APPENDIX H. DETERMINATION OF BASIC FURNACE AND BOILER MODELS

TABLE OF CONTENTS

H.1 Determination of Basic Furnace Models ................................... H-1

H.2 Determination of Basic Boiler Models .................................... H-3

H.3 Tables of Model Numbers and Specifications for Non-Weatherized Gas Furnaces .. H-7

H.3.1 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces ................. H-8

H.3.2 Condensing Single-Stage Non-Weatherized Gas Furnaces .................... H-26

H.3.3 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces ................. H-41

H.3.4 Condensing Two-Stage Non-Weatherized Gas Furnaces ..................... H-46

LIST OF TABLES

Table H.2.1 Input Capacity Bins representing 2% of the total number of Gas Boilers .... H-4

Table H.2.2 Selected Generic Input Capacity Bins for Gas Boilers Count ............ H-4

Table H.2.3 Selected Generic Input Capacity Bins for Gas Boilers Count ............ H-5

Table H.2.4 Input Capacity Bins representing 2% of the total number of Oil Boilers .... H-6

Table H.2.5 Selected Generic Input Capacity Bins for Oil Boilers Count ............. H-6

Table H.3.1 Variable Definitions ............................................. H-7

Table H.3.2 Manufacture Code Definitions ..................................... H-7

Table H.3.3 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 45 kBtu/h 800 CFM ........................................... H-8

Table H.3.4 Non-Condensing Single -Stage Non-Weatherized Gas Furnaces

at 45 kBtu/h 1200 CFM .......................................... H-9

Table H.3.5 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 50 kBtu/h 800 CFM ........................................... H-9

Table H.3.6 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 50 kBtu/h 1200 CFM ......................................... H-10

Table H.3.7 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 60 kBtu/h 800 CFM .......................................... H-11

Table H.3.8 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 60 kBtu/h 1200 CFM ......................................... H-11

Table H.3.9 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 70 kBtu/h 1200 CFM ......................................... H-12

Table H.3.10 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 70 kBtu/h 1600 CFM ......................................... H-12

Table H.3.11 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 75 kBtu/h 1200 CFM ......................................... H-13

Table H.3.12 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 75 kBtu/h 1600 CFM ......................................... H-14

Table H.3.13 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 80 kBtu/h 1200 CFM ......................................... H-15

Table H.3.14 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

H-i

 EE-RM/STD-01-350 COMMENT 164

APPENDIX H. DETERMINATION OF BASIC FURNACE AND BOILER MODELS 

TABLE OF CONTENTS 

H.l Determination of Basic Furnace Models ................................... H-l 

H.2 Determination of Basic Boiler Models .................................... H-3 

H.3 Tables of Model Numbers and Specifications farNan-Weatherized Gas Furnaces .. H-7 

H.3.1 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces ................. H-S 

H.3.2 Condensing Single-Stage Non-Weatherized Gas Furnaces .................... H-26 

H.3.3 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces ................. H-41 

H.3.4 Condensing Two-Stage Non-Weatherized Gas Furnaces ..................... H-46 

Table H.2.1 

Table H.2.2 

Table H.2.3 

Table H.2.4 

Table H.2.5 

Table H.3.l 

Table H.3.2 

Table H.3.3 

Table H.3.4 

Table H.3.5 

Table H.3.6 

Table H.3.7 

Table H.3.S 

Table H.3.9 

LIST OF TABLES 

Input Capacity Bins representing 2% of the total number of Gas Boilers .... H-4 

Selected Generic Input Capacity Bins for Gas Boilers Count ............ H-4 

Selected Generic Input Capacity Bins for Gas Boilers Count ............ H-5 

Input Capacity Bins representing 2% of the total number of Oil Boilers .... H-6 

Selected Generic Input Capacity Bins for Oil Boilers Count ............. H-6 

Variable Definitions . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-7 

Manufacture Code Definitions. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-7 

Non-Condensing Single-Stage N on-Weatherized Gas Furnaces 

at 45 kBtu/h SOO CFM ........................................... H-S 

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 45 kBtu/h 1200 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-9 

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 50 kBtu/h SOO CFM ........................................... H-9 

N on-Condensing Single-Stage N on-Weatherized Gas Furnaces 

at 50 kBtu/h 1200 CFM ......................................... H-I0 

Non-Condensing Single-Stage N on-Weatherized Gas Furnaces 

at 60 kBtu/h SOO CFM .......................................... H-ll 

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 60 kBtu/h 1200 CFM ......................................... H-ll 

N on-Condensing Single-Stage N on-Weatherized Gas Furnaces 

at 70 kBtu/h 1200 CFM ......................................... H-12 

Table H.3.10 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 70 kBtu/h 1600 CFM ......................................... H-12 

Table H.3.11 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 75 kBtu/h 1200 CFM ......................................... H-13 

Table H.3.l2 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 75 kBtu/h 1600 CFM ......................................... H-14 

Table H.3.l3 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at SO kBtu/h 1200 CFM ......................................... H-15 

Table H.3.14 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

H-i 
Table H.3.15

Table H.3.16

Table H.3.17

Table H.3.18

Table H.3.19

Table H.3.20

Table H.3.21

Table H.3.22

Table H.3.23

Table H.3.24

Table H.3.25

Table H.3.26

Table H.3.27

Table H.3.28

Table H.3.29

Table H.3.30

Table H.3.31

Table H.3.32

Table H.3.33

Table H.3.34

Table H.3.35

Table H.3.36

at 80 kBtu/h 1600 .............................................. H-15

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 80 kBtu/h 2000 CFM ......................................... H-16

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 90 kBtu/h 1200 CFM ......................................... H-16

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 90 kBtu/h 1600 CFM ......................................... H-17

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 90 kBtu/h 2000 .............................................. H-17

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 100 kBtu/h 1200 CFM ........................................ H-18

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 100 kBtu/h 1600 ............................................. H-19

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 100 kBtu/h 2000 CFM ........................................ H-20

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 115 kBtu/h 1600 CFM ........................................ H-21

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 115 kBtu/h 2000 CFM ........................................ H-22

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 120 kBtu/h 1600 CFM ........................................ H-23

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 120 kBtu/h 2000 CFM ........................................ H-23

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 125 kBtu/h 1600 CFM ........................................ H-23

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 125 kBtu/h 2000 CFM ........................................ H-24

Non-Condensing Single-Stage Non-Weatherized Gas Furnaces

at 140 kBtu/h 2000 CFM ........................................ H-25

Condensing Single-Stage Non-Weatherized Gas Furnaces

at 45 kBtu/h 800 CFM .......................................... H-26

Condensing Single-Stage Non-Weatherized Gas Furnaces

at 45 kBtu/h 1200 CFM ......................................... H-27

Condensing Single-Stage Non-Weatherized Gas Furnaces

at 50 kBtu/h 800 CFM .......................................... H-27

Condensing Single-Stage Non-Weatherized Gas Furnaces

at 50 kBtu/h 1200 CFM ......................................... H-28

Condensing Single-Stage Non-Weatherized Gas Furnaces

at 60 kBtu/h 800 CFM .......................................... H-28

Condensing Single-Stage Non-Weatherized Gas Furnaces

at 60 Btu/h 1200 CFM .......................................... H-29

Condensing Single-Stage Non-Weatherized Gas Furnaces

at 70 kBtu/h 1200 CFM ......................................... H-30

Condensing Single-Stage Non-Weatherized Gas Furnaces

H-ii

 EE-RM/STD-01-350 COMMENT 164

at 80 kBtu/h 1600 .............................................. H-15 

Table H.3.15 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 80 kBtu/h 2000 CFM ......................................... H-16 

Table H.3.16 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 90 kBtu/h 1200 CFM ......................................... H-16 

Table H.3.17 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 90 kBtu/h 1600 CFM ......................................... H-17 

Table H.3.18 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at90kBtu/h2000 .............................................. H-17 

Table H.3.19 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 100 kBtu/h 1200 CFM ........................................ H-18 

Table H.3.20 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 100 kBtu/h 1600 ............................................. H-19 

Table H.3.21 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 100 kBtu/h 2000 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-20 

Table H.3.22 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 115 kBtu/h 1600 CFM ........................................ H-21 

Table H.3.23 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 115 kBtu/h 2000 CFM ........................................ H-22 

Table H.3.24 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 120 kBtu/h 1600 CFM ........................................ H-23 

Table H.3.25 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 120 kBtu/h 2000 CFM ........................................ H-23 

Table H.3.26 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 125 kBtu/h 1600 CFM ........................................ H-23 

Table H.3.27 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 125 kBtu/h 2000 CFM ........................................ H-24 

Table H.3.28 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 140 kBtu/h 2000 CFM ........................................ H-25 

Table H.3.29 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 45 kBtu/h 800 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-26 

Table H.3.30 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 45 kBtu/h 1200 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-27 

Table H.3.31 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 50 kBtu/h 800 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-27 

Table H.3.32 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 50 kBtu/h 1200 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-28 

Table H.3.33 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 60 kBtu/h 800 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-28 

Table H.3.34 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 60 Btu/h 1200 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-29 

Table H.3.35 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 70 kBtu/h 1200 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-30 

Table H.3.36 Condensing Single-Stage Non-Weatherized Gas Furnaces 

H-ii 
at 70 kBtu/h 1600 CFM ......................................... H-31

Table H.3.37 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 75 kBtu/h 1200 ............................................. H-31

Table H.3.38 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 75 kBtu/h 1600 CFM ......................................... H-32

Table H.3.39 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 80 kBtu/h 1200 CFM ......................................... H-32

Table H.3.40 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 80 kBtu/h 1600 CFM ......................................... H-33

Table H.3.41 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 80 kBtu/h 2000 CFM ......................................... H-33

Table H.3.42 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 90 kBtu/h 1200 CFM ......................................... H-34

Table H.3.43 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 90 kBtu/h 1600 CFM ......................................... H-34

Table H.3.44 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 90 kBtu/h 2000 CFM ......................................... H-35

Table H.3.45 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 100 kBtu/h 1200 CFM ........................................ H-35

Table H.3.46 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 100 kBtu/h 1600 CFM ........................................ H-36

Table H.3.47 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 100 kBtu/h 2000 CFM ........................................ H-37

Table H.3.48 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 115 kBtu/h 1600 CFM ........................................ H-37

Table H.3.49 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 115 kBtu/h 2000 CFM ........................................ H-38

Table H.3.50 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 120 kBtu/h 1600 CFM ........................................ H-38

Table H.3.51 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 120 kBtu/h 2000 CFM ........................................ H-39

Table H.3.52 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 125 kBtu/h 2000 CFM ........................................ H-40

Table H.3.53 Condensing Single-Stage Non-Weatherized Gas Furnaces

at 140 kBtu/h 2000 CFM ........................................ H-41

Table H.3.54 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 50 kBtu/h 1200 CFM ......................................... H-41

Table H.3.55 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 60 kBtu/h 1200 CFM ......................................... H-42

Table H.3.56 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 70 kBtu/h 1200 CFM ........................................ H-42

Table H.3.57 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 70 kBtu/h 1600 CFM ......................................... H-42

Table H.3.58 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

H-iii

 EE-RM/STD-01-350 COMMENT 164

at 70 kBtu/h 1600 CFM 00000000000000000000000000000000000000000 H-31 

Table Ho3037 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 75 kBtulh 1200 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 H-31 

Table Ho3038 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 75 kBtu/h 1600 CFM 00000000000000000000 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0000 H-32 

Table Ho3039 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 80 kBtu/h 1200 CFM 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 H-32 

Table H.3.40 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 80 kBtu/h 1600 CFM 000000000 000000000000000 0 0 0 0 0 0 0 0 0 000 0 0 0 0 0 H-33 

Table Ho3.41 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 80 kBtu/h 2000 CFM 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 H-33 

Table Ho3.42 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 90 kBtu/h 1200 CFM 000000000000000000000000 0 0 0 0 0 0 0 0 0 0 0 0 0 0 000 H-34 

Table Ho3.43 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 90 kBtu/h 1600 CFM 00000000000000000000000000000000000000000 H-34 

Table Ho3.44 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 90 kBtu/h 2000 CFM 00000000000000000000000000000000000000000 H-35 

Table Ho3.45 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 100 kBtu/h 1200 CFM 00000000 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 00000000000 H-35 

Table Ho3.46 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 100 kBtu/h 1600 CFM 00000000000 0 0 0 0 0 0 0 0 0 0 0 0 00000000000000000 H-36 

Table Ho3.47 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 100 kBtu/h 2000 CFM 00000000000000000000000 0 0 0 0 0 0 00000000000 H-37 

Table Ho3.48 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 115 kBtu/h 1600 CFM 00000000000 0 0 0 0 0000 0 0 0 0 00000000000000000 H-37 

Table Ho3.49 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 115 kBtu/h 2000 CFM 00000000000 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 H-38 

Table H.3050 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 120 kBtu/h 1600 CFM 00000000000 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 H-38 

Table Ho3051 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 120 kBtu/h 2000 CFM 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 H-39 

Table Ho3052 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 125 kBtu/h 2000 CFM 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 H -40 

Table Ho3053 Condensing Single-Stage Non-Weatherized Gas Furnaces 

at 140 kBtu/h 2000 CFM 00000000000 0 0 0 0 0 0000000 00000000000000000 H-41 

Table Ho3054 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 50 kBtu/h 1200 CFM 000000000000 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 H-41 

Table Ho3055 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 60 kBtu/h 1200 CFM 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 H-42 

Table Ho3056 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 70 kBtu/h 1200 CFM 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 0 H-42 

Table H.3057 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 70 kBtu/h 1600 CFM 000000000000 0 0 0 0 0 0 0 0 0 0 0 0 0000000000000 0 0 0 0 H-42 

Table Ho3058 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

H-iii 
Table H.3.59

Table H.3.60

Table H.3.61

Table H.3.62

Table H.3.63

Table H.3.64

Table H.3.65

Table H.3.66

Table H.3.67

Table H.3.68

Table H.3.69

Table H.3.70

Table H.3.71

Table H.3.72

Table H.3.73

Table H.3.74

Table H.3.75

Table H.3.76

Table H.3.77

Table H.3.78

Table H.3.79

Table H.3.80

at 70 kBtu/h 2000 CFM ......................................... H-42

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 75 kBtu/h 1200 CFM ......................................... H-42

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 75 kBtu/h 1600 CFM ......................................... H-43

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 80 kBtu/h 1200 CFM ......................................... H-43

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 80 kBtu/h 1600 CFM ......................................... H-43

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 90 kBtu/h 1200 CFM ......................................... H-43

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 90 kBtu/h 1600 CFM ......................................... H-44

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 90 kBtu/h 2000 CFM ......................................... H-44

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 100 kBtu/h 1600 CFM ........................................ H-44

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 100 kBtu/h 2000 CFM ........................................ H-44

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 115 kBtu/h 2000 CFM ........................................ H-45

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 120 kBtu/h 2000 CFM ........................................ H-45

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 125 kBtu/h 2000 CFM ........................................ H-45

Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

at 140 kBtu/h 2000 CFM ........................................ H-45

Condensing Two-Stage Non-Weatherized Gas Furnaces

at 45 kBtu/h 1200 CFM Condensing Two-Stage ...................... H-46

Condensing Two-Stage Non-Weatherized Gas Furnaces

at 50 kBtu/h 1200 CFM ......................................... H-46

Condensing Two-Stage Non-Weatherized Gas Furnaces

at 60 kBtu/h 1200 CFM ......................................... H-46

Condensing Two-Stage Non-Weatherized Gas Furnaces

at 60 kBtu/h 2000 CFM ......................................... H-46

Condensing Two-Stage Non-Weatherized Gas Furnaces

at 70 kBtu/h 1200 CFM ......................................... H-47

Condensing Two-Stage Non-Weatherized Gas Furnaces

at 70 kBtu/h 1600 CFM ......................................... H-47

Condensing Two-Stage Non-Weatherized Gas Furnaces

at 75 kBtu/h 1200 CFM ......................................... H-47

Condensing Two-Stage Non-Weatherized Gas Furnaces

at 75 kBtu/h 1600 CFM Condensing Two-Stage ...................... H-47

Condensing Two-Stage Non-Weatherized Gas Furnaces

H-iv

 EE-RM/STD-01-350 COMMENT 164

at 70 kBtu/h 2000 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-42 

Table H.3.59 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 75 kBtu/h 1200 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-42 

Table H.3.60 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 75 kBtu/h 1600 CFM ......................................... H-43 

Table H.3.61 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 80 kBtu/h 1200 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-43 

Table H.3.62 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 80 kBtu/h 1600 CFM ......................................... H-43 

Table H.3.63 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 90 kBtu/h 1200 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-43 

Table H.3.64 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 90 kBtu/h 1600 CFM ......................................... H-44 

Table H.3.65 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 90 kBtu/h 2000 CFM ......................................... H-44 

Table H.3.66 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 100 kBtu/h 1600 CFM ........................................ H-44 

Table H.3.67 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 100 kBtu/h 2000 CFM ........................................ H-44 

Table H.3.68 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 115 kBtu/h 2000 CFM ........................................ H-45 

Table H.3.69 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 120 kBtu/h 2000 CFM ........................................ H-45 

Table H.3.70 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 125 kBtu/h 2000 CFM ........................................ H-45 

Table H.3.71 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 140 kBtu/h 2000 CFM ........................................ H-45 

Table H.3.72 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 45 kBtu/h 1200 CFM Condensing Two-Stage ...................... H-46 

Table H.3.73 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 50 kBtu/h 1200 CFM ......................................... H-46 

Table H.3.74 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 60 kBtu/h 1200 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H -46 

Table H.3.75 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 60 kBtu/h 2000 CFM ......................................... H-46 

Table H.3.76 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 70 kBtu/h 1200 CFM ......................................... H-47 

Table H.3.77 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 70 kBtu/h 1600 CFM ......................................... H-47 

Table H.3.78 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 75 kBtu/h 1200 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-47 

Table H.3.79 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 75 kBtu/h 1600 CFM Condensing Two-Stage ...................... H-47 

Table H.3.80 Condensing Two-Stage Non-Weatherized Gas Furnaces 

H-iv 
at 80 kBtu/h 1200 CFM ......................................... H-48

Table H.3.81 Condensing Two-Stage Non-Weatherized Gas Furnaces

at 80 kBtu/h 1600 CFM ......................................... H-48

Table H.3.82 Condensing Two-Stage Non-Weatherized Gas Furnaces

at 80 kBtu/h 2000 CFM ......................................... H-48

Table H.3.83 Condensing Two-Stage Non-Weatherized Gas Furnaces

at 90 kBtu/h 1200 CFM ......................................... H-48

Table H.3.84 Condensing Two-Stage Non-Weatherized Gas Furnaces

at 90 kBtu/h 1600 CFM ......................................... H-49

Table H.3.85 Condensing Two-Stage Non-Weatherized Gas Furnaces

at 90 kBtu/h 2000 CFM ......................................... H-49

Table H.3.86 Condensing Two-Stage Non-Weatherized Gas Furnaces

at 100 kBtu/h 1600 CFM ........................................ H-49

Table H.3.87 Condensing Two-Stage Non-Weatherized Gas Furnaces

at 100 kBtu/h 2000 CFM ........................................ H-49

Table H.3.88 Condensing Two-Stage Non-Weatherized Gas Furnaces

at 115 kBtu/h 2000 CFM ........................................ H-50

Table H.3.89 Condensing Two-Stage Non-Weatherized Gas Furnaces

at 120 kBtu/h 2000 CFM ........................................ H-50

Table H.3.90 Condensing Two-Stage Non-Weatherized Gas Furnaces

at 125 kBtu/h 2000 CFM ........................................ H-50

LIST OF FIGURES

Figure H. 1.1 Number of Non-Weatherized Furnace Models by Input Capacity ......... H-2

Figure H.2.1 Count of Gas Boiler Models by Input Capacity ....................... H-3

Figure H.2.2 Count of Oil Boiler Models by Input Capacity ........................ H-5

 EE-RM/STD-01-350 COMMENT 164

at 80 kBtu/h 1200 CFM ......................................... H-48 

Table H.3.81 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 80 kBtu/h 1600 CFM ......................................... H-48 

Table H.3.82 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 80 kBtu/h 2000 CFM ......................................... H-48 

Table H.3.83 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 90 kBtu/h 1200 CFM ......................................... H-48 

Table H.3.84 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 90 kBtu/h 1600 CFM ......................................... H-49 

Table H.3.85 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 90 kBtu/h 2000 CFM ......................................... H-49 

Table H.3.86 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 100 kBtu/h 1600 CFM ........................................ H-49 

Table H.3.87 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 100 kBtu/h 2000 CFM ........................................ H-49 

Table H.3.88 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 115 kBtu/h 2000 CFM ........................................ H-50 

Table H.3.89 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 120 kBtu/h 2000 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-50 

Table H.3.90 Condensing Two-Stage Non-Weatherized Gas Furnaces 

at 125 kBtu/h 2000 CFM . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .. H-50 

LIST OF FIGURES 

Figure H.I.I Number of Non-Weatherized Furnace Models by Input Capacity ......... H-2 

Figure H.2.1 Count of Gas Boiler Models by Input Capacity ....................... H-3 

Figure H.2.2 Count of Oil Boiler Models by Input Capacity ........................ H-5 

H-v 
APPENDIX H. DETERMINATION OF BASIC FURNACE AND BOILER MODELS

H.1 Determination of Basic Furnace Models

Input capacity for furnaces and boilers is an essential component of the virtual models used

in the LCC analysis. The basic methodology for obtaining the generic input capacities involves

using the reduced set of models for each product class and then using a histogram of input capacities

to pick the input capacities which are the most common.

To determine basic furnace models, DOE selected 25 airflow/capacity bins. The Department

selected the bins by looking at "common" (popular) sizes of input capacity in the March 2005 Gas

Appliances Manufacturers Association (GAMA) certified efficiency ratings directory.' The

Department assumed that the number of models at a particular size indicated how common or

popular that size was. Product literature and furnace manufacturer web sites helped in further

determining series of furnaces considered to be "basic models."

To determine the characteristics of basic furnace models of non-condensing, non-weatherized

gas furnaces, the Department examined single-stage, natural gas furnaces that are not intended for

mobile homes. DOE selected upflow and horizontal models since they represent the majority of

models and often have similar or identical specifications and efficiency values as downflow models

from the same manufacturer. (Of the 1,277 non-weatherized gas furnace models in the reduced set

of furnace models database (see Appendix F), 77 percent were either horizontal or upflow.)

Similarly, only non-condensing furnaces at or above 80 percent AFUE were picked since they

represent the majority of non-weatherized gas furnaces. To further refine the basic model selection

criteria, DOE used product literature to select models without variable speed blower motors.

Manufacturer web sites provided information describing their furnaces. This information further

helped distinguish between the different series of models.

The Department used a similar process to select basic models for condensing

non-weatherized gas furnaces. Model characteristics included single -stage furnaces not intended

for mobile homes. Since many condensing gas furnaces series are multi-position (upflow,

horizontal, and downflow), DOE included upflow, horizontal, and downflow models. The

Department gleaned this information from the GAMA database. To further refine the selection

criteria, DOE used product literature to select models without variable speed blower motors.

The Department selected similar models that had the same capacity and nominal airflow

(cfm). Most of the furnaces fit into four maximum nominal airflow sizes: 800 cfm (two-ton), 1200

efin (three-ton), 1600 cfm (four-ton), and 2000 cfm (five-ton).

In terms of input capacity, most models fit into 12 input capacity bins. Some models did not

exactly match the bins, but had similar enough values to be considered in the same bin. For

example, 40 KBtu/h and 45 KBtu/h models are grouped together into a single 45 KBtu/h bin. The

4 nominal airflow sizes and 12 input capacities were combined into bins. Only 25 of these bins are

H-1

 EE-RM/STD-01-350 COMMENT 164

APPENDIX H. DETERMINATION OF BASIC FURNACE AND BOILER MODELS 

H.t Determination of Basic Furnace Models 

Input capacity for furnaces and boilers is an essential component of the virtual models used 

in the LCC analysis. The basic methodology for obtaining the generic input capacities involves 

using the reduced set of models for each product class and then using a histogram of input capacities 

to pick the input capacities which are the most common. 

To determine basic furnace models, DOE selected 25 airflow/capacity bins. The Department 

selected the bins by looking at "common" (popular) sizes of input capacity in the March 2005 Gas 

Appliances Manufacturers Association (GAMA) certified efficiency ratings directory.l The 

Department assumed that the number of models at a particular size indicated how common or 

popular that size was. Product literature and furnace manufacturer web sites helped in further 

determining series of furnaces considered to be "basic models." 

To determine the characteristics of basic furnace models of non-condensing, non-weatherized 

gas furnaces, the Department examined single-stage, natural gas furnaces that are not intended for 

mobile homes. DOE selected upflow and horizontal models since they represent the majority of 

models and often have similar or identical specifications and efficiency values as downflow models 

from the same manufacturer. (Of the 1,277 non-weatherized gas furnace models in the reduced set 

of furnace models database (see Appendix F), 77 percent were either horizontal or upflow.) 

Similarly, only non-condensing furnaces at or above 80 percent AFUE were picked since they 

represent the majority of non-weatherized gas furnaces. To further refine the basic model selection 

criteria, DOE used product literature to select models without variable speed blower motors. 

Manufacturer web sites provided information describing their furnaces. This information further 

helped distinguish between the different series of models. 

The Department used a similar process to select basic models for condensing 

non-weatherized gas furnaces. Model characteristics included single-stage furnaces not intended 

for mobile homes. Since many condensing gas furnaces series are multi-position (upflow, 

horizontal, and downflow), DOE included upflow, horizontal, and downflow models. The 

Department gleaned this information from the GAMA database. To further refine the selection 

criteria, DOE used product literature to select models without variable speed blower motors. 

The Department selected similar models that had the same capacity and nominal airflow 

(cfm). Most of the furnaces fit into four maximum nominal airflow sizes: 800 cfm (two-ton), 1200 

cfm (three-ton), 1600 cfm (four-ton), and 2000 cfm (five-ton). 

In terms of input capacity, most models fit into 12 input capacity bins. Some models did not 

exactly match the bins, but had similar enough values to be considered in the same bin. For 

example, 40 KBtu/h and 45 KBtu/h models are grouped together into a single 45 KBtu/h bin. The 

4 nominal airflow sizes and 12 input capacities were combined into bins. Only 25 of these bins are 

H-I 
used in the analysis. Some combinations of nominal airflow size and input capacity are not

manufactured. Each of the 25 bins selected has at least three non-condensing or condensing gas

furnace models.

The 12 different input capacities from 45 KBtu/h to 140 KBtu/h give a good range to match

different home sizes.

Figure H. 1.1 shows the number of non-weatherized gas furnace models by input capacity for

non-weatherized gas furnaces.

3000

2500 -f2000

0 1500 -

L)

1000 F

500

0 0 0 0 0 0 0 0 0 0 0 0 0 0 0

N M d M C0 f- W M O N M CF to t0

Input Capacity (kBtu/h)

Figure H.1.1 Number of Non-Weatherized Furnace Models by Input

Capacity

Tables H.3.3 to H.3.95 contain tables of model numbers and specifications for the

non-condensing single-stage, condensing single-stage, non-condensing two-stage, and condensing

two-stage basic model non-weatherized gas furnaces the Department used for the LCC analysis.

 EE-RM/STD-01-350 COMMENT 164

used in the analysis. Some combinations of nominal airflow size and input capacity are not 

manufactured. Each of the 25 bins selected has at least three non-condensing or condensing gas 

furnace models. 

The 12 different input capacities from 45 KBtu/h to 140 KBtu/h give a good range to match 

different horne sizes. 

Figure H.1.1 shows the number of non-weatherized gas furnace models by input capacity for 

non-weatherized gas furnaces. 

+' 

s::: 

::::l 

0 

u 

3000~--------------------------------------. 

2500 

2000 

1500 --

1000 

500 

a a a a a a a a a a a a a a a 

N M ~ ~ ~ ~ ro m a ~ N M ~ ~ ~ 

Input Capacity (kBtu/h) 

Figure H.1.1 Number of Non-Weatherized Furnace Models by Input 

Capacity 

Tables H.3.3 to H.3.95 contain tables of model numbers and specifications for the 

non-condensing single-stage, condensing single-stage, non-condensing two-stage, and condensing 

two-stage basic model non-weatherized gas furnaces the Department used for the LCC analysis. 

H-2 
H.2 Determination of Basic Boiler Models

Generic Input Capacities for Gas Boilers

There are 1361 models in the reduced set of models developed using the March 2005 GAMA

Directory.' This set was then divided into bins of lkbtuh. Figure H.2.1 shows the count for each 1

kbtuh bin.

Figure H.2.1 Count of Gas Boiler Models by Input Capacity

Table H.2.1 shows the input capacity bins representing at least 2% of the total number of gas

boilers (the selected input capacities are marked in bold). The selected input capacities account for

50.5% of all gas boiler models. The Department decided to pick the input capacity bins with at least

2% of the total count. Of these the Department grouped 70 with 75, 100 with 105, 140 with 150,

210 with 200, 245 with 250, since they are fairly close and the selected capacities better represented

adjoining bins. In addition, the Department converted 299 to 300, since this was the maximum input

capacity available.

 EE-RM/STD-01-350 COMMENT 164

H.2 Determination of Basic Boiler Models 

Generic Input Capacities for Gas Boilers 

There are 1361 models in the reduced set of models developed using the March 2005 GAMA 

Directory.l This set was then divided into bins of 1kbtuh. Figure H.2.1 shows the count for each 1 

kbtuh bin. 

90 ,------------------------------ --------~----- ----~---- -----~---- -~------------ --

80 1~--------------~----~-- ---------- -~--------------- -------------

70~1~~~~~~~~~~~~~~~~~~~~~~~­ I 

I 

60~r--------------~r_-~------------------------

_ 50 I~----------II-~--- - ~--~-- - t: --~ ------- -~~----

:::I 

o 

o 40 1---------0- -1------1-- ----- --------D---I---~ --------~ 

30 1----------- -- ----- ------ ---------- ---- --- -----------

20 ~-__I_---

10 II 

o "m,u' ,A,RlJtl" ",11., ..... d 'I,JI~,l,~~ .. ~,. U~ .. tt .,~,~,! k;J!m.l,w.~,~J~".m~lJ, .. 25 35 45 55 65 75 85 95 105115125135145155165175185195205215225235245255265 275 285 295 

Bins 

Figure H.2.1 Count of Gas Boiler Models by Input Capacity 

Table H.2.1 shows the input capacity bins representing at least 2% of the total number of gas 

boilers (the selected input capacities are marked in bold). The selected input capacities account for 

50.5% of all gas boiler models. The Department decided to pick the input capacity bins with at least 

2% of the total count. Of these the Department grouped 70 with 75, 100 with 105, 140 with 150, 

210 with 200,245 with 250, since they are fairly close and the selected capacities better represented 

adjoining bins. In addition, the Department converted 299 to 300, since this was the maximum input 

capacity available. 

H-3 
Table H.2.1 Input Capacity Bins representing 2% of the total number of Gas Boilers

Input Capacity Bin I Count Percentage of Total

175 85 6.2%

150 60 4.4%

75 56 4.1%

105 52 3.8%

100 51 3.7%

140 50 3.7%

250 45 3.3%

70 44 3.2%

225 42 3.1%

210 41 3.0%

200 38 2.8%

245 34 2.5%

125 33 2.4%

50 28 2.1%

299 28 2.1%

Table H.2.2 shows the count for the selected bins expanded to include input capacities within

+ o - 5 kbtuh for the 10 selected generic input capacity bins. With the selected bins the generic input

capacities account for 73.5% of all gas boiler models.

Table H.2.2 Selected Generic Input Capacity Bins for Gas Boilers Count

Generic Input Input Capacity

Range

Count Percentage of Total

Number of Models

50 45-55 49 3.6%

75 65-80 129 9.5%

100 95-110 147 10.8%

125 120-130 84 6.2%

150 135-155 162 11.9%

175 170-180 114 8.4%

200 195-205 119 8.7%

225 220-230 58 4.3%

250 245-255 104 7.6%

300 290-300 35 2.6%

 EE-RM/STD-01-350 COMMENT 164

T a bi e H .. 21 I npu tC apaclty 't B' ms rep res en f m2 2o/i 00 f t e h to t a I num b er 0 fG as B'I 01 ers 

Input Capacity Bin Count Percentage of Total 

175 85 6.2% 

150 60 4.4% 

75 56 4.1% 

105 52 3.8% 

100 51 3.7% 

140 50 3.7% 

250 45 3.3% 

70 44 3.2% 

225 42 3.1% 

210 41 3.0% 

200 38 2.8% 

245 34 2.5% 

125 33 2.4% 

50 28 2.1% 

299 28 2.1% 

Table H.2.2 shows the count for the selected bins expanded to include input capacities within 

+ 0 - 5 kbtuh for the 10 selected generic input capacity bins. With the selected bins the generic input 

capacities account for 73.5% of all gas boiler models. 

T a e bi H 2 2 .. SIt e ec e d G . I enenc npu tC apaclry 't B' Ins ~ or G as B'I 01 ers C oun t 

Generic Input Input Capacity Count Percentage of Total 

Range Number of Models 

50 45-55 49 3.6% 

75 65-80 129 9.5% 

100 95-110 147 10.8% 

125 120-130 84 6.2% 

150 135-155 162 11.9% 

175 170-180 114 8.4% 

200 195-205 119 8.7% 

225 220-230 58 4.3% 

250 245-255 104 7.6% 

300 290-300 35 2.6% 

H-4 
Table H.2.3 Selected Generic Input Capacity Bins for Gas Boilers Count

Generic Input Capacity Bin Other Input

Capacity Range

Count Percentage of Total

50 0-62.5 104 7.6%

75 62.5-87.5 149 10.9%

100 87.5-112.5 202 14.8%

125 112.5-137.5 125 9.2%

150 137.5-162.5 174 12.8%

175 162.5-187.5 176 12.9%

200 187.5-212.5 131 9.6%

225 212.5-237.5 75 5.5%

250 237.5-275 158 11.6%

300 275-300 67 4.9%

Generic Input Capacities for Oil Boilers

There are 600 models in the reduced set of models developed using the March 2005 GAMA

Directory.' This set was then divided into bins of lkbtuh. Figure H.2.2 shows the count for each

1 kbtuh bin.

70

60-I

50

10

60 70 80 90 100 110 120 130 140 150 160 170 180 190 200 210 220 230 240 250 260 270 280 290 300

Bins

Figure H.2.2 Count of Oil Boiler Models by Input Capacity

Table H.2.3 shows the input capacity bins representing at least a count of 20 out of the total

number of gas boilers (the selected input capacities are marked in bold). The selected input

H-5

 EE-RM/STD-01-350 COMMENT 164

T a e bi H 2 3 .. SIt e ec e d G . I enenc npu tC apaclry ·t B· illS ~ or G as B·l 01 ers C oun t 

Generic Input Capacity Bin Other Input Count Percentage of Total 

Capacity Range 

50 0-62.5 104 7.6% 

75 62.5-87.5 149 10.9% 

100 87.5-112.5 202 14.8% 

125 112.5-137.5 125 9.2% 

150 137.5-162.5 174 12.8% 

175 162.5-187.5 176 12.9% 

200 187.5-212.5 131 9.6% 

225 212.5-237.5 75 5.5% 

250 237.5-275 158 11.6% 

300 275-300 67 4.9% 

Generic Input Capacities for Oil Boilers 

There are 600 models in the reduced set of models developed using the March 2005 GAMA 

Directory.l This set was then divided into bins of lkbtuh. Figure H.2.2 shows the count for each 

1 kbtuh bin. 

70 I ~~-~---- ~~~~~~-- --~-~ 

60 

50 ,-~~---- --~-- ~~--~ --~---. 

40 ~~~- ~~-~- ---~~- ~~~----

-

s::: 

+ 

::J 

0 

() ~- ---- ~-- ----~ "._- --

i "I··· . -~ -~~ ~~ --~~ --~-~I~--- --~--

': tJ ... J~.lt t'~.l.j"~,, J,t .. l1 ..... J .... ~,~.,,: .. IJ 60 70 80 90 100 110 120 130 140 150 160 170 180 190 200 210 220 230 240 250 260 270 280 290 300 

Bins 

Figure H.2.2 Count of Oil Boiler Models by Input Capacity 

Table H.2.3 shows the input capacity bins representing at least a count of20 out of the total 

number of gas boilers (the selected input capacities are marked in bold). The selected input 

H-5 
capacities account for 67.5% of all oil boiler models. The Department decided to pick all the input

capacity bins with at least 20 counts, which gave 10 different generic input capacities none of them

closer than 15 kbtuh. Some of the input capacities were rounded off for convenience.

Table H.2.4 Input Capacity Bins representing 2% of the total number of Oil Boilers

Input Capacity Bin Count Percentage of Total

140 65 10.8%

175 56 9.3%

210 45 7.5%

105 44 7.3%

154 39 6.5%

280 39 6.5%

245 37 6.2%

189 33 5.5%

119 25 4.2%

91 22 3.7%

Table H.2.4 shows the count for expanding of the selected bins to include input capacities

within + o - 5 kbtuh for the 10 selected generic input capacity bins. With the selected ranges the

generic input capacities account for 71.7% of all oil boilers. If the bins are expanded to + or - 7

kbtuh then they account for 91.2% of all oil boilers as shown in Table H.2.5.

Table H.2.5 Selected Generic Input Capacity Bins for Oil Boilers Count

Generic Input Capacity Bin Other Input

Capacity Range

Count Percentage of Total

90 85-95 24 4.0%

105 100-110 50 8.3%

120 115-125 29 4.8%

140 135-145 67 11.2%

155 150-155 40 6.7%

175 170-180 57 9.5%

190 185-195 37 6.2%

210 205-215 46 7.7%

245 240-250 39 6.5%

280 275-285 41 6.8%

 EE-RM/STD-01-350 COMMENT 164

capacities account for 67.5% of all oil boiler models. The Department decided to pick all the input 

capacity bins with at least 20 counts, which gave 1 0 different generic input capacities none of them 

closer than 15 kbtuh. Some of the input capacities were rounded off for convenience. 

T a bi e H 2 4 I • 0 nput c apaclty BO InS representIng 00 t e tota I num b er 0 fOOIB °1 I 01 ers 

Input Capacity Bin Count Percentage of Total 

140 65 10.8% 

175 56 9.3% 

210 45 7.5% 

105 44 7.3% 

154 39 6.5% 

280 39 6.5% 

245 37 6.2% 

189 33 5.5% 

119 25 4.2% 

91 22 3.7% 

Table H.2.4 shows the count for expanding of the selected bins to include input capacities 

within + 0 - 5 kbtuh for the 10 selected generic input capacity bins. With the selected ranges the 

generic input capacities account for 71.7% of all oil boilers. If the bins are expanded to + or - 7 

kbtuh then they account for 91.2% of all oil boilers as shown in Table H.2.5. 

T a e bi H o 2 5 0 SIt e ec e d G enenc ° I npu tC apacHy °t BO InS £ or 01 B 01 C t I 01 ers oun 

Generic Input Capacity Bin Other Input Count Percentage of Total 

Capacity Range 

90 85-95 24 4.0% 

105 100-110 50 8.3% 

120 115-125 29 4.8% 

140 135-145 67 11.2% 

155 150-155 40 6.7% 

175 170-180 57 9.5% 

190 185-195 37 6.2% 

210 205-215 46 7.7% 

245 240-250 39 6.5% 

280 275-285 41 6.8% 

H-6 
H.3 Tables of Model Numbers and Specifications for Non-Weatherized Gas Furnaces

Tables H.3.3 to H.3.95 contain tables of model numbers and specifications for the

non-condensing single-stage , condensing single-stage, non-condensing two-stage, and condensing

two-stage basic model non-weatherized gas furnaces the Department used for the LCC analysis. See

Table H.3.1 and H.3.2 for variable definitions.

Table H.3.1 Variable Definitions

Variable Definition

Models Manufacturer code (see Table H.3.2) and model number

Input Steady-state nameplate input rate in kBtu/h

Output Heating capacity rate in kBtu/h

CFM 0.5 Manufacturer default heating airflow (CFM) at 0.5 in w.g. static pressure (two-stage

furnaces have high and low setting)

Blower Size Blower wheel diameter (in) and width (in)

Motor Size Indoor blower motor horsepower (nominal)

Speed Taps Indoor blower tap default factory setting for heating (Variable for two-stage furnaces)

Air Supply Outlet Area Supply air outlet area (ft2)

FUE Annual Fuel Utilization Efficiency (AFUE) as reported in the GAMA Directory

EAE EAE value in kilowatt hours per year as reported in the GAMA Directory

E PE value in watts as reported in the GAMA Directory

Pre-purge Power burner pre-purge time period (seconds)

Post-purge t : power burner post-purge time period (seconds)

On-Delay C: delay time between burner startup and blower startup (seconds)

Off-Delay r: delay time between burner shutoff and the blower shutoff (seconds)

Table H.3.2 Manufacture Code Definitions

Manufacturer Code Manufacturer Name

Am Amana

Ar American Standard

Ai Armstrong Air

Ca Carrier

Du Ducane

Fr Frigidaire (Nordyne)

Le Lennox

Go Goodman

01 Olsen (ECR)

Rheem

Te Tempstar (ICP)

Th Thermo-Pride

Tr Trane

Yo York

H-7

 EE-RM/STD-01-350 COMMENT 164

H.3 Tables of Model Numbers and Specifications for Non-Weatherized Gas Furnaces 

Tables H.3.3 to H.3.95 contain tables of model numbers and specifications for the 

non-condensing single-stage, condensing single-stage, non-condensing two-stage, and condensing 

two-stage basic model non-weatherized gas furnaces the Department used for the LCC analysis. See 

Table H.3.1 and H.3.2 for variable definitions. 

