# Revision 4.2

5/12/09 

# Air Pollution Control Operating Permit

Significant Modification and Preconstruction Approval

Permit Activity Number: BOP090002 Program Interest Number: 18195

Mailing Address Plant Location

ALBERT BERGERON

PRESIDENT & FACILITY MGR

AES RED OAK LLC

832 RED OAK LN

Sayreville, NJ 08872 AES RED OAK LLC

832 Red Oak Ln

Sayreville Boro

Middlesex County

Initial Operating Permit Approval Date: July 28, 2005

Significant Modification Approval Date: February 1, 2010

Operating Permit Expiration Date: July 27, 2010

This significant modification is approved and issued under the authority of Chapter 106, P.L. 1967 (N.J.S.A. 26:2C9.2). The equipment at the facility must be operated in accordance with the requirements of this permit.

This approval, in response to your application, merges the provisions of the previously approved operating permit

and the changes from this significant modification into a single comprehensive permit that replaces the one

previously issued. This significant modification includes the following changes:

1. Include Clean Air Interstate Rule (CAIR) NOx Trading Program requirements in the operating permit.

2. Updating various permit conditions (including subchapter 19 requirements and turbine stack testing

language).

3. Correct the stack testing language at (U1, OSS, REF #2) to require stack testing of NOx, CO, VOC, SO2,

TSP, PM-10, Ammonia and (SO3 and H2SO4); the current permit only lists NOx, CO, VOC and Ammonia

but the rest are required to be stack tested by the monitoring requirement associated with the individual

emission limitations.

4. Allowing compliance with all NOx, CO, VOC and PM-10 limits to be demonstrated by the average of three

Department approved stack test runs in accordance with current Department policy; the current permit

requires compliance with each stack test run.

5. Correcting emission unit 1 to include PT5, instead of PT3.

6. Updating Appendix II: Cooling Tower Chemical Additives by removing several chemicals currently

allowed to be used in the cooling tower and adding sulfuric acid, and Depositrol to the list.

Equipment at the facility referenced by this significant modification is covered by the permit shield, pursuant to the

provisions of N.J.A.C. 7:27-22.17. However, this permit shield does not cover physical changes which were

undertaken at the facility after March 3, 2003 and for which the facility did not seek an applicability determination

for the Prevention of Significant Deterioration rule, codified at 40 CFR 52.21 (PSD), from the United States

Environmental Protection Agency (USEPA). The issuance of this permit should not in any way be construed as a

determination by the Department that the PSD rules do not apply. Any questions on applicability of PSD should be

directed to USEPA Region II, Air Compliance Branch, 21st Floor, 290 Broadway, New York, NY 10007-1866

(Phone: 212-637-4074). Pursuant to N.J.A.C. 7:27-22.33(e), this significant modification consists of both a

preconstruction approval and operating permit approval. This operating permit does not include compliance

schedules as part of the approved compliance plan. CHRIS CHRISTIE D EPARTMENT 

# of E NVIRONMENTAL 

# P ROTECTION 

# BOB MARTIN

Governor Acting Commissioner

Environmental Regulation

Bureau of Air Permits

401 E. State Street, 2 nd 

# floor, P.O. Box 27

Trenton, NJ 08625-0027

# Revision 4.2

5/12/09 

# The permittee shall submit to the Department and to the EPA on forms provided by the Department, at the addresses

given below, a periodic compliance certification, in accordance with N.J.A.C. 7:27-22.19 and the schedule for

compliance certifications set forth in the compliance plan in this operating permit. The annual compliance

certification reporting period will cover the calendar year ending December 31. The annual compliance

certification is due to the Department and the EPA within 60 days a fter the end of each calendar year during

which this permit was in effect. Forms provided by the Department can be found on the Department's website at:

http://www.nj.gov/dep/enfor cement/compliancecertsair.htm

. The annual compliance certification report may also be consid ered as your six month deviation report for the period

from July 1 through December 31 which is due by January 30 of each year, as required by paragraph 13 in Section

F, General Provisions and Authorities



# , of this permit, if the annual compliance certification is submitted by January

30.

New Jersey Department of Environmental Protection United States Environmental Protection Agency, Region II

Air & Environmental Quality Compliance & Enforcement Air Compliance Branch

401 East State Street, P. O. Box 422 290 Broadway

Trenton, New Jersey 08625-0422 New York, New York 10007-1866

New Jersey Department of Environmental Protection

Air and Environmental Quality Compliance & Enforcement

Central Regional Enforcement Office

300 Horizon Center, PO Box 407, Rt. 130 South

Robbinsville, New Jersey 08625-0407



# We are including two electronic files, PDF and RADIUS. The PDF file contains the complete operating permit for

your facility. The RADIUS file contains the Facility Name, Location, and Contact Information; the Facility Specific

Requirements (Compliance Plan) and Inventories; and any Compliance Schedules (if needed). Upon importing this

information into your personal computer with RADIUS software, you will have up-to-date information in RADIUS

format. RADIUS software, instructions, and help are available at the Department's website at

www.state.nj.us/dep/aqpp. We also have an Operating Permit Help Line available from 9:00 AM to 4:00 PM daily,

where you may speak to someone about any questions you may have. The Operating Permit Help Line number is

609-633-8248.

If, in your judgment, the Department is imposing any unreasonable condition of approval in this permit modification

action, you may contest the Department’s decision on the modification and request an adjudicatory hearing pursuant

to N.J.S.A. 52:14b-1 et seq. and N.J.A. C. 7:27-22.32(a). All requests for an adjudicatory hearing must be received

in writing by the Department within 20 calendar days of the date you receive this letter. The request must contain

the information requested in N.J.A.C. 7:27-1.32 and the information on the enclosed Administrative Hearing

Request Checklist and Tracking Form.

The permittee is responsible for submitting a timely and administratively complete operating permit renewal

application. The application is considered timely if it is received at least 12 months before the expiration date of the

operating permit. To be deemed administratively complete, an application for renewal of the operating permit shall

include all of the information required by the application form for the renewal and the information required pursuant

to N.J.A.C. 7:27-22.30(d). However, consistent with N.J.A.C. 7:27-22.30(c), the permittee is encouraged to submit

the renewal application at least 15 months prior to expiration of the operating permit, so that the Department can

notify the applicant of any deficiencies in the application. This will allow the permittee to correct any deficiencies,

and to better ensure that the application is administratively complete by the renewal deadline. Only applications

which are timely and administratively complete will be eligible for coverage by an application shield. The renewal

application can be found at our website, http://www.state.nj.us/dep/aqpp/downloads/forms/OPRenewal.PDF

.

Permittees that are subject to Compliance Assurance Monitoring (CAM), pursuant to 40 CFR 64, shall develop a

CAM Plan for modified equipment as well as existing sources. Details of the rule and guidance on how to prepare a

plan can be found at EPA’s website: www.epa.gov/ttn/emc/cam.html . In addition, CAM Plans must be included as

part of the permit renewal application. Permittees that do not submit a CAM Plan may have their modification

applications denied, pursuant to N.J.A.C. 7:27-22.3.

If you have any questions regarding this permit approval, please call your permit writer, Michael Hogan, at (609)

633-1124.

# Revision 4.2

5/12/09 

# Approved by:

______________________ Aliya Khan

Bureau of Air Permits

Enclosure

CC: S. Riva, USEPA Region II (diskette containing final permit)

P. Conti, Chief CRO (Signature Page Only)

M. Hogan (w/o enclosure)

# Revision 4.2

5/12/09 

# Administrative Hearing Request **Checklist and Tracking Form**

**I. Document Being Appealed**

**Name of the Facility Program Interest** 

**(PI) Number Permit Activity** 

**Number Issuance** 

**Date**

**AES RED OAK LLC 18195 BOP090002**

**II. Contact Information**

**Name of Person Requesting Hearing Name of Attorney (if applicable)**

**Address: Address:** 

**Telephone: Telephone:** 

**III. Please include the following information as part of your request:**

A. The date the permittee received the permit decision,

B. Two printed copies of the document being appealed – for submitting to address 1 below;

A PDF copy of the document being appealed on a CD – for submitting to address 2

below **;** C. The legal and factual questions you are appealing;

D. A statement as to whether or not you raised each legal and factual issues during the

permit application process;

E. Suggested revised or alternative permit conditions;

F. An estimate of the time required for the hearing;

G. A request, if necessary, for a barrier-free hearing location for physically disabled persons;

H. A clear indication of any willingness to negotiate a settlement with the Department prior to

the Departments processing of your hearing request to the Office of Administrative Law;

Mail this form, completed, signed and dated with all of the information listed above, including attachment,

to:

1. New Jersey Department of Environmental Protection

Office of Legal Affairs

Attention: Adjudicatory Hearing Requests

401 E. State Street, P.O. Box 402

Trenton, New Jersey 08625-0402

2. Mr. Robert Esposito

Air Quality Permitting Element

New Jersey Department of Environmental Protection

401 E. State Street, 2nd Floor, P.O. Box 027

Trenton, New Jersey 08625-0027

Phone: (609) 633-2829

**Signature Date**

# Revision 4.2

5/12/09 

# Administrative Hearing Request **Checklist and Tracking Form**

**IV. If you are not the applicant but rather an interested person claiming to be aggrieved by the**

**permit decision, please include the following information:**

1. The date you or your agent received notice of the permit decision (include a copy of that

permit decision with your hearing request);

2. Evidence that a copy of the request has been delivered to the applicant for the permit

which is the subject of the permit decision;

3. A detailed statement of which findings of fact and/or conclusion of law you are

challenging;

4. A description of your participation in any public hearings held in connection with the

permit application and copies of any written comments you submitted;

5. Whether you claim a statutory or constitutional right to a hearing, and, if you claim such a

right, a reference to the applicable statute or explanation of how your property interests

are affected by the permit decision;

6. If the appeal request concerns a CAFRA permit decision, evidence that a copy of the

request has been delivered to the clerks of the county and the municipality in which the

project which is the subject of the permit decision is located;

7. Suggested revised or alternative permit conditions;

8. An estimate of the time required for the hearing;

9. A request, if necessary, for a barrier-free hearing location for physically disable persons;

10. A clear indication of any willingness to negotiate a settlement with the Department prior to

the Department’s transmittal of the hearing request to the Office of Administrative Law;

Mail this form, completed, signed and dated with all of the information listed above, including attachment,

to:

1. New Jersey Department of Environmental Protection

Office of Legal Affairs

Attention: Adjudicatory Hearing Requests

401 East State Street, P.O. Box 402

Trenton, New Jersey 08625-0402

3. Mr. Robert Esposito

Air Quality Permitting Element

New Jersey Department of Environmental Protection

401 E. State Street, 2nd Floor, P.O. Box 027

Trenton, New Jersey 08625

Phone: (609) 633-2829

**Signature Date**

# Revision 4.2

5/12/09 

# Facility Name: AES RED OAK LLC

Program Interest Number: 18195

Permit Activity Number: BOP090002

TABLE OF CONTENTS

Section A

REASON FOR PERMIT

Section B

DEFINITIONS

Section C

POLLUTANT EMISSIONS SUMMARY

Section D

POLLUTION PREVENTION REPORTING

Section E

GENERAL PROVISIONS AND AUTHORITIES

Section F

STATE-ONLY APPLICABLE REQUIREMENTS

Section G

COMPLIANCE PLAN AND INVENTORIES

APPENDIX 1: ACID RAIN PERMIT

APPENDIX 2: CAIR PERMIT

APPENDIX 3: COOLING TOWER CHEMICALS

# Revision 4.2

5/12/09 

# Section A

Facility Name: AES RED OAK LLC

Program Interest Number: 18195

Permit Activity Number: BOP090002

REASON FOR PERMIT

The reason for issuance of this permit is to comply with the air pollution control permit provisions of Title V of the

federal Clean Air Act, federal rules promulgated at 40 CFR 70, and state regulations promulgated at N.J.A.C. 7:27-

22, which requires the state to issue operating permits to major facilities and minor facilities that are in certain

designated source categories. This is the operating permit for the facility listed on the cover page, which includes a

significant modification that includes the following changes:

1. Include Clean Air Interstate Rule (CAIR) NOx Trading Program requirements in the operating permit.

2. Updating various permit conditions (including subchapter 19 requirements and turbine stack testing

language).

3. Correct the stack testing language at (U1, OSS, REF #2) to require stack testing of NOx, CO, VOC, SO2,

TSP, PM-10, Ammonia and (SO3 and H2SO4); the current permit only lists NOx, CO, VOC and Ammonia

but the rest are required to be stack tested by the monitoring requirement associated with the individual

emission limitations.

4. Allowing compliance with all NOx, CO, VOC and PM-10 limits to be demonstrated by the average of three

Department approved stack test runs in accordance with current Department policy; the current permit

requires compliance with each stack test run.

5. Correcting emission unit 1 to include PT5, instead of PT3.

6. Updating Appendix II: Cooling Tower Chemical Additives by removing several chemicals currently

allowed to be used in the cooling tower and adding sulfuric acid, and Depositrol to the list.

New Jersey has elected to integrate its Title I New Source Review (NSR) preconstruction permits with the new Title

V operating permits instead of issuing separate permits. Consequently, the existing preconstruction permit

provisions that were previously approved for this facility have been consolidated into this permit. This permit may

also include applicable requirements for grandfathered sources.

This permit action consolidates previously approved permit terms and conditions into one single permit for the

facility. The New Jersey Department of Environmental Protection (Department) issues this operating permit

authorizing the facility to operate equipment and air pollution control devices. In the operating permit application,

the facility represented that it meets all applicable requirements of the federal Clean Air Act and the New Jersey Air

Pollution Control Act codified at N.J.S.A. 26:2C. Based on an evaluation of the data contained in the facility’s

application, the Department has approved this operating permit.

