Name: Steve Haleman

Title: Day Operator

Company: ACE CoGeneration

Sign Date: 8/24/2010

Name: Stafford D. Pease

Title: Vice President

Company: Delta air Quality Services, Inc.

Sign Date: 8/24/2010

Permitted Facility Representative / Date Testing Company Representative / Date

2010 ACE Cogeneration EPA ICR Testing

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Friday, February 18, 2011 Page 1 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Facility Information:

Ace Cogeneration Facility

12801 S Mariposa Street

Trona CA 93562

Contact: Steve Haleman

Phone: 760-372-2113

Fax: 760-372-2153

Email: shaleman@ace-cogen.com

Testing Company:

Delta Air Quality Services, Inc.

1845 N. Case St

Orange CA 92865

Contact: Stafford D. Pease

Phone: 714 279 6777

Fax:

Email: Staffordpease@deltaaqs.com

Air Permit Number:

B002110

Permitted Source ID/Name:

10002 Ace Cogeneration

Permitted Maximum Process Rate:

none

Max. Normal Operation Process Rate:

48 tn/hr

Target Process Test Rate

48 tn/hr

Industry/SCC/NAIS 221112 AFS #: 06071M0202 FRS #: 110000481924

SCC / Description 10100238 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Atmospheric Fluidized Bed Combustion - Circulating Bed (Subbitum Coal)

The following state and federal regulations that apply to the proposed testing:

Regulation Description Compound Limit Unit

All the following are Section 114 Carbon Monoxide 0 lb/million BTU 

using O2

Section 114 Carbon Monoxide 0 ppm corrected

Section 114 Total organic compounds 

(TOC) as Methane

0 lb/million BTU 

using O2

section 114 Total organic compounds 

(TOC) as Methane

0 ppm corrected

section 114 O2 0 percent(%)

section 114 CO2 0 percent(%)

section 114 Formaldehyde 0 lb/million BTU 

using O2

section 114 Formaldehyde 0 ppm corrected

section 114 methane 0 lb/million BTU 

using O2

section 114 methane 0 ppm corrected

section 114 1,2,3,4,6,7,8-HpCDD 0 lb/million BTU 

using O2

section 114 1,2,3,4,6,7,8-HpCDD 0 pg/dscm corrected

section 114 1,2,3,4,6,7,8-HpCDF 0 lb/million BTU 

using O2

1,2,3,4,6,7,8-HpCDF 0 pg/dscm corrected

1,2,3,4,7,8,9-HpCDF 0 lb/million BTU 

using O2

1,2,3,4,7,8,9-HpCDF 0 pg/dscm corrected

Friday, February 18, 2011 Page 2 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

1,2,3,4,7,8-HxCDD 0 lb/million BTU 

using O2

1,2,3,4,7,8-HxCDD 0 pg/dscm corrected

1,2,3,4,7,8-HxCDF 0 lb/million BTU 

using O2

1,2,3,6,7,8-HxCDF 0 pg/dscm corrected

1,2,3,7,8,9-HxCDD 0 lb/million BTU 

using O2

1,2,3,7,8,9-HxCDD 0 pg/dscm corrected

1,2,3,7,8,9-HxCDF 0 lb/million BTU 

using O2

1,2,3,7,8,9-HxCDF 0 pg/dscm corrected

1,2,3,7,8-PeCDD 0 lb/million BTU 

using O2

1,2,3,7,8-PeCDD 0 pg/dscm corrected

1,2,3,7,8-PeCDF 0 lb/million BTU 

using O2

1,2,3,7,8-PeCDF 0 pg/dscm corrected

2,3,3',4,4',5,5'-HpCB 

(PCB189)

0 lb/million BTU 

using O2

2,3,3',4,4',5,5'-HpCB 

(PCB189)

0 pg/dscm corrected

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

0 lb/million BTU 

using O2

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

0 pg/dscm corrected

2,3',4,4',5-PeCB (PCB118) 0 lb/million BTU 

using O2

2,3',4,4',5-PeCB (PCB118) 0 pg/dscm corrected

2,3,3',4,4'-PeCB (PCB105) 0 lb/million BTU 

using O2

2,3,3',4,4'-PeCB (PCB105) 0 pg/dscm corrected

2,3',4,4',5,5'-HxCB 

(PCB167)

0 lb/million BTU 

using O2

2,3',4,4',5,5'-HxCB 

(PCB167)

0 pg/dscm corrected

2,3,4,4',5-PeCB (PCB114) 0 lb/million BTU 

using O2

2,3,4,4',5-PeCB (PCB114) 0 pg/dscm corrected

2',3,4,4',5-PeCB (PCB123) 0 lb/million BTU 

using O2

2',3,4,4',5-PeCB (PCB123) 0 pg/dscm corrected

2,3,4,6,7,8-HxCDF 0 lb/million BTU 

using O2

2,3,4,6,7,8-HxCDF 0 pg/dscm corrected

2,3,4,7,8-PeCDF 0 lb/million BTU 

using O2

2,3,4,7,8-PeCDF 0 pg/dscm corrected

2,3,7,8-TCDD 0 lb/million BTU 

using O2

2,3,7,8-TCDD 0 pg/dscm corrected

2,3,7,8-TCDF 0 lb/million BTU 

using O2

Friday, February 18, 2011 Page 3 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

2,3,7,8-TCDF 0 pg/dscm corrected

1,2,3,6,7,8-HxCDD 0 lb/million BTU 

using O2

1,2,3,6,7,8-HxCDD 0 pg/dscm corrected

3,3',4,4',5,5'-HxCB 

(PCB169)

0 lb/million BTU 

using O2

3,3',4,4',5,5'-HxCB 

(PCB169)

0 pg/dscm corrected

3,3',4,4',5-PeCB (PCB126) 0 lb/million BTU 

using O2

3,3',4,4',5-PeCB (PCB126) 0 pg/dscm corrected

3,3',4,4'-TCB (PCB77) 0 lb/million BTU 

using O2

3,3',4,4'-TCB (PCB77) 0 pg/dscm corrected

3,4,4',5-TCB (PCB81) 0 lb/million BTU 

using O2

3,4,4',5-TCB (PCB81) 0 pg/dscm corrected

OCDD 0 lb/million BTU 

using O2

OCDD 0 pg/dscm corrected

OCDF 0 lb/million BTU 

using O2

OCDF 0 pg/dscm corrected

Other HpCDD 0 lb/million BTU 

using O2

Other HpCDD 0 pg/dscm corrected

Other TCDD 0 lb/million BTU 

using O2

Other TCDD 0 pg/dscm corrected

Other PeCDD 0 lb/million BTU 

using O2

Other PeCDD 0 pg/dscm corrected

Other HxCDD 0 lb/million BTU 

using O2

Other HxCDD 0 pg/dscm corrected

Other TCDF 0 lb/million BTU 

using O2

Other TCDF 0 pg/dscm corrected

Other PeCDF 0 lb/million BTU 

using O2

Other PeCDF 0 pg/dscm corrected

Other HxCDF 0 lb/million BTU 

using O2

Other HxCDF 0 pg/dscm corrected

Other HpCDF 0 lb/million BTU 

using O2

Other HpCDF 0 pg/dscm corrected

0

Friday, February 18, 2011 Page 4 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010 Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