Table H . 3.1 Variable Definitions 

lVariable Definition 

Models Manufacturer code (see Table H.3.2) and model number 

Input Steady-state nameplate input rate in kBtu/h 

Output Heating capacity rate in kBtu/h 

CFM 0.5 lManufacturer default heating airflow (CFM) at 0.5 in w.g. static pressure (two-stage 

furnaces have high and low setting) 

IBlower Size Blower wheel diameter (in) and width (in) 

Motor Size Indoor blower motor horsepower (nominal) 

Speed Taps Indoor blower tap default factory setting for heating (Variable for two-stage furnaces) 

Air Supply Outlet Area Supply air outlet area (fe) 

~FUE Annual Fuel Utilization Efficiency (AFUE) as reported in the GAMA Directory 

EAE EAE value in kilowatt hours per year as reported in the GAMA Directory 

!PE PE value in watts as reported in the GAMA Directory 

!Pre-purge Power burner pre-purge time period (seconds) 

lPost-purge to: power burner post-purge time period (seconds) 

On-Delay t+: delay time between burner startup and blower startup (seconds) 

Off-Delay r: delay time between burner shutoff and the blower shutoff (seconds) 

Table H.3.2 Manufacture Code Definitions 

Manufacturer Code Manufacturer Name 

~m Amana 

Ar American Standard 

!Ai !Armstrong Air 

Ca Carrier 

rou Ducane 

IFr Frigidaire (N ordyne) 

Le Lennox 

Go Goodman 

01 Olsen (ECR) 

~ Rheem 

Te Tempstar (ICP) 

Th Thermo-Pride 

Iff Trane 

Yo York 

H-7 
H.3.1 Non-Condensing Single-Stage Non-Weatherized Gas F urnaces

Table H.3.3 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 45Btu/h

800 CFM

Non-Condensing Single-Stage

45 kBtu/h 800 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Te - ABA040NH2R 40 33 10x4 1/4 Low 1 . 70 80 . 2 410 57 NA 5 30 NA

Am - CUB040A924C* 40 32 - 80 410 57 NA NA NA NA

Tr - TDD040C924F* 40 31 627 10x6 1/5 Med-Low 1.77 78 322 48 NA NA 45 NA

Tr - TUD040C924K* 40 32 610 10x6 1/5 Med-Low 1.81 80 424 76 NA NA 45 NA

Tr - TUE040A924L * 40 32 610 10x6 1/5 Med-Low 1.81 80 440 71 NA NA 45 NA

Ca - 58DLX045 -08* 42 34 620 10x6 1/5 Med-Low - 80 424 76 15 5 25 NA

Ca - 58STX045-08* 42 34 620 10x6 1 /5 Med-Low - 80 424 76 15 5 25 NA

Ca - 58DLA045 -08 44 35 620 10x6 1 /5 Med-Low - 80 428 57 15 5 25 NA

Ca - 58STA045-08 44 35 620 10x6 1 /5 Med-Low - 80 428 57 15 5 25 NA

Le - G40DF-24A-045-* 44 36 875 10x8 1 /5 Med 1 . 74 80 410 57 15 5 45 NA

Le - G40UH -24A-045-* 44 35 610 10x7 1/5 Low 1 . 81 80 410 57 15 5 45 NA

Le - G50DF-24A-045-* 44 36 875 10x8 1/5 Med 1 . 74 80 590 115 15 5 45 NA

Le - G50UH-24A-045 * 44 35 795 10x7 1/5 Med 1.81 80 471 108 15 5 45 NA

Fr - FG6RA045 *-08A 45 36 570 10x6 1 /5 Low 1 . 75 80 . 5 590 115 30 30 30 NA

Fr - L1 RA045 *08A 45 36 690 10 x 6 1 /5 Low 1 . 75 80 471 108 30 30 30 NA

 EE-RM/STD-01-350 COMMENT 164

H.3.1 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces 

Table H.3.3 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 45Btu/h 

800 CFM 

Non-Condensing Single-Stage 

45 kBtu/h 800 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Te - ABA040NH2R 40 33 10 x 4 1/4 Low 1.70 80.2 410 57 NA 5 30 NA 

Am - CUB040A924C* 40 32 - 80 410 57 NA NA NA NA 

Tr - TDD040C924F* 40 31 627 10 x 6 1/5 Med-Low 1.77 78 322 48 NA NA 45 NA 

Tr - TUD040C924K* 40 32 610 10 x 6 1/5 Med-Low 1.81 80 424 76 NA NA 45 NA 

Tr - TUE040A924L * 40 32 610 10 x 6 1/5 Med-Low 1.81 80 440 71 NA NA 45 NA 

Ca - 58 DLX045-08* 42 34 620 10 x 6 1/5 Med-Low - 80 424 76 15 5 25 NA 

Ca - 58STX045-08* 42 34 620 10 x 6 1/5 Med-Low - 80 424 76 15 5 25 NA 

Ca - 58DLA045-08 44 35 620 10 x 6 1/5 Med-Low - 80 428 57 15 5 25 NA 

Ca - 58ST A045-08 44 35 620 10 x 6 1/5 Med-Low - 80 428 57 15 5 25 NA 

Le - G40DF-24A-045-* 44 36 875 10 x 8 1/5 Med 1.74 80 410 57 15 5 45 NA 

Le - G40UH-24A-045-* 44 35 610 10 x 7 1/5 Low 1.81 80 410 57 15 5 45 NA 

Le - G50DF-24A-045-* 44 36 875 10 x 8 1/5 Med 1.74 80 590 115 15 5 45 NA 

Le - G50UH-24A-045-* 44 35 795 10 x 7 1/5 Med 1.81 80 471 108 15 5 45 NA 

Fr - FG6RA045*-08A 45 36 570 10 x 6 1/5 Low 1.75 80.5 590 115 30 30 30 NA 

Fr - L 1 RA045*08A 45 36 690 10 x 6 1/5 Low 1.75 80 471 108 30 30 30 NA 

H-8 
Table H.3.4 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 45 Btu/h

1200 CFM

Non-Condensing Single-Stage

45 kBtu/h 1200 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output 0.5 Size Size Taps Outlet AFUE Eae PE

purge purge Delay Delay

Area

Te - ABA040NH3R 40 33 615 10x6 1/3 Low 1.70 80 . 2 506 57 NA 5 30 NA

Yo - GY8SO40A12DN11 40 32 1270 10x8 1/2 Med-High 1.84 80 608 72 NA NA NA NA

Yo - GY8SO40A12DN11 40 32 1190 10x8 1/2 Med-High 1.84 80 608 72 NA NA NA NA

Yo - GY8SO40A12UH11 40 32 1190 10x8 1/2 Med-High 1.84 80 510 75 NA NA NA NA

Yo - GY8SO40A12UH11 40 32 1270 10x8 1/2 Med-High 1.84 80 510 75 NA NA NA NA

Yo - P4DNA12NO3201 40 32 1035 10x8 1 /3 Med-High 1 . 84 80 608 72 NA NA 30 NA

Yo - P4HUA12NO3201 40 32 1030 10x7 1 /3 Med-High 1.84 80 510 75 NA NA 30 NA

Yo - PS8A1 2NO40DN1 1 40 32 1220 10x8 1/3 Med-High 1.84 80 608 72 NA NA NA NA

Yo - PS8A1 2NO40UH1 1 40 32 1270 10x8 1/2 Med-High 1.84 80 510 75 NA NA NA NA

Yo - PS8A12NO40UH11 40 32 1190 10x8 1/2 Med-High 1.84 80 510 75 NA NA NA NA

Ca - 58DLX045 -12* 42 34 1040 10x6 1/3 Med -Low - 80 596 57 15 5 25 NA

Ca - 58STX045- 12* 42 34 1040 10x6 1 /3 Med-Low - 80 626 57 15 5 25 NA

Ca - 58DLA045- 12 44 36 1040 10x6 1/3 Med-Low - 80 570 57 15 5 25 NA

Ca - 58STA045 - 12 44 36 1040 10x6 1/3 Med-Low - 80 600 57 15 5 25 NA

Am - ADS80453AN 45 36 1039 10x6 1/3 Med 1 . 70 80 335 75 NA NA NA NA

Am - AMS80453AN 45 36 853 10x6 1/3 Med-Low 1.70 80 335 75 NA NA NA NA

Am - DHS80453AX 45 36 1045 10x6 1/2 Low 3 . 13 80 656 75 NA NA NA NA

Am - DMS80453AN 45 36 853 10x6 1/3 Med-Low 1.70 80 335 75 NA NA NA NA

Go - GDT045-3 45 36 1070 10x6 1/3 Med 1 . 70 80 335 75 NA NA 30 NA

Go - GMT045-3 45 36 669 10x6 1 /3 Low 1 . 91 80 335 75 NA NA 30 NA

Go - GMTH045 -3 45 36 - 80 656 75 NA NA NA NA

Am - GCIC045**30 46 37 560 9 x 8 1/3 Low 1 . 75 80 356 80 NA 15 30 NA

Am - GUIC045**30 46 37 575 9x8 1 /3 Low 2 . 10 80 332 69 NA 15 30 NA

Am - GUID045**30 46 37 575 10x7 1 /3 Low 2. 08 80 466 78 NA 15 30 NA

Am - GUIE045**30 46 37 - 80 419 80 NA NA NA NA

Table H.3.5 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 50 Btu/h

800 CFM

Non-Condensing Single-Stage

50 kBtu/h 800 CFM

Models Input Output CFM

0.5

Blower

Size

Motor

Size

Speed

Taps

Air

Supply

Outlet AFUE Eae PE

Prepurge

Postpurge

OnDelayOffDelay

Area

Th - MDA1-50 50 40 730 0 1/5 High 1.88 81 245 100 NA NA 60 NA

Th - MDA 50 50 40 420 0 1/5 Low 2.13 81 226 100 NA NA 60 NA

Th - MHA1-50 50 40 830 0 1/5 High 1.88 80 240 100 NA NA 60 NA

Th - MHA 50 50 40 430 0 1/5 Low 2.13 81 221 87 NA NA 60 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.4 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 45 Btu/h 

1200 CFM 

Non-Condensing Single-Stage 

45 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Oft0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Te - ABA040NH3R 40 33 615 10 x 6 1/3 Low 1.70 80.2 506 57 NA 5 30 NA 

Yo - GY8S040A12DN11 40 32 1270 10 x 8 1/2 Med-High 1.84 80 608 72 NA NA NA NA 

Yo - GY8S040A12DN11 40 32 1190 10 x 8 1/2 Med-High 1.84 80 608 72 NA NA NA NA 

Yo - GY8S040A12UH11 40 32 1190 10 x 8 1/2 Med-High 1.84 80 510 75 NA NA NA NA 

Yo - GY8S040A12UH11 40 32 1270 10 x 8 1/2 Med-High 1.84 80 510 75 NA NA NA NA 

Yo - P4DNA12N03201 40 32 1035 10 x 8 1/3 Med-High 1.84 80 608 72 NA NA 30 NA 

Yo - P4HUA12N03201 40 32 1030 10 x 7 1/3 Med-High 1.84 80 510 75 NA NA 30 NA 

Yo - PS8A12N040DN11 40 32 1220 10 x 8 1/3 Med-High 1.84 80 608 72 NA NA NA NA 

Yo - PS8A12N040UH11 40 32 1270 10 x 8 1/2 Med-High 1.84 80 510 75 NA NA NA NA 

Yo - PS8A12N040UH11 40 32 1190 10 x 8 1/2 Med-High 1.84 80 510 75 NA NA NA NA 

Ca - 58D LX045-12* 42 34 1040 10 x 6 1/3 Med-Low - 80 596 57 15 5 25 NA 

Ca - 58STX045-12* 42 34 1040 10 x 6 1/3 Med-Low - 80 626 57 15 5 25 NA 

Ca - 58DLA045-12 44 36 1040 10 x 6 1/3 Med-Low - 80 570 57 15 5 25 NA 

Ca - 58STA045-12 44 36 1040 10 x 6 1/3 Med-Low - 80 600 57 15 5 25 NA 

Am - ADS80453AN 45 36 1039 10 x 6 1/3 Med 1.70 80 335 75 NA NA NA NA 

Am - AMS80453AN 45 36 853 10 x 6 1/3 Med-Low 1.70 80 335 75 NA NA NA NA 

Am - DHS80453AX 45 36 1045 10 x 6 1/2 Low 3.13 80 656 75 NA NA NA NA 

Am - DMS80453AN 45 36 853 10 x 6 1/3 Med-Low 1.70 80 335 75 NA NA NA NA 

Go - GDT045-3 45 36 1070 10 x 6 1/3 Med 1.70 80 335 75 NA NA 30 NA 

Go - GMT045-3 45 36 669 10 x 6 1/3 Low 1.91 80 335 75 NA NA 30 NA 

Go - GMTH045-3 45 36 - 80 656 75 NA NA NA NA 

Am - GCIC045**30 46 37 560 9x8 1/3 Low 1.75 80 356 80 NA 15 30 NA 

Am - GUIC045**30 46 37 575 9x8 1/3 Low 2.10 80 332 69 NA 15 30 NA 

Am - GUID045**30 46 37 575 10 x 7 1/3 Low 2.08 80 466 78 NA 15 30 NA 

Am - GUIE045**30 46 37 - 80 419 80 NA NA NA NA 

Table H.3.5 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 50 Btu/h 

800 CFM 

Non-Condensing Single-Stage 

50 kBtu/h 800 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- 00-

0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Th - MDA1-50 50 40 730 0 1/5 High 1.88 81 245 100 NA NA 60 NA 

Th- MDA-50 50 40 420 0 1/5 Low 2.13 81 226 100 NA NA 60 NA 

Th- MHA1-50 50 40 830 0 1/5 High 1.88 80 240 100 NA NA 60 NA 

Th- MHA-50 50 40 430 0 1/5 Low 2.13 81 221 87 NA NA 60 NA 

H-9 
Table H.3.6 Non-Condensing Single-Stage Non -Weatherized Gas Furnaces at 50 Btu/h

1200 CFM

Non-Condensin g Single-Stage

50 kBtu/h 1 200 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output 0.5 Size Size Taps Outlet AFUE Eae PE

purge purge Delay Delay

Area

Du - DPGB050A3* 308 87 750 10x6 1/3 Low 1.51 80 308 87 15 NA 30 NA

Du - FPBB05OA3* 304 87 805 10x6 1/3 Low 1.73 80 304 87 15 15 30 NA

Ar- G1D80BR05OD12B`--*** 524 88 719 10x8 1/3 Low 2.06 80 524 88 NA NA NA NA

Ar - G1 D80BT050D12B*-*** 380 88 713 10x6 1/3 Low 2.24 80 380 88 NA NA NA NA

Ar- GlN80BR050D12A*-*** 524 82 716 10x6 1/3 Low 1.68 80 524 82 15 15 30 NA

Ar - G1 N80BT050D12A`--*** 390 88 10x6 1/3 1.83 80 390 88 15 15 30 NA

Ar - G1 N80BU050D12A'--*** 380 88 713 10x6 1/3 Low 1.83 80 380 88 15 15 30 NA

Yo - G8C05012M(DB,UB)12 451 65 814 10x8 1/3 Low 2.22 80 451 65 NA NA 30 NA

Yo - G8C05012M(DB,UB)12 451 65 849 10x8 1/3 Low 2.22 80 451 65 NA NA 30 NA

Yo - G8C05012M(DB,UB)12 451 65 818 10x8 1/3 Low 2.22 80 451 65 NA NA 30 NA

OI -GTM 50 337 60 555 10x8 1/3 Low 2.29 80 337 60 15 5 30 180

OI - GTM 50 337 60 555 10x8 1/3 Low 2.29 80 337 60 15 5 30 180

Du - MPGA050B3* 308 87 750 10x6 1/3 Low 1.63 80 308 87 15 15 30 NA

Te - N8MPL050B12 565 81 1035 11 x 8 1/2 Med-High 1.80 80 565 81 3 30 30 NA

Te - N8MPN05OB12 565 81 1035 11 x 8 1/2 Med-High 1.80 80 565 81 3 30 30 NA

Rh - RGLH-05EAUER 469 73 955 11 x 6 1/2 Med-Low 1.80 82 469 73 NA NA NA NA

Rh - RGLJ-05EAUER 469 73 955 11 x 6 1/2 Med-Low 1.78 80 469 73 30 5 20 NA

Rh - RGLN-05(E,N)AUER 657 99 - 80 657 99 NA NA NA NA

Rh - RGPH-05EAUER 503 96 860 11 x 6 1/2 Med-Low 1.78 81 503 96 NA NA NA NA

Rh - RGPJ-05EAUER 456 96 860 11 x 6 1/2 Med-Low 1.88 80 456 96 30 5 20 NA

Rh - RGPN-05(E,N)AUER 621 67 860 11 x 6 1/2 Med-Low 1.78 80 621 67 NA NA NA NA

Rh - RGPP-05(E,N)AUER 650 64 860 11 x 6 1/2 Med-Low 1.78 80 650 64 NA NA NA NA

Te - T8DNL050B12 586 85 1088 11x8 1/2 Med-High 1.80 80 586 85 3 30 30 NA

Te - T8MPL05OB12 605 83 1035 11 x 8 1/2 Med-High 1.80 80 605 83 3 30 30 NA

Te - T8MPN050B12 605 83 1035 11 x 8 1 /2 Med-High 1.80 80 605 83 3 30 30 NA

Fr - L1 RA054*12A 421 72 720 10 x 6 1 /3 Low 1.75 80 421 72 30 30 30 NA

Table H.3.7 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 60 Btu/h

800 CFM

Non-Condensing Single-Stage

60 kBtu/h 800 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Te - ABA060NH2R 60 49 560 10x4 1/4 Med-Low 1.70 80.2 475 57 NA 5 30 NA

Tr - TDD060C924F* 60 48 859 10x7 1/5 Med-High 1.77 80 575 70 NA NA 45 NA

Tr - TUD060C924K* 60 47 734 10x6 1/5 Med-High 1.81 80 611 77 NA NA 45 NA

Ca - 58DLX070-08* 63 51 600 10x6 1/5 Med-Low - 80 510 57 15 5 25 NA

Ca - 58STX070-08* 63 51 600 10x6, 1/5 Med-Low - 80 510 57 15 5 25 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.6 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 50 Btu/h 

1200 CFM 

Non-Condensing Single-Stage 

50 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0,5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Du - DPGB050A3* 308 87 750 10 x 6 1/3 Low 1,51 80 308 87 15 NA 30 NA 

Du - FPBB050A3* 304 87 805 10 x 6 1/3 Low 1,73 80 304 87 15 15 30 NA 

Ar - G1 D80BR050D12B*-*** 524 88 719 10x 8 1/3 Low 2,06 80 524 88 NA NA NA NA 

Ar - G1D80BT050D12B*-*** 380 88 713 10 x 6 1/3 Low 2.24 80 380 88 NA NA NA NA 

Ar - G1N80BR050D12A*-*** 524 82 716 10 x 6 1/3 Low 1,68 80 524 82 15 15 30 NA 

Ar - G1N80BT050D12A*-*** 390 88 10 x 6 1/3 1.83 80 390 88 15 15 30 NA 

Ar - G1 N80BU050D12A*-*** 380 88 713 10 x 6 113 Low 1,83 80 380 88 15 15 30 NA 

Yo - G8C05012M(DB,UB)12 451 65 814 10 x 8 1/3 Low 2,22 80 451 65 NA NA 30 NA 

Yo - G8C05012M(DB,UB)12 451 65 849 10 x 8 1/3 Low 2,22 80 451 65 NA NA 30 NA 

Yo - G8C05012M(DB,UB)12 451 65 818 10 x 8 1/3 Low 2.22 80 451 65 NA NA 30 NA 

01- GTM 50 337 60 555 10 x 8 1/3 Low 2.29 80 337 60 15 5 30 180 

01- GTM 50 337 60 555 10 x 8 1/3 Low 2,29 80 337 60 15 5 30 180 

Du - MPGA050B3* 308 87 750 10 x 6 1/3 Low 1,63 80 308 87 15 15 30 NA 

Te - N8MPL050B12 565 81 1035 11 x 8 1/2 Med-High 1,80 80 565 81 3 30 30 NA 

Te - N8MPN050B12 565 81 1035 11 x 8 1/2 Med-High 1,80 80 565 81 3 30 30 NA 

Rh - RGLH-05EAUER 469 73 955 11 x 6 1/2 Med-Low 1,80 82 469 73 NA NA NA NA 

Rh - RGLJ-05EAUER 469 73 955 11 x 6 1/2 Med-Low 1,78 80 469 73 30 5 20 NA 

Rh - RGLN-05(E,N)AUER 657 99 - 80 657 99 NA NA NA NA 

Rh - RGPH-05EAUER 503 96 860 11 x 6 1/2 Med-Low 1,78 81 503 96 NA NA NA NA 

Rh - RGPJ-05EAUER 456 96 860 11 x 6 1/2 Med-Low 1,88 80 456 96 30 5 20 NA 

Rh - RGPN-05(E,N)AUER 621 67 860 11 x 6 112 Med-Low 1,78 80 621 67 NA NA NA NA 

Rh - RGPP-05(E,N)AUER 650 64 860 11 x 6 1/2 Med-Low 1,78 80 650 64 NA NA NA NA 

Te - T8DNL050B12 586 85 1088 11 x 8 1/2 Med-High 1,80 80 586 85 3 30 30 NA 

Te - T8MPL050B12 605 83 1035 11 x 8 1/2 Med-High 1,80 80 605 83 3 30 30 NA 

Te - T8MPN050B12 605 83 1035 11 x 8 1/2 Med-High 1,80 80 605 83 3 30 30 NA 

Fr - L 1 RA054*12A 421 72 720 10 x 6 1/3 Low 1,75 80 421 72 30 30 30 NA 

Table H.3.7 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 60 Btu/h 

800 CFM 

Non-Condensing Single-Stage 

60 kBtu/h 800 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Oft0,5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Te - ABA060NH2R 60 49 560 10 x 4 1/4 Med-Low 1,70 80,2 475 57 NA 5 30 NA 

Tr - TDD060C924F* 60 48 859 10 x 7 115 Med-High 1,77 80 575 70 NA NA 45 NA 

Tr - TUD060C924K* 60 47 734 10 x 6 1/5 Med-High 1,81 80 611 77 NA NA 45 NA 

Ca - 58DLX070-08* 63 51 600 10 x6 1/5 Med-Low - 80 510 57 15 5 25 NA 

Ca - 58STX070-08* 63 51 600 10 x 6 1/5 Med-Low - 80 510 57 15 5 25 NA 

H-IO 
Table H.3.8 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 60 Btu/h

1200 CFM

Non-Condensing Single-Stage

60 kBtu/h 1200 CFM

Models Input Output CFM

0.5

Blower

Size

Motor

Size

Speed

Taps

Air

Supply

Outlet AFUE Eae PE

Prepurge

Postpurge

OnDelay

OffDelay

Area

Yo - GY8S060A12DN11 57 46 1190 10x8 1/2 Med-High 1.84 80 784 64 NA NA NA NA

Yo - GY8S060A1 2DN1 1 57 46 1280 10x8 1/2 Med-High 1.84 80 784 64 NA NA NA NA

Yo - GY8S060A12UH11 57 46 1280 10x8 1/2 Med-High 1.84 80 847 73 NA NA NA NA

Yo - GY8S060A12UH11 57 46 1190 10x8 1/2 Med-High 1.84 80 847 73 NA NA NA NA

Yo - P4DNA12NO4801 57 46 1035 10x8 1 /3 Med-High 1.84 80 784 64 NA NA 30 NA

Yo - P4HUA12NO4801 57 46 1030 10 x 7 1/3 Med-High 1.84 80 847 73 NA NA 30 NA

Yo - PS8A12N060DN1 1 57 46 1150 10x8 1 /3 Med-H ig h 1.84 80 784 64 NA NA NA NA

Yo-PS8A12NO60UH11 57 46 1280 10x8 1/2 Med-High 1.84 80 847 73 NA NA NA NA

Yo - PS8A12N060UH1 1 57 46 1190 10x8 1/2 Med-High 1.84 80 847 73 NA NA NA NA

Te - ABA060NH3R 60 49 600 10x6 1 /3 Low 1.70 80.2 573 61 NA 5 30 NA

Am - CDB060A936D* 60 48 80 912 73 NA NA NA NA

Am - CUB060A936C* 60 47 80 769 71 NA NA NA NA

Fr - FG6RA060*-12A 60 48 730 10x6 1 /3 Low 1.75 81 482 75 30 30 30 NA

Fr- FG6RK060*-12A 60 48 780 10x6 1/3 Low 1.75 80 471 50 30 30 30 NA

Tr - TDD060C936F* 60 48 1000 11 x 7 1/2 Med-Low 1.77 80 912 73 NA NA 45 NA

Tr - TDE06OA936M* 60 48 1000 11 x 7 1/2 Med-Low 1.77 80 912 73 NA NA 45 NA

Tr - TUD060C936K* 60 47 973 10x7 1/3 Med-Low 1.81 80 769 71 NA NA 45 NA

Tr - TUE060A936L* 60 47 973 10x7 1/3 Med-Low 1.81 80 769 71 NA NA 45 NA

Ca - 58DLX070-12* 63 51 1050 10x6 1/3 Med-Low 80 723 59 15 5 25 NA

Ca - 58STX070-12* 63 51 1050 10x6 1 /3 Med-Low 80 761 59 15 5 25 NA

Table H.3.9 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 70 Btu/h

1200 CFM

Non-Condensing Single-Stage

60 kBtu/h 1600 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

ABA060NH4R 60 49 1025 10x8 1/2 Low 2.10 80.2 1034 53 NA 5 30 NA

58DLX070-16* 63 51 1280 11x8 1/2 Med-Low - 80 874 60 15 5 25 NA

58STX070-16* 63 51 1280 11x8 1/2 Med-Low - 80 922 60 15 5 25 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.8 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 60 Btu/h 

1200 CFM 

Non-Condensing Single-Stage 

60 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Yo - GY8S060A12DN11 57 46 1190 10 x 8 112 Med-High 1.84 80 784 64 NA NA NA NA 

Yo - GY8S060A12DN11 57 46 1280 10 x 8 1/2 Med-High 1.84 80 784 64 NA NA NA NA 

Yo - GY8S060A12UH11 57 46 1280 10 x 8 1/2 Med-High 1.84 80 847 73 NA NA NA NA 

Yo - GY8S060A12UH11 57 46 1190 10 x 8 112 Med-High 1.84 80 847 73 NA NA NA NA 

Yo - P4DNA12N04801 57 46 1035 10 x 8 1/3 Med-High 1.84 80 784 64 NA NA 30 NA 

Yo - P4HUA12N04801 57 46 1030 10 x 7 1/3 Med-High 1.84 80 847 73 NA NA 30 NA 

Yo - PS8A12N060DN11 57 46 1150 10 x 8 113 Med-High 1.84 80 784 64 NA NA NA NA 

Yo - PS8A 12N060UH11 57 46 1280 10 x 8 1/2 Med-High 1.84 80 847 73 NA NA NA NA 

Yo - PS8A12N060UH11 57 46 1190 10 x 8 1/2 Med-High 1.84 80 847 73 NA NA NA NA 

Te - ABA060NH3R 60 49 600 10 x 6 113 Low 1.70 80.2 573 61 NA 5 30 NA 

Am - CDB060A936D* 60 48 - 80 912 73 NA NA NA NA 

Am - CUB060A936C* 60 47 - 80 769 71 NA NA NA NA 

Fr- FG6RA060*-12A 60 48 730 10 x 6 1/3 Low 1.75 81 482 75 30 30 30 NA 

Fr - FG6RK060*-12A 60 48 780 10 x 6 1/3 Low 1.75 80 471 50 30 30 30 NA 

Tr - TDD060C936F* 60 48 1000 11 x 7 1/2 Med-Low 1.77 80 912 73 NA NA 45 NA 

Tr - TDE060A936M* 60 48 1000 11 x 7 1/2 Med-Low 1.77 80 912 73 NA NA 45 NA 

Tr - TUD060C936K* 60 47 973 10 x 7 1/3 Med-Low 1.81 80 769 71 NA NA 45 NA 

Tr - TU E060A936L * 60 47 973 10 x 7 1/3 Med-Low 1.81 80 769 71 NA NA 45 NA 

Ca - 58DLX070-12* 63 51 1050 10 x 6 1/3 Med-Low - 80 723 59 15 5 25 NA 

Ca - 58STX070-12* 63 51 1050 10 x 6 113 Med-Low - 80 761 59 15 5 25 NA 

Table H.3.9 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 70 Btu/h 

1200 CFM 

Non-Condensing Single-Stage 

60 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

ABA060NH4R 60 49 1025 10 x 8 1/2 Low 2.10 80.2 1034 53 NA 5 30 NA 

58DLX070-16* 63 51 1280 11 x 8 1/2 Med-Low - 80 874 60 15 5 25 NA 

58STX070-16* 63 51 1280 11 x 8 1/2 Med-Low - 80 922 60 15 5 25 NA 

H-ll 
Table H.3.10 Non-Condensing Single -Stage Non-Weatherized Gas Furnaces at 70 Btu/h

1600 CFM

Non-Condensing Single-Stage

70 kBtu/h 1600 CFM

Air

CFM Motor Speed Supply Pre- Post- On- Off- Models Input Output 0 5 Blower Size AFUE Eae PE Size Taps Outlet purge purge Delay Delay

Area

Ca - 58DLA070-16 66 53 1280 11x8 1/2 Med-Low - 80 837 60 15 5 25 NA

Ca - 58STA070-16 66 53 1280 11x8 1/2 Med-Low - 80 883 60 15 5 25 NA

Le - G40UH48B-070-** 66 54 1420 10 x 10 1/2 Med-Low 2.21 80 800 111 15 5 45 NA

Le - G50UH-48B-070-** 66 54 1420 10 x 10 1/2 Med-Low 2.21 80 800 111 15 5 45 NA

Am - GCIC070**40 69 55 850 10x6 1/2 Low 1.75 80 522 85 NA 15 30 NA

Am - GUIC070**40 69 55 975 10x6 1/2 Low 2.10 80 549 72 NA 15 30 NA

Am - GUID070**40 69 55 975 10x7 1/2 Low 2.08 80 585 77 NA 15 30 NA

Am - GUIE070**40 69 55 - 80 565 89 NA NA NA NA

Am - AMS80704BN 70 56 1291 10x8 1/2 Med-Low 2.18 80 559 75 NA NA NA NA

Am - DHS80704BX 70 56 1519 10x8 3/4 Med 2.18 80 716 75 NA NA NA NA

Am - DMS80704BN 70 56 1291 10 x 8 1/2 Med-Low 2.18 80 559 75 NA NA NA NA

Go - GMT070-4 70 56 1320 10 x 8 1/2 Med 2.38 80 559 75 NA NA 30 NA

Go - GMTH070-4 70 56 - 80 716 75 NA NA NA NA

Fr - FG6RA072*-16B 72 59 1140 10 x 10 1/2 Low 2.50 81 500 75 30 30 30 NA

Fr - FG6RK072*-16B 72 57 955 10 x 10 1/2 Low 2.50 80 476 50 30 30 30 NA

Fr - L1 RA072*16B 72 58 1305 10 x 10 1/2 Med-Low 2.50 80 637 75 30 30 30 NA

Table H.3.11 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 75 Btu/h

1200 CFM

Non-Condensing Single-Stage

75 kBtu/h 1200 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output 0.5 Size Size Taps Outlet AFUE Eae PE

purge purge Delay Delay

Area

Du - DPGB075A3* 75 60 1010 10x6 1/3 Med 1.51 80 578 87 15 NA 30 NA

Du - FPBB075A3* 75 61 1160 10x6 1/3 Med 1.73 80 635 87 15 15 30 NA

Ar- G1N80BR075D12A*-*** 75 60 685 10x6 1/3 Low 1.68 80 727 86 15 15 30 NA

Ar- G1N80BT075D12A*-*** 75 60 10x6 1/3 1.83 80 570 93 15 15 30 NA

Ar- G1N80BU075D12A*-*** 75 60 677 10x6 1/3 Low 1.83 80 569 93 15 15 30 NA

Yo - G8C07512M(DB,UB)12 75 60 846 10x8 1/3 Low 2.22 80 665 70 NA NA 30 NA

Yo - G8C07512M(DB,UB)12 75 60 827 10x8 1/3 Low 2.22 80 665 70 NA NA 30 NA

Yo - G8C07512M(DB,UB)12 75 60 865 10x8 1/3 Low 2.22 80 665 70 NA NA 30 NA

Th - MDA1-75 75 60 1220 1/3 High 2.00 80 591 78 NA NA 60 NA

Du - MPGA075B3* 75 61 1010 10 x 6 1/3 Med 1.63 80 578 87 15 15 30 NA

Te - N8MPL075B12 75 60 1118 11 x 8 1/2 Med-High 1.80 80 ### 82 3 30 30 NA

Te - N8MPN075B12 75 60 1118 11x8 1/2 Med-High 1.80 80 ### 82 3 30 30 NA

Rh - RGLH-07EAUER 75 60 905 11 x 6 1/2 Med-Low 2.28 80.5 ### 64 NA NA NA NA

Rh - RGLJ-07EAUER 75 60 1050 11 x 6 1/2 Med 2.27 80 ### 64 30 5 20 NA

Rh - RGLN-07(E,N)AMER 75 60 - 80 ### 64 NA NA NA NA

Rh - RGPH-07EAUER* 75 60 880 11x6 1/2 Med-Low 2.27 80.6 942 74 NA NA NA NA

Rh - RGPJ-07EAUER 75 60 1010 11x6 1/2 Med 2.45 80 942 74 30 5 20 NA

Rh - RGPN-07(E,N)AMER 75 60 977 11x7 1/2 Med-Low 2.27 80 935 60 NA NA NA NA

Rh - RGPP-07(E,N)AMER 75 60 1118 11x7 1/2 Med 2.27 80 ### 66 NA NA NA NA

Te - T8DNL075B12 75 61 861 11x8 1/3 Med-High 1.80 80 977 82 3 30 30 NA

Te-T81VIPL0751312 75 60 1118 11x8 1/2 Med-High 1.80 80 ### 82 3 30 30 NA

Te - T8MPN075B12 75 60 1118 11 x8 1/2 Med-High 1.80 80 ### 82 3 30 30 NA

H-12

 EE-RM/STD-01-350 COMMENT 164

Table H.3.10 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 70 Btu/h 

1600 CFM 

Non-Condensing Single-Stage 

70 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay 

Area 

Ca - 5SDLA070-16 66 53 12S0 11 x S 1/2 Med-Low - SO S37 60 15 5 25 NA 

Ca - 5SSTA070-16 66 53 1280 11 x 8 1/2 Med-Low - 80 8S3 60 15 5 25 NA 

Le - G40UH-48B-070-** 66 54 1420 10 x 10 1/2 Med-Low 2.21 80 SOO 111 15 5 45 NA 

Le - G50UH-48B-070-** 66 54 1420 10 x 10 1/2 Med-Low 2.21 80 800 111 15 5 45 NA 

Am - GCIC070**40 69 55 S50 10x6 1/2 Low 1.75 80 522 85 NA 15 30 NA 

Am - GUIC070**40 69 55 975 10 x 6 1/2 Low 2.10 SO 549 72 NA 15 30 NA 

Am - GUID070**40 69 55 975 10 x 7 1/2 Low 2.08 SO 585 77 NA 15 30 NA 

Am - GUIE070**40 69 55 - 80 565 89 NA NA NA NA 

Am - AMSS0704BN 70 56 1291 10 x 8 1/2 Med-Low 2.18 80 559 75 NA NA NA NA 

Am - DHSS0704BX 70 56 1519 10 x 8 3/4 Med 2.18 80 716 75 NA NA NA NA 

Am - DMS80704BN 70 56 1291 10 x 8 1/2 Med-Low 2.18 80 559 75 NA NA NA NA 

Go - GMT070-4 70 56 1320 10 x S 1/2 Med 2.38 80 559 75 NA NA 30 NA 

Go - GMTH070-4 70 56 - SO 716 75 NA NA NA NA 

Fr - FG6RA072*-16B 72 59 1140 10 x 10 1/2 Low 2.50 S1 500 75 30 30 30 NA 

Fr - FG6RK072*-16B 72 57 955 10x 10 1/2 Low 2.50 80 476 50 30 30 30 NA 

Fr - L 1 RA072*16B 72 58 1305 10 x 10 1/2 Med-Low 2.50 80 637 75 30 30 30 NA 

Table H.3.11 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 75 Btu/h 

1200 CFM 

Non-Condensing Single-Stage 

75 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Du - DPGB075A3* 75 60 1010 10 x 6 1/3 Med 1.51 80 57S 87 15 NA 30 NA 

Du - FPBB075A3* 75 61 1160 10 x 6 1/3 Med 1.73 80 635 S7 15 15 30 NA 

Ar - G1N80BR075D12A*-*** 75 60 685 10 x 6 1/3 Low 1.68 80 727 86 15 15 30 NA 

Ar - G1NSOBT075D12A*-*** 75 60 10 x 6 1/3 1.83 80 570 93 15 15 30 NA 

Ar - G1N80BU075D12A*-*** 75 60 677 10 x 6 1/3 Low 1.S3 SO 569 93 15 15 30 NA 

Yo - G8C07512M(DB,UB)12 75 60 846 10 x S 1/3 Low 2.22 80 665 70 NA NA 30 NA 

Yo - G8C07512M(DB,UB)12 75 60 827 10 x 8 1/3 Low 2.22 80 665 70 NA NA 30 NA 

Yo - G8C07512M(DB,UB)12 75 60 865 10 x S 1/3 Low 2.22 SO 665 70 NA NA 30 NA 

Th - MDA1-75 75 60 1220 1/3 High 2.00 SO 591 78 NA NA 60 NA 

Du - MPGA075B3* 75 61 1010 10 x 6 1/3 Med 1.63 80 578 87 15 15 30 NA 

Te - NSMPL075B12 75 60 1118 11 x S 1/2 Med-High 1.80 SO ### 82 3 30 30 NA 

Te - N8MPN075B12 75 60 1118 11 x S 1/2 Med-High 1.80 SO ### 82 3 30 30 NA 

Rh - RGLH-07EAUER 75 60 905 11 x 6 1/2 Med-Low 2.28 80.5 ### 64 NA NA NA NA 

Rh - RGLJ-07EAUER 75 60 1050 11 x 6 1/2 Med 2.27 SO ### 64 30 5 20 NA 

Rh - RGLN-07(E,N)AMER 75 60 - SO ### 64 NA NA NA NA 

Rh - RGPH-07EAUER* 75 60 880 11 x6 1/2 Med-Low 2.27 SO.6 942 74 NA NA NA NA 

Rh - RGPJ-07EAUER 75 60 1010 11 x 6 1/2 Med 2.45 SO 942 74 30 5 20 NA 

Rh - RGPN-07(E,N)AMER 75 60 977 11 x 7 1/2 Med-Low 2.27 SO 935 60 NA NA NA NA 

Rh - RGPP-07(E,N)AMER 75 60 1118 11 x 7 1/2 Med 2.27 SO ### 66 NA NA NA NA 

Te - T8DNL075B12 75 61 861 11 x S 1/3 Med-High 1.80 SO 977 82 3 30 30 NA 

Te - TSMPL075B12 75 60 111S 11 x 8 1/2 Med-High 1.80 SO ### 82 3 30 30 NA 

Te - T8MPN075B12 75 60 111S 11 x 8 1/2 Med-High 1.80 SO ### 82 3 30 30 NA 

R-12 
Table H.3.12 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 75 Btu/h

1600 CFM

Non-Condensing Single-Stage

75 kBtu/h 1600 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output AFUE Eae PE 0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Du - DPGB075A4* 75 60 1550 12x9 1/2 Med 1.97 80 1106 87 15 NA 30 NA

Du - FPBB075A4* 75 61 1500 10x6 1/2 Med 1.73 80 940 87 15 15 30 NA

Ar - G1 N80BR075D16B*-*** 75 60 1039 10x8 1/2 Low 2.06 80 757 90 15 15 30 NA

Ar - G1N80BT075D16B*-*** 75 60 10x8 1/2 2.24 80 575 89 15 15 30 NA

Ar - G1N80BU075D16B*-*** 75 60 986 10x8 1/2 Low 2.24 80 574 89 15 15 30 NA

Yo - G8C07516M(DC,UC)12 75 60 1149 10 x 10 1/2 Low 2.71 80 828 70 NA NA 30 NA

Yo - G8C07516M(DC,UC)12 75 60 1175 10x 10 1/2 Low 2.71 80 828 70 NA NA 30 NA

Yo - G8C07516M(DC,UC)12 75 60 1198 10 x 10 1/2 Low 2.71 80 828 70 NA NA 30 NA

Th - MDA-75 75 59 850 1/2 Low 2.13 79.5 434 70 NA NA 60 NA

Th - MHA-75 75 59 470 1/2 Low 2.13 80 279 69 NA NA 60 NA

Du - MPGA075B4* 75 61 1550 12x9 1/2 Med 2.12 80 1106 87 15 15 30 NA

Te - N8MPL075F16 75 60 1343 11 x 10 1/2 Med-High 2.26 80 1188 50 3 30 30 NA

Te - N8MPN075F16 75 60 1343 11 x 10 1/2 Med-High 2.26 80 1188 50 3 30 30 NA

Rh - RGLH-07EAMGR 75 60 1495 11 x 7 3/4 Med-Low 1.80 80.8 937 72 NA NA NA NA

Rh - RGLJ-07EAMGR 75 60 1495 11 x 7 1/2 Med 2.27 80 937 72 30 5 20 NA

Rh - RGLN-07(E,N)AMGR 75 60 - 80 1277 63 NA NA NA NA

Rh - RGPH-07EAMGR 75 60 1395 11 x 7 3/4 Med-Low 2.27 80.5 941 73 NA NA NA NA

Rh - RGPJ-07EAMGR 75 60 1395 11 x 7 1/2 Med 2.45 80 941 73 30 5 20 NA

Rh - RGPN-07(E,N)AMGR 75 60 1395 11 x 7 3/4 Med-Low 2.27 80 1190 57 NA NA NA NA

Rh - RGPP-07(E,N)AMGR 75 60 1395 11 x 7 1/2 Med 2.27 80 1323 84 NA NA NA NA

Te - T8DNL075F16 75 61 1309 11 x 10 1/2 Med-High 2.26 80 1263 78 3 30 30 NA

Te - T8MPL075F16 75 60 1343 11 x 10 1/2 Med-High 2.26 80 1208 87 3 30 30 NA

Te - T8MPN075F16 75 60 1343 11 x 10 1/2 Med-High 2.26 80 1208 87 3 30 30 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.12 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 75 Btu/h 

1600 CFM 

Non-Condensing Single-Stage 

75 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Du - DPGB075A4* 75 60 1550 12 x 9 1/2 Med 1.97 80 1106 87 15 NA 30 NA 

Du - FPBB075A4* 75 61 1500 10 x 6 1/2 Med 1.73 80 940 87 15 15 30 NA 

Ar - G1 N80BR075D16B*-*** 75 60 1039 10 x 8 1/2 Low 2.06 80 757 90 15 15 30 NA 

Ar - G1N80BT075D16B*-*** 75 60 10 x 8 1/2 2.24 80 575 89 15 15 30 NA 

Ar - G1N80BU075D16B*-*** 75 60 986 10 x 8 1/2 Low 2.24 80 574 89 15 15 30 NA 

Yo - G8C07516M(DC,UC)12 75 60 1149 10 x 10 1/2 Low 2.71 80 828 70 NA NA 30 NA 

Yo - G8C07516M(DC,UC)12 75 60 1175 10x 10 1/2 Low 2.71 80 828 70 NA NA 30 NA 

Yo - G8C07516M(DC,UC)12 75 60 1198 10 x 10 1/2 Low 2.71 80 828 70 NA NA 30 NA 

Th - MDA-75 75 59 850 1/2 Low 2.13 79.5 434 70 NA NA 60 NA 

Th - MHA-75 75 59 470 1/2 Low 2.13 80 279 69 NA NA 60 NA 

Du - MPGA075B4* 75 61 1550 12 x 9 1/2 Med 2.12 80 1106 87 15 15 30 NA 

Te - N8MPL075F16 75 60 1343 11 x 10 1/2 Med-High 2.26 80 1188 50 3 30 30 NA 

Te - N8MPN075F16 75 60 1343 11 x 10 1/2 Med-High 2.26 80 1188 50 3 30 30 NA 

Rh - RGLH-07EAMGR 75 60 1495 11 x 7 3/4 Med-Low 1.80 80.8 937 72 NA NA NA NA 

Rh - RGLJ-07EAMGR 75 60 1495 11 x 7 1/2 Med 2.27 80 937 72 30 5 20 NA 

Rh - RGLN-07(E,N)AMGR 75 60 - 80 1277 63 NA NA NA NA 

Rh - RGPH-07EAMGR 75 60 1395 11 x 7 3/4 Med-Low 2.27 80.5 941 73 NA NA NA NA 

Rh - RGPJ-07EAMGR 75 60 1395 11 x 7 1/2 Med 2.45 80 941 73 30 5 20 NA 

Rh - RGPN-07(E,N)AMGR 75 60 1395 11 x 7 3/4 Med-Low 2.27 80 1190 57 NA NA NA NA 

Rh - RGPP-07(E,N)AMGR 75 60 1395 11 x 7 1/2 Med 2.27 80 1323 84 NA NA NA NA 

Te - T8DNL075F16 75 61 1309 11 x 10 1/2 Med-High 2.26 80 1263 78 3 30 30 NA 

Te - T8MPL075F16 75 60 1343 11 x 10 1/2 Med-High 2.26 80 1208 87 3 30 30 NA 

Te - T8MPN075F16 75 60 1343 11 x 10 1/2 Med-High 2.26 80 1208 87 3 30 30 NA 

H-13 
Table H.3.13 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 80 Btu/h

1200 CFM

Non-Condensing Single-Stage

80 kBtu/h 1200 CFM

Models Input Output CFM

0.5

Blower

Size

Motor

Size

Speed

Taps

Air

Supply

Outlet AFUE Eae PE

PrepurgePostpurge

OnDelayOffDelay

Area

Te - ABA080NH3R 80 65 1035 10x6 1 /3 Med-High 1.70 80.2 858 56 NA 5 30 NA

Am - CUB080A936C* 80 63 80 1007 77 NA NA NA NA

Yo - GY8S080A12DN11 80 64 1200 10x8 1/2 Med-High 1.84 80 907 71 NA NA NA NA

Yo - GY8S080A12DN11 80 64 1280 10x8 1/2 Med-High 1.84 80 907 71 NA NA NA NA

Yo - GY8S080A12UH11 80 64 1280 10x8 1/2 Med-High 1.84 80 854 73 NA NA NA NA

Yo - GY8S080A12UH1 1 80 64 1200 10x8 1 /2 Med-High 1.84 80 854 73 NA NA NA NA

Yo - P4DNA12NO6401 80 64 1035 1Ox8 1/3 Med-High 1.84 80 907 71 NA NA 30 NA

Yo - P4HUA12NO6401 80 64 1030 10x7 1/3 Med-High 1.84 80 854 73 NA NA 30 NA

Yo - PS8A12N080DN1 1 80 64 1150 10x8 1/3 Med-High 1.84 80 907 71 NA NA NA NA

Yo - PS8A12N080UH1 1 80 64 1280 10x8 1/2 Med-High 1.84 80 854 73 NA NA NA NA

Yo - PS8A12N080UH1 1 80 64 1200 10x8 1/2 Med-High 1.84 80 854 73 NA NA NA NA

Tr - TDD080C936F* 80 64 1223 10x7 1 /3 Med-High 2.17 80 837 79 NA NA 45 NA

Tr - TUD080C936K* 80 63 1147 10x7 1/3 Med-High 2.21 80 1007 77 NA NA 45 NA

Tr - TUE080A936L* 80 63 1147 10x7 1/3 Med-High 2.21 80 1007 77 NA NA 45 NA

Table H.3.14 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 80 Btu/h

1600

Non-Condensing Single-Stage

80 kBtu/h 1600 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output AFUE Eae PE 0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Te - ABA08ONH4R 80 65 990 10x8 1/2 Low 2.10 80.2 1075 55 NA 5 30 NA

