Instructions for Completing the Process Data Template

This template is to be used to record the 30 daily averages of specific process data required by the ICR. The ERT d

have the capability to store these daily averages. This spreadsheet included 4 separate surrogate worksheets, in 

boiler tested is tested for all surrogates at 4 different dates. This spreadsheet is intended to be used for one boi

facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet.

yellow are required (if applicable to your boilers' operation). You do not need to populate cells shaded in gray, a

automatically populated from the Boiler Information worksheet. Please Do Not modify the structure of this spr

by adding or subtracting rows, columns, cells. Please name each resulting spreadsheet with the following nami

convention: [FacilityID]_Unit_[BoilerID]_Processdata.xls (example: 8100_Unit_2_Processdata.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information workshee

Process Data Worksheets

Please use one process data worksheet for each HAP surrogate even is simultaneous testing of different HAP sur

was done. 
ta Template

s data required by the ICR. The ERT does not 

4 separate surrogate worksheets, in case the 

t is intended to be used for one boiler of one 

es of this spreadsheet. Fields shaded in 

d to populate cells shaded in gray, as they are 

Not modify the structure of this spreadsheet 

preadsheet with the following naming 

nit_2_Processdata.xls).

on the Boiler Information worksheet. 

taneous testing of different HAP surrogates 
EIA Facility Code Facility Name Boiler ID

6076 Colstrip Plant 3
EIA Facility Code Facility Name Boiler ID

6076 Colstrip Plant 3

Daily Average Process Data for a 30 Day Period Including the Testing Date

Date 

(MM/DD/YY) Coal Firing Rate (1,000 Tons/hr)

06/01/10 Day 1 0.411

06/02/10 Day 2 0.388

06/03/10 Day 3 0.384

06/04/10 Day 4 0.330

06/05/10 Day 5 0.213

06/06/10 Day 6 0.172

06/07/10 Day 7 0.178

06/08/10 Day 8 0.291

06/09/10 Day 9 0.191

06/10/10 Day 10 0.175

06/11/10 Day 11 0.273

06/12/10 Day 12 0.275

06/13/10 Day 13 0.202

06/14/10 Day 14 0.282

06/15/10 Day 15 0.196

06/16/10 Day 16 0.288

06/17/10 Day 17 0.209

06/18/10 Day 18 0.336

06/19/10 Day 19 0.201

06/20/10 Day 20 0.174

06/21/10 Day 21 0.345

06/22/10 Day 22 0.386

06/23/10 Day 23 0.389

06/24/10 Day 24 0.387

06/25/10 Day 25 0.340

06/26/10 Day 26 0.205

06/27/10 Day 27 0.284

06/28/10 Day 28 0.352

06/29/10 Day 29 0.348

06/30/10 Day 30 0.335

Tons/Hr

06/01/10 Day 1 410.5

06/02/10 Day 2 387.5

06/03/10 Day 3 384.0

06/04/10 Day 4 330.0

06/05/10 Day 5 213.0

06/06/10 Day 6 171.5

06/07/10 Day 7 178.0

06/08/10 Day 8 291.0

06/09/10 Day 9 191.0

06/10/10 Day 10 175.0

06/11/10 Day 11 272.5

06/12/10 Day 12 274.5

06/13/10 Day 13 202.0

06/14/10 Day 14 282.0

06/15/10 Day 15 196.0

06/16/10 Day 16 288.0
06/17/10 Day 17 208.5

06/18/10 Day 18 335.5

06/19/10 Day 19 200.5

06/20/10 Day 20 173.5

06/21/10 Day 21 345.0

06/22/10 Day 22 385.5

06/23/10 Day 23 389.0

06/24/10 Day 24 386.5

06/25/10 Day 25 340.0

06/26/10 Day 26 205.0

06/27/10 Day 27 284.0

06/28/10 Day 28 352.0

06/29/10 Day 29 348.0

06/30/10 Day 30 335.0
od Including the Testing Date

Synfuel Firing Rate (1,000 Tons/hr) Pet Coke Firing Rate (1,000 Tons/hr)

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

Coal Gas Firing Rate (ft^3/min) Fuel oil Firing Rate (Gal/hr) Average Heat Input (MMBtu/hr)

