amp circuit breaker
	 	 	 	 
	6.22	 	 	 	Install one three pole, 63 amp circuit breaker with 30mA earth leakage
	 	 	 	 
	6.23	 	 	 	Install one three pole, 63 amp circuit breaker with 100mA earth leakage
	 	 	 	 






OPTIONAL PRICING FOR SWITCHROOM GAS SUPPRESSION SYSTEM




	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	 
	7.1	 	James Engineering	 	Gas Suppression System, Primary Crushing LV Switch room
	 	1	 	 
	7.2	 	James Engineering	 	Gas Suppression System, Primary Crushing HV Switch room
	 	1	 	 
	7.3	 	James Engineering	 	Gas Suppression System, Primary Conveying LV Switch room
	 	1	 	 
	7.4	 	James Engineering	 	Gas Suppression System, Ore Stockpile LV Switchroom
	 	1	 	 
	7.5	 	James Engineering	 	Gas Suppression System, Wurtol Pumping Station LV Switchroom
	 	1	 	 






Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 12 of 15 Pages


 









 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule




	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	Price
	7.6	 	James Engineering	 	Gas Suppression System, Grinding LV Switchroom
	 	1	 	  
	7.7	 	James Engineering	 	Gas Suppression System, Grinding HV Switchroom
	 	1	 	 
	7.8	 	James Engineering	 	Gas Suppression System, Pressure Oxidation LV Switchroom
	 	1	 	 
	7.9	 	James Engineering	 	Gas Suppression System, Pressure Oxidation HV Switchroom
	 	1	 	 
	7.10	 	James Engineering	 	Gas Suppression System, Cyanidation & Adsorption LV Switchroom
	 	1	 	 
	7.11	 	James Engineering	 	Gas Suppression System, Cyanidation & Adsorption HV Switchroom
	 	1	 	 
	7.12	 	James Engineering	 	Gas Suppression System, Oxygen Plant LV Switchroom
	 	1	 	 
	7.13	 	James Engineering	 	Gas Suppression System, Oxygen Plant HV Switchroom
	 	1	 	 
	7.14	 	James Engineering	 	Gas Suppression System, Grinding Thickeners LV Switchroom
	 	1	 	 
	7.15	 	James Engineering	 	Gas Suppression System, Process Seawater LV Switchroom
	 	1	 	 
	7.16	 	James Engineering	 	Gas Suppression System, Bus C3, C4 & E LV Switchroom
	 	1	 	 
	7.17	 	James Engineering	 	Gas Suppression System, Bus C3 & C4 HV Switchroom
	 	1	 	 
	7.18	 	James Engineering	 	Gas Suppression System, Bus E HV Switchroom
	 	1	 	 
	7.19	 	James Engineering	 	Gas Suppression System, Bus F LV Switchroom
	 	1	 	 
	7.20	 	James Engineering	 	Gas Suppression System, Bus F HV Switchroom
	 	1	 	 
	7.21	 	Brice Engineers	 	Gas Suppression System, Primary Crushing LV Switchroom
	 	1	 	 
	7.22	 	Brice Engineers	 	Gas Suppression System, Primary Crushing HV Switchroom
	 	1	 	 
	7.23	 	Brice Engineers	 	Gas Suppression System, Primary Conveying LV Switchroom
	 	1	 	 
	7.24	 	Brice Engineers	 	Gas Suppression System, Ore Stockpile LV Switchroom
	 	1	 	 
	7.25	 	Brice Engineers	 	Gas Suppression System, Wurtol Pumping Station LV Switchroom
	 	1	 	 
	7.26	 	Brice Engineers	 	Gas Suppression System, Grinding LV Switchroom
	 	1	 	 
	7.27	 	Brice Engineers	 	Gas Suppression System, Grinding HV Switchroom
	 	1	 	 
	7.28	 	Brice Engineers	 	Gas Suppression System, Pressure Oxidation LV Switchroom
	 	1	 	 
	7.29	 	Brice Engineers	 	Gas Suppression System, Pressure Oxidation HV Switchroom
	 	1	 	 
	7.30	 	Brice Engineers	 	Gas Suppression System, Cyanidation & Adsorption LV Switchroom
	 	1	 	 
	7.31	 	Brice Engineers	 	Gas Suppression System, Cyanidation & Adsorption HV Switchroom
	 	1	 	 
	7.32	 	Brice Engineers	 	Gas Suppression System, Oxygen Plant LV Switchroom
	 	1	 	 
	7.33	 	Brice Engineers	 	Gas Suppression System, Oxygen Plant HV Switchroom
	 	1	 	 
	7.34	 	Brice Engineers	 	Gas Suppression System, Grinding Thickeners LV Switchroom
	 	1	 	 
	7.35	 	Brice Engineers	 	Gas Suppression System, Process Seawater LV Switchroom
	 	1	 	 
	7.36	 	Brice Engineers	 	Gas Suppression System, Bus C3, C4 & E LV Switchroom
	 	1	 	 
	7.37	 	Brice Engineers	 	Gas Suppression System, Bus C3 & C4 HV Switchroom
	 	1	 	 






Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 13 of 15 Pages

 









 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule




	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	Price
	7.38	 	Brice Engineers	 	Gas Suppression System, Bus E HV Switchroom
	 	1	 	 
	7.39	 	Brice Engineers	 	Gas Suppression System, Bus F LV Switchroom
	 	1	 	 
	7.40	 	Brice Engineers	 	Gas Suppression System, Bus F HV Switchroom
	 	1	 	 






OPTIONAL PRICING FOR 2 HOUR FIRE RATING OF SWITCHROOM WALLS

For Wall Adjacent to (or Floor Above) Transformers.




	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	Price
	8.1	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Primary Crushing LV Switchroom
	 	1	 	 
	8.2	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Primary Crushing HV Switchroom
	 	1	 	 
	8.3	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Primary Conveying LV Switchroom
	 	1	 	 
	8.4	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Ore Stockpile LV Switchroom
	 	1	 	 
	8.5	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Wurtol Pumping Station LV Switchroom
	 	1	 	 
	8.6	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Grinding LV Switchroom
	 	1	 	 
	8.7	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Grinding HV Switchroom
	 	1	 	 
	8.8	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Pressure Oxidation LV Switchroom
	 	1	 	 
	8.9	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Pressure Oxidation HV Switchroom
	 	1	 	 
	8.10	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Cyanidation & Adsorption LV Switchroom
	 	1	 	 
	8.11	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Cyanidation & Adsorption HV Switchroom
	 	1	 	 
	8.12	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Oxygen Plant LV Switchroom
	 	1	 	 
	8.13	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Oxygen Plant HV Switchroom
	 	1	 	 
	8.14	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Grinding Thickener LV Switchroom
	 	1	 	 
	8.15	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Process Seawater LV Switchroom
	 	1	 	 
	8.16	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Bus C3, C4 & E LV Switchroom
	 	1	 	 
	8.17	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Bus C3 & C4 HV Switchroom
	 	1	 	 
	8.18	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Bus E HV Switchroom
	 	1	 	 
	8.19	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Bus F LV Switchroom
	 	1	 	 
	8.20	 	James Engineering	 	Two (2) hour fire rating of Switchroom Walls, Bus F HV Switchroom
	 	1	 	 
	8.21	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Primary Crushing LV Switchroom
	 	1	 	 
	8.22	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Primary Crushing HV Switchroom
	 	1	 	 
	8.23	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Primary Conveying LV Switchroom
	 	1	 	 
	8.24	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Primary Conveying & Ore Stockpile LV Switchroom
	 	1	 	 
	8.25	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Wurtol Pumping Station LV Switchroom
	 	1	 	 





Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 14 of 15 Pages


 









 