The ACE Cogeneration Company Plant consists of a 1052 MMBtu/hour, circulating bed, coal-fired boiler designed 

to produce 910,000 lb/hr of steam at 1525 psig and 1005°F. The unit is equipped with the following pollution 

control systems:

1.	An ammonia injection system for control of NOx emissions;

2.	Cyclonic mixing of injected ammonia with flue gas to provide for a minimum amount of ammonia slip (emission);

3.	A limestone injection system to limit emissions of SO2;

4.	A baghouse to restrict opacity and emissions of sulfates and particulate;

Sampling Location Information:

Test Parameter Information:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

stack 115 0 0 0 13 13 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

stack Custom methane 3 120 0

stack Carbon Monoxide Method 10 3 120 0

stack Formaldehyde Method 0011 3 120 0

stack 2,3,7,8-TCDD Method 23 3 480 0

stack 1,2,3,7,8-PeCDD Method 23 3 480 0

stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0

stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0

stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0

stack 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

stack OCDD Method 23 3 480 0

stack 2,3,7,8-TCDF Method 23 3 480 0

stack 1,2,3,7,8-PeCDF Method 23 3 480 0

stack 2,3,4,7,8-PeCDF Method 23 3 480 0

stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0

stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0

stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0

stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0

stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

stack OCDF Method 23 3 480 0

stack Other TCDD Method 23 3 480 0

stack Other PeCDD Method 23 3 480 0

stack Other HxCDD Method 23 3 480 0

stack Other HpCDD Method 23 3 480 0

stack Other TCDF Method 23 3 480 0

stack Other PeCDF Method 23 3 480 0

stack Other HxCDF Method 23 3 480 0

stack Other HpCDF Method 23 3 480 0

stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0

stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Friday, February 18, 2011 Page 5 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

n/a

stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

stack Method 23 3 480 0

stack 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

stack Method 23 3 480 0

Total organic compounds 

(TOC) as Methane

stack Method 25A 3 120 0

stack Co2 Method 3A CO2 3 120 0

stack O2 Method 3A O2 3 120 0

Friday, February 18, 2011 Page 6 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Sampling / Stack Data Results Summary

Location stack - Method 0011

Average

Run Number 1-Form 2-Form 3-Form

Test Date 5/11/2010 5/12/2010 5/12/2010

Run Start Time 1:26:00 PM 8:42:00 

AM

12:20:00 PM

Run Finish Time 3:32:00 PM 10:49:00 

AM

2:37:00 PM

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 81.070 87.344 82.902 83.772

Moisture Content of Stack Gas, % 6.59 6.89 6.59 6.690

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 15.95 16.02 16.17 16.047

Oxygen, % 3.87 3.95 3.85 3.890

Average Stack Gas Temperature, °F 282.33 277.75 283.83 281.303

Dry Volumetric Flow Rate, dry scfm 251,717.4 251,189.2 250,262.4 251,056.333

Actual Wet Volumetric Flue Gas Flow Rate, acfm 404,265.4 400,933.0 401,452.3 402,216.900

Percent Isokinetic of Sampling Rate, % 96.3 104.0 99.0 99.767

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Fw 10351 10189 10351 10,297.000

Fc 1800 0 0 600.000

Location stack - Method 10

Average

Run Number 1-co 2-co 3-co

Test Date 5/11/2010 5/12/2010 5/12/2010

Run Start Time 1:26:00 PM 8:42:00 

AM

12:20:00 PM

Run Finish Time 3:26:00 PM 10:42:00 

AM

2:20:00 PM

Carbon Dioxide, % 15.95 16.02 16.17 16.047

Oxygen, % 3.87 3.95 3.85 3.890

Dry Volumetric Flow Rate, dry scfm 251800 251232 250321 251,117.667

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Moisture, % 6.6 6.9 6.6 6.700

Fuel Type Override Override Override

Fw 10351 10189 10233 10,257.667

Fc 1800 1800 1800 1,800.000

Friday, February 18, 2011 Page 7 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 23

Average

Run Number 1-Dioxins 2-Dioxins 3-Dioxins

Test Date 5/11/2010 5/12/2010 5/13/2010

Run Start Time 10:30:00 AM 8:02:00 

AM

7:46:00 AM

Run Finish Time 6:04:00 PM 3:37:00 PM 3:17:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 291.487 287.920 294.120 291.176

Moisture Content of Stack Gas, % 6.84 7.13 6.66 6.877

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 15.99 16.08 15.26 15.777

Oxygen, % 3.85 3.88 3.84 3.857

Average Stack Gas Temperature, °F 279.00 277.17 282.50 279.557

Dry Volumetric Flow Rate, dry scfm 256,467.4 249,277.3 253,871.8 253,205.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 411,146.7 398,595.9 406,818.8 405,520.467

Percent Isokinetic of Sampling Rate, % 101.1 102.7 103.0 102.267

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Fw 10351 10189 10159 10,233.000

Fc 0 0 0 0.000

Location stack - Method 25A

Average

Run Number 1-voc 2-voc 3-voc

Test Date 5/11/2010 5/12/2010 5/12/2010

Run Start Time 12:26:00 PM 8:42:00 

AM

12:20:00 PM

Run Finish Time 3:26:00 PM 10:42:00 

AM

2:20:00 PM

Carbon Dioxide, % 15.95 16.02 16.17 16.047

Oxygen, % 3.87 3.95 3.85 3.890

Dry Volumetric Flow Rate, dry scfm 251800 251232 250321 251,117.667

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Moisture, % 6.6 6.9 6.6 6.700

Fuel Type Override Override Override

Fw 10351 10189 10159 10,233.000

Fc 1800 1800 1800 1,800.000

Friday, February 18, 2011 Page 8 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 3A CO2

Average

Run Number 1-CO2 2-co2 3-CO2

Test Date 5/11/2010 5/11/2010 5/11/2010

Run Start Time 10:32:00 AM 1:26:00 PM 3:38:00 PM

Run Finish Time 12:32:00 PM 3:26:00 PM 6:04:00 PM

Carbon Dioxide, % 15.99 15.95 15.99 15.977

Oxygen, % 3.85 3.87 3.85 3.857

Dry Volumetric Flow Rate, dry scfm 256297 251800 256297 254,798.000

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Moisture, % 6.9 6.6 6.9 6.800

Fuel Type Override Override Override

Fw 10351 10351 10351 10,351.000

Fc 0 1800 0 600.000

Location stack - Method 3A CO2 3

Average

Run Number 4-co2 5-co2 6-CO2

Test Date 5/12/2010 5/12/2010 5/12/2010

Run Start Time 8:42:00 AM 12:20:00 

PM

3:12:00 PM

Run Finish Time 10:42:00 AM 2:20:00 PM 4:16:00 PM

Carbon Dioxide, % 16.02 16.17 16.08 16.090

Oxygen, % 3.95 3.85 3.88 3.893

Dry Volumetric Flow Rate, dry scfm 251232 250321 249057 250,203.333

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Moisture, % 6.9 6.6 7.2 6.900

