Revision 4.2 

5/12/09 

Air Pollution Control Operating Permit 

Significant Modification and Preconstruction Approval 

Permit Activity Number: BOP090002 Program Interest Number: 18195 

Mailing Address Plant Location 

ALBERT BERGERON 

PRESIDENT & FACILITY MGR 

AES RED OAK LLC 

832 RED OAK LN 

Sayreville, NJ 08872 

AES RED OAK LLC 

832 Red Oak Ln 

Sayreville Boro 

Middlesex County 

Initial Operating Permit Approval Date: July 28, 2005 

Significant Modification Approval Date: February 1, 2010 

Operating Permit Expiration Date: July 27, 2010 

This significant modification is approved and issued under the authority of Chapter 106, P.L. 1967 (N.J.S.A. 26:2C9.2). The equipment at the facility must be operated in accordance with the requirements of this permit. 

This approval, in response to your application, merges the provisions of the previously approved operating permit 

and the changes from this significant modification into a single comprehensive permit that replaces the one 

previously issued. This significant modification includes the following changes: 

1. Include Clean Air Interstate Rule (CAIR) NOx Trading Program requirements in the operating permit. 

2. Updating various permit conditions (including subchapter 19 requirements and turbine stack testing 

language). 

3. Correct the stack testing language at (U1, OSS, REF #2) to require stack testing of NOx, CO, VOC, SO2, 

TSP, PM-10, Ammonia and (SO3 and H2SO4); the current permit only lists NOx, CO, VOC and Ammonia 

but the rest are required to be stack tested by the monitoring requirement associated with the individual 

emission limitations. 

4. Allowing compliance with all NOx, CO, VOC and PM-10 limits to be demonstrated by the average of three 

Department approved stack test runs in accordance with current Department policy; the current permit 

requires compliance with each stack test run. 

5. Correcting emission unit 1 to include PT5, instead of PT3. 

6. Updating Appendix II: Cooling Tower Chemical Additives by removing several chemicals currently 

allowed to be used in the cooling tower and adding sulfuric acid, and Depositrol to the list. 

Equipment at the facility referenced by this significant modification is covered by the permit shield, pursuant to the 

provisions of N.J.A.C. 7:27-22.17. However, this permit shield does not cover physical changes which were 

undertaken at the facility after March 3, 2003 and for which the facility did not seek an applicability determination 

for the Prevention of Significant Deterioration rule, codified at 40 CFR 52.21 (PSD), from the United States 

Environmental Protection Agency (USEPA). The issuance of this permit should not in any way be construed as a 

determination by the Department that the PSD rules do not apply. Any questions on applicability of PSD should be 

directed to USEPA Region II, Air Compliance Branch, 21st Floor, 290 Broadway, New York, NY 10007-1866 

(Phone: 212-637-4074). Pursuant to N.J.A.C. 7:27-22.33(e), this significant modification consists of both a 

preconstruction approval and operating permit approval. This operating permit does not include compliance 

schedules as part of the approved compliance plan. 

CHRIS CHRISTIE DEPARTMENT of ENVIRONMENTAL PROTECTION BOB MARTIN Governor Acting Commissioner 

Environmental Regulation 

Bureau of Air Permits 

401 E. State Street, 2nd floor, P.O. Box 27 

Trenton, NJ 08625-0027
Revision 4.2 

5/12/09 

The permittee shall submit to the Department and to the EPA on forms provided by the Department, at the addresses 

given below, a periodic compliance certification, in accordance with N.J.A.C. 7:27-22.19 and the schedule for 

compliance certifications set forth in the compliance plan in this operating permit. The annual compliance 

certification reporting period will cover the calendar year ending December 31. The annual compliance 

certification is due to the Department and the EPA within 60 days after the end of each calendar year during 

which this permit was in effect. Forms provided by the Department can be found on the Department's website at: 

http://www.nj.gov/dep/enforcement/compliancecertsair.htm. 

The annual compliance certification report may also be considered as your six month deviation report for the period 

from July 1 through December 31 which is due by January 30 of each year, as required by paragraph 13 in Section 

F, General Provisions and Authorities, of this permit, if the annual compliance certification is submitted by January 

30. 

New Jersey Department of Environmental Protection United States Environmental Protection Agency, Region II 

Air & Environmental Quality Compliance & Enforcement Air Compliance Branch 

401 East State Street, P. O. Box 422 290 Broadway 

Trenton, New Jersey 08625-0422 New York, New York 10007-1866 

 

New Jersey Department of Environmental Protection 

Air and Environmental Quality Compliance & Enforcement 

Central Regional Enforcement Office 

300 Horizon Center, PO Box 407, Rt. 130 South 

Robbinsville, New Jersey 08625-0407 

We are including two electronic files, PDF and RADIUS. The PDF file contains the complete operating permit for 

your facility. The RADIUS file contains the Facility Name, Location, and Contact Information; the Facility Specific 

Requirements (Compliance Plan) and Inventories; and any Compliance Schedules (if needed). Upon importing this 

information into your personal computer with RADIUS software, you will have up-to-date information in RADIUS 

format. RADIUS software, instructions, and help are available at the Department's website at 

www.state.nj.us/dep/aqpp. We also have an Operating Permit Help Line available from 9:00 AM to 4:00 PM daily, 

where you may speak to someone about any questions you may have. The Operating Permit Help Line number is 

609-633-8248. 

If, in your judgment, the Department is imposing any unreasonable condition of approval in this permit modification 

action, you may contest the Department’s decision on the modification and request an adjudicatory hearing pursuant 

to N.J.S.A. 52:14b-1 et seq. and N.J.A.C. 7:27-22.32(a). All requests for an adjudicatory hearing must be received 

in writing by the Department within 20 calendar days of the date you receive this letter. The request must contain 

the information requested in N.J.A.C. 7:27-1.32 and the information on the enclosed Administrative Hearing 

Request Checklist and Tracking Form. 

The permittee is responsible for submitting a timely and administratively complete operating permit renewal 

application. The application is considered timely if it is received at least 12 months before the expiration date of the 

operating permit. To be deemed administratively complete, an application for renewal of the operating permit shall 

include all of the information required by the application form for the renewal and the information required pursuant 

to N.J.A.C. 7:27-22.30(d). However, consistent with N.J.A.C. 7:27-22.30(c), the permittee is encouraged to submit 

the renewal application at least 15 months prior to expiration of the operating permit, so that the Department can 

notify the applicant of any deficiencies in the application. This will allow the permittee to correct any deficiencies, 

and to better ensure that the application is administratively complete by the renewal deadline. Only applications 

which are timely and administratively complete will be eligible for coverage by an application shield. The renewal 

application can be found at our website, http://www.state.nj.us/dep/aqpp/downloads/forms/OPRenewal.PDF. 

Permittees that are subject to Compliance Assurance Monitoring (CAM), pursuant to 40 CFR 64, shall develop a 

CAM Plan for modified equipment as well as existing sources. Details of the rule and guidance on how to prepare a 

plan can be found at EPA’s website: www.epa.gov/ttn/emc/cam.html. In addition, CAM Plans must be included as 

part of the permit renewal application. Permittees that do not submit a CAM Plan may have their modification 

applications denied, pursuant to N.J.A.C. 7:27-22.3. 

If you have any questions regarding this permit approval, please call your permit writer, Michael Hogan, at (609) 

633-1124. 
Revision 4.2 

5/12/09 

Approved by: 

 ______________________ 

Aliya Khan 

Bureau of Air Permits 

Enclosure 

CC: S. Riva, USEPA Region II (diskette containing final permit) 

P. Conti, Chief CRO (Signature Page Only) 

 M. Hogan (w/o enclosure) 
Revision 4.2 

5/12/09 

Administrative Hearing Request Checklist and Tracking Form 

I. Document Being Appealed 

Name of the Facility 

Program Interest 

(PI) Number

Permit Activity 

Number

Issuance 

Date 

AES RED OAK LLC 18195 BOP090002 

II. Contact Information 

Name of Person Requesting Hearing Name of Attorney (if applicable) 

Address: Address:

Telephone: Telephone:

III. Please include the following information as part of your request: 

A. The date the permittee received the permit decision, 

B. Two printed copies of the document being appealed – for submitting to address 1 below; 

A PDF copy of the document being appealed on a CD – for submitting to address 2 

below;

C. The legal and factual questions you are appealing; 

D. A statement as to whether or not you raised each legal and factual issues during the 

permit application process; 

E. Suggested revised or alternative permit conditions; 

F. An estimate of the time required for the hearing; 

G. A request, if necessary, for a barrier-free hearing location for physically disabled persons; 

H. A clear indication of any willingness to negotiate a settlement with the Department prior to 

the Departments processing of your hearing request to the Office of Administrative Law; 

Mail this form, completed, signed and dated with all of the information listed above, including attachment, 

to: 

1. New Jersey Department of Environmental Protection 

Office of Legal Affairs 

Attention: Adjudicatory Hearing Requests 

401 E. State Street, P.O. Box 402 

Trenton, New Jersey 08625-0402 

2. Mr. Robert Esposito 

Air Quality Permitting Element 

New Jersey Department of Environmental Protection 

 401 E. State Street, 2nd Floor, P.O. Box 027 

Trenton, New Jersey 08625-0027 

Phone: (609) 633-2829 

Signature Date 
Revision 4.2 

5/12/09 

Administrative Hearing Request Checklist and Tracking Form 

IV. If you are not the applicant but rather an interested person claiming to be aggrieved by the 

permit decision, please include the following information: 

1. The date you or your agent received notice of the permit decision (include a copy of that 

permit decision with your hearing request); 

2. Evidence that a copy of the request has been delivered to the applicant for the permit 

which is the subject of the permit decision; 

3. A detailed statement of which findings of fact and/or conclusion of law you are 

challenging; 

4. A description of your participation in any public hearings held in connection with the 

permit application and copies of any written comments you submitted; 

5. Whether you claim a statutory or constitutional right to a hearing, and, if you claim such a 

right, a reference to the applicable statute or explanation of how your property interests 

are affected by the permit decision; 

6. If the appeal request concerns a CAFRA permit decision, evidence that a copy of the 

request has been delivered to the clerks of the county and the municipality in which the 

project which is the subject of the permit decision is located; 

7. Suggested revised or alternative permit conditions; 

8. An estimate of the time required for the hearing; 

9. A request, if necessary, for a barrier-free hearing location for physically disable persons; 

10. A clear indication of any willingness to negotiate a settlement with the Department prior to 

the Department’s transmittal of the hearing request to the Office of Administrative Law; 

Mail this form, completed, signed and dated with all of the information listed above, including attachment, 

to: 

1. New Jersey Department of Environmental Protection 

Office of Legal Affairs 

Attention: Adjudicatory Hearing Requests 

401 East State Street, P.O. Box 402 

Trenton, New Jersey 08625-0402 

 

3. Mr. Robert Esposito 

Air Quality Permitting Element 

New Jersey Department of Environmental Protection 

 401 E. State Street, 2nd Floor, P.O. Box 027 

Trenton, New Jersey 08625 

Phone: (609) 633-2829 

Signature Date 
Revision 4.2 

5/12/09 

 

Facility Name: AES RED OAK LLC 

Program Interest Number: 18195 

Permit Activity Number: BOP090002 

TABLE OF CONTENTS 

Section A

REASON FOR PERMIT 

Section B

DEFINITIONS 

Section C

POLLUTANT EMISSIONS SUMMARY 

Section D

POLLUTION PREVENTION REPORTING 

Section E

GENERAL PROVISIONS AND AUTHORITIES 

Section F

STATE-ONLY APPLICABLE REQUIREMENTS 

Section G

COMPLIANCE PLAN AND INVENTORIES

APPENDIX 1: ACID RAIN PERMIT 

APPENDIX 2: CAIR PERMIT 

APPENDIX 3: COOLING TOWER CHEMICALS 
Revision 4.2 

5/12/09 

Section A 

 

Facility Name: AES RED OAK LLC 

Program Interest Number: 18195 

Permit Activity Number: BOP090002 

REASON FOR PERMIT 

The reason for issuance of this permit is to comply with the air pollution control permit provisions of Title V of the 

federal Clean Air Act, federal rules promulgated at 40 CFR 70, and state regulations promulgated at N.J.A.C. 7:27-

22, which requires the state to issue operating permits to major facilities and minor facilities that are in certain 

designated source categories. This is the operating permit for the facility listed on the cover page, which includes a 

significant modification that includes the following changes: 

1. Include Clean Air Interstate Rule (CAIR) NOx Trading Program requirements in the operating permit. 

2. Updating various permit conditions (including subchapter 19 requirements and turbine stack testing 

language). 

3. Correct the stack testing language at (U1, OSS, REF #2) to require stack testing of NOx, CO, VOC, SO2, 

TSP, PM-10, Ammonia and (SO3 and H2SO4); the current permit only lists NOx, CO, VOC and Ammonia 

but the rest are required to be stack tested by the monitoring requirement associated with the individual 

emission limitations. 

4. Allowing compliance with all NOx, CO, VOC and PM-10 limits to be demonstrated by the average of three 

Department approved stack test runs in accordance with current Department policy; the current permit 

requires compliance with each stack test run. 

5. Correcting emission unit 1 to include PT5, instead of PT3. 

6. Updating Appendix II: Cooling Tower Chemical Additives by removing several chemicals currently 

allowed to be used in the cooling tower and adding sulfuric acid, and Depositrol to the list. 

New Jersey has elected to integrate its Title I New Source Review (NSR) preconstruction permits with the new Title 

V operating permits instead of issuing separate permits. Consequently, the existing preconstruction permit 

provisions that were previously approved for this facility have been consolidated into this permit. This permit may 

also include applicable requirements for grandfathered sources. 

This permit action consolidates previously approved permit terms and conditions into one single permit for the 

facility. The New Jersey Department of Environmental Protection (Department) issues this operating permit 

authorizing the facility to operate equipment and air pollution control devices. In the operating permit application, 

the facility represented that it meets all applicable requirements of the federal Clean Air Act and the New Jersey Air 

Pollution Control Act codified at N.J.S.A. 26:2C. Based on an evaluation of the data contained in the facility’s 

application, the Department has approved this operating permit. 