LIHIR MOPU Project

MOPU-1101 MCCs and Switchrooms

Variations Pricing Schedule




	 	 	 	 	 	 	 	 	 
	Item No.	 	Supplier	 	Description	 	Qty	 	Price
	8.26	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Grinding LV Switchroom
	 	1	 	 
	8.27	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Grinding HV Switchroom
	 	1	 	 
	8.28	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Pressure Oxidation LV Switchroom
	 	1	 	 
	8.29	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Pressure Oxidation HV Switchroom
	 	1	 	 
	8.30	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Cyanidation & Adsorption LV Switchroom
	 	1	 	 
	8.31	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Cyanidation & Adsorption HV Switchroom
	 	1	 	 
	8.32	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Oxygen Plant LV Switchroom
	 	1	 	 
	8.33	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Oxygen Plant HV Switchroom
	 	1	 	 
	8.34	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Grinding Thickeners LV Switchroom
	 	1	 	 
	8.35	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Process Seawater LV Switchroom
	 	1	 	 
	8.36	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus C3, C4 & E LV Switchroom
	 	1	 	 
	8.37	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus C3 & C4 HV Switchroom
	 	1	 	 
	8.38	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus E HV Switchroom
	 	1	 	 
	8.39	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus F LV Switchroom
	 	1	 	 
	8.40	 	Brice Engineers	 	Two (2) hour fire rating of Switchroom Walls, Bus F HV Switchroom
	 	1	 	 




Variations Pricing_Rev 00
Q 4929 — NHP — MOPU-1101_Pricing Schedules Page 15 of 15 Pages


 









 





	 	 	 
	From:
	 	 
	Sent:

	 	Friday, 30 January 2009 8:30 AM
	To:

	 	MOPU_11
	Subject:

	 	RE: MOPU-1101-L Post Tender Technical Query
	Attachments:

	 	MOPU-1101_02 Technical Query Plummers.doc; Copy of Revised MOPU-1101_UPS
Datasheet.xls; Rubber Matting.xls






Hi




Please find attached answers as per our meeting.




If you have any other queries, do not hesitate to call.




Best Regards.







Plummers Industries

+  Postal: 75, Wolston Road Sumner Park QLD 4074

(  Tel:

2  Fax:

*  E-mail:




From:          [mailto:          ]

Sent: 22 January, 2009 9:32 AM

To:

Cc: mopu_0801@lglgold.com;

Subject: MOPU-1101-L Post Tender Technical Query




Dear Sir,




Please find attached post tender technical query for your information and action.




Please submit your response at our meeting on 28 January 2009.




Regards,




Lihir Services Australia Pty Ltd

GPO Box 905, Brisbane QLD 4001

Level 9, 500 Queen St, Brisbane QLD 4000

T:

F:

E:




1









 





			
		 	 
	BEC Engineering Pty Ltd
	 	TECHNICAL QUERY






	 	 	 	 	 	 	 
	PROJECT:

	 	LIHIR MOPU PROJECT
	 	TQ No:
	 	1101-02
	CLIENT:

	 	LIHIR SERVICES AUSTRALIA PTY LTD
	 	Date Raised:
	 	20/01/2009
	JOB NO:

	 	8062 
	 	Response Req’d:
	 	28/01/2009
	 
	 	 	 	 	 	 
	 

	 	 
	 	 	 	 
	ATTENTION:

	 	Plummers -	 	 	 	 
	SUBJECT:

	 	TQ for package MOPU-1101 LV MCCs and Switchrooms
	 	 	 	 
	REFERENCE DOCS:
	 	 	 	 	 	 
	 	 	 





TECHNICAL QUERY









MCC





	 	1.	 	No PCS marshalling tier will be included in these MCCs. Terminals will be
installed in the cable zone of each tier. If the 500 terminals per MCC specified in the datasheets
is in addition to those terminals then please provide a cost impact of removing them from the
offer. Please delete per MCC
	 
	 	2.	 	Specify the rated power frequency insulation, BIL voltages and
temperatures for the MCCs offered. As per data sheets
	 
	 	3.	 	Specify the neutral busbar current ratings offered. As per data sheets
	 
	 	4.	 	Specify the total transport sizes for the MCCs offered. As per data sheets
	 
	 	5.	 	Complete the data sheet entries for CVTs, SMPS and specify the class of
CTs offered. As per data sheets
	 
	 	6.	 	Confirm all MCC incomer ratings and model numbers. Some appear to be
in error. As per data sheets
	 
	 	7.	 	Confirm that when coordination charts can be obtained from Moeller, that
type 2 coordination will be achieved at no cost impact. Cant confirm, Moeller do not have a type 2
chart in any of their manuals or test certificate as proof. Plummers contacted Moeller in Brisbane
and confirmed they do not have one.





