From: Hirsch, Bruce R [mailto:Bruce.R.Hirsch@bge.com]

Sent: Monday, October 24, 2011 11:35 AM

To: 'Ryan, Paul'; Phil Hopkinson; Richard Parker; Alex Hofmann; Andrew Delaski;

Aris Marantan; Art Rosenfeld; Bob Saint; Brian Coffey; Bruce Smith; Caitlin

Johnson; Carlos Gaytan; Caskey, John; Charlie Drexler; Charlie Stevens; Chris

Bolduc; Clark Silcox; Creevy, Jim; Dan Cohen; D aniel Youn g; Eric Peterson;

Freeman, Jeremiah; Gary Fernstrom; Greg Coulter; Greg Rosenquist; James Lass;

Jennifer Tiedeman; Jerry Corkran; Jerry Hodge; Jerry Schoen; Joanna Mauer; John

Cymbalsky; John Rossetti; Katie Coughlin; Ken Winder; Mahesh P. Sampat; Matt

Miller; Matthew Nardotti; Meg Waltner; Meyers, Aaron; Michael Hyland; Michael

Rivest; Millure, Dave; Phil Harter; P olinski, R aymond; Puesh Kumar; Rick

Anderson; Rob Greeson; Robert Berman; Robert van Buskirk; Robin Roy; Scott Beck;

Simmons, Chuck; Steve Nadel; Steve Rosenstock; Tim Ballo; Tom Eckman; Wes

Patterson; Zhimei Luo; maxinesavitz@aol.com

Subject: RE: Amorphous Core Experience at BGE

Paul,

Is there any salvage value to amorphous steel? I am being to ld that sa lvage

Companies have told some Utilities that the steel has no salvage value.

Bruce

‐‐‐‐‐ Original Message

‐‐‐‐‐

From: Ryan, Paul [mailto:Paul.Ryan@hitmet.com]

Sent: Thursday, October 20, 2011 8:49 AM

To: Phil Hopkinson; Hirsch, Bruce R; Richard Parker; Alex Hofmann; Andrew

Delaski; Aris Marantan; Art Rosenfeld; Bob Saint; Brian C offey; Bru ce Smith;

Caitlin Johnson; Carlos Gaytan; Caskey, John; Charlie Drexler; Charlie Stevens;

Chris Bolduc; Clark Silcox; Creevy, Jim; Dan Cohen; Daniel Young; Eric Peterson;

Freeman, Jeremiah; Gary Fernstrom; Greg Coulter; Greg Rosenquist; James Lass;

Jennifer Tiedeman; Jerry Corkran; Jerry Hodge; Jerry Schoen; Joanna Mauer; John

Cymbalsky; John Rossetti; Katie Coughlin; Ken W ind er; Mahesh P. Sampat; Matt

Miller; Matthew Nardotti; Meg Waltner; Meyers, Aaron; Michael Hyland; Michael

Rivest; Millure, Dave; Phil Harter; Polinski, Raymond; Puesh Kumar; Rick

Anderson; Rob Greeson; Robert Berman; Robert van Buskirk; Robin Roy; Scott Beck;

Simmons, Chuck; Steve Nadel; Steve Rosenstock; Tim Ballo; Tom Eckman; Wes

Patterson; Zhimei Lu o; maxi nesavitz@aol.com

Subject: RE: Amorphous Core Experience at BGE

Dear all,

As the saying goes, a picture is worth a 1,000 words. I'm attaching a few slides

showing that amorphous cores can easily be opened and closed multiple times;

thereby allowing repair of a transformer by coil replacement. In other words

,

epoxy d oes not prevent disassembly as noted below.

Additionally, considerable advances in amorphous core transformer techniques and

manufacturing practices have been implemented since the commercial launch of the

product in the 1980's. An estimated 2.3M amorphous core transformers have been

produced worldwide with no reported core failures.Lastly, the wind farm incident described below was related to imported

transformers from Asia which had some manufacturing issues that have since been

reported to be corrected by the OEM.

I hope this helps.

Sincerely,

Paul C. Ryan

paul.ryan@hitmet.com

Product Group Head

Hitachi Metals America

‐ Metglas Inc.

Tel: +760

‐ 720

‐ 0408

Mobile: +7 60

‐ 415

‐ 346 9

Fax: +760

‐ 720

‐ 0626

________________________________________ From: Phil Hopkinson [mailto:phopkinson@hvolt.com]

Sent: Friday, October 14, 2011 6:25 PM

To: Hirsch, Bruce R; 'Richard Parker'; Alex Hofmann; Andrew Delaski; Aris

Marantan; Art Rosenfeld; Bob Saint; Brian Coffey; Bruce Smith; Caitlin Johnson;

Carlos Gaytan; Caskey, John; Charlie Drexler; Charlie Stevens; Chri s B olduc;

Clark Silcox; Creevy, Jim; Dan Cohen; Daniel Young; Eric Peterson; Freeman,

Jeremiah; Gary Fernstrom; Greg Coulter; Greg Rosenquist; James Lass; Jennifer

Tiedeman; Jerry Corkran; Jerry Hodge; Jerry Schoen; Joanna Mauer; John Cymbalsky;