0 0 6401

0 0 6009

0 0 5977

0 0 5113

0 0 3412

0 0 2834

0 0 2936

0 0 4735

0 0 3041

0 0 2863

0 0 4350

0 0 4445

0 0 3173

0 0 4528

0 0 3033

0 0 4691

0 0 3300

0 0 5329

0 0 3020

0 0 2628

0 0 5463

0 0 6097

0 0 6098

0 0 6066

0 0 5368

0 0 3145

0 0 4643

0 0 5603

0 0 5363

0 0 5132

Steam Output (1,000 lbs steam/hr) Flue Gas Flow Rate (dscfm) Flue Gas Pressure (atm)

5,144.84 2,027,800 NA

5,018.41 1,928,000 NA

4,731.49 1,924,200 NA

4,167.47 1,713,100 NA

2,468.29 1,276,800 NA

1,973.21 1,146,300 NA

2,026.28 1,166,300 NA

3,477.68 1,604,800 NA

2,267.87 1,200,600 NA

2,105.75 1,153,400 NA

3,265.01 1,525,500 NA

3,257.42 1,537,000 NA

2,476.23 1,274,200 NA

3,447.91 1,588,500 NA

2,295.88 1,183,600 NA

3,354.98 1,601,300 NA

2,446.95 1,253,400 NA

4,008.83 1,753,100 NA

2,393.21 1,204,000 NA

2,040.74 1,135,900 NA

4,150.27 1,811,900 NA

4,656.11 1,949,200 NA

4,887.64 1,936,400 NA

4,781.54 1,948,900 NA

4,233.28 1,781,900 NA

2,435.10 1,215,200 NA

3,398.00 1,592,800 NA

4,391.61 1,845,500 NA

N/A 1,765,300 NA

N/A 1,743,600 NA

Flue Gas Sampling Point Temperature (Deg F) Flue Gas Oxygen Content (%)

193.5 NA

194.3 NA

195.1 NA

193.3 NA

191.3 NA

191.3 NA

191.3 NA

192.9 NA

191.1 NA

191.7 NA

192.8 NA

192.2 NA

192.0 NA

193.9 NA

188.6 NA

193.7 NA

192.4 NA

194.7 NA

192.2 NA

192.3 NA

195.2 NA

196.4 NA

189.8 NA

195.1 NA

193.9 NA

189.4 NA

189.3 NA

189.8 NA

189.4 NA

189.5 NA

Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)

10.39 15-18%

10.22 15-18%

10.09 15-18%

9.61 15-18%

8.69 15-18%

8.15 15-18%

8.29 15-18%

9.51 15-18%

8.35 15-18%

8.17 15-18%

9.20 15-18%

9.46 15-18%

8.14 15-18%

8.90 15-18%

8.47 15-18%

9.25 15-18%

8.63 15-18%

9.72 15-18%

8.13 15-18%

7.63 15-18%

9.47 15-18%

10.13 15-18%

10.33 15-18%

10.18 15-18%

9.72 15-18%

8.49 15-18%

9.23 15-18%

9.80 15-18%

9.68 15-18%

9.32 15-18%

Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe) Standard Pressure (atm)

667.4 717.4 29.92 "Hg

611.2 661.2 29.92 "Hg

603.0 653.0 29.92 "Hg

502.1 552.1 29.92 "Hg

278.9 328.9 29.92 "Hg

203.7 253.7 29.92 "Hg

214.5 264.5 29.92 "Hg

439.8 489.8 29.92 "Hg

241.1 291.1 29.92 "Hg

232.9 282.9 29.92 "Hg

420.3 470.3 29.92 "Hg

421.4 471.4 29.92 "Hg

254.7 304.7 29.92 "Hg

425.0 475.0 29.92 "Hg

242.3 292.3 29.92 "Hg

427.6 477.6 29.92 "Hg

270.9 320.9 29.92 "Hg

508.6 558.6 29.92 "Hg

255.0 305.0 29.92 "Hg

207.1 257.1 29.92 "Hg

533.0 583.0 29.92 "Hg

599.3 649.3 29.92 "Hg

608.8 658.8 29.92 "Hg

605.6 655.6 29.92 "Hg

526.7 576.7 29.92 "Hg

269.3 319.3 29.92 "Hg

432.9 482.9 29.92 "Hg

551.3 601.3 29.92 "Hg

528.5 578.5 29.92 "Hg

504.1 554.1 29.92 "Hg

Standard Temperature (Deg F) Pressure Drop across FGD (in H2O)