Fuel Type Override Override Override

Fw 10189 10159 10189 10,179.000

Fc 1800 1800 0 1,200.000

Friday, February 18, 2011 Page 9 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 3A CO2 3 6

Average

Run Number 7-CO2 8-CO2

Test Date 5/13/2010 5/13/2010

Run Start Time 7:52:00 AM 11:55:00 

AM

Run Finish Time 11:48:00 AM 3:51:00 PM

Carbon Dioxide, % 15.26 15.26 15.260

Oxygen, % 3.84 3.84 3.840

Dry Volumetric Flow Rate, dry scfm 253686 253686 253,686.000

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9,860.000

Moisture, % 6.7 6.7 6.700

Fuel Type Override Override

Fw 10159 10159 10,159.000

Fc 0 0 0.000

Location stack - Method 3A O2

Average

Run Number 1-o2 2-o2 3-o2

Test Date 5/11/2010 5/11/2010 5/11/2010

Run Start Time 10:32:00 AM 1:26:00 PM 3:38:00 PM

Run Finish Time 12:32:00 PM 3:26:00 PM 6:43:00 PM

Carbon Dioxide, % 15.99 15.95 15.99 15.977

Oxygen, % 3.85 3.87 3.85 3.857

Dry Volumetric Flow Rate, dry scfm 256297 251778 256297 254,790.667

F-Factor, dscfm/MMBtu @ %O2 9860 9860 0 6,573.333

Moisture, % 6.9 6.6 6.9 6.800

Fuel Type Override Override

Fw 10351 10351 0 6,900.667

Fc 1800 1800 0 1,200.000

Friday, February 18, 2011 Page 10 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 3A O2 3

Average

Run Number 4-o2 5-o2 6-O2

Test Date 5/12/2010 5/12/2010 5/12/2010

Run Start Time 8:42:00 AM 12:20:00 

PM

3:12:00 PM

Run Finish Time 10:42:00 AM 2:20:00 PM 4:16:00 PM

Carbon Dioxide, % 16.02 16.17 16.08 16.090

Oxygen, % 3.95 3.85 3.88 3.893

Dry Volumetric Flow Rate, dry scfm 251232 250321 249057 250,203.333

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Moisture, % 6.9 6.6 7.2 6.900

Fuel Type Override Override Override

Fw 10189 10159 10189 10,179.000

Fc 1800 1800 0 1,200.000

Location stack - Method 3A O2 3 6

Average

Run Number 7-O2 8-O2

Test Date 5/13/2010 5/13/2010

Run Start Time 7:52:00 AM 11:55:00 

AM

Run Finish Time 11:48:00 AM 3:51:00 PM

Carbon Dioxide, % 15.26 15.26 15.260

Oxygen, % 3.84 3.84 3.840

Dry Volumetric Flow Rate, dry scfm 243686 253686 248,686.000

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9,860.000

Moisture, % 6.7 6.7 6.700

Fuel Type Override Override

Fw 10159 10159 10,159.000

Fc 0 0 0.000

Friday, February 18, 2011 Page 11 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Emissions Summary

Location: stack - Method 0011

Compound: Formaldehyde

Average

RunNumber 1-Form 2-Form 3-Form

Mass_mg 0.00565 0.00677 0.0063 0.006

lb/mmBtuO2 1.86E-06 2.08E-06 2.02E-06 0.000

ppm 1.97E-03 2.19E-03 2.15E-03 0.002

ppm@7%O2 1.61E-03 1.80E-03 1.75E-03 0.002

Location: stack - Method 10

Compound: Carbon Monoxide

Average

Run 1-co 2-co 3-co

lb/mmBtuO2 4.12E-02 3.86E-02 3.26E-02 0.037

ppm 4.69E+01 4.37E+01 3.71E+01 42.567

ppm@7%O2 3.83E+01 3.58E+01 3.02E+01 34.767

Location: stack - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000457 0.0000000072 0.00000000599 0.000

lb/mmBtuO2 4.18E-13 6.68E-13 5.42E-13 0.000

pg/dscm 5.54E-01 8.83E-01 7.19E-01 0.719

pg/dscm@7%O2 4.52E-01 7.21E-01 5.86E-01 0.586

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000447 0.0000000051 0.00000000466 0.000

lb/mmBtuO2 4.09E-13 4.73E-13 4.22E-13 0.000

pg/dscm 5.42E-01 6.26E-01 5.60E-01 0.576

pg/dscm@7%O2 4.42E-01 5.11E-01 4.56E-01 0.470

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000146 0.00000000238 0.00000000286 0.000

lb/mmBtuO2 1.33E-13 2.21E-13 2.59E-13 0.000

pg/dscm 1.77E-01 2.92E-01 3.43E-01 0.271

pg/dscm@7%O2 1.44E-01 2.38E-01 2.79E-01 0.220

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000109 0.00000000214 0.00000000208 0.000

lb/mmBtuO2 9.96E-14 1.98E-13 1.88E-13 0.000

pg/dscm 1.32E-01 2.63E-01 2.50E-01 0.215

pg/dscm@7%O2 1.08E-01 2.15E-01 2.04E-01 0.176

Friday, February 18, 2011 Page 12 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000577 0.00000000451 0.00000000279 0.000

lb/mmBtuO2 5.27E-13 4.18E-13 2.53E-13 0.000

pg/dscm 6.99E-01 5.53E-01 3.35E-01 0.529

pg/dscm@7%O2 5.70E-01 4.52E-01 2.73E-01 0.432

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000148 0.00000000199 0.000000002 0.000

lb/mmBtuO2 1.35E-13 1.84E-13 1.81E-13 0.000

pg/dscm 1.79E-01 2.44E-01 2.40E-01 0.221

pg/dscm@7%O2 1.46E-01 1.99E-01 1.96E-01 0.180

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000589 0.00000000409 0.00000000271 0.000

lb/mmBtuO2 5.38E-13 3.79E-13 2.45E-13 0.000

pg/dscm 7.14E-01 5.02E-01 3.25E-01 0.514

pg/dscm@7%O2 5.82E-01 4.10E-01 2.65E-01 0.419

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000241 0.00000000242 0.00000000215 0.000

lb/mmBtuO2 2.20E-13 2.24E-13 1.95E-13 0.000

pg/dscm 2.92E-01 2.97E-01 2.58E-01 0.282

pg/dscm@7%O2 2.38E-01 2.43E-01 2.10E-01 0.230

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000145 0.00000000139 0.00000000172 0.000

lb/mmBtuO2 1.33E-13 1.29E-13 1.56E-13 0.000

pg/dscm 1.76E-01 1.71E-01 2.07E-01 0.185

pg/dscm@7%O2 1.43E-01 1.40E-01 1.69E-01 0.151

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000279 0.00000000192 0.000000002 0.000

lb/mmBtuO2 2.55E-13 1.78E-13 1.81E-13 0.000

pg/dscm 3.38E-01 2.36E-01 2.40E-01 0.271

pg/dscm@7%O2 2.76E-01 1.93E-01 1.96E-01 0.222

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.0000000117 0.0000000109 0.00000000466 0.000