This permit allows this facility to operate the equipment and air pollution control devices specified in this permit and

emit up to a level specified for each source operation. The signatories named in the application are responsible for

ensuring that the facility is operated in a manner consistent with this permit, its conditions, and applicable rules.

# Revision 4.2

5/12/09 

# Section B

Facility Name: AES RED OAK LLC

Program Interest Number: 18195

Permit Activity Number: BOP090002

DEFINITIONS

The terms used in this permit are used consistent with the definitions at N.J.A.C. 7:27-1 and N.J.A.C. 7:27-22. Any

terms defined in this section are not defined at N.J.A.C. 7:27-1 or N.J.A.C. 7:27-22, and are needed for clarifying

the permit.

“Permitting Authority” means the New Jersey Department of Environmental Protection (NJDEP).

“The EPA,” or the “Administrator,” means the Administrator of the EPA or his designee.

“M” preceding a unit of measure means one thousand. For example, “10 M gal.” means ten thousand gallons.

“MM” preceding a unit of measure means one million. For example, “10 MM gal.” means ten million gallons.

“Grandfathered” means, in reference to equipment or co ntrol apparatus, that construction, reconstruction, or

modification occurred prior to enactment of N.J.S.A. 26:2C-9.2 on June 15, 1967, or prior to the subsequent

applicable revisions to rules and regulations codified at N.J.A.C. 7:27-8 that occurred March 5, 1973, June 1, 1976,

April 5, 1985, and October 31, 1994, and no construction, reconstruction, or modification of the equipment or

control apparatus has occurred since.

“Compliance Plan” means the applicable requirements, mo nitoring requirements, recordkeeping requirements, and

submittal/action requirements detailed in Section J, Facility Specific Requirements, of the operating permit.

# Revision 4.2

5/12/09 

# Section C

Facility Name: AES RED OAK LLC

Program Interest Number: 18195

Permit Activity Number: BOP090002

POLLUTANT EMISSIONS SUMMARY



# The following table indicates the facility’s Potential to Emit (PTE) emissions summary:

Facility Total Potential to Emit

(tons per year)

Primary Secondary Source Categories

VOC

(total) NO

x 

# CO SO 2 

# TSP

(total) Other

(total) PM 10 

# (total) Pb HAPs

(total)

Emission Unit

Summary 102.9 292.4 704.8 104.1 345.1 63.6 345.1 N/A N/A

Batch Process

Summary N/A N/A N/A N/A N/A N/A N/A N/A N/A

Non-Source Fugitive

Emissions 1 

# N/A N/A N/A N/A N/A N/A N/A N/A N/A

Group

Summary N/A N/A N/A N/A N/A N/A N/A N/A N/A

Total

Emissions 2 

# 102.9 292.4 704.8 104.1 345.1 63.6 345.1 N/A N/A

VOC Volatile Organic Compounds PM 10 

# Particulates under 10 microns

NO

x 

# Nitrogen Oxides Pb Lead

CO Carbon Monoxide HAPs Hazardous Air Pollutants

SO 2 

# Sulfur Dioxide

TSP Total Suspended Particulates

Other Any other air contaminant regulated under the Federal Clean Air Act

1 

# Not applicable to this facility.

2 

# Total emissions from this facility do not include emissions from Insignificant Sources.

# Revision 4.2

5/12/09 

# Section C

Facility Name: AES RED OAK LLC

Program Interest Number: 18195

Permit Activity Number: BOP090002

POLLUTANT EMISSIONS SUMMARY



# The following table indicates the facility’s ha zardous air pollutants (HAP) emissions summary: 3



# HAP TPY

3 

# Do not sum these values for the purpose of establishing a total HAP potential to emit. See previous page for the

allowable total HAP emissions.

# Revision 4.2

5/12/09 

# Section D

Facility Name: AES RED OAK LLC

Program Interest Number: 18195

Permit Activity Number: BOP090002

POLLUTION PREVENTION REPORTING

General Pollution Prevention Conditions

The following evaluation requirements are included to track the facility’s progress in several critical areas identified

in the National Environmental Performance Partnership System (NEPPS). Nitrogen Oxides (NOx) and Volatile

Organic Compounds (VOC) are precursors to the air pollutant Ozone, for which New Jersey is non-attainment with

the air quality standard for the protection of public health . The control of hazardous air pollutants (HAPs) is also a

focus item for the next decade in order to minimize localized hot spots and general urban air toxics levels.

Therefore, the Department is requiring evaluation of emission trends at 5-year intervals for major sources of these

air contaminants. Also, as part of significant modification applications, proposed major increases of these air

contaminants require evaluation of pollu tion prevention and cross media effects.

The evaluation of these trends requires no increased monito ring. Rather it utilizes existing monitoring data, as

reported annually in Emission Statements (for NOx and VOC) and annual Release and Pollution Prevention Reports

(for HAPs). The intent of this evaluation is to better utilize the existing data by having the company, the public and

the Department review major source trends periodically, as part of the 5-year renewal review and public comment

process. The Department requests that the facility-wide tr ends be presented on graphs for attachment to the public

information document for the 5-year renewal.

Pollution prevention includes changes that result in the reduction in use or generation of non-product output per unit

of product. Cross media effects are practices that result in transferring the ultimate release or disposal of a

contaminant from one environmental medium (e.g. air) to another environmental medium (e.g. water, solid or

hazardous wastes).

Information to include with the renewal application:

1. The facility will evaluate annual emission trends over the last five years for actual air contaminant

emissions of Volatile Organic Compounds (VOC), Nitr ogen Oxides (NOx), if the facility’s potential to

emit VOC or NOx is greater than 25 tons per year, or any Hazardous Air Pollutants (HAP), for which the

facility’s potential to emit is greater than 10 tons per year. The VOC and NOx emission data should reflect

annual emission statement reports submitted pursuant to N.J.A.C. 7:27-21, and the HAP emissions data

should reflect the annual Release and Pollution Prevention Report submitted pursuant to N.J.A.C. 7:1G-4

and 5 and N.J.A.C. 7:1K-6. Although not required, the Department encourages the facility to explain the

reason for any significant trend, including whether it is the result of cross media shifts (to air, water, or

solid waste) and/or pollution preven tion. Changes should be itemized for each emission unit (or process)

with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton per year

of any HAP. Also, show the net change for the facility.

2. The facility will summarize annual potential to emit limits (allowable emissions) for VOC, NOx, and

HAPs, which are subject to reporting under 1 above, for the last five years. Changes should be itemized for

each emission unit (or process) with a potential to emit over five tons per year of VOC or NOx or a

potential to emit over one ton per year of any HAP. Also, show the net change for the facility.

3. The facility will summarize five-year trends in annual VOC, NOx, and HAP emissions, which are subject

to reporting under 1 above, on a pound per unit of pr oduct basis, based on annual actual emissions and

annual production over the five year period. Changes should be itemized for each emission unit (or

# Revision 4.2

5/12/09 

# process) with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton

per year of any HAP. Also, show the net change for the facility.

4. The facility will discuss five-year trends in actual air contaminant emissions of non-source VOC and HAP

fugitives, which are subject to reporting under 1 above; explain measures taken to minimize such fugitives;

and provide an explanation for any significant changes.

Information to include with an application for a Significant Modification to this permit:

1. For any significant modifications, the facility is encouraged to explain any cross media shifts of VOC and

HAP air contaminants as part of the significant modifica tion application. If an explanation is provided, the

facility should identify the pollutant and the specific environmental media to which the pollutant is

anticipated to be transferred, whether it be from air to solid waste or water, or from water or solid waste to

the air.

# Revision 4.2

5/12/09 

# Section E

Facility Name: AES RED OAK LLC

Program Interest Number: 18195

Permit Activity Number: BOP090002

GENERAL PROVISIONS AND AUTHORITIES

Operating Permits

1. No permittee shall allow any air contaminant, including an air contaminant detectable by the sense of

smell, to be present in the outdoor atmosphere in a quantity and duration which is, or tends to be, injurious

to human health or welfare, animal or plant life or property, or which would unreasonably interfere with the

enjoyment of life or property. This shall not include an air contaminant that occurs only in areas over

which the permittee has exclusive use or occupancy. Conditions relative only to nuisance situations,

including odors, are not considered Federa lly enforceable. [N.J.A.C. 7:27-22.16(g)8]

2. Any deviation from operating permit requirements which results in a release of air contaminants shall be

reported to the Department as follows:

If the air contaminants are released in a quantity or concentration which poses a potential threat to public

health, welfare or the environment or which might reasonably result in citizen complaints, the permittee

shall report the release to the Department:

i. Immediately on the Department hotline at 1-877-927-6337, pursuant to N.J.S.A. 26:2C-19(e); and

ii. As part of the compliance certification required in N.J.A.C. 7:27-22.19(f). However, if the

deviation is identified through source emissions testing, it shall be reported through the source

emissions testing and monitoring procedures at N.J.A.C. 7:27-22.18(e)3; or

If the air contaminants are released in a quantity or co ncentration which poses no potential threat to public

health, welfare or the environment and which will not likely result in citizen complaints, the permittee shall

report the release to the Department as part of th e compliance certification required in N.J.A.C. 7:27-

22.19(f), except for deviations identified by source emissions testing reports, which shall be reported

through the procedures at N.J.A.C. 7:27-22.18(e)3; or

If the air contaminants are released in a quantity or co ncentration which poses no potential threat to public

health, welfare or the environment and which will not likely result in citizen complaints, and the permittee

intends to assert the affirmative defense afforded by N.J.A.C. 7:27-22.16(l), the violation shall be reported

by 5:00 P.M. of the second full calendar day following the occurrence, or of becoming aware of the

occurrence, consistent with N.J.A.C. 7:27-22.16(l). [N.J.A.C. 7:27-22.19(g)]

3. The permittee shall comply with all conditions of the operating permit including the approved compliance

plan. Any non-compliance with a permit condition constitutes a violation of the New Jersey Air Pollution

Control Act N.J.S.A. 26:2C-1 et seq., or the CAA, 42 U.S.C. §7401 et seq., or both, and is grounds for

enforcement action; for termination, revocation and reissuance, or for modification of the operating permit;

or for denial of an application for a renewal of the operating permit. [N.J.A.C. 7:27-22.16(g)1]

4. It shall not be a defense for the permittee in an enfo rcement action that it would have been necessary to halt

or reduce the permitted activity in order to maintain compliance with the conditions of its operating permit.

[N.J.A.C. 7:27-22.16(g)2]

# Revision 4.2

5/12/09 

# 5. This operating permit may be modified, terminated, or revoked for cause by the EPA pursuant to 40 CFR

70.7(g) and revoked or reopened and modified for cause by the Department pursuant to N.J.A.C. 7:27-

22.25. [N.J.A.C. 7:27-22.16(g)3]

6. The permittee shall furnish to the Department, within a reasonable time, any information that the

Department may request in writing to determine whether cause exists for modifying, revoking and

reissuing, or terminating this operating permit; or to determine compliance with the operating permit.

[N.J.A.C. 7:27-22.16(g)4]

7. The filing of an application for a modification of an operating permit, or of a notice of planned changes or

anticipated non-compliance, does not stay any operating permit condition. [N.J.A.C. 7:27-22.16(g)5]

8. The operating permit does not convey any property rights of any sort, or any exclusive privilege. [N.J.A.C.

7:27-22.16(g)6]

9. Upon request, the permittee shall furnish to the Department copies of records required by the operating

permit to be kept. [N.J.A.C. 7:27-22.16(g)7]

10. The Department and its authorized representatives shall have the right to enter and inspect any facility

subject to N.J.A.C. 7:27-22, or portion thereof, pursuant to N.J.A.C. 7:27-1.31. [N.J.A.C. 7:27-22.16(g)9]

11. The permittee shall pay fees to the Department pursuant to N.J.A.C. 7:27. [N.J.A.C. 7:27-22.16(g)10]

12. Each permittee shall maintain records of all source emi ssions testing or monitoring performed at the facility

and required by the operating permit in accordance with N.J.A.C. 7:27-22.19. Records shall be maintained,

for at least five years from the date of each sample, measurement, or report. Each permittee shall maintain

all other records required by this operating permit for a period of five years from the date each record is

made. At a minimum, source emission testing or mon itoring records shall contain the information specified

at N.J.A.C. 7:27-22.19(b). [N.J.A.C. 7:27-22.19(a) and N.J.A.C. 7:27-22.19(b)]

13. In accordance with N.J.A.C. 7:27-22.19(c) and 22.19(d) 3, each permittee shall submit to the Department,

on forms provided by the Department, a six month deviation report relating to testing and monitoring

required by the operating permit, not including information for testing and monitoring which have other

reporting schedules specified in the permit. Normally, stack testing reporting is submitted within 45 days

of test completion and continuous monitoring reporting is done quarterly. The six month report must

address other specified monitoring, including, but not limited to, continuous and periodic monitoring data

required by this permit. (See column two and three entitled "Monitoring Requirement" and

"Recordkeeping Requirement," respectively, in the Facili ty Specific Requirement Section of this permit.).

The six month reports for the testing and monitoring performed from January 1 through June 30, shall be

reported by July 30 of the same calendar year; or from July 1 through December 31, shall be reported by

January 30 of the following calendar year. Pursuant to N.J.A.C. 7:27-22.19(e), these six month reports

shall clearly identify all deviations from operating permit requirements, the probable cause of such

deviations, and any corrective actions taken. Any "None" listed in the Submittal/Action Requirement in the

operating permit is not intended to override the six-month deviation report. The report shall be certified

pursuant to N.J.A.C. 7:27-1.39 by a responsible official. Forms provided by the Department can be found

on the Department's web site at: http://www.nj.gov/dep/enforcement/compliancecertsair.htm . [N.J.A.C.