68 25.8

68 25.0

68 24.6

68 22.3

68 15.9

68 14.3

68 13.5

68 20.2

68 13.8

68 13.9

68 18.8

68 18.4

68 15.4

68 20.0

68 15.8

68 21.4

68 17.2

68 22.5

68 14.7

68 13.9

68 22.1

68 21.1

68 21.5

68 20.9

68 22.2

68 13.9

68 18.2

68 21.1

68 21.7

68 21.6

FGD Scrubber Liquor Flow Rate (gals/min) FGD Scrubber Liquor pH (pH) Sorbent Type

NA 5.58 ACI

NA 5.71 ACI

NA 5.84 ACI

NA 5.88 ACI

NA 6.09 ACI

NA 6.25 ACI

NA 6.25 ACI

NA 5.90 ACI

NA 6.33 ACI

NA 6.45 ACI

NA 6.13 ACI

NA 5.93 ACI

NA 6.10 ACI

NA 6.07 ACI

NA 6.15 ACI

NA 5.96 ACI

NA 6.21 ACI

NA 5.86 ACI

NA 6.40 ACI

NA 6.37 ACI

NA 5.98 ACI

NA 6.18 ACI

NA 6.16 ACI

NA 6.09 ACI

NA 5.99 ACI

NA 6.77 ACI

NA 6.36 ACI

NA 6.14 ACI

NA 6.15 ACI

NA 6.04 ACI

Actvated Carbon

Sorbent Injection Rate (lb/hr)

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

ated Carbon
EIA Facility Code Facility Name Boiler ID

6076 Colstrip Plant 3

Daily Average Process Data for a 30 Day Period Including the Testing Date

Date 

(MM/DD/YYYY) Coal Firing Rate (1,000 Tons/hr)

06/01/10 Day 1 0.4105

06/02/10 Day 2 0.3875

06/03/10 Day 3 0.384

06/04/10 Day 4 0.33

06/05/10 Day 5 0.213

06/06/10 Day 6 0.1715

06/07/10 Day 7 0.178

06/08/10 Day 8 0.291

06/09/10 Day 9 0.191

06/10/10 Day 10 0.175

06/11/10 Day 11 0.2725

06/12/10 Day 12 0.2745

06/13/10 Day 13 0.202

06/14/10 Day 14 0.282

06/15/10 Day 15 0.196

06/16/10 Day 16 0.288

06/17/10 Day 17 0.2085

06/18/10 Day 18 0.3355

06/19/10 Day 19 0.2005

06/20/10 Day 20 0.1735

06/21/10 Day 21 0.345

06/22/10 Day 22 0.3855

06/23/10 Day 23 0.389

06/24/10 Day 24 0.3865

06/25/10 Day 25 0.34

06/26/10 Day 26 0.205

06/27/10 Day 27 0.284

06/28/10 Day 28 0.352

06/29/10 Day 29 0.348

06/30/10 Day 30 0.335

Tons/Hr
od Including the Testing Date

Synfuel Firing Rate (1,000 Tons/hr) Pet Coke Firing Rate (1,000 Tons/hr)

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0
Coal Gas Firing Rate (ft^3/min) Fuel oil Firing Rate (Gal/hr) Average Heat Input (MMBtu/hr)

0 0 6401

0 0 6009

0 0 5977

0 0 5113

0 0 3412

0 0 2834

0 0 2936

0 0 4735

0 0 3041

0 0 2863

0 0 4350

0 0 4445

0 0 3173

0 0 4528

0 0 3033

0 0 4691

0 0 3300

0 0 5329

0 0 3020

0 0 2628

0 0 5463

0 0 6097

0 0 6098

0 0 6066

0 0 5368

0 0 3145

0 0 4643

0 0 5603

0 0 5363

0 0 5132

0 0 0
Steam Output (1,000 lbs steam/hr) Flue Gas Flow Rate (dscfm) Flue Gas Pressure (atm)

5144.840349 2027800.049 NA

5018.411289 1928000 NA

4731.488497 1924199.951 NA

4167.472049 1713099.976 NA

2468.290979 1276800.049 NA

1973.208217 1146300.049 NA

2026.279082 1166300.049 NA

3477.676298 1604800.049 NA

2267.86641 1200599.976 NA

2105.752648 1153400.024 NA

3265.011314 1525500 NA

3257.424008 1537000 NA

2476.227664 1274199.951 NA

3447.906784 1588500 NA

2295.877454 1183599.976 NA

3354.983222 1601300.049 NA

2446.953586 1253400.024 NA

4008.833832 1753099.976 NA

2393.21495 1204000 NA

2040.744953 1135900.024 NA

4150.267506 1811900.024 NA

4656.113016 1949199.951 NA

4887.638221 1936400.024 NA

4781.544355 1948900.024 NA

4233.278482 1781900.024 NA

2435.101906 1215199.951 NA

3398.002746 1592800.049 NA

4391.608776 1845500 NA

N/A 1765300.049 NA

N/A 1743599.976 NA

0 0 0
Flue Gas Sampling Point Temperature (Deg F) Flue Gas Oxygen Content (%)