This permit allows this facility to operate the equipment and air pollution control devices specified in this permit and 

emit up to a level specified for each source operation. The signatories named in the application are responsible for 

ensuring that the facility is operated in a manner consistent with this permit, its conditions, and applicable rules. 
Revision 4.2 

5/12/09 

Section B 

Facility Name: AES RED OAK LLC 

Program Interest Number: 18195 

Permit Activity Number: BOP090002 

DEFINITIONS 

The terms used in this permit are used consistent with the definitions at N.J.A.C. 7:27-1 and N.J.A.C. 7:27-22. Any 

terms defined in this section are not defined at N.J.A.C. 7:27-1 or N.J.A.C. 7:27-22, and are needed for clarifying 

the permit. 

“Permitting Authority” means the New Jersey Department of Environmental Protection (NJDEP). 

“The EPA,” or the “Administrator,” means the Administrator of the EPA or his designee. 

“M” preceding a unit of measure means one thousand. For example, “10 M gal.” means ten thousand gallons. 

“MM” preceding a unit of measure means one million. For example, “10 MM gal.” means ten million gallons. 

“Grandfathered” means, in reference to equipment or control apparatus, that construction, reconstruction, or 

modification occurred prior to enactment of N.J.S.A. 26:2C-9.2 on June 15, 1967, or prior to the subsequent 

applicable revisions to rules and regulations codified at N.J.A.C. 7:27-8 that occurred March 5, 1973, June 1, 1976, 

April 5, 1985, and October 31, 1994, and no construction, reconstruction, or modification of the equipment or 

control apparatus has occurred since. 

“Compliance Plan” means the applicable requirements, monitoring requirements, recordkeeping requirements, and 

submittal/action requirements detailed in Section J, Facility Specific Requirements, of the operating permit. 
Revision 4.2 

5/12/09 

Section C 

Facility Name: AES RED OAK LLC 

Program Interest Number: 18195 

Permit Activity Number: BOP090002 

POLLUTANT EMISSIONS SUMMARY

The following table indicates the facility’s Potential to Emit (PTE) emissions summary: 

Facility Total Potential to Emit 

(tons per year) 

Source Categories Primary Secondary 

VOC 

(total) 

NOx CO SO2 TSP 

(total) 

Other 

(total) 

PM10

(total) 

Pb HAPs 

(total) 

Emission Unit 

Summary 102.9 292.4 704.8 104.1 345.1 63.6 345.1 N/A N/A 

Batch Process 

Summary N/A N/A N/A N/A N/A N/A N/A N/A N/A 

Non-Source Fugitive 

Emissions1 N/A N/A N/A N/A N/A N/A N/A N/A N/A 

Group 

Summary N/A N/A N/A N/A N/A N/A N/A N/A N/A 

Total 

Emissions2 102.9 292.4 704.8 104.1 345.1 63.6 345.1 N/A N/A 

VOC Volatile Organic Compounds PM10 Particulates under 10 microns 

NOx Nitrogen Oxides Pb Lead 

CO Carbon Monoxide HAPs Hazardous Air Pollutants 

SO2 Sulfur Dioxide 

TSP Total Suspended Particulates 

Other Any other air contaminant regulated under the Federal Clean Air Act 

 

1

 Not applicable to this facility. 

2

 Total emissions from this facility do not include emissions from Insignificant Sources. 
Revision 4.2 

5/12/09 

Section C 

Facility Name: AES RED OAK LLC 

Program Interest Number: 18195 

Permit Activity Number: BOP090002 

POLLUTANT EMISSIONS SUMMARY

The following table indicates the facility’s hazardous air pollutants (HAP) emissions summary:3

HAP TPY 

 

 

3

 Do not sum these values for the purpose of establishing a total HAP potential to emit. See previous page for the 

allowable total HAP emissions. 
Revision 4.2 

5/12/09 

Section D 

Facility Name: AES RED OAK LLC 

Program Interest Number: 18195 

Permit Activity Number: BOP090002 

POLLUTION PREVENTION REPORTING 

General Pollution Prevention Conditions

The following evaluation requirements are included to track the facility’s progress in several critical areas identified 

in the National Environmental Performance Partnership System (NEPPS). Nitrogen Oxides (NOx) and Volatile 

Organic Compounds (VOC) are precursors to the air pollutant Ozone, for which New Jersey is non-attainment with 

the air quality standard for the protection of public health. The control of hazardous air pollutants (HAPs) is also a 

focus item for the next decade in order to minimize localized hot spots and general urban air toxics levels. 

Therefore, the Department is requiring evaluation of emission trends at 5-year intervals for major sources of these 

air contaminants. Also, as part of significant modification applications, proposed major increases of these air 

contaminants require evaluation of pollution prevention and cross media effects. 

The evaluation of these trends requires no increased monitoring. Rather it utilizes existing monitoring data, as 

reported annually in Emission Statements (for NOx and VOC) and annual Release and Pollution Prevention Reports 

(for HAPs). The intent of this evaluation is to better utilize the existing data by having the company, the public and 

the Department review major source trends periodically, as part of the 5-year renewal review and public comment 

process. The Department requests that the facility-wide trends be presented on graphs for attachment to the public 

information document for the 5-year renewal. 

Pollution prevention includes changes that result in the reduction in use or generation of non-product output per unit 

of product. Cross media effects are practices that result in transferring the ultimate release or disposal of a 

contaminant from one environmental medium (e.g. air) to another environmental medium (e.g. water, solid or 

hazardous wastes). 

Information to include with the renewal application:

1. The facility will evaluate annual emission trends over the last five years for actual air contaminant 

emissions of Volatile Organic Compounds (VOC), Nitrogen Oxides (NOx), if the facility’s potential to 

emit VOC or NOx is greater than 25 tons per year, or any Hazardous Air Pollutants (HAP), for which the 

facility’s potential to emit is greater than 10 tons per year. The VOC and NOx emission data should reflect 

annual emission statement reports submitted pursuant to N.J.A.C. 7:27-21, and the HAP emissions data 

should reflect the annual Release and Pollution Prevention Report submitted pursuant to N.J.A.C. 7:1G-4 

and 5 and N.J.A.C. 7:1K-6. Although not required, the Department encourages the facility to explain the 

reason for any significant trend, including whether it is the result of cross media shifts (to air, water, or 

solid waste) and/or pollution prevention. Changes should be itemized for each emission unit (or process) 

with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton per year 

of any HAP. Also, show the net change for the facility. 

2. The facility will summarize annual potential to emit limits (allowable emissions) for VOC, NOx, and 

HAPs, which are subject to reporting under 1 above, for the last five years. Changes should be itemized for 

each emission unit (or process) with a potential to emit over five tons per year of VOC or NOx or a 

potential to emit over one ton per year of any HAP. Also, show the net change for the facility. 

3. The facility will summarize five-year trends in annual VOC, NOx, and HAP emissions, which are subject 

to reporting under 1 above, on a pound per unit of product basis, based on annual actual emissions and 

annual production over the five year period. Changes should be itemized for each emission unit (or 
Revision 4.2 

5/12/09 

process) with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton 

per year of any HAP. Also, show the net change for the facility. 

4. The facility will discuss five-year trends in actual air contaminant emissions of non-source VOC and HAP 

fugitives, which are subject to reporting under 1 above; explain measures taken to minimize such fugitives; 

and provide an explanation for any significant changes. 

Information to include with an application for a Significant Modification to this permit:

1. For any significant modifications, the facility is encouraged to explain any cross media shifts of VOC and 

HAP air contaminants as part of the significant modification application. If an explanation is provided, the 

facility should identify the pollutant and the specific environmental media to which the pollutant is 

anticipated to be transferred, whether it be from air to solid waste or water, or from water or solid waste to 

the air. 
Revision 4.2 

5/12/09 

Section E 

 

Facility Name: AES RED OAK LLC 

Program Interest Number: 18195 

Permit Activity Number: BOP090002 

GENERAL PROVISIONS AND AUTHORITIES 

Operating Permits

1. No permittee shall allow any air contaminant, including an air contaminant detectable by the sense of 

smell, to be present in the outdoor atmosphere in a quantity and duration which is, or tends to be, injurious 

to human health or welfare, animal or plant life or property, or which would unreasonably interfere with the 

enjoyment of life or property. This shall not include an air contaminant that occurs only in areas over 

which the permittee has exclusive use or occupancy. Conditions relative only to nuisance situations, 

including odors, are not considered Federally enforceable. [N.J.A.C. 7:27-22.16(g)8] 

2. Any deviation from operating permit requirements which results in a release of air contaminants shall be 

reported to the Department as follows: 

If the air contaminants are released in a quantity or concentration which poses a potential threat to public 

health, welfare or the environment or which might reasonably result in citizen complaints, the permittee 

shall report the release to the Department: 

i. Immediately on the Department hotline at 1-877-927-6337, pursuant to N.J.S.A. 26:2C-19(e); and 

ii. As part of the compliance certification required in N.J.A.C. 7:27-22.19(f). However, if the 

deviation is identified through source emissions testing, it shall be reported through the source 

emissions testing and monitoring procedures at N.J.A.C. 7:27-22.18(e)3; or 

If the air contaminants are released in a quantity or concentration which poses no potential threat to public 

health, welfare or the environment and which will not likely result in citizen complaints, the permittee shall 

report the release to the Department as part of the compliance certification required in N.J.A.C. 7:27-

22.19(f), except for deviations identified by source emissions testing reports, which shall be reported 

through the procedures at N.J.A.C. 7:27-22.18(e)3; or 

If the air contaminants are released in a quantity or concentration which poses no potential threat to public 

health, welfare or the environment and which will not likely result in citizen complaints, and the permittee 

intends to assert the affirmative defense afforded by N.J.A.C. 7:27-22.16(l), the violation shall be reported 

by 5:00 P.M. of the second full calendar day following the occurrence, or of becoming aware of the 

occurrence, consistent with N.J.A.C. 7:27-22.16(l). [N.J.A.C. 7:27-22.19(g)] 

3. The permittee shall comply with all conditions of the operating permit including the approved compliance 

plan. Any non-compliance with a permit condition constitutes a violation of the New Jersey Air Pollution 

Control Act N.J.S.A. 26:2C-1 et seq., or the CAA, 42 U.S.C. §7401 et seq., or both, and is grounds for 

enforcement action; for termination, revocation and reissuance, or for modification of the operating permit; 

or for denial of an application for a renewal of the operating permit. [N.J.A.C. 7:27-22.16(g)1] 

4. It shall not be a defense for the permittee in an enforcement action that it would have been necessary to halt 

or reduce the permitted activity in order to maintain compliance with the conditions of its operating permit. 

[N.J.A.C. 7:27-22.16(g)2] 
Revision 4.2 

5/12/09 

5. This operating permit may be modified, terminated, or revoked for cause by the EPA pursuant to 40 CFR 

70.7(g) and revoked or reopened and modified for cause by the Department pursuant to N.J.A.C. 7:27-

22.25. [N.J.A.C. 7:27-22.16(g)3] 

6. The permittee shall furnish to the Department, within a reasonable time, any information that the 

Department may request in writing to determine whether cause exists for modifying, revoking and 

reissuing, or terminating this operating permit; or to determine compliance with the operating permit. 

[N.J.A.C. 7:27-22.16(g)4] 

7. The filing of an application for a modification of an operating permit, or of a notice of planned changes or 

anticipated non-compliance, does not stay any operating permit condition. [N.J.A.C. 7:27-22.16(g)5] 

8. The operating permit does not convey any property rights of any sort, or any exclusive privilege. [N.J.A.C. 

7:27-22.16(g)6] 

9. Upon request, the permittee shall furnish to the Department copies of records required by the operating 

permit to be kept. [N.J.A.C. 7:27-22.16(g)7] 

10. The Department and its authorized representatives shall have the right to enter and inspect any facility 

subject to N.J.A.C. 7:27-22, or portion thereof, pursuant to N.J.A.C. 7:27-1.31. [N.J.A.C. 7:27-22.16(g)9] 

11. The permittee shall pay fees to the Department pursuant to N.J.A.C. 7:27. [N.J.A.C. 7:27-22.16(g)10] 

12. Each permittee shall maintain records of all source emissions testing or monitoring performed at the facility 

and required by the operating permit in accordance with N.J.A.C. 7:27-22.19. Records shall be maintained, 

for at least five years from the date of each sample, measurement, or report. Each permittee shall maintain 

all other records required by this operating permit for a period of five years from the date each record is 

made. At a minimum, source emission testing or monitoring records shall contain the information specified 

at N.J.A.C. 7:27-22.19(b). [N.J.A.C. 7:27-22.19(a) and N.J.A.C. 7:27-22.19(b)] 

13. In accordance with N.J.A.C. 7:27-22.19(c) and 22.19(d) 3, each permittee shall submit to the Department, 

on forms provided by the Department, a six month deviation report relating to testing and monitoring 

required by the operating permit, not including information for testing and monitoring which have other 

reporting schedules specified in the permit. Normally, stack testing reporting is submitted within 45 days 

of test completion and continuous monitoring reporting is done quarterly. The six month report must 

address other specified monitoring, including, but not limited to, continuous and periodic monitoring data 

required by this permit. (See column two and three entitled "Monitoring Requirement" and 

"Recordkeeping Requirement," respectively, in the Facility Specific Requirement Section of this permit.). 

The six month reports for the testing and monitoring performed from January 1 through June 30, shall be 

reported by July 30 of the same calendar year; or from July 1 through December 31, shall be reported by 

January 30 of the following calendar year. Pursuant to N.J.A.C. 7:27-22.19(e), these six month reports 

shall clearly identify all deviations from operating permit requirements, the probable cause of such 

deviations, and any corrective actions taken. Any "None" listed in the Submittal/Action Requirement in the 

operating permit is not intended to override the six-month deviation report. The report shall be certified 

pursuant to N.J.A.C. 7:27-1.39 by a responsible official. Forms provided by the Department can be found 

on the Department's web site at: http://www.nj.gov/dep/enforcement/compliancecertsair.htm. [N.J.A.C. 

7:27-22.19(d) 3 and N.J.A.C. 7:27-22.19(e)] 

An annual compliance certification required by paragraph 2 above and required by N.J.A.C. 7:27-19(f) may 

also be considered as your six month deviation report for the period from July 1 through December 31 

which is due by January 30 of each year if the annual compliance certification is submitted by January 30. 