7:27-22.19(d) 3 and N.J.A.C. 7:27-22.19(e)]

An annual compliance certification required by paragraph 2 above and required by N.J.A.C. 7:27-19(f) may

also be considered as your six month deviation report for the period from July 1 through December 31

which is due by January 30 of each year if the annual compliance certification is submitted by January 30.

14. For emergencies (as defined at 40 CFR 70.6(g)(1)) that result in non-compliance with any promulgated

federal technology-based standard such as NSPS, NESHAPS, or MACT, a federal affirmative defense is

available, pursuant to 40 CFR 70. To assert a federal affirmative defense, the permittee must use the

procedures set forth in 40 CFR 70. The affirmative defense provisions described in 15 below may not be

applied to any situation that caused the Facility to exceed any federally delegated regulation, including but

not limited to NSPS, NESHAP, or MACT.

# Revision 4.2

5/12/09 

# 15. For situations other than those covered by 14 above, an affirmative defense is available for a violation of a

provision or condition of the operating permit only if:

i. The violation occurred as a result of an eq uipment malfunction, an equipment start-up or

shutdown, or during the performance of necessary equipment maintenance; and

ii. The affirmative defense is asserted and established as required by N.J.S.A. 26:2C-19.1 through

19.5 and any implementing rules. [N.J.A.C. 7:27-22.16(l)]

16. Each permittee shall meet all requirements of the approved source emissions testing and monitoring

protocol during the term of the operating permit. [N.J.A.C. 7:27-22.18(j)]

The following paragraphs of this section are included for the permittee's convenience to remind them of their

obligations with certain key applicable requirements. These paragraphs are not enforceable since they paraphrase

areas of the operating permits rule. Also, these paragraphs do not reference all the applicable requirements with

which the permittee must comply.

17. Each owner and each operator of any facility, source operation, or activity to which this permit applies is

responsible for ensuring compliance with all requirements of N.J.A.C. 7:27-22. If the owner and operator

are separate persons, or if there is more than one owner or operator, each owner and each operator is jointly

and severally liable for any fees due under N.J.A.C. 7:27-22, and for any penalties for violation of N.J.A.C.

7:27-22.

18. In the event of a challenge to any part of this operating permit, all other parts of the permit shall continue to

be valid.

19. The permittee shall ensure that no air contaminant is emitted from any significant source operation at a rate,

calculated as the potential to emit, that exceeds the app licable threshold for reporting emissions set forth in

the Appendix to N.J.A.C. 7:27-22, unless emission of the air contaminant is authorized by this operating

permit.

20. Consistent with the provisions of N.J.A.C. 7:27-22.3(e), the permittee shall ensure that all requirements of

this operating permit are met. In the event that there are multiple emission limitations, monitoring,

recordkeeping, and/or reporting requirements for a give n source operation, the facility must comply with all

requirements, including the most stringent.

21. Consistent with the provisions of N.J.A.C. 7:27-22.9(c), the permittee shall use monitoring of operating

parameters, where required by the compliance plan, as a surrogate for direct emissions testing or

monitoring, to demonstrate compliance with applicable requirements.

22. The permittee shall file a timely and complete application for:

Administrative Amendments;

Seven-Day-Notice changes;

Minor Modifications;

Significant Modifications; and

Renewals.

23. Process monitors must be operated at all times wh en the associated process equipment is operating except

during outage time allowed by Department guidelines/procedures or as outlined in Technical Manual 1005.

The permittee must keep a service log as required.

# Revision 4.2

5/12/09 

# Section F

Facility Name: AES RED OAK LLC

Program Interest Number: 18195

Permit Activity Number: BOP090002

STATE-ONLY APPLI CABLE REQUIREMENTS

N.J.A.C. 7:27-22.16(b)5 requires the Department to specifi cally designate as not being federally enforceable any

permit conditions based only on applicable state requirements. The applicable state requirements to which this

provision applies are listed in the table titled “State-Only Applicable Requirements.”

STATE-ONLY APPLICABLE REQUIREMENTS

The following applicable requirements are not federally enforceable:

SECTION SUBJECT ITEM ITEM # REF. #

E --- 15 ---

G FC --- 3

G FC --- 10

G FC --- 18

# Revision 4.2

5/12/09 

# Section G

Facility Name: AES RED OAK LLC

Program Interest Number: 18195

Permit Activity Number: BOP090002

COMPLIANCE PLAN AND INVENTORIES

• FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX

• FACILITY SPECIFIC REQUIREMENTS (COMPLIANCE PLAN)

• ATTACHMENTS TO THE FACILITY SPECIFIC REQUIREMENTS

• FACILITY PROFILE (ADMINISTRATIVE INFORMATION)

• REASON FOR APPLICATION

• NON-SOURCE FUGITIVE EMISSIONS

• INSIGNIFICANT SOURCE EMISSIONS

• EQUIPMENT INVENTORY

• EQUIPMENT DETAILS

• CONTROL DEVICE INVENTORY

• CONTROL DEVICE DETAILS

• EMISSION POINT INVENTORY

• EMISSION UNIT/BATCH PROCESS INVENTORY

• SUBJECT ITEM GROUP INVENTORY

• POTENTIAL TO EMIT – BATCH PROCESS INVENTORY

# Revision 4.2

5/12/09 

# Facility Name: AES RED OAK LLC

Program Interest Number: 18195

Permit Activity Number: BOP090002

FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX

Subject Item and Name Page Number

Facility (FC) :

FC 1

Groups (GR)

GR1 – Facility Annual Emission Limit Cap for U1, U2, U3 and U7 6

Emission Units (U):

U1 – Combined Cycle Units - Three turbines each with a heat input of 2180 MMBTU/hr

OS Summary 13

OS1/OS4/OS7 Normal Operation 33

OS2/OS5/OS8 Startup 38

OS3/OS6/OS9 Shut down 40

U2 – Ten Cell Cooling Tower (Heat Input = 200,000 gal/min capacit

OS Summary 42

OS1 Normal Operation 43

U3 – 20,000 Gallon Ammonia Storage Tank

OS Summary 44

U7 – Fuel Gas Heater (16 MMBTU/hr)