193.5 NA

194.3000031 NA

195.1000061 NA

193.3000031 NA

191.3000031 NA

191.3000031 NA

191.3000031 NA

192.8999939 NA

191.1000061 NA

191.6999969 NA

192.8000031 NA

192.1999969 NA

192 NA

193.8999939 NA

188.6000061 NA

193.6999969 NA

192.3999939 NA

194.6999969 NA

192.1999969 NA

192.3000031 NA

195.1999969 NA

196.3999939 NA

189.8000031 NA

195.1000061 NA

193.8999939 NA

189.3999939 NA

189.3000031 NA

189.8000031 NA

189.3999939 NA

189.5 NA

0 0
Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)

10.39000034 15-18%

10.22000027 15-18%

10.09000015 15-18%

9.609999657 15-18%

8.68999958 15-18%

8.149999619 15-18%

8.289999962 15-18%

9.510000229 15-18%

8.350000381 15-18%

8.170000076 15-18%

9.199999809 15-18%

9.460000038 15-18%

8.140000343 15-18%

8.899999619 15-18%

8.470000267 15-18%

9.25 15-18%

8.630000114 15-18%

9.720000267 15-18%

8.130000114 15-18%

7.630000114 15-18%

9.470000267 15-18%

10.13000011 15-18%

10.32999992 15-18%

10.18000031 15-18%

9.720000267 15-18%

8.489999771 15-18%

9.229999542 15-18%

9.800000191 15-18%

9.680000305 15-18%

9.319999695 15-18%

0 0
Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe) Standard Pressure (atm)

667.4000244 717.4000244 29.92 "Hg

611.2000122 661.2000122 29.92 "Hg

603 653 29.92 "Hg

502.0999756 552.0999756 29.92 "Hg

278.8999939 328.8999939 29.92 "Hg

203.6999969 253.6999969 29.92 "Hg

214.5 264.5 29.92 "Hg

439.7999878 489.7999878 29.92 "Hg

241.1000061 291.1000061 29.92 "Hg

232.8999939 282.8999939 29.92 "Hg

420.2999878 470.2999878 29.92 "Hg

421.3999939 471.3999939 29.92 "Hg

254.7000122 304.7000122 29.92 "Hg

425 475 29.92 "Hg

242.2999878 292.2999878 29.92 "Hg

427.6000061 477.6000061 29.92 "Hg

270.8999939 320.8999939 29.92 "Hg

508.5999756 558.5999756 29.92 "Hg

255 305 29.92 "Hg

207.1000061 257.1000061 29.92 "Hg

533 583 29.92 "Hg

599.2999878 649.2999878 29.92 "Hg

608.7999878 658.7999878 29.92 "Hg

605.5999756 655.5999756 29.92 "Hg

526.7000122 576.7000122 29.92 "Hg

269.2999878 319.2999878 29.92 "Hg

432.8999939 482.8999939 29.92 "Hg

551.2999878 601.2999878 29.92 "Hg

528.5 578.5 29.92 "Hg

504.0999756 554.0999756 29.92 "Hg

0 0 0
Standard Temperature (Deg F) Pressure Drop across FGD (in H2O)

68 25.77938337

68 24.97580237

68 24.63277823

68 22.33638754

68 15.91364544

68 14.32163987

68 13.54912876

68 20.1792178

68 13.78538781

68 13.9152888

68 18.76786307

68 18.44743875

68 15.40752899

68 19.9948886

68 15.80418177

68 21.42783306

68 17.18906035

68 22.46344431

68 14.7487373

68 13.92715861

68 22.12222286

68 21.13897328

68 21.54840432

68 20.90599434

68 22.15940782

68 13.91827737

68 18.24071524

68 21.08742568

68 21.6577429

68 21.57821456

0 0
FGD Scrubber Liquor Flow Rate (gals/min) FGD Scrubber Liquor pH (pH) Sorbent Type