14. For emergencies (as defined at 40 CFR 70.6(g)(1)) that result in non-compliance with any promulgated 

federal technology-based standard such as NSPS, NESHAPS, or MACT, a federal affirmative defense is 

available, pursuant to 40 CFR 70. To assert a federal affirmative defense, the permittee must use the 

procedures set forth in 40 CFR 70. The affirmative defense provisions described in 15 below may not be 

applied to any situation that caused the Facility to exceed any federally delegated regulation, including but 

not limited to NSPS, NESHAP, or MACT. 
Revision 4.2 

5/12/09 

15. For situations other than those covered by 14 above, an affirmative defense is available for a violation of a 

provision or condition of the operating permit only if: 

i. The violation occurred as a result of an equipment malfunction, an equipment start-up or 

shutdown, or during the performance of necessary equipment maintenance; and 

ii. The affirmative defense is asserted and established as required by N.J.S.A. 26:2C-19.1 through 

19.5 and any implementing rules. [N.J.A.C. 7:27-22.16(l)] 

16. Each permittee shall meet all requirements of the approved source emissions testing and monitoring 

protocol during the term of the operating permit. [N.J.A.C. 7:27-22.18(j)] 

The following paragraphs of this section are included for the permittee's convenience to remind them of their 

obligations with certain key applicable requirements. These paragraphs are not enforceable since they paraphrase 

areas of the operating permits rule. Also, these paragraphs do not reference all the applicable requirements with 

which the permittee must comply. 

17. Each owner and each operator of any facility, source operation, or activity to which this permit applies is 

responsible for ensuring compliance with all requirements of N.J.A.C. 7:27-22. If the owner and operator 

are separate persons, or if there is more than one owner or operator, each owner and each operator is jointly 

and severally liable for any fees due under N.J.A.C. 7:27-22, and for any penalties for violation of N.J.A.C. 

7:27-22. 

18. In the event of a challenge to any part of this operating permit, all other parts of the permit shall continue to 

be valid. 

19. The permittee shall ensure that no air contaminant is emitted from any significant source operation at a rate, 

calculated as the potential to emit, that exceeds the applicable threshold for reporting emissions set forth in 

the Appendix to N.J.A.C. 7:27-22, unless emission of the air contaminant is authorized by this operating 

permit. 

20. Consistent with the provisions of N.J.A.C. 7:27-22.3(e), the permittee shall ensure that all requirements of 

this operating permit are met. In the event that there are multiple emission limitations, monitoring, 

recordkeeping, and/or reporting requirements for a given source operation, the facility must comply with all 

requirements, including the most stringent. 

21. Consistent with the provisions of N.J.A.C. 7:27-22.9(c), the permittee shall use monitoring of operating 

parameters, where required by the compliance plan, as a surrogate for direct emissions testing or 

monitoring, to demonstrate compliance with applicable requirements. 

22. The permittee shall file a timely and complete application for: 

Administrative Amendments; 

Seven-Day-Notice changes; 

Minor Modifications; 

Significant Modifications; and 

Renewals. 

23. Process monitors must be operated at all times when the associated process equipment is operating except 

during outage time allowed by Department guidelines/procedures or as outlined in Technical Manual 1005. 

The permittee must keep a service log as required. 
Revision 4.2 

5/12/09 

Section F 

Facility Name: AES RED OAK LLC 

Program Interest Number: 18195 

Permit Activity Number: BOP090002 

STATE-ONLY APPLICABLE REQUIREMENTS 

N.J.A.C. 7:27-22.16(b)5 requires the Department to specifically designate as not being federally enforceable any 

permit conditions based only on applicable state requirements. The applicable state requirements to which this 

provision applies are listed in the table titled “State-Only Applicable Requirements.” 

STATE-ONLY APPLICABLE REQUIREMENTS 

The following applicable requirements are not federally enforceable: 

 SECTION SUBJECT ITEM ITEM # REF. #

 E --- 15 --- 

 G FC --- 3 

 G FC --- 10 

 G FC --- 18 
Revision 4.2 

5/12/09 

Section G 

 

Facility Name: AES RED OAK LLC 

Program Interest Number: 18195 

Permit Activity Number: BOP090002 

COMPLIANCE PLAN AND INVENTORIES 

• FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX 

• FACILITY SPECIFIC REQUIREMENTS (COMPLIANCE PLAN) 

• ATTACHMENTS TO THE FACILITY SPECIFIC REQUIREMENTS 

• FACILITY PROFILE (ADMINISTRATIVE INFORMATION) 

• REASON FOR APPLICATION 

• NON-SOURCE FUGITIVE EMISSIONS 

• INSIGNIFICANT SOURCE EMISSIONS 

• EQUIPMENT INVENTORY 

• EQUIPMENT DETAILS 

• CONTROL DEVICE INVENTORY 

• CONTROL DEVICE DETAILS 

• EMISSION POINT INVENTORY 

• EMISSION UNIT/BATCH PROCESS INVENTORY 

• SUBJECT ITEM GROUP INVENTORY 

• POTENTIAL TO EMIT – BATCH PROCESS INVENTORY 
Revision 4.2 

5/12/09 

Facility Name: AES RED OAK LLC 

Program Interest Number: 18195 

Permit Activity Number: BOP090002 

FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX 

Subject Item and Name Page Number

 Facility (FC): 

 FC 1 

Groups (GR) 

 GR1 – Facility Annual Emission Limit Cap for U1, U2, U3 and U7 6 

Emission Units (U):

 U1 – Combined Cycle Units - Three turbines each with a heat input of 2180 MMBTU/hr 

 OS Summary 13 

 OS1/OS4/OS7 Normal Operation 33 

 OS2/OS5/OS8 Startup 38 

 OS3/OS6/OS9 Shut down 40 

 U2 – Ten Cell Cooling Tower (Heat Input = 200,000 gal/min capacit 

 OS Summary 42 

 OS1 Normal Operation 43 

 U3 – 20,000 Gallon Ammonia Storage Tank 

 OS Summary 44 

U7 – Fuel Gas Heater (16 MMBTU/hr) 

 OS Summary 45 

 OS1 Normal Operation 46 

Note: See Attachments for additional requirements 
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Subject Item: FC

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 General Provisions: Defines numerous terms

used in N.J.A.C. 7:27. Specifies proceduresfor making confidentiality claims, certifyingapplications, reports, and other documentsto the Department, and requestingadjudicatory hearings and stays of theeffective date of departmental decisions.Also, provides provisions regardingapplicability, severability, and liberalconstruction of N.J.A.C. 7:27. [N.J.A.C.7:27- 1]

None. None. None.

2 Control and Prohibition of Open Burning:

Prohibits any person from open burning ofrubbish, garbage, trade waste, buildings,structures, leaves, other plant life andsalvage. Open burning of infested plant lifeor dangerous material may only beperformed with a permit from theDepartment. [N.J.A.C. 7:27- 2]

None. None. Obtain an 

occurrence [N.J.A.C. 

3 Prohibition of Air Pollution:

Notwithstanding compliance with othersubchapters of N.J.A.C. 7:27, no personshall suffer, allow, or permit to be emittedinto the outdoor atmosphere substances inquantities that result in air pollution asdefined at N.J.A.C. 7:27-5.1. Applicable toall facilities located in New Jersey.[N.J.A.C. 7:27- 5]

None. None. None.

4 Prevention and Control of Air Pollution

Control Emergencies: Requires that writtenStandby Plans, consistent with goodindustrial practice and safe operatingprocedures, be prepared for reducing theemission of air contaminants during periodsof an air pollution alert, warning, oremergency. Any person responsible for theoperation of a source of air contaminationnot set forth in Table 1 of N.J.A.C. 7:27-12is not required to prepare such a plan unlessrequested by the Department in writing.[N.J.A.C. 7:27-12]

None. None. Comply w

occurrence the Governwarning, oput the Stathe permitapplicable N.J.A.C. 7complied wpollution a[N.J.A.C. 

Page 1 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

5 Emission Offsets Rules. [N.J.A.C. 7:27-18] Other: When applying for minor/significant

modification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].

Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].

Comply woccurrence administraapplying fto N.J.A.Cmodificati7:27-22.24

6 Emissions Statements: Submit an annual

emission statement (if required)electronically to the NJDEP by May 15 ofeach year (or by mutually agreed upon date,but no later than June 15 of each year).[N.J.A.C. 7:27-21]

Other: The emission statement will be basedon monitoring, recording and recordkeepingof actual emissions, capture and controlefficiencies, process rate and operating datafor source operations with the potential toemit certain air contaminants. [N.J.A.C.7:27-21].

Other: The emission statement and allsupporting records shall be maintained onthe operating premises for a period of five(5) years from the due date of each emissionstatement. [N.J.A.C. 7:27-21].

Submit an Annually (15 or by anot later th[N.J.A.C. 

7 Compliance Certification: Submit annual

compliance certification for each applicablerequirement, pursuant to N.J.A.C.7:27-22.19(f), within 60 days after the endof each calendar year during which thispermit was in effect. [N.J.A.C. 7:27-22]

None. None. Submit an 

Annually tforms provdays after during whannual comperiod wilDecember DepartmenDepartmenhttp://wwwcomplianc [N.J.A.C

8 Prevention of Air Pollution from

Architectural Coatings and ConsumerProducts. [N.J.A.C. 7:27-23]

None. None. None.

9 Any operation of equipment which causes

off-property effects, including odors, orwhich might reasonably result in citizen'scomplaints shall be reported to theDepartment to the extent required by the AirPollution Control Act, N.J.S.A.26:2C-19(e). [N.J.S.A. 26:2C-19(e)]

Other: Observation of plant operations.[N.J.S.A. 26:2C-19(e)].

Other: Maintain a copy of all informationsubmitted to the Department. [N.J.S.A.26:2C-19(e)].

Notify by A person wcontaminawhich poshealth, wemight reasshall immeSuch notifthe Enviro927-6337. 

Page 2 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

10 Prevention of Significant Deterioration

(PSD). [40 CFR 52.21]

Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].

Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].

Comply woccurrence permittee complete asignificant N.J.A.C. 7

11 National Emission Standards for Hazardous

Air Pollutants (NESHAPS) for Asbestos. [40 CFR 61]

Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].

Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].

Comply woccurrence comply wiwhen conddemolition 61]

12 Protection of Stratospheric Ozone:1) If the

permittee manufactures, transforms,destroys, imports, or exports a Class I orClass II substance, the permittee is subjectto all the requirements as specified at 40CFR 82, Subpart A; 2) If the permitteeperforms a service on motor "fleet" vehicleswhen this service involves an ozonedepleting substance refrigerant (or regulatedsubstance) in the motor vehicle airconditioner (MVAC), the permittee issubject to all the applicable requirements asspecified at 40 CFR 82, Subpart B. 3) Thepermittee shall comply with the standardsfor labeling of products containing ormanufactured with ozone depletingsubstances pursuant to 40 CFR 82, SubpartE. 4). The permittee shall comply with thestandards for recycling and emissionreductions of Class I and Class IIrefrigerants or a regulated substitutesubstance during the service, maintenance,repair, and disposal of appliances pursuantto 40 CFR 82, Subpart F, except as providedfor motor vehicle air conditioners (MVACs)in Subpart B. 5) The permittee shall beallowed to switch from any ozone depletingsubstance to any alternative that is listed inthe Significant New Alternative Program(SNAP) promulgated pursuant to 40 CFR82, Subpart G. [40 CFR 82]

Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].

Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].

Comply woccurrence comply wiF, and G. 

Page 3 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

13 Deviation Report: In accordance with

N.J.A.C. 7:27-22.19(c) and 22.19(d)3, thepermittee shall submit to the Department, onforms provided by the Department, acertified six-month deviation report relatingto testing and monitoring required by theoperating permit, not including informationfor stack emissions testing or continuousemissions monitoring which have otherreporting schedules specified in the permit(normally, stack test report is submittedwithin 45 days of test completion andcontinuous monitor reporting is donequarterly). Pursuant to N.J.A.C.7:27-22.19(e), the six-month report mustaddress other specified monitoring,including continuous and periodicmonitoring requirements found in column 2and 3, entitled "Monitoring Requirement"and "Recordkeeping Requirement,"respectively, of the Facility SpecificRequirements section of this permit. Thesesix-month reports shall clearly identify alldeviations from operating permitrequirements, the probable cause of suchdeviations, and any corrective actions orpreventive measures taken. If no deviationsoccurred, the report should say so. Any"None" listed in the Submittal/ActionRequirement in the Operating Permit is notintended to override the six-month deviationreport. [N.J.A.C. 7.27-22.19(d)3, N.J.A.C.7.27-22.19(e), and [N.J.A.C. 7:27-22.19(c)]

None. Other: The permittee shall maintain

deviation reports for a period of five yearsfrom the date each report is submitted to theDepartment. [N.J.A.C. 7:27-22.19(a)].

Submit a rschedule. specified tthe operatiJanuary 1 submitted year, and fshall be sufollowing submitted Office and N.J.A.C. 7official. Fcan be fouthe followhttp://wwwcomplianc [N.J.A.C. 

14 No person shall combust used oil except as

authorized pursuant to N.J.A.C. 7:27-20.[N.J.A.C. 7:27-20.2]

None. None. Comply w

occurrence oil) either pursuant tpermit issto N.J.A.Capplicable

Page 4 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

15 Prevention of Accidental Releases: Facilities

producing, processing, handling or storing achemical, listed in the tables of 40 CFR Part68.130, and present in a process in aquantity greater than the listed ThresholdQuantity, shall comply with 40 CFR 68. [40CFR 68]

Other: Comply with 40 CFR 68. [40 CFR68].

Other: Comply with 40 CFR 68. [40 CFR68].

Other (prowith 40 CFApplicable 

16 For equipment subject to CO2 Budget

Trading Program, comply with N.J.A.C.7:27C. [N.J.A.C. 7:27C]

Other: See N.J.A.C. 7:27C. [N.J.A.C.7:27C].

Other: See N.J.A.C. 7:27C. [N.J.A.C.7:27C].