Am - CUB080A948C* 80 64 - 80 984 78 NA NA NA NA

Yo - GY8S080B16DN11 80 64 1390 11x8 3/4 Med 2.26 80 1075 68 NA NA NA NA

Yo - GY8S080B16DN11 80 64 1400 11 x 8 3/4 Med 2.26 80 1075 68 NA NA NA NA

Yo - GY8S080B16UH11 80 64 1390 11 x 8 3/4 Med 2.26 80 1137 72 NA NA NA NA

Yo - GY8S080B16UH11 80 64 1400 11 x 8 3/4 Med 2.26 80 1137 72 NA NA NA NA

Yo - P4DNB16NO6401 80 64 1840 10x8 1/2 High 2.26 80 1075 68 NA NA 30 NA

Yo - P4HUB16NO6401 80 64 1405 11 x 8 3/4 Med 2.26 80 1137 72 NA NA 30 NA

Yo - PS8B16N080DN11 80 64 1490 10x8 1/2 Med 2.26 80 1075 68 NA NA NA NA

Yo - PS8B16N080UH11 80 64 1390 11 x 8 3/4 Med 2.26 80 1137 72 NA NA NA NA

Yo - PS8B16N080UH11 80 64 1400 11 x 8 3/4 Med 2.26 80 1137 72 NA NA NA NA

Tr - TDE080A945M* 80 64 1275 10x8 1/3 Med-High 2.17 80 822 79 NA NA 45 NA

Tr - TUD080C948K* 80 64 1308 10x8 1/3 Med-High 2.21 80 984 78 NA NA 45 NA

Tr - TUE080A948L* 80 64 1308 10x8 1/3 Med-High 2.21 80 984 78 NA NA 45 NA

Ca - 58DLX090-16* 84 68 1375 10 x 10 1/2 Med-Low - 80 925 77 15 5 25 NA

Ca - 58STX090-16* 84 68 1375 1 10x10 1/2 Med-Low - 80 983 77 15 5 25 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.13 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 

1200 CFM 

Non-Condensing Single-Stage 

80 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Te - ABA080NH3R 80 65 1035 10 x 6 1/3 Med-High 1.70 80.2 858 56 NA 5 30 NA 

Am - CUB080A936C* 80 63 - 80 1007 77 NA NA NA NA 

Yo - GY8S080A12DN11 80 64 1200 10 x 8 1/2 Med-High 1.84 80 907 71 NA NA NA NA 

Yo - GYSS080A12DN11 80 64 1280 10 x 8 1/2 Med-High 1.84 80 907 71 NA NA NA NA 

Yo - GYSS080A12UH11 80 64 1280 10 x 8 1/2 Med-High 1.84 80 854 73 NA NA NA NA 

Yo - GYSS080A12UH11 80 64 1200 10 x 8 1/2 Med-High 1.84 80 854 73 NA NA NA NA 

Yo - P4DNA12N06401 80 64 1035 10 x 8 1/3 Med-High 1.84 80 907 71 NA NA 30 NA 

Yo - P4HUA12N06401 80 64 1030 10 x 7 1/3 Med-High 1.S4 80 854 73 NA NA 30 NA 

Yo - PS8A12N080DN11 80 64 1150 10 x 8 1/3 Med-High 1.84 80 907 71 NA NA NA NA 

Yo - PS8A12N080UH11 80 64 1280 10 x 8 1/2 Med-High 1.84 SO 854 73 NA NA NA NA 

Yo - PS8A12N080UH11 80 64 1200 10 x 8 1/2 Med-High 1.84 80 854 73 NA NA NA NA 

Tr - TDD080C936F* 80 64 1223 10 x 7 1/3 Med-High 2.17 80 837 79 NA NA 45 NA 

Tr - TUD080C936K* 80 63 1147 10 x 7 1/3 Med-High 2.21 80 1007 77 NA NA 45 NA 

Tr - TUE080A936L* 80 63 1147 10x7 1/3 Med-High 2.21 80 1007 77 NA NA 45 NA 

Table H.3.14 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 

1600 

Non-Condensing Single-Stage 

80 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Te - ABA080NH4R 80 65 990 10 x 8 112 Low 2.10 80.2 1075 55 NA 5 30 NA 

Am - CUB080A948C* 80 64 - 80 984 78 NA NA NA NA 

Yo - GY8S080B16DN11 80 64 1390 11 x 8 3/4 Med 2.26 80 1075 68 NA NA NA NA 

Yo - GY8S080B16DN11 80 64 1400 11 x 8 3/4 Med 2.26 80 1075 68 NA NA NA NA 

Yo - GY8S080B16UH11 80 64 1390 11 x 8 3/4 Med 2.26 80 1137 72 NA NA NA NA 

Yo - GY8S080B16UH11 80 64 1400 11 x 8 3/4 Med 2.26 80 1137 72 NA NA NA NA 

Yo - P4DNB16N06401 80 64 1840 10 x 8 1/2 High 2.26 80 1075 68 NA NA 30 NA 

Yo - P4HUB16N06401 80 64 1405 11 x 8 3/4 Med 2.26 80 1137 72 NA NA 30 NA 

Yo - PS8B16N080DN11 80 64 1490 10 x 8 1/2 Med 2.26 80 1075 68 NA NA NA NA 

Yo - PS8B16N080UH11 80 64 1390 11 x 8 3/4 Med 2.26 80 1137 72 NA NA NA NA 

Yo - PS8B16N080UH11 80 64 1400 11 x 8 3/4 Med 2.26 80 1137 72 NA NA NA NA 

Tr - TDE080A945M* 80 64 1275 10 x 8 1/3 Med-High 2.17 80 822 79 NA NA 45 NA 

Tr - TUD080C948K* 80 64 1308 10 x 8 1/3 Med-High 2.21 80 984 78 NA NA 45 NA 

Tr - TUE080A948L* 80 64 1308 10 x 8 1/3 Med-High 2.21 80 984 78 NA NA 45 NA 

Ca - 58DLX090-16* 84 68 1375 10 x 10 1/2 Med-Low - 80 925 77 15 5 25 NA 

Ca - 58STX090-16* 84 68 1375 10 x 10 1/2 Med-Low - 80 983 77 15 5 25 NA 

H-14 
Table 11.3.15 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 80 Btu/h

2000 CFM

Non-Condensing Single-Stage

80 kBtu/h 2000 CFM

Air

CFM Motor Speed Supply Pre- Post- On- Off- Models Input Output Blower Size AFUE Eae PE 0.5 Size Taps Outlet purge purge Delay Delay

Area

Te - ABA080NH5R 80 65 1155 10 x 4 (Dual) 3/4 Low 2.49 80.2 953 55 NA 5 30 NA

Yo - LY8SO8OC20UH11 80 64 11 x 11 1 2.74 80 1220 74 NA NA NA NA

Yo - P4HUC20NO6401 80 64 1855 11 x 10 1 Med 2.74 80 1220 74 NA NA 30 NA

Yo - P4HUC20NO6401 80 64 1880 11 x 10 1 Med 2.74 80 1220 74 NA NA 30 NA

Yo - PS8C20LO80UH11 80 64 11 x 11 1 3.23 80 1220 74 NA NA NA NA

Tr - TUD080C960K* 80 63 1431 11 x 10 3/4 Low 2.69 80 1191 70 NA NA 45 NA

Ca - 58DLX090-20* 84 68 1730 11X11 3/4 Med-Low - 80 1272 71 15 5 25 NA

Ca - 58DLX090-20* 84 68 1770 11 X11 3/4 Med-Low - 80 1272 71 15 5 25 NA

Ca - 58DLX090-20* 84 68 1730 11 X11 3/4 Med-Low - 80 1272 71 15 5 25 NA

Ca - 58STX090-20* 84 68 1730 11 x 11 3/4 Med-Low - 80 1258 74 15 5 25 NA

Ca - 58STX090-20* 84 68 1730 11X11 3/4 Med-Low - 80 1258 74 15 5 25 NA

Ca - 58STX090-20* 84 68 1770 11 X11 3/4 Med-Low - 80 1258 74 15 5 25 NA

OI -GTM 85T 85 68 1367 12 x 10 3/4 Low 2.78 80 1220 60 15 5 30 180

OI - GTM 85T 85 68 1345 12 x 10 3/4 Low 2.78 80 1220 60 15 5 30 180

Table H.3.16 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 90 Btu/h

1200 CFM

Non-Condensing Single-Stage

90 kBtu/h 1200 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Le - G40DF-36B-090 ` 88 71 1055 10x8 1/3 Med-Low 2.14 80 685 121 15 5 45 NA

Le - G401_11-1-36B-090-* 88 71 1135 10x8 1/3 Med-High 2.21 80 894 118 15 5 45 NA

Le - G50DF-36B-090-* 88 71 1055 10x8 1/3 Med-Low 2.14 80 685 121 15 5 45 NA

Le - G501_11-1-36B-090-* 88 71 1135 10x8 1/3 Med-High 2.21 80 894 118 15 5 45 NA

Am - AMS80903BN 90 72 1493 10x8 1/3 High 2.18 80 494 75 NA NA NA NA

Go - GMT090-3 90 72 1038 10x8 1/3 Med 2.38 80 494 75 NA NA 30 NA

Fr - L1 RA090*12B 90 72 930 9 x 9 1/4 Low 2.50 80 715 75 30 30 30 NA

Am - GCIC090**30 92 74 1265 10x8 1/2 High 2.26 80 696 122 NA 15 30 NA

Am - GUIC090**30 92 74 1380 10x8 1/2 High 2.66 80 724 80 NA 15 30 NA

Am - GUID090**30 92 74 1380 10 x 9 1/2 High 2.64 80 724 80 NA 15 30 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.15 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 

2000 CFM 

Non-Condensing Single-Stage 

80 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay 

Area 

Te - ABA080NH5R 80 65 1155 10 x 4 (Dual) 3/4 Low 2.49 80.2 953 55 NA 5 30 NA 

Yo - L Y8S080C20UH11 80 64 11 x 11 1 2.74 80 1220 74 NA NA NA NA 

Yo - P4HUC20N06401 80 64 1855 11 x 10 1 Med 2.74 80 1220 74 NA NA 30 NA 

Yo - P4HUC20N06401 80 64 1880 11 x 10 1 Med 2.74 80 1220 74 NA NA 30 NA 

Yo - PS8C20L080UH11 80 64 11 x 11 1 3.23 80 1220 74 NA NA NA NA 

Tr - TUD080C960K* 80 63 1431 11 x 10 3/4 Low 2.69 80 1191 70 NA NA 45 NA 

Ca - 58DLX090-20* 84 68 1730 11 x 11 3/4 Med-Low - 80 1272 71 15 5 25 NA 

Ca - 58DLX090-20* 84 68 1770 11 x 11 3/4 Med-Low - 80 1272 71 15 5 25 NA 

Ca - 58DLX090-20* 84 68 1730 11 x 11 3/4 Med-Low - 80 1272 71 15 5 25 NA 

Ca - 58STX090-20* 84 68 1730 11 x 11 3/4 Med-Low - 80 1258 74 15 5 25 NA 

Ca - 58STX090-20* 84 68 1730 11 x 11 3/4 Med-Low - 80 1258 74 15 5 25 NA 

Ca - 58STX090-20* 84 68 1770 11 x 11 3/4 Med-Low - 80 1258 74 15 5 25 NA 

01- GTM 85T 85 68 1367 12 x 10 3/4 Low 2.78 80 1220 60 15 5 30 180 

01- GTM 85T 85 68 1345 12 x 10 3/4 Low 2.78 80 1220 60 15 5 30 180 

Table H.3.16 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 

1200 CFM 

Non-Condensing Single-Stage 

90 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Le - G40DF-36B-090-* 88 71 1055 10 x 8 1/3 Med-Low 2.14 80 685 121 15 5 45 NA 

Le - G40UH-36B-090-* 88 71 1135 10 x 8 1/3 Med-High 2.21 80 894 118 15 5 45 NA 

Le - G50DF-36B-090-* 88 71 1055 10 x 8 1/3 Med-Low 2.14 80 685 121 15 5 45 NA 

Le - G50UH-36B-090-* 88 71 1135 10 x 8 1/3 Med-High 2.21 80 894 118 15 5 45 NA 

Am - AMS80903BN 90 72 1493 10 x 8 1/3 High 2.18 80 494 75 NA NA NA NA 

Go - GMT090-3 90 72 1038 10 x 8 1/3 Med 2.38 80 494 75 NA NA 30 NA 

Fr - L 1 RA090*12B 90 72 930 9x9 1/4 Low 2.50 80 715 75 30 30 30 NA 

Am - GCIC090**30 92 74 1265 10 x 8 1/2 High 2.26 80 696 122 NA 15 30 NA 

Am - GUIC090**30 92 74 1380 10 x 8 1/2 High 2.66 80 724 80 NA 15 30 NA 

Am - GUID090**30 92 74 1380 10 x 9 1/2 High 2.64 80 724 80 NA 15 30 NA 

H-15 
Table H.3.17 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 90 Btu/h

1600 CFM

Non-Condensing Single-Stage

90 kBtu/h 1600 CFM

Air

CFM Motor Speed Supply Pre- Post- On- Off- Models Input Output 0 5 Blower Size AFUE Eae PE Size Taps Outlet purge purge Delay Delay

Area

Ca - 58DLA090-16 88 71 1375 10 x 10 1/2 Med-Low - 80 885 77 15 5 25 NA

Ca - 58STA090-16 88 71 1375 10 x 10 1 /2 Med-Low - 80 940 77 15 5 25 NA

Le - G40DF-48C-090-* 88 71 1335 10 x 10 1/2 Med-Low 2.61 80 662 116 15 5 45 NA

Le - G40UH-48B-090 * 88 71 1360 10 x 10 1/2 Med-Low 2. 21 80 864 115 15 5 45 NA

Le - G50DF-48C-090-* 88 71 1335 10 x 10 1 /2 Med-Low 2. 61 80 662 116 15 5 45 NA

Le - G50UH-48B-090' 88 71 1360 10 x 10 1 /2 Med-Low 2. 21 80 864 115 15 5 45 NA

Am - ADS80904BN 90 72 1501 10x8 1 /2 Med 2.18 80 595 75 NA NA NA NA

Am - AMS80904BN 90 72 1313 10x8 1 /2 Med-Low 2 . 18 80 595 75 NA NA NA NA

Am - DDS80904BX 90 72 1222 10x8 1/2 Med-Low 2.18 80 595 75 NA NA NA NA

Am - DMS80904BN 90 72 1313 10x8 1 /2 Med-Low 2. 18 80 595 75 NA NA NA NA

Go - GDT090-4 90 72 1465 10 x 8 1/2 Med 2. 18 80 595 75 NA NA 30 NA

Go - GMT090-4 90 72 1113 10x8 1 /2 Low 2.38 80 595 75 NA NA 30 NA

Fr - L1 RA090*16B 90 72 1545 10 x 10 1/2 Med-High 2.50 80 855 76 30 30 30 NA

Am - GUIE090**40 92 74 - 80 691 90 NA NA NA NA

Table H.3.18 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 90 Btu/h

2000

Non-Condensing Single-Stage

90 kBtu/h 2000 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output AFUE Eae PE 0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Ca - 58DLA090-20 88 71 1730 11 x11 3/4 Med-Low - 80 1218 71 15 5 25 NA

Ca - 58DLA090-20 88 71 1770 11 x 1l 3/4 Med-Low - 80 1218 71 15 5 25 NA

Ca - 58DLA090-20 88 71 1730 11 x 1l 3/4 Med-Low - 80 1218 71 15 5 25 NA

Ca - 58STA090-20 88 71 1730 11 x 1l 3/4 Med-Low - 80 1204 74 15 5 25 NA

Ca - 58STA090-20 88 71 1770 11 x 1l 3/4 Med-Low - 80 1204 74 15 5 25 NA

Ca - 58STA090-20 88 71 1730 11 x 1l 3/4 Med-Low - 80 1204 74 15 5 25 NA

Am - AMS80905CN 90 72 1325 10 x 10 1/2 Med-Low 2.66 80 600 75 NA NA NA NA

Am - DHS80905CX 90 72 1581 11 x 10 3/4 Med 2.66 80 736 75 NA NA NA NA

Am - DMS80905CN 90 72 1589 10 x 10 1/2 Med 2.66 80 600 75 NA NA NA NA

Go - GMT090-5 90 72 1338 10 x 10 1/2 Low 2.86 80 600 75 NA NA 30 NA

Go - GMTH090-5 90 72 - 80 736 75 NA NA NA NA

Fr - L1 RA090*-20B 90 72 1280 11 x 10 3/4 Low 2.50 80 1105 75 30 30 30 NA

Am - GCIC090**50 92 74 1170 10x8 1/2 Med-Low 2.26 80 684 106 NA 15 30 NA

Am - GCID090**50 92 74 1170 10x8 1/2 Med-Low 2.26 80 684 106 NA 15 30 NA

Am - GUIC090**50 92 74 1280 10x8 1/2 Med-Low 2.66 80 698 74 NA 15 30 NA

Am - GUID090**50 92 74 1280 10x9 3/4 Med-Low 2.64 80 701 80 NA 15 30 NA

Am - GUIE090**50 92 74 - 80 677 84 NA NA NA NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.17 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 

1600 CFM 

Non-Condensing Single-Stage 

90 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay 

Area 

Ca - 58DLA090-16 88 71 1375 10 x 10 1/2 Med-Low - 80 885 77 15 5 25 NA 

Ca - 58STA090-16 88 71 1375 10 x 10 1/2 Med-Low - 80 940 77 15 5 25 NA 

Le - G40DF-48C-090-* 88 71 1335 10 x 10 1/2 Med-Low 2.61 80 662 116 15 5 45 NA 

Le - G40UH-48B-090-* 88 71 1360 10x 10 1/2 Med-Low 2.21 80 864 115 15 5 45 NA 

Le - G50DF-48C-090-* 88 71 1335 10 x 10 1/2 Med-Low 2.61 80 662 116 15 5 45 NA 

Le - G50UH-48B-090-* 88 71 1360 10 x 10 1/2 Med-Low 2.21 80 864 115 15 5 45 NA 

Am - ADS80904BN 90 72 1501 10 x 8 1/2 Med 2.18 80 595 75 NA NA NA NA 

Am - AMS80904BN 90 72 1313 10 x 8 1/2 Med-Low 2.18 80 595 75 NA NA NA NA 

Am - DDS80904BX 90 72 1222 10x 8 1/2 Med-Low 2.18 80 595 75 NA NA NA NA 

Am - DMS80904BN 90 72 1313 10x 8 1/2 Med-Low 2.18 80 595 75 NA NA NA NA 

Go - GDT090-4 90 72 1465 10x 8 1/2 Med 2.18 80 595 75 NA NA 30 NA 

Go - GMT090-4 90 72 1113 10 x 8 1/2 Low 2.38 80 595 75 NA NA 30 NA 

Fr - L 1 RA090*16B 90 72 1545 10 x 10 1/2 Med-High 2.50 80 855 76 30 30 30 NA 

Am - GUIE090**40 92 74 - 80 691 90 NA NA NA NA 

Table H.3.18 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 

2000 

Non-Condensing Single-Stage 

90 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Ca - 58DLA090-20 88 71 1730 11 x 11 3/4 Med-Low - 80 1218 71 15 5 25 NA 

Ca - 58DLA090-20 88 71 1770 11 xii 3/4 Med-Low - 80 1218 71 15 5 25 NA 

Ca - 58DLA090-20 88 71 1730 11 xii 3/4 Med-Low - 80 1218 71 15 5 25 NA 

Ca - 58ST A090-20 88 71 1730 11 x 11 3/4 Med-Low - 80 1204 74 15 5 25 NA 

Ca - 58ST A090-20 88 71 1770 11 x 11 3/4 Med-Low - 80 1204 74 15 5 25 NA 

Ca - 58ST A090-20 88 71 1730 11 x 11 3/4 Med-Low - 80 1204 74 15 5 25 NA 

Am - AMS80905CN 90 72 1325 10 x 10 1/2 Med-Low 2.66 80 600 75 NA NA NA NA 

Am - DHS80905CX 90 72 1581 11 x 10 3/4 Med 2.66 80 736 75 NA NA NA NA 

Am - DMS80905CN 90 72 1589 10 x 10 1/2 Med 2.66 80 600 75 NA NA NA NA 

Go - GMT090-5 90 72 1338 10 x 10 1/2 Low 2.86 80 600 75 NA NA 30 NA 

Go - GMTH090-5 90 72 - 80 736 75 NA NA NA NA 

Fr - L 1 RA090*-20B 90 72 1280 11 x 10 3/4 Low 2.50 80 1105 75 30 30 30 NA 

Am - GCIC090**50 92 74 1170 10 x 8 1/2 Med-Low 2.26 80 684 106 NA 15 30 NA 

Am - GCID090**50 92 74 1170 10 x 8 1/2 Med-Low 2.26 80 684 106 NA 15 30 NA 

Am - GUIC090**50 92 74 1280 10 x 8 1/2 Med-Low 2.66 80 698 74 NA 15 30 NA 

Am - GUID090**50 92 74 1280 10 x 9 3/4 Med-Low 2.64 80 701 80 NA 15 30 NA 

Am - GUIE090**50 92 74 - 80 677 84 NA NA NA NA 

H-16 
Table H.3.19 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 100 Btu/h

1200 CFM

Non-Condensing Single-Stage

100 kBtu/h 1200 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output 0.5 Size Size Taps Outlet AFUE Eae PE

purge purge Delay Delay

Area

Fr- FG6RA096*-12B 96 78 750 10x9 1/3 Low 2.50 80.5 757 75 30 30 30 NA

Fr- FG6RK096*-12B 96 76 1145 10x8 1/3 Med 2.50 80 715 50 30 30 30 NA

Te - ABA100NH3R 100 81 1060 10x6 1/3 Med-High 2.10 80.2 862 79 NA 5 30 NA

Am - CUB100A936C* 100 79 - 80 972 79 NA NA NA NA

Yo - GY8S100B12DN1 1 100 80 1230 11 x8 3/4 Med-High 2.26 80 840 80 NA NA NA NA

Yo - GY8S100B12DN11 100 80 1280 11 x 8 3/4 Med-High 2.26 80 840 80 NA NA NA NA

Yo - GY8S100B12UH11 100 80 1280 11 x 8 3/4 Med-High 2.26 80 1136 72 NA NA NA NA

Yo - GY8S100B12UH11 100 80 1230 11 x8 3/4 Med-High 2.26 80 1136 72 NA NA NA NA

Yo - P4DNB12NO8001 100 80 1510 11 x 10 3/4 High 2.26 80 840 80 NA NA 30 NA

Yo - P4HUB12NO8001 100 80 1465 10x8 1/2 High 2.26 80 1136 72 NA NA 30 NA

Yo - PS8B12N1000N11 100 80 1270 11 x 10 3/4 Med-High 2.26 80 840 80 NA NA NA NA

Yo - PS8B12N100UH11 100 80 1230 10x8 1/2 Med-High 1.84 80 1136 72 NA NA NA NA

Yo - PS8B12N1000H11 100 80 1280 10x8 1/2 Med-High 1.84 80 1136 72 NA NA NA NA

Rh - RGLH-10EAMER 100 80 980 11 x 7 1/2 Med-Low 2.28 80.2 1034 75 NA NA NA NA

Rh - RGLJ-10EAMER 100 80 1135 11 x 7 1/2 Med 2.27 80 1034 75 30 5 20 NA

Rh - RGLN-10(E,N)AMER 100 80 - 80 1220 70 NA NA NA NA

Rh - RGPH-10EAMER 100 80 960 11 x 7 1/2 Med-Low 2.27 80 941 68 NA NA NA NA

Rh - RGPJ-10EAMER 100 80 1105 11 x 7 1/2 Med 2.45 80 941 68 30 5 20 NA

Rh - RGPN-10(E,N)AMER 100 80 960 11 x 7 1/2 Med-Low 2.76 80 986 59 NA NA NA NA

Rh - RGPP-10(E,N)AMER 100 80 1105 11 x 7 1/2 Med 2.27 80 1010 70 NA NA NA NA

Tr - TUD1000936K* 100 79 1203 10x7 1/3 Med-High 2.21 80 972 79 NA NA 45 NA

Tr - TUE100A936L* 100 79 1203 10x7 1/3 Med-High 2.21 80 972 79 NA NA 45 NA

Ca - 58DLX110-12* 105 85 1180 10x8 1/3 Med-Low - 80 831 91 15 5 25 NA

Ca - 58STX110-12* 105 85 1180 10 x 8 1/3 Med-Low - 80 878 91 15 5 25 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.19 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 

1200 CFM 

Non-Condensing Single-Stage 

100 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Ott0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Fr - FG6RA096*-12B 96 78 750 10 x 9 1/3 Low 2.50 80.5 757 75 30 30 30 NA 

Fr - FG6RK096*-12B 96 76 1145 10 x 8 1/3 Med 2.50 80 715 50 30 30 30 NA 

Te - ABA100NH3R 100 81 1060 10 x 6 1/3 Med-High 2.10 80.2 862 79 NA 5 30 NA 

Am - CUB100A936C* 100 79 - 80 972 79 NA NA NA NA 

Yo - GY8S100B12DN11 100 80 1230 11 x 8 3/4 Med-High 2.26 80 840 80 NA NA NA NA 

Yo - GY8S100B12DN11 100 80 1280 11 x 8 3/4 Med-High 2.26 80 840 80 NA NA NA NA 

Yo - GY8S100B12UH11 100 80 1280 11 x 8 3/4 Med-High 2.26 80 1136 72 NA NA NA NA 

Yo - GY8S100B12UH11 100 80 1230 11 x 8 3/4 Med-High 2.26 80 1136 72 NA NA NA NA 

Yo - P4DNB12N08001 100 80 1510 11 x 10 3/4 High 2.26 80 840 80 NA NA 30 NA 

Yo - P4HUB12N08001 100 80 1465 10 x 8 1/2 High 2.26 80 1136 72 NA NA 30 NA 

Yo - PS8B12N100DN11 100 80 1270 11 x 10 3/4 Med-High 2.26 80 840 80 NA NA NA NA 

Yo - PS8B12N100UH11 100 80 1230 10 x 8 1/2 Med-High 1.84 80 1136 72 NA NA NA NA 

Yo - PS8B12N100UH11 100 80 1280 10 x 8 1/2 Med-High 1.84 80 1136 72 NA NA NA NA 

Rh - RGLH-10EAMER 100 80 980 11 x 7 1/2 Med-Low 2.28 80.2 1034 75 NA NA NA NA 

Rh - RGLJ-10EAMER 100 80 1135 11 x 7 1/2 Med 2.27 80 1034 75 30 5 20 NA 

Rh - RGLN-10(E,N)AMER 100 80 - 80 1220 70 NA NA NA NA 

Rh - RGPH-10EAMER 100 80 960 11 x 7 1/2 Med-Low 2.27 80 941 68 NA NA NA NA 

Rh - RGPJ-10EAMER 100 80 1105 11 x 7 1/2 Med 2.45 80 941 68 30 5 20 NA 

Rh - RGPN-10(E,N)AMER 100 80 960 11 x 7 1/2 Med-Low 2.76 80 986 59 NA NA NA NA 

Rh - RGPP-10(E,N)AMER 100 80 1105 11 x 7 1/2 Med 2.27 80 1010 70 NA NA NA NA 

Tr - TUD100C936K* 100 79 1203 10 x 7 1/3 Med-High 2.21 80 972 79 NA NA 45 NA 

Tr - TUE100A936L* 100 79 1203 10 x 7 1/3 Med-High 2.21 80 972 79 NA NA 45 NA 

Ca - 58DLX110-12* 105 85 1180 10 x 8 1/3 Med-Low - 80 831 91 15 5 25 NA 

Ca - 58STX110-12* 105 85 1180 10 x 8 1/3 Med-Low - 80 878 91 15 5 25 NA 

H-17 
Table H.3.20 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 100 Btu/h

1600

Non-Condensing Single-Stage

100 kBtu/h 1600 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output AFUE Eae PE

0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Fr- FG6RA096*-16B 96 78 1140 10 x 10 1/2 Low 2.50 80.5 757 75 30 30 30 NA

Fr- FG6RK096*-16B 96 76 1275 10x8 1/2 Med-Low 2.50 80 715 50 30 30 30 NA

Te - ABA100NH4R 100 81 1205 10x8 1/2 Med-Low 2.10 80.2 1288 77 NA 5 30 NA

Am - CUB100A948C* 100 79 - 80 1186 81 NA NA NA NA

Du - DPGB100A4* 100 80 1550 12 x 9 1/2 Med 1.97 80 1052 87 15 NA 30 NA

Du - FPBB100A4* 100 81 1410 12 x 9 1/2 Med 2.25 80 760 87 15 15 30 NA

Le - G24M314-100S-** 100 80 1210 12 x 8 1/2 Med - 80 801 60 15 5 45 NA

Yo - G8C10016M(DC,UC)12 100 80 1181 10 x 10 1/2 Low 2.71 80 830 70 NA NA 30 NA

Yo - G8C10016M(DC,UC)12 100 80 1171 10 x 10 1/2 Low 2.71 80 830 70 NA NA 30 NA

Yo - G8C10016M(DC,UC)12 100 80 1132 10 x 10 1/2 Low 2.71 80 830 70 NA NA 30 NA

Yo - GY8S100B16UH11 100 80 1350 11 x 8 3/4 Med 2.26 80 1139 73 NA NA NA NA

Yo - GY8S100B16UH11 100 80 1360 11 x 8 3/4 Med 2.26 80 1139 73 NA NA NA NA

Th - MDA-100 100 80 810 1/2 Low 2.38 80.5 809 69 NA NA 60 NA

Th - MHA-100 100 79 770 1/2 Low 2.38 80 697 69 NA NA 60 NA

Th - MHA1-100 100 79 1560 1/2 High 2.38 80 818 80 NA NA 60 NA

Du - MPGA100B4* 100 81 1550 12 x 9 1/2 Med 2.12 80 1052 87 15 15 30 NA

Yo - P4HUB16NO8001 100 80 1550 10 x 10 1/2 Med 2.26 80 1139 73 NA NA 30 NA

Yo - PS8B16N1000H11 100 80 1730 11 x8 3/4 High 2.26 80 1139 73 NA NA NA NA

Yo - PS8B16N1000H11 100 80 1650 11 x8 3/4 High 2.26 80 1139 73 NA NA NA NA

Rh - RGLJ-10EBRGR 100 80 1585 11 x 10 1/2 Med 2.76 80 1139 77 30 5 20 NA

Rh - RGPJ-10EBRGR 100 81 1510 11 x 10 1/2 Med 3.02 80 1322 59 30 5 20 NA

Rh - RGPP-10(E,N)BRGR 100 80 1510 11 x 10 1/2 Med 2.76 80 1304 71 NA NA NA NA

Tr - TDD1000948F* 100 80 1535 10x8 1/2 Med-High 2.65 80 1149 80 NA NA 45 NA

Tr - TDE100A945M* 100 80 1254 10x8 1/3 Med-High 2.17 80 1168 79 NA NA 45 NA

Tr - TUD1000948K* 100 79 1493 10x8 1/2 Med-High 2.69 80 1186 81 NA NA 45 NA

Tr - TUE100A948L* 100 79 1493 10x8 1/2 Med-High 2.69 80 1186 81 NA NA 45 NA

Ca - 58DLX110-16* 105 85 1310 10 x 10 1/2 Med-Low - 80 861 93 15 5 25 NA

Ca - 58STX110-16* 105 85 1310 10 x 10 1/2 Med-Low - 80 803 93 15 5 25 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.20 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 

1600 

Non-Condensing Single-Stage 

100 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Fr - FG6RA096*-16B 96 78 1140 10 x 10 1/2 Low 2.50 80.5 757 75 30 30 30 NA 

Fr - FG6RK096*-16B 96 76 1275 10x 8 1/2 Med-Low 2.50 80 715 50 30 30 30 NA 

Te - ABA100NH4R 100 81 1205 10 x 8 1/2 Med-Low 2.10 80.2 1288 77 NA 5 30 NA 

Am - CUB100A948C* 100 79 - 80 1186 81 NA NA NA NA 

Du - DPGB100A4* 100 80 1550 12 x 9 1/2 Med 1.97 80 1052 87 15 NA 30 NA 

Du - FPBB100A4* 100 81 1410 12 x 9 1/2 Med 2.25 80 760 87 15 15 30 NA 

Le - G24M3/4-100S-** 100 80 1210 12 x 8 1/2 Med - 80 801 60 15 5 45 NA 

Yo - G8C10016M(DC,UC)12 100 80 1181 10 x 10 1/2 Low 2.71 80 830 70 NA NA 30 NA 

Yo - G8C10016M(DC,UC)12 100 80 1171 10 x 10 1/2 Low 2.71 80 830 70 NA NA 30 NA 

Yo - G8C10016M(DC,UC)12 100 80 1132 10 x 10 1/2 Low 2.71 80 830 70 NA NA 30 NA 

Yo - GY8S100B16UH11 100 80 1350 11 x 8 3/4 Med 2.26 80 1139 73 NA NA NA NA 

Yo - GY8S100B16UH11 100 80 1360 11 x 8 3/4 Med 2.26 80 1139 73 NA NA NA NA 

Th - MDA-100 100 80 810 1/2 Low 2.38 80.5 809 69 NA NA 60 NA 

Th - MHA-100 100 79 770 1/2 Low 2.38 80 697 69 NA NA 60 NA 

Th - MHA1-100 100 79 1560 1/2 High 2.38 80 818 80 NA NA 60 NA 

Du - MPGA100B4* 100 81 1550 12 x 9 1/2 Med 2.12 80 1052 87 15 15 30 NA 

Yo - P4HUB16N08001 100 80 1550 10 x 10 1/2 Med 2.26 80 1139 73 NA NA 30 NA 

Yo - PS8B16N100UH11 100 80 1730 11 x 8 3/4 High 2.26 80 1139 73 NA NA NA NA 

Yo - PS8B16N100UH11 100 80 1650 11 x 8 3/4 High 2.26 80 1139 73 NA NA NA NA 

Rh - RGLJ-10EBRGR 100 80 1585 11 x 10 1/2 Med 2.76 80 1139 77 30 5 20 NA 

Rh - RGPJ-10EBRGR 100 81 1510 11 x 10 1/2 Med 3.02 80 1322 59 30 5 20 NA 

Rh - RGPP-10(E,N)BRGR 100 80 1510 11 x 10 1/2 Med 2.76 80 1304 71 NA NA NA NA 

Tr - TDD100C948F* 100 80 1535 10 x 8 1/2 Med-High 2.65 80 1149 80 NA NA 45 NA 

Tr - TDE100A945M* 100 80 1254 10 x 8 1/3 Med-High 2.17 80 1168 79 NA NA 45 NA 

Tr - TUD100C948K* 100 79 1493 10 x 8 1/2 Med-High 2.69 80 1186 81 NA NA 45 NA 

Tr - TUE100A948L* 100 79 1493 10 x 8 1/2 Med-High 2.69 80 1186 81 NA NA 45 NA 

Ca - 58DLX110-16* 105 85 1310 10 x 10 1/2 Med-Low - 80 861 93 15 5 25 NA 

Ca - 58STX110-16* 105 85 1310 10 x 10 1/2 Med-Low - 80 803 93 15 5 25 NA 

H-18 
Table H.3.21 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 100 Btu/h

2000 CFM

Non-Condensing Single-Stage

100 kBtu/h 2000 CFM

Air

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay

Area

Fr- FG6RA096*-20C 96 78 1300 11 x 10 3/4 Low 2.88 81 845 75 30 30 30 NA

Te - ABA100NH5R 100 81 1390 10 x 4 (Dual) 3/4 Med-Low 2.49 80.2 1111 83 NA 5 30 NA

Am - CDB100A960D* 100 81 NA - 80 1010 78 NA NA NA NA

Am - CUB100A96OC* 100 79 NA - 80 1096 50 NA NA NA NA

Du - DPGB10OA5* 100 80 1840 12 x 12 1/2 Med 2.43 80 1116 87 15 NA 30 NA

Du - FPBB100A5* 100 81 1760 12 x 9 3/4 Med 2.25 80 1143 87 15 15 30 NA

Ar - G1 D80BR10OD20C*-*** 100 80 1231 12x 10 3/4 Med-Low 2.50 80 745 92 NA NA NA NA

Ar - G1 D80BT100D20C*-*** 100 80 1208 12x 10 3/4 Med-Low 2.72 80 745 92 NA NA NA NA

Ar - G1 N80BR100D20C*-*** 100 80 1231 12x 10 3/4 Med-Low 2.50 80 894 93 15 15 30 NA

Ar-G1N80BT100D20C*-*** 100 80 NA 12x10 3/4 2.72 80 897 92 15 15 30 NA

Ar - G1 N80BT125D20C*-*** 100 80 NA 12 x 10 3/4 2.72 80 986 92 15 15 30 NA

Ar - G1 N80BU100D20C*-*** 100 80 1208 12 x 10 3/4 Med-Low 2.72 80 897 92 15 15 30 NA

Le - G24M4/5-1005-** 100 80 1610 12 x 9 3/4 Med-Low - 80 664 60 15 5 45 NA

Yo - G8C10020M(DD,UD)12 100 80 1293 10 x 6 (Dual) 3/4 Low 3.19 80 937 70 NA NA 30 NA

Yo - G8C10020M(DD,UD)12 100 80 1307 10 x 6 (Dual) 3/4 Low 3.19 80 937 70 NA NA 30 NA

OI -GTM 100T 100 80 1345 12 x 10 3/4 Low 2.78 80 1345 60 15 5 30 180

OI - GTM 100T 100 80 1367 12 x 10 3/4 Low 2.78 80 1345 60 15 5 30 180

Yo - GY8S100020DN11 100 80 1900 11x11 1 Med-High 2.74 80 1363 79 NA NA NA NA

Yo - GY8S100020DN11 100 80 1950 11x11 1 Med-High 2.74 80 1363 79 NA NA NA NA

Yo - GY8S100020UH11 100 80 1950 11x11 1 Med-High 2.74 80 1488 75 NA NA NA NA

Yo - GY8S100020UH11 100 80 1900 11x11 1 Med-High 2.74 80 1488 75 NA NA NA NA

Du - MPGA10OB5* 100 81 1840 12 x 12 1/2 Med 2.62 80 1116 87 15 15 30 NA

Te - N8MPL100F20 100 80 1577 11 x 10 3/4 Med-High 2.26 80 1442 46 3 30 30 NA

Te-N8MPN100F20 100 80 1577 11 x 10 1/2 Med-High 2.26 80 1442 46 3 30 30 NA

Yo - P4DNC20NO8001 100 80 1925 11 x 10 3/4 Med 2.74 80 1363 79 NA NA 30 NA

Yo - P4HUC20NO8001 100 80 1855 11 x 10 1 Med 2.74 80 1488 75 NA NA 30 NA

Yo - P4HUC20NO8001 100 80 1880 11 x 10 1 Med 2.74 80 1488 75 NA NA 30 NA

Yo - PS8C20N100DN11 100 80 1840 11 x 10 3/4 Med-High 2.74 80 1363 79 NA NA NA NA

Yo - PS8C20N1000H11 100 80 1900 11x11 I Med-High 3.23 80 1488 75 NA NA NA NA

Yo - PS8C20N1000H11 100 80 1950 11 x 11 1 Med-High 3.23 80 1488 75 NA NA NA NA

Rh - RGLH-IOEBRJR 100 80 1585 11 x 10 3/4 Med-Low 2.76 80.1 1139 77 NA NA NA NA

Rh - RGLJ-10EBRJR 100 80 1970 11 x 10 3/4 Med 2.76 80 1139 77 30 5 20 NA

Rh - RGLN-10(E,N)BRJR 100 80 NA - 80 1220 63 NA NA NA NA

Rh - RGPH-10EBRJR 100 81 1510 11 x 10 3/4 Med-Low 2.76 80 1322 59 NA NA NA NA

Rh - RGPJ-10EBRJR 100 81 1845 11 x 10 3/4 Med 3.02 80 1322 59 30 5 20 NA

Rh - RGPN-10(E,N)BRJR 100 80 1510 11 x 10 3/4 Med-Low 2.76 80 1261 69 NA NA NA NA

Rh - RGPP-10(E,N)BRJR 100 80 1510 11 x 10 3/4 Low 2.76 80 1102 63 NA NA NA NA

Te - T8DNL100L20 100 81 1922 11 x 10 3/4 Med-High 2.95 80 1458 81 3 30 30 NA

Te - T8MPL100F20 100 81 1577 11 x 10 1/2 Med-High 2.26 80 1285 81 3 30 30 NA

Te-T8MPL100J20 100 81 1459 11 x 10 1/2 Med-High 2.73 80 1289 88 3 30 30 NA

Te - T8MPN100F20 100 81 1577 11 x 10 1/2 Med-High 2.26 80 1285 81 3 30 30 NA

Te-T8MPN100J20 100 81 1459 11 x 10 1/2 Med-High 2.73 80 1289 88 3 30 30 NA

Tr - TDE10OA960M* 100 81 1653 11 x 10 1/2 Med-Low 2.65 80 1010 78 NA NA 45 NA

Tr-TUD1000960K* 100 79 1567 11x10 1/2 Med-Low 2.69 80 1096 50 NA NA 45 NA

Tr-TUE100A960L* 100 79 1567 11x10 1/2 Med-Low 2.69 80 1096 50 NA NA 45 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.21 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 

2000 CFM 

Non-Condensing Single-Stage 

100 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay 

Area 

Fr- FG6RA096*-20C 96 78 1300 11 x 10 3/4 Low 2.88 81 845 75 30 30 30 NA 

Te - ABA 1 00NH5R 100 81 1390 10 x4 (Dual) 3/4 Med-Low 2.49 80.2 1111 83 NA 5 30 NA 

Am - COB 1 00A960D* 100 81 NA - 80 1010 78 NA NA NA NA 

Am - CUB100A960C* 100 79 NA - 80 1096 50 NA NA NA NA 

Du - DPGB 1 00A5* 100 80 1840 12x 12 1/2 Med 2.43 80 1116 87 15 NA 30 NA 

Du - FPBB100A5* 100 81 1760 12x 9 3/4 Med 2.25 80 1143 87 15 15 30 NA 

Ar - G1080BR100D20C*-*** 100 80 1231 12x 10 3/4 Med-Low 2.50 80 745 92 NA NA NA NA 

Ar - G1080BT100D20C*-*** 100 80 1208 12x 10 3/4 Med-Low 2.72 80 745 92 NA NA NA NA 

Ar - G1N80BR100D20C*-*** 100 80 1231 12x 10 3/4 Med-Low 2.50 80 894 93 15 15 30 NA 

Ar - G1 N80BT1 00D20C*-*** 100 80 NA 12x 10 3/4 2.72 80 897 92 15 15 30 NA 

Ar - G1N80BT125D20C*-*** 100 80 NA 12x 10 3/4 2.72 80 986 92 15 15 30 NA 

Ar - G1N80BU100D20C*-*** 100 80 1208 12 x 10 3/4 Med-Low 2.72 80 897 92 15 15 30 NA 

Le - G24M4/5-100S-** 100 80 1610 12x9 3/4 Med-Low - 80 664 60 15 5 45 NA 

Yo - G8C10020M(DD,UD)12 100 80 1293 10x 6 (Dual) 3/4 Low 3.19 80 937 70 NA NA 30 NA 

Yo - G8C10020M(DD,UD)12 100 80 1307 10x6 (Dual) 3/4 Low 3.19 80 937 70 NA NA 30 NA 

Ol-GTM 100T 100 80 1345 12x 10 3/4 Low 2.78 80 1345 60 15 5 30 180 

Ol-GTM 100T 100 80 1367 12x 10 3/4 Low 2.78 80 1345 60 15 5 30 180 

Yo - GY8S100C20DN11 100 80 1900 11 x 11 1 Med-High 2.74 80 1363 79 NA NA NA NA 

Yo - GY8S100C20DN11 100 80 1950 11 x 11 1 Med-High 2.74 80 1363 79 NA NA NA NA 

Yo - GY8S100C20UH11 100 80 1950 11 x 11 1 Med-High 2.74 80 1488 75 NA NA NA NA 

Yo - GY8S100C20UH11 100 80 1900 11 x 11 1 Med-High 2.74 80 1488 75 NA NA NA NA 

Du - MPGA100B5* 100 81 1840 12x 12 1/2 Med 2.62 80 1116 87 15 15 30 NA 

Te - N8MPL100F20 100 80 1577 11 x 10 3/4 Med-High 2.26 80 1442 46 3 30 30 NA 

Te - N8MPN100F20 100 80 1577 11 x 10 1/2 Med-High 2.26 80 1442 46 3 30 30 NA 

Yo - P4DNC20N08001 100 80 1925 11 x 10 3/4 Med 2.74 80 1363 79 NA NA 30 NA 

Yo - P4HUC20N08001 100 80 1855 11 x 10 1 Med 2.74 80 1488 75 NA NA 30 NA 

Yo - P4HUC20N08001 100 80 1880 11 x 10 1 Med 2.74 80 1488 75 NA NA 30 NA 

Yo - PS8C20N100DN11 100 80 1840 11 x 10 3/4 Med-High 2.74 80 1363 79 NA NA NA NA 

Yo - PS8C20N100UH11 100 80 1900 11 x 11 1 Med-High 3.23 80 1488 75 NA NA NA NA 

Yo - PS8C20N100UH11 100 80 1950 11 x 11 1 Med-High 3.23 80 1488 75 NA NA NA NA 

Rh - RGLH-10EBRJR 100 80 1585 11 x 10 3/4 Med-Low 2.76 80.1 1139 77 NA NA NA NA 

Rh - RGLJ-10EBRJR 100 80 1970 11 x 10 3/4 Med 2.76 80 1139 77 30 5 20 NA 

Rh - RGLN-10(E,N)BRJR 100 80 NA - 80 1220 63 NA NA NA NA 

Rh - RGPH-10EBRJR 100 81 1510 11 x 10 3/4 Med-Low 2.76 80 1322 59 NA NA NA NA 

Rh - RGPJ-10EBRJR 100 81 1845 11 x 10 3/4 Med 3.02 80 1322 59 30 5 20 NA 

Rh - RGPN-10(E,N)BRJR 100 80 1510 11 x 10 3/4 Med-Low 2.76 80 1261 69 NA NA NA NA 