UPS





	 	8.	 	64 x 12V/7Ah batteries were specified for the 8KVA UPS, to provide 30 minutes backup
time at full load (as per table found at
http://www.powerware.com.au/australia/ups/9155_specs.asp#battery%20cabinets). Your offer of 96 x
12V/7Ah provides excessive backup time (presumably at increased cost). Please review your choice
and consider providing the battery configuration specified and adjusting pricing
accordingly. Please delete per 8kVA UPS
	 
	 	9.	 	The total transport size for the UPS units is less than the size of the
batteries. Please review and adjust accordingly. See new data sheets
	 
	 	10.	 	According to the manufacturers data (see








Page 1 of 1









 





			
		 	 
	BEC Engineering Pty Ltd
	 	TECHNICAL QUERY











	 	 	http://www.powerware.com.au/australia/ups/9155_specs.asp#battery%20cabinets), the
total weight of the UPS and 2 battery units (each 32 x 12V/7Ah) should be approximately
265kg. Please review and confirm your quoted weights. See revised attached data sheets





Distribution Board





	 	11.	 	Confirm that CIRLOCK lockouts will be provided on Distribution Boards and
provide details for the DB door lock type and CB earth leakage settings.






	 	 	A No Circlock has been allowed for add pole. (QTY yet to be determined) E/L as required.






	 	12.	 	Confirm that the 36 and 72 pole DBs will have a busbar rating of 250A/415V and a
250A isolator. Confirmed





Battery Charger





	 	13.	 	Confirm whether the Battery Chargers can have Modbus TCP communications and state any
cost impact. Already Included
	 
	 	14.	 	Confirm that the Battery Chargers will have contacts available for external signals
and specify the number. Yes, Alarm card included — 6 x voltage free contacts user
programmable
	 
	 	15.	 	Specify the panel and plinth materials for the Battery Chargers. Cubicle is 2mm
steel and Base is 100 x 50 x 5mm channel Sides only
	 
	 	16.	 	Confirm the dimensions and weights of the Battery Chargers.





	 	 	 	 	 	 	 
	 

	 	BC70AHR
	 	750W x 750D x 1205
	 	160kgs
	 

	 	BC160AHR
	 	750W x 750D x 1605
	 	300kgs
	 

	 	BC230AHR
	 	750W x 750D x 1605
	 	420kgs






Switchroom





	 	17.	 	Where is ex-factory for the Brice Engineers Switchrooms? Brice Engineers have
confirmed they will lease suitable workshop facilities in Townsville, this will provide
adequate room for building trades to work on switchrooms progressively. Brice eng revised
pricing will include the facility costs.
	 
	 	18.	 	If the above location is different to Brisbane, please provide installation costs for
installing equipment in the Brice Engineers Switchrooms. To be forwarded with Brices
revised pricing.
	 
	 	19.	 	Confirm that Switchroom earth bars have been included in James Engineering’s offer.
Included already
	 
	 	20.	 	Confirm that LV rescue kits Yes, rubber mats NO and cupboards Yes have been
included in James Engineering’s offer. If not, please state the cost impact of including
them. Desks and chairs YES. See attached mat pricing.
	 
	 	21.	 	Confirm the number of A/C supply cables and isolator switches installed in each Switchroom
in James Engineering’s offer. It appears that 6 of each have been allowed








Page 1 of 1









 





			
		 	 
	BEC Engineering Pty Ltd
	 	TECHNICAL QUERY











	 	 	for, regardless of the number of A/C units. Please state any cost impact to rectify this.
Yes already included, isolators have been allowed for as per A/C quantities as per data
sheets.






	22.	 	Provide details of all subcontractors to be used by Brice Engineers.



 Electrical installation : Plummers Industries





HVAC : MVO Airconditioning




Fire Detection and Protection : Premier Fire





	 	23.	 	Provide a cost for lifting equipment from both James Engineering and Brice Engineers.
James’s for two spreader bars from James’s, does not include chains and hooks need to come from
the riggers
	 
	 	24.	 	Provide a cost for LV rescue kits, rubber mats, desks, chairs and cupboards, as
specified, from Brice Engineers. Brice will submit a revised price as soon as
possible.
	 
	 	25.	 	Provide details and cost for signage, as specified, from Brice Engineers. Brice will
submit a revised price as soon as possible.
	 