Comply woccurrence 

Page 5 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Subject Item: GR1 Facility Annual Emission Limit Cap for U1, U2, U3, and U7 combined

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 NOx (Total) <= 292.4 tons/yr. Maximum

allowable emission limit for facility basedon sum of annual limits from emission unitsU1, U2, U3, and U7. [N.J.A.C.7:27-22.16(a)]

NOx (Total): Monitored by calculationseach month during operation, based on onecalendar year. The annual emissions of totalNOx shall be calculated as follows:Total Facility Monthly NOx Emissions =[tons of NOx during the normal operatingscenario per month (from CEM data)] +[startup hours per month x 111 lbs/hr x 1ton/2000 lbs.] + [1.917 lbs/hr for the fuelgas heater x hours of operation per month x1 ton/2000 lbs.]Total Facility Annual NOx Emissions is thesum of the monthly calculated values.The permittee may use CEM data todemonstrate compliance. [N.J.A.C.7:27-22.16(a)]

NOx (Total): Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]

None.

2 CO <= 704.8 tons/yr. Maximum allowable

emission limit for facility based on sum ofannual limits from emission units U1, U2,U3, and U7. [N.J.A.C. 7:27-22.16(e)]

The annual emissions of total CO shall becalculated as follows:Total Facility Monthly CO Emissions =[tons of CO during the normal operatingscenario (from CEM data)] + [startup hoursfor three turbines per month x 504 lbs/hr x 1ton/2000 lbs.] + [ 0.88 lbs/hr for the fuelgas heater x hours of operation per month x1 ton/2000 lbs.]Total Facility Annual CO Emissions is thesum of the monthly calculated values.The permittee may use CEM data todemonstrate compliance. CO: Monitored bycalculations each month during operation,based on one calendar year. [N.J.A.C.7:27-22.16(a)]

CO: Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(e)]

None.

Page 6 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

3 VOC (Total) <= 102.9 tons/yr. Maximum

allowable emission limit for facility basedon sum of annual limits from emission unitsU1, U2, U3, and U7. [N.J.A.C.7:27-22.16(e)]

VOC (Total): Monitored by calculationseach month during operation, based on onecalendar year The annual emissions of totalVOC shall be calculated as follows:Total Facility Monthly VOC Emissions =[MMft^3 of natural gas burned for all threeturbines for each operating scenario permonth x 1,000 BTU/ft^3 x 0.00405lbs./MMBtu x 1 ton/2,000 lbs.] +[startuphours for three turbines per month x 87lbs/hr x 1 ton/2,000 lbs.] + [0.11 lbs./hr forthe fuel gas heater x hours of operation permonth x 1ton/2,000 lbs.]Total Facility Annual VOC Emissions is thesum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor (lb./MMBtu) determined asthe average value in compliance stacktesting may also be substituted for thedefault emission factor, at the discretion ofthe permittee.Startup is defined as being the periodbeginning when fuel is first fired and endingwhen emissions are within permit limits.[N.J.A.C. 7:27-22.16(a)]

VOC (Total): Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]

None.

Page 7 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

4 SO2 <= 104.1 tons/yr. Maximum allowable

emission limit for facility based on sum ofannual limits from emission units U1, U2,U3, and U7. [N.J.A.C. 7:27-22.16(a)]

SO2: Monitored by calculations each monthduring operation, based on one calendaryear The annual emissions of total SO2 shallbe calculated as follows:Total Facility Monthly SO2 Emissions =[MMft^3 of natural gas burned for all threeturbines for each operating scenario permonth x 1,000 BTU/ft^3 x 0.0043lbs/MMBtu x 1 ton/2,000 lbs] + [0.069lbs/hr for the fuel gas heater x hours ofoperation per month x 1ton/2,000 lbs]Total Facility Annual SO2 Emissions is thesum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor (lb/mmBtu) determined asthe average value in compliance stacktesting may also be substituted for thedefault emission factor, at the discretion ofthe permittee.The permittee may use CEM data todemonstrate compliance. [N.J.A.C.7:27-22.16(a)]

SO2: Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(e)]

None.

Page 8 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

5 TSP <= 345.1 tons/yr. Maximum allowable

emission limit for facility based on sum ofannual limits from emission units U1, U2,U3, and U7. [N.J.A.C. 7:27-22.16(a)]

TSP: Monitored by calculations each monthduring operation, based on one calendaryear The annual emissions of total TSP shallbe calculated as follows:Total Facility Monthly TSP Emissions =[MMft^3 of natural gas burned for all threeturbines for each operating scenario permonth x 1,000 BTU/ft^3 x 0.01351lbs./MMBtu x 1 ton/2,000 lbs.] + [1.316tons per month for the cooling tower] +[0.12 lbs/hr for the fuel gas heater x hours ofoperation per month x 1ton/2,000 lbs.]Total Facility Annual TSP Emissions is thesum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor (lb/MMBtu) determined asthe average value in compliance stacktesting may also be substituted for thedefault emission factor, at the discretion ofthe permittee. The permittee may use CEMdata to demonstrate compliance. [N.J.A.C.7:27-22.16(a)]

TSP: Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(e)]

None.

Page 9 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

6 PM-10 (Total) <= 345.1 tons/yr. Maximum

allowable emission limit for facility basedon sum of annual limits from emission unitsU1, U2, U3, and U7. [N.J.A.C.7:27-22.16(a)]

PM-10 (Total): Monitored by calculationseach month during operation, based on onecalendar year The annual emissions of totalPM10 shall be calculated as follows:Total Facility Monthly PM10 Emissions =[MMft^3 of natural gas burned for all threeturbines for each operating scenario permonth x 1,000 BTU/ft^3 x 0.01351lbs./MMBtu x 1 ton/2,000 lbs.] + [1.316tons per month for the cooling tower] +[0.12 lbs/hr for the fuel gas heater x hours ofoperation per month x 1ton/2,000 lbs.]Total Facility Annual PM10 Emissions isthe sum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor (lb/MMBtu) determined asthe average value in compliance stacktesting may also be substituted for thedefault emission factor, at the discretion ofthe permittee. The permittee may use CEMdata to demonstrate compliance. [N.J.A.C.7:27-22.16(a)]

PM-10 (Total): Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]

None.

Page 10 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

7 Ammonia <= 347 tons/yr. Maximum

allowable emission limit for facility basedon sum of annual limits from emission unitsU1, U2, and U3. [N.J.A.C. 7:27-22.16(a)]

Ammonia: Monitored by calculations eachmonth during operation, based on onecalendar year Annual emissions of totalAmmonia shall be calculated as follows:Total Facility Monthly Ammonia Emissions=[MMft^3 of natural gas burned per year forall three turbines for each operating scenarioper month x 1000 Btu/ft^3 x 0.015lbs./MMBtu x 1 ton/2,000 lbs.]Total Facility Annual Ammonia Emissionsis the sum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor (lb/MMBtu) determined asthe average value in compliance stacktesting may also be substituted for thedefault emission factor, at the discretion ofthe permittee. [N.J.A.C. 7:27-22.16(e)]

Ammonia: Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]

None.

Page 11 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 SO3 and H2SO4, as converted and

expressed as H2SO4 <= 63.6 tons/yr.Maximum allowable emission limit forfacility based on sum of annual limits fromemission units U1, U2, U3, and U7.[N.J.A.C. 7:27-22.16(a)]

SO3 and H2SO4, as converted andexpressed as H2SO4: Monitored bycalculations each month during operation.The annual emissions of total Sulfur shall becalculated as follows:Total Facility Monthly Sulfur Emissions =[MMFt^3 of natural gas burned for all threeturbines for each operating scenario permonth x 1000 BTU/ft^3 x 0.00263 lbs./MMBtu x 1 ton/ 2000 lbs.]Total Facility Annual Sulfur Emissions isthe sum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor (lb./MMBtu) determined asthe average value in compliance stacktesting may also be substituted for thedefault emission factor, at the discretion ofthe permittee. [N.J.A.C. 7:27-22.16(e)]

SO3 and H2SO4, as converted andexpressed as H2SO4: Recordkeeping bymanual logging of parameter each monthduring operation showing the calculatedvalue for the month and sum-to-date.[N.J.A.C. 7:27-22.16(e)]

None.

Page 12 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Emission Unit: U1 Combined Cycle Units - Three turbines each with a heat input of 2180 MMBtu/hr

Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Continuously monitor NOx, CO and O2

emitted from emission points PT1, PT2 andPT3, using a Continuous EmissionMonitoring (CEM) system. Emissions shallbe monitored during all operation of theturbine. [N.J.A.C. 7:27-22.16(o)]

Monitored by continuous emissionmonitoring system continuously. [N.J.A.C.7:27-22.16(o)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]

CEMS/COsubmit a Psubmit resschedule. 

OS Summary

Page 13 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

2 Conduct a comprehensive stack test at

emission points PT1, PT2 and PT3 at least18 months prior to the expiration date of theapproved operating permit to demonstratecompliance with the NOx, CO, VOC, SO2,TSP, PM-10, Ammonia, and (SO3 andH2SO4) emission limits.Three tests shall be conducted at worst-casepermitted operating conditions for thecorresponding test, such as ambient (relativehumidity and temperature) conditions, withregard to meeting the applicable emissionstandards, but without creating an unsafecondition. The Permittee shall submit toBTS all data necessary to substantiate theambient conditions. The testing shall beconducted in accordance with a protocolapproved by Chief, BTS. [N.J.A.C.7:27-22.16(a)] [N.J.A.C. 7:27-22.16(a)]

Monitored by stack emission testing at theapproved frequency Unless otherwiseapproved in the stack test protocol or by theDepartment, each test run shall be 60minutes in sampling duration. Complianceperiod shall be as specified in themonitoring requirement for each applicableemission limit.Stack tests shall be conducted for NOx, CO,VOC, SO2, TSP, PM-10, Ammonia, and(SO3 and H2SO4) emissions whilecombusting natural gas. [N.J.A.C.7:27-22.16(o)]

Recordkeeping by stack test results at theapproved frequency. [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule Sconduct teapproved protocol to (BTS) at Pleast 30 mapproved Within 30 permittee 609-530-4acceptable must be susummary tprotocol, mEnforcemeperforming N.J.A.C. 7must be ceengineer oA copy of must be surenewal apprior to exThe test recorrected tlb/MWHr lb/MMBTFor the puwith NSPS corrected t7:27-22.187:27-22.18

Page 14 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

3 Opacity <= 20 %. No person shall cause,

suffer, allow or permit smoke greater than20 percent opacity, exclusive of visiblecondensed water vapor, to be emitted intothe outdoor air from the combustion of fuelin any stationary internal combustion engineor any stationary turbine engine for a periodof more than 10 consecutive seconds.[N.J.A.C. 7:27- 3.5]

None. None. None.

4 Particulate Emissions <= 218 lb/hr

Particulate emission limit from thecombustion of fuel based on rated heat inputof source. [N.J.A.C. 7:27- 4.2(a)]

None. None. None.

5 CO <= 250 ppmvd @ 15% O2. [N.J.A.C.

7:27-16.9(b)]

CO: Monitored by continuous emissionmonitoring system continuously, based onone calendar day , not including periods ofdowntime. [N.J.A.C. 7:27-16.23(a)1]

CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

6 VOC (Total) <= 50 ppmvd @ 15% O2.

[N.J.A.C. 7:27-16.9(c)]

VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (For stack testing details, see U1OS Summary, Ref #2). [N.J.A.C.7:27-16.23(a)1]

VOC (Total): Recordkeeping by stack testresults prior to permit renewal (For stacktesting details, see U1 OS Summary, Ref#2). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule (OS Summ7:27-22.16

7 NOx (Total) <= 1.3 lb/MW-hr. NOx RACT

emission limit for non-HEDD turbinesapplies during all periods of natual gascombustion. To calculate lb/MWh, for unitswhere energy is used for other than electricgeneration, for example combined heat andpower unit, that useful energy should beconverted to equivalent MWh and added tothe electric output. Emission rate is basedon net energy output (both electric anduseful heat). N.J.A.C. 7:27-19.5(d) and.[N.J.A.C. 7:27-19.5(f)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a calendar day (in ozone season) or30 day rolling (at other times) average. (seeU1 / OS Summary / Ref. #1). [N.J.A.C.7:27-22.16(o)]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. (see U1 / OSSummary / Ref. #1). [N.J.A.C.7:27-22.16(o)]

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

Page 15 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 NOx (Total) <= 1.3 lb/MW-hr. NOx RACT

emission limit for non-HEDD turbinesapplies during all periods of natual gascombustion. To calculate lb/MWh, for unitswhere energy is used for other than electricgeneration, for example combined heat andpower unit, that useful energy should beconverted to equivalent MWh and added tothe electric output. Emission rate is basedon net energy output (both electric anduseful heat). N.J.A.C. 7:27-19.5(d) and.[N.J.A.C. 7:27-19.5(f)]

NOx (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs. (see U1 / OS Summary / Ref. #2).[N.J.A.C. 7:27-22.16(o)]

NOx (Total): Recordkeeping by stack testresults at the approved frequency. (see U1 /OS Summary / Ref. #2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule. [N.J.A.C. 

9 The Permittee shall adjust the combustion

process in accordance with the procedure setforth at N.J.A.C. 7:27-19.16, in order tooptimize the emission of NOx, CO andVOC. Adjustment of the combustionprocess shall be carried out according tomanufacturer's recommended proceduresand maintenance schedules for the turbine.[N.J.A.C. 7:27-16.9(f)2, N.J.A.C.7:27-19.5(e)2] & [N.J.A.C. 7:27-19.16(g)]

Monitored by continuous emissionmonitoring system upon performingcombustion adjustment Or PeriodicEmission Monitoring. [N.J.A.C.7:27-19.16(h)]

Recordkeeping by data acquisition system(DAS) / electronic data storage uponperforming combustion adjustment ormanual logging of parameter. All recordsshall be kept in a permanent form suitablefor inspections, retained for a minimum of 5years, and made readily accessible to theDepartment, upon request.The owner or operator shall record thefollowing information for each adjustment:1. The date of the adjustment and the timesat which it began and ended;2. The name, title and affiliation of theperson who performed the procedure andadjustment;3. The type of procedure and maintenanceperformed;4. The concentration of NOx, CO and O2measured before and after the adjustmentwas made; and5. The type and amount of fuel used sincethe last combustion adjustment wasperformed. [N.J.A.C. 7:27-19.16(h)]

None.

