### Instructionsfor Completing the Process Data Template

This template is to be used to record the 30 daily averages of specific process data required by the ICR. The ERT does not have the capability to store these daily averages. This spreadsheet included 4 separate surrogate worksheets,in case the boiler tested is tested for all surrogates at 4 different dates.This spreadsheet is intended to be used for one boiler of one facility.Data for multiple boilers should be handled by using separate copies of this spreadsheet. yelloware required (if applicable to your boilers' operation). You do not need to populate cells shaded in gray, as they ar automaticallypopulated from the Boiler Information worksheet. Please Do Not modify the structure of this spreadsheet by adding or subtracting rows, columns, cells. Please name each resulting spreadsheet with the following naming

convention:[FacilityID]_Unit_[BoilerID]_Processdata.xls(example: 8100_Unit_2_Processdata.xls).

Please refer to the following steps when using these spreadsheets.

BoilerInformation Worksheet

Pleaseenter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Informationworksheet.

ProcessData Worksheets

Pleaseuse one process data worksheetfor each HAP surrogate even is simultaneous testing of different HAP surrogates was done.

### Instructionsfor Completing the Process Data Template

This template is to be used to record the 30 daily averages of specific process data required by the ICR. The ERT does not have the capability to store these daily averages. This spreadsheet included 4 separate surrogate worksheets,in case the This spreadsheet is intended to be used for one boiler of one facility.Data for multiple boilers should be handled by using separate copies of this spreadsheet. Fields shaded in yelloware required (if applicable to your boilers' operation). You do not need to populate cells shaded in gray, as they are Please Do Not modify the structure of this spreadsheet Please name each resulting spreadsheet with the following naming

convention:[FacilityID]_Unit_[BoilerID]_Processdata.xls(example: 8100_Unit_2_Processdata.xls).

Pleaseenter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Informationworksheet.

Pleaseuse one process data worksheetfor each HAP surrogate even is simultaneous testing of different HAP surrogatesEIA

Facility Code Facility Name Boiler ID

963 Dallman 31.32EIA

Facility Code Facility Name Boiler ID

963 Dallman 31.32

Daily A verage Process Data for a 30 Day Period Including the Testing Date Date Coal Firing Rate Coal Firing Rate (units) Fuel oil Firing Rate Day 1 3/15/2010 835 Tons/day 5260 Day 2 3/16/2010 792 Tons/day 3296 Day 3 3/17/2010 1686 Tons/day 0 Day 4 3/18/2010 1596 Tons/day 0 Day 5 3/19/2010 1568 Tons/day 0 Day 6 3/20/2010 1664 Tons/day 0 Day 7 3/21/2010 1550 Tons/day 606 Day 8 3/22/2010 1644 Tons/day 114 Day 9 3/23/2010 1605 Tons/day 82 Day 10 3/24/2010 1544 Tons/day 0 Day 11 3/25/2010 1554 Tons/day 291 Day 12 3/26/2010 1586 Tons/day 585 Day 13 3/27/2010 1512 Tons/day 753 Day 14 3/28/2010 1637 Tons/day 3323 Day 15 3/29/2010 1639 Tons/day 511 Day 16 3/30/2010 1517 Tons/day 170 Day 17 3/31/2010 1450 Tons/day 2746 Day 18 4/1/2010 774 Tons/day 0 Day 19 4/2/2010 775 Tons/day 0 Day 20 4/3/2010 790 Tons/day 0 Day 21 4/4/2010 766 Tons/day 0 Day 22 4/5/2010 1698 Tons/day 5056 Day 23 4/6/2010 1693 Tons/day 210 Day 24 4/7/2010 1710 Tons/day 0 Day 25 4/8/2010 1618 Tons/day 0 Day 26 4/9/2010 1533 Tons/day 48 Day 27 4/10/2010 800 Tons/day 0 Day 28 4/11/2010 812 Tons/day 0 Day 29 4/12/2010 1603 Tons/day 3472 Day 30 4/13/2010 1713 Tons/day 514Daily A verage Process Data for a 30 Day Period Including the Testing Date Fuel oil Firing Rate (units) Average Heat Input (MMBtu/hr) Unit Net Electric Generation (MWh) Gal/day 821 59 Gal/day 869 62 Gal/day 1606 125 Gal/day 1540 120 Gal/day 1514 118 Gal/day 1601 125 Gal/day 1477 114 Gal/day 1578 123 Gal/day 1544 120 Gal/day 1486 116 Gal/day 1476 115 Gal/day 1515 118 Gal/day 1441 112 Gal/day 1473 115 Gal/day 1557 121 Gal/day 1450 113 Gal/day 1363 106 Gal/day 730 58 Gal/day 751 58 Gal/day 753 59 Gal/day 757 59 Gal/day 1627 127 Gal/day 1622 127 Gal/day 1637 128 Gal/day 1539 120 Gal/day 1426 110 Gal/day 766 60 Gal/day 771 60 Gal/day 1586 122 Gal/day 1646 128Control Device Operating Parameters, A s Appicable Unit Gross Electric Generation (MWe) Flue Gas Flow Rate (dscfm) 64 248168 67 307321 135 438430 129 426357 127 418334 134 437521 123 414033 132 431787 129 422888 125 415129 124 419929 127 427025 121 409635 124 419532 130 439660 122 420681 115 412151 63 255493 63 246661 64 251258 64 290274 136 458955 136 449040 137 453315 129 429423 118 402180 65 242893 65 269411 131 441585 137 455192Pressure Drop across FGD (in H2O) FGD Scrubber Liquor Flow Rate (gals/min) Sorbent TypeOther Boiler or Control Device Operating Parameters (e.g., Boiler O2)

Sorbent Injection Rate (lb/hr) Flue Gas Pressure (atm)Other Boiler or Control Device Operating Parameters (e.g., Boiler O2)

Flue Gas Sampling Point Temperature (Deg F) Flue Gas Oxygen Content (%) 135 8.9 157 11 131 7.5 131 7.8 130 7.8 130 7.6 132 8 130 7.7 130 7.7 130 7.9 128 8.1 127 7.9 127 8.1 127 8.2 128 8 128 8.4 133 9 138 10.2 127 9.9 125 10 134 11.2 131 8 131 7.9 131 7.9 129 7.9 130 8.1 132 9.3 136 10.1 133 7.8 132 7.6Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%) 9.9 8.1 11 10.8 10.8 11 10.7 10.9 10.9 10.7 10.5 10.6 10.5 10.5 10.6 10.3 9.8 8.6 9.1 9 8 10.6 10.8 10.8 10.7 10.5 9.5 8.8 10.7 10.8