OS Summary 45

OS1 Normal Operation 46

Note: See Attachments for additional requirementsNew Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Subject Item:FCRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1General Provisions: Defines numerous termsused in N.J.A.C. 7:27. Specifies proceduresfor making confidentiality claims, certifyingapplications, reports, and other documentsto the Department, and requestingadjudicatory hearings and stays of theeffective date of departmental decisions.Also, provides provisions regardingapplicability, severability, and liberalconstruction of N.J.A.C. 7:27. [N.J.A.C.7:27- 1]None.None.None.2Control and Prohibition of Open Burning:Prohibits any person from open burning ofrubbish, garbage, trade waste, buildings,structures, leaves, other plant life andsalvage. Open burning of infested plant lifeor dangerous material may only beperformed with a permit from theDepartment. [N.J.A.C. 7:27- 2]None.None.Obtain an approved permit: Prior tooccurrence of event (prior to open burning).[N.J.A.C. 7:27- 2]3Prohibition of Air Pollution:Notwithstanding compliance with othersubchapters of N.J.A.C. 7:27, no personshall suffer, allow, or permit to be emittedinto the outdoor atmosphere substances inquantities that resultin air pollution asdefined at N.J.A.C. 7:27-5.1. Applicable toall facilities located in New Jersey.[N.J.A.C. 7:27- 5]None.None.None.4Prevention and Control of Air PollutionControl Emergencies: Requires that writtenStandby Plans, consistent with goodindustrial practice and safe operatingprocedures, be prepared for reducing theemission of air contaminants during periodsof an air pollution alert, warning, oremergency. Any person responsible for theoperation of a source of air contaminationnot set forth in Table 1 of N.J.A.C. 7:27-12is not required to prepare such a plan unlessrequested by the Department in writing.[N.J.A.C. 7:27-12]None.None.Comply with the requirement: Uponoccurrence of event. Upon proclamation bythe Governor of an air pollution alert,warning, or emergency, the permittee shallput the Standby Plan into effect. In addition,the permittee shall ensure that all of theapplicable emission reduction objectives ofN.J.A.C. 7:27-12.4, Table I, II, and III arecomplied with whenever there is an airpollution alert, warning, or emergency.[N.J.A.C. 7:27-12]Page 1 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5Emission Offsets Rules. [N.J.A.C. 7:27-18]Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].Comply with the requirement: Uponoccurrence of event. Submit anadministratively complete application whenapplying for a minor modification pursuantto N.J.A.C. 7:27-22.23 or a significantmodification pursuant to N.J.A.C.7:27-22.24. [N.J.A.C. 7:27-22]6Emissions Statements: Submit an annualemission statement (if required)electronically to the NJDEP by May 15 ofeach year (or by mutually agreedupon date,but no later than June 15 of each year).[N.J.A.C. 7:27-21]Other: The emission statement will be basedon monitoring, recording and recordkeepingof actual emissions, capture and controlefficiencies, process rate and operating datafor source operations with the potential toemit certain air contaminants. [N.J.A.C.7:27-21].Other: The emission statement and allsupporting records shall be maintained onthe operating premises for a period of five(5) years from the due date of each emissionstatement. [N.J.A.C. 7:27-21].Submit an Annual Emission Statement:Annually (if required) electronically by May15 or by any mutually agreed upon date, butnot later than June 15 of each year.[N.J.A.C. 7:27-21]7Compliance Certification: Submit annualcompliance certification for each applicablerequirement, pursuant to N.J.A.C.7:27-22.19(f), within 60 days after the endof each calendar year during which thispermit was in effect. [N.J.A.C. 7:27-22]None.None.Submit an Annual Compliance Certification:Annually to the Department and EPA onforms provided by the Department within 60days after the end of each calendar yearduring which this permit was in effect. Theannual compliance certification reportingperiod will cover the calendar year endingDecember 31. Forms provided by theDepartment can be found on theDepartment's web site at the following link:http://www.nj.gov/dep/enforcement/compliancecertsair.htm[N.J.A.C. 7:27-22]8Prevention of Air Pollution fromArchitectural Coatings and ConsumerProducts. [N.J.A.C. 7:27-23]None.None.None.9Any operation of equipment which causesoff-property effects, including odors, orwhich might reasonably result in citizen'scomplaints shall be reported to theDepartment to the extent required by the AirPollution Control Act, N.J.S.A.26:2C-19(e). [N.J.S.A. 26:2C-19(e)]Other: Observation of plant operations.[N.J.S.A. 26:2C-19(e)].Other: Maintain a copy of all informationsubmitted to the Department. [N.J.S.A.26:2C-19(e)].Notify by phone: Upon occurrence of event.A person who causes a release of aircontaminants in a quantity or concentrationwhich poses a potential threat to publichealth, welfare or the environment or whichmight reasonably result in citizen complaintsshall immediately notify the Department.Such notification shall be made by callingthe Environmental Action Hotline at (877)927-6337. [N.J.S.A. 26:2C-19(e)]Page 2 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement10Prevention of Significant Deterioration(PSD). [40 CFR 52.21]Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].Comply with the requirement: Uponoccurrence of event. If subject to PSD, thepermittee shall submit an administrativelycomplete application when applying for asignificant modification pursuant toN.J.A.C. 7:27-22.24. [N.J.A.C. 7:27-22]11National Emission Standards for HazardousAir Pollutants (NESHAPS) for Asbestos.[40 CFR 61]Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].Comply with the requirement: Uponoccurrence of event. The permittee shallcomply with 40 CFR 61.145 and 61.150when conducting any renovation ordemolition activities at the facility. [40 CFR61]12Protection of Stratospheric Ozone:1) If thepermittee manufactures, transforms,destroys, imports, or exports a Class I orClass II substance, the permittee is subjectto all the requirements as specified at 40CFR 82, Subpart A; 2) If the permitteeperforms a service on motor "fleet" vehicleswhen this service involves an ozonedepleting substance refrigerant (or regulatedsubstance) in the motor vehicle airconditioner (MVAC), the permittee issubject to all the applicable requirements asspecified at 40 CFR 82, Subpart B. 3) Thepermittee shall comply with the standardsfor labeling of products containing ormanufactured with ozone depletingsubstances pursuant to 40 CFR 82, SubpartE. 4). The permittee shall comply with thestandards for recycling and emissionreductions of Class I and Class IIrefrigerants or a regulated substitutesubstance during the service, maintenance,repair, and disposal of appliances pursuantto 40 CFR 82, Subpart F, except as providedfor motor vehicle air conditioners (MVACs)in Subpart B. 5) The permittee shall beallowed to switch from any ozone depletingsubstance to any alternative that is listed inthe Significant New Alternative Program(SNAP) promulgated pursuant to 40 CFR82, Subpart G. [40 CFR 82]Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].Comply with the requirement: Uponoccurrence of event. The permittee shallcomply with 40 CFR 82 Subparts A, B, E,F, and G. [40 CFR 82]Page 3 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement13Deviation Report: In accordance withN.J.A.C. 7:27-22.19(c) and 22.19(d)3, thepermittee shall submit to the Department, onforms provided by the Department, acertified six-month deviation report relatingto testing and monitoring required by theoperating permit, not including informationfor stack emissions testing or continuousemissions monitoring which have otherreporting schedules specified in the permit(normally, stack test report is submittedwithin 45 days of test completion andcontinuous monitor reporting is donequarterly). Pursuant to N.J.A.C.7:27-22.19(e), the six-month report mustaddress other specified monitoring,including continuous and periodicmonitoring requirements found in column 2and 3, entitled "Monitoring Requirement"and "Recordkeeping Requirement,"respectively, of the Facility SpecificRequirements section of this permit. Thesesix-month reports shall clearly identify alldeviations from operating permitrequirements, the probable cause of suchdeviations, and any corrective actions orpreventive measures taken. If no deviationsoccurred, the report should say so. Any"None" listed in the Submittal/ActionRequirement in the Operating Permit is notintended to override the six-month deviationreport. [N.J.A.C. 7.27-22.19(d)3, N.J.A.C.7.27-22.19(e), and [N.J.A.C. 7:27-22.19(c)]None.Other: The permittee shall maintaindeviation reports for a period of five yearsfrom the date each report is submitted to theDepartment. [N.J.A.C. 7:27-22.19(a)].Submit a report: As per the approvedschedule. The six-month reports for otherspecified testing or monitoring required bythe operating permit performed fromJanuary 1 through June 30 shall besubmitted by July 30 of the same calendaryear, and from July 1 through December 31,shall be submitted by January 30 of thefollowing calendar year. The report shall besubmitted to the Regional EnforcementOffice and shall be certified pursuant toN.J.A.C. 7:27-1.39 by the responsibleofficial. Forms provided by the Departmentcan be found on the Department's web site atthe following link:http://www.nj.gov/dep/enforcement/compliancecertsair.htm[N.J.A.C. 7:27-22]14No person shall combust used oil except asauthorized pursuant to N.J.A.C. 7:27-20.[N.J.A.C. 7:27-20.2]None.None.Comply with the requirement: Prior tooccurrence of event (prior to burning usedoil) either register with the Departmentpursuant to N.J.A.C. 7:27-20.3 or obtain apermit issued by the Department pursuantto N.J.A.C. 7:27-8 or 7:27-22, whichever isapplicable. [N.J.A.C. 7:27-20.2(d)]Page 4 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement15Prevention of Accidental Releases: Facilitiesproducing, processing, handling or storing achemical, listed in the tables of 40 CFR Part68.130, and present in a process in aquantity greater than the listed ThresholdQuantity, shall comply with 40 CFR 68. [40CFR 68]Other: Comply with 40 CFR 68. [40 CFR68].Other: Comply with 40 CFR 68. [40 CFR68].Other (provide description): Other. Complywith 40 CFR 68 as described in theApplicable Requirement. [40 CFR 68]16For equipment subject to CO2 BudgetTrading Program, comply with N.J.A.C.7:27C. [N.J.A.C. 7:27C]Other: See N.J.A.C. 7:27C. [N.J.A.C.7:27C].Other: See N.J.A.C. 7:27C. [N.J.A.C.7:27C].Comply with the requirement: Uponoccurrence of event. [N.J.A.C. 7:27C]Page 5 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Subject Item:GR1 Facility Annual Emission Limit Cap for U1, U2, U3, and U7 combinedRef.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1NOx (Total) <= 292.4 tons/yr. Maximumallowable emission limit for facility basedon sum of annual limits from emission unitsU1, U2, U3, and U7. [N.J.A.C.7:27-22.16(a)]NOx (Total): Monitored by calculationseach month during operation, based on onecalendar year. The annual emissions of totalNOx shall be calculated as follows:Total Facility Monthly NOx Emissions =[tons of NOx during the normal operatingscenario per month (from CEM data)] +[startup hours per month x 111 lbs/hr x 1ton/2000 lbs.] + [1.917 lbs/hr for the fuelgas heater x hours of operation per month x1 ton/2000 lbs.]Total Facility Annual NOx Emissions is thesum of the monthly calculated values.The permittee may use CEM data todemonstrate compliance. [N.J.A.C.7:27-22.16(a)]NOx (Total): Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]None.2CO <= 704.8 tons/yr. Maximum allowableemission limit for facility based on sum ofannual limits from emission units U1, U2,U3, and U7. [N.J.A.C. 7:27-22.16(e)]The annual emissions of total CO shall becalculated as follows:Total Facility Monthly CO Emissions =[tons of CO during the normal operatingscenario (from CEM data)] + [startup hoursfor three turbines per month x 504 lbs/hr x 1ton/2000 lbs.] + [ 0.88 lbs/hr for the fuelgas heater x hours of operation per month x1 ton/2000 lbs.]Total Facility Annual CO Emissions is thesum of the monthly calculated values.The permittee may use CEM data todemonstrate compliance. CO: Monitored bycalculations each month during operation,based on one calendar year. [N.J.A.C.7:27-22.16(a)]CO: Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(e)]None.Page 6 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement3VOC (Total) <= 102.9 tons/yr. Maximumallowable emission limit for facility basedon sum of annual limits from emission unitsU1, U2, U3, and U7. [N.J.A.C.7:27-22.16(e)]VOC (Total): Monitored by calculationseach month during operation, based on onecalendar year The annual emissions of totalVOC shall be calculated as follows:Total Facility Monthly VOC Emissions =[MMft^3 of natural gas burned for all threeturbines for each operating scenario permonth x 1,000 BTU/ft^3 x 0.00405lbs./MMBtu x 1 ton/2,000 lbs.] +[startuphours for three turbines per month x 87lbs/hr x 1 ton/2,000 lbs.] + [0.11 lbs./hr forthe fuel gas heater x hours of operation permonth x 1ton/2,000 lbs.]Total Facility Annual VOC Emissions is thesum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor (lb./MMBtu) determined asthe average value in compliance stacktesting may also be substituted for thedefault emission factor, at the discretion ofthe permittee.Startup is defined as being the periodbeginning when fuel is first fired and endingwhen emissions are within permit limits.[N.J.A.C. 7:27-22.16(a)]VOC (Total): Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]None.Page 7 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement4SO2 <= 104.1 tons/yr. Maximum allowableemission limit for facility based on sum ofannual limits from emission units U1, U2,U3, and U7. [N.J.A.C. 7:27-22.16(a)]SO2: Monitored by calculations each monthduring operation, based on one calendaryear The annual emissions of total SO2 shallbe calculated as follows:Total Facility Monthly SO2 Emissions =[MMft^3 of natural gas burned for all threeturbines for each operating scenario permonth x 1,000 BTU/ft^3 x 0.0043lbs/MMBtu x 1 ton/2,000 lbs] + [0.069lbs/hr for the fuel gas heater x hours ofoperation per month x 1ton/2,000 lbs]Total Facility Annual SO2 Emissions is thesum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor (lb/mmBtu) determined asthe average value in compliance stacktesting may also be substituted for thedefault emission factor, at the discretion ofthe permittee.The permittee may use CEM data todemonstrate compliance. [N.J.A.C.7:27-22.16(a)]SO2: Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(e)]None.Page 8 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement5TSP <= 345.1 tons/yr. Maximum allowableemission limit for facility based on sum ofannual limits from emission units U1, U2,U3, and U7. [N.J.A.C. 7:27-22.16(a)]TSP: Monitored by calculations each monthduring operation, based on one calendaryear The annual emissions of total TSP shallbe calculated as follows:Total Facility Monthly TSP Emissions =[MMft^3 of natural gas burned for all threeturbines for each operating scenario permonth x 1,000 BTU/ft^3 x 0.01351lbs./MMBtu x 1 ton/2,000 lbs.] + [1.316tons per month for the cooling tower] +[0.12 lbs/hr for the fuel gas heater x hours ofoperation per month x 1ton/2,000 lbs.]Total Facility Annual TSP Emissions is thesum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor (lb/MMBtu) determined asthe average value in compliance stacktesting may also be substituted for thedefault emission factor, at the discretion ofthe permittee. The permittee may use CEMdata to demonstrate compliance. [N.J.A.C.7:27-22.16(a)]TSP: Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(e)]None.Page 9 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6PM-10 (Total) <= 345.1 tons/yr. Maximumallowable emission limit for facility basedon sum of annual limits from emission unitsU1, U2, U3, and U7. [N.J.A.C.7:27-22.16(a)]PM-10 (Total): Monitored by calculationseach month during operation, based on onecalendar year The annual emissions of totalPM10 shall be calculated as follows:Total Facility Monthly PM10 Emissions =[MMft^3 of natural gas burned for all threeturbines for each operating scenario permonth x 1,000 BTU/ft^3 x 0.01351lbs./MMBtu x 1 ton/2,000 lbs.] + [1.316tons per month for the cooling tower] +[0.12 lbs/hr for the fuel gas heater x hours ofoperation per month x 1ton/2,000 lbs.]Total Facility Annual PM10 Emissions isthe sum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor (lb/MMBtu) determined asthe average value in compliance stacktesting may also be substituted for thedefault emission factor, at the discretion ofthe permittee. The permittee may use CEMdata to demonstrate compliance. [N.J.A.C.7:27-22.16(a)]PM-10 (Total): Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]None.Page 10 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement7Ammonia <= 347 tons/yr. Maximumallowable emission limit for facility basedon sum of annual limits from emission unitsU1, U2, and U3. [N.J.A.C. 7:27-22.16(a)]Ammonia: Monitored by calculations eachmonth during operation, based on onecalendar year Annual emissions of totalAmmonia shall be calculated as follows:Total Facility Monthly Ammonia Emissions=[MMft^3 of natural gas burned per year forall three turbines for each operating scenarioper month x 1000 Btu/ft^3 x 0.015lbs./MMBtu x 1 ton/2,000 lbs.]Total Facility Annual Ammonia Emissionsis the sum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor (lb/MMBtu) determined asthe average value in compliance stacktesting may also be substituted for thedefault emission factor, at the discretion ofthe permittee. [N.J.A.C. 7:27-22.16(e)]Ammonia: Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]None.Page 11 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement8SO3 and H2SO4, as converted andexpressed as H2SO4 <= 63.6 tons/yr.Maximum allowable emission limit forfacility based on sum of annual limits fromemission units U1, U2, U3, and U7.[N.J.A.C. 7:27-22.16(a)]SO3 and H2SO4, as converted andexpressed as H2SO4: Monitored bycalculations each month during operation.The annual emissions of total Sulfur shall becalculated as follows:Total Facility Monthly Sulfur Emissions =[MMFt^3 of natural gas burned for all threeturbines for each operating scenario permonth x 1000 BTU/ft^3 x 0.00263 lbs./MMBtu x 1 ton/ 2000 lbs.]Total Facility Annual Sulfur Emissions isthe sum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor (lb./MMBtu) determined asthe average value in compliance stacktesting may also be substituted for thedefault emission factor, at the discretion ofthe permittee. [N.J.A.C. 7:27-22.16(e)]SO3 and H2SO4, as converted andexpressed as H2SO4: Recordkeeping bymanual logging of parameter each monthduring operation showing the calculatedvalue for the month and sum-to-date.