Page 16 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

10 An exceedance of an emission limit that

occurs during an adjustment of thecombustion process under N.J.A.C.7:27-19.16(g) is not a violation of thissubchapter if it occurs as a result of theadjustment. After the combustionadjustment has been completed, themaximum emission rate of any contaminantshall not exceed the maximum allowableemission rate applicable under thissubchapter or under an operating permitissued pursuant to N.J.A.C. 7:27-22 or anapplicable certificate issued pursuant toN.J.A.C. 7:27-8. [N.J.A.C. 7:27-19.16(f)]

None. None. None.

11 NOx (Total) <= 284 tons/yr. Maximum

annual emission limit from preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]

NOx (Total): Monitored by calculationseach month during operation, based on onecalendar year. The annual emissions of totalNOx shall be calculated as follows:Total Monthly NOx Emissions =[tons of NOx during the normal operatingscenario per month (from CEM data)] +[startup hours per month x 111 lbs/hr x 1ton/2000 lbs.]Total Annual NOx Emissions is the sum ofthe monthly calculated values.See U1, OS Summary Ref #17 for Startupperiod definition.The permittee may use CEM data todemonstrate compliance. [N.J.A.C.7:27-22.16(e)]

NOx (Total): Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]

None.

Page 17 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

12 CO <= 701.1 tons/yr. Maximum annual

emission limit from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

The annual emissions of total CO shall becalculated as follows:Total Monthly CO Emissions =[tons of CO during the normal operatingscenario per month (from CEM data)] +[startup hours per month x 504 lbs/hr x 1ton/2000 lbs.]Total Annual CO Emissions is the sum ofthe monthly calculated values.See U1, OS Summary Ref #17 for Startupperiod definition.The permittee may use CEM data todemonstrate compliance. CO: Monitored bycalculations each month during operation,based on one calendar year. [N.J.A.C.7:27-22.16(e)]

CO: Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(e)]

None.

Page 18 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

13 VOC (Total) <= 102.5 tons/yr. Maximum

annual emission limit from preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]

VOC (Total): Monitored by calculationseach month during operation, based on onecalendar year The annual emissions of totalVOC shall be calculated as follows:Total Monthly VOC Emissions =[MMft^3 of natural gas burned for all threeturbines per month x 1,000 BTU/ft^3 x0.00405 lbs./MMBtu x 1 ton/2,000 lbs.] +[startup hours per month x 87 lbs/hr x 1ton/2,000 lbs.]Total Annual VOC Emissions is the sum ofthe monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor of 0.00038 lb./MMBtudetermined as the average value incompliance stack testing, may also besubstituted for the default emission factor, atthe discretion of the permittee.See U1, OS Summary Ref #17 for Startupperiod definition. [N.J.A.C. 7:27-22.16(e)]

VOC (Total): Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]

None.

Page 19 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

14 SO2 <= 103.8 tons/yr. Maximum annual

emission limit from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

SO2: Monitored by calculations each monthduring operation, based on one calendaryear The annual emissions of total SO2 shallbe calculated as follows:Total Monthly SO2 Emissions =[MMft^3 of natural gas burned for all threeturbines per month x 1,000 BTU/ft^3 x0.0043 lbs/MMBtu x 1 ton/2,000 lbs].Total Annual SO2 Emissions is the sum ofthe monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor of 0.0004 lb/mmBtudetermined as the average value incompliance stack testing, may also besubstituted for the default emission factor, atthe discretion of the permittee. [N.J.A.C.7:27-22.16(e)]

SO2: Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(e)]

None.

Page 20 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

15 TSP <= 328.8 tons/yr. Maximum annual

emission limit from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

TSP: Monitored by calculations each monthduring operation, based on one calendaryear The annual emissions of total TSP shallbe calculated as follows:Total Monthly TSP Emissions =[MMft^3 of natural gas burned for all threeturbines per month x 1,000 BTU/ft^3 x0.01351 lbs./MMBtu x 1 ton/2,000 lbs.]Total Annual TSP Emissions is the sum ofthe monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor of 0.00133 lb/MMBtudetermined as the average value incompliance stack testing, may also besubstituted for the default emission factor, atthe discretion of the permittee. [N.J.A.C.7:27-22.16(e)]

TSP: Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(e)]

None.

Page 21 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

16 PM-10 (Total) <= 328.8 tons/yr. Maximum

annual emission limit from preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]

PM-10 (Total): Monitored by calculationseach month during operation, based on onecalendar year The annual emissions of totalPM-10 shall be calculated as follows:Total Monthly PM-10 Emissions =[MMft^3 of natural gas burned for all threeturbines per month x 1,000 BTU/ft^3 x0.01351 lbs./MMBtu x 1 ton/2,000 lbs.]Total Annual PM10 Emissions is the sum ofthe monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor of 0.00477 lb/MMBtudetermined as the average value incompliance stack testing, may also besubstituted for the default emission factor, atthe discretion of the permittee. [N.J.A.C.7:27-22.16(e)]

PM-10 (Total): Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]

None.

Page 22 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

17 Ammonia <= 347 tons/yr. Maximum annual

emission limit from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

Ammonia: Monitored by calculations eachmonth during operation, based on onecalendar year Annual emissions of totalAmmonia shall be calculated as follows:Total Monthly Ammonia Emissions=[MMft^3 of natural gas burned per monthfor all three turbines x 1000 Btu/ft^3 x0.0135 lbs./MMBtu x 1 ton/2,000 lbs.]Total Annual Ammonia Emissions is thesum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor of 0.0003 lb/MMBtudetermined as the average value incompliance stack testing, may also besubstituted for the default emission factor, atthe discretion of the permittee. [N.J.A.C.7:27-22.16(e)]

Ammonia: Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]

None.

Page 23 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

18 SO3 and H2SO4, as converted and

expressed as H2SO4 <= 63.6 tons/yr.Maximum annual emission limit frompreconstruction permit. [N.J.A.C.7:27-22.16(e)]

SO3 and H2SO4, as converted andexpressed as H2SO4: Monitored bycalculations each month during operation,based on one calendar year. The annualemissions of total Sulfur shall be calculatedas follows:Total Monthly Sulfur Emissions =[MMFt^3 of natural gas burned for all threeturbines per month x 1000 BTU/ft^3 x0.00263 lbs./ MMBtu x 1 ton/ 2000 lbs.]Total Annual Sulfur Emissions is the sumof the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor of 0.0003 lb./MMBtudetermined as the average value incompliance stack testing, may also besubstituted for the default emission factor, atthe discretion of the permittee. [N.J.A.C.7:27-22.16(e)]

SO3 and H2SO4, as converted andexpressed as H2SO4: Recordkeeping bymanual logging of parameter each monthduring operation showing the calculatedvalue for the month and sum-to-date.[N.J.A.C. 7:27-22.16(e)]

None.

19 Ammonia <= 10 ppmdv. [N.J.A.C.

7:27-22.16(e)]

Ammonia: Monitored by stack emissiontesting prior to permit renewal, based oneach of three Department validated stack testruns (For stack testing details, see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]

Ammonia: Recordkeeping by stack testresults prior to permit renewal (For stacktesting details, see U1 OS Summary, Ref#2). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule (OS Summ7:27-22.16

20 Only natural gas shall be combusted into the

stationary gas turbine. [N.J.A.C.7:27-22.16(e)]

None. None. None.

Page 24 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

21 Natural Gas Usage <= 63,122.16

MMft^3/yr. [N.J.A.C. 7:27-22.16(a)]

Natural Gas Usage: Monitored by fuelflow/firing rate instrument continuously,based on a consecutive 365 day period(rolling 1 day basis). The permittee shallinstall and operate a running gasuse-totallizing meter on each turbine tomonitor the consumption of natural gas, perturbine, in any 365 consecutive days period.The running gas meter shall be installed,operated, and calibrated according tomanufacturer's recommendations. [N.J.A.C.7:27-22.16(o)]

Natural Gas Usage: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. Compliance shall bedetermined based on any 365 consecutiveday period. Cubic feet per any 365consecutive days period shall be calculatedby the sum of the cubic feet calculatedduring any one day added to the sum of thecubic feet calculated during the preceding364 days. This procedure will begin with thefirst day following the final issuance of theOperating permit. This accounting will notinclude cubic feet consumed prior to theapproval of the Operating Permit. [N.J.A.C.7:27-22.16(o)]

None.

22 Start-up Period: Start-up commences with

the initiation of the combustion of fuel inthe combustion turbine and concludes whenthe turbine reaches a steady state operationload. Start up period shall not exceed 21hours total for the combustion turbine units.[N.J.A.C. 7:27-22.16(e)]

Start-up Period: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]

Start-up Period: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(o)]

None.

23 Shutdown Period: Combustion turbine

shutdown is defined as the period of timefrom the initial lowering of combustionturbine output of the base load until fuelflow is completely off and combustion hasceased. [N.J.A.C. 7:27-22.16(e)]

Shutdown Period: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]

Shutdown Period: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(o)]

None.

24 Except during startup and shutdown, the

SCR system (including the ammoniainjection) and the oxidation catalyst shall beoperational at all times the turbine isoperating. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

25 The SCR catalyst array(s) shall be

maintained and replaced in accordance withthe recommendations of the manufacturer,and as necessary based on emission levelsindicated through continuous/portableemission monitoring. [N.J.A.C.7:27-22.16(e)]

Other: Monitored by emission levelsindicated through continuous/portableemission monitoring.[N.J.A.C.7:27-22.16(o)].

Other: Maintain the SCR catalystsmaintenance and replacementrecords.[N.J.A.C. 7:27-22.16(o)].

None.

Page 25 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

26 Ammonia Flow Rate to SCR <= 72.11

gal/hr (19% Ammonium Hydroxide solutionin water). [N.J.A.C. 7:27-22.16(e)]

Ammonia Flow Rate to SCR: Monitored bymaterial feed/flow monitoring continuously.[N.J.A.C. 7:27-22.16(o)]

Ammonia Flow Rate to SCR:Recordkeeping by data acquisition system(DAS) / electronic data storage at theapproved frequency. [N.J.A.C.7:27-22.16(o)]

None.

27 The oxidizer catalyst array(s) shall be

maintained and replaced or changed inaccordance with the recommendations of themanufacturer. [N.J.A.C. 7:27-22.16(e)]

Other: Monitored by emission levelsindicated through continuous emissionmonitoring.[N.J.A.C. 7:27-22.16(o)].

Other: Maintain the oxidation catalystsmaintenance, replacement or changingrecords including date and time ofmaintenance, replacement or change of theoxidation catalyst.[N.J.A.C. 7:27-22.16(o)].

None.

28 Minimum VOC Destruction and Removal

Efficiency >= 80 %. The catalytic oxidizershall be designed for a minimum VOCdestruction and removal efficiency.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

29 Temperature at Catalyst Bed <= 800 degrees

F , while working at 100% load. [N.J.A.C.7:27-22.16(a)]

Temperature at Catalyst Bed: Monitored bytemperature instrument continuously.[N.J.A.C. 7:27-22.16(o)]

Temperature at Catalyst Bed:Recordkeeping by strip chart continuously.[N.J.A.C. 7:27-22.16(o)]

None.

30 The permittee shall submit an Excess

Emission Monitoring Performance Report tothe Department for review and approval[N.J.A.C. 7:27-22.16(e)]

None. None. Submit an 

Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

Page 26 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

31 The owner or operator shall develop a

QA/QC plan for all CEMS/COMS requiredby this permit. This QA/QC plan shallincorporate at a minimum those proceduresoutlined in 40 CFR, Part 60, Appendix Fand/or 40 CFR, Part 75, Appendix B forCEMS and those procedures outlined in 40CFR, Part 60, Appendix B, SpecificationOne and 40 CFR, Part 51, Proposed RM203 for COMS, published DepartmentTechnical Manuals or other proceduresapproved in writing by the Department. TheQA/QC plan shall designate a coordinatorfor the facility who is responsible to ensurethat the QA/QC plan is implemented. TheDepartment reserves the right to require theQA/QC plan to be revised at any time basedon the results of quarterly EEMPR reviews,inspections, audits or any other informationavailable to the Department. All proceduresoutlined in the QA/QC plan shall commenceupon the completion date of the PST. Allredundant CEMS/COMS must undergo theQA/QC procedure. [N.J.A.C. 7:27-22.16(a)][N.J.A.C. 7:27-22.16(a)]

Other: The QA/QC coordinator shall beresponsible for reviewing the QA/QC planon an annual basis.[N.J.A.C. 7:27-22.16(o)].

Other: Maintain readily accessible recordsof the QA/QC plan including QA date andquarterly reports.[N.J.A.C. 7:27-22.16(o)].

Submit a rOctober 3preceding begin on JOctober 1data shall reports anQA data mDepartmen7:27-22.16

32 All requests, reports, applications,

submittals, and other communications to theAdministrator pursuant to Part 60 shall besubmitted in duplicate to the RegionalOffice of US Environmental ProtectionAgency. Submit information to: Region II,Director, Air and Waste ManagementDivision, US Environmental ProtectionAgency, 21st Floor, 290 Broadway, NewYork, NY 10007. [40 CFR 60.4(a)]

None. None. Submit a r

schedule tCFR 60. [

33 Copies of all information submitted to EPA

pursuant to 40 CFR Part 60, must also besubmitted to the appropriate RegionalEnforcement Office of NJDEP. [40 CFR60.4(b)]

None. None. Submit a r

to NJDEP Office, 1 PCamden, N

Page 27 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

34 The owner or operator subject to the

provisions of 40 CFR Part 60 shall furnishthe Administrator written notification or, ifacceptable to both the Administrator and theowner or operator of a source, electronicnotification, of the date of construction orreconstruction of an affected facility asdefined under 40 CFR Part 60 Subpart A.Notification shall be postmarked no laterthan 30 days after such date. [40 CFR60.7(a)(1)]

None. None. Submit no

event to ERegional Erequired b60.7(a)(1)

35 The owner or operator subject to the

provisions of 40 CFR Part 60 shall furnishthe Administrator written notification or, ifacceptable to both the Administrator and theowner or operator of a source, electronicnotification, of the actual date of initialstartup of an affected facility postmarkedwithin 15 days after such date. [40 CFR60.7(a)(3)]

None. None. Submit no

event to ERegional Erequired b60.7(a)(3)

36 The owner or operator subject to the

provisions of 40 CFR Part 60 shall furnishthe Administrator written notification or, ifacceptable to both the Administrator and theowner or operator of a source, electronicnotification, of any physical or operationalchange to an existing facility which mayincrease the emission rate of any airpollutant to which a standard applies, unlessthat change is specifically exempted underan applicable subpart or in section 60.14(e).The notification shall include informationdescribing the precise nature of the change,present and proposed emission controlsystems, productive capacity of facilitybefore and after the change and the expectedcompletion date of the change. Notificationshall be postmarked within 60 days or assoon as practicable before any change iscommenced. The Administrator mayrequest additional relevant informationsubsequent to this notice. [40 CFR60.7(a)(4)]

None. None. Submit no

event. Subdays prior commence60.7(a)(4)

Page 28 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

37 The owner or operator shall furnish the

Administrator written notification as follows:A notification of the date upon whichdemonstration of the continuous emissionmonitoring system performance commencesin accordance to 40 CFR 60.13(c). Thenotification shall be postmarked no less than30 days prior to such date. [40 CFR60.7(a)(5)]

Submit noOctober 3preceding begin on JOctober 1approval. 