NA 5.581145057 ACI

NA 5.710995121 ACI

NA 5.843646407 ACI

NA 5.879940632 ACI

NA 6.087080553 ACI

NA 6.245396236 ACI

NA 6.247172139 ACI

NA 5.900320737 ACI

NA 6.330431804 ACI

NA 6.446028312 ACI

NA 6.128895258 ACI

NA 5.929403501 ACI

NA 6.09508959 ACI

NA 6.073065887 ACI

NA 6.154818911 ACI

NA 5.957471335 ACI

NA 6.21269535 ACI

NA 5.855237147 ACI

NA 6.404861925 ACI

NA 6.366108211 ACI

NA 5.982503437 ACI

NA 6.180862232 ACI

NA 6.163054294 ACI

NA 6.091446285 ACI

NA 5.98757595 ACI

NA 6.768674705 ACI

NA 6.355505853 ACI

NA 6.13576982 ACI

NA 6.145649754 ACI

NA 6.036283933 ACI

0 0 Actvated Carbon
Sorbent Injection Rate (lb/hr)

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

0
EIA Facility Code Facility Name Boiler ID

6076 Colstrip Plant 3

Daily Average Process Data for a 30 Day Period Including the Testing Date

Date 

(MM/DD/YYYY) Coal Firing Rate (1,000 Tons/hr)

06/01/10 Day 1 0.4105

06/02/10 Day 2 0.3875

06/03/10 Day 3 0.384

06/04/10 Day 4 0.33

06/05/10 Day 5 0.213

06/06/10 Day 6 0.1715

06/07/10 Day 7 0.178

06/08/10 Day 8 0.291

06/09/10 Day 9 0.191

06/10/10 Day 10 0.175

06/11/10 Day 11 0.2725

06/12/10 Day 12 0.2745

06/13/10 Day 13 0.202

06/14/10 Day 14 0.282

06/15/10 Day 15 0.196

06/16/10 Day 16 0.288

06/17/10 Day 17 0.2085

06/18/10 Day 18 0.3355

06/19/10 Day 19 0.2005

06/20/10 Day 20 0.1735

06/21/10 Day 21 0.345

06/22/10 Day 22 0.3855

06/23/10 Day 23 0.389

06/24/10 Day 24 0.3865

06/25/10 Day 25 0.34

06/26/10 Day 26 0.205

06/27/10 Day 27 0.284

06/28/10 Day 28 0.352

06/29/10 Day 29 0.348

06/30/10 Day 30 0.335
a for a 30 Day Period Including the Testing Date

Synfuel Firing Rate (1,000 Tons/hr) Pet Coke Firing Rate (1,000 Tons/hr)

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0
Coal Gas Firing Rate (ft^3/min) Fuel oil Firing Rate (Gal/hr) Average Heat Input (MMBtu/hr)

0 0 6401

0 0 6009

0 0 5977

0 0 5113

0 0 3412

0 0 2834

0 0 2936

0 0 4735

0 0 3041

0 0 2863

0 0 4350

0 0 4445

0 0 3173

0 0 4528

0 0 3033

0 0 4691

0 0 3300

0 0 5329

0 0 3020

0 0 2628

0 0 5463

0 0 6097

0 0 6098

0 0 6066

0 0 5368

0 0 3145

0 0 4643

0 0 5603

0 0 5363

0 0 5132
Steam Output (1,000 lbs steam/hr) Flue Gas Flow Rate (dscfm) Flue Gas Pressure (atm)

5144.840349 2027800.049 NA

5018.411289 1928000 NA

4731.488497 1924199.951 NA

4167.472049 1713099.976 NA

2468.290979 1276800.049 NA

1973.208217 1146300.049 NA

2026.279082 1166300.049 NA

3477.676298 1604800.049 NA

2267.86641 1200599.976 NA

2105.752648 1153400.024 NA

3265.011314 1525500 NA

3257.424008 1537000 NA

2476.227664 1274199.951 NA

3447.906784 1588500 NA

2295.877454 1183599.976 NA

3354.983222 1601300.049 NA

2446.953586 1253400.024 NA

4008.833832 1753099.976 NA

2393.21495 1204000 NA

2040.744953 1135900.024 NA

4150.267506 1811900.024 NA

4656.113016 1949199.951 NA

4887.638221 1936400.024 NA

4781.544355 1948900.024 NA

4233.278482 1781900.024 NA

2435.101906 1215199.951 NA

3398.002746 1592800.049 NA

4391.608776 1845500 NA

N/A 1765300.049 NA

N/A 1743599.976 NA
Flue Gas Sampling Point Temperature (Deg F) Flue Gas Oxygen Content (%)