	 	26.	 	Provide details and cost for skirting, as specified, from Brice Engineers. Brice will
submit a revised price as soon as possible.
	 
	 	27.	 	Provide details and cost for cable gland boxes to be mounted below MCCs, as specified,
from Brice Engineers. Plummers already included in MCC price
	 
	 	28.	 	Provide a cost for rain hoods to be mounted above switchrooms doorways, as specified
(and drawings were issued during the tender period), from Brice Engineers. Brice will
submit a revised price as soon as possible.
	 
	 	29.	 	Provide a cost for automatic closers and panic bars to be fitted to switchroom doors,
as specified, from Brice Engineers. Brice will submit a revised price as soon as possible.
	 
	 	30.	 	Provide a cost for services design drawings from Brice Engineers. Brice will
submit a revised price as soon as possible.
	 
	 	31.	 	The cabling allowed for from the Battery Chargers to HV Panels by Brice Engineers is
inadequate. Please provide a cost impact for increasing the number of cores or cables.
Plummers will include in revised install price.
	 
	 	32.	 	Provide details of the A/C mountings by Brice Engineers, including location of units.
It appears that units may be too large to mount on the roof of some switchrooms. Brice are
reviewing design and should incorporate in new price. (conforming bid)
	 
	 	33.	 	There is conflict in the documentation from Brice Engineers about the number, type and
size of A/C units. Please confirm these details. Brice are reviewing design and should
incorporate in new price. (conforming bid)
	 
	 	34.	 	Confirm whether steel doors specified by Brice Engineers are stainless. Provide a
model/part number for the doors. Brice are reviewing design and should incorporate in new
price. (conforming bid)









Page 1 of 1











 





			
		 	 
	BEC Engineering Pty Ltd
	 	TECHNICAL QUERY 






	 	 	 
	SUBMITTED BY:

	 	SIGNED:






ANSWER



As discussed in the meeting, Plummers Industries will be doing the install work in
both cases.



An additional site cost will be incurred if installation is in Townsville



Brice Engineering must confirm if they are able to submit a fully conforming bid and confirm what
facilities they can provide.



Some free issued equipment will need to be directly sent to Brice in Townsville.



All free issue gear for James Eng offer will be shipped to and stored at Plummers Industries
facility’s in Sumner Park.




	 	 	 
	ANSWERED BY:

	 	SIGNED:






Page 1 of 1





 








 








	 	 	 	 	 	 	 
	SwitchRoom	 	Mtrs	 	$ per MTR	 	Total
	SS2000

415V mat 

11kV mat 

33kV mat

	 	 
	 	 
	 	 
	 
	 	 	 	 	 	 
	SS2051

415V mat 

11kV mat 

33kV mat
	 	 	 	 	 	 
	 
	 	 	 	 	 	 
	SS2101

415V mat 

11kV mat 

33kV mat
	 	 	 	 	 	 
	 
	 	 	 	 	 	 
	SS2160

415V mat 

11kV mat 

33kV mat
	 	 	 	 	 	 
	 
	 	 	 	 	 	 
	SS2200

415V mat 

11kV mat 

33kV mat
	 	 	 	 	 	 
	 
	 	 	 	 	 	 
	SS2400

415V mat 

11kV mat 

33kV mat
	 	 	 	 	 	 
	 
	 	 	 	 	 	 
	SS2551

415V mat 

11kV mat 

33kV mat
	 	 	 	 	 	 
	 
	 	 	 	 	 	 
	SS2560

415V mat 

11kV mat 

33kV mat
	 	 	 	 	 	 
	 
	 	 	 	 	 	 
	SS2931

415V mat 

11kV mat 

33kV mat
	 	 	 	 	 	 
	 
	 	 	 	 	 	 
	SS2932

415V mat 

11kV mat 

33kV mat
	 	 	 	 	 	 
	 
	 	 	 	 	 	 
	SS2741

415V mat
	 	 	 	 	 	 
	 
	 	 	 	 	 	 





 









 






	 	 	 	 	 	 	 
	SwitchRoom	 	Mtrs	 	$ per MTR	 	Total
	11kV mat 

33kV mat
	 	 	 	 	 	 
	 
	 	 	 	 	 	 
	SS2850

415V mat 

11kV mat 

33kV mat
	 	 	 	 	 	 
	 
	 	 	 	 	 	 
	Variation
Prices: per Meter 

415V mat 

11kV mat 

33kV mat
	 	 	 	 	 	 






 









 





	 	 	 
	From:
	 	 
	Sent:

	 	Monday, 2 March 2009 2.47 PM
	To:
	 	 
	Cc:

	 	MOPU_0801
	Subject:

	 	RE: MOPU-1101-L LV MCCs and Switchroom — Post Tender Technical Query
	Attachments:

	 	Spares.xls






Hi



Please find attached spares list.