[N.J.A.C. 7:27-22.16(e)]None.Page 12 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Emission Unit:U1 Combined Cycle Units -Three turbines each with aheat input of 2180 MMBtu/hrOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Continuously monitor NOx, CO and O2emitted from emission points PT1, PT2 andPT3, using a Continuous EmissionMonitoring (CEM) system. Emissions shallbe monitored during all operation of theturbine. [N.J.A.C. 7:27-22.16(o)]Monitored by continuous emissionmonitoring system continuously. [N.J.A.C.7:27-22.16(o)]Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]CEMS/COMS - Submit equipment protocol,submit a PST protocol, conduct PST andsubmit results: As per the approvedschedule. [N.J.A.C. 7:27-22.16(o)]OS SummaryPage 13 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement2Conduct a comprehensive stack test atemission points PT1, PT2 and PT3 at least18 months prior to the expiration date of theapproved operating permit to demonstratecompliance with the NOx, CO, VOC, SO2,TSP, PM-10, Ammonia, and (SO3 andH2SO4) emission limits.Three tests shall be conducted at worst-casepermitted operating conditions for thecorresponding test, such as ambient (relativehumidity and temperature) conditions, withregard to meeting the applicable emissionstandards, but without creating an unsafecondition. The Permittee shall submit toBTS all data necessary to substantiate theambient conditions. The testing shall beconducted inaccordance with a protocolapproved by Chief, BTS. [N.J.A.C.7:27-22.16(a)] [N.J.A.C. 7:27-22.16(a)]Monitored by stack emission testing at theapproved frequency Unless otherwiseapproved in the stack test protocol or by theDepartment, each test run shall be 60minutes in sampling duration. Complianceperiod shall be as specified in themonitoring requirement for each applicableemission limit.Stack tests shall be conducted for NOx, CO,VOC, SO2, TSP, PM-10, Ammonia, and(SO3 and H2SO4) emissions whilecombusting natural gas. [N.J.A.C.7:27-22.16(o)]Recordkeeping by stack test results at theapproved frequency. [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule Stack Test - Submit a protocol,conduct test, submit results: As per theapproved schedule. Submit a stack testprotocol to the Bureau of Technical Services(BTS) at PO Box 437, Trenton, NJ 08625 atleast 30 months prior to the expiration of theapproved operating permit.Within 30 days of protocol approval, thepermittee must contact BTS at609-530-4041 to schedule a mutuallyacceptable test date. A full stack test reportmust be submitted to BTS and a certifiedsummary test report, as described in theprotocol, must be submitted to the RegionalEnforcement Office within 45 days afterperforming the stack test pursuant toN.J.A.C. 7:27-22.19(d). The test resultsmust be certified by a licensed professionalengineer or certified industrial hygienist.A copy of the certified summary test resultsmust be submitted with the operating permitrenewal application due at least 12 monthsprior to expiration of the Operating Permit.The test results shall report lb/hr, lb/hrcorrected to ISO conditions (for NOx only),lb/MWHr (for NOx only),lb/MMBTU(HHV) and ppmdv@15% O2.For the purpose of determining compliancewith NSPS Subpart GG, loads shall becorrected to ISO conditions. [N.J.A.C.7:27-22.18(e)] and [N.J.A.C.7:27-22.18(h)]. [N.J.A.C. 7:27-22.16(e)]Page 14 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement3Opacity <= 20 %. No person shall cause,suffer, allow or permit smoke greater than20 percent opacity, exclusive of visiblecondensed water vapor, to be emitted intothe outdoor air from the combustion of fuelin any stationary internal combustion engineor any stationary turbine engine for a periodof more than 10 consecutive seconds.[N.J.A.C. 7:27- 3.5]None.None.None.4Particulate Emissions <= 218 lb/hrParticulate emission limit from thecombustion of fuel based on rated heat inputof source. [N.J.A.C. 7:27- 4.2(a)]None.None.None.5CO <= 250 ppmvd @ 15% O2. [N.J.A.C.7:27-16.9(b)]CO: Monitored by continuous emissionmonitoring system continuously, based onone calendar day , not including periods ofdowntime. [N.J.A.C. 7:27-16.23(a)1]CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-22.16(e)]6VOC (Total) <= 50 ppmvd @ 15% O2.[N.J.A.C. 7:27-16.9(c)]VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (For stacktesting details, see U1OS Summary, Ref #2). [N.J.A.C.7:27-16.23(a)1]VOC (Total): Recordkeeping by stack testresults prior to permit renewal (For stacktesting details, see U1 OS Summary, Ref#2). [N.J.A.C. 7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (For stack testing details, see U1OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]7NOx (Total) <= 1.3 lb/MW-hr. NOx RACTemission limit for non-HEDD turbinesapplies during all periods of natual gascombustion. To calculate lb/MWh, for unitswhere energy is used for other than electricgeneration, for example combined heat andpower unit, that useful energy should beconverted to equivalent MWh and added tothe electric output. Emission rate is basedon net energy output (both electric anduseful heat). N.J.A.C. 7:27-19.5(d) and.[N.J.A.C. 7:27-19.5(f)]NOx (Total): Monitored by continuousemission monitoring system continuously,based on a calendar day (in ozone season) or30 day rolling (at other times) average. (seeU1 / OS Summary / Ref. #1). [N.J.A.C.7:27-22.16(o)]NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. (see U1 / OSSummary / Ref. #1). [N.J.A.C.7:27-22.16(o)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-21.16(o)]Page 15 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement8NOx (Total) <= 1.3 lb/MW-hr. NOx RACTemission limit for non-HEDD turbinesapplies during all periods of natual gascombustion. To calculate lb/MWh, for unitswhere energy is used for other than electricgeneration, for example combined heat andpower unit, that useful energy should beconverted to equivalent MWh and added tothe electric output. Emission rate is basedon net energy output (both electric anduseful heat). N.J.A.C. 7:27-19.5(d) and.[N.J.A.C. 7:27-19.5(f)]NOx (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs. (see U1 / OS Summary / Ref. #2).[N.J.A.C. 7:27-22.16(o)]NOx (Total): Recordkeeping by stack testresults at the approved frequency. (see U1 /OS Summary / Ref. #2). [N.J.A.C.7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule. (see U1 / OS Summary / Ref. #2).[N.J.A.C. 7:27-21.16(o)]9The Permittee shall adjust the combustionprocess in accordance with the procedure setforth at N.J.A.C. 7:27-19.16, in order tooptimize the emission of NOx, CO andVOC. Adjustment of the combustionprocess shall be carried out according tomanufacturer's recommended proceduresand maintenance schedules for the turbine.[N.J.A.C. 7:27-16.9(f)2, N.J.A.C.7:27-19.5(e)2] & [N.J.A.C. 7:27-19.16(g)]Monitored by continuous emissionmonitoring system upon performingcombustion adjustment Or PeriodicEmission Monitoring. [N.J.A.C.7:27-19.16(h)]Recordkeeping by data acquisition system(DAS) / electronic data storage uponperforming combustion adjustment ormanual logging of parameter. All recordsshall be kept in a permanent form suitablefor inspections, retained for a minimum of 5years, and made readily accessible to theDepartment, upon request.The owner or operator shall record thefollowing information for each adjustment:1. The date of the adjustment and the timesat which it began and ended;2. The name, title and affiliation of theperson who performed the procedure andadjustment;3. The type of procedure and maintenanceperformed;4. The concentration of NOx, CO and O2measured before and after the adjustmentwas made; and5. The type and amount of fuel used sincethe last combustion adjustment wasperformed. [N.J.A.C. 7:27-19.16(h)]None.Page 16 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement10An exceedance of an emission limit thatoccurs during an adjustment of thecombustion process under N.J.A.C.7:27-19.16(g) is not a violation of thissubchapter if it occurs as a result of theadjustment. After the combustionadjustment has been completed, themaximum emission rate of any contaminantshall not exceed the maximum allowableemission rate applicable under thissubchapter or under an operating permitissued pursuant to N.J.A.C. 7:27-22 or anapplicable certificate issued pursuant toN.J.A.C. 7:27-8. [N.J.A.C. 7:27-19.16(f)]None.None.None.11NOx (Total) <= 284 tons/yr. Maximumannual emission limit from preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]NOx (Total): Monitored by calculationseach month during operation, based on onecalendar year. The annual emissions of totalNOx shall be calculated as follows:Total Monthly NOx Emissions =[tons of NOx during the normal operatingscenario per month (from CEM data)] +[startup hours per month x 111 lbs/hr x 1ton/2000 lbs.]Total Annual NOx Emissions is the sum ofthe monthly calculated values.See U1, OS Summary Ref #17 for Startupperiod definition.The permittee may use CEM data todemonstrate compliance. [N.J.A.C.7:27-22.16(e)]NOx (Total): Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]None.Page 17 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement12CO <= 701.1 tons/yr. Maximum annualemission limit from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]The annual emissions of total CO shall becalculated as follows:Total Monthly CO Emissions =[tons of CO during the normal operatingscenario per month (from CEM data)] +[startup hours per month x 504 lbs/hr x 1ton/2000 lbs.]Total Annual CO Emissions is the sum ofthe monthly calculated values.See U1, OS Summary Ref #17 for Startupperiod definition.The permittee may use CEM data todemonstrate compliance. CO: Monitored bycalculations each month during operation,based on one calendar year. [N.J.A.C.7:27-22.16(e)]CO: Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(e)]None.Page 18 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement13VOC (Total) <= 102.5 tons/yr. Maximumannual emission limit from preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]VOC (Total): Monitored by calculationseach month during operation, based on onecalendar year The annual emissions of totalVOC shall be calculated as follows:Total Monthly VOC Emissions =[MMft^3 of natural gas burned for all threeturbines per month x 1,000 BTU/ft^3 x0.00405 lbs./MMBtu x 1 ton/2,000 lbs.] +[startup hours per month x 87 lbs/hr x 1ton/2,000 lbs.]Total Annual VOC Emissions is the sum ofthe monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor of 0.00038 lb./MMBtudetermined as the average value incompliance stack testing, may also besubstituted for the default emission factor, atthe discretion of the permittee.See U1, OS Summary Ref #17 for Startupperiod definition. [N.J.A.C. 7:27-22.16(e)]VOC (Total): Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]None.Page 19 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement14SO2 <= 103.8 tons/yr. Maximum annualemission limit from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]SO2: Monitored by calculations each monthduring operation, based on one calendaryear The annual emissions of total SO2 shallbe calculated as follows:Total Monthly SO2 Emissions =[MMft^3 of natural gas burned for all threeturbines per month x 1,000 BTU/ft^3 x0.0043 lbs/MMBtu x 1 ton/2,000 lbs].Total Annual SO2 Emissions is the sum ofthe monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor of 0.0004 lb/mmBtudetermined as the average value incompliance stack testing, may also besubstituted for the default emission factor, atthe discretion of the permittee. [N.J.A.C.7:27-22.16(e)]SO2: Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(e)]None.Page 20 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement15TSP <= 328.8 tons/yr. Maximum annualemission limit from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]TSP: Monitored by calculations each monthduring operation, based on one calendaryear The annual emissions of total TSP shallbe calculated as follows:Total Monthly TSP Emissions =[MMft^3 of natural gas burned for all threeturbines per month x 1,000 BTU/ft^3 x0.01351 lbs./MMBtu x 1 ton/2,000 lbs.]Total Annual TSP Emissions is the sum ofthe monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor of 0.00133 lb/MMBtudetermined as the average value incompliance stack testing, may also besubstituted for the default emission factor, atthe discretion of the permittee. [N.J.A.C.7:27-22.16(e)]TSP: Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(e)]None.Page 21 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement16PM-10 (Total) <= 328.8 tons/yr. Maximumannual emission limit from preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]PM-10 (Total): Monitored by calculationseach month during operation, based on onecalendar year The annual emissions of totalPM-10 shall be calculated as follows:Total Monthly PM-10 Emissions =[MMft^3 of natural gas burned for all threeturbines per month x 1,000 BTU/ft^3 x0.01351 lbs./MMBtu x 1 ton/2,000 lbs.]Total Annual PM10 Emissions is the sum ofthe monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor of 0.00477 lb/MMBtudetermined as the average value incompliance stack testing, may also besubstituted for the default emission factor, atthe discretion of the permittee. [N.J.A.C.7:27-22.16(e)]PM-10 (Total): Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]None.Page 22 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement17Ammonia <= 347 tons/yr. Maximum annualemission limit from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]Ammonia: Monitored by calculations eachmonth during operation, based on onecalendar year Annual emissions of totalAmmonia shall be calculated as follows:Total Monthly Ammonia Emissions=[MMft^3 of natural gas burned per monthfor all three turbines x 1000 Btu/ft^3 x0.0135 lbs./MMBtu x 1 ton/2,000 lbs.]Total Annual Ammonia Emissions is thesum of the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor of 0.0003 lb/MMBtudetermined as the average value incompliance stack testing, may also besubstituted for the default emission factor, atthe discretion of the permittee. [N.J.A.C.7:27-22.16(e)]Ammonia: Recordkeeping by manuallogging of parameter each month duringoperation showing the calculated value forthe month and sum-to-date. [N.J.A.C.7:27-22.16(e)]None.Page 23 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement18SO3 and H2SO4, as converted andexpressed as H2SO4 <= 63.6 tons/yr.Maximum annual emission limit frompreconstruction permit. [N.J.A.C.7:27-22.16(e)]SO3 and H2SO4, as converted andexpressed as H2SO4: Monitored bycalculations each month during operation,based on one calendar year. The annualemissions of total Sulfur shall be calculatedas follows:Total Monthly Sulfur Emissions =[MMFt^3 of natural gas burned for all threeturbines per month x 1000 BTU/ft^3 x0.00263 lbs./ MMBtu x 1 ton/ 2000 lbs.]Total Annual Sulfur Emissions is the sumof the monthly calculated values.In calculating the turbine emissions, thepermittee may substitute the actual measuredfuel heat content for the default value. Anemission factor of 0.0003 lb./MMBtudetermined as the average value incompliance stack testing, may also besubstituted for the default emission factor, atthe discretion of the permittee. [N.J.A.C.7:27-22.16(e)]SO3 and H2SO4, as converted andexpressed as H2SO4: Recordkeeping bymanual logging of parameter each monthduring operation showing the calculatedvalue for the month and sum-to-date.[N.J.A.C. 7:27-22.16(e)]None.19Ammonia <= 10 ppmdv. [N.J.A.C.7:27-22.16(e)]Ammonia: Monitored by stack emissiontesting prior to permit renewal, based oneach of three Department validated stack testruns (For stack testing details, see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]Ammonia: Recordkeeping by stack testresults prior to permit renewal (For stacktesting details, see U1 OS Summary, Ref#2). [N.J.A.C. 7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (For stack testing details, see U1OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]20Only natural gas shallbe combusted into thestationary gas turbine. [N.J.A.C.7:27-22.16(e)]None.None.None.Page 24 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement21Natural Gas Usage <= 63,122.16MMft^3/yr. [N.J.A.C. 7:27-22.16(a)]Natural Gas Usage: Monitored by fuelflow/firing rate instrument continuously,based on a consecutive 365 day period(rolling 1 day basis). The permittee shallinstall and operate a running gasuse-totallizing meter on each turbine tomonitor the consumption of natural gas, perturbine, in any 365 consecutive days period.The running gas meter shall be installed,operated, and calibrated according tomanufacturer's recommendations. [N.J.A.C.7:27-22.16(o)]Natural Gas Usage: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. Compliance shall bedetermined based on any 365 consecutiveday period. Cubic feet per any 365consecutive days period shall be calculatedby the sum of the cubic feet calculatedduring any one day added to the sum of thecubic feet calculated during the preceding364 days. This procedure will begin with thefirst day following the final issuance of theOperating permit. This accounting will notinclude cubic feet consumed prior to theapproval of the Operating Permit. [N.J.A.C.7:27-22.16(o)]None.22Start-up Period: Start-up commences withthe initiation of the combustion of fuel inthe combustion turbine and concludes whenthe turbine reaches a steady state operationload. Start up period shall not exceed 21hours total for the combustion turbine units.[N.J.A.C. 7:27-22.16(e)]Start-up Period: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]Start-up Period: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(o)]None.23Shutdown Period: Combustion turbineshutdown is defined as the period of timefrom the initial lowering of combustionturbine output of the base load until fuelflow is completely off and combustion hasceased. [N.J.A.C. 7:27-22.16(e)]Shutdown Period: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]Shutdown Period: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(o)]None.24Except during startup and shutdown, theSCR system (including the ammoniainjection) and the oxidation catalyst shall beoperational at all times the turbine isoperating. [N.J.A.C. 7:27-22.16(e)]None.None.None.25The SCR catalyst array(s) shall bemaintained and replaced in accordance withthe recommendations of the manufacturer,and as necessary based on emission levelsindicated through continuous/portableemission monitoring. [N.J.A.C.7:27-22.16(e)]Other: Monitored by emission levelsindicated through continuous/portableemission monitoring.[N.J.A.C.7:27-22.16(o)].Other: Maintain the SCR catalystsmaintenance and replacementrecords.[N.J.A.C. 7:27-22.16(o)].None.Page 25 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement26Ammonia Flow Rate to SCR <= 72.11gal/hr (19% Ammonium Hydroxide solutionin water). [N.J.A.C. 7:27-22.16(e)]Ammonia Flow Rate to SCR: Monitored bymaterial feed/flow monitoring continuously.[N.J.A.C. 7:27-22.16(o)]Ammonia Flow Rate to SCR:Recordkeeping by data acquisition system(DAS) / electronic data storage at theapproved frequency. [N.J.A.C.7:27-22.16(o)]None.27The oxidizer catalyst array(s) shall bemaintained and replaced or changed inaccordance with the recommendations of themanufacturer. [N.J.A.C. 7:27-22.16(e)]Other: Monitored by emission levelsindicated through continuous emissionmonitoring.[N.J.A.C. 7:27-22.16(o)].Other: Maintain the oxidation catalystsmaintenance, replacement or changingrecords including date and time ofmaintenance, replacement or change of theoxidation catalyst.