193.5 NA

194.3000031 NA

195.1000061 NA

193.3000031 NA

191.3000031 NA

191.3000031 NA

191.3000031 NA

192.8999939 NA

191.1000061 NA

191.6999969 NA

192.8000031 NA

192.1999969 NA

192 NA

193.8999939 NA

188.6000061 NA

193.6999969 NA

192.3999939 NA

194.6999969 NA

192.1999969 NA

192.3000031 NA

195.1999969 NA

196.3999939 NA

189.8000031 NA

195.1000061 NA

193.8999939 NA

189.3999939 NA

189.3000031 NA

189.8000031 NA

189.3999939 NA

189.5 NA
Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)

10.39000034 15-18%

10.22000027 15-18%

10.09000015 15-18%

9.609999657 15-18%

8.68999958 15-18%

8.149999619 15-18%

8.289999962 15-18%

9.510000229 15-18%

8.350000381 15-18%

8.170000076 15-18%

9.199999809 15-18%

9.460000038 15-18%

8.140000343 15-18%

8.899999619 15-18%

8.470000267 15-18%

9.25 15-18%

8.630000114 15-18%

9.720000267 15-18%

8.130000114 15-18%

7.630000114 15-18%

9.470000267 15-18%

10.13000011 15-18%

10.32999992 15-18%

10.18000031 15-18%

9.720000267 15-18%

8.489999771 15-18%

9.229999542 15-18%

9.800000191 15-18%

9.680000305 15-18%

9.319999695 15-18%
Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe) Standard Pressure (atm)

667.4000244 717.4000244 29.92 "Hg

611.2000122 661.2000122 29.92 "Hg

603 653 29.92 "Hg

502.0999756 552.0999756 29.92 "Hg

278.8999939 328.8999939 29.92 "Hg

203.6999969 253.6999969 29.92 "Hg

214.5 264.5 29.92 "Hg

439.7999878 489.7999878 29.92 "Hg

241.1000061 291.1000061 29.92 "Hg

232.8999939 282.8999939 29.92 "Hg

420.2999878 470.2999878 29.92 "Hg

421.3999939 471.3999939 29.92 "Hg

254.7000122 304.7000122 29.92 "Hg

425 475 29.92 "Hg

242.2999878 292.2999878 29.92 "Hg

427.6000061 477.6000061 29.92 "Hg

270.8999939 320.8999939 29.92 "Hg

508.5999756 558.5999756 29.92 "Hg

255 305 29.92 "Hg

207.1000061 257.1000061 29.92 "Hg

533 583 29.92 "Hg

599.2999878 649.2999878 29.92 "Hg

608.7999878 658.7999878 29.92 "Hg

605.5999756 655.5999756 29.92 "Hg

526.7000122 576.7000122 29.92 "Hg

269.2999878 319.2999878 29.92 "Hg

432.8999939 482.8999939 29.92 "Hg

551.2999878 601.2999878 29.92 "Hg

528.5 578.5 29.92 "Hg

504.0999756 554.0999756 29.92 "Hg
Standard Temperature (Deg F) Pressure Drop across FGD (in H2O)

68 25.77938337

68 24.97580237

68 24.63277823

68 22.33638754

68 15.91364544

68 14.32163987

68 13.54912876

68 20.1792178

68 13.78538781

68 13.9152888

68 18.76786307

68 18.44743875

68 15.40752899

68 19.9948886

68 15.80418177

68 21.42783306

68 17.18906035

68 22.46344431

68 14.7487373

68 13.92715861

68 22.12222286

68 21.13897328

68 21.54840432

68 20.90599434

68 22.15940782

68 13.91827737

68 18.24071524

68 21.08742568

68 21.6577429

68 21.57821456
FGD Scrubber Liquor Flow Rate (gals/min) FGD Scrubber Liquor pH (pH) Sorbent Type

NA 5.581145057 ACI

NA 5.710995121 ACI

NA 5.843646407 ACI

NA 5.879940632 ACI

NA 6.087080553 ACI

NA 6.245396236 ACI

NA 6.247172139 ACI

NA 5.900320737 ACI

NA 6.330431804 ACI

NA 6.446028312 ACI

NA 6.128895258 ACI

NA 5.929403501 ACI

NA 6.09508959 ACI

NA 6.073065887 ACI

NA 6.154818911 ACI

NA 5.957471335 ACI

NA 6.21269535 ACI

NA 5.855237147 ACI

NA 6.404861925 ACI

NA 6.366108211 ACI

NA 5.982503437 ACI

NA 6.180862232 ACI

NA 6.163054294 ACI

NA 6.091446285 ACI

NA 5.98757595 ACI

NA 6.768674705 ACI

NA 6.355505853 ACI

NA 6.13576982 ACI

NA 6.145649754 ACI

NA 6.036283933 ACI
Sorbent Injection Rate (lb/hr)