I don’t think you will require commissioning spares as we will be testing all the equipment in our
workshop prior to delivery. If any equipment fails in this time we will be replacing from our stock
and installing before shipment.




Best Regards,




Plummers Industries

+  Postal: 75, Wolston Road Sumner Park QLD 4074

(  Tel:

2  Fax:

*  E-mail:




From:

Sent: 27 February, 2009 1:27 PM

To:

Cc: mopumailbox@lglgold.com

Subject: MOPU-1101-L LV MCCs and Switchroom — Post Tender Technical Query




Dear Sir,



Please find attached Technical Query for Tender Package No. MOPU-1101.



Could you please respond to this Query by close of business, Wednesday
4th March, 2009?



Regards,




Administrative Assistant — Purchasing

MOPU Project

Lihir Services Australia Pty Ltd

GPO Box 905, Brisbane QLD 4001

Level 9, 500 Queen St, Brisbane QLD 4000




T:

F:

E:




CONFIDENTIALITY CAUTION AND DISCLAIMER



This message is intended only for the use of the individual or entity to which it is addressed
and contains information that is privileged and confidential. If the reader of this message is not
the intended recipient, or the employee or agent responsible for delivering the message to the
intended recipient, you are hereby notified that any dissemination, distribution or copying of this
communication is strictly prohibited. If you have received this communication in error, please
notify us immediately at (61-7) 3318 3300 and delete the original message. If you are the intended
recipient of this message, we remind you that electronic mail on the Internet may not be secure and
that this message was not and future messages will not be encrypted or otherwise protected, unless
specifically requested, in which case, special arrangements will be made.






1









 