[N.J.A.C. 7:27-22.16(o)].None.28Minimum VOC Destruction and RemovalEfficiency >= 80 %. The catalytic oxidizershall be designed for a minimum VOCdestruction and removal efficiency.[N.J.A.C. 7:27-22.16(e)]None.None.None.29Temperature at Catalyst Bed <= 800 degreesF , while working at 100% load. [N.J.A.C.7:27-22.16(a)]Temperature at Catalyst Bed: Monitored bytemperature instrument continuously.[N.J.A.C. 7:27-22.16(o)]Temperature at Catalyst Bed:Recordkeeping by strip chart continuously.[N.J.A.C. 7:27-22.16(o)]None.30The permittee shall submit an ExcessEmission Monitoring Performance Report tothe Department for review and approval[N.J.A.C. 7:27-22.16(e)]None.None.Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-22.16(e)]Page 26 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement31The owner or operator shall develop aQA/QC plan for all CEMS/COMS requiredby this permit. This QA/QC plan shallincorporate at a minimum those proceduresoutlined in 40 CFR, Part 60, Appendix Fand/or 40 CFR, Part 75, Appendix B forCEMS and those procedures outlined in 40CFR, Part 60, Appendix B, SpecificationOne and 40 CFR, Part 51, Proposed RM203 for COMS, published DepartmentTechnical Manuals or other proceduresapproved in writing by the Department. TheQA/QC plan shall designate a coordinatorfor the facility who is responsible to ensurethat the QA/QC plan is implemented. TheDepartment reserves the right to require theQA/QC plan to be revised at any time basedon the results of quarterly EEMPR reviews,inspections, audits or any other informationavailable to the Department. All proceduresoutlined in the QA/QC plan shall commenceupon the completion date of the PST. Allredundant CEMS/COMS must undergo theQA/QC procedure. [N.J.A.C. 7:27-22.16(a)][N.J.A.C. 7:27-22.16(a)]Other: The QA/QC coordinator shall beresponsible for reviewing the QA/QC planon an annual basis.[N.J.A.C. 7:27-22.16(o)].Other: Maintain readily accessible recordsof the QA/QC plan including QA date andquarterly reports.[N.J.A.C. 7:27-22.16(o)].Submit a report: Every April 30, July 30,October 30, and January 30 for thepreceding quarter year (the quarter yearsbegin on January 1, April 1, July 1, andOctober 1). All quarterly and annual QAdata shall be included in quarterly EEMPRreports and kept on file at the facility. TheQA data must be made available to theDepartment upon request. [N.J.A.C.7:27-22.16(o)]. [N.J.A.C. 7:27-22.16(o)]32All requests, reports, applications,submittals, and other communications to theAdministrator pursuant to Part 60 shall besubmitted in duplicate to the RegionalOffice of US Environmental ProtectionAgency. Submit information to: Region II,Director, Air and Waste ManagementDivision, US Environmental ProtectionAgency, 21st Floor, 290 Broadway, NewYork, NY 10007. [40 CFR 60.4(a)]None.None.Submit a report: As per the approvedschedule to EPA Region II as required by 40CFR 60. [40 CFR 60.4(a)]33Copies of all information submitted to EPApursuant to 40 CFR Part 60, must also besubmitted to the appropriate RegionalEnforcement Office of NJDEP. [40 CFR60.4(b)]None.None.Submit a report: Upon occurrence of eventto NJDEP Southern Regional EnforcementOffice, 1 Port Center, 2 Riverside Drive,Camden, NJ 08013. [40 CFR 60.4(b)]Page 27 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement34The owner or operator subject to theprovisions of 40 CFR Part 60 shall furnishthe Administrator written notification or, ifacceptable to both the Administrator and theowner or operator of a source, electronicnotification, of the date of construction orreconstruction of an affected facility asdefined under 40 CFR Part 60 Subpart A.Notification shall be postmarked no laterthan 30 days after such date. [40 CFR60.7(a)(1)]None.None.Submit notification: Upon occurrence ofevent to EPA Region II and the appropriateRegional Enforcement Office of NJDEP asrequired by 40 CFR 60.7 [40 CFR60.7(a)(1)]35The owner or operator subject to theprovisions of 40 CFR Part 60 shall furnishthe Administrator written notification or, ifacceptable to both the Administrator and theowner or operator of a source, electronicnotification, of the actual date of initialstartup of an affected facility postmarkedwithin 15 days after such date. [40 CFR60.7(a)(3)]None.None.Submit notification: Upon occurrence ofevent to EPA Region II and the appropriateRegional Enforcement Office of NJDEP asrequired by 40 CFR 60.7 [40 CFR60.7(a)(3)]36The owner or operator subject to theprovisions of 40 CFR Part 60 shall furnishthe Administrator written notification or, ifacceptable to both the Administrator and theowner or operator of a source, electronicnotification, of any physical or operationalchange to an existing facility which mayincrease the emission rate of any airpollutant to which a standard applies, unlessthat change is specifically exempted underan applicable subpart or in section 60.14(e).The notification shall include informationdescribing the precise nature of the change,present and proposed emission controlsystems, productive capacity of facilitybefore and after the change and the expectedcompletion date of the change. Notificationshall be postmarked within 60 days or assoon as practicable before any change iscommenced. The Administrator mayrequest additional relevant informationsubsequent to this notice. [40 CFR60.7(a)(4)]None.None.Submit notification: Prior to occurrence ofevent. Submit written notification within 60days prior to, or as soon as practicable, thecommencement of the change. [40 CFR60.7(a)(4)]Page 28 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement37The owner or operator shall furnish theAdministrator written notification as follows:A notification of the date upon whichdemonstration of the continuous emissionmonitoring system performance commencesin accordance to 40 CFR 60.13(c). Thenotification shall be postmarked no less than30 days prior to such date. [40 CFR60.7(a)(5)]Submit notification: Every April 30, July 30,October 30, and January 30 for thepreceding quarter year (the quarter yearsbegin on January 1, April 1, July 1, andOctober 1) to the Department for review andapproval. [40 CFR 60.7(a)(5)]38The owner or operator shall maintainrecords of the occurrence and duration ofany startup, shutdown, or malfunction in theoperation of an affected facility, anymalfunction of air pollution controlequipment or any periods during whichcontinuous monitoring system or monitoringdevice is inoperative. [40 CFR 60.7(b)]None.Recordkeeping by manual logging ofparameter upon occurrence of event. Therecords should be kept in a permanent formsuitable for inspections. [40 CFR 60.7(b)]None.39Each owner or operator required to install acontinuous monitoring device shall submitan excess emissions and monitoring systemsperformance report (excess emissions aredefined in applicable subparts) and/or asummary report form (see section 60.7(d))to the Administrator semiannually, exceptwhen: more frequent reporting isspecifically required by an applicablesubpart; or the Administrator, on acase-by-case basis, determines that morefrequent reporting is necessary to accuratelyassess the compliance status of the source.All reports shall be postmarked by the 30thday following the end of each six-monthperiod. [40 CFR 60.7(c)]None.Other: Written reports of excess emissionsshall include the following information: (1)The magnitude of excess emissionscomputed in accordance with section60.13(h), any conversion factor(s) used, andthe date and time of commencement andcompletion of each time period and excessemissions. The process operating timeduring the reporting period. (2) Specificidentification of each period of excessemissions that occurs during startups,shutdowns, and malfunctions of the affectedfacility. The nature and cause of anymalfunction (if known), the corrective actiontaken or preventative measures adopted. (3)The date and time identifying each periodduring which the continuous monitoringsystem was inoperative except for zero andspan checks and the nature of the systemrepairs or adjustments. (4) When no excessemissions have occurred or the continuousmonitoring system(s) have not beeninoperative, repaired, or adjusted, suchinformation shall be stated in the report. [40CFR 60.7(c)].Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Semi-annually beginning on the30th day of the 6th month following initialperformance tests. The report shall bepostmarked by the 30th day following theend of each six-month period. The reportshall be submitted to the EPA Region IIAdministrator and the appropriate RegionalEnforcement Office of NJDEP and be in theformat specified at 40 CFR Part 60.7(c) and40 CFR Part 60.7(d). [40 CFR 60.7(c)]Page 29 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement40The owner or operator shall maintain a file,suitable for inspection, of all monitoringmeasurements as indicated inRecordkeeping Requirement column. [40CFR 60.7(f)]None.Other: The file shall include allmeasurements (including continuousmonitoring system, monitoring device, andperformance testing measurements), allcontinuous monitoring system performanceevaluations, all continuous monitoringsystem or monitoring device calibrationchecks, all adjustments/maintenanceperformed on these systems or devices, andall other information required by 40 CFRPart 60 recorded in a permanent formsuitable for inspection. [40 CFR 60.7(f)].None.41At all times, including periods of start-up,shutdown, and malfunction, owners andoperators shall, to the extent practicable,maintain and operate any affected facilityincluding associated air pollution controlequipment in a manner consistent with goodair pollution control practice for minimizingemissions. Determination of whetheracceptable operating and maintenanceprocedures are being used will be based oninformation available to the Administratorwhich may include, but is not limited to,monitoring results, opacity observations,review of operation and maintenanceprocedures, and inspection of the source.[40 CFR 60.11(d)]None.None.None.42No owner or operator subject to NSPSstandards in Part 60, shall build, erect,install, or use any article, machine,equipment or process, the use of whichconceals an emission which wouldotherwise constitute a violation of anapplicable standard. Such concealmentincludes, but is not limited to, the use ofgaseous diluents to achieve compliance withan opacity standard or with a standard whichis based on the concentration of a pollutantin the gases discharged to the atmosphere.[40 CFR 60.12]None.None.None.Page 30 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement43The owner or operator shall perform zeroand span adjustments daily for continuousemission monitors and continuous opacitymonitors following procedures outlined in40 CFR Part 60.13(d)1 & 2. [40 CFR60.13(d)]None.Maintain records in accordance with 40CFR 60.7(f). Recordkeeping by strip chart,round chart or data acquisition (DAS)system / electronic data storage at theapproved frequency. [40 CFR 60.13(d)]None.44Except for system breakdowns, repairs,calibration checks, and zero and spanadjustments, all continuous monitoringsystems measuring emissions except opacityshall be in continuous operation. They shallcomplete a minimum of one cycle ofoperation (sampling, analyzing and datarecording) for each successive 15-minuteperiod. [40 CFR 60.13(e)(2)]Other: See Applicable Requirement. [40CFR 60.13(e)(2)].Other: See Applicable Requirement. [40CFR 60.13(e)(2)].None.45The owner or operator shall reduce allcontinuous monitoring systems (other thanopacity) data to 1-hour averages which shallbe computed from four or more data pointsequally spaced over each 1-hour period.Data recorded during periods of continuousmonitoring system breakdowns, repairs,calibration checks, and zero and spanadjustments shall not be included in the dataaverages computed under this paragraph.For owners and operators complying withthe requirements in 40 CFR 60.7(f)(1) or(2), data averages must include any datarecorded during periods of monitorbreakdown or malfunction. An arithmeticor integrated average of all data may beused. The data may be recorded in reducedor nonreduced form (e.g., ppm pollutant andpercent O2 or ng of pollutant per J of heatinput). All excess emissions shall beconverted into units of the standard usingthe applicable conversion proceduresspecified in subparts. After conversion intounits of the standard, the data may berounded to the same number of significantdigits as used in the applicable subparts tospecify the emission limit (e.g. rounded tothe nearest 1 percent opacity). [40 CFR60.13(h)]None.Recordkeeping by strip chart, round chart ordata acquisition (DAS) system / electronicdata storage continuously. The data may berecorded in reduced or non-reduced form.[40 CFR 60.13(h)]None.Page 31 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement46Changes in time periods for submittal ofinformation and postmark deadlines set forthin this subpart, may be made only uponapproval by the Administrator and shallfollow procedures outlined in 40 CFR Part60.19. [40 CFR 60.19]None.None.None.47NOx (Total) <= 75 ppmvd @ 15% O2. [40CFR 60.332(a)(1)]NOx (Total): Monitored by stack emissiontesting once initially, based on any 60minute period. Test methods andprocedures shall be consistent with therequirements of 40 CFR Part 60.335 [40CFR 60.335]NOx (Total): Recordkeeping by stack testresults initial calculations only no later than45 days after the completion of stack testing.[40 CFR 60.335]None.48Sulfur Content in Fuel <= 0.8 % by weight.No owner or operator subject to theprovisions of this subpart shall burn any fuelwhich contains total sulfur in excess of 0.8percent by weight (8000 ppmw). [40 CFR60.333(b)]Other: the owner or operator may elect notto monitor the total sulfur content of thegaseous fuel combusted in the turbine, if thegaseous fuel is demonstrated to meet thedefinition of natural gas in ?60.331(u),regardless of whether an existing customschedule approved by the administrator forsubpart GG requires such monitoring. Theowner or operator shall use one of thefollowing sources of information to makethe required demonstration:(i) The gas quality characteristics in acurrent, valid purchase contract, tariff sheetor transportation contract for the gaseousfuel, specifying that the maximum totalsulfur content of the fuel is 20.0 grains/100scf or less; or(ii) Representative fuel sampling data whichshow that the sulfur content of the gaseousfuel does not exceed 20 grains/100 scf. At aminimum, the amount of fuel sampling dataspecified in section 2.3.1.4 or 2.3.2.4 ofappendix D to part 75 of this chapter isrequired.[40 CFR 60.334(h)(3)].None.None.49The permittee shall comply with all of therequirements of the Phase II Acid RainPermit issued for this affected unit. [40 CFR72]Other: See attached Phase II Acid RainPermit. (Appendix I).[40 CFR 72].Other: See attached Phase II Acid RainPermit. (Appendix I).[40 CFR 72].Comply with the requirement: As per theapproved schedule. See attached Phase IIAcid Rain Permit. (Appendix I). [40 CFR72]Page 32 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement50For equipment subject to Clean AirInterstate Rule (CAIR) NOx TradingProgram, comply with N.J.A.C. 7:27-30.[N.J.A.C. 7:27-30]None.None.Comply with the requirement: Uponoccurrence of event. The owner or operatorshall comply with the reportingrequirements specified in N.J.A.C.7:27-30.6. [N.J.A.C. 7:27-30]51The permittee shall comply with all of therequirements of Clean Air Interstate Rule(CAIR) permit for the CAIR NOX AnnualTrading Program, CAIR NOX OzoneSeason Trading Program, and CAIR SO2Trading Program issued for this affectedunit. [40 CFR 97]Other: See attached CAIR Permit(Appendix II).[40 CFR 97].Other: See attached CAIR Permit(Appendix II).[40 CFR 97].Comply with the requirement: Uponoccurrence of event. See attached CAIRPermit (Appendix II). [40 CFR 97]Page 33 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Emission Unit:U1 Combined Cycle Units -Three turbines each with aheat input of 2180 MMBtu/hrOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Particulate Emissions <= 218 lb/hr.[N.J.A.C. 7:27- 4.2(a)]Particulate Emissions: Monitored by stackemission testing prior to permit renewal,based on each of three Department validatedstack test runs (see U1 OS Summary, Ref#2). [N.J.A.C. 7:27- 4.4]Particulate Emissions: Recordkeeping bystack test results prior to permit renewal (seeU1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]2NOx (Total) <= 3 ppmvd @ 15% O2 exceptfor periods of start-up, shutdown and fueltransfer as defined in this permit. [N.J.A.C.7:27-22.16(e)]NOx (Total): Monitored by continuousemission monitoring system continuously,based on a 3 hour rolling average based on a1 hour block average (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(e)]NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-22.16(e)]3NOx (Total) <= 3 ppmvd @ 15% O2 exceptfor periods of start-up, shutdown and fueltransfer as defined in this permit. [N.J.A.C.7:27-22.16(e)]NOx (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]NOx (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]4NOx (Total) <= 0.0117 lb/MMBTU exceptfor periods of start-up, shutdown and fueltransfer as defined in this permit. [N.J.A.C.7:27-22.16(e)]NOx (Total): Monitored by continuousemission monitoring system continuously,based on a 3 hour rolling average based on a1 hour block average (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(e)]NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-22.16(e)]5NOx (Total) <= 0.0117 lb/MMBTU exceptfor periods of start-up, shutdown and fueltransfer as defined in this permit. [N.J.A.C.7:27-22.16(e)]NOx (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]NOx (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]OS1 Combined Cycle Unit No. 1-Normal Operations, OS4Combined Cycle Unit No. 2-NormalOperations, OS7 Combined Cycle UnitNo. 3-Normal OperationsPage 34 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6NOx (Total) <= 25.3 lb/hr except for periodsof start-up, shutdown and fuel transfer asdefined in this permit. [N.J.A.C.7:27-22.16(e)]NOx (Total): Monitored by continuousemission monitoring system continuously,based on a 3 hour rolling average based on a1 hour block average (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(e)]NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-22.16(e)]7NOx (Total) <= 25.3 lb/hr except for periodsof start-up, shutdown and fuel transfer asdefined in this permit. [N.J.A.C.7:27-22.16(a)]NOx (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]NOx (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]8CO <= 4 ppmvd @ 15% O2 except forperiods of start-up, shutdown and fueltransfer as defined in this permit. [N.J.A.C.7:27-22.16(e)]CO: Monitored by continuous emissionmonitoring system continuously, based on a3 hour rolling average based on a 1 hourblock average (see U1 OS Summary, Ref#1). [N.J.A.C. 7:27-22.16(e)]CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-22.16(e)]9CO <= 4 ppmvd @ 15% O2 except forperiods of start-up, shutdown and fueltransfer as defined in this permit. [N.J.A.C.7:27-22.16(e)]CO: Monitored by stack emission testingprior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]CO: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]10CO <= 0.01 lb/MMBTU except for periodsof start-up, shutdown and fuel transfer asdefined in this permit. [N.J.A.C.7:27-22.16(e)]CO: Monitored by continuous emissionmonitoring system continuously, based on a3 hour rolling average based on a 1 hourblock average (see U1 OS Summary, Ref#1). [N.J.A.C. 7:27-22.16(e)]CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-22.16(e)]11CO <= 0.01 lb/MMBTU except for periodsof start-up, shutdown and fuel transfer asdefined in this permit. [N.J.A.C.7:27-22.16(e)]CO: Monitored by stack emission testingprior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]CO: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]Page 35 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement12CO <= 20.69 lb/hr except for periods ofstart-up, shutdown and fuel transfer asdefined in this permit. [N.J.A.C.7:27-22.16(a)]CO: Monitored by continuous emissionmonitoring system continuously, based on a3 hour rolling average based on a 1 hourblock average (see U1 OS Summary, Ref#1). [N.J.A.C. 7:27-22.16(e)]CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-22.16(e)]13CO <= 20.69 lb/hr except for periods ofstart-up, shutdown and fuel transfer asdefined in this permit. [N.J.A.C.7:27-22.16(a)]CO: Monitored by stack emission testingprior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]CO: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]14VOC (Total) <= 3 ppmvd @ 15% O2.