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA
EIA Facility Code Facility Name Boiler ID

6076 Colstrip Plant 3

Daily Average Process Data for a 30 Day Period Including the Testing Date

Date 

(MM/DD/YYYY) Coal Firing Rate (Tons/hr)

06/01/10 Day 1 0.4105

06/02/10 Day 2 0.3875

06/03/10 Day 3 0.384

06/04/10 Day 4 0.33

06/05/10 Day 5 0.213

06/06/10 Day 6 0.1715

06/07/10 Day 7 0.178

06/08/10 Day 8 0.291

06/09/10 Day 9 0.191

06/10/10 Day 10 0.175

06/11/10 Day 11 0.2725

06/12/10 Day 12 0.2745

06/13/10 Day 13 0.202

06/14/10 Day 14 0.282

06/15/10 Day 15 0.196

06/16/10 Day 16 0.288

06/17/10 Day 17 0.2085

06/18/10 Day 18 0.3355

06/19/10 Day 19 0.2005

06/20/10 Day 20 0.1735

06/21/10 Day 21 0.345

06/22/10 Day 22 0.3855

06/23/10 Day 23 0.389

06/24/10 Day 24 0.3865

06/25/10 Day 25 0.34

06/26/10 Day 26 0.205

06/27/10 Day 27 0.284

06/28/10 Day 28 0.352

06/29/10 Day 29 0.348

06/30/10 Day 30 0.335
a for a 30 Day Period Including the Testing Date

Synfuel Firing Rate (1,000 Tons/hr) Pet Coke Firing Rate (1,000 Tons/hr)

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0

0 0
Coal Gas Firing Rate (ft^3/min) Fuel oil Firing Rate (Gal/day) Average Heat Input (MMBtu/hr)

0 0 6401

0 0 6009

0 0 5977

0 0 5113

0 0 3412

0 0 2834

0 0 2936

0 0 4735

0 0 3041

0 0 2863

0 0 4350

0 0 4445

0 0 3173

0 0 4528

0 0 3033

0 0 4691

0 0 3300

0 0 5329

0 0 3020

0 0 2628

0 0 5463

0 0 6097

0 0 6098

0 0 6066

0 0 5368

0 0 3145

0 0 4643

0 0 5603

0 0 5363

0 0 5132
Steam Output (1,000 lbs steam/hr) Flue Gas Flow Rate (dscfm) Flue Gas Pressure (atm)

5144.840349 2027800.049 NA

5018.411289 1928000 NA

4731.488497 1924199.951 NA

4167.472049 1713099.976 NA

2468.290979 1276800.049 NA

1973.208217 1146300.049 NA

2026.279082 1166300.049 NA

3477.676298 1604800.049 NA

2267.86641 1200599.976 NA

2105.752648 1153400.024 NA

3265.011314 1525500 NA

3257.424008 1537000 NA

2476.227664 1274199.951 NA

3447.906784 1588500 NA

2295.877454 1183599.976 NA

3354.983222 1601300.049 NA

2446.953586 1253400.024 NA

4008.833832 1753099.976 NA

2393.21495 1204000 NA

2040.744953 1135900.024 NA

4150.267506 1811900.024 NA

4656.113016 1949199.951 NA

4887.638221 1936400.024 NA

4781.544355 1948900.024 NA

4233.278482 1781900.024 NA

2435.101906 1215199.951 NA

3398.002746 1592800.049 NA

4391.608776 1845500 NA

N/A 1765300.049 NA

N/A 1743599.976 NA
Flue Gas Sampling Point Temperature (Deg F) Flue Gas Oxygen Content (%)