Rh - RGPP-10(E,N)BRJR 100 80 1510 11 x 10 3/4 Low 2.76 80 1102 63 NA NA NA NA 

Te - T8DNL 1 00L20 100 81 1922 11 x 10 3/4 Med-High 2.95 80 1458 81 3 30 30 NA 

Te - T8MPL 1 00F20 100 81 1577 11 x 10 1/2 Med-High 2.26 80 1285 81 3 30 30 NA 

Te - T8MPL100J20 100 81 1459 11 x 10 1/2 Med-High 2.73 80 1289 88 3 30 30 NA 

Te - T8MPN100F20 100 81 1577 11 x 10 1/2 Med-High 2.26 80 1285 81 3 30 30 NA 

Te - T8MPN100J20 100 81 1459 11 x 10 1/2 Med-High 2.73 80 1289 88 3 30 30 NA 

Tr- TDE100A960M* 100 81 1653 11 x 10 1/2 Med-Low 2.65 80 1010 78 NA NA 45 NA 

Tr- TUD100C960K* 100 79 1567 11 x 10 1/2 Med-Low 2.69 80 1096 50 NA NA 45 NA 

Tr- TUE100A960L* 100 79 1567 11 x 10 1/2 Med-Low 2.69 80 1096 50 NA NA 45 NA 

H-19 
Table H.3.22 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 115 Btu/h

1600 CFM

Non-Condensing Single-Stage

115 kBtu /h 1600 CFM

Models Input Output CFM

0.5

Blower

Size

Motor

Size

Speed

Taps

Air

Supply

Outlet AFUE Eae PE

PrepurgePostpurgeOnDelayOffDelay

Area

Fr- L1 RA108*16B 108 86 1545 11 x 10 1 /2 Med-High 2.50 80 1018 75 30 30 30 NA

Ca - 58DLA110-16 110 89 1310 10x10 1 /2 Med-Low 80 823 93 15 5 25 NA

Ca - 58STA110-16 110 89 1310 10x10 1 /2 Med-Low 80 768 93 15 5 25 NA

Le - G40DF-48C-110-' 110 89 1280 10x10 1/2 Med-Low 2.61 80 807 110 15 5 45 NA

Le - G40UH-48C-110-** 110 89 1475 10x10 1/2 Med-High 2.68 80 939 118 15 5 45 NA

Le - G50DF-48C-110 110 89 1280 10x10 1/2 Med-Low 2.61 80 807 110 15 5 45 NA

Le - G50UH-48C-110-** 110 89 1475 10x10 1 /2 Med-High 2.63 80 939 118 15 5 45 NA

Am - GCIC115**40 115 94 1660 10x7 1 /2 High 2.78 80 967 80 NA 15 30 NA

Am - GCID115**40 115 94 1840 10x7 1 /2 High 2.78 80 967 80 NA 15 30 NA

Am - GUIC115**40 115 92 1590 10x7 1 /2 High 3.21 80 1161 87 NA 15 30 NA

Yo - GY8S115C16DN11 115 92 1560 11x11 Med 2.74 80 1161 78 NA NA NA NA

Yo-GY8S115C16DN11 115 92 1490 11 x 11 Med 2.74 80 1161 78 NA NA NA NA

Yo-GY8S115C16UH11 115 92 1490 11 x 11 Med 2.74 80 1217 80 NA NA NA NA

Yo - GY8S115C16UH11 115 92 1560 11x11 Med 2.74 80 1217 80 NA NA NA NA

Yo - P4DNC16NO9201 115 92 1940 11 x 10 High 2.74 80 1161 78 NA NA 30 NA

Yo - P4HUC16NO9201 115 92 1780 10x10 1/2 High 2.74 80 1217 80 NA NA 30 NA

Yo-PS8C16N115DN11 115 92 1940 11 x 10 High 2.74 80 1161 78 NA NA NA NA

Yo-PS8C16N115UH11 115 92 1490 10x10 3/4 Med 2.74 80 1217 80 NA NA NA NA

Yo-PS8C16N115UHII 115 92 1560 10x10 3/4 Med i 2.74 80 1217 80 NA NA NA NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.22 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 115 Btu/h 

1600 CFM 

Non-Condensing Single-Stage 

115 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Fr - L 1 RA108*16B 108 86 1545 11 x 10 1/2 Med-High 2.50 80 1018 75 30 30 30 NA 

Ca - 58DLA110-16 110 89 1310 10 x 10 1/2 Med-Low - 80 823 93 15 5 25 NA 

Ca - 58STA110-16 110 89 1310 10 x 10 1/2 Med-Low - 80 768 93 15 5 25 NA 

Le - G40DF-48C-11 0-* 110 89 1280 10 x 10 1/2 Med-Low 2.61 80 807 110 15 5 45 NA 

Le - G40UH-48C-11 0-** 110 89 1475 10 x 10 1/2 Med-High 2.68 80 939 118 15 5 45 NA 

Le - G50DF-48C-11 0-* 110 89 1280 10 x 10 1/2 Med-Low 2.61 80 807 110 15 5 45 NA 

Le - G50UH-48C-110-** 110 89 1475 10 x 10 1/2 Med-High 2.63 80 939 118 15 5 45 NA 

Am - GCIC115**40 115 94 1660 10 x 7 1/2 High 2.78 80 967 80 NA 15 30 NA 

Am - GCID115**40 115 94 1840 10 x 7 1/2 High 2.78 80 967 80 NA 15 30 NA 

Am-GUIC115**40 115 92 1590 10 x 7 1/2 High 3.21 80 1161 87 NA 15 30 NA 

Yo - GY8S115C16DN11 115 92 1560 11 x 11 1 Med 2.74 80 1161 78 NA NA NA NA 

Yo - GY8S115C16DN11 115 92 1490 11 x 11 1 Med 2.74 80 1161 78 NA NA NA NA 

Yo - GY8S115C16UH11 115 92 1490 11 x 11 1 Med 2.74 80 1217 80 NA NA NA NA 

Yo - GY8S115C16UH11 115 92 1560 11 x 11 1 Med 2.74 80 1217 80 NA NA NA NA 

Yo - P4DNC16N09201 115 92 1940 11 x 10 1 High 2.74 80 1161 78 NA NA 30 NA 

Yo - P4HUC16N09201 115 92 1780 10 x 10 1/2 High 2.74 80 1217 80 NA NA 30 NA 

Yo - PS8C16N115DN11 115 92 1940 11 x 10 1 High 2.74 80 1161 78 NA NA NA NA 

Yo - PS8C16N115UH11 115 92 1490 10 x 10 3/4 Med 2.74 80 1217 80 NA NA NA NA 

Yo - PS8C16N115UH11 115 92 1560 10 x 10 3/4 Med 2.74 80 1217 80 NA NA NA NA 

H-20 
Table 13.3.23 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 115 Btu/h

2000 CFM

Non-Condensing Single-Stage

115 kBtu/h 2000 CFM

Air

CFM Motor Speed Supply Pre- Post- On- Off- Models Input Output Blower Size AFUE Eae PE 0.5 Size Taps Outlet purge purge Delay Delay

Area

Fr - L1 RA108*-20B 108 86 1400 11 x 10 3/4 Low 2.50 80 1168 75 30 30 30 NA

Fr- LIRA108*20C 108 86 1790 11 x 10 3/4 Med-High 2.88 80 1069 76 30 30 30 NA

Le - G40DF-60C- 110-** 110 90 1835 11.5 x 10 3/4 Med-Low 2.61 80 1029 122 15 5 45 NA

Le - G40UH-60C-110-** 110 89 1895 11.5 x 10 3/4 Med-Low 2. 68 80 1206 119 15 5 45 NA

Le - G40UH-60C-110--** 110 89 1750 11.5 x 10 3/4 Med-Low 2 . 68 80 1206 119 15 5 45 NA

Le - G50DF-60C-110-** 110 90 1835 U .S x 10 1 Med-Low 2. 61 80 1029 122 15 5 45 NA

Le - G50UH-60C- 110-** 110 89 1750 11.5 x 10 3/4 Med-Low 2.63 80 1206 119 15 5 45 NA

Le - G50UH-60C- 110-** 110 89 1895 11.5 x 10 3/4 Med-Low 2. 63 80 1206 119 15 5 45 NA

Am - ADS81155CN 115 92 1613 10 x 10 1/2 Med 2. 66 80 701 75 NA NA NA NA

Am - AMS81155CN 115 92 1639 10 x 10 1/2 Med 2.66 80 701 75 NA NA NA NA

Am - DDS81155CX 115 92 1613 10 x 10 1/2 Med 2.66 80 701 75 NA NA NA NA

Am - DMS81155CN 115 92 1639 10 x 10 1/2 Med 2.66 80 701 75 NA NA NA NA

Am - GCIC115**50 115 92 1710 10 x 9 3/4 Med-High 2. 78 80 815 93 NA 15 30 NA

Go - GDT115-5 115 92 1660 10 x 10 1 /2 Med 2. 66 80 701 75 NA NA 30 NA

Go - GMT115-5 115 92 1650 10 x 10 1/2 Med 2 . 86 80 701 75 NA NA 30 NA

Go - GMTH115-5 115 92 - 80 930 75 NA NA NA NA

Am - GUIC115**50 115 92 1850 10 x 9 3/4 Med-High 3. 21 80 1051 75 NA 15 30 NA

Am - GUID115**50 115 92 1850 10 x 10 3/4 Med-High 3. 19 80 1015 75 NA 15 30 NA

Am - GUIE0115**50 115 92 - 80 1095 87 NA NA NA NA

Yo - GY8S115C20DN11 115 92 1940 11 x 11 1 Med-High 2. 74 80 1513 84 NA NA NA NA

Yo - GY8S115C20DN11 115 92 1840 11 x 11 1 Med-High 2. 74 80 1513 84 NA NA NA NA

Yo - GY8S1 15C20UH1 1 115 92 1940 11X11 1 Med-High 2. 74 80 1579 79 NA NA NA NA

Yo - GY8S1 15C20UH1 1 115 92 1840 11 x 11 1 Med-High 2. 74 80 1579 79 NA NA NA NA

Yo - P4DNC20NO9201 115 92 2190 11 x 10 1 High 2. 74 80 1513 84 NA NA 30 NA

Yo - P4HUC20NO9201 115 92 2115 11 x 10 1 High 2. 74 80 1579 79 NA NA 30 NA

Yo - P4HUC20NO9201 115 92 2130 11 x 10 1 High 2. 74 80 1579 79 NA NA 30 NA

Yo - PS8C20N1 1 5DN1 1 115 92 1790 11 x 10 1 Med-High 2. 74 80 1513 84 NA NA NA NA

Yo - PS8C20N1 15UH1 1 115 92 1940 11 x 11 1 Med-High 3.23 80 1579 79 NA NA NA NA

Yo - PS8C20N115UH11 115 92 1840 11 x 11 1 Med-High 3 . 23 80 1579 79 NA NA NA NA

Table 13.3.24 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 120 Btu/h

1600 CFM

Non-Condensing Single-Stage

120 kBtu/h 1600 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Te - ABA120NH4R 1335 82 1440 10x8 1 /2 Med-High 2.49 80.2 1335 82 NA 5 30 NA

Fr - FG6RA1 20*- 1 6B 882 75 1120 10 x 10 1 /2 Low 2. 50 81 882 75 30 30 30 NA

Le - G24M3/4-120*-** 810 60 1420 12 x 8 1/2 Med-High - 80 810 60 15 5 45 NA

H-21

 EE-RM/STD-01-350 COMMENT 164

Table H.3.23 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 115 Btu/h 

2000 CFM 

Non-Condensing Single-Stage 

115 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay 

Area 

Fr - LiRA 1 08*-20B 108 86 1400 11 x 10 3/4 Low 2.50 80 1168 75 30 30 30 NA 

Fr - L 1RA108*20C 108 86 1790 11 x 10 3/4 Med-High 2.88 80 1069 76 30 30 30 NA 

Le - G40DF-60C-110-** 110 90 1835 11.5 x 10 3/4 Med-Low 2.61 80 1029 122 15 5 45 NA 

Le - G40UH-60C-110-** 110 89 1895 11.5x10 3/4 Med-Low 2.68 80 1206 119 15 5 45 NA 

Le - G40UH-60C-11 0-** 110 89 1750 11.5 x 10 3/4 Med-Low 2.68 80 1206 119 15 5 45 NA 

Le - G50DF-60C-11 0-** 110 90 1835 11.5 x 10 1 Med-Low 2.61 80 1029 122 15 5 45 NA 

Le - G50UH-60C-110-** 110 89 1750 11.5 x 10 3/4 Med-Low 2.63 80 1206 119 15 5 45 NA 

Le - G50UH-60C-110-** 110 89 1895 11.5 x 10 3/4 Med-Low 2.63 80 1206 119 15 5 45 NA 

Am - ADS81155CN 115 92 1613 10 x 10 1/2 Med 2.66 80 701 75 NA NA NA NA 

Am - AMS81155CN 115 92 1639 10x 10 1/2 Med 2.66 80 701 75 NA NA NA NA 

Am - DDS81155CX 115 92 1613 10x 10 1/2 Med 2.66 80 701 75 NA NA NA NA 

Am - DMS81155CN 115 92 1639 10x 10 1/2 Med 2.66 80 701 75 NA NA NA NA 

Am - GCIC115**50 115 92 1710 10 x 9 3/4 Med-High 2.78 80 815 93 NA 15 30 NA 

Go - GDT115-5 115 92 1660 10 x 10 1/2 Med 2.66 80 701 75 NA NA 30 NA 

Go - GMT115-5 115 92 1650 10x 10 1/2 Med 2.86 80 701 75 NA NA 30 NA 

Go - GMTH115-5 115 92 - 80 930 75 NA NA NA NA 

Am - GUIC115**50 115 92 1850 10 x 9 3/4 Med-High 3.21 80 1051 75 NA 15 30 NA 

Am - GUID115**50 115 92 1850 10 x 10 3/4 Med-High 3.19 80 1015 75 NA 15 30 NA 

Am - GUIE0115**50 115 92 - 80 1095 87 NA NA NA NA 

Yo - GY8S115C20DN11 115 92 1940 11 xii 1 Med-High 2.74 80 1513 84 NA NA NA NA 

Yo - GY8S115C20DN11 115 92 1840 11 xii 1 Med-High 2.74 80 1513 84 NA NA NA NA 

Yo - GY8S115C20UH11 115 92 1940 11 xii 1 Med-High 2.74 80 1579 79 NA NA NA NA 

Yo - GY8S115C20UH11 115 92 1840 11 x 11 1 Med-High 2.74 80 1579 79 NA NA NA NA 

Yo - P4DNC20N09201 115 92 2190 11 x 10 1 High 2.74 80 1513 84 NA NA 30 NA 

Yo - P4HUC20N09201 115 92 2115 11 x 10 1 High 2.74 80 1579 79 NA NA 30 NA 

Yo - P4HUC20N09201 115 92 2130 11 x 10 1 High 2.74 80 1579 79 NA NA 30 NA 

Yo - PS8C20N115DN11 115 92 1790 11 x 10 1 Med-High 2.74 80 1513 84 NA NA NA NA 

Yo - PS8C20N115UH11 115 92 1940 11 xii 1 Med-High 3.23 80 1579 79 NA NA NA NA 

Yo - PS8C20N115UH11 115 92 1840 11 xii 1 Med-High 3.23 80 1579 79 NA NA NA NA 

Table H.3.24 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 120 Btu/h 

1600 CFM 

Non-Condensing Single-Stage 

120 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Te - ABA120NH4R 1335 82 1440 10 x 8 1/2 Med-High 2.49 80.2 1335 82 NA 5 30 NA 

Fr- FG6RA120*-16B 882 75 1120 10 x 10 1/2 Low 2.50 81 882 75 30 30 30 NA 

Le - G24M3/4-120* -** 810 60 1420 12 x8 1/2 Med-High - 80 810 60 15 5 45 NA 

B-21 
Table 11.3.25 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 120 Btu/h

2000 CFM

Non-Condensing Single-Stage

120 kBtu/h 2000 CF M

Air

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay

Area

Te - ABA120NH5R 120 98 1540 10 x 4 ( Dual) 3/4 Med- High 2.49 80. 2 1226 88 NA 5 30 NA

Am - COB120A960D * 120 96 - 80 1461 85 NA NA NA NA

Am - CUB120A960C* 120 96 - 80 1429 75 NA NA NA NA

Fr - FG6RA120*-20C 120 97 1260 11 x 10 3/4 Low 2. 88 80.5 790 75 30 30 30 NA

Fr - FG6RK120*-20B 120 97 1875 11 x 10 3/4 Med-High 2.50 80 960 50 30 30 30 NA

Le - G24M4/5-120S-** 120 96 1610 12 x 9 3/4 Med-Low - 80 1234 60 15 5 45 NA

Tr-TDD120C960F * 120 96 1866 11 x 10 1/2 Med-High 3. 12 80 1461 85 NA NA 45 NA

Tr - TDE120A960M* 120 96 1786 11 x 10 1/2 Med- High 3. 12 80 1461 85 NA NA 45 NA

Tr - TUD120C960K* 120 96 1777 11 x 10 1/2 Med-High 3.17 80 1429 75 NA NA 45 NA

Tr - TUE120A960L* 120 96 1777 11 x 10 1 /2 Med-High 3 . 17 80 1429 75 NA NA 45 NA

Table H.3.26 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 125 Btu/h

1600 CFM

Non-Condensing Single-Stage

125 kBtu/h 1600 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Th - MDA1-125 968 81 1790 3/4 High 2.75 81 968 81 NA NA 60 NA

Th - MDA-125 945 72 1240 1/2 Low 2.75 81 945 72 NA NA 60 NA

Th - MHA-125 959 72 1250 1/2 Low 2.75 80.5 959 72 NA NA 60 NA

Rh - RGLJ-12EARGR 1252 68 1580 11 x 10 1/2 Med 3.24 80 1252 68 30 5 20 NA

Rh - RGPJ-12EARGR 1520 79 1560 11 x 10 1/2 Med 3.60 80 1520 79 30 5 20 NA

Ca - 58DLX135-16* 994 95 1380 10 x 10 1/2 Med-Low - 80 994 95 15 5 25 NA

Ca - 58STX135-16* 1030 95 1720 10 x 10 1/2 Med-Low - 80 1030 95 15 5 25 NA

Ca - 58STX135-16* 1030 95 1380 10x 10 1/2 Med-Low - 80 1030 95 15 5 25 NA

Ca - 58DLA135-16 950 95 1380 10x 10 1/2 Med-Low - 80 950 95 15 5 25 NA

Ca - 58STA135-16 984 95 1380 10 x 10 1/2 Med-Low - 80 984 95 15 5 25 NA

Le - G40UH-48C-135-* 979 121 1495 10 x 10 1/2 Med-High 2.68 80 979 121 15 5 45 NA

Le - G50UH-48C-135-* 979 121 1495 10 x 10 1/2 Med-High 2.63 80 979 121, 15 5 45 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.25 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 120 Btu/h 

2000 CFM 

Non-Condensing Single-Stage 

120 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay 

Area 

Te - ABA120NH5R 120 98 1540 10 x 4 (Dual) 3/4 Med-High 2.49 80.2 1226 88 NA 5 30 NA 

Am - CDB120A960D* 120 96 - 80 1461 85 NA NA NA NA 

Am - CUB120A960C* 120 96 - 80 1429 75 NA NA NA NA 

Fr - FG6RA 120*-20C 120 97 1260 11 x 10 3/4 Low 2.88 80.5 790 75 30 30 30 NA 

Fr - FG6RK120*-20B 120 97 1875 11 x 10 3/4 Med-High 2.50 80 960 50 30 30 30 NA 

Le - G24M4/5-120S-** 120 96 1610 12 x 9 3/4 Med-Low - 80 1234 60 15 5 45 NA 

Tr - TDD120C960F* 120 96 1866 11 x 10 1/2 Med-High 3.12 80 1461 85 NA NA 45 NA 

Tr - TDE120A960M* 120 96 1786 11 x 10 1/2 Med-High 3.12 80 1461 85 NA NA 45 NA 

Tr - TUD120C960K* 120 96 1777 11 x 10 1/2 Med-High 3.17 80 1429 75 NA NA 45 NA 

Tr - TUE120A960L* 120 96 1777 11 x 10 1/2 Med-High 3.17 80 1429 75 NA NA 45 NA 

Table H.3.26 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 125 Btu/h 

1600 CFM 

Non-Condensing Single-Stage 

125 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Th - MDA1-125 968 81 1790 3/4 High 2.75 81 968 81 NA NA 60 NA 

Th - MDA-125 945 72 1240 1/2 Low 2.75 81 945 72 NA NA 60 NA 

Th - MHA-125 959 72 1250 1/2 Low 2.75 80.5 959 72 NA NA 60 NA 

Rh - RGLJ-12EARGR 1252 68 1580 11 x 10 1/2 Med 3.24 80 1252 68 30 5 20 NA 

Rh - RGPJ-12EARGR 1520 79 1560 11 x 10 1/2 Med 3.60 80 1520 79 30 5 20 NA 

Ca - 58DLX135-16* 994 95 1380 10 x 10 1/2 Med-Low - 80 994 95 15 5 25 NA 

Ca - 58STX135-16* 1030 95 1720 10 x 10 1/2 Med-Low - 80 1030 95 15 5 25 NA 

Ca - 58STX135-16* 1030 95 1380 10 x 10 1/2 Med-Low - 80 1030 95 15 5 25 NA 

Ca - 58DLA135-16 950 95 1380 10 x 10 1/2 Med-Low - 80 950 95 15 5 25 NA 

Ca - 58STA135-16 984 95 1380 10 x 10 1/2 Med-Low - 80 984 95 15 5 25 NA 

Le - G40UH-48C-135-* 979 121 1495 10 x 10 1/2 Med-High 2.68 80 979 121 15 5 45 NA 

Le - G50UH-48C-135-* 979 121 1495 10 x 10 1/2 Med-High 2.63 80 979 121 15 5 45 NA 

H-22 
Table H.3.27 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 125 Btu/h

2000 CFM

Non-Condensing Single-Stage

125 kBtu/h 2000 C FM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output AFUE Eae PE

0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Du - DPGB125A5* 125 101 2050 12 x 12 1/2 Med 2.43 90 1082 87 15 NA 30 NA

Du - FPBB125A5* 125 101 1910 12 x 12 3/4 Med 2 . 76 90 1082 87 15 15 30 NA

Ar - G1 D80BR125D20C*-*** 125 100 1840 12 x 10 3/4 Med-Low 2. 50 80 1054 92 NA NA NA NA

Ar - G1 D80BT125D20C*-*** 125 100 1800 12 x 10 3/4 Med-Low 2 . 72 80 986 92 NA NA NA NA

Ar - G1 N80BR125D20C*-*** 125 100 1256 12 x 10 3/4 Med-Low 2 . 50 80 1054 91 15 15 30 NA

Ar - G1 N80BU125D20C *-*** 125 100 1225 12 x 10 3/4 Med-Low 2 . 72 80 986 92 15 15 30 NA

Yo - G8C12520M ( DD,UD ) 12 125 100 1256 x 6 (Du 3/4 Low 3 . 19 80 1015 75 NA NA 30 NA

Yo - G8C12520M (DD,UD ) 12 125 100 1225 x 6 (Du 3/4 Low 3 . 19 80 1015 75 NA NA 30 NA

Th - MHA1-125 125 99 1343 3/4 High 2 . 75 80 910 78 NA NA 60 NA

Du - MPGA125B5* 125 101 1323 12 x 12 1/2 Med 2 . 62 80 1082 87 15 15 30 NA

Te - N8MPL125J20 125 100 1970 11 x 10 3/4 Med-High 2. 73 80 1879 73 3 30 30 NA

Te - N8MPN125J20 125 100 1840 11 x 10 1 /2 Med-High 2 . 73 80 1879 73 3 30 30 NA

Rh - RGLH-12EARJR 125 100 1561 11 x 10 3/4 Med-Low 3 . 24 80 1252 68 NA NA NA NA

Rh - RGLJ- 12EARJR 125 100 1561 11 x 10 3/4 Med 3.24 80 1252 68 30 5 20 NA

Rh - RGLN -12(E,N )ARJR 125 100 1580 - 80 . 1 1469 71 NA NA NA NA

Rh - RGPH-12EARJR 125 101 1930 11 x 10 3/4 Med-Low 3.24 80 1611 79 NA NA NA NA

Rh - RGPJ -12EARJR 125 101 11 x 10 3/4 Med 3 . 60 80 1520 79 30 5 20 NA

Rh - RGPN-12(E,N)ARJR 125 100 1560 11 x 10 3/4 Med-Low 3.24 80 1430 60 NA NA NA NA

Rh - RGPP- 12(E,N )ARJR 125 100 1885 11 x 10 3/4 Low 3 . 24 80 1315 62 NA NA NA NA

Te - T8DNL125L20 125 101 1560 11 x 10 3/4 Med-High 2 . 95 80 1063 80 3 30 30 NA

Te - T8MPL125J20 125 101 1560 11 x 10 1/2 Med-High 2.73 80 1815 90 3 30 30 NA

Te - T8MPN125J20 125 101 2061 11x10 1/2 Med-High 2 . 73 80 1815 90 3 30 30 NA

Fr - L1 RA126*20C 126 101 1561 11 x 10 3/4 Med-High 2 . 88 80 1390 78 30 30 30 NA

Yo - GY8S130D20DN11 130 104 1561 11 x 1l 1 Med-High 2 . 74 80 1609 76 NA NA NA NA

Yo - GY8S130D20DN11 130 104 1790 11 x 11 1 Med-High 2 . 74 80 1609 76 NA NA NA NA

Yo - GY8S130D20UH11 130 105 1930 11 x 1l 1 Med-High 2.74 80 1811 78 NA NA NA NA

Yo - GY8S130D20UH11 130 105 1890 11 x 11 1 Med-High 2. 74 80 1811 78 NA NA NA NA

Yo - P4DND20N10401 130 104 1930 11 x10 1 High 3 . 23 80 1609 76 NA NA 30 NA

Yo - P4HUD20N10401 130 105 1890 11 x10 1 High 3 . 23 80 1811 78 NA NA 30 NA

Yo - P4HUD20N10401 130 105 2095 11 x10 1 High 3 . 23 80 1811 78 NA NA 30 NA

Yo - PS8D20N130DN11 130 104 2120 11 x10 1 High 3 . 23 80 1609 76 NA NA NA NA

Yo - PS8D20N130UH11 130 105 2120 11 x 1l 1 High 3 . 23 80 1811 78 NA NA NA NA

Yo - PS8D20N130UH11 130 105 2110 11 x 1l 1 High 3 . 23 80 1811 78 NA NA NA NA

Le - G40DF-60D - 135-* 132 108 2230 1.5 x 1 3/4 Med-Low 3 . 07 80 1099 125 15 5 45 NA

Le - G40UH-60D-135 ` 132 107 2300 1 . 5 x 1 3/4 Low 3.16 80 1179 119 15 5 45 NA

Le - G40UH-60D-135 * 132 107 1870 1.5 x 1 3/4 Low 3 . 16 80 1179 119 15 5 45 NA

Le - G50DF-60D - 135-* 132 108 1605 1.5 x 1 1 Med-Low 3 . 07 80 1099 125 15 5 45 NA

Le - G50UH-60D-135-* 132 107 1535 1.5 x 1 3/4 Med-Low 3 . 16 80 1179 119 15 5 45 NA

Le - G50UH-60D-135-* 132 107 1870 1.5 x 1 3/4 Med-Low 3 . 16 80 1179 119 15 5 45 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.27 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 125 Btu/h 

2000 CFM 

Non-Condensing Single-Stage 

125 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Du - DPGB125A5* 125 101 2050 12 x 12 1/2 Med 2.43 90 1082 87 15 NA 30 NA 

Du - FPBB125A5* 125 101 1910 12 x 12 3/4 Med 2.76 90 1082 87 15 15 30 NA 

Ar - G1D80BR125D20C*-*** 125 100 1840 12 x 10 3/4 Med-Low 2.50 80 1054 92 NA NA NA NA 

Ar - G1D80BT125D20C*-*** 125 100 1800 12 x 10 3/4 Med-Low 2.72 80 986 92 NA NA NA NA 

Ar - G1 N80BR125D20C*-*** 125 100 1256 12 x 10 3/4 Med-Low 2.50 80 1054 91 15 15 30 NA 

Ar - G1 N80BU125D20C*-*** 125 100 1225 12 x 10 3/4 Med-Low 2.72 80 986 92 15 15 30 NA 

Yo - G8C12520M(DD.UD)12 125 100 1256 x 6 (Du 3/4 Low 3.19 80 1015 75 NA NA 30 NA 

Yo - G8C12520M(DD.UD)12 125 100 1225 x 6 (Du 3/4 Low 3.19 80 1015 75 NA NA 30 NA 

Th - MHA1-125 125 99 1343 3/4 High 2.75 80 910 78 NA NA 60 NA 

Du - MPGA125B5* 125 101 1323 12 x 12 1/2 Med 2.62 80 1082 87 15 15 30 NA 

Te - N8MPL 125J20 125 100 1970 11 x 10 3/4 Med-High 2.73 80 1879 73 3 30 30 NA 

Te - N8MPN125J20 125 100 1840 11 x 10 1/2 Med-High 2.73 80 1879 73 3 30 30 NA 

Rh - RGLH-12EARJR 125 100 1561 11 x 10 3/4 Med-Low 3.24 80 1252 68 NA NA NA NA 

Rh - RGLJ-12EARJR 125 100 1561 11 x 10 3/4 Med 3.24 80 1252 68 30 5 20 NA 

Rh - RGLN-12(E.N)ARJR 125 100 1580 - 80.1 1469 71 NA NA NA NA 

Rh - RGPH-12EARJR 125 101 1930 11 x 10 3/4 Med-Low 3.24 80 1611 79 NA NA NA NA 

Rh - RGPJ-12EARJR 125 101 11 x 10 3/4 Med 3.60 80 1520 79 30 5 20 NA 

Rh - RGPN-12(E.N)ARJR 125 100 1560 11 x 10 3/4 Med-Low 3.24 80 1430 60 NA NA NA NA 

Rh - RGPP-12(E.N)ARJR 125 100 1885 11 x 10 3/4 Low 3.24 80 1315 62 NA NA NA NA 

Te - T8DNL 125L20 125 101 1560 11 x 10 3/4 Med-High 2.95 80 1063 80 3 30 30 NA 

Te - T8MPL 125J20 125 101 1560 11 x 10 1/2 Med-High 2.73 80 1815 90 3 30 30 NA 

Te - T8MPN125J20 125 101 2061 11 x 10 1/2 Med-High 2.73 80 1815 90 3 30 30 NA 

Fr - L 1RA126*20C 126 101 1561 11 x 10 3/4 Med-High 2.88 80 1390 78 30 30 30 NA 

Yo - GY8S130D20DN11 130 104 1561 11 x 11 1 Med-High 2.74 80 1609 76 NA NA NA NA 

Yo - GY8S130D20DN11 130 104 1790 11 x 11 1 Med-High 2.74 80 1609 76 NA NA NA NA 

Yo - GY8S130D20UH11 130 105 1930 11 x 11 1 Med-High 2.74 80 1811 78 NA NA NA NA 

Yo - GY8S130D20UH11 130 105 1890 11 x 11 1 Med-High 2.74 80 1811 78 NA NA NA NA 

Yo - P4DND20N10401 130 104 1930 11 x 10 1 High 3.23 80 1609 76 NA NA 30 NA 

Yo - P4HUD20N10401 130 105 1890 11 x 10 1 High 3.23 80 1811 78 NA NA 30 NA 

Yo - P4HUD20N10401 130 105 2095 11 x 10 1 High 3.23 80 1811 78 NA NA 30 NA 

Yo - PS8D20N130DN11 130 104 2120 11 x 10 1 High 3.23 80 1609 76 NA NA NA NA 

Yo - PS8D20N130UH11 130 105 2120 11 x 11 1 High 3.23 80 1811 78 NA NA NA NA 

Yo - PS8D20N130UH11 130 105 2110 11 x 11 1 High 3.23 80 1811 78 NA NA NA NA 

Le - G40DF-60D-135-* 132 108 2230 1.5 x 1 3/4 Med-Low 3.07 80 1099 125 15 5 45 NA 

Le - G40UH-60D-135-* 132 107 2300 1.5 x 1 3/4 Low 3.16 80 1179 119 15 5 45 NA 

Le - G40UH-60D-135-* 132 107 1870 1.5 x 1 3/4 Low 3.16 80 1179 119 15 5 45 NA 

Le - G50DF-60D-135-* 132 108 1605 1.5 x 1 1 Med-Low 3.07 80 1099 125 15 5 45 NA 

Le - G50UH-60D-135-* 132 107 1535 1.5 x 1 3/4 Med-Low 3.16 80 1179 119 15 5 45 NA 

Le - G50UH-60D-135-* 132 107 1870 1.5 x 1 3/4 Med-Low 3.16 80 1179 119 15 5 45 NA 

H-23 
Table H.3.28 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 140 Btu/h

2000 CFM

Non-Condensing Single-Stage

140 kBtu/h 2000 C FM

Air

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay

Area

Go - GMT135-3 135 108 1700 11 x 10 3/4 Med 3.34 80 850 75 NA NA 30 NA

Am - GCIC140**50 138 112 1845 10x9 3/4 High 2.78 80 1314 89 NA 15 30 NA

Am - GUIC140**50 138 111 2050 10x9 3/4 High 3.21 80 1126 82 NA 15 30 NA

Te - ABA140NH5R 140 114 1715 10 x 6 (Dual) 3/4 Med-High 2.89 80.2 1294 88 NA 5 30 NA

Am - AMS81405CX 140 112 1672 11 x 10 3/4 Med 3.13 80 850 75 NA NA NA NA

Am - AMS81405DN 140 112 1672 11 x 10 3/4 Med 3.13 80 850 75 NA NA NA NA

Am - CUB140A960C* 140 111 - 80 1614 85 NA NA NA NA

Am - DMS81405DN 140 112 1435 10 x 10 3/4 Med-Low 2.66 80 850 75 NA NA NA NA

Le - G24M4/5-140S-** 140 112 2000 12 x 9 3/4 Med-High - 80 678 60 15 5 45 NA

Go - GMT140-5 140 112 - 80 850 75 NA NA 30 NA

Tr - TDD140C960F* 140 113 1938 11 x 10 3/4 Med-High 3.12 80 1444 77 NA NA 45 NA

Tr - TUD140C960K* 140 111 2011 11 x 10 3/4 Med-High 3.17 80 1614 85 NA NA 45 NA

Tr - TUE140A960L* 140 111 2011 11 x 10 3/4 Med-High 3.17 80 1614 85 NA NA 45 NA

Fr - FG6RA144*-20C 144 116 1250 11 x 10 3/4 Low 2.88 80 1389 75 30 30 30 NA

Ca - 58DLX155-20* 147 119 1695 11 x 11 3/4 Med-Low - 80 1562 96 15 5 25 NA

Ca - 58STX155-20* 147 119 1695 11 x 11 3/4 Med-Low - 80 1534 96 15 5 25 NA

Ca - 58STX155-20* 147 119 1695 11 x 11 3/4 Med-Low - 80 1534 96 15 5 25 NA

H.3.2 Condensing Single-Stage Non-Weatherized Gas Furnaces

Table H.3.29 Condensing Single-Stage Non-Weatherized Gas Furnaces at 45 Btu/h 800

CFM

Condensing Single-Stage

45 kBtu/h 800 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Ca - 58MCA040-08 40 37 685 10x6 1/5 Med-Low 2.09 92.1 325 70 15 15 66 NA

Ca - 58MCA040-08* 40 37 685 10x6 1/5 Med-Low 2.09 91 329 70 15 15 66 NA

Ca - 58MSA040-08 40 37 685 10x6 1/5 Med-Low 2.09 90 332 70 15 15 66 NA

Ca - 58MXA040-08 40 38 685 10x6 1/5 Med-Low 2.09 94.3 317 70 15 15 66 NA

Ca - 58MXA040-08* 40 38 685 10x6 1/5 Med-Low 2.09 92.9 322 70 15 15 66 NA

Ca - 58MXA040-08** 40 38 685 10x6 1/5 Med-Low 2.09 93.7 319 70 15 15 66 NA

Am - CDC040A924A* 40 38 - 90 329 79 NA NA NA NA

Am - CUC040A924A* 40 37 - 90 333 78 NA NA NA NA

Fr - FG6RC040*-08A 40 37 470 10x6 1/5 Low 1.75 92.1 339 90 30 30 30 NA

Tr - TDC040C924B* 40 38 596 10x7 1/5 Med-Low 2.11 91 326 79 NA NA 45 NA

Tr - TDX040C924D* 40 38 596 10x7 1/5 Med-Low 2.17 91 335 74 NA NA 45 NA

Tr-T00040C924B* 40 37 649 9 x 7 1/5 Med-Low 2.21 92.1 326 78 NA NA 45 NA

Tr - TUX040C924D* 40 38 649 9 x 7 1/5 Med-Low 2.21 92.1 346 75 NA NA 45 NA

Le - G41 OF-24B-045-** 44 40 740 10x7 1/5 Low 2.21 90 373 140 15 5 45 NA

Le - G43UF-24B-045-** 44 41 700 10x7 1/5 Med-Low 2.21 92.1 427 , 139 , 15 5 45 NA

H-24

 EE-RM/STD-01-350 COMMENT 164

Table H.3.28 Non-Condensing Single-Stage Non-Weatherized Gas Furnaces at 140 Btu/h 

2000 CFM 

Non-Condensing Single-Stage 

140 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Oft0.5 Size Taps Outlet purge purge Delay Delay 

Area 

Go - GMT135-3 135 108 1700 11 x 10 3/4 Med 3.34 80 850 75 NA NA 30 NA 

Am - GCIC140**50 138 112 1845 10 x 9 3/4 High 2.78 80 1314 89 NA 15 30 NA 

Am - GUIC140**50 138 111 2050 10 x 9 3/4 High 3.21 80 1126 82 NA 15 30 NA 

Te - ABA140NH5R 140 114 1715 10 x 6 (Dual) 3/4 Med-High 2.89 80.2 1294 88 NA 5 30 NA 

Am - AMS81405CX 140 112 1672 11 x 10 3/4 Med 3.13 80 850 75 NA NA NA NA 

Am - AMS81405DN 140 112 1672 11 x 10 3/4 Med 3.13 80 850 75 NA NA NA NA 

Am - CUB140A960C* 140 111 - 80 1614 85 NA NA NA NA 

Am - DMS81405DN 140 112 1435 10 x 10 3/4 Med-Low 2.66 80 850 75 NA NA NA NA 

Le - G24M4/5-140S-** 140 112 2000 12 x 9 3/4 Med-High - 80 678 60 15 5 45 NA 

Go - GMT140-5 140 112 - 80 850 75 NA NA 30 NA 

Tr - TDD140C960F* 140 113 1938 11 x 10 3/4 Med-High 3.12 80 1444 77 NA NA 45 NA 

Tr - TUD140C960K* 140 111 2011 11 x 10 3/4 Med-High 3.17 80 1614 85 NA NA 45 NA 

Tr - TUE140A960L * 140 111 2011 11 x 10 3/4 Med-High 3.17 80 1614 85 NA NA 45 NA 

Fr - FG6RA144*-20C 144 116 1250 11 x 10 3/4 Low 2.88 80 1389 75 30 30 30 NA 

Ca - 58DLX155-20* 147 119 1695 11 xii 3/4 Med-Low - 80 1562 96 15 5 25 NA 

Ca - 58STX 155-20* 147 119 1695 11 x 11 3/4 Med-Low - 80 1534 96 15 5 25 NA 

Ca - 58STX155-20* 147 119 1695 11 x 11 3/4 Med-Low - 80 1534 96 15 5 25 NA 

H.3.2 Condensing Single-Stage Non-Weatherized Gas Furnaces 

Table H.3.29 Condensing Single-Stage Non-Weatherized Gas Furnaces at 45 Btu/h 800 

CFM 

Condensing Single-Stage 

45 kBtu/h 800 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Ca - 58MCA040-08 40 37 685 10 x 6 1/5 Med-Low 2.09 92.1 325 70 15 15 66 NA 

Ca - 58MCA040-08* 40 37 685 10 x 6 1/5 Med-Low 2.09 91 329 70 15 15 66 NA 

Ca - 58MSA040-08 40 37 685 10 x 6 1/5 Med-Low 2.09 90 332 70 15 15 66 NA 

Ca - 58MXA040-08 40 38 685 10 x 6 1/5 Med-Low 2.09 94.3 317 70 15 15 66 NA 

Ca - 58MXA040-08* 40 38 685 10 x 6 1/5 Med-Low 2.09 92.9 322 70 15 15 66 NA 

Ca - 58MXA040-08** 40 38 685 10 x 6 1/5 Med-Low 2.09 93.7 319 70 15 15 66 NA 

Am - CDC040A924A* 40 38 - 90 329 79 NA NA NA NA 

Am - CUC040A924A* 40 37 - 90 333 78 NA NA NA NA 

Fr - FG6RC040*-08A 40 37 470 10 x 6 1/5 Low 1.75 92.1 339 90 30 30 30 NA 

Tr - TDC040C924B* 40 38 596 10 x 7 1/5 Med-Low 2.11 91 326 79 NA NA 45 NA 

Tr - TDX040C924D* 40 38 596 10 x 7 1/5 Med-Low 2.17 91 335 74 NA NA 45 NA 

Tr - TUC040C924B* 40 37 649 9x7 1/5 Med-Low 2.21 92.1 326 78 NA NA 45 NA 

Tr - TUX040C924D* 40 38 649 9x7 1/5 Med-Low 2.21 92.1 346 75 NA NA 45 NA 

Le - G41 UF-24B-045-** 44 40 740 10 x 7 1/5 Low 2.21 90 373 140 15 5 45 NA 

Le - G43UF-24B-045-** 44 41 700 10 x 7 1/5 Med-Low 2.21 92.1 427 139 15 5 45 NA 

H-24 
Table H.3.30 Condensing Single-Stage Non-Weatherized Gas Furnaces at 45 Btu/h 1200

CFM

Condensing Single-Stage

45 kBtu/h 1200 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output AFUE Eae PE 0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Ca - 58MCA040-12 40 37 990 10x7 1/3 Med-Low 2.09 92.1 474 71 15 15 66 NA

Ca - 58MCA040-12* 40 37 990 10x7 1/3 Med-Low 2.09 91 480 71 15 15 66 NA

Ca - 58MSA040-12 40 37 990 10x7 1/3 Med-Low 2.09 90 484 71 15 15 66 NA

Ca - 58MXA040-12 40 38 990 10x7 1/3 Med-Low 2.09 95.5 458 71 15 15 66 NA

Ca - 58MXA040-12* 40 38 990 10x7 1/3 Med-Low 2.09 94 465 71 15 15 66 NA

Ca - 58MXA040-12** 40 38 990 10x7 1/3 Med-Low 2.09 94.9 460 71 15 15 66 NA

Fr - FG6RC040*-12A 40 37 720 10x6 1/3 Low 1.75 92.1 442 90 30 30 30 NA

Fr - FG6RL040*-12A 40 36 780 10x6 1/3 Low 1.75 90 894 70 30 30 30 NA

Go - GMNT040-3 40 36 1040 10x6 1/3 Med 1.70 92.6 331 90 15 NA 30 NA

Yo - GY9S040A12UP11* 40 38 955 11x8 1/2 Med-Low 1.84 94 506 130 NA NA NA NA

Yo - PS9A1 2NO40UP1 1 40 38 955 11 x 8 1/2 Med-Low 1.84 94 506 130 NA NA NA NA

Le - G41 OF-36B-045-** 44 41 1080 10x8 1/3 Med-Low 2.21 90 501 143 15 5 45 NA

Le - G51 MP-36B-045-** 44 41 1080 10x8 1/3 Med-Low 2.21 92.1 468 143 15 5 45 NA

Ar - CG90CB045D12B*--*** 45 40 - 90 450 123 15 15 30 NA

Ar - G1D93BC045D12B`--*** 45 41 798 10x8 1/3 Med 2.06 92.5 660 123 NA NA NA NA

Ar-G1D93BU045D12B*-*** 45 41 816 10x8 1/3 Med 2.24 92.5 660 123 NA NA NA NA

Rh - RGRA-04(E,N)MAES 45 42 775 11 x 7 1/2 Med-Low 2.27 93.5 412 109 NA NA NA NA

Rh - RGRJ-04(E,N)MAES 45 42 775 11 x 7 1/2 Med-Low 2.27 93.5 412 109 30 5 20 NA

Rh - RGRK-04(E,N)MAES 45 41 775 11 x 7 1/2 Med-Low 2.27 92 737 101 NA NA NA NA

Rh - RGTA-04(E,N)MAES 45 41 785 11 x 7 1/2 Med-Low 2.27 92 436 89 NA NA NA NA

Rh - RGTJ-04(E,N)MAES 45 41 785 11 x 7 1/2 Med-Low 2.27 92 436 89 30 5 20 NA

Am - ACS90453BX 46 43 1012 10x7 1/3 Med 1.88 93 512 132 NA NA NA NA

Am - AMS90453BX 46 43 1012 10x7 1/3 Med 2.18 93 592 132 NA NA NA NA

Am - DMS90453BX 46 43 1012 10x7 1/3 Med 2.18 93 592 132 NA NA NA NA

Am - GCCA045*X30 46 43 816 11 x6 1/3 Med-Low 1.75 92.1 512 133 NA 15 30 NA

Am - GUCA045*X30 46 43 807 11 x6 1/3 Med-Low 2.10 92.1 592 132 NA 15 30 NA

Am - GULA045*X30 46 42 807 11X6 , 1/3 Med-Low 2.10 92.1 592 132 NA NA NA NA

Table H.3.31 Condensing Single-Stage Non-Weatherized Gas Furnaces at 50 Btu/h 800