[N.J.A.C. 7:27-22.16(e)]VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]VOC (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]15VOC (Total) <= 0.00405 lb/MMBTU.[N.J.A.C. 7:27-22.16(e)]VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]VOC (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]16VOC (Total) <= 9.14 lb/hr. [N.J.A.C.7:27-22.16(a)]VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]VOC (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]17SO2 <= 0.0043 lb/MMBTU. [N.J.A.C.7:27-22.16(e)]SO2: Monitored by stack emission testingprior to permit renewal, based on each ofthree Department validated stack test runs(see U1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]SO2: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]18SO2 <= 9.34 lb/hr. [N.J.A.C. 7:27-22.16(a)]SO2: Monitored by stack emission testingprior to permit renewal, based on each ofthree Department validated stack test runs(see U1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]SO2: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]19TSP <= 0.0135 lb/MMBTU. [N.J.A.C.7:27-22.16(e)]TSP: Monitored by stack emission testingprior to permit renewal, based on each ofthree Department validated stack test runs(see U1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]TSP: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]Page 36 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement20TSP <= 29.43 lb/hr. [N.J.A.C.7:27-22.16(a)]TSP: Monitored by stack emission testingprior to permit renewal, based on each ofthree Department validated stack test runs(see U1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]TSP: Recordkeeping by stack test resultsprior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]21PM-10 (Total) <= 0.0135 lb/MMBTU.[N.J.A.C. 7:27-22.16(e)]PM-10 (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]PM-10 (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]22PM-10 (Total) <= 29.43 lb/hr. [N.J.A.C.7:27-22.16(a)]PM-10 (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]PM-10 (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(o)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(o)]23Ammonia <= 10 ppmvd @ 15% O2.[N.J.A.C. 7:27-22.16(e)]Ammonia: Monitored by stack emissiontesting prior to permit renewal, based oneach of three Department validated stack testruns (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]Ammonia: Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]24Ammonia <= 0.0135 lb/MMBTU. [N.J.A.C.7:27-22.16(e)]Ammonia: Monitored by stack emissiontesting prior to permit renewal, based oneach of three Department validated stack testruns (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]Ammonia: Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]25Ammonia <= 29.11 lb/hr. [N.J.A.C.7:27-22.16(a)]Ammonia: Monitored by stack emissiontesting prior to permit renewal, based oneach of three Department validated stack testruns (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]Ammonia: Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]26SO3 and H2SO4, as converted andexpressed as H2SO4 <= 0.0027lb/MMBTU. [N.J.A.C. 7:27-22.16(e)]SO3 and H2SO4, as converted andexpressed as H2SO4: Monitored by stackemission testing prior to permit renewal,based on each of three Department validatedstack test runs (see U1 OS Summary, Ref#2). [N.J.A.C. 7:27-22.16(e)]SO3 and H2SO4, as converted andexpressed as H2SO4: Recordkeeping bystack test results prior to permit renewal (seeU1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]27SO3 and H2SO4, as converted andexpressed as H2SO4 <= 5.72 lb/hr.[N.J.A.C. 7:27-22.16(a)]SO3 and H2SO4, as converted andexpressed as H2SO4: Monitored by stackemission testing prior to permit renewal,based on each of three Department validatedstack test runs (see U1 OS Summary, Ref#2). [N.J.A.C. 7:27-22.16(e)]SO3 and H2SO4, as converted andexpressed as H2SO4: Recordkeeping bystack test results prior to permit renewal (seeU1 OS Summary, Ref #2). [N.J.A.C.7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]Page 37 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement28Maximum Gross Heat Input <= 2,180MMBTU/hr (HHV) (HHV) for each gasturbine while buring natural gas. [N.J.A.C.7:27-22.16(a)]Maximum Gross Heat Input: Monitored byfuel flow/firing rate instrumentcontinuously, based on a 1 hour blockaverage. [N.J.A.C. 7:27-22.16(e)]Maximum Gross Heat Input: Recordkeepingby data acquisition system (DAS) /electronic data storage eachhour duringoperation. [N.J.A.C. 7:27-22.16(e)]None.Page 38 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Emission Unit:U1 Combined Cycle Units -Three turbines each with aheat input of 2180 MMBtu/hrOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Opacity <= 20 %. No person shall cause,suffer, allow or permit smoke greater than20 percent opacity, exclusive of visiblecondensed water vapor, to be emitted intothe outdoor air from the combustion of fuelin any stationary internal combustion engineor any stationary turbine engine for a periodof more than 10 consecutive seconds.[N.J.A.C. 7:27- 3.5]None.None.None.2Particulate Emissions <= 218 lb/hrParticulate emission limit from thecombustion of fuel based on rated heat inputof source. [N.J.A.C. 7:27- 4.2(a)]None.None.None.3CO <= 250 ppmvd @ 15% O2. [N.J.A.C.7:27-16.9(b)]CO: Monitored by continuous emissionmonitoring system continuously, based onone calendar day , not including periods ofdowntime. (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-16.23(a)1]CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-22.16(e)]4VOC (Total) <= 50 ppmvd @ 15% O2.[N.J.A.C. 7:27-16.9(c)]VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-16.23(a)1]VOC (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]5NOx (Total) <= 1.3 lb/MW-hr. NOx RACTemission limit for non-HEDD turbinesapplies during all periods of natual gascombustion. To calculate lb/MWh, for unitswhere energy is used for other than electricgeneration, for example combined heat andpower unit, that useful energy should beconverted to equivalent MWh and added tothe electric output. Emission rate is basedon net energy output (both electric anduseful heat). N.J.A.C. 7:27-19.5(d) and.[N.J.A.C. 7:27-19.5(f)]NOx (Total): Monitored by continuousemission monitoring system continuously,based on a calendar day (in ozone season) or30 day rolling (at other times) average (seeU1 OS Summary, Ref #1). [N.J.A.C.7:27-22.16(o)]NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(o)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-21.16(o)]OS2 Combined Cycle Unit No. 1-Startup,OS5 Combined Cycle Unit No. 2-Startup,OS8 Combined Cycle Unit No. 3-StartupPage 39 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6The annual emissions (in tons per year)during startup shall be calculated as follows:1) Weighted Emission Rate Limit (in lbs/hr)x Total Hours of startups during a year(hrs/yr) x 1/2,000 (lbs/ton).Where Weighted Emission Rate = (cold startemissions (lbs) + warm start emissions (lbs)+ hot start emissions (lbs))/(cold startduration (hrs) + warm start duration (hrs) +hot start duration (hrs)) [N.J.A.C.7:27-22.16(e)]Monitored by hour/time monitorcontinuously. [N.J.A.C. 7:27-22.16(o)]Recordkeeping by manual logging ofparameter each month during operationshowing the calculated value for the monthand sum-to-date. [N.J.A.C. 7:27-22.16(o)]None.7NOx (Total) <= 111 lb/hr based on a 3 hourrolling average based on a 1 hour blockaverage. [N.J.A.C. 7:27-22.16(a)]None.None.None.8CO <= 504 lb/hr based on a 3 hour rollingaverage based on a 1 hour block average.[N.J.A.C. 7:27-22.16(a)]None.None.None.9VOC (Total) <= 87 lb/hr based on a 3 hourrolling average based on a 1 hour blockaverage. [N.J.A.C. 7:27-22.16(e)]None.None.None.10SO2 <= 9.34 lb/hr. [N.J.A.C. 7:27-22.16(a)]None.None.None.11TSP <= 29.43 lb/hr. [N.J.A.C.7:27-22.16(a)]None.None.None.12PM-10 (Total) <= 29.43 lb/hr. [N.J.A.C.7:27-22.16(a)]None.None.None.13SO3 and H2SO4, as converted andexpressed as H2SO4 <= 5.7 lb/hr. [N.J.A.C.7:27-22.16(a)]None.None.None.Page 40 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Emission Unit:U1 Combined Cycle Units -Three turbines each with aheat input of 2180 MMBtu/hrOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Opacity <= 20 %. No person shall cause,suffer, allow or permit smoke greater than20 percent opacity, exclusive of visiblecondensed water vapor, to be emitted intothe outdoor air from the combustion of fuelin any stationary internal combustion engineor any stationary turbine engine for a periodof more than 10 consecutive seconds.[N.J.A.C. 7:27- 3.5]None.None.None.2Particulate Emissions <= 218 lb/hrParticulate emission limit from thecombustion of fuel based on rated heat inputof source. [N.J.A.C. 7:27- 4.2(a)]None.None.None.3CO <= 250 ppmvd @ 15% O2. [N.J.A.C.7:27-16.9(b)]CO: Monitored by continuous emissionmonitoring system continuously, based onone calendar day , not including periods ofdowntime. (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-16.23(a)1]CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously (see U1 OS Summary, Ref #1).[N.J.A.C. 7:27-22.16(e)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-22.16(e)]4VOC (Total) <= 50 ppmvd @ 15% O2.[N.J.A.C. 7:27-16.9(c)]VOC (Total): Monitored by stack emissiontesting prior to permit renewal, based on theaverage of three Department validated stacktest runs (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-16.23(a)2]VOC (Total): Recordkeeping by stack testresults prior to permit renewal (see U1 OSSummary, Ref #2). [N.J.A.C. 7:27-22.16(e)]Stack Test - Submit protocol, conduct testand submit results: As per the approvedschedule (see U1 OS Summary, Ref #2).[N.J.A.C. 7:27-22.16(e)]5NOx (Total) <= 1.3 lb/MW-hr. NOx RACTemission limit for non-HEDD turbinesapplies during all periods of natual gascombustion. To calculate lb/MWh, for unitswhere energy is used for other than electricgeneration, for example combined heat andpower unit, that useful energy should beconverted to equivalent MWh and added tothe electric output. Emission rate is basedon net energy output (both electric anduseful heat). N.J.A.C. 7:27-19.5(d) and.[N.J.A.C. 7:27-19.5(f)]NOx (Total): Monitored by continuousemission monitoring system continuously,based on a calendar day (in ozone season) or30 day rolling (at other times) average (seeU1 OS Summary, Ref #1). [N.J.A.C.7:27-22.16(o)]NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously (see U1 OS Summary,Ref #1). [N.J.A.C. 7:27-22.16(o)]Submit an Excess Emissions andMonitoring Systems Performance Report(EEMPR): Every April 30, July 30, October30, and January 30 for the preceding quarteryear (the quarter years begin on January 1,April 1, July 1, and October 1) electronicallythrough the NJDEP online EEMPR webportal. [N.J.A.C. 7:27-21.16(o)]OS3 Combined Cycle Unit No. 1-Shutdown, OS6 Combined CycleUnit No. 2-Shutdown, OS9 Combined Cycle Unit No. 3-ShutdownPage 41 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement6NOx (Total) <= 111 lb/hr. [N.J.A.C.7:27-22.16(e)]None.None.None.7CO <= 504 lb/hr. [N.J.A.C. 7:27-22.16(e)]None.None.None.8VOC (Total) <= 87 lb/hr. [N.J.A.C.7:27-22.16(e)]None.None.None.9SO2 <= 9.34 lb/hr. [N.J.A.C. 7:27-22.16(a)]None.None.None.10TSP <= 29.43 lb/hr. [N.J.A.C.7:27-22.16(a)]None.None.None.11PM-10 (Total) <= 29.43 lb/hr. [N.J.A.C.7:27-22.16(a)]None.None.None.12SO3 and H2SO4, as converted andexpressed as H2SO4 <= 5.7 lb/hr. [N.J.A.C.7:27-22.16(a)]None.None.None.Page 42 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Emission Unit:U2 Ten Cell Cooling Tower (200,000 gal/min capacity)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1TSP <= 15.79 tons/yr. Maximum annualemission limit from preconstruction permit.[N.J.A.C. 7:27-22.16(e)]None.None.None.2PM-10 (Total) <= 15.79 tons/yr. Maximumannual emission limit from preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]None.None.None.OS SummaryPage 43 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Emission Unit:U2 Ten Cell Cooling Tower (200,000 gal/min capacity)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Particulate Emissions <= 7.8 lb/hr based on0.02 grains per SCF (maximum SCF emittedfrom emission point). [N.J.A.C. 7:27-6.2(a)]None.None.None.2Opacity <= 20 %. Opacity limited to 20%,exclusive of condensed water vapor, for aperiod of not longer than three minutes inany consecutive 30-minute period. [N.J.A.C.7:27- 6.2(d)]None.None.None.3TSP <= 3.6 lb/hr. [N.J.A.C. 7:27-22.16(e)]None.None.None.4PM-10 (Total) <= 3.6 lb/hr. [N.J.A.C.7:27-22.16(e)]None.None.None.5Total solids concentration in the coolingtower circulating water =<12,000 mg/liter.[N.J.A.C. 7:27-22.16(a)]Other: Circulating water analysis, once permonth during cooling toweroperation.[N.J.A.C. 7:27-22.16(o)].Recordkeeping by manual logging ofparameter each month during operation.Maintain records of circulating wateranalysis. [N.J.A.C. 7:27-22.16(o)]None.6Water treatment chemicals containinghexavalent chromium shall not be added tothe circulating water. [N.J.A.C.7:27-22.16(e)]Other: By review of process recordsshowing materials/chemicalsadded/mixed.[N.J.A.C. 7:27-22.16(o)].Other: Maintain process records showingdate, time, and amount ofmaterials/chemicals added/mixed.[N.J.A.C.7:27-22.16(o)].None.7The raw materials shall be limited to thechemicals listed in Appendix 3. [N.J.A.C.7:27-22.16(a)]Other: By review of process recordsshowing materials/chemicalsadded/mixed.[N.J.A.C. 7:27-22.16(o)].Other: Maintain process records showinglist of materials/chemicalsadded/mixed.[N.J.A.C. 7:27-22.16(o)].None.8Total Material Transferred <= 364.5 tons/yrof chemical additives (For a list of chemicaladditives, see document attached at the endof this section). Maximum throughput ratebased on operating permit application.[N.J.A.C. 7:27-22.16(a)]Total Material Transferred: Monitored bymaterial feed/flow monitoring continuously.[N.J.A.C. 7:27-22.16(o)]Total Material Transferred: Recordkeepingby manual logging of parameter each weekduring operation in a permanently bound logbook or readilyaccessible computer memoryshowing type of raw materials and amountof each chemical added with sum-to-date.[N.J.A.C. 7:27-22.16(o)]None.9Cooling tower circulation water flow rate <=200,000 gallons per minute (gpm), based onoperating permit application. [N.J.A.C.7:27-22.16(a)]None.None.None.OS1 Ten Cell Cooling Tower - Normal OperationPage 44 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Emission Unit:U3 20,000 Gallon Ammonia Storage TankOperating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1If the tank is equipped with gauging and/orsampling systems, such systems shall bevapor-tight except when gauging orsampling is taking place. [N.J.A.C.7:27-22.16(e)]None.None.None.2Tank contents < 20.00% AmmoniumHydroxide solution. [N.J.A.C.7:27-22.16(e)]Other: For each delivery, monitor byreviewing delivery records such as MSDS,invoice, and/or bill of lading that showcontent, composition, and quantity of thedelivery.[N.J.A.C. 7:27-22.16(o)].Other: Maintain delivery records perdelivery. The records shall indicate contentof delivery, composition, quantity delivered,and date of delivery.[N.J.A.C.7:27-22.16(o)].None.3Total Material Transferred <= 1.895MMgal/yr ammonia. [N.J.A.C.7:27-22.16(e)]Other: For each delivery, monitor byreviewing delivery records, invoice, and/orbill of lading that show content,composition, and quantity of thedelivery.[N.J.A.C. 7:27-22.16(o)].Other: Maintain delivery records perdelivery. The records shall indicate contentof delivery, composition, quantity delivered,and date of delivery withsum-to-date.[N.J.A.C. 7:27-22.16(o)].None.OS SummaryPage 45 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Emission Unit:U7 Fuel Gas Heater (16 MMBTU/hr)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Maximum annual emission limit frompreconstruction permit. NOx (Total) <= 8.4tons/yr. [N.J.A.C. 7:27-22.16(a)]None.None.None.2Maximum annual emission limit frompreconstruction permit. CO <= 3.77 tons/yr.[N.J.A.C. 7:27-22.16(a)]None.None.None.3Maximum annual emission limit frompreconstruction permit. VOC (Total) <=0.48 tons/yr. [N.J.A.C. 7:27-22.16(a)]None.None.None.4Maximum annual emission limit frompreconstruction permit. SO2 <= 0.3 tons/yr.[N.J.A.C. 7:27-22.16(a)]None.None.None.5Maximum annual emission limit frompreconstruction permit. TSP <= 0.53tons/yr. [N.J.A.C. 7:27-22.16(a)]None.None.None.6Maximum Gross Heat Input <= 16MMBTU/hr. [N.J.A.C. 7:27-22.16(e)]OS SummaryPage 46 of 47New Jersey Department of Environmental ProtectionFacility Specific RequirementsDate: 2/3/2010AES RED OAK LLC (18195)BOP090002Emission Unit:U7 Fuel Gas Heater (16 MMBTU/hr)Operating Scenario:Ref.#Applicable RequirementMonitoring RequirementRecordkeeping RequirementSubmittal/Action Requirement1Visible Emissions: Novisible emissions,exclusive of visible condensed water vapor,except for a period of not longer than threeminutes in any consecutive 30 minuteperiod. [N.J.A.C. 7:27-3.2(a)] & [N.J.A.C.7:27- 3.2(c)]None.None.None.2Particulate Emissions <= 7.2 lb/hrParticulate emission limit from thecombustion of fuel based on rated heat inputof source. [N.J.A.C. 7:27- 4.2(a)]None.None.None.3NOx (Total) <= 1.917 lb/hr. [N.J.A.C.7:27-22.16(e)]None.None.None.4CO <= 0.86 lb/hr. [N.J.A.C. 7:27-22.16(e)]None.None.None.5VOC (Total) <= 0.11 lb/hr. [N.J.A.C.7:27-22.16(e)]None.None.None.6SO2 <= 0.069 lb/hr. [N.J.A.C.7:27-22.16(e)]None.None.None.7PM-10 (Total) <= 0.12 lb/hr. [N.J.A.C.7:27-22.16(e)]None.None.None.8Permittee's self imposed fuel type limit.Natural Gas only. [N.J.A.C. 7:27-22.16(e)]None.None.None.9Permittee's self imposed annual natural gasuse limit. 140.16 MMSCF per year[N.J.A.C. 7:27-22.16(a)]Monitored by fuel flow/firing rateinstrument continuously. [N.J.A.C.7:27-22.16(o)]Recordkeeping by manual logging ofparameter annually. Manual logging of fuelusage (Permanently Bound). [N.J.A.C.7:27-22.16(o)]None.OS1 Fuel Gas Heater NormalPage 47 of 47