lb/mmBtuO2 1.07E-12 1.01E-12 4.22E-13 0.000

Friday, February 18, 2011 Page 13 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

pg/dscm 1.42E+00 1.34E+00 5.60E-01 1.107

pg/dscm@7%O2 1.16E+00 1.09E+00 4.56E-01 0.902

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000554 0.0000000136 0.00000000512 0.000

lb/mmBtuO2 5.06E-13 1.26E-12 4.64E-13 0.000

pg/dscm 6.71E-01 1.67E+00 6.15E-01 0.985

pg/dscm@7%O2 5.47E-01 1.36E+00 5.01E-01 0.803

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000003102 0.0000001306 0.0000000498 0.000

lb/mmBtuO2 2.84E-12 1.21E-11 4.51E-12 0.000

pg/dscm 3.76E+00 1.60E+01 5.98E+00 8.580

pg/dscm@7%O2 3.07E+00 1.31E+01 4.87E+00 7.013

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.0000000528 0.000000198 0.000000104 0.000

lb/mmBtuO2 4.83E-12 1.84E-11 9.42E-12 0.000

pg/dscm 6.40E+00 2.43E+01 1.25E+01 14.400

pg/dscm@7%O2 5.22E+00 1.98E+01 1.02E+01 11.740

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.0000000111 0.0000000491 0.0000000185 0.000

lb/mmBtuO2 1.01E-12 4.55E-12 1.68E-12 0.000

pg/dscm 1.35E+00 6.02E+00 2.22E+00 3.197

pg/dscm@7%O2 1.10E+00 4.92E+00 1.81E+00 2.610

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000349 0.0000000114 0.00000000749 0.000

lb/mmBtuO2 3.19E-13 1.06E-12 6.78E-13 0.000

pg/dscm 4.23E-01 1.40E+00 8.99E-01 0.907

pg/dscm@7%O2 3.45E-01 1.14E+00 7.32E-01 0.739

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.000000121 0.000000447 0.000000229 0.000

lb/mmBtuO2 1.11E-11 4.14E-11 2.07E-11 0.000

pg/dscm 1.47E+01 5.48E+01 2.75E+01 32.333

pg/dscm@7%O2 1.20E+01 4.48E+01 2.24E+01 26.400

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Friday, February 18, 2011 Page 14 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Mass_mg 0.00000000638 0.0000000129 0.00000000716 0.000

lb/mmBtuO2 5.83E-13 1.20E-12 6.48E-13 0.000

pg/dscm 7.73E-01 1.58E+00 8.60E-01 1.071

pg/dscm@7%O2 6.30E-01 1.29E+00 7.01E-01 0.874

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000472 0.00000000309 0.00000000176 0.000

lb/mmBtuO2 4.31E-13 2.86E-13 1.59E-13 0.000

pg/dscm 5.72E-01 3.79E-01 2.11E-01 0.387

pg/dscm@7%O2 4.66E-01 3.10E-01 1.72E-01 0.316

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.0000000171 0.0000000115 0.00000000495 0.000

lb/mmBtuO2 1.56E-12 1.07E-12 4.48E-13 0.000

pg/dscm 2.07E+00 1.41E+00 5.94E-01 1.358

pg/dscm@7%O2 1.69E+00 1.15E+00 4.84E-01 1.108

Compound: 2,3,7,8-TCDD

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000148 0.00000000122 0.00000000124 0.000

lb/mmBtuO2 1.35E-13 1.13E-13 1.12E-13 0.000

pg/dscm 1.79E-01 1.50E-01 1.49E-01 0.159

pg/dscm@7%O2 1.46E-01 1.23E-01 1.21E-01 0.130

Compound: 2,3,7,8-TCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.0000000209 0.0000000242 0.00000000879 0.000

lb/mmBtuO2 1.91E-12 2.24E-12 7.96E-13 0.000

pg/dscm 2.53E+00 2.97E+00 1.06E+00 2.187

pg/dscm@7%O2 2.06E+00 2.43E+00 8.64E-01 1.785

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000364 0.00000000351 0.00000000392 0.000

lb/mmBtuO2 3.33E-13 3.25E-13 3.55E-13 0.000

pg/dscm 4.41E-01 4.31E-01 4.71E-01 0.448

pg/dscm@7%O2 3.60E-01 3.52E-01 3.84E-01 0.365

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000918 0.0000000122 0.00000000585 0.000

lb/mmBtuO2 8.39E-13 1.13E-12 5.30E-13 0.000

pg/dscm 1.11E+00 1.50E+00 7.03E-01 1.104

pg/dscm@7%O2 9.05E-01 1.23E+00 5.73E-01 0.903

Friday, February 18, 2011 Page 15 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.0000000264 0.0000000433 0.0000000344 0.000

lb/mmBtuO2 2.41E-12 4.01E-12 3.11E-12 0.000

pg/dscm 3.20E+00 5.31E+00 4.13E+00 4.213

pg/dscm@7%O2 2.61E+00 4.34E+00 3.37E+00 3.440

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000416 0.0000000111 0.00000000462 0.000

lb/mmBtuO2 3.80E-13 1.03E-12 4.18E-13 0.000

pg/dscm 5.04E-01 1.36E+00 5.55E-01 0.806

pg/dscm@7%O2 4.11E-01 1.11E+00 4.52E-01 0.658

Compound: OCDD

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.0000000107 0.0000000159 0.0000000187 0.000

lb/mmBtuO2 9.78E-13 1.47E-12 1.69E-12 0.000

pg/dscm 1.30E+00 1.95E+00 2.25E+00 1.833

pg/dscm@7%O2 1.06E+00 1.59E+00 1.83E+00 1.493

Compound: OCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000363 0.00000000673 0.00000000758 0.000

lb/mmBtuO2 3.32E-13 6.24E-13 6.86E-13 0.000

pg/dscm 4.40E-01 8.26E-01 9.10E-01 0.725

pg/dscm@7%O2 3.59E-01 6.75E-01 7.41E-01 0.592

Compound: Other HpCDD

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.00000000452 0.00000000832 0.00000000761 0.000

lb/mmBtuO2 4.13E-13 7.71E-13 6.89E-13 0.000

pg/dscm 5.48E-01 1.02E+00 9.14E-01 0.827

pg/dscm@7%O2 4.47E-01 8.33E-01 7.45E-01 0.675

Compound: Other HpCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

pg/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

pg/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.0000000113 0.0000000181 0.00000000643 0.000

lb/mmBtuO2 1.03E-12 1.68E-12 5.82E-13 0.000

Friday, February 18, 2011 Page 16 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Process Run Data

pg/dscm 1.37E+00 2.22E+00 7.72E-01 1.454

pg/dscm@7%O2 1.12E+00 1.81E+00 6.29E-01 1.186

Compound: Other HxCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.0000000236 0.0000000184 0.00000000994 0.000

lb/mmBtuO2 2.16E-12 1.71E-12 9.00E-13 0.000

pg/dscm 2.86E+00 2.26E+00 1.19E+00 2.103

pg/dscm@7%O2 2.33E+00 1.85E+00 9.70E-01 1.717

Compound: Other PeCDD

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.000000021 0.0000000153 0.00000000766 0.000