CFM

Condensing Single-Stage

50 kBtu/h 800 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Th - CDB-50 50 47 420 1/5 Low 2.13 93 311 120 15 5 45 NA

Th - CDBI-50 50 47 930 1/5 High 1.88 91.5 329 119 15 5 45 NA

Th - CHB-50 50 47 420 1/5 Low 2.13 94.5 322 115 15 5 45 NA

Th - CHBI-50 50 47 860 1/5 High 1.88 94.5 309 119 15 5 45 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.30 Condensing Single-Stage Non-Weatherized Gas Furnaces at 45 Btu/h 1200 

CFM 

Condensing Single-Stage 

45 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On0.5 Size Size Taps Outlet purge purge Delay 

Area 

Ca - 58MCA040-12 40 37 990 10 x 7 1/3 Med-Low 2.09 92.1 474 71 15 15 66 

Ca - 58MCA040-12* 40 37 990 10 x 7 1/3 Med-Low 2.09 91 480 71 15 15 66 

Ca - 58MSA040-12 40 37 990 10 x 7 1/3 Med-Low 2.09 90 484 71 15 15 66 

Ca - 58MXA040-12 40 38 990 10 x 7 1/3 Med-Low 2.09 95.5 458 71 15 15 66 

Ca - 58MXA040-12* 40 38 990 10 x 7 1/3 Med-Low 2.09 94 465 71 15 15 66 

Ca - 58MXA040-12** 40 38 990 10 x 7 1/3 Med-Low 2.09 94.9 460 71 15 15 66 

Fr - FG6RC040*-12A 40 37 720 10 x 6 1/3 Low 1.75 92.1 442 90 30 30 30 

Fr - FG6RL040*-12A 40 36 780 10 x 6 1/3 Low 1.75 90 894 70 30 30 30 

Go - GMNT040-3 40 36 1040 10 x 6 1/3 Med 1.70 92.6 331 90 15 NA 30 

Yo - GY9S040A12UP11* 40 38 955 11 x 8 1/2 Med-Low 1.84 94 506 130 NA NA NA 

Yo - PS9A12N040UP11 40 38 955 11 x 8 1/2 Med-Low 1.84 94 506 130 NA NA NA 

Le - G41 UF-36B-045-** 44 41 1080 10 x 8 1/3 Med-Low 2.21 90 501 143 15 5 45 

Le - G51MP-36B-045-** 44 41 1080 10 x 8 1/3 Med-Low 2.21 92.1 468 143 15 5 45 

Ar - CG90CB045D12B*-*** 45 40 - 90 450 123 15 15 30 

Ar - G1D93BC045D12B*-*** 45 41 798 10 x 8 1/3 Med 2.06 92.5 660 123 NA NA NA 

Ar - G1D93BU045D12B*-*** 45 41 816 10 x 8 1/3 Med 2.24 92.5 660 123 NA NA NA 

Rh - RGRA-04(E,N)MAES 45 42 775 11 x 7 1/2 Med-Low 2.27 93.5 412 109 NA NA NA 

Rh - RGRJ-04(E,N)MAES 45 42 775 11 x 7 1/2 Med-Low 2.27 93.5 412 109 30 5 20 

Rh - RGRK-04(E,N)MAES 45 41 775 11 x 7 1/2 Med-Low 2.27 92 737 101 NA NA NA 

Rh - RGTA-04(E,N)MAES 45 41 785 11 x 7 1/2 Med-Low 2.27 92 436 89 NA NA NA 

Rh - RGT J-04(E,N)MAES 45 41 785 11 x 7 1/2 Med-Low 2.27 92 436 89 30 5 20 

Am - ACS90453BX 46 43 1012 10 x 7 1/3 Med 1.88 93 512 132 NA NA NA 

Am - AMS90453BX 46 43 1012 10 x 7 1/3 Med 2.18 93 592 132 NA NA NA 

Am - DMS90453BX 46 43 1012 10 x 7 1/3 Med 2.18 93 592 132 NA NA NA 

Am - GCCA045*X30 46 43 816 11 x 6 1/3 Med-Low 1.75 92.1 512 133 NA 15 30 

Am - GUCA045*X30 46 43 807 11 x 6 1/3 Med-Low 2.10 92.1 592 132 NA 15 30 

Am - GULA045*X30 46 42 807 11 x 6 1/3 Med-Low 2.10 92.1 592 132 NA NA NA 

Table H.3.31 Condensing Single-Stage Non-Weatherized Gas Furnaces at 50 Btu/h 800 

CFM 

Condensing Single-Stage 

50 kBtu/h 800 CFM 

Air 

CFM Blower Motor Speed Supply Pre- Post- OnOffDelay 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

Off- Models Input Output AFUE Eae PE 

0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Th - COB-50 50 47 420 1/5 Low 2.13 93 311 120 15 5 45 NA 

Th - CDBI-50 50 47 930 1/5 High 1.88 91.5 329 119 15 5 45 NA 

Th - CHB-50 50 47 420 1/5 Low 2.13 94.5 322 115 15 5 45 NA 

Th - CHBI-50 50 47 860 1/5 High 1.88 94.5 309 119 15 5 45 NA 

H-25 
Table H.3.32 Condensing Single-Stage Non-Weatherized Gas Furnaces at 50 Btu/h 1200

CFM

Condensing Single-Stage

50 kBtu/h 1 200 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output AFUE Eae PE 0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Ar-CG90T13050D12B* 50 45 - 90 680 123 15 15 30 NA

Ar-CG90UB050D12B*-*** 50 45 - 90 680 123 15 15 30 NA

Du - CMPB050C3* 50 46 1110 10x6 1/3 Med 1.51 92 615 87 15 15 30 NA

Du - CMPE050U3* 50 46 928 10x6 1/3 Med 1.51 92 583 84 15 15 30 NA

Ar - G1 D90AH050D12A*-*** 50 45 750 12 x 6 1/3 Low 1.92 90 828 82 NA NA NA NA

Ar - G1 D91 BT050D12B* 50 45 816 10x8 1/3 Med 2.24 91 680 123 15 15 30 NA

Ar-G1D91BU050131213*-*** 50 45 816 10x8 1/3 Med 2.24 91 680 123 NA NA NA NA

01 - GTH 050 50 47 755 12x7 1/2 Med-Low 2.29 94 808 75 15 5 30 180

Te - N9MP1050B12** 50 44 1093 11x8 1/2 Med-High 1.80 90 710 112 3 30 30 NA

Te - N9MP2050B12** 50 44 1093 11x8 1/2 Med-High 1.80 90 707 112 3 30 30 NA

Te - T9MPD050F12** 50 46 1093 11 x 8 1/2 Med-High 2.26 92 720 119 3 30 30 NA

Te - CSA054NH3R 54 48 1040 10x6 1/3 Med-High 2.10 90 625 74 NA 5 30 NA

Te - VSA054NH3R 54 49 1040 10 x 6 1/3 Med-High 2.10 91 695 77 NA 5 30 NA

Table H.3.33 Condensing Single-Stage Non-Weatherized Gas Furnaces at 60 Btu/h 800

CFM

Condensing Single-Stage

60 kBtu/h 800 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output AFUE Eae PE 0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Ca - 58MCA060-08 60 56 705 10x6 1/5 Med-Low 2 . 09 92 . 1 419 80 15 15 66 NA

Ca - 58MCA060-08* 60 56 705 10x6 1/5 Med-Low 2.09 91 423 80 15 15 66 NA

Ca - 58MSA060 -08 60 55 705 10x6 1/5 Med-Low 2 .09 90 428 80 15 15 66 NA

Ca - 58MXA060-08 60 56 705 10x6 1/5 Med-Low 2.09 93.1 414 80 15 15 66 NA

Ca - 58MXA060 -08* 60 56 705 10x6 1/5 Med-Low 2 .09 91.7 420 80 15 15 66 NA

Ca - 58MXA060 -08** 60 56 705 10x6 1/5 Med-Low 2 . 09 92. 5 416 80 15 15 66 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.32 Condensing Single-Stage Non-Weatherized Gas Furnaces at 50 Btu/h 1200 

CFM 

Condensing Single-Stage 

50 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Ar - CG90TB050D12B* 50 45 - 90 680 123 15 15 30 NA 

Ar - CG90UB050D12B*-*** 50 45 - 90 680 123 15 15 30 NA 

Du - CMPB050C3* 50 46 1110 10 x 6 1/3 Med 1.51 92 615 87 15 15 30 NA 

Du - CMPE050U3* 50 46 928 10 x 6 1/3 Med 1.51 92 583 84 15 15 30 NA 

Ar - G1090AH050D12A*-*** 50 45 750 12 x 6 1/3 Low 1.92 90 828 82 NA NA NA NA 

Ar - G1 D91 BT050D12B* 50 45 816 10 x 8 1/3 Med 2.24 91 680 123 15 15 30 NA 

Ar - G1 091BU050D12B*-*** 50 45 816 10 x 8 1/3 Med 2.24 91 680 123 NA NA NA NA 

01- GTH 050 50 47 755 12 x 7 1/2 Med-Low 2.29 94 808 75 15 5 30 180 

Te - N9MP1050B12** 50 44 1093 11 x 8 1/2 Med-High 1.80 90 710 112 3 30 30 NA 

Te - N9MP2050B12** 50 44 1093 11 x 8 1/2 Med-High 1.80 90 707 112 3 30 30 NA 

Te - T9MPD050F12** 50 46 1093 11 x 8 1/2 Med-High 2.26 92 720 119 3 30 30 NA 

Te - CSA054NH3R 54 48 1040 10 x 6 1/3 Med-High 2.10 90 625 74 NA 5 30 NA 

Te - VSA054NH3R 54 49 1040 10 x 6 1/3 Med-High 2.10 91 695 77 NA 5 30 NA 

Table H.3.33 Condensing Single-Stage Non-Weatherized Gas Furnaces at 60 Btu/h 800 

CFM 

Condensing Single-Stage 

60 kBtu/h 800 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Ca - 58MCA060-08 60 56 705 10 x 6 1/5 Med-Low 2.09 92.1 419 80 15 15 66 NA 

Ca - 58MCA060-08* 60 56 705 10 x 6 1/5 Med-Low 2.09 91 423 80 15 15 66 NA 

Ca - 58MSA060-08 60 55 705 10 x 6 1/5 Med-Low 2.09 90 428 80 15 15 66 NA 

Ca - 58MXA060-08 60 56 705 10 x 6 1/5 Med-Low 2.09 93.1 414 80 15 15 66 NA 

Ca - 58MXA060-08* 60 56 705 10 x 6 1/5 Med-Low 2.09 91.7 420 80 15 15 66 NA 

Ca - 58MXA060-08** 60 56 705 10 x 6 1/5 Med-Low 2.09 92.5 416 80 15 15 66 NA 

H-26 
Table H.3.34 Condensing Single-Stage Non-Weatherized Gas Furnaces at 60 Btu/h 1200

CFM

Condensing Single-Stage

60 kBtu/h 1200 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output 0.5 Size Size Taps Outlet AFUE Eae PE

purge purge Delay Delay

Area

Ca - 58MCA060-12 60 56 975 10 x 7 1/3 Med-Low 2.09 92.1 483 76 15 15 66 NA

Ca - 58MCA060-12* 60 56 975 10x7 1/3 Med-Low 2.09 91 489 76 15 15 66 NA

Ca - 58MSA060-12 60 55 975 10x7 1/3 Med-Low 2.09 90 493 76 15 15 66 NA

Ca - 58MXA060-12 60 56 975 10x7 1/3 Med-Low 2.09 93.1 477 76 15 15 66 NA

Ca - 58MXA060-12* 60 56 975 10x7 1/3 Med-Low 2.09 91.7 484 76 15 15 66 NA

Ca - 58MXA060-12** 60 56 975 10 x 7 1/3 Med-Low 2.09 92.5 480 76 15 15 66 NA

Am - CDC060A936A* 60 56 - 90 504 80 NA NA NA NA

Am - CUC060A936A* 60 56 - 90 497 84 NA NA NA NA

Fr - FG6RC060*-12A 60 55 710 10x6 1/3 Low 1.75 92.1 835 90 30 30 30 NA

Fr - FG6RL060*-12A 60 54 760 10x6 1/3 Low 1.75 90 891 70 30 30 30 NA

Go - GMNT060-3 60 55 1035 10 x 6 1/3 Med 1.70 92.6 467 90 15 NA 30 NA

Yo - GY9S060B12DH11* 60 56 902 11 x8 1/2 Med-Low 1.84 91 940 150 NA NA NA NA

Yo - GY9S060B1 2UP1 1 * 60 56 940 11 x8 1/2 Med-Low 2.26 92 939 150 NA NA NA NA

Fr- L1RC060*-12A 60 56 985 10x6 1/3 Med 1.76 92.1 650 135 30 30 30 NA

Yo - PS9B12N060DH11 60 57 902 11 x8 1/2 Med-Low 1.84 92 710 155 NA NA NA NA

Yo - PS9B12N060UP11* 60 56 940 11 x8 1/2 Med-Low 2.26 92 939 150 NA NA NA NA

Rh - RGRA-06(E,N)MAES 60 56 760 11 x 7 1/2 Med-Low 2.27 92.5 490 92 NA NA NA NA

Rh - RGRJ-06(E,N)MAES 60 56 760 11 x 7 1/2 Low 2.27 92.5 490 92 30 5 20 NA

Rh - RGRK-06(E,N)MAES 60 55 760 11 x 7 1/2 Med-Low 2.27 92 578 104 NA NA NA NA

Rh - RGTA-06(E,N)MAES 60 56 770 11 x 7 1/2 Med-Low 2.27 92.4 484 110 NA NA NA NA

Rh - RGTJ-06(E,N)MAES 60 56 770 11 x 7 1/2 Low 2.27 92.4 484 110 30 5 20 NA

Tr - TDC060C936B* 60 56 901 10x8 1/3 Med-Low 2.11 91 499 80 NA NA 45 NA

Tr - TDX060C936D* 60 56 1009 10x8 1/3 Med-Low 2.17 91 512 90 NA NA 45 NA

Tr - TUC060C936B* 60 56 1106 10x7 1/3 Med-High 2.21 92.1 487 84 NA NA 45 NA

Tr - TUX060C936D* 60 56 1106 10 x 7 1/3 Med-High 2.21 92.1 544 74 NA NA 45 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.34 Condensing Single-Stage Non-Weatherized Gas Furnaces at 60 Btu/h 1200 

CFM 

Condensing Single-Stage 

60 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Ca - 58MCA060-12 60 56 975 10 x 7 1/3 Med-Low 2.09 92.1 483 76 15 15 66 NA 

Ca - 58MCA060-12* 60 56 975 10 x 7 1/3 Med-Low 2.09 91 489 76 15 15 66 NA 

Ca - 58MSA060-12 60 55 975 10 x 7 1/3 Med-Low 2.09 90 493 76 15 15 66 NA 

Ca - 58MXA060-12 60 56 975 10 x 7 1/3 Med-Low 2.09 93.1 477 76 15 15 66 NA 

Ca - 58MXA060-12* 60 56 975 10 x 7 113 Med-Low 2.09 91.7 484 76 15 15 66 NA 

Ca - 58MXA060-12** 60 56 975 10 x 7 1/3 Med-Low 2.09 92.5 480 76 15 15 66 NA 

Am - CDC060A936A* 60 56 - 90 504 80 NA NA NA NA 

Am - CUC060A936A* 60 56 - 90 497 84 NA NA NA NA 

Fr - FG6RC060*-12A 60 55 710 10 x 6 1/3 Low 1.75 92.1 835 90 30 30 30 NA 

Fr - FG6RL060*-12A 60 54 760 10 x 6 1/3 Low 1.75 90 891 70 30 30 30 NA 

Go - GMNT060-3 60 55 1035 10 x 6 1/3 Med 1.70 92.6 467 90 15 NA 30 NA 

Yo - GY9S060B12DH11* 60 56 902 11 x 8 1/2 Med-Low 1.84 91 940 150 NA NA NA NA 

Yo - GY9S060B12UP11 * 60 56 940 11 x 8 1/2 Med-Low 2.26 92 939 150 NA NA NA NA 

Fr- L 1RC060*-12A 60 56 985 10 x 6 1/3 Med 1.76 92.1 650 135 30 30 30 NA 

Yo - PS9B12N060DH11 60 57 902 11 x 8 1/2 Med-Low 1.84 92 710 155 NA NA NA NA 

Yo - PS9B12N060UP11 * 60 56 940 11 x 8 1/2 Med-Low 2.26 92 939 150 NA NA NA NA 

Rh - RGRA-06(E,N)MAES 60 56 760 11 x 7 1/2 Med-Low 2.27 92.5 490 92 NA NA NA NA 

Rh - RGRJ-06(E,N)MAES 60 56 760 11 x 7 1/2 Low 2.27 92.5 490 92 30 5 20 NA 

Rh - RGRK-06(E,N)MAES 60 55 760 11 x 7 1/2 Med-Low 2.27 92 578 104 NA NA NA NA 

Rh - RGTA-06(E,N)MAES 60 56 770 11 x 7 1/2 Med-Low 2.27 92.4 484 110 NA NA NA NA 

Rh - RGT J-06(E,N)MAES 60 56 770 11 x 7 1/2 Low 2.27 92.4 484 110 30 5 20 NA 

Tr - TDC060C936B* 60 56 901 10 x 8 1/3 Med-Low 2.11 91 499 80 NA NA 45 NA 

Tr - TDX060C936D* 60 56 1009 10 x 8 1/3 Med-Low 2.17 91 512 90 NA NA 45 NA 

Tr - TUC060C936B* 60 56 1106 10 x 7 113 Med-High 2.21 92.1 487 84 NA NA 45 NA 

Tr - TUX060C936D* 60 56 1106 10 x 7 113 Med-High 2.21 92.1 544 74 NA NA 45 NA 

H-27 
Table H.3.35 Condensing Single-Stage Non-Weatherized Gas Furnaces at 70 Btu/h 1200

CFM

Condensing Single-Stage

70 kBtu/h 1200 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Le - G41 OF-36B-070-** 66 61 1080 10 x 8 1/3 Med-Low 2.21 90 706 140 15 5 45 NA

Le - G43UF-36B-070-** 66 62 1080 10x8 1/3 Med-Low 2.21 92.1 700 147 15 5 45 NA

Le - G51 MP-36B-070** 66 62 1080 10x8 1/3 Med-Low 2.21 92.1 700 147 15 5 45 NA

Ar - CG90CB067D12B*-*** 67.5 60 - 90 650 123 15 15 30 NA

Ar - G1D93BC067D12B*-*** 67.5 62 943 10 x 8 1/3 Med 2.06 92.5 850 123 NA NA NA NA

Ar - G1D93BU067D12B`--*** 67.5 62 912 10x8 1/3 Med 2.24 92.5 850 123 NA NA NA NA

Am - ACS90703BX 69 64 1046 10x8 1/3 Med 1.88 93 690 123 NA NA NA NA

Am - AMS90703BX 69 64 1046 10x8 1/3 Med 2.18 93 743 123 NA NA NA NA

Am - DCS90703BX 69 64 1046 10x8 1/3 Med 2.66 93 690 123 NA NA NA NA

Am - DMS90703BX 69 64 1046 10 x 8 1/3 Med 2.18 93 743 123 NA NA NA NA

Am - GCCA070*X30 69 65 1016 11 x 7 1/2 Med-Low 1.75 92.1 690 117 NA 15 30 NA

Am - GCLA070**30 69 65 1016 11 x 7 1/2 Med-Low 1.75 92.1 690 117 NA NA NA NA

Am - GUCA070*X30 69 64 1243 11 x 7 1/2 Med 2.10 92.1 743 123 NA 15 30 NA

Am - GULA070*X30 69 64 1243 11 x 7 1/2 Med 2.10 92.1 743 123 NA NA NA NA

OI - GTH 070 70 66 1060 12 x 7 1/2 Med-High 2.29 94 895 75 15 5 30 180

Te - CSA072NH3R 72 65 1091 10x8 1/2 Med-Low 2.10 90.4 920 77 NA 5 30 NA

Te - VSA072NH3R 72 66 1091 10 x 8 1/2 Med-Low 2.10 90.9 930 79 NA 5 30 NA

Table H.3.36 Condensing Single-Stage No-Weatherized Gas Furnaces at 70 Btu/h 1600

CFM

Condensing Single-Stage

70 kBtu/h 1600 CFM

Air

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay

Area

Ar-CG90CB067D16C*-*** 67.5 60 - 90 650 143 15 15 30 NA

Ar-GlD93BC067D16C*-*** 67.5 62 1256 12x10 3/4 Med-Low 2.53 92.5 850 143 NA NA NA NA

Ar-G1D93BU067D16C*-*** 67.5 62 1213 12x10 3/4 Med-Low 2.72 92.5 850 143 NA NA NA NA

Am - ACS90704CX 69 64 1488 10 x 10 1/2 Med 2.33 93 370 115 NA NA NA NA

Am - AMS90704CX 69 64 1488 10 x 10 1/2 Med 2.66 93 627 123 NA NA NA NA

Am - DMS90704CX 69 64 1488 10 x 10 1/2 Med 2.66 93 627 123 NA NA NA NA

Am - GCCA070*X40 69 63 1234 11X9 1/2 Med-Low 2.26 92.1 370 115 NA 15 30 NA

Am - GUCA070*X40 69 63 1224 11X9 1/2 Med-Low 2.66 92.1 627 123 NA 15 30 NA

Am - GULA070*X40 69 63 1224 11X9 1/2 Med-Low 2.66 92.1 627 123 NA NA NA NA

Te - CSA072NH4R 72 65 1248 10 x 4 (Dual) 3/4 Med-Low 2.49 90.4 812 77 NA 5 30 NA

Te - VSA072NH4R 72 66 1248 10 x 4 (Dual) 3/4 Med-Low 2.49 90.9 780 80 NA 5 30 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.35 Condensing Single-Stage Non-Weatherized Gas Furnaces at 70 Btu/h 1200 

CFM 

Condensing Single-Stage 

70 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On0.5 Size Size Taps Outlet purge purge Delay 

Area 

Le - G41 U F-36B-070-** 66 61 1080 10 x 8 113 Med-Low 2.21 90 706 140 15 5 45 

Le - G43UF-36B-070-** 66 62 1080 10 x 8 113 Med-Low 2.21 92.1 700 147 15 5 45 

Le - G51 MP-36B-070-** 66 62 1080 10 x 8 1/3 Med-Low 2.21 92.1 700 147 15 5 45 

Ar - CG90CB067D12B*-*** 67.5 60 - 90 650 123 15 15 30 

Ar - G1093BC067D12B*-*** 67.5 62 943 10 x 8 1/3 Med 2.06 92.5 850 123 NA NA NA 

Ar - G1093BU067D12B*-*** 67.5 62 912 10 x 8 1/3 Med 2.24 92.5 850 123 NA NA NA 

Am - ACS90703BX 69 64 1046 10 x 8 113 Med 1.88 93 690 123 NA NA NA 

Am - AMS90703BX 69 64 1046 10 x 8 113 Med 2.18 93 743 123 NA NA NA 

Am - DCS90703BX 69 64 1046 10 x 8 1/3 Med 2.66 93 690 123 NA NA NA 

Am - DMS90703BX 69 64 1046 10 x 8 1/3 Med 2.18 93 743 123 NA NA NA 

Am - GCCA070*X30 69 65 1016 11 x 7 112 Med-Low 1.75 92.1 690 117 NA 15 30 

Am - GCLA070**30 69 65 1016 11 x 7 112 Med-Low 1.75 92.1 690 117 NA NA NA 

Am - GUCA070*X30 69 64 1243 11 x 7 1/2 Med 2.10 92.1 743 123 NA 15 30 

Am - GULA070*X30 69 64 1243 11 x 7 1/2 Med 2.10 92.1 743 123 NA NA NA 

01- GTH 070 70 66 1060 12 x 7 1/2 Med-High 2.29 94 895 75 15 5 30 

Te - CSA072NH3R 72 65 1091 10 x 8 1/2 Med-Low 2.10 90.4 920 77 NA 5 30 

Te - VSA072NH3R 72 66 1091 10 x 8 1/2 Med-Low 2.10 90.9 930 79 NA 5 30 

Table H.3.36 Condensing Single-Stage No-Weatherized Gas Furnaces at 70 Btu/h 1600 

CFM 

Condensing Single-Stage 

70 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On0.5 Size Taps Outlet purge purge Delay 

Area 

Ar - CG90CB067D16C*-*** 67.5 60 - 90 650 143 15 15 30 

Ar - G1 D93BC067D16C*-*** 67.5 62 1256 12x 10 3/4 Med-Low 2.53 92.5 850 143 NA NA NA 

Ar - G1093BU067D16C*-*** 67.5 62 1213 12x 10 3/4 Med-Low 2.72 92.5 850 143 NA NA NA 

Am - ACS90704CX 69 64 1488 10 x 10 1/2 Med 2.33 93 370 115 NA NA NA 

Am - AMS90704CX 69 64 1488 10 x 10 1/2 Med 2.66 93 627 123 NA NA NA 

Am - DMS90704CX 69 64 1488 10 x 10 1/2 Med 2.66 93 627 123 NA NA NA 

Am - GCCA070*X40 69 63 1234 11 x 9 1/2 Med-Low 2.26 92.1 370 115 NA 15 30 

Am - GUCA070*X40 69 63 1224 11 x 9 1/2 Med-Low 2.66 92.1 627 123 NA 15 30 

Am - GULA070*X40 69 63 1224 11 x 9 1/2 Med-Low 2.66 92.1 627 123 NA NA NA 

Te - CSA072NH4R 72 65 1248 10 x 4 (Dual) 3/4 Med-Low 2.49 90.4 812 77 NA 5 30 

Te - VSA072NH4R 72 66 1248 10 x 4 (Dual) 3/4 Med-Low 2.49 90.9 780 80 NA 5 30 

H-28 

OffDelay 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

180 

NA 

NA 

OffDelay 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 
Table H.3.37 Condensing Single-Stage Non-Weatherized Gas Furnaces at 75 Btu/h 1200

Condensing Single-Stage

75 kBtu/h 1200 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Ar-CG90TB075D1213* 75 68 - 90 780 131 15 15 30 NA

Ar-CG901_113075D1213*-*** 75 68 - 90 780 131 15 15 30 NA

Du - CMPB075C3* 75 70 1110 10x6 1/3 Med 1.51 92 701 87 15 15 30 NA

Du - CMPE075U3* 75 69 1205 10x6 1/3 Med 1.51 92.1 614 84 15 15 30 NA

Ar - G1 D91 BT075D12B* 75 68 912 10x8 1/3 Med 2.24 91 750 131 15 15 30 NA

Ar - G1 D91 BU075D12B*-*** 75 68 912 10x8 1/3 Med 2.24 91 750 131 NA NA NA NA

Te - N9MP1075B12** 75 69 987 11x8 1/2 Med-High 1.80 90 954 127 3 30 30 NA

Te - N9MP2075B12** 75 68 987 11x8 1/2 Med-High 1.80 90 959 127 3 30 30 NA

Rh - RGRA-07(E,N)MAES 75 70 925 11x7 1/2 Med-High 2.27 92.8 512 100 NA NA NA NA

Rh - RGRJ-07(E,N)MAES 75 70 925 11x7 1/2 Med 2.27 92.8 512 100 30 5 20 NA

Rh - RGRJ-07(E,N)YBES 75 70 1270 12 x 7 1/2 Med 2.27 92 788 93 30 5 20 NA

Rh - RGRK-07(E,N)MAES 75 69 925 11 x 7 1/2 Med-High 2.27 92 607 98 NA NA NA NA

Rh - RGTA-07(E,N)MAES 75 69 940 11x7 1/2 Med-High 2.27 92 588 110 NA NA NA NA

Rh - RGTJ-07(E,N)MAES 75 69 940 11x7 1/2 Med 2.27 92 588 110 30 5 20 NA

Rh - RGTJ-07(E,N)YBES 75 70 1195 12 x 7 1/2 Med 2.76 92.3 750 81 30 5 20 NA

Te - T9MPDO75F12** 75 70 987 11 x 10 1/2 Med-High 2.26 92.1 849 121 3 30 30 NA

Table H.3.38 Condensing Single-Stage Non-Weatherized Gas Furnaces at 7513tu/h 1600

CFM

Condensing Single-Stage

75 kBtu/h 1600 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Ar-CG90TB075D16C* 75 68 - 90 780 127 15 15 30 NA

Ar - CG90UB075D16C*-*** 75 68 - 90 780 127 15 15 30 NA

Ar-G1D91BT075D16C* 75 68 1213 12x10 3/4 Med-Low 2.72 91 750 127 15 15 30 NA

Ar - G1 D91BU075D16C*-*** 75 68 1213 12x 10 3/4 Med-Low 2.72 91 750 127 NA NA NA NA

Rh - RGRA-07(E,N)YBGS 75 70 1270 12 x 7 3/4 Med-Low 2.76 92 788 93 NA NA NA NA

Rh - RGRJ-07(E,N)YBGS 75 70 1270 12 x 7 3/4 Low 2.76 92 788 93 30 5 20 NA

Rh - RG RK-07(E, N)YBGS 75 69 1270 12 x 7 3/4 Med-Low 2.76 92 974 95 NA NA NA NA

Rh - RGTA-07(E,N)YBGS 75 70 1195 12 x 7 3/4 Med-Low 2.76 92.3 750 81 NA NA NA NA

Rh - RGTJ-07(E,N)YBGS 75 70 1195 12 x 7 3/4 Low 2.76 92.3 750 81 30 5 20 NA

 EE-RM/STD-01-350 COMMENT 164

Table H . 3.37 Condensing Single-Stage Non-Weatherized Gas Furnaces at 75 Btu/h 1200 

Condensing Single-Stage 

75 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Ott0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Ar - CG90TB075D12B* 75 68 - 90 780 131 15 15 30 NA 

Ar - CG90UB075D12B*-*** 75 68 - 90 780 131 15 15 30 NA 

Du - CMPB075C3* 75 70 1110 10 x 6 1/3 Med 1.51 92 701 87 15 15 30 NA 

Du - CMPE075U3* 75 69 1205 10 x 6 1/3 Med 1.51 92.1 614 84 15 15 30 NA 

Ar - G1D91BT075D12B* 75 68 912 10 x 8 1/3 Med 2.24 91 750 131 15 15 30 NA 

Ar - G1D91 BU075D12B*-*** 75 68 912 10 x 8 1/3 Med 2.24 91 750 131 NA NA NA NA 

Te - N9MP1075B12** 75 69 987 11 x 8 1/2 Med-High 1.80 90 954 127 3 30 30 NA 

Te - N9MP2075B12** 75 68 987 11 x 8 1/2 Med-High 1.80 90 959 127 3 30 30 NA 

Rh - RGRA-07(E,N)MAES 75 70 925 11 x 7 1/2 Med-High 2.27 92.8 512 100 NA NA NA NA 

Rh - RGRJ-07(E,N)MAES 75 70 925 11 x 7 1/2 Med 2.27 92.8 512 100 30 5 20 NA 

Rh - RGRJ-07(E,N)YBES 75 70 1270 12x 7 1/2 Med 2.27 92 788 93 30 5 20 NA 

Rh - RGRK-07(E,N)MAES 75 69 925 11 x 7 1/2 Med-High 2.27 92 607 98 NA NA NA NA 

Rh - RGTA-07(E,N)MAES 75 69 940 11 x 7 1/2 Med-High 2.27 92 588 110 NA NA NA NA 

Rh - RGT J-07(E,N)MAES 75 69 940 11 x 7 1/2 Med 2.27 92 588 110 30 5 20 NA 

Rh - RGT J-07(E,N)YBES 75 70 1195 12 x 7 1/2 Med 2.76 92.3 750 81 30 5 20 NA 

Te - T9MPD075F12** 75 70 987 11 x 10 1/2 Med-High 2.26 92.1 849 121 3 30 30 NA 

Table H.3.38 Condensing Single-Stage Non-Weatherized Gas Furnaces at 75 Btu/h 1600 

CFM 

Condensing Single-Stage 

75 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Ott0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Ar - CG90TB075D16C* 75 68 - 90 780 127 15 15 30 NA 

Ar - CG90UB075D16C*-*** 75 68 - 90 780 127 15 15 30 NA 

Ar-G1D91BT075D16C* 75 68 1213 12 x 10 3/4 Med-Low 2.72 91 750 127 15 15 30 NA 

Ar - G1 D91BU075D16C*-*** 75 68 1213 12 x 10 3/4 Med-Low 2.72 91 750 127 NA NA NA NA 

Rh - RGRA-07(E,N)YBGS 75 70 1270 12 x 7 3/4 Med-Low 2.76 92 788 93 NA NA NA NA 

Rh - RGRJ-07(E,N)YBGS 75 70 1270 12 x 7 3/4 Low 2.76 92 788 93 30 5 20 NA 

Rh - RGRK-07(E,N)YBGS 75 69 1270 12 x 7 3/4 Med-Low 2.76 92 974 95 NA NA NA NA 

Rh - RGTA-07(E,N)YBGS 75 70 1195 12 x 7 3/4 Med-Low 2.76 92.3 750 81 NA NA NA NA 

Rh - RGT J-07(E,N)YBGS 75 70 1195 12 x 7 3/4 Low 2.76 92.3 750 81 30 5 20 NA 

H-29 
Table H.3.39 Condensing Single-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 1200

CFM

Condensing Single-Stage

80 kBtu/h 1200 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output AFUE Eae PE

0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Br - 351 DAS036080 80 75 1030 10x7 1/3 Med-Low 2.09 91.7 527 78 15 15 60 NA

Ca - 58MCA080-12 80 74 1030 10x7 1/3 Med-Low 2.09 92.1 525 78 15 15 66 NA

Ca - 58MCA080-12* 80 74 1030 10x7 1/3 Med-Low 2.09 91 531 78 15 15 66 NA

Ca - 58MSA080-12 80 74 1030 10x7 1/3 Med-Low 2.09 90 536 78 15 15 66 NA

Ca - 58MXA080-12 80 75 1030 10x7 1/3 Med-Low 2.09 93.1 519 78 15 15 66 NA

Ca - 58MXA080-12* 80 75 1030 10x7 1/3 Med-Low 2.09 91.7 526 78 15 15 66 NA

Ca - 58MXA080-12** 80 74 1030 10x7 1/3 Med-Low 2.09 92.5 522 78 15 15 66 NA

Fr - FG6RC080*-12B 80 74 630 10x8 1/3 Low 2.50 92.1 656 90 30 30 30 NA

Yo - GY9S080B12DH11* 80 74 1534 11 x 8 1/2 High 2.26 91 1198 160 NA NA NA NA

Yo - GY9S080B12UP1 1 * 80 74 1465 11 x 8 1/2 High 2.26 92 1186 150 NA NA NA NA

Fr - L1 RC080*-12B 80 76 1050 10x8 1/3 Med 2.51 92.1 775 125 30 30 30 NA

Yo - PS9B12N080DH11 80 74 934 11 x 8 1/2 Med-Low 2.26 92 864 135 NA NA NA NA

Yo - PS9B12N080UP11* 80 74 1465 11 x 8 1/2 High 2.26 92 1186 150 NA NA NA NA

Table H.3.40 Condensing Single-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 1600

CFM

Condensing Single-Stage

80 kBtu/h 1600 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output AFUE Eae PE

0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Br - 351 DAS048080 80 75 1125 11 x 8 1/2 Med-Low 2.09 91.7 873 80 15 15 60 NA

Ca - 58MCA080-16 80 74 1125 11 x 8 1/2 Med-Low 2.09 92.1 869 80 15 15 66 NA

Ca - 58MCA080-16* 80 74 1125 11 x 8 1/2 Med-Low 2.09 91 879 80 15 15 66 NA

Ca - 58MSA080-16 80 74 1125 11 x 8 1/2 Med-Low 2.09 90 888 80 15 15 66 NA

Ca - 58MXA080-16 80 75 1125 11 x 8 1/2 Med-Low 2.09 93.1 860 80 15 15 66 NA

Ca - 58MXA080-16* 80 75 1125 11 x 8 1/2 Med-Low 2.09 91.7 872 80 15 15 66 NA

Ca - 58MXA080-16** 80 75 1125 11 x 8 1/2 Med-Low 2.09 92.5 865 80 15 15 66 NA

Fr - FG6RC080*-16B 80 74 1190 10 x 10 1/2 Med-Low 2.50 92.1 774 75 30 30 30 NA

Fr - FG6RL080*-16B 80 72 1090 10 x 10 1/2 Med-Low 2.50 90 837 70 30 30 30 NA

Go - GMNT080-4 80 74 1485 10x8 1/2 Med 2.18 92.6 623 90 15 NA 30 NA

Yo - GY9S080C16DH11 * 80 74 1275 11 x 8 1/2 Med-Low 2.26 91 1176 162 NA NA NA NA

Yo- GY9S080C16UP11* 80 75 1310 11 x 10 3/4 Med-Low 2.74 92 1172 162 NA NA NA NA

Fr - L1 RC080*-168 80 76 1285 10 x 10 1/2 Med-Low 2.51 92.1 744 130 30 30 30 NA

Te - N9MP1080F16** 80 73 1317 11 x 10 1/2 Med-High 2.26 90 927 125 3 30 30 NA

Te - N9MP2080F16** 80 72 1317 11 x 10 1/2 Med-High 2.26 90 974 118 3 30 30 NA

Yo - PS9C1 6NO80DHI 1 80 75 1864 11 x 8 1/2 High 2.26 92 1003 174 NA NA NA NA

Yo - PS9C16NO80UP11* 80 75 1310 11 x 10 3/4 Med-Low 2.74 92 1172 162 NA NA NA NA

Te - T9MPD080J16** 80 75 1317 11 x 10 1/2 Med-High 2.73 92.1 973 122 3 30 30 NA

01 - GTH 085 85 81 1455 12 x 10 3/4 Med-Low 2.78 95 1089 75 15 5 30 180

 EE-RM/STD-01-350 COMMENT 164

Table H.3.39 Condensing Single-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 1200 

CFM 

Condensing Single-Stage 

80 kBtu/h 1200 CFM 

I Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Br - 351 DAS036080 80 75 1030 10 x 7 1/3 Med-Low 2.09 91.7 527 78 15 15 60 NA 

Ca - 58MCA080-12 80 74 1030 10 x 7 1/3 Med-Low 2.09 92.1 525 78 15 15 66 NA 

Ca - 58MCA080-12* 80 74 1030 10 x 7 1/3 Med-Low 2.09 91 531 78 15 15 66 NA 

Ca - 58MSA080-12 80 74 1030 10 x 7 1/3 Med-Low 2.09 90 536 78 15 15 66 NA 

Ca - 58MXA080-12 80 75 1030 10 x 7 113 Med-Low 2.09 93.1 519 78 15 15 66 NA 

Ca - 58MXA080-12* 80 75 1030 10 x 7 1/3 Med-Low 2.09 91.7 526 78 15 15 66 NA 

Ca - 58MXA080-12** 80 74 1030 10 x 7 1/3 Med-Low 2.09 92.5 522 78 15 15 66 NA 

Fr - FG6RC080*-12B 80 74 630 10 x 8 1/3 Low 2.50 92.1 656 90 30 30 30 NA 

Yo - GY9S080B12DH11* 80 74 1534 11 x 8 1/2 High 2.26 91 1198 160 NA NA NA NA 

Yo - GY9S080B12UP11* 80 74 1465 11 x 8 1/2 High 2.26 92 1186 150 NA NA NA NA 

Fr - L 1 RC080*-12B 80 76 1050 10 x 8 1/3 Med 2.51 92.1 775 125 30 30 30 NA 

Yo - PS9B12N080DH11 80 74 934 11 x 8 1/2 Med-Low 2.26 92 864 135 NA NA NA NA 

Yo - PS9B12N080UP11* 80 74 1465 11 x 8 1/2 High 2.26 92 1186 150 NA NA NA NA 

Table H.3.40 Condensing Single-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 1600 

CFM 

Condensing Single-Stage 

80 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- ott0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Br - 351 DAS048080 80 75 1125 11 x 8 1/2 Med-Low 2.09 91.7 873 80 15 15 60 NA 

Ca - 58MCA080-16 80 74 1125 11 x 8 1/2 Med-Low 2.09 92.1 869 80 15 15 66 NA 

Ca - 58MCA080-16* 80 74 1125 11 x 8 1/2 Med-Low 2.09 91 879 80 15 15 66 NA 

Ca - 58MSA080-16 80 74 1125 11 x 8 1/2 Med-Low 2.09 90 888 80 15 15 66 NA 

Ca - 58MXA080-16 80 75 1125 11 x 8 1/2 Med-Low 2.09 93.1 860 80 15 15 66 NA 

Ca - 58MXA080-16* 80 75 1125 11 x 8 1/2 Med-Low 2.09 91.7 872 80 15 15 66 NA 

Ca - 58MXA080-16** 80 75 1125 11 x 8 1/2 Med-Low 2.09 92.5 865 80 15 15 66 NA 

Fr - FG6RC080*-16B 80 74 1190 10 x 10 1/2 Med-Low 2.50 92.1 774 75 30 30 30 NA 

Fr - FG6RL080*-16B 80 72 1090 10 x 10 1/2 Med-Low 2.50 90 837 70 30 30 30 NA 

Go - GMNT080-4 80 74 1485 10 x 8 1/2 Med 2.18 92.6 623 90 15 NA 30 NA 

Yo - GY9S080C16DH11* 80 74 1275 11 x 8 1/2 Med-Low 2.26 91 1176 162 NA NA NA NA 

Yo - GY9S080C16UP11* 80 75 1310 11 x 10 3/4 Med-Low 2.74 92 1172 162 NA NA NA NA 

Fr - L 1 RC080*-16B 80 76 1285 10 x 10 1/2 Med-Low 2.51 92.1 744 130 30 30 30 NA 

Te - N9MP1080F16** 80 73 1317 11 x 10 1/2 Med-High 2.26 90 927 125 3 30 30 NA 

Te - N9MP2080F16** 80 72 1317 11 x 10 1/2 Med-High 2.26 90 974 118 3 30 30 NA 

Yo - PS9C16N080DH11 80 75 1864 11 x 8 1/2 High 2.26 92 1003 174 NA NA NA NA 

Yo - PS9C16N080UP11* 80 75 1310 11 x 10 3/4 Med-Low 2.74 92 1172 162 NA NA NA NA 

Te - T9MPD080J16** 80 75 1317 11 x 10 1/2 Med-High 2.73 92.1 973 122 3 30 30 NA 

01- GTH 085 85 81 1455 12 x 10 3/4 Med-Low 2.78 95 1089 75 15 5 30 180 

H-30 
Table 11.3.41 Condensing Single-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 2000

CFM

Condensing Single-Stage

80 kBtu/h 2000 CFM

Air

CFM Motor Speed Supply Pre- Post- On- Off- Models Input Output Blower Size AFUE Eae PE