38 The owner or operator shall maintain

records of the occurrence and duration ofany startup, shutdown, or malfunction in theoperation of an affected facility, anymalfunction of air pollution controlequipment or any periods during whichcontinuous monitoring system or monitoringdevice is inoperative. [40 CFR 60.7(b)]

None. Recordkeeping by manual logging of

parameter upon occurrence of event. Therecords should be kept in a permanent formsuitable for inspections. [40 CFR 60.7(b)]

None.

39 Each owner or operator required to install a

continuous monitoring device shall submitan excess emissions and monitoring systemsperformance report (excess emissions aredefined in applicable subparts) and/or asummary report form (see section 60.7(d))to the Administrator semiannually, exceptwhen: more frequent reporting isspecifically required by an applicablesubpart; or the Administrator, on acase-by-case basis, determines that morefrequent reporting is necessary to accuratelyassess the compliance status of the source.All reports shall be postmarked by the 30thday following the end of each six-monthperiod. [40 CFR 60.7(c)]

None. Other: Written reports of excess emissions

shall include the following information: (1)The magnitude of excess emissionscomputed in accordance with section60.13(h), any conversion factor(s) used, andthe date and time of commencement andcompletion of each time period and excessemissions. The process operating timeduring the reporting period. (2) Specificidentification of each period of excessemissions that occurs during startups,shutdowns, and malfunctions of the affectedfacility. The nature and cause of anymalfunction (if known), the corrective actiontaken or preventative measures adopted. (3)The date and time identifying each periodduring which the continuous monitoringsystem was inoperative except for zero andspan checks and the nature of the systemrepairs or adjustments. (4) When no excessemissions have occurred or the continuousmonitoring system(s) have not beeninoperative, repaired, or adjusted, suchinformation shall be stated in the report. [40CFR 60.7(c)].

Submit an Monitorin(EEMPR)30th day operformanpostmarkeend of eacshall be suAdministrEnforcemeformat spe40 CFR P

Page 29 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

40 The owner or operator shall maintain a file,

suitable for inspection, of all monitoringmeasurements as indicated inRecordkeeping Requirement column. [40CFR 60.7(f)]

None. Other: The file shall include all

measurements (including continuousmonitoring system, monitoring device, andperformance testing measurements), allcontinuous monitoring system performanceevaluations, all continuous monitoringsystem or monitoring device calibrationchecks, all adjustments/maintenanceperformed on these systems or devices, andall other information required by 40 CFRPart 60 recorded in a permanent formsuitable for inspection. [40 CFR 60.7(f)].

None.

41 At all times, including periods of start-up,

shutdown, and malfunction, owners andoperators shall, to the extent practicable,maintain and operate any affected facilityincluding associated air pollution controlequipment in a manner consistent with goodair pollution control practice for minimizingemissions. Determination of whetheracceptable operating and maintenanceprocedures are being used will be based oninformation available to the Administratorwhich may include, but is not limited to,monitoring results, opacity observations,review of operation and maintenanceprocedures, and inspection of the source.[40 CFR 60.11(d)]

None. None. None.

42 No owner or operator subject to NSPS

standards in Part 60, shall build, erect,install, or use any article, machine,equipment or process, the use of whichconceals an emission which wouldotherwise constitute a violation of anapplicable standard. Such concealmentincludes, but is not limited to, the use ofgaseous diluents to achieve compliance withan opacity standard or with a standard whichis based on the concentration of a pollutantin the gases discharged to the atmosphere.[40 CFR 60.12]

None. None. None.

Page 30 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

43 The owner or operator shall perform zero

and span adjustments daily for continuousemission monitors and continuous opacitymonitors following procedures outlined in40 CFR Part 60.13(d)1 & 2. [40 CFR60.13(d)]

None. Maintain records in accordance with 40

CFR 60.7(f). Recordkeeping by strip chart,round chart or data acquisition (DAS)system / electronic data storage at theapproved frequency. [40 CFR 60.13(d)]

None.

44 Except for system breakdowns, repairs,

calibration checks, and zero and spanadjustments, all continuous monitoringsystems measuring emissions except opacityshall be in continuous operation. They shallcomplete a minimum of one cycle ofoperation (sampling, analyzing and datarecording) for each successive 15-minuteperiod. [40 CFR 60.13(e)(2)]

Other: See Applicable Requirement. [40CFR 60.13(e)(2)].

Other: See Applicable Requirement. [40CFR 60.13(e)(2)].

None.

45 The owner or operator shall reduce all

continuous monitoring systems (other thanopacity) data to 1-hour averages which shallbe computed from four or more data pointsequally spaced over each 1-hour period.Data recorded during periods of continuousmonitoring system breakdowns, repairs,calibration checks, and zero and spanadjustments shall not be included in the dataaverages computed under this paragraph.For owners and operators complying withthe requirements in 40 CFR 60.7(f)(1) or(2), data averages must include any datarecorded during periods of monitorbreakdown or malfunction. An arithmeticor integrated average of all data may beused. The data may be recorded in reducedor nonreduced form (e.g., ppm pollutant andpercent O2 or ng of pollutant per J of heatinput). All excess emissions shall beconverted into units of the standard usingthe applicable conversion proceduresspecified in subparts. After conversion intounits of the standard, the data may berounded to the same number of significantdigits as used in the applicable subparts tospecify the emission limit (e.g. rounded tothe nearest 1 percent opacity). [40 CFR60.13(h)]

None. Recordkeeping by strip chart, round chart or

data acquisition (DAS) system / electronicdata storage continuously. The data may berecorded in reduced or non-reduced form.[40 CFR 60.13(h)]

None.

Page 31 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

46 Changes in time periods for submittal of

information and postmark deadlines set forthin this subpart, may be made only uponapproval by the Administrator and shallfollow procedures outlined in 40 CFR Part60.19. [40 CFR 60.19]

None. None. None.

47 NOx (Total) <= 75 ppmvd @ 15% O2. [40

CFR 60.332(a)(1)]

NOx (Total): Monitored by stack emissiontesting once initially, based on any 60minute period. Test methods andprocedures shall be consistent with therequirements of 40 CFR Part 60.335 [40CFR 60.335]

NOx (Total): Recordkeeping by stack testresults initial calculations only no later than45 days after the completion of stack testing.[40 CFR 60.335]

None.

48 Sulfur Content in Fuel <= 0.8 % by weight.

No owner or operator subject to theprovisions of this subpart shall burn any fuelwhich contains total sulfur in excess of 0.8percent by weight (8000 ppmw). [40 CFR60.333(b)]

Other: the owner or operator may elect notto monitor the total sulfur content of thegaseous fuel combusted in the turbine, if thegaseous fuel is demonstrated to meet thedefinition of natural gas in ?60.331(u),regardless of whether an existing customschedule approved by the administrator forsubpart GG requires such monitoring. Theowner or operator shall use one of thefollowing sources of information to makethe required demonstration:(i) The gas quality characteristics in acurrent, valid purchase contract, tariff sheetor transportation contract for the gaseousfuel, specifying that the maximum totalsulfur content of the fuel is 20.0 grains/100scf or less; or(ii) Representative fuel sampling data whichshow that the sulfur content of the gaseousfuel does not exceed 20 grains/100 scf. At aminimum, the amount of fuel sampling dataspecified in section 2.3.1.4 or 2.3.2.4 ofappendix D to part 75 of this chapter isrequired.[40 CFR 60.334(h)(3)].

None. None.

49 The permittee shall comply with all of the

requirements of the Phase II Acid RainPermit issued for this affected unit. [40 CFR72]

Other: See attached Phase II Acid RainPermit. (Appendix I).[40 CFR 72].

Other: See attached Phase II Acid RainPermit. (Appendix I).[40 CFR 72].

Comply wapproved Acid Rain 72]

Page 32 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

50 For equipment subject to Clean Air

Interstate Rule (CAIR) NOx TradingProgram, comply with N.J.A.C. 7:27-30.[N.J.A.C. 7:27-30]

None. None. Comply w

occurrence shall comprequireme7:27-30.6. 

51 The permittee shall comply with all of the

requirements of Clean Air Interstate Rule(CAIR) permit for the CAIR NOX AnnualTrading Program, CAIR NOX OzoneSeason Trading Program, and CAIR SO2Trading Program issued for this affectedunit. [40 CFR 97]

Other: See attached CAIR Permit(Appendix II).[40 CFR 97].

Other: See attached CAIR Permit(Appendix II).[40 CFR 97].

Comply woccurrence Permit (Ap

Page 33 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Emission Unit: U1 Combined Cycle Units - Three turbines each with a heat input of 2180 MMBtu/hr

Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Particulate Emissions <= 218 lb/hr.

[N.J.A.C. 7:27- 4.2(a)]

Particulate Emissions: Monitored by stackemission testing prior to permit renewal,based on each of three Department validatedstack test runs (see U1 OS Summary, Ref#2). [N.J.A.C. 7:27- 4.4]

Particulate Emissions: Recordkeeping bystack test results prior to permit renewal (seeU1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]

Stack Test and submischedule ([N.J.A.C. 

2 NOx (Total) <= 3 ppmvd @ 15% O2 except

for periods of start-up, shutdown and fueltransfer as defined in this permit. [N.J.A.C.7:27-22.16(e)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a 3 hour rolling average based on a1 hour block average (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(e)]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(e)]

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

3 NOx (Total) <= 3 ppmvd @ 15% O2 except

for periods of start-up, shutdown and fueltransfer as defined in this permit. [N.J.A.C.7:27-22.16(e)]

NOx (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]

NOx (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

4 NOx (Total) <= 0.0117 lb/MMBTU except

for periods of start-up, shutdown and fueltransfer as defined in this permit. [N.J.A.C.7:27-22.16(e)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a 3 hour rolling average based on a1 hour block average (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(e)]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(e)]

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

5 NOx (Total) <= 0.0117 lb/MMBTU except

for periods of start-up, shutdown and fueltransfer as defined in this permit. [N.J.A.C.7:27-22.16(e)]

NOx (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]

NOx (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

OS1 Combined Cycle Unit No. 1-Normal Operations, OS4 Combined Cycle Unit No. 2-Normal Operations, OS7 C

No. 3-Normal Operations

Page 34 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

6 NOx (Total) <= 25.3 lb/hr except for periods

of start-up, shutdown and fuel transfer asdefined in this permit. [N.J.A.C.7:27-22.16(e)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a 3 hour rolling average based on a1 hour block average (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(e)]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(e)]

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

7 NOx (Total) <= 25.3 lb/hr except for periods

of start-up, shutdown and fuel transfer asdefined in this permit. [N.J.A.C.7:27-22.16(a)]

NOx (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]

NOx (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

8 CO <= 4 ppmvd @ 15% O2 except for

periods of start-up, shutdown and fueltransfer as defined in this permit. [N.J.A.C.7:27-22.16(e)]

CO: Monitored by continuous emissionmonitoring system continuously, based on a3 hour rolling average based on a 1 hourblock average (see U1 OS Summary, Ref#1). [N.J.A.C. 7:27-22.16(e)]

CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-22.16(e)]

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

9 CO <= 4 ppmvd @ 15% O2 except for

periods of start-up, shutdown and fueltransfer as defined in this permit. [N.J.A.C.7:27-22.16(e)]

CO: Monitored by stack emission testingprior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]

CO: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

10 CO <= 0.01 lb/MMBTU except for periods

of start-up, shutdown and fuel transfer asdefined in this permit. [N.J.A.C.7:27-22.16(e)]

CO: Monitored by continuous emissionmonitoring system continuously, based on a3 hour rolling average based on a 1 hourblock average (see U1 OS Summary, Ref#1). [N.J.A.C. 7:27-22.16(e)]

CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-22.16(e)]

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

11 CO <= 0.01 lb/MMBTU except for periods

of start-up, shutdown and fuel transfer asdefined in this permit. [N.J.A.C.7:27-22.16(e)]

CO: Monitored by stack emission testingprior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]

CO: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

Page 35 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

12 CO <= 20.69 lb/hr except for periods of

start-up, shutdown and fuel transfer asdefined in this permit. [N.J.A.C.7:27-22.16(a)]

CO: Monitored by continuous emissionmonitoring system continuously, based on a3 hour rolling average based on a 1 hourblock average (see U1 OS Summary, Ref#1). [N.J.A.C. 7:27-22.16(e)]

CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-22.16(e)]

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

13 CO <= 20.69 lb/hr except for periods of

start-up, shutdown and fuel transfer asdefined in this permit. [N.J.A.C.7:27-22.16(a)]

CO: Monitored by stack emission testingprior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]

CO: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

14 VOC (Total) <= 3 ppmvd @ 15% O2.

[N.J.A.C. 7:27-22.16(e)]

VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]

VOC (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

15 VOC (Total) <= 0.00405 lb/MMBTU.

[N.J.A.C. 7:27-22.16(e)]

VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]

VOC (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

16 VOC (Total) <= 9.14 lb/hr. [N.J.A.C.

7:27-22.16(a)]

VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]

VOC (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

17 SO2 <= 0.0043 lb/MMBTU. [N.J.A.C.

7:27-22.16(e)]

SO2: Monitored by stack emission testingprior to permit renewal, based on each ofthree Department validated stack test runs(see U1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]

SO2: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule ([N.J.A.C. 