lb/mmBtuO2 1.92E-12 1.42E-12 6.94E-13 0.000

pg/dscm 2.54E+00 1.88E+00 9.20E-01 1.780

pg/dscm@7%O2 2.07E+00 1.54E+00 7.50E-01 1.453

Compound: Other PeCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.000000154 0.000000159 0.0000000612 0.000

lb/mmBtuO2 1.41E-11 1.47E-11 5.54E-12 0.000

pg/dscm 1.87E+01 1.95E+01 7.35E+00 15.183

pg/dscm@7%O2 1.52E+01 1.59E+01 5.99E+00 12.363

Compound: Other TCDD

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.0000000277 0.0000000212 0.0000000114 0.000

lb/mmBtuO2 2.53E-12 1.97E-12 1.03E-12 0.000

pg/dscm 3.36E+00 2.60E+00 1.37E+00 2.443

pg/dscm@7%O2 2.74E+00 2.12E+00 1.12E+00 1.993

Compound: Other TCDF

Average

RunNumber 1-Dioxins 2-Dioxins 3-Dioxins

Mass_mg 0.000000641 0.000001 0.000000311 0.000

lb/mmBtuO2 5.86E-11 9.27E-11 2.82E-11 0.000

pg/dscm 7.77E+01 1.23E+02 3.73E+01 79.333

pg/dscm@7%O2 6.33E+01 1.00E+02 3.04E+01 64.567

Location: stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1-voc 2-voc 3-voc

lb/mmBtuO2 1.30E-03 1.51E-03 1.80E-03 0.002

ppm 2.58E+00 2.99E+00 3.57E+00 3.047

ppm@7%O2 2.11E+00 2.45E+00 2.91E+00 2.490

Friday, February 18, 2011 Page 17 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Subbituminous Coal Burned 47.5 Tons/hr 48

2 Subbituminous Coal Burned 47.5 Tons/hr 48

3 Subbituminous Coal Burned 47.6 Tons/hr 48

1 nh3 inj 16.7 lb/hr 40

2 nh3 inj 19.5 lb/hr 40

3 nh3 inj 41.6 lb/hr 40

1 lime inj 6.28 klb/hr 8

2 lime inj 6.21 klb/hr 8

3 lime inj 7.49 klb/hr 8

1 mwatts 103 mw 104

2 mwatts 102.8 mw 104

3 mwatts 104.2 mw 104

1 steam flow 936.4 klb/hr 940

2 steam flow 931.5 klb/hr 940

3 steam flow 939.9 klb/hr 940

Run Name Value UOM Comments

Target

Value

1 BAGHOUSE 4.94 "WC 6

2 BAGHOUSE 5.38 "WC 6

3 BAGHOUSE 5.37 "WC 6

1 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

16.7 lb/hr 40

2 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

19.5 lb/hr 40

3 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

41.6 lb/hr 40

1 LIMESTONE INJECTION SYSTEM 6280 lb/hr 7000

2 LIMESTONE INJECTION SYSTEM 6210 lb/hr 7000

3 LIMESTONE INJECTION SYSTEM 7490 lb/hr 7000

Run Name Value UOM Comments

1 higher heating value 12791 btu/lb

Friday, February 18, 2011 Page 18 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

2 higher heating value 13267 btu/lb

3 higher heating value 13237 btu/lb

1 moisture 6.72 %

2 moisture 6.54 %

3 moisture 6.4 %

1 mercury 0.08 ppm

2 mercury 0.15 ppm

3 mercury 0.14 ppm

1 total selected metals 466 ppm

2 total selected metals 303 ppm

3 total selected metals 252 ppm

1 chlorine 530 ppm

2 chlorine 490 ppm

3 chlorine 510 ppm

1 fluorine 70 ppm

2 fluorine 80 ppm

3 fluorine 100 ppm

Friday, February 18, 2011 Page 19 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Sampling / Stack Data Results Detail

Location stack - Method 0011

Average

Run Number 1-Form 2-Form 3-Form

Test Date 5/11/2010 5/12/2010 5/12/2010

Run Start Time 1:26:00 PM 8:42:00 AM 12:20:00 PM

Run Finish Time 3:32:00 PM 10:49:00 AM 2:37:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.192 0.192 0.192 0.192

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.002 1.002 1.002 1.002

Barometric Pressure, inches of Mercury 28.11 28.2 28.2 28.170

Average Orifice Meter Differential, inches H2O 2.06 2.28 2.08 2.140

Dry Gas Meter Volume Sampled, cubic feet 89.895 93.725 91.870 91.830

Average Dry Gas Meter Temperature, °F 94.13 78.25 95.58 89.320

Dry Gas Meter Volume Sampled, dscf 81.070 87.344 82.902 83.772

Total Moisture Liquid collected, g 121.6 137.2 124.3 127.700

Volume of Water Vapor, standard cubic feet 5.72 6.46 5.85 6.010

Moisture Content of Stack Gas, % 6.59 6.89 6.59 6.690

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9341 0.9311 0.9341 0.933

Carbon Dioxide, % 15.95 16.02 16.17 16.047

Oxygen, % 3.87 3.95 3.85 3.890

Carbon Monoxide & Nitrogen, % 80.18 80.03 79.98 80.063

Fuel Factor 1.07 1.06 1.05

Dry Molecular Weight, lb/lb-Mole 30.71 30.72 30.74 30.723

Wet Molecular weight, lb/lb-Mole 29.87 29.84 29.90 29.870

Flue Gas Static Pressure, inches of H2O -0.95 -1 -1 -0.983

Absolute Flue Gas Pressure, inches of Mercury 28.04 28.13 28.13 28.100

Average Stack Gas Temperature, °F 282.33 277.75 283.83 281.303

Average Velocity Head, inches of H2O 1.9091958852

19

1.893398333

11148

1.886622793

75288

1.896

Average Stack Gas Velocity, feet/second 93.41 92.64 92.76 92.937

Stack Cross-Sectional Area, square feet 72.131 72.131 72.131 72.131

Dry Volumetric Flow Rate, dry scfm 251,717.4 251,189.2 250,262.4 251,056.333

Actual Wet Volumetric Flue Gas Flow Rate, acfm 404,265.4 400,933.0 401,452.3 402,216.900

Percent Isokinetic of Sampling Rate, % 96.3 104.0 99.0 99.767

Percent Excess Air, % 22.4 23.0 22.3 22.567

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Round Duct Diameter, inches 115 115 115

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10351 10189 10351 10,297.000

Fc 1800 0 0 600.000

Friday, February 18, 2011 Page 20 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 10

Average

Run Number 1-co 2-co 3-co

Test Date 5/11/2010 5/12/2010 5/12/2010

Run Start Time 1:26:00 PM 8:42:00 AM 12:20:00 PM

Run Finish Time 3:26:00 PM 10:42:00 AM 2:20:00 PM

Carbon Dioxide, % 15.95 16.02 16.17 16.047

Oxygen, % 3.87 3.95 3.85 3.890

Fuel Factor 1.07 1.06 1.05

Dry Volumetric Flow Rate, dry scfm 251800 251232 250321 251,117.667

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Moisture, % 6.6 6.9 6.6 6.700