0.5 Size Taps Outlet purge purge Delay Delay

Area

Br - 351 DAS060080 80 75 1620 11 X10 3/4 Med-Low 2.56 91.7 998 81 15 15 60 NA

Ca - 58MCA080-20 80 74 1620 11 x 10 3/4 Med-Low 2.56 92.1 994 81 15 15 66 NA

Ca - 58MCA080-20* 80 74 1620 11 x 10 3/4 Med-Low 2. 56 91 1006 81 15 15 66 NA

Ca - 58MSA080-20 80 74 1620 11 x 10 3/4 Med-Low 2.56 90 1016 81 15 15 66 NA

Ca - 58MXA080-20 80 75 1620 11 x 10 3/4 Med-Low 2.56 93.1 983 81 15 15 66 NA

Ca - 58MXA080-20* 80 75 1620 11 x 10 3/4 Med-Low 2.56 91.7 998 81 15 15 66 NA

Ca - 58MXA080-20** 80 75 1620 11 x 10 3/4 Med-Low 2.56 92.5 990 81 15 15 66 NA

Yo - GY9SO8OC20UP11 80 75 1390 11 X11 1 Med-Low 2.74 92 1172 162 NA NA NA NA

Yo - GY9S08OC20UP11 80 75 1485 11 x 11 1 Med-Low 2.74 92 1172 162 NA NA NA NA

Yo - PS9C20N080UP11* 80 75 1390 11 x 10 3/4 Med-Low 2.74 92 1172 162 NA NA NA NA

Yo - PS9C20NO80UP11 80 75 1485 11 x 10 3/4 Med-Low 2.74 92 1172 162 NA NA NA NA

Tr - TUX080C960D* 80 76 1611 11 x 10 3/4 Med-Low 2.69 92.1 860 75 NA NA 45 NA

Table H.3.42 Condensing Single-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 1200

CFM

Condensing Single-Stage

90 kBtu/h 1200 CFM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output 0.5 Size Size Taps Outlet AFUE Eae PE

purge purge Delay Delay

Area

Le - G41 OF-36C-090-** 88 80 1125 10x8 1/3 Med-Low 2.68 90 805 141 15 5 45 NA

Le - G43UF-36C-090-** 88 82 1300 10x8 1/3 Med-High 2.68 92.1 895 144 15 5 45 NA

Le - G43UF-36C-090H ** 88 81 1140 10x8 1/3 Med-Low 2.68 90 775 145 15 5 45 NA

Le - G51 MP-36C-090-** 88 82 1300 10x8 1/3 Med-High 2.68 92.1 895 144 15 5 45 NA

Te - CSA090NH3R 90 81 1316 10x8 1/2 Med-High 2.10 90.4 985 89 NA 5 30 NA

Te - VSA090NH3R 90 82 1316 10x8, 1/2 Med-High 2.10 90.9 910 91 NA 5 30 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.41 Condensing Single-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 2000 

CFM 

Condensing Single-Stage 

80 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay 

Area 

Br - 351 DAS060080 80 75 1620 11 x 10 3/4 Med-Low 2.56 91.7 998 81 15 15 60 NA 

Ca - 58MCA080-20 80 74 1620 11 x 10 3/4 Med-Low 2.56 92.1 994 81 15 15 66 NA 

Ca - 58MCA080-20* 80 74 1620 11 x 10 3/4 Med-Low 2.56 91 1006 81 15 15 66 NA 

Ca - 58MSA080-20 80 74 1620 11 x 10 3/4 Med-Low 2.56 90 1016 81 15 15 66 NA 

Ca - 58MXA080-20 80 75 1620 11 x 10 3/4 Med-Low 2.56 93.1 983 81 15 15 66 NA 

Ca - 58MXA080-20* 80 75 1620 11 x 10 3/4 Med-Low 2.56 91.7 998 81 15 15 66 NA 

Ca - 58MXA080-20** 80 75 1620 11 x 10 3/4 Med-Low 2.56 92.5 990 81 15 15 66 NA 

Yo - GY9S080C20UP11 80 75 1390 11 x 11 1 Med-Low 2.74 92 1172 162 NA NA NA NA 

Yo - GY9S080C20UP11 80 75 1485 11 x 11 1 Med-Low 2.74 92 1172 162 NA NA NA NA 

Yo - PS9C20N080UP11* 80 75 1390 11 x 10 3/4 Med-Low 2.74 92 1172 162 NA NA NA NA 

Yo - PS9C20N080UP11 80 75 1485 11 x 10 3/4 Med-Low 2.74 92 1172 162 NA NA NA NA 

Tr - TUX080C960D* 80 76 1611 11 x 10 3/4 Med-Low 2.69 92.1 860 75 NA NA 45 NA 

Table H.3.42 Condensing Single-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 1200 

CFM 

Condensing Single-Stage 

90 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Le - G41 UF-36C-090-** 88 80 1125 10 x 8 1/3 Med-Low 2.68 90 805 141 15 5 45 NA 

Le - G43UF-36C-090-** 88 82 1300 10 x 8 1/3 Med-High 2.68 92.1 895 144 15 5 45 NA 

Le - G43UF-36C-090H-** 88 81 1140 10 x 8 1/3 Med-Low 2.68 90 775 145 15 5 45 NA 

Le - G51 MP-36C-090-** 88 82 1300 10 x 8 1/3 Med-High 2.68 92.1 895 144 15 5 45 NA 

Te - CSA090NH3R 90 81 1316 10 x 8 1/2 Med-High 2.10 90.4 985 89 NA 5 30 NA 

Te - VSA090NH3R 90 82 1316 10 x 8 1/2 Med-High 2.10 90.9 910 91 NA 5 30 NA 

H-31 
Table H.3.43 Condensing Single-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 1600

CFM

Condensing Single-Stage

90 kBtu/h 1600 CFM

Air

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay

Area

Le - G41 UF-48C-090-** 88 81 1430 10x 10 1/2 Med-Low 2.68 90 844 141 15 5 45 NA

Le - G43UF-48C-090 ** 88 83 1430 10 x 10 1/2 Med-Low 2.68 92.1 820 177 15 5 45 NA

Le - G51MP-48C-090-** 88 82 1660 10 x 10 1/2 Med-High 2.68 92.1 820 171 15 5 45 NA

Ar - CG90CB090D16C*-*** 90 81 - 90 950 133 15 15 30 NA

Te - CSA090NH4R 90 81 1416 10 x 4 (Dual 3/4 Med-High 2.49 90.4 916 87 NA 5 30 NA

Ar - G1D93BC090D16C*-*** 90 83 1221 12 x 10 3/4 Med-Low 2.53 92.5 900 133 NA NA NA NA

Ar-G1D93BU090D16C*-*** 90 83 1184 12x10 3/4 Med-Low 2.72 92.5 900 133 NA NA NA NA

Rh - RGRJ-09(E,N)ZAGS 90 84 1375 12 x 11 1/2 Med 2.76 93.5 848 99 30 5 20 NA

Rh - RGTJ-09(E,N)ZAGS 90 84 1350 12 x 11 1/2 Med 2.76 92.4 832 98 30 5 20 NA

Te - VSA090NH4R 90 82 1416 10 x 4 (Dual 3/4 Med-High 2.49 90.9 839 94 NA 5 30 NA

Am - ACS90904CX 92 86 1418 10 x 10 1/2 Med 2.33 93 883 123 NA NA NA NA

Am - AMS90904CX 92 85 1418 10 x 10 1/2 Med 2.66 93 833 123 NA NA NA NA

Am - DCS90904CX 92 86 1418 10 x 10 1/2 Med 2.66 93 883 123 NA NA NA NA

Am - DMS90904CX 92 85 1418 10 x 10 1/2 Med 2.66 93 833 123 NA NA NA NA

Am - GCCA090*X40 92 87 1581 11X9 1/2 High 2.26 92.1 883 128 NA 15 30 NA

Am - GCLA090**40 92 87 1581 11X9 1/2 High 2.26 92.1 883 128 NA NA NA NA

Am - GUCA090*X40 92 86 1544 11X9 1/2 High 2.66 92.1 837 129 NA 15 30 NA

Am - GULA090*X40 92 86 1544 11X9 1/2 High 2.66 92.1 837 129 NA NA NA NA

Table H.3 .44 Condensing Single-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 2000

CFM

Condensing Single-Stage

90 kBtu/h 2000 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Le - G41 OF-60C-090-** 88 81 1915 1.5 x 1 3/4 Med-Low 2.68 90 1081 140 15 5 45 NA

Le - G51 MP-60C-090-** 88 82 1970 1.5 x 1 1 Med-Low 2.68 92.1 1075 177 15 5 45 NA

Le - G51 MP-60C-090-** 88 82 1850 1.5 x 1 I Med-Low 2.68 92.1 1075 177 15 5 45 NA

Ar - CG90CB09OD20C*-*** 90 81 - 90 950 146 15 15 30 NA

Ar - G1 D93BC090D20C*-*** 90 83 1509 12 x 10 9/10 Med-Low 2.53 92.5 900 146 NA NA NA NA

Ar - G1 D93BU09OD20C* `** 90 83 1726 12 x 10 9/10 Med-Low 2.72 92.5 900 146 NA NA NA NA

Rh - RGRA-09(E,N)ZAJS 90 84 1375 12 x 11 3/4 Med-Low 2.76 93.5 848 99 NA NA NA NA

Rh - RGRJ-09(E,N)ZAJS 90 84 1375 12 x 11 3/4 Low 2.76 93.5 848 99 30 5 20 NA

Rh - RGRK-09(E,N)ZAJS 90 83 1580 12 x 11 3/4 Med-High 2.76 92 969 93 NA NA NA NA

Rh - RGTA-09(E,N)ZAJS 90 84 1350 12 x 11 3/4 Med-Low 2.76 92.4 832 98 NA NA NA NA

Rh - RGTJ-09(E,N)ZAJS 90 84 1350 12 x 11 3/4 Low 2.76 92.4 832 98 30 5 20 NA

Am - ACS90905DX 92 85 1557 11 x 10 3/4 Med 2.78 93 909 123 NA NA NA NA

Am - AMS90905DX 92 85 1557 11 x 10 3/4 Med 3.13 93 761 123 NA NA NA NA

Am - DMS90905DX 92 85 1557 11 x 10 3/4 Med 3.13 93 761 123 NA NA NA NA

Am - GCCA090*X50 92 85 1595 11 x 9 1/3 Med 2.78 92.1 909 125 NA 15 30 NA

Am - GUCA090*X50 92 85 1345 11 x9 3/4 Med-Low 3.22 92.1 761 124 NA 15 30 NA

Am - GULA090*X50 92 85 1345 11 x 9 3/4 Med-Low 3.22 92.1 761 124 NA NA NA NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.43 Condensing Single-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 1600 

CFM 

Condensing Single-Stage 

90 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay 

Area 

Le - G41 UF-48C-090-** 88 81 1430 10 x 10 1/2 Med-Low 2.68 90 844 141 15 5 45 NA 

Le - G43UF-48C-090-** 88 83 1430 10 x 10 1/2 Med-Low 2.68 92.1 820 177 15 5 45 NA 

Le - G51MP-48C-090-** 88 82 1660 10 x 10 1/2 Med-High 2.68 92.1 820 171 15 5 45 NA 

Ar - CG90CB090D16C*-*** 90 81 - 90 950 133 15 15 30 NA 

Te - CSA090NH4R 90 81 1416 10 x 4 (Dual 3/4 Med-High 2.49 90.4 916 87 NA 5 30 NA 

Ar - G1D93BC090D16C*-*** 90 83 1221 12 x 10 3/4 Med-Low 2.53 92.5 900 133 NA NA NA NA 

Ar - G1D93BU090D16C*-*** 90 83 1184 12 x 10 3/4 Med-Low 2.72 92.5 900 133 NA NA NA NA 

Rh - RGRJ-09(E.N)ZAGS 90 84 1375 12 xii 1/2 Med 2.76 93.5 848 99 30 5 20 NA 

Rh - RGT J-09(E.N)ZAGS 90 84 1350 12 xii 1/2 Med 2.76 92.4 832 98 30 5 20 NA 

Te - VSA090NH4R 90 82 1416 10 x 4 (Dual 3/4 Med-High 2.49 90.9 839 94 NA 5 30 NA 

Am - ACS90904CX 92 86 1418 10x 10 1/2 Med 2.33 93 883 123 NA NA NA NA 

Am - AMS90904CX 92 85 1418 10 x 10 1/2 Med 2.66 93 833 123 NA NA NA NA 

Am - DCS90904CX 92 86 1418 10 x 10 1/2 Med 2.66 93 883 123 NA NA NA NA 

Am - DMS90904CX 92 85 1418 10 x 10 1/2 Med 2.66 93 833 123 NA NA NA NA 

Am - GCCA090*X40 92 87 1581 11 x 9 1/2 High 2.26 92.1 883 128 NA 15 30 NA 

Am - GCLA090**40 92 87 1581 11 x 9 1/2 High 2.26 92.1 883 128 NA NA NA NA 

Am - GUCA090*X40 92 86 1544 11 x 9 1/2 High 2.66 92.1 837 129 NA 15 30 NA 

Am - GULA090*X40 92 86 1544 11 x 9 1/2 High 2.66 92.1 837 129 NA NA NA NA 

Table H.3.44 Condensing Single-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 2000 

CFM 

Condensing Single-Stage 

90 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Le - G41UF-60C-090-** 88 81 1915 1.5 x 1 3/4 Med-Low 2.68 90 1081 140 15 5 45 NA 

Le - G51 MP-60C-090-** 88 82 1970 1.5 x 1 1 Med-Low 2.68 92.1 1075 177 15 5 45 NA 

Le - G51 MP-60C-090-** 88 82 1850 1.5 xi 1 Med-Low 2.68 92.1 1075 177 15 5 45 NA 

Ar - CG90CB090D20C*-*** 90 81 - 90 950 146 15 15 30 NA 

Ar - G1D93BC090D20C*-*** 90 83 1509 12 x 10 9/10 Med-Low 2.53 92.5 900 146 NA NA NA NA 

Ar - G1 D93BU090D20C*-*** 90 83 1726 12 x 10 9/10 Med-Low 2.72 92.5 900 146 NA NA NA NA 

Rh - RGRA-09(E.N)ZAJS 90 84 1375 12 xii 3/4 Med-Low 2.76 93.5 848 99 NA NA NA NA 

Rh - RGRJ-09(E.N)ZAJS 90 84 1375 12 xii 3/4 Low 2.76 93.5 848 99 30 5 20 NA 

Rh - RGRK-09(E.N)ZAJS 90 83 1580 12 xii 3/4 Med-High 2.76 92 969 93 NA NA NA NA 

Rh - RGTA-09(E.N)ZAJS 90 84 1350 12 xii 3/4 Med-Low 2.76 92.4 832 98 NA NA NA NA 

Rh - RGT J-09(E.N)ZAJS 90 84 1350 12 xii 3/4 Low 2.76 92.4 832 98 30 5 20 NA 

Am - ACS90905DX 92 85 1557 11 x 10 3/4 Med 2.78 93 909 123 NA NA NA NA 

Am - AMS90905DX 92 85 1557 11 x 10 3/4 Med 3.13 93 761 123 NA NA NA NA 

Am - DMS90905DX 92 85 1557 11 x 10 3/4 Med 3.13 93 761 123 NA NA NA NA 

Am - GCCA090*X50 92 85 1595 11 x 9 1/3 Med 2.78 92.1 909 125 NA 15 30 NA 

Am - GUCA090*X50 92 85 1345 11 x 9 3/4 Med-Low 3.22 92.1 761 124 NA 15 30 NA 

Am - GULA090*X50 92 85 1345 11 x 9 3/4 Med-Low 3.22 92.1 761 124 NA NA NA NA 

H-32 
Table H.3.45 Condensing Single-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 1200

CFM

Condensing Single-Stage

100 kBtu/h 1200 CFM

Models

Du - CMPE10003*

Input

100

Output

92

CFM

0.5

11157

Blower

Size

10x9

Motor

Size

1/3

Speed

Taps

Med

Air

Supply

Outlet

Area

1.97

AFUE

92.1

Eae

611

PE

84

Prepurge

15

Postpurge

15

OnDelay

30

OffDelay

NA

Table H.3.46 Condensing Single-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 1600

CFM

Condensing Single-Stage

100 kBtu/h 1600 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Ca - 58MCA100-16 100 93 1235 11 x8 1/2 Med-Low 2.56 92.1 794 82 15 15 66 NA

Ca - 58MCA100-16* 100 93 1235 11 x8 1/2 Med-Low 2.56 91 803 82 15 15 66 NA

Ca - 58MSA100-16 100 92 1235 11 x8 1/2 Med-Low 2.56 90 811 82 15 15 66 NA

Ca - 58MXA100-16 100 94 1235 11 x8 1/2 Med-Low 2.56 93.1 942 82 15 15 66 NA

Ca - 58MXA100-16* 100 94 1235 11 x 8 1/2 Med-Low 2.56 91.7 956 82 15 15 66 NA

Ca - 58MXA100-16** 100 93 1235 11 x 8 1/2 Med-Low 2.56 92.5 790 82 15 15 66 NA

Th - CDB-100 100 94 1230 1/2 Low 2.38 92.5 763 127 15 5 45 NA

Th - CDBI-100 100 94 1590 1/2 High 2.38 92.5 763 127 15 5 45 NA

Am - CDC100A948A* 100 93 - 90 828 78 NA NA NA NA

Ar-CG90TB100D16C* 100 91 - 90 903 133 15 15 30 NA

Ar-CG90UB10OD14C*-*** 100 91 - 90 903 133 15 15 30 NA

Th - CHB-100 100 94 1220 1/2 Low 2.38 94 772 126 15 5 45 NA

Th - CHBI-100 100 94 1700 1/2 High 2.38 94 772 126 15 5 45 NA

Du - CMPB10004* 100 93 1550 12 x 9 1/2 Med 1.97 92 920 87 15 15 30 NA

Du - CMPE10004* 100 92 1393 12 x 9 1/2 Med 1.97 92.1 1106 84 15 15 30 NA

Am - CUC100A948A* 100 94 - 90 982 48 NA NA NA NA

Fr - FG6RC1 00*-1 6B 100 93 1420 10 x 10 1/2 Med-High 2.50 92.1 987 90 30 30 30 NA

Fr - FG6RL100*-16B 100 90 1290 10 x 10 1/2 Med-High 2.50 90 982 70 30 30 30 NA

Ar - G1 D91 BT100D16C* 100 91 1184 12 x 10 3/4 Med-Low 2.72 91 903 133 15 15 30 NA

Ar- G1D91BU100D16C*-*** 100 91 1184 12 x 10 3/4 Med-Low 2.72 91 903 133 NA NA NA NA

Go - GMNT100-4 100 92 1550 10 x 10 1/2 Med 2.66 92.6 686 90 15 NA 30 NA

OI - GTH 100 100 95 1496 12 x 10 3/4 Med-High 2.78 95 1294 75 15 5 30 180

Yo - GY9S100C16DH11* 100 94 1488 11 x10 3/4 Med-High 2.74 91 1589 185 NA NA NA NA

Yo- GY9S100C16UP11* 100 93 1545 11 x 10 3/4 Med-High 2.74 92 1295 156 NA NA NA NA

Fr- L1RC100*-16B 100 93 1480 10 x 10 1/2 Med-High 2.51 92.1 900 127 30 30 30 NA

Yo - PS9C16N100DH11 100 93 1488 11 x 10 3/4 Med-High 2.74 92 725 155 NA NA NA NA

Yo - PS9C16N100UP11* 100 93 1545 11 x 11 1 Med-High 2.74 92 1295 156 NA NA NA NA

Tr-TDC10009488* 100 93 1538 11 x 10 1/2 Med-High 2.57 91 820 78 NA NA 45 NA

Tr - TDX1000948D* 100 94 1538 11 x 10 1/2 Med-High 2.65 91 955 70 NA NA 45 NA

Tr-TUC1000948B* 100 94 1673 10 x 10 1/2 Med-High 2.69 92.1 960 48 NA NA 45 NA

Tr - TUX1000948D* 100 94 1673 10 x 10 1/2 Med-High 2.69 92.1 929 70 NA NA 45 NA

Rh - RGRJ-10(E,N)ZAGS 105 97 1350 12 x 11 1/2 Med 2.76 92 862 97 30 5 20 NA

Rh - RGTJ-10(E,N)ZAGS 105 97 1360 12 x 11 1/2 Med 2.76 92 885 101 30 5 20 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.45 Condensing Single-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 1200 

CFM 

Condensing Single-Stage 

100 kBtu/h 1200 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Du - CMPE100U3* 100 92 1157 10 x 9 1/3 Med 1.97 92.1 611 84 15 15 30 NA 

Table H.3.46 Condensing Single-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 1600 

CFM 

Condensing Single-Stage 

100 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Ca - 58MCA100-16 100 93 1235 11 x 8 1/2 Med-Low 2.56 92.1 794 82 15 15 66 NA 

Ca - 58MCA100-16* 100 93 1235 11 x 8 1/2 Med-Low 2.56 91 803 82 15 15 66 NA 

Ca - 58MSA100-16 100 92 1235 11 x 8 1/2 Med-Low 2.56 90 811 82 15 15 66 NA 

Ca - 58MXA100-16 100 94 1235 11 x 8 1/2 Med-Low 2.56 93.1 942 82 15 15 66 NA 

Ca - 58MXA100-16* 100 94 1235 11 x 8 1/2 Med-Low 2.56 91.7 956 82 15 15 66 NA 

Ca - 58MXA100-16** 100 93 1235 11 x 8 1/2 Med-Low 2.56 92.5 790 82 15 15 66 NA 

Th - CDB-100 100 94 1230 1/2 Low 2.38 92.5 763 127 15 5 45 NA 

Th - CDBI-100 100 94 1590 1/2 High 2.38 92.5 763 127 15 5 45 NA 

Am - CDC100A948A* 100 93 - 90 828 78 NA NA NA NA 

Ar - CG90TB1 00D16C* 100 91 - 90 903 133 15 15 30 NA 

Ar - CG90UB1 00D14C*-*** 100 91 - 90 903 133 15 15 30 NA 

Th - CHB-100 100 94 1220 1/2 Low 2.38 94 772 126 15 5 45 NA 

Th - CHBI-100 100 94 1700 1/2 High 2.38 94 772 126 15 5 45 NA 

Du - CMPB100C4* 100 93 1550 12 x 9 1/2 Med 1.97 92 920 87 15 15 30 NA 

Du - CMPE100U4* 100 92 1393 12 x 9 1/2 Med 1.97 92.1 1106 84 15 15 30 NA 

Am - CUC100A948A* 100 94 - 90 982 48 NA NA NA NA 

Fr - FG6RC1 00*-16B 100 93 1420 10 x 10 1/2 Med-High 2.50 92.1 987 90 30 30 30 NA 

Fr - FG6RL 100*-16B 100 90 1290 10 x 10 1/2 Med-High 2.50 90 982 70 30 30 30 NA 

Ar-G1D91BT100D16C* 100 91 1184 12 x 10 3/4 Med-Low 2.72 91 903 133 15 15 30 NA 

Ar - G1091 BU1 00D16C*-*** 100 91 1184 12 x 10 3/4 Med-Low 2.72 91 903 133 NA NA NA NA 

Go - GMNT100-4 100 92 1550 10 x 10 112 Med 2.66 92.6 686 90 15 NA 30 NA 

01- GTH 100 100 95 1496 12 x 10 3/4 Med-High 2.78 95 1294 75 15 5 30 180 

Yo - GY9S100C16DH11* 100 94 1488 11 x 10 3/4 Med-High 2.74 91 1589 185 NA NA NA NA 

Yo - GY9S100C16UP11* 100 93 1545 11 x 10 3/4 Med-High 2.74 92 1295 156 NA NA NA NA 

Fr- L1RC100*-16B 100 93 1480 10 x 10 1/2 Med-High 2.51 92.1 900 127 30 30 30 NA 

Yo - PS9C16N100DH11 100 93 1488 11 x 10 3/4 Med-High 2.74 92 725 155 NA NA NA NA 

Yo - PS9C16N100UP11* 100 93 1545 11 x 11 1 Med-High 2.74 92 1295 156 NA NA NA NA 

Tr - TDC100C948B* 100 93 1538 11 x 10 1/2 Med-High 2.57 91 820 78 NA NA 45 NA 

Tr - TDX100C948D* 100 94 1538 11 x 10 1/2 Med-High 2.65 91 955 70 NA NA 45 NA 

Tr - TUC100C948B* 100 94 1673 10 x 10 1/2 Med-High 2.69 92.1 960 48 NA NA 45 NA 

Tr - TUX100C948D* 100 94 1673 10 x 10 1/2 Med-High 2.69 92.1 929 70 NA NA 45 NA 

Rh - RGRJ-10(E,N)ZAGS 105 97 1350 12 x 11 1/2 Med 2.76 92 862 97 30 5 20 NA 

Rh - RGTJ-10(E,N)ZAGS 105 97 1360 12 x 11 1/2 Med 2.76 92 885 101 30 5 20 NA 

H-33 
Table H.3.47 Condensing Single-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 2000

CFM

Condensing Single-Stage

100 kBtu/h 2000 CFM

Air

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay

Area

Ca - 58MCA100-20 100 93 1575 11 x 10 3/4 Med-Low 2. 56 92.1 1045 80 15 15 66 NA

Ca - 58MCA100-20* 100 93 1575 11 x 10 3/4 Med-Low 2. 56 91 1057 80 15 15 66 NA

Ca - 58MSA100-20 100 92 1575 11 x 10 3/4 Med-Low 2. 56 90 1067 80 15 15 66 NA

Ca - 58MXA100-20 100 94 1575 11 x 10 3/4 Med-Low 2. 56 93. 1 1240 80 15 15 66 NA

Ca - 58MXAI00-20* 100 94 1575 11 x 10 3/4 Med-Low 2. 56 91.7 1258 80 15 15 66 NA

Ca - 58MXA100-20** 100 93 1575 11 x 10 3/4 Med-Low 2.56 92. 5 1040 80 15 15 66 NA

Ar-CG90TB100D20C* 100 91 - 90 903 143 15 15 30 NA

Ar - CG90UB100D20C*-*** 100 91 - 90 903 143 15 15 30 NA

Am - CUC100A960A* 100 93 - 90 935 53 NA NA NA NA

Ar - G1 D90AH100D20B *--*** 100 90 1550 12x 9 3/4 Med 2. 37 90 1006 79 NA NA NA NA

Ar-G1D91BT100D20C* 100 91 1726 12x10 9/10 Med 2.72 91 920 143 15 15 30 NA

Ar-G1D91BU100D20C*-*** 100 91 1726 12x10 9/10 Med 2. 72 91 920 143 NA NA NA NA

Yo - GY9S100020DH11 * 100 94 1750 11 x 11 1 Med-High 2. 74 91 1795 190 NA NA NA NA

Yo - GY9S100020UP11 * 100 93 1680 11 x 11 1 Med-High 2.74 92 1295 156 NA NA NA NA

Yo-GY9S100020UP11 * 100 93 1800 11 x 11 1 Med-High 2. 74 92 1295 156 NA NA NA NA

Te - N9MP1100J20 ** 100 91 1825 11 x 10 3/4 Med-High 2.73 90 1036 130 3 30 30 NA

Te - N9MP2100J20 ** 100 92 1825 11 x 10 3/4 Med-High 2. 73 90 1036 130 3 30 30 NA

Yo - PS9C20N100DH11 100 94 1750 11 x 10 3/4 Med-High 2. 74 92 870 155 NA NA NA NA

Yo - PS9C20N1000P11 * 100 93 1680 11 x 11 1 Med-High 2.74 92 1295 156 NA NA NA NA

Yo- PS9C20N1000P11 * 100 93 1800 11 x 11 1 Med-High 2. 74 92 1295 156 NA NA NA NA

Te - T9MPD100J20** 100 93 1825 11 x 10 3/4 Med-High 2. 73 92. 1 1041 131 3 30 30 NA

Tr - TUC1000960B* 100 93 1700 11 x 10 3/4 Med-Low 3. 17 92. 1 914 53 NA NA 45 NA

Tr - TUX1000960D* 100 93 1700 11 x 10 3/4 Med-Low 3.17 92. 1 919 55 NA NA 45 NA

Rh - RGRA-10(E,N)ZAJS 105 97 1350 12 x 11 3/4 Med-Low 2. 76 92 862 97 NA NA NA NA

Rh - RGRJ -10(E,N )ZAJS 105 97 1350 12 x 11 3/4 Low 2. 76 92 862 97 30 5 20 NA

Rh - RGRK-10 (E,N)ZAJS 105 97 1540 12 x 11 3/4 Med-High 2. 76 92 1088 109 NA NA NA NA

Rh - RGTA-10(E,N)ZAJS 105 97 1360 12 x 11 3/4 Med-Low 2. 76 92 885 101 NA NA NA NA

Rh - RGTJ- 10(E,N)ZAJS 105 97 1360 12 x 11 3/4 Low 3. 24 92 885 101 30 5 20 NA

Table H.3.48 Condensing Single-Stage Non-Weatherized Gas Furnaces at 115 Btu/h 1600

CFM

Condensing Single-Stage

115 kBtu/h 1600 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Le - G41 OF-48C-110-** 110 100 1420 10 x 10 1 /2 Med-Low 2.68 90 803 139 15 5 45 NA

Le - G43UF-48C- 110-** 110 103 1420 10 x 10 1 /2 Med-Low 2 . 68 92 . 1 888 175 15 5 45 NA

Le -G43UF-48C- 110H-* 110 101 1420 10 x 10 1 /2 Med-Low 2 .68 90 830 168 15 5 45 NA

Le - G51 MP-48C- 110-** 110 103 1630 1 10x 10 1/2 Med-High 2 . 68 92.1 888 175 15 5 45 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.47 Condensing Single-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 2000 

CFM 

Condensing Single-Stage 

100 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay 

Area 

Ca - 58MCA100-20 100 93 1575 11 x 10 3/4 Med-Low 2.56 92.1 1045 80 15 15 66 NA 

Ca - 58MCA 100-20* 100 93 1575 11 x 10 3/4 Med-Low 2.56 91 1057 80 15 15 66 NA 

Ca - 58MSA 100-20 100 92 1575 11 x 10 3/4 Med-Low 2.56 90 1067 80 15 15 66 NA 

Ca - 58MXA 100-20 100 94 1575 11 x 10 3/4 Med-Low 2.56 93.1 1240 80 15 15 66 NA 

Ca - 58MXA100-20* 100 94 1575 11 x 10 3/4 Med-Low 2.56 91.7 1258 80 15 15 66 NA 

Ca - 58MXA 100-20** 100 93 1575 11 x 10 3/4 Med-Low 2.56 92.5 1040 80 15 15 66 NA 

Ar - CG90TB 1 00D20C* 100 91 - 90 903 143 15 15 30 NA 

Ar - CG90UB100D20C*-*** 100 91 - 90 903 143 15 15 30 NA 

Am - GUC100A960A* 100 93 - 90 935 53 NA NA NA NA 

Ar - G1D90AH100D20B*-*** 100 90 1550 12 x 9 3/4 Med 2.37 90 1006 79 NA NA NA NA 

Ar- G1D91BT100D20C* 100 91 1726 12x 10 9/10 Med 2.72 91 920 143 15 15 30 NA 

Ar - G1D91BU100D20C*-*** 100 91 1726 12x 10 9/10 Med 2.72 91 920 143 NA NA NA NA 

Yo - GY9S100C20DH11* 100 94 1750 11 x 11 1 Med-High 2.74 91 1795 190 NA NA NA NA 

Yo - GY9S100C20UP11* 100 93 1680 11 x 11 1 Med-High 2.74 92 1295 156 NA NA NA NA 

Yo - GY9S100C20UP11* 100 93 1800 11 x 11 1 Med-High 2.74 92 1295 156 NA NA NA NA 

Te - N9MP1100J20** 100 91 1825 11 x 10 3/4 Med-High 2.73 90 1036 130 3 30 30 NA 

Te - N9MP2100J20** 100 92 1825 11 x 10 3/4 Med-High 2.73 90 1036 130 3 30 30 NA 

Yo - PS9C20N100DH11 100 94 1750 11 x 10 3/4 Med-High 2.74 92 870 155 NA NA NA NA 

Yo - PS9C20N100UP11* 100 93 1680 11 x 11 1 Med-High 2.74 92 1295 156 NA NA NA NA 

Yo - PS9C20N100UP11* 100 93 1800 11 x 11 1 Med-High 2.74 92 1295 156 NA NA NA NA 

Te - T9MPD100J20** 100 93 1825 11 x 10 3/4 Med-High 2.73 92.1 1041 131 3 30 30 NA 

Tr - TUC100C960B* 100 93 1700 11 x 10 3/4 Med-Low 3.17 92.1 914 53 NA NA 45 NA 

Tr - TUX1 00C960D* 100 93 1700 11 x 10 3/4 Med-Low 3.17 92.1 919 55 NA NA 45 NA 

Rh - RGRA-10(E,N)ZAJS 105 97 1350 12x 11 3/4 Med-Low 2.76 92 862 97 NA NA NA NA 

Rh - RGRJ-10(E,N)ZAJS 105 97 1350 12x 11 3/4 Low 2.76 92 862 97 30 5 20 NA 

Rh - RGRK-10(E,N)ZAJS 105 97 1540 12x 11 3/4 Med-High 2.76 92 1088 109 NA NA NA NA 

Rh - RGTA-10(E,N)ZAJS 105 97 1360 12x 11 3/4 Med-Low 2.76 92 885 101 NA NA NA NA 

Rh - RGTJ-10(E,N)ZAJS 105 97 1360 12 x 11 3/4 Low 3.24 92 885 101 30 5 20 NA 

Table H.3.48 Condensing Single-Stage Non-Weatherized Gas Furnaces at 115 Btu/h 1600 

CFM 

Condensing Single-Stage 

115 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Le - G41 UF-48C-110-** 110 100 1420 10 x 10 112 Med-Low 2.68 90 803 139 15 5 45 NA 

Le - G43UF-48C-110-** 110 103 1420 10 x 10 112 Med-Low 2.68 92.1 888 175 15 5 45 NA 

Le - G43UF-48C-110H-* 110 101 1420 10 x 10 1/2 Med-Low 2.68 90 830 168 15 5 45 NA 

ILe - G51 MP-48C-110-** 110 103 1630 10 x 10 1/2 Med-High 2.68 92.1 888 175 15 5 45 NA 

H-34 
Table 11.3.49 Condensing Single-Stage Non-Weatherized Gas Furnaces at 115 Btu/h 2000

CFNI

Condensing Single-Stage

115 kBtu/h 2000 CFM

Air

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay

Area

Te - CSA108NH5R 108 97 1621 10 x 6 (Dual) 3/4 Med-Low 2.89 90.4 909 103 NA 5 30 NA

Te - VSA108NH5R 108 99 1621 10 x 6 (Dual) 3/4 Med-Low 2.89 90.9 1089 103 NA 5 30 NA

Le - G41 OF-60C-1 10-** 110 102 1870 11.5 x 10 3/4 Med-Low 2.68 90 1035 142 15 5 45 NA

Le - G43UF-60C-110-** 110 103 1895 11.5 x 10 1 Med-Low 2.68 92.1 993 178 15 5 45 NA

Le - G43UF-60C-110-** 110 103 1975 11.5 x 10 1 Med-Low 2.68 92.1 993 178 15 5 45 NA

Le - G51 MP-60C-1 10-" 110 103 1975 11.5 x 10 1 Med-Low 2.68 92.1 993 178 15 5 45 NA

Le - G51MP-60C-110-** 110 103 1895 11.5 x 10 1 Med-Low 2.68 92.1 993 178 15 5 45 NA

Ar - CG90CB112D20D*-*** 112 100 - 90 1100 147 15 15 30 NA

Ar - G1 D93BC112D20D*-*** 113 104 1707 12 x 10 9/10 Med 2.95 92.5 1150 147 NA NA NA NA

Ar - G1 D93BU112D20D*-*** 113 104 1738 12 x 10 9/10 Med 3.19 92.5 1150 147 NA NA NA NA

Am - ACS91155DX 115 108 1527 11 x 10 3/4 Med 2.78 93 418 133 NA NA NA NA

Am - AMS91155DX 115 106 1527 11 x 10 3/4 Med 3.13 93 897 144 NA NA NA NA

Am - DCS91155DX 115 108 1527 11 x 10 3/4 Med 3.13 93 418 133 NA NA NA NA

Am - DMS91155DX 115 106 1527 11 x 10 3/4 Med 3.13 93 897 144 NA NA NA NA

Am - GCCA115*X50 115 108 1849 11 x 10 1/3 High 2.78 92.1 418 133 NA 15 30 NA

Am - GCLA115**50 115 108 1849 11 x 10 1/3 High 2.78 92.1 418 133 NA NA NA NA

Am - GUCA115*X50 115 106 1562 11 x 10 1/2 Med 3.22 92.1 897 144 NA 15 30 NA

Am - GULA115*X50 115 106 1562 __1_1_x_10___ 1/2 Med 3.22 92.1 897 144 NA NA NA NA

Table 14.3.50 Condensing Single-Stage Non-Weatherized Gas Furnaces at 120 Btu/h 1600

CFM

Condensing Single-Stage

120 kBtu/h 1600 CFM

Air

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Fr - FG6RC 120*-1 6C 120 110 1410 10x 10 1/2 Med-High 2.88 92.1 967 69 30 30 30 NA

Fr-L1RC120*-16C 120 112 1490 10x10 1/2 Med-High 2.89 92.1 1029 133 30 30 30 NA

Rh - RGRJ-12(E,N)RAGS 120 113 1475 11 x 10 1/2 Med 3.24 93.5 961 99 30 5 20 NA

Rh - RGTJ-12(E,N)RAGS 120 112 1475 11 x 10 1/2 Med 3.24 92.1 961 118 30 5 20 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3,49 Condensing Single-Stage Non-Weatherized Gas Furnaces at 115 Btu/h 2000 

CFM 

Condensing Single-Stage 

115 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay 

Area 

Te - CSA108NH5R 108 97 1621 10 x 6 (Dual) 3/4 Med-Low 2.89 90.4 909 103 NA 5 30 NA 

Te - VSA108NH5R 108 99 1621 10 x 6 (Dual) 3/4 Med-Low 2.89 90.9 1089 103 NA 5 30 NA 

Le - G41 UF-60C-110-** 110 102 1870 11.5 x 10 3/4 Med-Low 2.68 90 1035 142 15 5 45 NA 

Le - G43UF-60C-110-** 110 103 1895 11.5 x 10 1 Med-Low 2.68 92.1 993 178 15 5 45 NA 

Le - G43UF-60C-110-** 110 103 1975 11.5x 10 1 Med-Low 2.68 92.1 993 178 15 5 45 NA 

Le - G51MP-60C-110-** 110 103 1975 11.5x10 1 Med-Low 2.68 92.1 993 178 15 5 45 NA 

Le - G51MP-60C-110-** 110 103 1895 11.5x 10 1 Med-Low 2.68 92.1 993 178 15 5 45 NA 

Ar - CG90CB112D20D*-*** 112 100 - 90 1100 147 15 15 30 NA 

Ar - G1D93BC112D20D*-*** 113 104 1707 12 x 10 9/10 Med 2.95 92.5 1150 147 NA NA NA NA 

Ar - G1D93BU112D20D*-*** 113 104 1738 12 x 10 9/10 Med 3.19 92.5 1150 147 NA NA NA NA 

Am - ACS91155DX 115 108 1527 11 x 10 3/4 Med 2.78 93 418 133 NA NA NA NA 

Am - AMS91155DX 115 106 1527 11 x 10 3/4 Med 3.13 93 897 144 NA NA NA NA 

Am - DCS91155DX 115 108 1527 11 x 10 3/4 Med 3.13 93 418 133 NA NA NA NA 

Am - DMS91155DX 115 106 1527 11 x 10 3/4 Med 3.13 93 897 144 NA NA NA NA 

Am - GCCA115*X50 115 108 1849 11 x 10 1/3 High 2.78 92.1 418 133 NA 15 30 NA 

Am - GCLA 115**50 115 108 1849 11 x 10 1/3 High 2.78 92.1 418 133 NA NA NA NA 

Am - GUCA115*X50 115 106 1562 11 x 10 1/2 Med 3.22 92.1 897 144 NA 15 30 NA 

Am - GULA115*X50 115 106 1562 11 x 10 1/2 Med 3.22 92.1 897 144 NA NA NA NA 

Table H.3.50 Condensing Single-Stage Non-Weatherized Gas Furnaces at 120 Btu/h 1600 

CFM 

Condensing Single-Stage 

120 kBtu/h 1600 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Fr - FG6RC120*-16C 120 110 1410 10 x 10 1/2 Med-High 2.88 92.1 967 69 30 30 30 NA 

Fr- L 1RC120*-16C 120 112 1490 10 x 10 1/2 Med-High 2.89 92.1 1029 133 30 30 30 NA 

Rh - RGRJ-12(E,N)RAGS 120 113 1475 11 x 10 1/2 Med 3.24 93.5 961 99 30 5 20 NA 

Rh - RGTJ-12(E,N)RAGS 120 112 1475 11 x 10 1/2 Med 3.24 92.1 961 118 30 5 20 NA 

H-35 
Table H.3.51 Condensing Single-Stage Non-Weatherized Gas Furnaces at 120 Btu/h 2000

CFM

Condensing Single-Stage

9 20 kBtu/h 2000 CF M

Air

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay

Area

Ca - 58MCA120-20 120 112 1575 11 X10 3/4 Med-Low 3.02 92.1 1241 88 15 15 66 NA

Ca - 58MCA120-20* 120 112 1575 11 X10 3/4 Med-Low 3.02 91 1256 88 15 15 66 NA

Ca - 58MSA120-20 120 111 1575 11 x 10 3/4 Med-Low 3.02 90 1269 88 15 15 66 NA

Ca - 58MXA120-20 120 113 1575 11 x 10 3/4 Med-Low 3.02 93. 1 1228 88 15 15 66 NA

Ca - 58MXA120-20* 120 113 1575 11 x 10 3/4 Med-Low 3.02 91.7 1246 88 15 15 66 NA

Ca - 58MXAl20-20** 120 112 1575 11 x 10 3/4 Med-Low 3.02 92.5 1236 88 15 15 66 NA

Am - CDC120A960A* 120 112 - 90 1174 80 NA NA NA NA

Am - CUC120A960A* 120 113 - 90 1291 70 NA NA NA NA

Fr- FG6RC120*-20C 120 1 1 0 1430 11 x 10 3/4 Med-Low 2.88 92.1 967 69 30 30 30 NA

Fr - FG6RL120*-20C 120 110 1728 11 x 10 3/4 Med-High 2.88 90 1244 115 30 30 30 NA

Go - GMNT120-5 120 111 1600 11 x 10 3/4 Med 3.13 92.6 1130 90 15 NA 30 NA

Yo - GY9S120D20DH11 * 120 112 1863 11 x 10 3/4 Med-High 2.74 91 1953 199 NA NA NA NA

Yo - GY9S120D20UP11* 120 112 1885 11 x 11 1 Med-High 3.23 92 1905 169 NA NA NA NA

Yo - GY9S120D20UP11* 120 112 1932 11 x 11 1 Med-High 3.23 92 1905 169 NA NA NA NA

Fr- L1 RC120*-20C 120 112 1505 11 x 10 3/4 Med-Low 2.89 92.1 1134 130 30 30 30 NA

Yo - PS9D20N120DH11 120 112 1863 11 X11 1 Med-High 3.23 92 1326 132 NA NA NA NA

Yo - PS9D20N120UP11* 120 112 1885 11 X11 1 Med-High 3.23 92 1905 169 NA NA NA NA

Yo - PS9D20N120UP11* 120 112 1932 11 X11 1 Med-High 3.23 92 1905 169 NA NA NA NA

Rh - RGRA-12(E,N)RAJS 120 113 1475 11 x 10 3/4 Med-Low 3.24 93.5 961 99 NA NA NA NA

Rh - RGRJ-12(E,N)RAJS 120 113 1475 11 x 10 1/2 Low 3.24 93.5 961 99 30 5 20 NA

Rh - RGRK-12(E,N)RAJS 120 110 1660 11 x 10 3/4 Med-High 3.24 92 1131 98 NA NA NA NA

Rh - RGTA-12(E,N)RAJS 120 112 1475 11 x 10 3/4 Med-Low 3.24 92.1 961 118 NA NA NA NA

Rh - RGTJ-1 2(E, N)RAJS 120 112 1475 11 x 10 3/4 Low 3.24 92.1 961 118 30 5 20 NA

Tr-TDC120C960B* 120 112 1822 11 x 10 1/2 Med-High 3.03 91 1161 80 NA NA 45 NA

Tr - TDX1 20C960D* 120 112 1822 11 x 10 3/4 Med-High 3.12 91 1164 73 NA NA 45 NA

Tr-TUC120C960B* 120 113 2012 11 x 10 3/4 Med-High 3.17 92.1 1262 70 NA NA 45 NA

Tr - TUX1 20C960D* 120 113 2012 11 x 10 3/4 Med-High 3.17 92.1 1320 84 NA NA 45 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.S1 Condensing Single-Stage Non-Weatherized Gas Furnaces at 120 Btu/h 2000 

CFM 

Condensing Single-Stage 

120 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay 

Area 

Ca - 58MCA120-20 120 112 1575 11 x 10 3/4 Med-Low 3.02 92.1 1241 88 15 15 66 NA 

Ca - 58MCA120-20* 120 112 1575 11 x 10 3/4 Med-Low 3.02 91 1256 88 15 15 66 NA 

Ca - 58MSA120-20 120 111 1575 11 x 10 3/4 Med-Low 3.02 90 1269 88 15 15 66 NA 

Ca - 58MXA120-20 120 113 1575 11 x 10 3/4 Med-Low 3.02 93.1 1228 88 15 15 66 NA 

Ca - 58MXA120-20* 120 113 1575 11 x 10 3/4 Med-Low 3.02 91.7 1246 88 15 15 66 NA 

Ca - 58MXA120-20** 120 112 1575 11 x 10 3/4 Med-Low 3.02 92.5 1236 88 15 15 66 NA 