18 SO2 <= 9.34 lb/hr. [N.J.A.C. 7:27-22.16(a)] SO2: Monitored by stack emission testing

prior to permit renewal, based on each ofthree Department validated stack test runs(see U1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]

SO2: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule ([N.J.A.C. 

19 TSP <= 0.0135 lb/MMBTU. [N.J.A.C.

7:27-22.16(e)]

TSP: Monitored by stack emission testingprior to permit renewal, based on each ofthree Department validated stack test runs(see U1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]

TSP: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule ([N.J.A.C. 

Page 36 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

20 TSP <= 29.43 lb/hr. [N.J.A.C.

7:27-22.16(a)]

TSP: Monitored by stack emission testingprior to permit renewal, based on each ofthree Department validated stack test runs(see U1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]

TSP: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule ([N.J.A.C. 

21 PM-10 (Total) <= 0.0135 lb/MMBTU.

[N.J.A.C. 7:27-22.16(e)]

PM-10 (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]

PM-10 (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

22 PM-10 (Total) <= 29.43 lb/hr. [N.J.A.C.

7:27-22.16(a)]

PM-10 (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]

PM-10 (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule ([N.J.A.C. 

23 Ammonia <= 10 ppmvd @ 15% O2.

[N.J.A.C. 7:27-22.16(e)]

Ammonia: Monitored by stack emissiontesting prior to permit renewal, based oneach of three Department validated stack testruns (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]

Ammonia: Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule ([N.J.A.C. 

24 Ammonia <= 0.0135 lb/MMBTU. [N.J.A.C.

7:27-22.16(e)]

Ammonia: Monitored by stack emissiontesting prior to permit renewal, based oneach of three Department validated stack testruns (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]

Ammonia: Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule ([N.J.A.C. 

25 Ammonia <= 29.11 lb/hr. [N.J.A.C.

7:27-22.16(a)]

Ammonia: Monitored by stack emissiontesting prior to permit renewal, based oneach of three Department validated stack testruns (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]

Ammonia: Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule ([N.J.A.C. 

26 SO3 and H2SO4, as converted and

expressed as H2SO4 <= 0.0027lb/MMBTU. [N.J.A.C. 7:27-22.16(e)]

SO3 and H2SO4, as converted andexpressed as H2SO4: Monitored by stackemission testing prior to permit renewal,based on each of three Department validatedstack test runs (see U1 OS Summary, Ref#2). [N.J.A.C. 7:27-22.16(e)]

SO3 and H2SO4, as converted andexpressed as H2SO4: Recordkeeping bystack test results prior to permit renewal (seeU1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]

Stack Test and submischedule ([N.J.A.C. 

27 SO3 and H2SO4, as converted and

expressed as H2SO4 <= 5.72 lb/hr.[N.J.A.C. 7:27-22.16(a)]

SO3 and H2SO4, as converted andexpressed as H2SO4: Monitored by stackemission testing prior to permit renewal,based on each of three Department validatedstack test runs (see U1 OS Summary, Ref#2). [N.J.A.C. 7:27-22.16(e)]

SO3 and H2SO4, as converted andexpressed as H2SO4: Recordkeeping bystack test results prior to permit renewal (seeU1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]

Stack Test and submischedule ([N.J.A.C. 

Page 37 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

28 Maximum Gross Heat Input <= 2,180

MMBTU/hr (HHV) (HHV) for each gasturbine while buring natural gas. [N.J.A.C.7:27-22.16(a)]

Maximum Gross Heat Input: Monitored byfuel flow/firing rate instrumentcontinuously, based on a 1 hour blockaverage. [N.J.A.C. 7:27-22.16(e)]

Maximum Gross Heat Input: Recordkeepingby data acquisition system (DAS) /electronic data storage each hour duringoperation. [N.J.A.C. 7:27-22.16(e)]

None.

Page 38 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Emission Unit: U1 Combined Cycle Units - Three turbines each with a heat input of 2180 MMBtu/hr

Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Opacity <= 20 %. No person shall cause,

suffer, allow or permit smoke greater than20 percent opacity, exclusive of visiblecondensed water vapor, to be emitted intothe outdoor air from the combustion of fuelin any stationary internal combustion engineor any stationary turbine engine for a periodof more than 10 consecutive seconds.[N.J.A.C. 7:27- 3.5]

None. None. None.

2 Particulate Emissions <= 218 lb/hr

Particulate emission limit from thecombustion of fuel based on rated heat inputof source. [N.J.A.C. 7:27- 4.2(a)]

None. None. None.

3 CO <= 250 ppmvd @ 15% O2. [N.J.A.C.

7:27-16.9(b)]

CO: Monitored by continuous emissionmonitoring system continuously, based onone calendar day , not including periods ofdowntime. (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-16.23(a)1]

CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-22.16(e)]

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

4 VOC (Total) <= 50 ppmvd @ 15% O2.

[N.J.A.C. 7:27-16.9(c)]

VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-16.23(a)1]

VOC (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule ([N.J.A.C. 

5 NOx (Total) <= 1.3 lb/MW-hr. NOx RACT

emission limit for non-HEDD turbinesapplies during all periods of natual gascombustion. To calculate lb/MWh, for unitswhere energy is used for other than electricgeneration, for example combined heat andpower unit, that useful energy should beconverted to equivalent MWh and added tothe electric output. Emission rate is basedon net energy output (both electric anduseful heat). N.J.A.C. 7:27-19.5(d) and.[N.J.A.C. 7:27-19.5(f)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a calendar day (in ozone season) or30 day rolling (at other times) average (seeU1 OS Summary, Ref #1). [N.J.A.C.7:27-22.16(o)]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(o)]

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

OS2 Combined Cycle Unit No. 1-Startup, OS5 Combined Cycle Unit No. 2-Startup, OS8 Combined Cycle Unit No

Page 39 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

6 The annual emissions (in tons per year)

during startup shall be calculated as follows:1) Weighted Emission Rate Limit (in lbs/hr)x Total Hours of startups during a year(hrs/yr) x 1/2,000 (lbs/ton).Where Weighted Emission Rate = (cold startemissions (lbs) + warm start emissions (lbs)+ hot start emissions (lbs))/(cold startduration (hrs) + warm start duration (hrs) +hot start duration (hrs)) [N.J.A.C.7:27-22.16(e)]

Monitored by hour/time monitorcontinuously. [N.J.A.C. 7:27-22.16(o)]

Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(o)]

None.

7 NOx (Total) <= 111 lb/hr based on a 3 hour

rolling average based on a 1 hour blockaverage. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

8 CO <= 504 lb/hr based on a 3 hour rolling

average based on a 1 hour block average.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

9 VOC (Total) <= 87 lb/hr based on a 3 hour

rolling average based on a 1 hour blockaverage. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

10 SO2 <= 9.34 lb/hr. [N.J.A.C. 7:27-22.16(a)] None. None. None.11 TSP <= 29.43 lb/hr. [N.J.A.C.

7:27-22.16(a)]

None. None. None.

12 PM-10 (Total) <= 29.43 lb/hr. [N.J.A.C.

7:27-22.16(a)]

None. None. None.

13 SO3 and H2SO4, as converted and

expressed as H2SO4 <= 5.7 lb/hr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

Page 40 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Emission Unit: U1 Combined Cycle Units - Three turbines each with a heat input of 2180 MMBtu/hr

Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Opacity <= 20 %. No person shall cause,

suffer, allow or permit smoke greater than20 percent opacity, exclusive of visiblecondensed water vapor, to be emitted intothe outdoor air from the combustion of fuelin any stationary internal combustion engineor any stationary turbine engine for a periodof more than 10 consecutive seconds.[N.J.A.C. 7:27- 3.5]

None. None. None.

2 Particulate Emissions <= 218 lb/hr

Particulate emission limit from thecombustion of fuel based on rated heat inputof source. [N.J.A.C. 7:27- 4.2(a)]

None. None. None.

3 CO <= 250 ppmvd @ 15% O2. [N.J.A.C.

7:27-16.9(b)]

CO: Monitored by continuous emissionmonitoring system continuously, based onone calendar day , not including periods ofdowntime. (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-16.23(a)1]

CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-22.16(e)]

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

4 VOC (Total) <= 50 ppmvd @ 15% O2.

[N.J.A.C. 7:27-16.9(c)]

VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-16.23(a)2]

VOC (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]

Stack Test and submischedule ([N.J.A.C. 

5 NOx (Total) <= 1.3 lb/MW-hr. NOx RACT

emission limit for non-HEDD turbinesapplies during all periods of natual gascombustion. To calculate lb/MWh, for unitswhere energy is used for other than electricgeneration, for example combined heat andpower unit, that useful energy should beconverted to equivalent MWh and added tothe electric output. Emission rate is basedon net energy output (both electric anduseful heat). N.J.A.C. 7:27-19.5(d) and.[N.J.A.C. 7:27-19.5(f)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a calendar day (in ozone season) or30 day rolling (at other times) average (seeU1 OS Summary, Ref #1). [N.J.A.C.7:27-22.16(o)]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(o)]

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal. [N.

OS3 Combined Cycle Unit No. 1-Shutdown, OS6 Combined Cycle Unit No. 2-Shutdown, OS9 Combined Cycle Un

Page 41 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

6 NOx (Total) <= 111 lb/hr. [N.J.A.C.

7:27-22.16(e)]

None. None. None.

7 CO <= 504 lb/hr. [N.J.A.C. 7:27-22.16(e)] None. None. None.8 VOC (Total) <= 87 lb/hr. [N.J.A.C.

7:27-22.16(e)]

None. None. None.

9 SO2 <= 9.34 lb/hr. [N.J.A.C. 7:27-22.16(a)] None. None. None.10 TSP <= 29.43 lb/hr. [N.J.A.C.

7:27-22.16(a)]

None. None. None.

11 PM-10 (Total) <= 29.43 lb/hr. [N.J.A.C.

7:27-22.16(a)]

None. None. None.

12 SO3 and H2SO4, as converted and

expressed as H2SO4 <= 5.7 lb/hr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

Page 42 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Emission Unit: U2 Ten Cell Cooling Tower (200,000 gal/min capacity)Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 TSP <= 15.79 tons/yr. Maximum annual

emission limit from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

2 PM-10 (Total) <= 15.79 tons/yr. Maximum

annual emission limit from preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

OS Summary

Page 43 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Emission Unit: U2 Ten Cell Cooling Tower (200,000 gal/min capacity)Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Particulate Emissions <= 7.8 lb/hr based on

0.02 grains per SCF (maximum SCF emittedfrom emission point). [N.J.A.C. 7:27-6.2(a)]

None. None. None.

2 Opacity <= 20 %. Opacity limited to 20%,

exclusive of condensed water vapor, for aperiod of not longer than three minutes inany consecutive 30-minute period. [N.J.A.C.7:27- 6.2(d)]

None. None. None.

3 TSP <= 3.6 lb/hr. [N.J.A.C. 7:27-22.16(e)] None. None. None.4 PM-10 (Total) <= 3.6 lb/hr. [N.J.A.C.

7:27-22.16(e)]

None. None. None.

5 Total solids concentration in the cooling

tower circulating water =<12,000 mg/liter.[N.J.A.C. 7:27-22.16(a)]

Other: Circulating water analysis, once permonth during cooling toweroperation.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter each month during operation.Maintain records of circulating wateranalysis. [N.J.A.C. 7:27-22.16(o)]

None.

6 Water treatment chemicals containing

hexavalent chromium shall not be added tothe circulating water. [N.J.A.C.7:27-22.16(e)]

Other: By review of process recordsshowing materials/chemicalsadded/mixed.[N.J.A.C. 7:27-22.16(o)].

Other: Maintain process records showingdate, time, and amount ofmaterials/chemicals added/mixed.[N.J.A.C.7:27-22.16(o)].

None.

7 The raw materials shall be limited to the

chemicals listed in Appendix 3. [N.J.A.C.7:27-22.16(a)]

Other: By review of process recordsshowing materials/chemicalsadded/mixed.[N.J.A.C. 7:27-22.16(o)].

Other: Maintain process records showinglist of materials/chemicalsadded/mixed.[N.J.A.C. 7:27-22.16(o)].

None.

8 Total Material Transferred <= 364.5 tons/yr

of chemical additives (For a list of chemicaladditives, see document attached at the endof this section). Maximum throughput ratebased on operating permit application.[N.J.A.C. 7:27-22.16(a)]

Total Material Transferred: Monitored bymaterial feed/flow monitoring continuously.[N.J.A.C. 7:27-22.16(o)]

Total Material Transferred: Recordkeepingby manual logging of parameter each weekduring operation in a permanently bound logbook or readily accessible computer memoryshowing type of raw materials and amountof each chemical added with sum-to-date.[N.J.A.C. 7:27-22.16(o)]

None.

9 Cooling tower circulation water flow rate <=

200,000 gallons per minute (gpm), based onoperating permit application. [N.J.A.C.7:27-22.16(a)]

None. None. None.

OS1 Ten Cell Cooling Tower - Normal Operation

Page 44 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Emission Unit: U3 20,000 Gallon Ammonia Storage TankOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 If the tank is equipped with gauging and/or

sampling systems, such systems shall bevapor-tight except when gauging orsampling is taking place. [N.J.A.C.7:27-22.16(e)]

None. None. None.

2 Tank contents < 20.00% Ammonium

Hydroxide solution. [N.J.A.C.7:27-22.16(e)]

Other: For each delivery, monitor byreviewing delivery records such as MSDS,invoice, and/or bill of lading that showcontent, composition, and quantity of thedelivery.[N.J.A.C. 7:27-22.16(o)].

Other: Maintain delivery records perdelivery. The records shall indicate contentof delivery, composition, quantity delivered,and date of delivery.[N.J.A.C.7:27-22.16(o)].

None.

3 Total Material Transferred <= 1.895

MMgal/yr ammonia. [N.J.A.C.7:27-22.16(e)]

Other: For each delivery, monitor byreviewing delivery records, invoice, and/orbill of lading that show content,composition, and quantity of thedelivery.[N.J.A.C. 7:27-22.16(o)].