Analyzer Make Teco Teco Teco

Analyzer Model 48i 48i 48i

Analyzer Serial Number 818330853 818330853 818330853 818,330,853

.000

Operating Range 100 100 100 100.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 10 10 10 10.000

Calibration Pre Zero Cylinder ID CC318342-nit CC318342-

nit

CC318342-nit

Calibration Pre Zero Cylinder Instrument Response -0.07 -0.2 -0.2 -0.157

Calibration Pre Zero Cylinder Bias -0.07 -0.2 -0.2 -0.157

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC182225-CO CC182225-

CO

CC182225-

CO

Calibration Pre High Cylinder Instrument Response 44.8 44.6 44.5 44.633

Calibration Pre High Cylinder Bias -0.6 -0.8 -0.9 -0.767

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC318342-nit CC318342-

nit

CC318342-nit

Calibration Post Zero Cylinder Instrument Response -0.6 -0.2 -0.3 -0.367

Calibration Post Zero Cylinder Bias -0.6 -0.2 -0.3 -0.367

Calibration Post Zero Cylinder Drift 0.53 0 0.1 0.210

Calibration Post High Cylinder ID CC182225-CO CC182225-

CO

CC182225-

CO

Calibration Post High Cylinder Instrument Response 44.6 44.5 45.3 44.800

Calibration Post High Cylinder Bias -0.8 -0.9 -0.1 -0.600

Calibration Post High Cylinder Drift 0.2 0.1 0.8 0.367

Cavg 47.2 43.8 37.5 42.833

Cavg Units ppmvd ppmvd ppmvd

Cgas 46.8647 43.6559 37.1229 42.548

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 10351 10189 10233 10,257.667

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 18, 2011 Page 21 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 23

Average

Run Number 1-Dioxins 2-Dioxins 3-Dioxins

Test Date 5/11/2010 5/12/2010 5/13/2010

Run Start Time 10:30:00 AM 8:02:00 AM 7:46:00 AM

Run Finish Time 6:04:00 PM 3:37:00 PM 3:17:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.176 0.176 0.176 0.176

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.997 0.997 0.997 0.997

Barometric Pressure, inches of Mercury 28.11 28.2 28.2 28.170

Average Orifice Meter Differential, inches H2O 1.19 1.13 1.16 1.160

Dry Gas Meter Volume Sampled, cubic feet 330.570 324.785 331.635 328.997

Average Dry Gas Meter Temperature, °F 102.63 101.33 101.13 101.697

Dry Gas Meter Volume Sampled, dscf 291.487 287.920 294.120 291.176

Total Moisture Liquid collected, g 454.5 469.6 446.2 456.767

Volume of Water Vapor, standard cubic feet 21.39 22.10 21.00 21.497

Moisture Content of Stack Gas, % 6.84 7.13 6.66 6.877

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9316 0.9287 0.9334 0.931

Carbon Dioxide, % 15.99 16.08 15.26 15.777

Oxygen, % 3.85 3.88 3.84 3.857

Carbon Monoxide & Nitrogen, % 80.16 80.04 80.9 80.367

Fuel Factor 1.07 1.06 1.12

Dry Molecular Weight, lb/lb-Mole 30.71 30.73 30.60 30.680

Wet Molecular weight, lb/lb-Mole 29.84 29.82 29.76 29.807

Flue Gas Static Pressure, inches of H2O -1 -1 -1 -1.000

Absolute Flue Gas Pressure, inches of Mercury 28.04 28.13 28.13 28.100

Average Stack Gas Temperature, °F 279.00 277.17 282.50 279.557

Average Velocity Head, inches of H2O 1.9814594677

497

1.871914086

82844

1.931958007

17421

1.928

Average Stack Gas Velocity, feet/second 95.00 92.10 94.00 93.700

Stack Cross-Sectional Area, square feet 72.131 72.131 72.131 72.131

Dry Volumetric Flow Rate, dry scfm 256,467.4 249,277.3 253,871.8 253,205.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 411,146.7 398,595.9 406,818.8 405,520.467

Percent Isokinetic of Sampling Rate, % 101.1 102.7 103.0 102.267

Percent Excess Air, % 22.2 22.5 21.9 22.200

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Round Duct Diameter, inches 115 115 115

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10351 10189 10159 10,233.000

Fc 0 0 0 0.000

Friday, February 18, 2011 Page 22 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 25A

Average

Run Number 1-voc 2-voc 3-voc

Test Date 5/11/2010 5/12/2010 5/12/2010

Run Start Time 12:26:00 PM 8:42:00 AM 12:20:00 PM

Run Finish Time 3:26:00 PM 10:42:00 AM 2:20:00 PM

Carbon Dioxide, % 15.95 16.02 16.17 16.047

Oxygen, % 3.87 3.95 3.85 3.890

Fuel Factor 1.07 1.06 1.05

Dry Volumetric Flow Rate, dry scfm 251800 251232 250321 251,117.667

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Moisture, % 6.6 6.9 6.6 6.700

Analyzer Make Teco Teco Teco

Analyzer Model 51 51 51 51.000

Analyzer Serial Number 100590 100590 100590 100,590.000

Operating Range 50 50 50 50.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 20 20 20 20.000

Calibration Pre Zero Cylinder ID CC318342-nit CC318342-

nit

CC318342-nit

Calibration Pre Zero Cylinder Instrument Response 0.1 0 0 0.033

Calibration Pre Zero Cylinder Bias 0 -0.2 -0.2 -0.133

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID SA7160-pro SA7160-pro SA7160-pro

Calibration Pre High Cylinder Instrument Response 26.1 26.3 26.2 26.200

Calibration Pre High Cylinder Bias 0.6 0.4 0.2 0.400

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC318342-nit CC318342-

nit

CC318342-nit

Calibration Post Zero Cylinder Instrument Response 0.1 0 0.1 0.067

Calibration Post Zero Cylinder Bias 0 -0.2 0 -0.067

Calibration Post Zero Cylinder Drift 0 0 0.2 0.067

Calibration Post High Cylinder ID SA7160-pro SA7160-pro SA7160-pro

Calibration Post High Cylinder Instrument Response 25.4 26.2 26 25.867

Calibration Post High Cylinder Bias -0.8 0.2 -0.2 -0.267

Calibration Post High Cylinder Drift 1.4 0.2 0.4 0.667

Cavg 2.7 3.08 3.7 3.160

Cavg Units ppmvd ppmvd ppmvd

Cgas 2.5848 2.992 3.5729 3.050

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 10351 10189 10159 10,233.000

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 18, 2011 Page 23 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 3A CO2

Average

Run Number 1-CO2 2-co2 3-CO2

Test Date 5/11/2010 5/11/2010 5/11/2010

Run Start Time 10:32:00 AM 1:26:00 PM 3:38:00 PM

Run Finish Time 12:32:00 PM 3:26:00 PM 6:04:00 PM

Carbon Dioxide, % 15.99 15.95 15.99 15.977

Oxygen, % 3.85 3.87 3.85 3.857

Fuel Factor 1.07 1.07 1.07

Dry Volumetric Flow Rate, dry scfm 256297 251800 256297 254,798.000

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Moisture, % 6.9 6.6 6.9 6.800