	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	Commissioning	 	Operational	 	Price
	 	 	Spares	 	Spares	 	Each
	XM30PB 1.4
	 	 	1	 	 	 	2	 	 	 	 	 
	XM30PB 2
	 	 	1	 	 	 	2	 	 	 	 	 
	XM30PB 2.6
	 	 	1	 	 	 	2	 	 	 	 	 
	XM30PB 4
	 	 	1	 	 	 	2	 	 	 	 	 
	XM30PB 5
	 	 	1	 	 	 	2	 	 	 	 	 
	XM30PB 8
	 	 	1	 	 	 	2	 	 	 	 	 
	XM30PB 10
	 	 	1	 	 	 	2	 	 	 	 	 
	XM30PB 12
	 	 	1	 	 	 	2	 	 	 	 	 
	XM30PB ST 110VAC
	 	 	1	 	 	 	2	 	 	 	 	 
	XM30PB AUX
	 	 	1	 	 	 	2	 	 	 	 	 
	S125GJ20
	 	 	1	 	 	 	2	 	 	 	 	 
	S125GJ32
	 	 	1	 	 	 	2	 	 	 	 	 
	S125GJ50
	 	 	1	 	 	 	2	 	 	 	 	 
	S125GJ63
	 	 	1	 	 	 	2	 	 	 	 	 
	S125GJ100
	 	 	1	 	 	 	2	 	 	 	 	 
	S125GJ125
	 	 	1	 	 	 	2	 	 	 	 	 
	S125 ST 110VAC
	 	 	1	 	 	 	2	 	 	 	 	 
	S125 ST AUX
	 	 	1	 	 	 	2	 	 	 	 	 
	S160GJ160
	 	 	1	 	 	 	2	 	 	 	 	 
	S250GJ250
	 	 	1	 	 	 	2	 	 	 	 	 
	S250 ST 110VAC
	 	 	1	 	 	 	2	 	 	 	 	 
	S250 AUX
	 	 	1	 	 	 	2	 	 	 	 	 
	S400GJ400
	 	 	1	 	 	 	2	 	 	 	 	 
	S400 ST 110VAC
	 	 	1	 	 	 	2	 	 	 	 	 
	S400 AUX
	 	 	1	 	 	 	2	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 
	CA7-9
	 	 	2	 	 	 	4	 	 	 	 	 
	CA7-16
	 	 	2	 	 	 	4	 	 	 	 	 
	CA7-30
	 	 	2	 	 	 	4	 	 	 	 	 
	CA7-43
	 	 	2	 	 	 	4	 	 	 	 	 
	CA7-72
	 	 	1	 	 	 	2	 	 	 	 	 
	CA7-85
	 	 	1	 	 	 	2	 	 	 	 	 
	CA6-95
	 	 	1	 	 	 	2	 	 	 	 	 
	CA6-140
	 	 	1	 	 	 	2	 	 	 	 	 
	CA6-180
	 	 	1	 	 	 	2	 	 	 	 	 
	CA6-210
	 	 	1	 	 	 	2	 	 	 	 	 
	CA6-250
	 	 	1	 	 	 	2	 	 	 	 	 
	CA6-300
	 	 	1	 	 	 	2	 	 	 	 	 
	CA6-420
	 	 	1	 	 	 	2	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 
	CEP7C3232
	 	 	1	 	 	 	2	 	 	 	 	 
	CEP7C3235
	 	 	1	 	 	 	2	 	 	 	 	 
	CEP7C32315
	 	 	1	 	 	 	2	 	 	 	 	 
	CEP7C32325
	 	 	1	 	 	 	2	 	 	 	 	 
	CEP7C34325
	 	 	1	 	 	 	2	 	 	 	 	 
	CEP7C34345
	 	 	1	 	 	 	2	 	 	 	 	 
	CEP7C38545
	 	 	1	 	 	 	2	 	 	 	 	 
	CEP7C38590
	 	 	1	 	 	 	2	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 
	CEP7CPM1
	 	 	1	 	 	 	2	 	 	 	 	 
	CEP7CPM2
	 	 	1	 	 	 	2	 	 	 	 	 
	CEP7CPM3
	 	 	1	 	 	 	2	 	 	 	 	 






 









 






	 	 	 	 	 	 	 	 	 	 	 	 	 
	 	 	Commissioning	 	Operational	 	Price
	 	 	Spares	 	Spares	 	Each
	CEP7CBCT1
	 	 	1	 	 	 	2	 	 	 	 	 
	CEP7CBCT2
	 	 	1	 	 	 	2	 	 	 	 	 
	CEP7CBCT3
	 	 	1	 	 	 	2	 	 	 	 	 
	CEP7CBCT4
	 	 	1	 	 	 	2	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 
	DTCB06204C
	 	 	5	 	 	 	5	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 
	D7P-P4-PN5R
	 	 	5	 	 	 	10	 	 	 	 	 
	D7P-P4-PN5A
	 	 	5	 	 	 	10	 	 	 	 	 
	D7P-P4-PN5W
	 	 	5	 	 	 	10	 	 	 	 	 
	D7P-P4-PN5B
	 	 	3	 	 	 	6	 	 	 	 	 
	D7P-P4-PN5G
	 	 	3	 	 	 	6	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 
	LY2N AC110
	 	 	5	 	 	 	10	 	 	 	 	 
	PTF08A-E
	 	 	10	 	 	 	20	 	 	 	 	 
	LY2N DC48
	 	 	5	 	 	 	10	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 
	ELR-2M
	 	 	2	 	 	 	5	 	 	 	 	 
	ELR-2M-F
	 	 	2	 	 	 	5	 	 	 	 	 
	CT-1/35
	 	 	1	 	 	 	2	 	 	 	 	 
	CT-1/60
	 	 	1	 	 	 	2	 	 	 	 	 
	CT-1/80
	 	 	1	 	 	 	2	 	 	 	 	 
	CT-1/110
	 	 	1	 	 	 	2	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 
	MM300
	 	 	1	 	 	 	2	 	 	 	 	 
	 
	 	 	 	 	 	 	 	 	 	 	 	 
	QUINT P/S 240/24VDC
	 	 	 	 	 	 	 	 	 	 	 	 
	 
	 	 	1	 	 	 	2