193.5 NA

194.3000031 NA

195.1000061 NA

193.3000031 NA

191.3000031 NA

191.3000031 NA

191.3000031 NA

192.8999939 NA

191.1000061 NA

191.6999969 NA

192.8000031 NA

192.1999969 NA

192 NA

193.8999939 NA

188.6000061 NA

193.6999969 NA

192.3999939 NA

194.6999969 NA

192.1999969 NA

192.3000031 NA

195.1999969 NA

196.3999939 NA

189.8000031 NA

195.1000061 NA

193.8999939 NA

189.3999939 NA

189.3000031 NA

189.8000031 NA

189.3999939 NA

189.5 NA
Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)

10.39000034 15-18%

10.22000027 15-18%

10.09000015 15-18%

9.609999657 15-18%

8.68999958 15-18%

8.149999619 15-18%

8.289999962 15-18%

9.510000229 15-18%

8.350000381 15-18%

8.170000076 15-18%

9.199999809 15-18%

9.460000038 15-18%

8.140000343 15-18%

8.899999619 15-18%

8.470000267 15-18%

9.25 15-18%

8.630000114 15-18%

9.720000267 15-18%

8.130000114 15-18%

7.630000114 15-18%

9.470000267 15-18%

10.13000011 15-18%

10.32999992 15-18%

10.18000031 15-18%

9.720000267 15-18%

8.489999771 15-18%

9.229999542 15-18%

9.800000191 15-18%

9.680000305 15-18%

9.319999695 15-18%
Unit Net Electric Generation (MW) Unit Gross Electric Generation (MW) Standard Pressure (atm)

667.4000244 717.4000244 29.92 "Hg

611.2000122 661.2000122 29.92 "Hg

603 653 29.92 "Hg

502.0999756 552.0999756 29.92 "Hg

278.8999939 328.8999939 29.92 "Hg

203.6999969 253.6999969 29.92 "Hg

214.5 264.5 29.92 "Hg

439.7999878 489.7999878 29.92 "Hg

241.1000061 291.1000061 29.92 "Hg

232.8999939 282.8999939 29.92 "Hg

420.2999878 470.2999878 29.92 "Hg

421.3999939 471.3999939 29.92 "Hg

254.7000122 304.7000122 29.92 "Hg

425 475 29.92 "Hg

242.2999878 292.2999878 29.92 "Hg

427.6000061 477.6000061 29.92 "Hg

270.8999939 320.8999939 29.92 "Hg

508.5999756 558.5999756 29.92 "Hg

255 305 29.92 "Hg

207.1000061 257.1000061 29.92 "Hg

533 583 29.92 "Hg

599.2999878 649.2999878 29.92 "Hg

608.7999878 658.7999878 29.92 "Hg

605.5999756 655.5999756 29.92 "Hg

526.7000122 576.7000122 29.92 "Hg

269.2999878 319.2999878 29.92 "Hg

432.8999939 482.8999939 29.92 "Hg

551.2999878 601.2999878 29.92 "Hg

528.5 578.5 29.92 "Hg

504.0999756 554.0999756 29.92 "Hg
Standard Temperature (Deg F) Pressure Drop across FGD (in H2O)

68 25.77938337

68 24.97580237

68 24.63277823

68 22.33638754

68 15.91364544

68 14.32163987

68 13.54912876

68 20.1792178

68 13.78538781

68 13.9152888

68 18.76786307

68 18.44743875

68 15.40752899

68 19.9948886

68 15.80418177

68 21.42783306

68 17.18906035

68 22.46344431

68 14.7487373

68 13.92715861

68 22.12222286

68 21.13897328

68 21.54840432

68 20.90599434

68 22.15940782

68 13.91827737

68 18.24071524

68 21.08742568

68 21.6577429

68 21.57821456
FGD Scrubber Liquor Flow Rate (gals/min) FGD Scrubber Liquor pH (pH) Sorbent Type

NA 5.581145057 ACI

NA 5.710995121 ACI

NA 5.843646407 ACI

NA 5.879940632 ACI

NA 6.087080553 ACI

NA 6.245396236 ACI

NA 6.247172139 ACI

NA 5.900320737 ACI

NA 6.330431804 ACI

NA 6.446028312 ACI

NA 6.128895258 ACI

NA 5.929403501 ACI

NA 6.09508959 ACI

NA 6.073065887 ACI

NA 6.154818911 ACI

NA 5.957471335 ACI

NA 6.21269535 ACI

NA 5.855237147 ACI

NA 6.404861925 ACI

NA 6.366108211 ACI

NA 5.982503437 ACI

NA 6.180862232 ACI

NA 6.163054294 ACI

NA 6.091446285 ACI

NA 5.98757595 ACI

NA 6.768674705 ACI

NA 6.355505853 ACI

NA 6.13576982 ACI

NA 6.145649754 ACI

NA 6.036283933 ACI
Sorbent Injection Rate (lb/hr)

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA

NA