Analyzer Make HORBIA Horbia HORBIA

Analyzer Model PIR-2000 PIR-2000 PIR-2000

Analyzer Serial Number 001008 001008 001008 1,008.000

Operating Range 20 20 20 20.000

Operating Units % % %

No. Readings/Avg. 120 120 120 120.000

Calibration Set 40 40 40 40.000

Calibration Pre Zero Cylinder ID CC318342-nit CC318342-

nit

CC318342-nit

Calibration Pre Zero Cylinder Instrument Response 0.06 0.05 0.01 0.040

Calibration Pre Zero Cylinder Bias 0.25 0.2 0 0.150

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC326093-

co2

CC326093-

co2

CC326093-

co2

Calibration Pre High Cylinder Instrument Response 9.91 9.79 10.04 9.913

Calibration Pre High Cylinder Bias -0.65 -1.25 0 -0.633

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC318342-nit CC318342-

nit

CC318342-nit

Calibration Post Zero Cylinder Instrument Response 0.07 0.05 0.06 0.060

Calibration Post Zero Cylinder Bias 0.3 0.2 0.25 0.250

Calibration Post Zero Cylinder Drift 0.05 0 0.25 0.100

Calibration Post High Cylinder ID CC326093-

co2

CC326093-

co2

CC326093-

co2

Calibration Post High Cylinder Instrument Response 9.79 9.68 9.78 9.750

Calibration Post High Cylinder Bias -1.25 -1.8 -1.3 -1.450

Calibration Post High Cylinder Drift 0.6 0.55 1.3 0.817

Cavg 15.56 15.33 15.38 15.423

Cavg Units %vd %vd %vd

Cgas 15.9938 15.9347 15.6946 15.874

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw 10351 10351 10351 10,351.000

Fc 0 1800 0 600.000

Cgasw 0 0 0 0.000

Cgasw Units %vw

Friday, February 18, 2011 Page 24 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 3A CO2 3

Average

Run Number 4-co2 5-co2 6-CO2

Test Date 5/12/2010 5/12/2010 5/12/2010

Run Start Time 8:42:00 AM 12:20:00 PM 3:12:00 PM

Run Finish Time 10:42:00 AM 2:20:00 PM 4:16:00 PM

Carbon Dioxide, % 16.02 16.17 16.08 16.090

Oxygen, % 3.95 3.85 3.88 3.893

Fuel Factor 1.06 1.05 1.06

Dry Volumetric Flow Rate, dry scfm 251232 250321 249057 250,203.333

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Moisture, % 6.9 6.6 7.2 6.900

Analyzer Make Horbia Horbia HORBIA

Analyzer Model PIR 2000 PIR 2000 PIR-2000

Analyzer Serial Number 001008 001008 001008 1,008.000

Operating Range 20 20 20 20.000

Operating Units % % %

No. Readings/Avg. 120 120 120 120.000

Calibration Set 40 40 40 40.000

Calibration Pre Zero Cylinder ID CC318342-nit CC318342-

nit

CC318342-nit

Calibration Pre Zero Cylinder Instrument Response 0.05 0.06 0.05 0.053

Calibration Pre Zero Cylinder Bias 0.2 0.25 0.2 0.217

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC326093-

co2

CC326093-

co2

CC326093-

co2

Calibration Pre High Cylinder Instrument Response 10.1 9.9 9.61 9.870

Calibration Pre High Cylinder Bias -0.1 -1.1 -2.15 -1.117

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC318342-nit CC318342-

nit

CC318342-nit

Calibration Post Zero Cylinder Instrument Response 0.06 0.05 0.05 0.053

Calibration Post Zero Cylinder Bias 0.25 0.2 0.2 0.217

Calibration Post Zero Cylinder Drift 0.05 0.05 0 0.033

Calibration Post High Cylinder ID CC326093-

co2

CC326093-

co2

CC326093-

co2

Calibration Post High Cylinder Instrument Response 9.9 9.61 9.72 9.743

Calibration Post High Cylinder Bias -1.1 -2.55 -1.6 -1.750

Calibration Post High Cylinder Drift 1 1.45 0.55 1.000

Cavg 15.83 15.58 15.32 15.577

Cavg Units %vd %vd %vd

Cgas 16.0209 16.1652 16.0402 16.075

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw 10189 10159 10189 10,179.000

Fc 1800 1800 0 1,200.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 18, 2011 Page 25 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 3A CO2 3 6

Average

Run Number 7-CO2 8-CO2

Test Date 5/13/2010 5/13/2010

Run Start Time 7:52:00 AM 11:55:00 AM

Run Finish Time 11:48:00 AM 3:51:00 PM

Carbon Dioxide, % 15.26 15.26 15.260

Oxygen, % 3.84 3.84 3.840

Fuel Factor 1.12 1.12

Dry Volumetric Flow Rate, dry scfm 253686 253686 253,686.000

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9,860.000

Moisture, % 6.7 6.7 6.700

Analyzer Make HORBIA HORBIA

Analyzer Model PIR-2000 PIR-2000

Analyzer Serial Number 001008 001008 1,008.000

Operating Range 20 20 20.000

Operating Units % %

No. Readings/Avg. 120 120 120.000

Calibration Set 40 40 40.000

Calibration Pre Zero Cylinder ID CC318342-nit CC318342-

nit

Calibration Pre Zero Cylinder Instrument Response 0.07 0.1 0.085

Calibration Pre Zero Cylinder Bias 0.3 0.45 0.375

Calibration Pre Zero Cylinder Drift 0 0 0.000

Calibration Pre High Cylinder ID CC326093-

co2

CC326093-

co2

Calibration Pre High Cylinder Instrument Response 9.85 9.81 9.830

Calibration Pre High Cylinder Bias -0.95 -1.15 -1.050

Calibration Pre High Cylinder Drift 0 0 0.000

Calibration Post Zero Cylinder ID CC318342-nit CC318342-

nit

Calibration Post Zero Cylinder Instrument Response 0.1 0.12 0.110

Calibration Post Zero Cylinder Bias 0.45 0.55 0.500

Calibration Post Zero Cylinder Drift 0.15 0.1 0.125

Calibration Post High Cylinder ID CC326093-

co2

CC326093-

co2

Calibration Post High Cylinder Instrument Response 9.81 9.67 9.740

Calibration Post High Cylinder Bias -1.15 -1.85 -1.500

Calibration Post High Cylinder Drift 0.2 0.7 0.450

Cavg 14.83 14.64 14.735

Cavg Units %vd %vd

Cgas 15.2821 15.2391 15.261

Cgas Units %vd %vd

Fuel Type Override Override

Fw 10159 10159 10,159.000

Fc 0 0 0.000

Cgasw 0 0 0.000

Cgasw Units

Friday, February 18, 2011 Page 26 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 3A O2