Other: Maintain delivery records perdelivery. The records shall indicate contentof delivery, composition, quantity delivered,and date of delivery withsum-to-date.[N.J.A.C. 7:27-22.16(o)].

None.

OS Summary

Page 45 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Emission Unit: U7 Fuel Gas Heater (16 MMBTU/hr)Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Maximum annual emission limit from

preconstruction permit. NOx (Total) <= 8.4tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Maximum annual emission limit from

preconstruction permit. CO <= 3.77 tons/yr.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

3 Maximum annual emission limit from

preconstruction permit. VOC (Total) <=0.48 tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 Maximum annual emission limit from

preconstruction permit. SO2 <= 0.3 tons/yr.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 Maximum annual emission limit from

preconstruction permit. TSP <= 0.53tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

6 Maximum Gross Heat Input <= 16

MMBTU/hr. [N.J.A.C. 7:27-22.16(e)]

OS Summary

Page 46 of 47
New Jersey Department of Environmental Protection

Facility Specific Requirements

AES RED OAK LLC (18195) BOP090002

Emission Unit: U7 Fuel Gas Heater (16 MMBTU/hr)Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Visible Emissions: No visible emissions,

exclusive of visible condensed water vapor,except for a period of not longer than threeminutes in any consecutive 30 minuteperiod. [N.J.A.C. 7:27-3.2(a)] & [N.J.A.C.7:27- 3.2(c)]

None. None. None.

2 Particulate Emissions <= 7.2 lb/hr

Particulate emission limit from thecombustion of fuel based on rated heat inputof source. [N.J.A.C. 7:27- 4.2(a)]

None. None. None.

3 NOx (Total) <= 1.917 lb/hr. [N.J.A.C.

7:27-22.16(e)]

None. None. None.

4 CO <= 0.86 lb/hr. [N.J.A.C. 7:27-22.16(e)] None. None. None.5 VOC (Total) <= 0.11 lb/hr. [N.J.A.C.

7:27-22.16(e)]

None. None. None.

6 SO2 <= 0.069 lb/hr. [N.J.A.C.

7:27-22.16(e)]

None. None. None.

7 PM-10 (Total) <= 0.12 lb/hr. [N.J.A.C.

7:27-22.16(e)]

None. None. None.

8 Permittee's self imposed fuel type limit.

Natural Gas only. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

9 Permittee's self imposed annual natural gas

use limit. 140.16 MMSCF per year[N.J.A.C. 7:27-22.16(a)]

Monitored by fuel flow/firing rateinstrument continuously. [N.J.A.C.7:27-22.16(o)]

Recordkeeping by manual logging ofparameter annually. Manual logging of fuelusage (Permanently Bound). [N.J.A.C.7:27-22.16(o)]

None.

OS1 Fuel Gas Heater Normal

Page 47 of 47
AES RED OAK LLC (18195) Date: 2/3/2010

BOP090002

New Jersey Department of Environmental Protection

Facility Profile (General)

Borough of Sayreville, Middlesex County,

New Jersey

4911 

State Plane Coordinates:

X-Coordinate:

Y-Coordinate:

Units:

Datum:

Source Org.:

Source Type:

County: Industry:

Location

Description: Primary SIC:

Secondary SIC:

Middlesex

Mailing

Address:

Street

Address:

AES RED OAK LLC

832 RED OAK LN

SAYREVILLE, NJ 08872

AES RED OAK LLC

832 RED OAK LN

SAYREVILLE, NJ 08872

Facility Name (AIMS): AES RED OAK LLC Facility ID (AIMS): 18195

NAICS:

Page 1 of 3
AES RED OAK LLC (18195) Date: 2/3/2010

BOP090002

New Jersey Department of Environmental Protection

Facility Profile (General)

(201) 933-5601 x 

( ) - x 

dshotts@trcsolutions.com

TRC Environmental Corporation

David J. Shotts, PE

Manager, Air Quality Engineering

(201) 933-5541 x0112 TRC Environmental Corporation

1200 Wall Street West

Lyndhurst, NJ 07071

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Private

NJ EIN:

Contact Type: Consultant

(732) 238-4702 x 

( ) - x 

chip.bergeron@aes.com

AES Red Oak, L.L.C.

Albert Bergeron

President and Facility Manager

(732) 238-1462 x0101 AES Red Oak, L.L.C

832 Red Oak Lane

Sayreville, NJ 08872

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Private

NJ EIN:

Contact Type: General Contact

(732) 238-4702 x 

( ) - x 

chip.bergeron@aes.com

AES Red Oak, L.L.C.

Albert Bergeron

Project Director

(732) 238-1462 x0101 AES Red Oak, L.L.C

832 Red Oak Lane

Sayreville, NJ 08872

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Private

NJ EIN:

Contact Type: On-Site Manager

Page 2 of 3
AES RED OAK LLC (18195) Date: 2/3/2010

BOP090002

New Jersey Department of Environmental Protection

Facility Profile (General)

(732) 238-4702 x 

( ) - x 

chip.bergeron@aes.com

AES Red Oak, L.L.C.

Albert Bergeron

President and Facility Manager

(732) 238-1462 x0101 AES Red Oak, L.L.C

832 Red Oak Lane

Sayreville, NJ 08872

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Private

NJ EIN:

Contact Type: Operator

( ) - x 

( ) - x 

AES Red Oak, L.L.C.

( ) - x AES Red Oak, L.L.C

832 Red Oak Lane

Sayreville, NJ 08872

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Private

NJ EIN:

Contact Type: Owner (Current Primary)

(732) 238-4702 x 

( ) - x 

chip.bergeron@aes.com

AES Red Oak, L.L.C.

Albert Bergeron

President and Facility Manager

(732) 238-1462 x0101 AES Red Oak, L.L.C

832 Red Oak Lane

Sayreville, NJ 08872

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Private

NJ EIN:

Contact Type: Responsible Official

Page 3 of 3
AES RED OAK LLC (18195)

BOP090002

New Jersey Department of Environmental Protection

Reason for Application

Date:2/3/2010

 Permit Being Modified

Permit Class: BOP Number:60002

Description

of Modifications:

1) Include CAIR permit as an attachment to the operating permit.

2) Update Subchapter 19 and other requirements.

3) Correct emission unit 1 to include PT5, instead of PT3.

4) Update Appendix II: Cooling Tower Chemical Additives by removing several chemicals

currently allowed to be used in the cooling tower and adding sulfuric acid, and depositrol to

the list

5) Update stack testing requirement

 Replace with updated stack test language

 Correct list of pollutants required to be stack tested to include NOx, CO, VOC, SO2,

TSP, PM-10, Ammonia and (SO3 and H2SO4)

 Allow compliance with all NOx, CO, VOC and PM-10 limits to be demonstrated by the

average of three Department approved stack test runs in accordance with current

Department policy.

Page 1 of 1
AES RED OAK LLC (18195)

BOP090002

New Jersey Department of Environmental Protection

Non-Source Fugitive Emissions

FG

 NJID

Description of 

Activity Causing

Emission

Location 

Description

Reasonable Estimate of Emissions (tpy)

VOC

(Total)

NOx CO SO TSP

(Total)

PM-10 Pb H

(

FG1

Total 0.000 0.000 0.000 0.000 0.000 0.000 0.000 

Page 1 of 1
AES RED OAK LLC (18195)

BOP090002

New Jersey Department of Environmental Protection

Insignificant Source Emissions 

IS

 NJID

Source/Group

Description

Equipment Type Location 

Description

Estimate of Emissions (tpy

VOC

(Total)

NOx CO SO TSP PM-10 

IS1

Total 0.000 0.000 0.000 0.000 0.000 0.000 

Page 1 of 1
Equip.

NJID

Facility's 

Designation

Equipment

Description

Equipment Type Certificate

Number

Install

Date

GrandFathered L

(S

New Jersey Department of Environmental Protection

Equipment Inventory

BOP090002AES RED OAK LLC (18195) 

E1 Combine Cyc1 Combined Cycle Unit No. 1 PCP020001 1/31/2000 No 

SWPC 501F

Combustion Turbine

E2 Combine Cyc2 Combined Cycle Unit No. 2 PCP020001 1/31/2000 No 

SWPC 501F

Combustion Turbine

E3 Combine Cyc3 Combined Cycle Unit No. 3 PCP020001 1/31/2000 No 

SWPC 501F

Combustion Turbine

E4 CoolingTower Ten Cell Cooling Tower Other Equipment PCP020001 1/31/2000 No E5 NH3 Tank 20,000 Gallon Ammonia PCP020001 1/31/2000 No 

Storage Tank

Storage Vessel

E10 Heater Fuel Gas Heater Boiler PCP020001 1/31/2000 No 

Page 1 of 1
AES RED OAK LLC (18195) Da

New Jersey Department of Environmental Protection

Control Device Inventory

CD

 NJID

Facility's 

Designation

Description CD Type Install

Date

GrandFathered Last Mod. (Since 1968) 

BOP090002

CD1 Combined Cycle Unit No. 1

Selective Catalytic ReductionSystem

SCR1 Selective Catalytic 1/31/2000 No

Reduction

CD2 Combined Cycle Unit No. 1

Oxidation Catalyst

OxCat1 Other 1/31/2000 No

CD3 Combined Cycle Unit No. 2

Selective Catalytic ReductionSystem

SCR2 Selective Catalytic 1/31/2000 No

Reduction

CD4 Combined Cycle Unit No. 2

Oxidation Catalyst

OxCat2 Other 1/31/2000 No

CD5 Combined Cycle Unit No. 3

Selective Catalytic ReductionSystem

SCR3 Selective Catalytic 1/31/2000 No

Reduction

CD6 Combined Cycle Unit No. 3

Oxidation Catalyst

OxCat3 Other 1/31/2000 No

Page 1 of 1
AES RED OAK LLC (18195) 

New Jersey Department of Environmental Protection

Emission Points Inventory

PT

 NJID

Facility's 

Designation

Description Config. Equiv.

Diam.

(in.)

Height

(ft.)

Dist. to

Prop.

Line (ft)

Exhaust Temp. (deg. F) Exhaust V

Avg. Min. Max. Avg. Mi

BOP090002

PT1 Stack Unit 1 Stack for Combined Cycle

Unit 1

Round 228 150 250 225.0 172.0 245.0 1,070,000.0 798

PT2 Stack Unit 2 Stack for Combined Cycle

Unit 2

Round 228 150 250 225.0 172.0 245.0 1,070,000.0 798

PT3 Stack Unit 3 Stack for Combined Cycle

Unit 3

Round 228 150 250 225.0 172.0 245.0 1,070,000.0 798

PT4 Cooling Towe Cooling Tower Round 845 46 50 100.0 32.0 125.0 102,912.0 50PT5 NH3 Tank Aqueous Ammonia Tank Round 6 22 250 55.0 0.0 95.0 10.0 PT7 Heater Stack Stack 1 for Fuel Gas Heater Round 16 30 200 559.0 300.0 818.0 2,437.3 PT8 Heater Stack Stack 2 for Fuel Gas Heater Round 16 30 200 559.0 300.0 818.0 2,437.3 

Page 1 of 1
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

AES RED OAK LLC (18195)BOP090002

U 1 Elec Gen Combined Cycle Units - Three turbines each with a heat input of 2180 MMBtu/hr

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 501F1-Normal Combined Cycle Unit No.

1-Normal Operations

Normal - SteadyState

E1 CD1 (P)

CD2 (P)

PT1 2-01-002-01 0.0 8,760.0

OS2 501F1-SU Combined Cycle Unit No.

1-Startup

Startup E1 PT1 2-01-002-01 0.0 8,760.0

OS3 501F1-SD Combined Cycle Unit No.

1-Shutdown

Shutdown E1 PT1 2-01-002-01 0.0 8,760.0

OS4 501F2-Normal Combined Cycle Unit No.

2-Normal Operations

Normal - SteadyState

E2 CD3 (P)

CD4 (P)

PT2 2-01-002-01 0.0 8,760.0

OS5 501F2-SU Combined Cycle Unit No.

2-Startup

Startup E2 PT2 2-01-002-01 0.0 8,760.0

OS6 501F2-SD Combined Cycle Unit No.

2-Shutdown

Shutdown E2 PT2 2-01-002-01 0.0 8,760.0

OS7 501F3-Normal Combined Cycle Unit No.

3-Normal Operations

Normal - SteadyState

E3 CD5 (P)

CD6 (P)

PT3 2-01-002-01 0.0 8,760.0

OS8 501F3-SU Combined Cycle Unit No.

3-Startup

Startup E3 PT3 2-01-002-01 0.0 8,760.0

OS9 501F3-SD Combined Cycle Unit No.

3-Shutdown

Shutdown E3 PT3 2-01-002-01 0.0 8,760.0

Page 1 of 3
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

AES RED OAK LLC (18195)BOP090002

U 2 Cooling Towe Ten Cell Cooling Tower (200,000 gal/min capacity)

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 Cool Tower Ten Cell Cooling Tower -

Normal Operation

Normal - SteadyState

E4 PT4 3-02-999-99 0.0 8,760.0

U 3 NH3 Tank 20,000 Gallon Ammonia Storage Tank

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 NH3 Tank 20,000 Gallon Ammonia

Storage Tank - NormalOperations

Normal - SteadyState

E5 PT5 4-03-011-97 0.0 8,760.0

Page 2 of 3
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

AES RED OAK LLC (18195)BOP090002

U 7 Heater Fuel Gas Heater (16 MMBTU/hr)

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 Heater-Gas Fuel Gas Heater Normal Normal - Steady

State

E10 PT7 

PT8 

0.0 8,760.0 

Page 3 of 3
New Jersey Department of Environmental Protection

Subject Item Group Inventory

Group NJID: GR1 Facility

Members: Type ID OS Step 

U U 1 OS0 SummaryU U 2 OS0 SummaryU U 3 OS0 SummaryU U 7 OS0 Summary

Formal Reason(s) for Group/Cap:

9 Other

Other (explain): To restrict facility's total emissions

Condition/Requirements that will be complied with or are no longerapplicable as a result of this Group: Operating Circumstances:

Page 1 of 1