Am - CDC120A960A* 120 112 - 90 1174 80 NA NA NA NA 

Am - CUC120A960A* 120 113 - 90 1291 70 NA NA NA NA 

Fr - FG6RC120*-20C 120 110 1430 11 x 10 3/4 Med-Low 2.88 92.1 967 69 30 30 30 NA 

Fr - FG6RL 120*-20C 120 110 1728 11 x 10 3/4 Med-High 2.88 90 1244 115 30 30 30 NA 

Go - GMNT120-5 120 111 1600 11 x 10 3/4 Med 3.13 92.6 1130 90 15 NA 30 NA 

Yo - GY9S120D20DH11 * 120 112 1863 11 x 10 3/4 Med-High 2.74 91 1953 199 NA NA NA NA 

Yo - GY9S120D20UP11* 120 112 1885 11 x 11 1 Med-High 3.23 92 1905 169 NA NA NA NA 

Yo - GY9S120D20UP11* 120 112 1932 11 x 11 1 Med-High 3.23 92 1905 169 NA NA NA NA 

Fr - L 1 RC120*-20C 120 112 1505 11 x 10 3/4 Med-Low 2.89 92.1 1134 130 30 30 30 NA 

Yo - PS9D20N120DH11 120 112 1863 11 x 11 1 Med-High 3.23 92 1326 132 NA NA NA NA 

Yo - PS9D20N120UP11* 120 112 1885 11 x 11 1 Med-High 3.23 92 1905 169 NA NA NA NA 

Yo - PS9D20N120UP11* 120 112 1932 11 x 11 1 Med-High 3.23 92 1905 169 NA NA NA NA 

Rh - RGRA-12(E.N)RAJS 120 113 1475 11 x 10 3/4 Med-Low 3.24 93.5 961 99 NA NA NA NA 

Rh - RGRJ-12(E.N)RAJS 120 113 1475 11 x 10 1/2 Low 3.24 93.5 961 99 30 5 20 NA 

Rh - RGRK-12(E.N)RAJS 120 110 1660 11 x 10 3/4 Med-High 3.24 92 1131 98 NA NA NA NA 

Rh - RGTA-12(E.N)RAJS 120 112 1475 11 x 10 3/4 Med-Low 3.24 92.1 961 118 NA NA NA NA 

Rh - RGTJ-12(E.N)RAJS 120 112 1475 11 x 10 3/4 Low 3.24 92.1 961 118 30 5 20 NA 

Tr - TDC120C960B* 120 112 1822 11 x 10 1/2 Med-High 3.03 91 1161 80 NA NA 45 NA 

Tr - TDX120C960D* 120 112 1822 11 x 10 3/4 Med-High 3.12 91 1164 73 NA NA 45 NA 

Tr - TUC120C960B* 120 113 2012 11 x 10 3/4 Med-High 3.17 92.1 1262 70 NA NA 45 NA 

Tr - TUX120C960D* 120 113 2012 11 x 10 3/4 Med-High 3.17 92.1 1320 84 NA NA 45 NA 

H-36 
Table 11.3.52 Condensing Single -Stage Non-Weatherized Gas Furnaces at 125 Btu/h 2000

CFM

Condensing Single-Stage

125 kBtu/h 2000 C FM

Air

CFM Blower Motor Speed Supply Pre- Post- On- Off- Models Input Output AFUE Eae PE

0.5 Size Size Taps Outlet purge purge Delay Delay

Area

Th - CDB-125 125 116 1530 3/4 Low 2 . 75 92 1081 128 15 5 45 NA

Th - CDBI-125 125 116 2010 3/4 High 2 . 75 92 1081 128 15 5 45 NA

Ar - CG90TB125D20C* 125 113 - 90 1150 147 15 15 30 NA

Ar - CG90UB125D20D*-*** 125 113 - 90 1150 147 15 15 30 NA

Th - CHB-125 125 116 1550 3/4 Low 2 . 75 93 1028 131 15 5 45 NA

Th - CHBI-125 125 116 2060 3/4 High 2 . 75 93 1028 131 15 5 45 NA

Du - CMPB125U5 * 125 116 2115 12 x 12 3/4 High 2 .43 92 1130 87 15 15 30 NA

Du - CMPE125U5* 125 116 2028 12 x 12 3/4 High 2 .43 92.1 1396 84 15 15 30 NA

Ar-G1D90AH125D20C`--*** 125 112 1620 12x9 3/4 Med 2 . 97 90 1247 86 NA NA NA NA

Ar - G1 D91 BT125D20C * 125 113 1738 12 x 10 9/10 Med 2 . 72 91 1100 142 15 15 30 NA

Ar-G1D91BU125D20D `--*** 125 113 1738 12x10 9/10 Med 3.19 91 1100 142 NA NA NA NA

Te - N9MP1 125J20 ** 125 116 1891 11 x 10 3/4 Med-High 2.73 90 1280 90 3 30 30 NA

Te - N9MP2125J20 ** 125 116 1891 11 x 10 3/4 Med-High 2.73 90 1272 87 3 30 30 NA

Te -T9MPD125L20 ** 125 117 1891 11 x 10 3/4 Med-High 2.95 92 . 1 1216 89 3 30 30 NA

Te - CSA126NH5R 126 114 1827 x 6 ( D 3/4 Med-High 2.89 90 . 4 962 102 NA 5 30 NA

Te - VSA126NH5R 126 115 1827 x 6 ( D 3/4 Med-High 2.89 90 . 9 1262 102 NA 5 30 NA

Le - G41 OF-60D-135-** 132 112 1865 1.5 x 1 3/4 Med-Low 3 . 16 90 1015 144 15 5 45 NA

Le - G43UF-60D-135-** 132 123 1890 1.5 x 1 1 Med-Low 3.16 92.1 1112 164 15 5 45 NA

Le - G43UF-60D-135-** 132 123 1960 1.5 x 1 1 Med-Low 3.16 92 . 1 1112 164 15 5 45 NA

Le - G51 MP-60D -1 35-- 132 123 2120 1.5 x 1 1 Med-High 3.16 92 . 1 1112 164 15 5 45 NA

Le - G51 MP-60D - 1 35-** 132 123 2195 1.5 x 1 1 Med-High 3.16 92 . 1 1112 164 15 5 45 NA

 EE-RM/STD-01-350 COMMENT 164

Table H.3.52 Condensing Single-Stage N on-Weatherized Gas Furnaces at 125 Btu/h 2000 

CFM 

Condensing Single-Stage 

125 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Size Taps Outlet purge purge Delay Delay 

Area 

Th - CDB-125 125 116 1530 3/4 Low 2.75 92 1081 128 15 5 45 NA 

Th - CDBI-125 125 116 2010 3/4 High 2.75 92 1081 128 15 5 45 NA 

Ar - CG90TB125D20C* 125 113 - 90 1150 147 15 15 30 NA 

Ar - CG90UB125D20D*-*** 125 113 - 90 1150 147 15 15 30 NA 

Th - CHB-125 125 116 1550 3/4 Low 2.75 93 1028 131 15 5 45 NA 

Th - CHBI-125 125 116 2060 3/4 High 2.75 93 1028 131 15 5 45 NA 

Du - CMPB125U5* 125 116 2115 12 x 12 3/4 High 2.43 92 1130 87 15 15 30 NA 

Du - CMPE125U5* 125 116 2028 12 x 12 3/4 High 2.43 92.1 1396 84 15 15 30 NA 

Ar - G1090AH125D20C*-*** 125 112 1620 12 x 9 3/4 Med 2.97 90 1247 86 NA NA NA NA 

Ar-G1091BT125D20C* 125 113 1738 12 x 10 9/10 Med 2.72 91 1100 142 15 15 30 NA 

Ar - G1D91BU125D20D*-*** 125 113 1738 12 x 10 9/10 Med 3.19 91 1100 142 NA NA NA NA 

Te - N9MP1125J20** 125 116 1891 11 x 10 3/4 Med-High 2.73 90 1280 90 3 30 30 NA 

Te - N9MP2125J20** 125 116 1891 11 x 10 3/4 Med-High 2.73 90 1272 87 3 30 30 NA 

Te - T9MPD125L20** 125 117 1891 11 x 10 3/4 Med-High 2.95 92.1 1216 89 3 30 30 NA 

Te - CSA126NH5R 126 114 1827 x 6 (Dl 3/4 Med-High 2.89 90.4 962 102 NA 5 30 NA 

Te - VSA126NH5R 126 115 1827 x 6 (Dl 3/4 Med-High 2.89 90.9 1262 102 NA 5 30 NA 

Le - G41 UF-60D-135-** 132 112 1865 1.5 xi 3/4 Med-Low 3.16 90 1015 144 15 5 45 NA 

Le - G43UF-60D-135-** 132 123 1890 1.5 xi 1 Med-Low 3.16 92.1 1112 164 15 5 45 NA 

Le - G43UF-60D-135-** 132 123 1960 1.5 xi 1 Med-Low 3.16 92.1 1112 164 15 5 45 NA 

Le - G51 MP-60D-135-** 132 123 2120 1.5x 1 1 Med-High 3.16 92.1 1112 164 15 5 45 NA 

Le - G51 MP-60D-135-** 132 123 2195 1.5x 1 1 Med-High 3.16 92.1 1112 164 15 5 45 NA 

H-37 
Table H.3.53 Condensing Single-Stage Non-Weatherized Gas Furnaces at 140 Btu/h 2000

CFM

Condensing Single-Stage

140 kBtu/h 2000 CFM

Air

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On- Off0.5 Size Taps Outlet purge purge Delay Delay

Area

Yo- GY9S135D20UP11 135 127 2220 11 x 11 1 High 3 . 23 92 1425 165 NA NA NA NA

Yo- GY9S135D20UP11 135 127 2285 11 x 11 1 High 3 . 23 92 1425 165 NA NA NA NA

Yo- PS9D20N135UP11 135 127 2285 11 x 11 1 High 3.23 92 1425 165 NA NA NA NA

Yo - PS9D20N1 35UP1 1 135 127 2220 11 x 11 I High 3.23 92 1425 165 NA NA NA NA

Ca - 58MCA140-20 138 127 1805 11 X10 3/4 Med-High 3 .02 92 . 1 1039 100 15 15 66 NA

Ca - 58MCA140 -20 138 127 1725 11 X10 3/4 Med-High 3.02 92 . 1 1039 100 15 15 66 NA

Ca - 58MCA140 -20 138 127 1835 11 x 10 3/4 Med-High 3 . 02 92 . 1 1039 100 15 15 66 NA

Ca - 58MCA140-20* 138 128 1725 11 X10 3/4 Med-High 3.02 91 1202 100 15 15 66 NA

Ca - 58MCA140 -20* 138 128 1835 11 x 10 3/4 Med-High - 91 1202 100 15 15 66 NA

Ca - 58MCA140 -20* 138 128 1805 11X10 3/4 Med-High 3 . 02 91 1202 100 15 15 66 NA

Ca - 58MCA140-20** 138 127 1725 11 x 10 3/4 Med-High 3.02 92 1040 100 15 15 66 NA

Ca - 58MCA140-20** 138 127 1835 11 X10 3/4 Med-High 3 . 02 92 1040 100 15 15 66 NA

Ca - 58MCA140-20** 138 127 1805 11 X10 3/4 Med-High 3 . 02 92 1040 100 15 15 66 NA

Ca - 58MXA140-20 138 129 1725 11 x 10 3/4 Med-High 3. 02 92 . 6 1 182 100 15 15 66 NA

Ca - 58MXA140-20 138 129 1835 11 x 10 3/4 Med-High 3.02 92. 6 1182 100 15 15 66 NA

Ca - 58MXA140-20 138 129 1805 11 x 10 3/4 Med-High 3.02 92. 6 1182 100 15 15 66 NA

Ca - 58MXA140 -20* 138 129 1725 11 x 10 3/4 Med-High 3.02 91 . 2 1199 100 15 15 66 NA

Ca - 58MXA140 -20* 138 129 1805 11 x 10 3/4 Med-High 3.02 91 . 2 1199 100 15 15 66 NA

Ca - 58MXA140 -20* 138 129 1835 11 X10 3/4 Med-High 3 . 02 91.2 1 199 100 15 15 66 NA

Ca - 58MXA140-20** 138 128 1835 11 X10 3/4 Med-High 3 . 02 92 1189 100 15 15 66 NA

Ca - 58MXA140-20** 138 128 1725 11 x 10 3/4 Med-High 3. 02 92 1189 100 15 15 66 NA

Ca - 58MXA140-20** 138 128 1805 11 x 10 3/4 Med-High 3. 02 92 1189 100 15 15 66 NA

H.3.3 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces

Table H.3.54 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 50 Btu/h

1200 CFM

Gor ing Two-Stage

50 kBtu/h 1200 CFM

High L ON Air

Mxiels High LoN High Low CFM Saner Motor Speecl Supply

ARE Eae PE Pre- Post- QrDday Off Delay

Input Input Output Output 0.5

0.5 0.5 Sze Size Taps Outlet P Jge PAW

Area

T91VPv 50F12** 35 46 33 268 595 325 11x8 1/2 Variable 226 921 268 140 3 5 30 140

 EE-RM/STD-01-350 COMMENT 164

Table H.3.S3 Condensing Single-Stage Non-Weatherized Gas Furnaces at 140 Btu/h 2000 

CFM 

Condensing Single-Stage 

140 kBtu/h 2000 CFM 

Air 

Models Input Output CFM Blower Size Motor Speed Supply AFUE Eae PE Pre- Post- On0.5 Size Taps Outlet purge purge Delay 

Area 

Yo - GY9S135D20UP11 135 127 2220 11 x 11 1 High 3.23 92 1425 165 NA NA NA 

Yo - GY9S135D20UP11 135 127 2285 11 xii 1 High 3.23 92 1425 165 NA NA NA 

Yo - PS9D20N135UP11 135 127 2285 11 xii 1 High 3.23 92 1425 165 NA NA NA 

Yo - PS9D20N135UP11 135 127 2220 11 x 11 1 High 3.23 92 1425 165 NA NA NA 

Ca - 58MCA 140-20 138 127 1805 11 x 10 3/4 Med-High 3.02 92.1 1039 100 15 15 66 

Ca - 58MCA140-20 138 127 1725 11 x 10 3/4 Med-High 3.02 92.1 1039 100 15 15 66 

Ca - 58MCA140-20 138 127 1835 11 x 10 3/4 Med-High 3.02 92.1 1039 100 15 15 66 

Ca - 58MCA140-20* 138 128 1725 11 x 10 3/4 Med-High 3.02 91 1202 100 15 15 66 

Ca - 58MCA140-20* 138 128 1835 11 x 10 3/4 Med-High - 91 1202 100 15 15 66 

Ca - 58MCA140-20* 138 128 1805 11 x 10 3/4 Med-High 3.02 91 1202 100 15 15 66 

Ca - 58MCA140-20** 138 127 1725 11 x 10 3/4 Med-High 3.02 92 1040 100 15 15 66 

Ca - 58MCA 140-20** 138 127 1835 11 x 10 3/4 Med-High 3.02 92 1040 100 15 15 66 

Ca - 58MCA140-20** 138 127 1805 11 x 10 3/4 Med-High 3.02 92 1040 100 15 15 66 

Ca - 58MXA 140-20 138 129 1725 11 x 10 3/4 Med-High 3.02 92.6 1182 100 15 15 66 

Ca - 58MXA140-20 138 129 1835 11 x 10 3/4 Med-High 3.02 92.6 1182 100 15 15 66 

Ca - 58MXA 140-20 138 129 1805 11 x 10 3/4 Med-High 3.02 92.6 1182 100 15 15 66 

Ca - 58MXA 140-20* 138 129 1725 11 x 10 3/4 Med-High 3.02 91.2 1199 100 15 15 66 

Ca - 58MXA 140-20* 138 129 1805 11 x 10 3/4 Med-High 3.02 91.2 1199 100 15 15 66 

Ca - 58MXA 140-20* 138 129 1835 11 x 10 3/4 Med-High 3.02 91.2 1199 100 15 15 66 

Ca - 58MXA140-20** 138 128 1835 11 x 10 3/4 Med-High 3.02 92 1189 100 15 15 66 

Ca - 58MXA140-20** 138 128 1725 11 x 10 3/4 Med-High 3.02 92 1189 100 15 15 66 

Ca - 58MXA140-20** 138 128 1805 11 x 10 3/4 Med-High 3.02 92 1189 100 15 15 66 

H.3.3 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces 

Table H.3.S4 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at SO Btu/h 

1200 CFM 

O:ndensirg T\t\O-Stage 

50 kBtuth 1200 CFM 

f-igh LoN Plr 

OffDelay 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

NA 

M:x:leIs f-igh LoN f-igh LoN a=M a=M SICMel' fllbtor Spea:l SWy PFUE Eae PE Fre- Fbst- Ol-D=lay CJf-D=lay Inpl Inpl ruput ruput Size Size Taps ruet p..rge p..rge 0.5 0.5 Area 

T9I'VPIA)5()F12** 35 46 33 268 595 325 11 x8 1/2 Variable 226 921 268 140 3 5 30 140 

H-38 
Table H.3.55 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 60 Btu/h

1200 CFM

Non-Condensing Tvw-Stage

60 kBtu/h 1200 CFM

Air

High Low high Low high Low Blaney Moto Speed Suppl Pre- Post- Models Input Input Output Output CFM CFM Size Size Taps Outlet AFUE Eae PE

purge purge

On-Delay Of-Delay

0.5 0.5

Area

TDD060R9V3F* 39 48 31.2 228 881 658 10x7 1/2 Variable 2.21 80 228 97 45 100.00

TUD060R9V3K` 48 48 31 228 942 684 10x7 1/2 Variable 2.21 80 228 97 45 100.00

58CVX070-12` 44 51 35 162 1180 725 10x6 1/2 Variable - 80 162 25 15 5 25 120.00

58CVA070-12 44 54 35 162 1180 725 10x6 1/2 Variable - 80 162 25 15 5 25 120.00

660DFV-36A-070-- 45 54 36 296 995 900 10x8 1/2 Variable 1.74 80 296 57 15 5 45 90.00

660UI-N-36/.070 ** 45 54 36 271 940 865 10x8 1/2 Variable 1.81 80 271 62 15 5 45 90.00

Table H.3.56 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 70 Btu/h

1200 CFM

Non-Condensing Tv o-Stage

70 kBtu/h 1200 CFM

Models

AMv80703BX

Agh

Input

Lowy

Input

56

ligh

Output

Law

Output

251

tigh

CFM

as

Law

CFM

0.5

BaAer

Size

Meld

Sze

Speed

Taps

Variable

i

Air

aatlet

Area

ARE

80

Eae

251 104

PrepurgePbstpurge

Or-Delay Off-Delay

Table H.3.57 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 70 Btu/h

1600 CFM

Non-Condensing Tu4o,Stage

70 kBtu/h 1600 CFM

high Law Air

Models high

I

Law

I

High

O

Low

O

aW CFM Blom

Si

Wor

S¢

Speed

T C l

ARE Eae PE Pre- Post- On-Delay Off-Delay nput nput utput utput 0.5 0.5 ze e aps ut et page purge

Area

AMv807043X 52.5 56 42 251 1330 1000 10x8 314 Variable 2.18 80 251 104

 EE-RM/STD-01-350 COMMENT 164

Table H.3.55 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 60 Btu/h 

1200 CFM 

f\bn-Condensing T VI.O-SI:age 

60 kBtu/h 1200 CFM 

Hgh Low Air 

f'vtx:les Hgh Low Hgh Low CFM CFM BiCMer M:Jtor Speed Suppl AFUE Eae PE Pre- Post- ar-Deay Off-Deay Input Input OJtput OJtput Size Size Taps rue! purge purge 0.5 0.5 hea 

T!)[)()OOR9\/.3P 39 48 31.2 228 881 658 10x7 1/2 Variable 2.21 80 228 97 45 

lUXl6OR9\/.3K* 48 48 31 228 942 684 10x7 1/2 Variable 2.21 80 228 97 45 

580JX07Q.12' 44 51 35 162 1180 725 10x6 1/2 Variable - 80 162 25 15 5 25 

58CVf\D7Q.12 44 54 35 162 1180 725 10x6 1/2 Variable - 80 162 25 15 5 25 

C?6ODFV-36A-07Q. - 45 54 36 296 995 900 10x8 1/2 Variable 1.74 80 296 57 15 5 45 

C?6OUHV-36A-07Q. - 45 54 36 271 940 865 10x8 1/2 Variable 1.81 80 271 62 15 5 45 

Table H.3.56 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 70 Btu/h 

1200 CFM 

I\bn-O:lndensing T VI.O-SI:age 

70 kBtu/h 1200 CFM 

Hgh LoN Air 

100.00 

100.00 

120.00 

120.00 

90.00 

90.00 

f'vtx:les Hgh LoN Hgh LoN CFM CFM SlCMer fllbtcr Speed Supply AFUE Eae PE Pre- Post- ar-Deay Off-Deay Input Input 0Jtput OJtput Size Size Taps rue! purge purge 0.5 0.5 Nea 

AMv807038X 56 251 Variable - 80 251 104 

Table H.3.57 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 70 Btu/h 

1600 CFM 

I\bn-O:lndensing TV\O-Stage 

70 kBtu/h 1600 CFM 

Hgh LoN Air 

f'vtx:les Hgh LoN Hgh Low CFM CFM SlCMer fllbtcr Speed SuppI AFUE Eae PE Pre- Post- ar-Deay Off-Deay Input Input 0Jtput 0Jtput Size Size Taps rue! purge purge 0.5 0.5 hea 

AMv80704BX 52.5 56 42 251 1330 1000 10x8 2.'4 Variable 2.18 80 251 104 

H-39 
Table H.3.58 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 70 Btu/h

2000 CFM

r bi rgT

7OkRLVbMGM

Ntxs

FCETP072"=\8 48

Lav

ir1)xt

H

Q.W

Lour

o 4a

384

Hi

CFM

0.5

Lav

CFM

0.5

Bona

11x10

Ntta

SUM

314

SqDqed

Tars

liaiadd 250

PFD

80

Ead

381

FE

75

Ra

30

Ftt

p

30

Ovl)da/

30

Of-Diaj

Table H.3.59 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 75 Btu/h

1200 CFM

Non-Condensing Tv o-Std

75 kBtu/h 1200 CFM

xlds Filth Low Figh La3

ugh

CFM

Low

CFM

Boner Moor EcOe-I

Air

suppy

FLE ae E

Pre- Postn-Delay ff-Delay input Input Output Output 0.5 0.5 Sze Size Taps Outlet purge purge

Area

RGLL-07( E,N BRKR 52 61 41 373 980 700 11x10 1/2 Variable 2.76 80.3 373 97

RGPL-07(E,N)BR R 52 60 41 423 1060 700 11 x 10 1/2 Variable 2.76 80.3 423 77

Table H.3.60 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 75 Btu/h

1600 CFM

Non-Condensing Tvu>Stage

75 iLI/h 1600 CFM

Filth Lcm Air

Models H9h Low Filth Lan CFM CFM saner Moor Speecl Sipoy ARE Eae PE Pre PbSt- OrrDelay Off Delay Input Irxat Output Output 0.5 0.5 Size Size Taps OutIE# purge purge

Area

RGCL-07(E N)BROR 52 61 41 373 980 700 11 x 10 34 Viable 2.76 80.3 373 110

RC-PI -07(E N)BRC} 52 60 1 41 423 1060 700 11 x 10 34 Vaiat e 2.76 80.3 423 77

 EE-RM/STD-01-350 COMMENT 164

Table H.3.58 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 70 Btu/h 

2000 CFM 

~rgT~ 

70 kBtihamCFfV1 

Hg, LoN AT 

M:rl3s Hg, LoN Hg, LoN CRv1 CRv1 80J1H IVt:tcr ~ 18.qly 1JlR..E I fa: FE Re- M- OJ-():jCo/ Of..[)3Co/ IrpJ IrpJ 0Jp1 0Jp1 S2e S2e Tq:s rua p..rg3 p..rg3 0.5 0.5 Am 

R33TJlO7'Z-\A3 48 ffi :£ :£4 1CID ffi) 11x10 3'4 \fcricJje 2m 8J 1:£4 70 3J 3J 3J 

Table H.3.59 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 75 Btu/h 

1200 CFM 

1\bn-0000000ing T I/I.O-Stage 

75 kBtu/h 1200 CFM 

I-igh LoN Air 

121m 

MxleIs I-igh LoN I-igh LoN a=M a=M BiCMef fvbtor Speed StqJIy ARE Eae PE Pre- Post- Qr.DlIay Cff-Dliay Input Input OJtput 0Jtput Size Size Taps ruet plI"ge purge 0.5 0.5 ftrea 

RCll-07(E,N)BRKR 52 61 41 373 980 700 11 x10 112 Variable 2.76 80.3 373 97 

RGPL -07(E,N)BRKR 52 60 41 423 1060 700 11 x10 1/2 Variable 2.76 80.3 423 77 

Table H.3.60 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 75 Btu/h 

1600 CFM 

1\bn-00000000ng TVI.O-Stage 

75 kBtu/h 1600 CFM 

I-igh LON Air 

MxleIs I-igh LoN I-igh LoN a=M a=M BiCMef fvbtor Speed 9Jppy ARE Eae PE Pre- Post- Qr.DlIay Cff-Dliay Input Input 0Jtput 0Jtput 0.5 0.5 Size Size Taps ruet purge purge 

hea 

RCll-07(E,N)BRCR 52 61 41 373 980 700 11 x10 :Y4 Variable 2.76 80.3 373 110 

RGPL-07(E,N)BRCR 52 60 41 423 1060 700 11 x10 :Y4 Variable 2.76 80.3 423 77 

H-40 
Table H.3.61 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 80 Btu/h

1200 CFM

Noy-Ca ring Tv o-S't

80 kBu/h 1200 CFM

Models ugh

Input

Lane

Input

figh

Output

Low

Output

rig,

CFM

0.5

Low

CFM

0.5

Blov

Size

Motor

Size

Speed

Taps

Par

SuppY

OuBet

Area

AFUE Fee PE

PrePurgePcstpige

On--Delay Off-Delay

P1DUA12Vn6401 59 63 48 469 1315 880 10x8 1/2 Vaiate 1.84 80 469 35 15 30 60.00

Pv8A12N080UH11 59 63 48 469 1490 990 10x8 1/2 Variable 1.84 80 469 35

TDD08098V3P 52 63 41.6 332 1170 820 10x7 1/2 Vaiable 2.21 80 332 67 45 100.00

TUD0808V3{C 64 64 41 299 1240 875 10x7 1/2 Variable 2.21 80 299 68 45 100.00

Table H.3.62 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 80 Btu/h

1600 CFM

N -Condensing Tvao-Stage

80 kBu/h 1600 CFM

Modes

TLU080iR9V4K"

58Cr/X090-16` l

High

Input

64

58

Loa

Input

64

68

ligh

Qiput

41

47

Low

Output

265

226

ligh

CFM

0.5

1243

1210

Low

CFM

0.5

861

985

Baker

size

10x10

10x8

Motor

Size

1/2

1/2

Speed

Taps

Variable

Variable

Par

SLOY

Outlet

Area

2.69

PFUE

80

80

Eae

265

226

PE

64

15

PostP

5

Cn-Delay

45

25

Off-Delay

100.00

120.00

Table H.3.63 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 90 Btu/h

1200 CFM

Non-Condensing Two-Stage

90 kBtu/h 1200 CFM

Hgh LJOW Par

Models ugh

I t

Low

I t

ugh

O t t

Low

O t t

CFM CFIVI Boner

S

Moor

Si

Speed

T

Suppl

O l

AFUE Eae PE Pre- OrrDelay Off-Delay npu npu u pu u pu 0.5 0.5 ize ze aps ut et purge purge

Area

65ODFV-36B 090 *" 60 72 48 414 1055 955 10x8 1/2 Variable 2.14 80 414 58 15 5 45 90.00

600UI N 36B 090 60 72 48 412 930 840 10x8 1/2 Variat le 2.21 80 412 60 15 5 45 90.00

 EE-RM/STD-01-350 COMMENT 164

Table H.3.61 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 

1200 CFM 

f\bn-Conclensing T \t\O-Stage 

80 kStu/h 1200 CFM 

Hgh LoN Air 

I\tbdeIs Hgh LoN Hgh LoN CFM CFM BiCMer Mltcr Speed 8JppI, .AfUE Eae PE Pre- Pcst- Ol-Delay Off-Delay Inp.Jt InPJI 0Jtp.Jt 0JtPJl Size Size Taps Outlet PJrg9 PJrg9 0.5 0.5 Area 

P1DUA12\AJ6401 59 63 48 469 1315 880 10x8 1/2 Vaiable 1.84 80 469 35 15 30 60.00 

PV8A 121\kJ8OUH11 59 63 48 469 1490 990 10x8 1/2 Vaiable 1.84 80 469 35 

TlXXJ8OR9V3P 52 63 41.6 332 1170 820 10x7 1/2 Vaiable 2.21 80 332 67 45 100.00 

lUXl8OR9V3K* 84 64 41 299 1240 875 10x7 1/2 Vaiable 2.21 80 299 68 45 100.00 

Table H.3.62 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 

1600 CFM 

f\bn-Conclensing T \I\O-Stage 

80 kStu/h 1600 CFM 

Hgh LoN Air 

I\tbdeIs Hgh LoN Hgh LoN CFM CFM BiCMer Mltcr Speed 8JppIy .AfUE Eae PE Pre- Pcst- Ol-Delay Off-Delay InPJI Irput 0Jtp.Jt 0JtPJl Size Size Taps Outlet PJrg9 PJrg9 0.5 0.5 hea 

1UXl8OR9V4K* 64 64 41 265 1243 861 10x10 1/2 Vaiable 2.69 80 265 64 45 100.00 

5P/.J..!Xfro-16* 58 68 47 226 1210 985 10x8 1/2 Vaiable - 80 226 29 15 5 25 120.00 

Table H.3.63 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 

1200 CFM 

f\bn-O:>ndensing TIAO-8tage 

00 kStu/h 1200 CFM 

Hgh LoN Air 

I\tbdeIs Hgh LoN Hgh LoN CFM CFM BiCMer Mltcr Speed &i~ PFUE Eae PE Fre- Pcst- Ol-Delay Off-Delay Irput InPJI 0Jtp.Jt 0JtPJl Size Size Taps Outlet PJrg9 PJrg9 0.5 0.5 hea 

GBQI:RI-36B-09[).. ** 80 72 48 414 1055 955 10x8 1/2 Vaiable 2.14 80 414 58 15 5 45 90.00 

GBOUHI/-36B-090-** 80 72 48 412 930 840 10x8 1/2 Vaiable 2.21 80 412 80 15 5 45 90.00 

HAl 
Table H.3.64 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 90 Btu/h

1600 CFM

Nom- ing Two-Stage

90 kBtu/h 1600 CFM

mxlels Hgh

Input

Low

Input

Fiji

CuOut

L ON

Output

Hgh

CFM

0.5

LOv

a

0.5

Blaner

Sze

Nuor

Sze deed Taps

Ar

Supply

Outlet

Area

PFUE PE

Prep

PbstP-Rie

Cn-Delay Off--Delay

7-090-16 158 1 71 1 47 1 226 112101 985 1 10x8 1 1/2 1 Variable I - I 80 12261 29 I 15 I 5 I 25 1120.00

Table H.3.65 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 90 Btu/h

2000 CFM

N n-Condensing Two-Stage,

90 kBtLdh 2000 CFM

Air

F1gh Low Hgh LaN F§gh Lane Blaney Nbtor Speed Supply Pre- Post- Models Input Input Output Output CFM CFM Sze Sze Taps Outlet ARE Eae PE

purge purge

On-Delay Off-Delay

0.5 0.5

Area

O60DFV-606090-" 60 72 48 424 1660 1515 11.5x1 1 Variable 2.61 80 424 60 15 5 45 90.00

C OUHV-606090- " 60 72 48 460 1560 1440 11.5x 1 1 Variable 2.68 80 460 58 15 5 45 90.00

C OUM/-60 -09" 60 72 48 460 1515 1395 11.5x1 1 Variable 2.68 80 460 58 15 5 45 90.00

AMv309050X 67.5 72 54 237 1530 1150 10x 10 314 Variable 2.66 80 237 137

GUI D90""50 64 74 51 237 1368 950 10x8 314 Variable 2.64 80 237 137 , 15 30 90.00

Table H.3.66 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 100 Btu/h

1600 CFM

NorrCaidensing Tmo-Stage

1 00 kWLWh 1600 CFM

Fib LOW Ar

Nodels FEgh Lav 1gh Low CFM CFM

Blaney Nbtor Speed Supply

ARE Eae PE Pre- PostOn-Delay Off -Delay Input input Wput Output 0.5 .50

Sze Sze Taps Outlet purge

pmje

Area

P1D1616W8001 65 80 53 493 1490 990 10 x 10 314 Variable 226 80 493 41 15 30 60.00

Pv8B16N100LH11 65 80 53 493 1480 975 10x 10 314 Variable 2251 80 493 41

 EE-RM/STD-01-350 COMMENT 164

Table H.3.64 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 

1600 CFM 

t\b1-On:lensirg T \J\O-Stage 

90 kBbih 1600 CFM 

Hgh LoN Ar 

M:x:!eIs Hgh LoN Hgh LoN CFM CFM BiCMer M::tcr Speed Tap; SWy .AfUE IEae FE Pre- R::st- O"t-celay Of-celay IrpJt IrpJt 0JtpJt 0JtpJt Size Size a.tIe! Ill96 Ill96 0.5 0.5 Iw3. 

53OIJl£ID 16 53 71 47 Z26 1210 935 10x8 1/2 Vaialle - 00 Z26 29 15 5 25 120.00 

Table H.3.65 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 

2000 CFM 

t\b1-O:nlensirg T \i\O-Stage 

90 kBtulh 2000 CFM 

Hgh LON Ar 

M::x:leIs Hgh LoN Hgh LoN CFM CFM BiCMel' M::tcr Speed &ipply flFUE Eae FE Pre- Post- O"t-celay Of-celay Input Input ruput ruput 0.5 0.5 Size Size Taps a.tIe! purge purge 

ftrea 

G6OOFV-6OC-OOO-- 60 72 48 424 1660 1515 11.5x 1 1 Vaialle 2.61 00 424 60 15 5 45 90.00 

C:OOUHII-6OC-OOO-- 60 72 48 460 1560 1440 11.5x1 1 Vaialle 2.68 00 460 53 15 5 45 90.00 

C:OOUHII-6OC-OOO-- 60 72 48 460 1515 1395 11.5x1 1 Vaialle 2.68 00 460 53 15 5 45 90.00 

AMV'80905CX 67.5 72 54 Z37 1530 1150 10x10 2/4 Varialle 2.66 00 Z37 137 

GUII!1),Xr50 64 74 51 Z37 1368 950 10x8 2/4 Varialle 2.64 00 237 137 15 30 90.00 

Table H.3.66 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 

1600 CFM 

t\b1-Corx:Iensirg T \fI.O-Stage 

100 kBtulh 1600 CFM 

Hgh LoN Ar 

M::x:leIs Hgh LoN Hgh LoN CFM CFM BiCMer M::tcr Speed SWy fIFUE Eae FE Pre- R::st- O"t-celay Of-celay IrpJt IrpJt 0JtpJt 0JtpJt 0.5 0.5 SIze Size Taps rue! purge purge 

ftrea 

P1DLB16VOOOO1 65 00 53 493 1490 990 10x10 2/4 Varialle 226 00 493 41 15 30 60.00 

Pv8B16N100lJ-111 65 00 53 493 1460 975 10x10 2/4 Varialle 226 00 493 41 

H-42 
Table H.3.67 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 100 Btu/h

2000 CFM

Nan-Condensing Tw>Stage

100 kBtu/h 2000 CFM

Air High Low -Igh Low High Law Blaaer Motor Speed Supply Pre- Post Models Input Input Output Output CFM CFM Sze Size Taps Outlet AFUE Eae PE

purge purge

CrrDelay Off-Delay

0.5 0.5

Area

FG6TA100*-VB 60 79 48 461 1240 750 11x10 314 Variable 2.50 80.5 461 76 30 30 30 120.00

62D80BT100V20C'-'- 80 80 64 212 1150 860 12x 10 3/4 Variable 272 80 212 128 90 180.00

P1DUC20V08001 65 80 53 482 1480 975 11 x10 1 Variable 269 80 482 41 15 30 60.00

PJ8C20N1000H11 65 80 53 482 1480 975 11 x10 1 Variable 274 80 482 41

RGLL-10(E,N)BRMR 70 81 56 494 1250 942 11x10 1 Variable 276 80.3 494 110

RGPL-10(E,N)BRMR 70 81 56 551 1320 942 11x10 1 Variable 276 80 551 82

T8MPd100J20 70 81 61 243 11X10 1 Variable 273 80 243 47 3 30 30 140.00

TDD100R9V5F* 65 81 52 347 1560 1080 11x10 1 Variable 269 80 347 70 45 100.00

TUD100R9V5W 80 79 52 298 1610 1060 10x`101 1 Variable 269 80 298 65 45 100.00

Table H.3.68 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 115 Btu/h

2000 CFM

Non-Condensing Two-Stage

120 kBtu/h 2000 CFM

Air

High Low High Low High Low Blaney Motor Speed Suppl AF Pre- Post- Models Input Input Output Output CFM CFM Sze Size Taps Outlet E

Eae PE

purge purge

On Dray of Delay

0.5 0.5

Area

FG6TA120*-VB 72 95 58 465 1680 1220 11x10 3/4 Variable 2.50 80 465 76 30 30 30 120.00

P1DUC20V09601 78 96 64 485 1950 1330 11x10 1 Variable 2.69 80 485 51 15 30 60.00

PV8C20N120UH11 78 96 64 485 1950 1330 111x10 1 Variable 2.74 80 485 51

TDD120R9V5F* 78 95 62.4 393 1640 1115 11x'10 1 Variable 2.69 80 393 91 45 100.00

TUD120R9V5K* 96 97 62 454 1666 1211 10 x 10 1 Variable 3.17 80 454 75 45 100.00

 EE-RM/STD-01-350 COMMENT 164

Table H.3.67 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 

2000 CFM 

I\bn-Condensing T IAO-Stage 

100 kBtulh 2000 CFM 

High LON Plr 

M:x:IeIs Hgh LON Hgh LON CFM CFM BiCl'Mll" fvbtor Speed Suppy ,AfUE Eae PE Pre- Post- Ol-D9Iay af-D9Iay Inp..il Inp..il OJtp..il OJtp..il 0.5 0.5 Size Size Taps 0Jt1e! purge purge 

kea 

FG6TA100*-\IB 60 79 48 461 1240 750 11 x 10 3'4 Variable 2.50 80.5 461 76 30 30 30 120.00 

G208OOT1 00'v20C*-*** 80 80 64 212 1150 860 12x10 3'4 Variable 272 80 212 128 90 180.00 

P1DUC20V08001 65 80 53 482 1480 975 11 x 10 1 Variable 269 80 482 41 15 30 60.00 

Pv8C2ON100UH11 65 80 53 482 1480 975 11 x 10 1 Variable 274 80 482 41 

RGLL -10(E,N)BRMR 70 81 56 494 1250 942 11 x10 1 Variable 276 80.3 494 110 

RGPL-10(E,N)BRMR 70 81 56 551 1320 942 11 x10 1 Variable 276 80 551 82 

T8IvPI/100J20 70 81 61 243 11 x10 1 Variable 273 80 243 47 3 30 30 140.00 

1ID100R9V5P 65 81 52 347 1560 1080 11 x10 1 Variable 269 80 347 70 45 100.00 

TUD100R9V5K' 80 79 52 298 1610 1060 10x10 1 Variable 269 80 298 65 45 100.00 

Table H.3.68 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 115 Btu/h 

2000 CFM 

Non-Condensing T IM)-Stage 

120 kBtulh 2000 CFM 

Hgh Low Plr 

M:xlels High Low Hgh Low CFM CFM BICMeI' M:>tor Speed Suppl AFL Eae PE Pre- Post- Ol-D9Iay Off-D9Iay Inp..il Input 0Jtput OJtp..il 0.5 0.5 Size Size Taps 0Jt1e! E purge purge 

kea 

FG6TA120*-\IB 72 95 58 465 1680 1220 11 x 10 3'4 Variable 2.50 80 465 76 30 30 30 120.00 

P1DUC20V09801 78 96 64 485 1950 1330 11 x 10 1 Variable 2.69 80 485 51 15 30 60.00 

PV8C2ON120UH11 78 96 64 485 1950 1330 11 x 10 1 Variable 2.74 80 485 51 

IDD120R9V5P 78 95 62.4 393 1640 1115 11 x10 1 Variable 2.69 80 393 91 45 100.00 

TUD120R9V5K* 96 97 62 454 1666 1211 10x 10 1 Variable 3.17 80 454 75 45 100.00 

H-43 
Table 11.3.69 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 120 Btu/h

2000 CFM

Non-Condensing Two-Stage

120 kBtu/h 2000 CFM

I-figh Low Ar High Law High Low Blower Motor Speed Suppt AF E

Pre- Post- On-Delay may Off-Delay Input Input Output Output 0.5

0.5

0.5

0.5 Size Size Taps Outlet E purge purge

Area

FG6TA120*-VB 72 95 58 465 1680 1220 11x10 3/4 Variable 2.50 80 465 76 30 30 30 120.00

P1 DUC20VO9601 78 96 64 485 1950 1330 11x10 1 Variable 2.69 80 485 51 15 30 60.00

PV8C20N120UH11 78 96 64 485 1950 1330 11 x 10 1 Variable 2.74 80 485 51

TDD120R9V5F* 78 95 62.4 393 1640 1115 11x10 1 Variable 2.69 80 393 91 45 100.00

TUD120R9V5K* 96 97 62 454 1666 1211 10x10 1 Variable 3.17 80 454 75 45 100.00

Table H.3.70 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 125 Btu/h

2000 CFM

Non-Condensing Two-Stage

125 kBtu/h 2000 CFM

High Law Ar

Mks N9h Low High Law CFM CFM Blower or Speed Supply

AFUE Eae PE Pre- Post- On-Delay Off--Delay Input Input Output Output Sue Sze Taps Outlet purge purge 0.5 0.5 Area

G2D80BT125V20C*--:- 100 100 80 316 1612 1210 12x 10 314 Variable 2.72 80 316 160 90 180.00

RG1I-12(E,N)ARMR 87 101 70 840 1670 1296 11 x10 1 Variable 3.24 80 840 101

RGPL-12(E,N)ARNR 87 101 70 1106 1890 1296 11x10 1 Variable 3.24 80 1106 102

T8M'V125J20 87.5 101 71 685 11x10 1 Variable 2.73 80 685 49 3 30 30 140.00

060DFV-60D-135- ` 90 109 73 797 1610 1465 1.5x1 I Variable 3.07 80 797 62 15 5 45 90.00

C60UFN-60D-135-** 90 108 72 547 1475 1345 1.5x1 1 Variable 3.16 80 547 65 15 5 45 90.00

C-BOUFN-60D-135-** 90 108 72 547 1570 1435 111.5x 1 Variable 3.16 80 547 65 15 5 45 90.00

Table H.3.71 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 140 Btu/h

2000 CFM

Nbr derrir Tvva

140 k&h.Vt 2000 CFM

Hqt LON Hit LON

Hit LON

BoA9'

iAir

Fl& Ft-t- Mxhs CFM QM ARE Eae FE C).gbay Cff-Edaj Irp.t Irp.t QJPU oi1}xt 9m Sim Taps CLtlet PLIT IJ 0.5 0.5

GJ\M0`*50 96 111 76 260 1594 1100 10x9 3/4 'faiaki 319 80 311 112 15 30 9D.0)

7LD14Cf v& 112

1

111 72 477

1

1810

1

1280

1

10x10 1 Vaiak! 317

1

80 477 95 45 100.00

C 8CBT19S/1(JD *"* 120 120 96 293 170D 1275 12x 10 314 Vaiakl 319 80 296 187 90 180.00

 EE-RM/STD-01-350 COMMENT 164

Table H.3.69 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 120 Btu/h 

2000 CFM 

Non-o:>ndensing T WJ-Stage 

120 kBtu/h 2000 CFM 

High Low PJr 

MJdels High Low High Low CFM CFM Blov.er fvbtor Speed Suppl AFL Eae PE Pre- Post- On-Delay Off-Delay Input Input Qrtput Qrtput Size Size Taps Qrtlet E purge purge 0.5 0.5 Area 

FG6TA120*-VB 72 95 58 465 1680 1220 11 x 10 314 Variable 2.50 80 465 76 30 30 30 120.00 