Average

Run Number 1-o2 2-o2 3-o2

Test Date 5/11/2010 5/11/2010 5/11/2010

Run Start Time 10:32:00 AM 1:26:00 PM 3:38:00 PM

Run Finish Time 12:32:00 PM 3:26:00 PM 6:43:00 PM

Carbon Dioxide, % 15.99 15.95 15.99 15.977

Oxygen, % 3.85 3.87 3.85 3.857

Fuel Factor 1.07 1.07 1.07

Dry Volumetric Flow Rate, dry scfm 256297 251778 256297 254,790.667

F-Factor, dscfm/MMBtu @ %O2 9860 9860 0 6,573.333

Moisture, % 6.9 6.6 6.9 6.800

Analyzer Make AMI AMI AMI

Analyzer Model 201 201 201 201.000

Analyzer Serial Number 020111-1 020111-1 020111-1

Operating Range 10 10 10 10.000

Operating Units % % %

No. Readings/Avg. 120 120 120 120.000

Calibration Set 0 0 0 0.000

Calibration Pre Zero Cylinder ID CC318342-nit CC318342-

nit

CC318342-nit

Calibration Pre Zero Cylinder Instrument Response 0.07 0.05 0.05 0.057

Calibration Pre Zero Cylinder Bias 0.3 0.1 0.1 0.167

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC326093-o2 CC326093-

o2

CC326093-o2

Calibration Pre High Cylinder Instrument Response 4.91 5.14 5.1 5.050

Calibration Pre High Cylinder Bias -0.1 2.2 1.8 1.300

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC318342-nit CC318342-

nit

CC318342-nit

Calibration Post Zero Cylinder Instrument Response 0.05 0.05 0.05 0.050

Calibration Post Zero Cylinder Bias 0.1 0.1 0.1 0.100

Calibration Post Zero Cylinder Drift 0.2 0 0 0.067

Calibration Post High Cylinder ID CC326093-o2 CC326093-

o2

CC326093-o2

Calibration Post High Cylinder Instrument Response 5.14 5.1 4.86 5.033

Calibration Post High Cylinder Bias 2.2 1.8 -0.6 1.133

Calibration Post High Cylinder Drift 2.3 0.4 2.4 1.700

Cavg 3.84 4.02 3.95 3.937

Cavg Units %vd %vd %vd

Cgas 3.761 3.8682 3.9079 3.846

Cgas Units %vd %vd %vd

Fuel Type Override Override

Fw 10351 10351 0 6,900.667

Fc 1800 1800 0 1,200.000

Cgasw 0 0 0 0.000

Cgasw Units %vw

Friday, February 18, 2011 Page 27 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 3A O2 3

Average

Run Number 4-o2 5-o2 6-O2

Test Date 5/12/2010 5/12/2010 5/12/2010

Run Start Time 8:42:00 AM 12:20:00 PM 3:12:00 PM

Run Finish Time 10:42:00 AM 2:20:00 PM 4:16:00 PM

Carbon Dioxide, % 16.02 16.17 16.08 16.090

Oxygen, % 3.95 3.85 3.88 3.893

Fuel Factor 1.06 1.05 1.06

Dry Volumetric Flow Rate, dry scfm 251232 250321 249057 250,203.333

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9860 9,860.000

Moisture, % 6.9 6.6 7.2 6.900

Analyzer Make AMI AMI AMI

Analyzer Model 201 201 201 201.000

Analyzer Serial Number 020111-1 020111-1 020111-1

Operating Range 10 10 10 10.000

Operating Units % % %

No. Readings/Avg. 120 120 120 120.000

Calibration Set 0 0 0 0.000

Calibration Pre Zero Cylinder ID CC318342-nit CC318342-

nit

CC318342-nit

Calibration Pre Zero Cylinder Instrument Response 0.05 0.04 0.04 0.043

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC326093-o2 CC326093-

o2

CC326093-o2

Calibration Pre High Cylinder Instrument Response 4.99 4.89 4.87 4.917

Calibration Pre High Cylinder Bias 0.7 -0.8 -0.5 -0.200

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC318342-nit CC318342-

nit

CC318342-nit

Calibration Post Zero Cylinder Instrument Response 0.04 0.04 0.04 0.040

Calibration Post Zero Cylinder Bias 0 0 0 0.000

Calibration Post Zero Cylinder Drift 0 0 0 0.000

Calibration Post High Cylinder ID CC326093-o2 CC326093-

o2

CC326093-o2

Calibration Post High Cylinder Instrument Response 4.89 4.87 4.86 4.873

Calibration Post High Cylinder Bias -0.3 -1 -0.6 -0.633

Calibration Post High Cylinder Drift 1 0.2 0.1 0.433

Cavg 3.95 3.81 3.8 3.853

Cavg Units %vd %vd %vd

Cgas 3.9409 3.8479 3.8496 3.879

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw 10189 10159 10189 10,179.000

Fc 1800 1800 0 1,200.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 18, 2011 Page 28 of 29
2010 ACE Cogeneration EPA ICR Testing

8/24/2010

Location stack - Method 3A O2 3 6

Average

Run Number 7-O2 8-O2

Test Date 5/13/2010 5/13/2010

Run Start Time 7:52:00 AM 11:55:00 AM

Run Finish Time 11:48:00 AM 3:51:00 PM

Carbon Dioxide, % 15.26 15.26 15.260

Oxygen, % 3.84 3.84 3.840

Fuel Factor 1.12 1.12

Dry Volumetric Flow Rate, dry scfm 243686 253686 248,686.000

F-Factor, dscfm/MMBtu @ %O2 9860 9860 9,860.000

Moisture, % 6.7 6.7 6.700

Analyzer Make AMI AMI

Analyzer Model 201 201 201.000

Analyzer Serial Number 020111-1 020111-1

Operating Range 10 10 10.000

Operating Units % %

No. Readings/Avg. 120 120 120.000

Calibration Set 0 0 0.000

Calibration Pre Zero Cylinder ID CC318342-nit CC318342-

nit

Calibration Pre Zero Cylinder Instrument Response 0.06 0.05 0.055

Calibration Pre Zero Cylinder Bias 0.2 0.1 0.150

Calibration Pre Zero Cylinder Drift 0 0 0.000

Calibration Pre High Cylinder ID CC326093-o2 CC326093-

o2

Calibration Pre High Cylinder Instrument Response 4.98 4.93 4.955

Calibration Pre High Cylinder Bias 0.6 0.1 0.350

Calibration Pre High Cylinder Drift 0 0 0.000

Calibration Post Zero Cylinder ID CC318342-nit CC318342-

nit

Calibration Post Zero Cylinder Instrument Response 0.05 0.06 0.055

Calibration Post Zero Cylinder Bias 0.1 0.2 0.150

Calibration Post Zero Cylinder Drift 0.1 0.1 0.100

Calibration Post High Cylinder ID CC326093-o2 CC326093-

o2

Calibration Post High Cylinder Instrument Response 4.93 5.02 4.975

Calibration Post High Cylinder Bias 0.1 1 0.550

Calibration Post High Cylinder Drift 0.5 0.9 0.700

Cavg 3.87 3.89 3.880

Cavg Units %vd %vd

Cgas 3.8461 3.8506 3.848

Cgas Units %vd %vd

Fuel Type Override Override

Fw 10159 10159 10,159.000

Fc 0 0 0.000

Cgasw 0 0 0.000

Cgasw Units

Friday, February 18, 2011 Page 29 of 29