John Rossetti; Katie Coughlin; Ken Winder; Mahesh P. Sampat; Matt Miller; Matthew

Nardotti; Meg Waltner; Meyers, Aaron; Mi chael H yland; Michael Rivest; Millure,

Dave; Phil Harter; Polinski, Raymond; Puesh Kumar; Rick Anderson; Rob Greeson;

Robert Berman; Robert van Buskirk; Robin Roy; Ryan, Paul; Scott Beck; Simmons,

Chuck; Steve Nadel; Steve Rosenstock; Tim Ballo; Tom Eckman; Wes Patterson;

Zhimei Luo

Subject: RE: Amorphous Core Experience at BGE

Hi all:

I have had consid era ble experience with amorphous cores and they can be made to

work. However, the process is not forgiving because the material is britle after

anneal and flakes off and breaks into tiny shards that remain loose and

undisciplined in the laced up core. Some manufacturers have learned to conta in

the sha rds. It is relatively easy in small single phase transformers. It is

more difficult in three phase cores. It is extremely difficult for large three

phase cores that require two or more cores wide to be packaged together. This

leaves blind locations where containment is not very easy. Some ha ve tried

sealing wi th epoxy but this prevents disassembly if a winding failure occurs.

Some have tried pressboard boxes with cotton tape wrappers. However, the cores

have greater magnetostriction than silicon iron and vibrate with greater

amplitude, and if not well contained may pump the shards of metal out of the

contain men t and into the windings where catastrophic failures have occurred. I

investigated a wind farm in 2008

‐ 9 where all 200 transformers had to be removed

from service, scrapped and rebuilt with silicon iron. Not all manufacturers have

had such negative experience, but a few incidents can destroy a bus iness.This experience suggests that limitations should be anticipated in the use of

amorphous. I certainly salute all who are successful because it can be made to

work. I continue to believe that amorphous should not be the basis of a minimum

national standard for energy efficiency. It is something that I r ecommend is

for app lications where customers have needs for extremely low core loss and where

the manufacturers have a proven track record of design and application.

All the best,

Phil

Philip J Hopkinson, PE

President & CEO HVOLT Inc.

3704 High Ridge Rd.

Charlotte, NC 28270

phopkinson@hvolt.com

Ph 704

‐ 846

‐ 32 90

Fx 704

‐ 845

‐ 25 20

Cell 704

‐ 236

‐ 3320

www.hvolt.com

From: Hirsch, Bruce R [mailto:Bruce.R.Hirsch@bge.com]

Sent: Friday, October 14, 2011 12:16 PM

To: 'Richard Parker'; Alex Hofmann; Andrew Delaski; Aris Marantan; Art Rosenfeld;

Bob Saint; Brian Coffey; Bruce Smith; Caitlin Johnson; Carlos Gaytan; Caskey,

John; Charlie Drexler; Charlie Stevens; Chris Bolduc; Cla rk Silcox; Cr eevy, Jim;

Dan Cohen; Daniel Young; Eric Peterson; Freeman, Jeremiah; Gary Fernstrom; Greg

Coulter; Greg Rosenquist; James Lass; Jennifer Tiedeman; Jerry Corkran; Jerry

Hodge; Jerry Schoen; Joanna Mauer; John Cymbalsky; John Rossetti; Katie Coughlin;

Ken Winder; Mahesh P. Sampat; Matt Miller; Matthew Nardotti; Meg Waltner; Meyers,

Aaron; Michael Hy land; Mich ael Rivest; Millure, Dave; Phil Harter; Phil

Hopkinson; Polinski, Raymond; Puesh Kumar; Rick Anderson; Rob Greeson; Robert

Berman; Robert van Buskirk; Robin Roy; Ryan, Paul; Scott Beck; Simmons, Chuck;

Steve Nadel; Steve Rosenstock; Tim Ballo; Tom Eckman; Wes Patterson; Zhimei Luo

Cc: Hirsch, Bruce R

Subject: RE:Amorphous Core Experience at BGE

Importa nce : High

This is just a single Company's experience with amorphous core transformers.

Please note that based on this data we have NOT ruled out using amorphous steel

in our transformers, however, the numbers are troubling.

BGE owns 2,770 transformers with amorphous steel cores. Most are three phase

units p urchased in th e mid to late 80's.

Of that number, 201 have failed in service. The cause of failure is not known but

to be considered a failure the probability is that either the core or coil

failed. This represents an 7% failure rate.

The average age of the failed amorpho us core tr ansformers is 10.97 years.

The average age of failed transformers for BGE's entire fleet is 29.4 years.BGE has over 216,000 transformers in the fleet, thus the quantity of amorphous

core transformers represents 1.4% of the total.

While we could debate the cause of failure for any particular class or design of

transformer, the average age to failure date is a good apples to apples

comparison of the pe rformance of the tra nsformers since the exact same criteria

was used across the board.

Hope this information, along with other user responses is helpful in the decision

making process.

Bruce

>>> This e

‐ mail and any attachments are confidential, may contain legal,

professional or other privileged information, and are int ended sole ly for the

addressee. If you are not the intended recipient, do not use the information in

this e

‐ mail in any way, delete this e

‐ mail and notify the sender. CEG

‐ IP2