P1 DUC2OV09601 78 96 64 485 1950 1330 11 x10 1 Variable 2.69 80 485 51 15 30 80.00 

PV8C20N12OUH11 78 96 64 485 1950 1330 11 x10 1 Variable 2.74 80 485 51 

TDD120R9V5P 78 95 62.4 393 1640 1115 11 x10 1 Variable 2.69 80 393 91 45 100.00 

TUD12OR9V5K* 96 97 62 454 1666 1211 10x10 1 Variable 3.17 80 454 75 45 100.00 

Table H.3.70 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 125 Btu/h 

2000 CFM 

Non-O:>ndensing T V\O-Stage 

125 kBtu/h 2000 CFM 

High Low PJr 

MxleIs High Low High Low CFM CFM Blov.er fvbtor Speed Supply AFUE Eae PE Pre- Post- On-Delay Off-Delay Input Input Qrtput Qrtput Size Size Taps Qrtlet purge purge 0.5 0.5 Area 

G2D8OBT125V2OC*-*** 100 100 80 316 1612 1210 12x10 314 Variable 2.72 80 316 160 90 180.00 

RGLL-12(E,N)ARfVR 87 101 70 840 1670 1296 11 x10 1 Variable 3.24 80 840 101 

RGFL-12(E,N)ARIvR 87 101 70 1106 1890 1296 11 x 10 1 Variable 3.24 80 1106 102 

T8MPV125J2O 87.5 101 71 685 11 x10 1 Variable 2.73 80 685 49 3 30 30 140.00 

G30DFV-60D-135-** 90 109 73 797 1610 1465 ~1.5x1 1 Variable 3.07 80 797 62 15 5 45 90.00 

G30UHV-60D-135-** 90 108 72 547 1475 1345 r1.5x1 1 Variable 3.16 80 547 65 15 5 45 90.00 

G30UHV-60D-135-** 90 108 72 547 1570 1435 h1.5x1 1 Variable 3.16 80 547 65 15 5 45 90.00 

Table H.3.71 Non-Condensing Two-Stage Non-Weatherized Gas Furnaces at 140 Btu/h 

2000 CFM 

~rgT\J\0Scg3 

140 kB.u'h2XD CFM 

Hg, LoN Pir 

I\/Ixi:ls Hg, LoN Hg, LoN a=rv1 CRv1 BOA6' I\Itia ~ s.w PRE Ere FE Re- R:S:- Qr[):jC¥ Of-D3C¥ Irpl Irpl Clip1 Clip1 S2e S2e Tcp:; Gila p..rg3 p1g3 0.5 0.5 Prffi 

GJVl4O"*5J ffi 111 76 33J 1ffi4 11m 10x9 3'4 \fcJicije 319 8J 33J 112 15 3) moo llD1~ 112 111 72. 477 1810 1Lm 10x10 1 \fcJicije 317 8J 417 ffi 45 100.00 

Gllr8T1fI)..£llJ'-*"* 12) 12) ffi 2B 170J 1275 12x10 3'4 \fcJicije 319 8J 2B 187 m 18J.m 

H-44 
14.3.4 Condensing Two-Stage Non-Weatherized Gas Furnaces

Table H.3.72 Condensing Two-Stage Non-Weatherized Gas Furnaces at 45 Btu/h 1200

CFM Condensing Two-Stage

Condensing Two-Stage

45 kBtu/h 1200 CFM

Models

G2D95BC04OV12B-1

High

Input

28

Low

Input

38

High

Output

Low

Output

80

High

CFM

0.5

836

Low

CFM

0.5

544

Blower

Size

10x8

Motor

Size

1/2

Speed

Taps

Variable

Air

Supply

Outlet

Area

2.06

AFUE

94.5

Eae PE

180 123

Prepurge

Postpurge

OnDelay Off-Delay

Table H.3.73 Condensing Two-Stage Non-Weatherized Gas Furnaces at 50 Btu/h 1200

CFM

Cur sing Tv o-Stage

50 kBtu/h 1200 CFM

Models

T9UPV050F12"*

High

Input

35

Low

Input

46

i gh

output

33

Low

Output

268

High

CFM

0.5

Law

CFM

0.5

595 325

Banff

Sze

11x8

Motor

Sze

1/2

Speed

Taps

VaiaUe

Air

Supply

Cutlet

Area

2.26

ARE

921

Eae PE

268 140

Rt;

pub

Postpurge

Oa-Delay

Table H.3.74 Condensing Two-Stage Non-Weatherized Gas Furnaces at 60 Btu/h 1200

CFM

Off-Delay

140

Condensing Two-Stage

60 kBtu/h 1200 CFM

Air

Iigh Low High LOS

High LOW Blaner Motor Speed Suppl^ Pre Post Models Input Input Output Output

CFM Sze Sze Taps Outlet AFUE Eae PE

purge purge

On Delay Off Delay

0.5 0.5

Area

Pv9B12N060UP11 39 56 36 127 1110 710 11x8 1/2 Variable 2.26 93.2 127 68

RGFf}06(E N)fV1CKS" 24 56 22 254 795 320 11x7 1/2 Var able 2.27 93.5 254 105

RGGD 06(E N)MCKS 24 57 21.888 354 795 320 11x7 1/2 Variable 2.29 91.4 354 124

TDY06080U3W 39 56 37 200 1150 750 10x8 1/2 Variable 2.21 921 200 62 0 5 45 100.00

11UY060R9V3W 39 56 37 199 1125 , 775 10x8 1/2 Variable 2.21 93 199 52 0 5 45 100.00

 EE-RM/STD-01-350 COMMENT 164

H.3.4 Condensing Two-Stage Non-Weatherized Gas Furnaces 

Table H.3.72 Condensing Two-Stage Non-Weatherized Gas Furnaces at 45 Btu/h 1200 

CFM Condensing Two-Stage 

Condensing T vvo-Stage 

45 kBtU/h 1200 CFM 

High Low Air 

fvbdels High Low High Low CFM CFM Blower Motor Speed Suppl\ AFUE Eae PE Pre- Post- 01- Off-Delay Input Input Output Output 0.5 0.5 Size Size Taps Outlet purge purge Delay 

Area 

G2D95BC040V12B-1 28 38 180 836 544 10x8 1/2 VariablE 2.06 94.5 180 123 

Table H.3.73 Condensing Two-Stage Non-Weatherized Gas Furnaces at 50 Btu/h 1200 

CFM 

Qrdensing TIAO-Stage 

50 kBtu/h 1200 CFM 

Hgh LoN Jlir 

M.:x:!eIs Hgh LoN Hgh LON CFM CFM EilCM€f M::tor ~ Si.Wy PFl.E Eae PE R-e- Fb5t- Ol-D=Jay af-D=Jay 1rpJ! Inp..il 0Jtp..il illp..il 0.5 0.5 Size Size Taps rue! purge purge 

Prea 

T9fvPv1J5OF12'* 35 46 33 268 595 325 11 x8 1/2 Variable 2.26 92.1 268 140 3 5 30 140 

Table H.3.74 Condensing Two-Stage Non-Weatherized Gas Furnaces at 60 Btu/h 1200 

CFM 

O:lndensing T IAO-Stage 

60 kBtu/h 1200 CFM 

Hgh LoN Air 

M.:x:!eIs Hgh LoN Hgh LoN CFM CFM EilCM€f rvbtor Speed Su~ AFUE Eae PE R-e- Fb5t- Ol-De!ay af-D=Jay 1rpJ! Inp..il illput illp..il 0.5 0.5 Size Size Taps rule! purge purge 

Nea 

Pv9B12N:l6OlJP11 39 56 36 127 1110 710 11x8 1/2 Variable 2.26 93.2 127 68 

RGFD-06(E,N)fI/CKS** 24 56 22 254 795 320 11x7 1/2 Variable 2.27 93.5 254 105 

RGGD-06(E,N)rvD<S 24 57 21.888 354 795 320 11x7 1/2 Variable 2.29 91.4 354 124 

IDYOOOR9V3W 39 56 37 200 1150 750 10x8 1/2 Variable 2.21 92.1 200 62 0 5 45 100.00 

TUYOOOR9V3W 39 56 37 199 1125 775 10x8 1/2 Variable 2.21 93 199 52 0 5 45 100.00 

HA5 
Table H.3.75 Condensing Two-Stage Non-Weatherized Gas Furnaces at 60 Btu/h 2000

CFM

Condensing Two-Stage

60 kBtu/h 2000 CFM

M>s ligh I

Input

Lary

Input

Fight

Ouput

Law I

Output CFM I

CFFM

I

B.

Size

NU.,

size aps

Air

T.UIet FLE Eael PE ( Prepurge

Postpurge

,Dday ff-Day

0.5 0.5

Area

FG6TC060"-\/B 40 520 1240 750 2.50 123 30 120.00

FGSTL060'-\/B 40 404 1240 750 2.50 127 30 120.00

Table H.3.76 Condensing Two-Stage Non-Weatherized Gas Furnaces at 70 Btu/h 1200

CFM

Condensing Tvo-Sae

70 kBtu/h 1200 CFM

bdd ugh Lane Figh Low

Figh

CFM

Low

CFM

Blaney Nor Speed

Air

Suppl

FUE ae E

Pre- Post- n-Delay ff-Delay Input Input Output Output 0.5 0.5 am Size Taps Outlet purge purge

Prey

G61NPd36B-07V 45 61 43 301 960 865 0x8 1/2 Variable 2.28 94.1 301 59

PMv90703BX 48 65 46.4 275 Variable 1.73 93 275 86

Table H.3.77 Condensing Two-Stage Non-Weatherized Gas Furnaces at 70 Btu/h 1600

CFM

Condensing Tv o-Stage

70 kBtu/h 1600 CFM

Figh LOW Air

Nbdds ugh

I t

Low

I t

Figh

O t t

Low

O t t CFM CFM Blaney

Si

Motor Speed Suppl AFUE Eae PE Pre Post On Delay Off-Delay npu npu u pu u pu 0.5 0.5 ze Sze Taps Outlet purge purge

Prey

AGy907040( 48 65 45 225 1318 915 10x 10 3/4 Variable 2.33 93.3 225 100

PMv90704CX 48 67 46.4 275 1325 920 10x10 3/4 Variat e 2.30 95.5 275 86

GGUPU70**40 48 65 45 225 1318 915 11x9 314 Variable 1.89 93.3 225 100 10 15 30 90.00

CWPD70"X40 48 67 46.4 275 1325 920 11x9 34 Varial^e 2.66 95.5 275 -

-

0

9().00

 EE-RM/STD-01-350 COMMENT 164

Table H.3.75 Condensing Two-Stage Non-Weatherized Gas Furnaces at 60 Btu/h 2000 

CFM 

O:lndensi ng T \i\O-Stage 

60 kBtulh 2000 CFM 

Hgh LoN .Air 

rvbdeIs Hgh LoN Hgh LoN CFM CFM BiCMer fvbI:or Sp3ed &1W AFUE Eae PE A-e- Past- Or-Delay at-Delay Inrut Inrut 0Jtput 0Jtput Size Size Taps rue! purge purge 0.5 0.5 f:>rea 

FG6TCXX:lO*-VS 40 55 37 520 1240 7fJJ 11 x 10 314 VaiaI:Je 2.fJJ 92.1 520 123 30 30 30 120.00 

FG3Tl.06O'"-VS 40 55 37 404 1240 7fJJ 11x10 314 VaiaI:Je 2.fJJ 90 404 127 30 30 30 120.00 

Table H.3.76 Condensing Two-Stage Non-Weatherized Gas Furnaces at 70 Btu/h 1200 

CFM 

O:lndensing T V\O-Stage 

70 kBtulh 1200 CFM 

Hgh LoN .Air 

rvbdeIs Hgh LON Hgh LON CFM CFM BiCMer fvbI:or Sp3ed &1W~ flfUE Eae PE A-e- Past- Or-celay at-celay Inrut Inrut a.rtrut 0Jtput Size Size Taps rue! purge purge 0.5 0.5 ftrf£j 

831 rvP11-368-070-* 45 61 43 301 900 865 10x8 1/2 VaiaI:Je 2.28 94.1 301 59 

PMv'90703BX 48 65 46.4 275 VaiaI:Je 1.73 93 275 86 

Table H.3.77 Condensing Two-Stage Non-Weatherized Gas Furnaces at 70 Btu/h 1600 

CFM 

O:>ndensing T V\O-Stage 

70 kBtulh 1600 CFM 

Hgh LoN .Air 

rvbdeIs Hgh LoN Hgh LoN CFM CFM BlCMer MJtor Sp3ed &1W AFUE Eae PE A-e- Past- Or-Delay at-Delay Inrut Inrut 0Jtput a.rtrut Size Size Taps ruet purge purge 0.5 0.5 ftrf£j 

AOJ9J704CX 48 65 45 225 1318 915 10x10 314 VaiaI:Je 2.33 93.3 225 100 

PMv'90704CX 48 67 46.4 275 1325 920 10x10 314 VaiaI:Je 2.30 95.5 275 86 

WJNJ70""4O 48 65 45 225 1318 915 11 x9 314 VaiaI:Je 1.89 93.3 225 100 10 15 30 90.00 

GlNNJ70*X4O 48 67 46.4 275 1325 920 11x9 314 VaiaI:Je 2.66 95.5 275 86 10 15 30 90.00 

H-46 
Table 13.3.78 Condensing Two-Stage Non-Weatherized Gas Furnaces at 75 Btu/h 1200

CFM

C ndensing Two-Ste

75 kBtu/h 1200 CFM

odels Figh Low High Low

High

CFM

Low

CFM

Baaer Motor Speed

Air

`may RE ae E

Pre_ post- rrDelay ff--Delay Input lr ut OutW Output 0.5 0.5 Size Size Taps Cutlet trge purge

Area

RGFD-07(E,"MD(S** 30 70 28 404 995 430 11 x7 1/2 Viable 2.27 92.9 404 118

RGC-D07(E,MMCKS 30 72 27.6 441 995 430 11x7 1/2 Variable 2.29 92.4 441 25

T9NPd075F12** 52.5 70 49.8 314 990 595 11x10 1 Variable 2.26 92.1 314 14 140.00

Table H.3.79 Condensing Two-Stage Non-Weatherized Gas Furnaces at 75 Btu/h 1600

CFM Condensing Two-Stage

Condensing Two-Stage

75 kBt Vh 1600 CFM

odels High Low High Low

High

CFM

Low

CFM

Boner Motor qoead

Air

S p> y RE ae E

PrePoet_ rrDeley ff-Delay Input Ir put Output Output 0.5 0.5 Sze Size Taps Outlet purge purge

Area

RGFD.07(E,"MCKS** 30 70 28 404 995 430 11x7 1/2 Variable 227 929 404 118

R0007(E,I)MCKS 30 72 27.6 441 995 430 11x7 1/2 Variable 229 92.4 441 125

T9M:%Q75F12** 52.5 70 49.8 314 990 11 x 10 1 Variable 2.26 921 314 114 3 5 30 140.00

Table H.3.80 Condensing Two-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 1200

CFM

Condensing Twa-Stage

80 kRu/h 1200 CFM

High LOW Air

Models High

I t

Lav

I

High

C

Low CFM CFM Bow Moor Speed Suppl AFUE Eae PE Re PbSt- Cn Delay Off-Delay npu nput utput Output 0.5 0.5 Size Size Taps Cutlet purge purge

Area

Pv96121W80uP11 52 75 49 184 1330 880 11x8 1/2 Variable 226 92.5 184 69

TDY080I V3W* 52 74 49 332 1220 1000 10x8 1/2 Variable 2.21 92.5 332 67 0 5 45 100.00

TU D80R9V3W* 52 73 49 265 1400 1000 10x8 1/2 Variable 2.21 92.5 265 61 0 5 45 100.00

 EE-RM/STD-01-350 COMMENT 164

Table H.3.78 Condensing Two-Stage Non-Weatherized Gas Furnaces at 75 Btu/h 1200 

CFM 

OJndensing T 'AO-Stage 

75 kBtulh 1200 CFM 

Hi~ LoN Air 

MJdeIs High LoN High LoN CFM CFM BiCMer MJlcr Sj:Eed SJppy .AFlE Eae PE Pre- Fbst- Or-Oliay at-Oliay Input Input 0Jtput C\.Jtpu! Size Size Taps a.rtIet pu-ge purge 0.5 0.5 /:>rea 

RGfD.07(E,N)rvcKS*' 30 70 28 404 995 430 11 x7 1/2 Varialle 2.27 92.9 404 118 

R0C007(E,N)rv'CKS 30 72 27.6 441 995 430 11 x7 1/2 Varialle 2.29 92.4 441 125 

T9I'vPJ075F12'* 52.5 70 49.8 314 990 595 11 x 10 1 Varialle 2.26 92.1 314 114 3 5 30 140.00 

Table H.3.79 Condensing Two-Stage Non-Weatherized Gas Furnaces at 75 Btu/h 1600 

CFM Condensing Two-Stage 

OJndensing T 'AO-Stage 

75 kBtulh 1600 CFM 

Hi~ LoN Air 

MJdeIs High LoN Hi~ LoN CFM CFM BiCMer MJlcr Sj:Eed 9Jppy .AFlE Eae PE Pre- Fbst- Or-Oliay at-Oliay Input Input 0Jtput 0Jtput 0.5 0.5 Size Size Taps a.rtIet purge purge 

!>rea 

RGfD.07(E,N)rvn<S** 30 70 28 404 995 430 11 x7 112 Varialle 227 929 404 118 

R0C007(E,N)rv'CKS 30 72 27.6 441 995 430 11 x7 112 Varialle 229 92.4 441 125 

T9I'vPJ075F12'* 52.5 70 49.8 314 990 595 11 x 10 1 Varialle 2.26 921 314 114 3 5 30 140.00 

Table H.3.80 Condensing Two-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 1200 

CFM 

Cmdensing T'AO-Stage 

80 kBtulh 1200 CFM 

Hi~ LoN Air 

MJdeIs Hi~ LoN Hi~ LoN CFM CFM BiCMer MJlcr Sj:Eed SJpp J\FUE Eae PE Fre- Fbst- Or-Oliay at-Oliay Input Input 0Jtput OJtput Size Size Taps a.rtIet purge purge 0.5 0.5 !>rea 

Pv'9B12NJ8OUP11 52 75 49 184 1330 880 11 x8 1/2 Varialle 226 92.5 184 69 

TDY080R9V3W' 52 74 49 332 1220 1000 10x8 1/2 Varialle 2.21 92.5 332 67 0 5 45 100.00 

nJY08ORlV3W 52 73 49 265 1400 1000 10x8 1/2 Varialle 2.21 92.5 265 61 0 5 45 100.00 

H-47 
Table H.3.81 Condensing Two-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 1600

CFM

Condensing Two-Stage

80 kBtu/h 1600 CM

xlels Hgh Low Hgh Lana Hgh

CFM

Lana

CFM Blow Motor Speed

Pir

Supply

FLE ae

Pre- Pbstr-Delay ff--Delay Input Input Output Output 0.5 0.5 Size Size Taps Outlet purge tu'ge

Area

G2D95B3080V16C-1 56 76 250 1248 907 12x 10 3/4 Variable 2.50 94.5 250 127

G2D95BT080V16G1 64 76 250 1248 907 12x10 3(4 Variable 2.72 94.5 250 127 15 15 30 120.00

Pv9C16r10801P11 52 75 136 1490 990 11x10 3,4 Variable 2.74 92.8 136 81

Table H.3.82 Condensing Two-Stage Non-Weatherized Gas Furnaces at 80 Btu/h 2000

CFM

Condensing Two-Stage

80 kBtu/h 2000 CFM

A r

M d l Hgh L= Hgh Low ligh Loon Glover Nbtor Speed Supply Pre- Posto e s

Input Input Output Output CFM CFM Size Size Taps Outlet AFUE Eae PE

purge purge

Delay Of Delay

0.5 0.5 Area

58MVP080 20 52 75 49 103 1500 675 11x10 1 Variable 2.56 94.1 103 31 25 15 35 120.00

58MVP08020* 52 75 49 110 1 500 675 11x10 1 Variable 2.56 92.7 110 31 25 15 35 120.00

58MVP080 20` 52 75 49 105 1500 675 11x10 1 Variable 2.56 93.7 105 31 25 15 35 120.00

FG6TC080*-VB 48 74 44 321 1240 750 11x10 3/4 Variable 2.50 92.1 321 136 30 30 30 120.00

FC6TL080*-VB 48 74 44 477 1240 750 11x10 3/4 Variable 2.50 90 477 136 30 30 30 120.00

G2D9580080V20G1 56 76 280 1332 932 12 x 10 1 Variable 2.50 94.5 280 133

G2D958T080V20G1 64 76 280 1332 932 12x10 1 Variable 2.72 94.5 280 133 15 15 30 120.00

G2D95BT080V20Q1 64 76 280 12x10 1 Variable 2.72 94.5 280 133 15 15 30 120.00

G2D95BU080V16G1 64 76 250 1248 907 12 x 10 34 Variable 2.50 94.5 250 127

G2D95BW80V20D1 64 76 280 1332 932 12x 10 1 Variable 2.50 94.5 280 133

Table H.3.83 Condensing Two-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 1200

CFM

Condensing Two-Stage

90 kBtu/h 1200 CFM

Mxlels Hgh

Input

Low

Input

High

Output

Law

Output

1361MA/-36G090-* 1 60 1 79 57 367

Hgh

CFM

0.5

925

Lane

CFM

0.5

860

Siang'

Size

10x10

Moor

Size

1/2

Speed

Taps

Variable

Air

Supp1

Cutlet

Area

2.76

AFUE

94.3

Eae PE

65

Prepurge

Postpurge

On-Delay Cff-Delay

 EE-RM/STD-01-350 COMMENT 164

Table H.3.S1 Condensing Two-Stage Non-Weatherized Gas Furnaces at SO Btu/h 1600 

CFM 

ili1densing T \fI.O-Stage 

80 kBtulh 1600 CFM 

High LoN )\ir 

M:xleIs High LoN High LoN CFM CFM SCMe!" I'vticr S!:BOO &.pf:Iy ftFUE Eae PE A-e- R::st- Ol-celay Of-celay If1XIl Input UJtput OJtput Size Size Tap:; rue! purge purge 0.5 0.5 hea 

G2COO3COOOV16C-1 56 76 250 1248 007 12x10 3'4 Varialle 2.50 94.5 250 127 

G2I:B58TIJOOV16C-1 64 76 250 1248 007 12x10 3'4 Varialle 2.72 94.5 250 127 15 15 30 120.00 

Pv9C161\OOOUP11 52 75 49 136 1490 900 11 x10 3'4 Varialle 2.74 92.8 136 81 

Table H.3.S2 Condensing Two-Stage Non-Weatherized Gas Furnaces at SO Btu/h 2000 

CFM 

Condensing T \fI.O-Stage 

80 kBtu/h 2000 CFM 

High Low )\ir 

M:xleIs High Low High LoN CFM CFM B/O'Mlr M:l!cr Speed Supply AFUE Eae PE Pre- Pos!- Ol-Delay Of-Delay Input Input OJtput OJtput Size Size Tap:; rue! purge purge 0.5 0.5 hea 

58MVP080-2O 52 75 49 103 1500 675 11 x 10 1 Variable 2.56 94.1 103 31 25 15 35 

58MVP080-20* 52 75 49 110 1500 675 11 x 10 1 Variable 2.56 92.7 110 31 25 15 35 

58MVP080-2O** 52 75 49 105 1500 675 11 x10 1 Variable 2.56 93.7 105 31 25 15 35 

FG6TCOBO*-VB 48 74 44 321 1240 750 11 x10 3'4 Variable 2.50 92.1 321 136 30 30 30 

FG6TLOBO*-VB 48 74 44 477 1240 750 11 x 10 3'4 Variable 2.50 00 477 136 30 30 30 

G2D95BCOBOV2OC-1 56 76 280 1332 932 12x 10 1 Variable 2.50 94.5 280 133 

G2D95BTOBOV2QC.1 64 76 280 1332 932 12x10 1 Variable 2.72 94.5 280 133 15 15 30 

G2D95BTOBOV20[)'1 64 76 280 12x 10 1 Variable 2.72 94.5 280 133 15 15 30 

G2D95BUOBOV16C-1 64 76 250 1248 007 12x 10 3'4 Variable 2.50 94.5 250 127 

G2D95BUOBOV20[)'1 64 76 280 1332 932 12x 10 1 Variable 2.50 94.5 280 133 

Table H.3.S3 Condensing Two-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 1200 

CFM 

Condensing T\fI.O-Stage 

90 kBtulh 1200 CFM 

High LoN )\ir 

120.00 

120.00 

120.00 

120.00 

120.00 

120.00 

120.00 

M:xleIs High LoN High LoN CFM CFM SCMe!" I'vticr S!:BOO &.pf:I AFUE Eae PE A-e- R::st- Ol-celay Of-celay If1XIl Input UJtput UJtput Size Size Tap:; rue! purge purge 0.5 0.5 />rea 

G61 fvPv'-36C-QOO. * 60 79 57 367 925 860 10x 10 1/2 Varialle 2.76 94.3 367 65 

H-48 
Table H.3.84 Condensing Two-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 1600

CFM

Caxb^ng T

90 kBtu/h 1600 CFM

Models

AMv90904CJ(

Hgh

64

Lane

Irxut

87

Fib

Cuput

61.7

Law

Output

333

Hgh

CFM

0.5

LON

CFM

0.5

Blaney

Sze

Motor

Size Speed Taps

Variable

Air

aY

O llet

Area

230

Ead FbstPurge

97

Ch-E)day Off-Delay

Table H.3.85 Condensing Two-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 2000

CFM

Condensing Tm-Stage

90 kBtu/h 2000 CFM

ligh Law Air

Models I-gh Law ligh Law CFM CFM Blanc- Motor Speed Supply AFUE Eae PE Pre- Post- Can-Delay Of-Delay Input Input Output Output 0.5 0.5 Size Sze Taps Outlet purge purge

Area

G61MI\/-60G090-" 60 82 55 726 1490 1360 1.5x1 1 Variable 276 94.6 726 67

G61 FvW 60C090-* 60 82 55 726 1490 1375 11.5x 1 1 Variable 276 94.6 726 67

G61MPV-60G09P 60 82 55 726 1525 1395 1.5x 1 1 Variable 276 94.6 726 67

F43FD-09(F,NJ)ZCMS"* 36 85 33 386 1195 515 12x7 1 Variable 276 94.1 386 123

RGGD-09(E,N)ZCMS 36 85 33.264 492 1195 515 12x11 1 Variable 278 922 492 119

ACV90905DX 64 87 60.1 374 1706 1185 11x10 1 Variable 278 927 374 97

AMv90905DX 64 90 61.7 333 1721 1195 11x10 1 Variable 2.86 95.7 333 92

FG5TC092*-VB 55 84 50 514 1240 750 11x10 3/4 Variable 250 921 514 70 30 30 30 120.00

F65TL0922-VB 55 84 50 525 1240 750 11x10 3/4 Variable 250 90 525 70 30 30 30 120.00

GGVA090 50 64 87 60.1 374 1706 1185 11 x 10 1 Variable 2.41 927 374 97 10 15 30 90.00

GUVPD9O*X50 64 90 61.7 333 1721 1195 11 x 10 1 Variable 3.22 95.7 333 92 10 15 30 90.00

Table 11.3.86 Condensing Two-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 1600

CFM

Condensing Tm-Stage

1 00 kBtu/h 1600 CFM

Air

Models Figh Law ugh Law CFM CFM

Bow Motor Speed Supply ARE Eae PE Fre- Post OrrDday Off-Delay Ir put Input Output Output 0.5 0.5 Size Size Taps Cutlet Purge purge

Area

CDX1-100N 75 94 69.75 320 1340 1094 314 Variable 238 93 320 97 30 5 45 120.00

CF-D(1 -100N 70 95 66.15 340 1243 1015 314 Variable 238 94.5 340 95 30 5 45 120.00

TDY103F62f4W 65 94 62 484 1650 1172 10x10 314 Variable 269 93 484 66 0 5 45 100.00

TX190I /4W 65 93 62 452 1690 , 1165 10x10 314 Variable 269 , 93 452 , 69 0 5 45 100.00

 EE-RM/STD-01-350 COMMENT 164

Table H.3.84 Condensing Two-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 1600 

CFM 

Ccndensing TV\O-Stage 

00 kBtu'h 1ffX) aM 

Hg, lDN Ar 

M:x:IeIs Hg, lDN Hg, lDN CFM CFM BCMer IVticr ~Tcp> s.wy JlFLE I Ere FE Fre- Ft6t- Ol-D3Iay Of-D3Iay IrpJ IrpJ OJIpLt 0Jtpl1 Sze Sze rue! p.rge p.rge 0.5 0.5 ftrea 

PJ'vMID)4()( 64 fIT 61.7 333 Vaialle 2.30 93 333 W 

Table H.3.85 Condensing Two-Stage Non-Weatherized Gas Furnaces at 90 Btu/h 2000 

CFM 

Condensing T VI.O-Stage 

00 kBtu/h 2000 CFM 

High lDN Ar 

M:JdeIs High lDN Hgh LoN CFM CFM BiCMer M:J!or Speed SUWly AFUE Eae PE Pre- Pos!- Ol-Delay Off-Delay InpLt InpLt o.rtput QrtpLt 0.5 0.5 Size Size Taps Qrtle! purge purge 

Nea 

G61 rvPV-6QC.OOO-* 60 82 55 726 1400 1360 1.5 x 1 1 Vaiable 2.76 94.6 726 67 

G61 rvPV-6QC.OOO-* 60 82 55 726 1400 1375 1.5 x 1 1 Variable 2.76 94.6 726 67 

G61 rvPV-6OG-OOO-* 60 82 55 726 1525 1395 1.5x1 1 Variable 2.76 94.6 726 67 

RGFD-09(E,N)ZCMS** 36 85 33 386 1195 515 12x7 1 Variable 2.76 94.1 386 123 

RGGD-09(E,N)ZCMS 36 85 33.264 492 1195 515 12x 11 1 Variable 2.78 92.2 492 119 

ACV00905DX 64 87 60.1 374 1700 1185 11 x10 1 Variable 2.78 92.7 374 97 

ArvMm05DX 64 90 61.7 333 1721 1195 11 x10 1 Variable 2.86 95.7 333 92 

FG6TCXJ92* -\113 55 84 50 514 1240 750 11 x10 314 Variable 2.50 92.1 514 70 30 30 30 120.00 

FG61L092' -\113 55 84 50 525 1240 750 11 x 10 314 Variable 2.50 90 525 70 30 30 30 120.00 

OOVNEJ**50 64 87 60.1 374 1700 1185 11 x10 1 Variable 2.41 92.7 374 97 10 15 30 90.00 

GlNNEJ*X50 64 90 61.7 333 1721 1195 11 x10 1 Variable 3.22 95.7 333 92 10 15 30 90.00 

Table H.3.86 Condensing Two-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 1600 

CFM 

C01densing T VI.O-SI:age 

100 kBtu'h 1ffX) CFM 

Hg, lDN Ar 

M:JdeIs Hg, lDN Hgh LoN CFM CFM BCMer lVtior ~ SUj:py AFUE Ere FE Fre- Ft6t- Ol-Delay Of-D3Iay IrpJ IrpJ 0Jtpl1 0Jtpl1 0.5 0.5 Sze Sze Taps rue! p.rge purge 

Nea 

aJX1-100N 75 94 69.75 320 1340 1094 314 Varialle 2.38 93 320 97 30 5 45 120.00 

Q-lX1-100N 70 95 ffi.15 340 1243 1015 314 Varialle 2.38 94.5 340 95 30 5 45 120.00 

IDY1r::J:RN4W 65 94 62 484 1650 1172 10x10 314 Varialle 2.69 93 484 00 0 5 45 100.00 

TlJY1r::J:RN4W 65 93 62 452 1690 1165 10x10 314 Varialle 2.69 93 452 69 0 5 45 100.00 

H-49 
Table H.3.87 Condensing Two-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 2000

CFNI

Condensing Tvw-Stage

100 kBtu/h 2000 CFM

Air High Low FGgh Law High Low Blamer Motor Speed Supply Pre- Post- Models CFM CM AFUE Eae PE On-Delay Off Delay Input Input Output Output 0.5 0.5 Size Size Taps Outlet purge purge

Area

58M'P100-20 65 94 61 225 1520 920 11 x 10 1 Variable 2.56 94.1 225 32 25 15 35 120.00

58MVP100.20* 65 94 61 245 1520 920 11 x 10 1 Variable 2.56 92.7 245 33 25 15 35 120.00

58MVP100-20*` 65 93 61 167 1520 920 11x10 1 Variable 2.56 93.7 167 31 25 15 35 120.00

G2D95BC100V20D-1 70 95 280 1565 1045 12 x 10 1 Variable 2.95 94.5 280 143

G2D95BC125V20D-1 87.5 118 370 2019 1321 12 x 10 1 Variable 2.95 94 370 142

G2D95BT100V20C-1 80 95 280 1565 1045 12x10 1 Variable 2.72 94.5 280 143 15 15 30 120.00

G2D95BT100V20D-1 80 95 280 12x10 1 Variable 2.72 94.5 280 143 15 15 30 120.00

G2D95BU100V20D-1 80 95 280 1565 1045 12 x 10 1 Variable 2.95 94.5 280 143

Pv9C20N1000P11 65 93 60 194 1880 1230 11x11 1 Variable 2.74 92.8 194 82

T9MPV100J20`" 70 93 65.8 401 1400 830 11 x 10 1 Variable 2.73 92.1 401 136 3 5 30 140.00

RGFD•10(E,N)ZCMS'* 42 97 39 714 1395 600 12x7 I Variable 2.76 92 714 109

RGGD-10(E,N)ZCMS 42 99 38.346 692 1395 , 600 12x11 I Variable 2.78 91.2 692 102

Table H.3.88 Condensing Two-Stage Non-Weatherized Gas Furnaces at 115 Btu/h 2000

CFM

Condensing Two-Stage

115 kBtu/h 2000 CFM

Air Hgh Low

Models ligh Low Figh Low CCFM CFM Blamer Motor Speed Supply AFUE E PE Pre- Post- O D l Off D l

Irput Input Output Output Size Size Taps Outlet aepurge purge

n- e ay -- e ay

0.5 0.5 Area

FG6TC110*-VC 74 100 68 517 1680 1220 11x10 3/4 Variable 2.88 921 517 70 30 30 30 120.00

F00TL110*-VC 74 100 68 874 1680 1220 11x10 3/4 Variable 2.88 90 874 130 30 30 30 120.00

001Ma/-60G110•' 75 99 72 542 1545 1435 1.5x1 1 Variable 276 94.3 542 66

G61M'V-60C-110-' 75 99 72 542 1510 1380 1.5 x l 1 Variable 276 94.3 542 66

001 M'V-60G11 V 75 99 72 542 1510 1400 1.5 x 1 1 Variable 276 94.3 542 66

AMv91155DX 80 109 77.4 397 1822 1265 11x10 1 Variable 2.86 95.8 397 90

GWA115`X50 80 109 , 77.4 397 1822 , 1265 11x10 1 Variable 3.22 95.8 397 90 10 15 30 90.00

 EE-RM/STD-01-350 COMMENT 164

Table H.3.87 Condensing Two-Stage Non-Weatherized Gas Furnaces at 100 Btu/h 2000 

CFM 

Condensing T\M)-Stage 

100 kBtu/h 2000 CFM 

High Low Air 

tvbdels High Low High Low CFM CFM BiCMer I'vbtor Speed Supply AFUE Eae PE Pre- Post- O1-Delay Off-Delay Input Input OJtput OJtput Size Size Taps 0Jt1e! purge purge 0.5 0.5 hea 

58MVP100-20 65 94 61 225 1520 920 11 x 10 1 Variable 2.56 94.1 225 32 25 15 35 120.00 

58MVP100-20* 65 94 61 245 1520 920 11 x 10 1 Variable 2.56 92.7 245 33 25 15 35 120.00 

58MVP100-20~ 65 93 61 167 1520 920 11 x 10 1 Variable 2.56 93.7 167 31 25 15 35 120.00 

G2D95BC100V2OD-1 70 95 280 1565 1045 12x10 1 Variable 2.95 94.5 280 143 

G2D95BC125V2OD-1 87.5 118 370 2019 1321 12x10 1 Variable 2.95 94 370 142 

G2D95BT100V20C-1 80 95 280 1565 1045 12x10 1 Variable 2.72 94.5 280 143 15 15 30 120.00 

G2D95BT100V20D-1 80 95 280 12x10 1 Variable 2.72 94.5 280 143 15 15 30 120.00 

G2D95BU100V20D-1 80 95 280 1565 1045 12x 10 1 Variable 2.95 94.5 280 143 

PV9C2ON100UP11 65 93 60 194 1880 1230 11 x 11 1 Variable 2.74 92.8 194 82 

T9I'vPV100J20~ 70 93 65.8 401 1400 830 11 x 10 1 Variable 2.73 92.1 401 136 3 5 30 140.00 

RGFD-10(E,N}ZavIS'* 42 97 39 714 1395 600 12x7 1 Variable 2.76 92 714 109 

RGGD-10(E,N)ZCMS 42 99 38.346 692 1395 600 12x11 1 Variable 2.78 91.2 692 102 

Table H.3.88 Condensing Two-Stage Non-Weatherized Gas Furnaces at 115 Btu/h 2000 

CFM 

Condensing T\M)-Stage 

115 kBtu/h 2000 CFM 

High Low Air 

M:x:leIs High Low High Low CFM CFM BiCMer I'vbtor Speed Supply AFUE Eae PE Pre- Pest- Ol-Delay at-Delay Input Input 0Jtput OJtput 0.5 0.5 Size Size Taps rue! purge purge 

hea 

FG6TC110*-VC 74 100 68 517 1660 1220 11 x 10 314 Variable 2.88 921 517 70 30 30 30 120.00 

FG6TL 110*-VC 74 100 68 874 1660 1220 11 x 10 314 Variable 2.88 90 874 130 30 30 30 120.00 

G61 f\1F\1-6OC-11 Q. * 75 99 72 542 1545 1435 1.5x1 1 Variable 276 94.3 542 66 

G61 f\1F\1-6OC-11 Q. * 75 99 72 542 1510 1380 1.5 x 1 1 Variable 276 94.3 542 66 

G61 f\1F\1-6OC-11 Q. * 75 99 72 542 1510 1400 1.5 x 1 1 Variable 276 94.3 542 66 

AMv91155DX 80 109 77.4 397 1822 1265 11 x 10 1 Variable 2.66 95.8 397 90 

GlNA115*X50 80 109 77.4 397 1822 1265 11 x10 1 Variable 3.22 95.8 397 90 10 15 30 90.00 

H-50 
Table 13.3.89 Condensing Two-Stage Non-Weatherized Gas Furnaces at 120 Btu/h 2000

CFNI

Condensing Two-Stage

120 kBtu/h 2000 CFM

High Low A r

Models High Low High Low CFM CFM Blovaer Motor Speed Suppl AF Eae PE Pre- Post- On-Delay Off-Delay Input Input Output Output 0.5 0.5 Size Size Taps Outlet E purge purge

Area

58MMP120-20 78 113 73 258 1885 1180 11 x10 3/4 Variable 3.02 94 258 34 25 15 35 120.00

58MVP120-20* 78 113 73 272 1885 1180 11x10 3/4 Variable 3.02 93 272 33 25 15 35 120.00

58MVP120-20** 78 112 73 266 1885 1180 11x10 3/4 Variable 3.02 94 266 32 25 15 35 120.00

PV9D20N120UP11 78 112 73 422 2150 1420 11 x11 1 Variable 3.23 93 422 85

RGFD-12(E,N)RCMS** 48 112 45 836 1595 685 11 x10 1 Variable 3.25 93 836 130

RGGD-12(E,N)RCMS 48 113 44.352 671 1595 685 11 x 10 1 Variable 3.26 92 671 126

TDY120R9V5W* 78 112 74 555 1850 1350 10x10 1 Variable 3.17 93 555 90 0 5 45 100.00

TUY120R9V5W* 78 112 74 550 1850 1370 10x101 1 Variable 3.17 93 550 74 0 5 45 100.00

Table H.3.90 Condensing Two-Stage Non-Weatherized Gas Furnaces at 125 Btu/h 2000

CFM

Condensing Tw-Stage

125 kBtu/h 2000 CFM

High Low Air

Models High Low High Low CFM OFM Blow Motor Speed Supply AFUE Eae PE Pre- Post- On-Delay Off-Delay Input Input Output Output Sim Size Taps Outlet purge purge 0.5 0.5

Area

CHX1-125N 93.8 117 82.25 359 1556 1270 1 Variable 275 94 359 97 30 5 45 120.00

G2D95BT125V20C-1 100 118 370 2019 1321 12x10 1 Variable 272 94 370 142 15 15 30 120.00

G2D95BT125V20D-1 100 118 370 12x10 1 Variable 3.19 94 370 142 15 15 30 120.00

G2D95BU125V20D-1 100 118 370 2019 1321 12x10 1 Variable 2.95 94 370 142

T9MPV125L20** 87.5 118 82.25 328 1750 12€0 11x10 1 Variable 295 92.1 328 87 3 5 30 140.00

G61MPv-60D-1352" 90 122 87 569 1455 1355 1.5x 1 1 Variable 3.24 94.6 569 68

G61 NE's/-60D 1352* 90 122 87 569 1440 1325 11.5x 1 1 Variable 3.24 94.6 569 68

681MPV-60D.135-* 90 122 87 569 1535 1380 1.5x1 1 Variable 3.24 94.6 569 68

 EE-RM/STD-01-350 COMMENT 164

Table H.3.89 Condensing Two-Stage Non-Weatherized Gas Furnaces at 120 Btu/h 2000 

CFM 

Condensing T\AO-Stage 

120 kBtU/h 2000 CFM 

High LON Air 

M:xJels High Low High LON CFM CFM BitMer fvbtor Speed Suppl AFU Eae PE Pre- Post- Ol-Delay Off-Delay Input Input Output Output 0.5 0.5 Size Size Taps Outlet E purge purge 

Area 

58MMP120-20 78 113 73 258 1885 1180 11 x10 3/4 Variable 3.02 94 258 34 25 15 35 120.00 

58MVP120-20* 78 113 73 272 1885 1180 11 x 10 314 Variable 3.02 93 272 33 25 15 35 120.00 

58MMP120-20** 78 112 73 266 1885 1180 11 x 10 314 Variable 3.02 94 266 32 25 15 35 120.00 

PV9D2ON120UP11 78 112 73 422 2150 1420 11 x 11 1 Variable 3.23 93 422 85 

RGFD-12(E,N)RCMS** 48 112 45 836 1595 685 11 x10 1 Variable 3.25 93 836 130 

RGGD-12(E,N)RCMS 48 113 44.352 671 1595 685 11 x 10 1 Variable 3.26 92 671 126 

TDY120R9V5W' 78 112 74 555 1850 1350 10x 10 1 Variable 3.17 93 555 90 0 5 45 100.00 

l1JY120R9V5W' 78 112 74 550 1850 1370 10x 10 1 Variable 3.17 93 550 74 0 5 45 100.00 

Table H.3.90 Condensing Two-Stage Non-Weatherized Gas Furnaces at 125 Btu/h 2000 

CFM 

Condensing T \ID-Stage 

125 kBtu/h 2000 CFM 

High Low Air 

M:JdeIs High LON High Low CFM CFM BiCMer Motor Speed Suppl, AiFUE Eae PE Pre- Post- Ol-Delay Off-Delay Input Input Output Output 0.5 0.5 Size Size Taps Outlet purge purge 

Area 

CHX1-125N 93.8 117 82.25 359 1556 1270 1 Variable 275 94 359 97 30 5 45 120.00 

G2D95BT125V2OC-1 100 118 370 2019 1321 12x10 1 Variable 272 94 370 142 15 15 30 120.00 

G2D95BT125V20D-1 100 118 370 12x10 1 Variable 3.19 94 370 142 15 15 30 120.00 

G2D95BU125v20D-1 100 118 370 2019 1321 12x10 1 Variable 2.95 94 370 142 

T9MPII125L20** 87.5 118 82.25 328 1750 1200 11 x10 1 Variable 295 92.1 328 87 3 5 30 140.00 

G61MFV-60D-135-* 90 122 87 569 1455 1355 1.5x1 1 Variable 3.24 94.6 569 68 

G61 MFV-60D-135-* 90 122 87 569 1440 1325 1.5x1 1 Variable 3.24 94.6 569 68 

G61MFV-60D-135-* 90 122 87 569 1535 1380 1.5 x 1 1 Variable 3.24 94.6 569 68 

H-Sl 
REFERENCES

Gas Appliance Manufacturers Association (GAMA), GAMA Directory March 2005,

2005. (Last accessed March, 2005.)

<<http://www. gamanet. org/gama/inforesources.nsf/vAllDocs/Product+Directories?Open

Document>>

 EE-RM/STD-01-350 COMMENT 164

REFERENCES 

1. Gas Appliance Manufacturers Association (GAMA), GAMA Directory March 2005, 

2005. (Last accessed March, 2005.) 

< <http://www . gamanet.orgl gama/inforesources.nsf/v AllDocs/Product+ Directories ?Open 

Document» 

H-52