# AES RED OAK LLC (18195) Date: 2/3/2010



# BOP090002



# New Jersey Department of Environmental Protection

Facility Profile (General)

Borough of Sayreville, Middlesex County,

New Jersey 4911 State Plane Coordinates:

X-Coordinate:

Y-Coordinate:

Units:

Datum:

Source Org.:

Source Type:

County: Industry:

Location

Description: Primary SIC:

Secondary SIC: Middlesex Mailing

Address: Street

Address: AES RED OAK LLC

832 RED OAK LN

SAYREVILLE, NJ 08872

AES RED OAK LLC

832 RED OAK LN

SAYREVILLE, NJ 08872 Facility Name (AIMS): AES RED OAK LLC Facility ID (AIMS): 18195

NAICS:

Page 1 of 3

# AES RED OAK LLC (18195) Date: 2/3/2010



# BOP090002



# New Jersey Department of Environmental Protection

Facility Profile (General)

(201) 933-5601 x

( ) - x

dshotts@trcsolutions.com TRC Environmental Corporation

David J. Shotts, PE

Manager, Air Quality Engineering

(201) 933-5541 x0112 TRC Environmental Corporation

1200 Wall Street West

Lyndhurst, NJ 07071 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Private

NJ EIN: Contact Type: Consultant

(732) 238-4702 x

( ) - x

chip.bergeron@aes.com AES Red Oak, L.L.C.

Albert Bergeron

President and Facility Manager

(732) 238-1462 x0101 AES Red Oak, L.L.C

832 Red Oak Lane

Sayreville, NJ 08872 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Private

NJ EIN: Contact Type: General Contact

(732) 238-4702 x

( ) - x

chip.bergeron@aes.com AES Red Oak, L.L.C.

Albert Bergeron

Project Director

(732) 238-1462 x0101 AES Red Oak, L.L.C

832 Red Oak Lane

Sayreville, NJ 08872 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Private

NJ EIN: Contact Type: On-Site Manager

Page 2 of 3

# AES RED OAK LLC (18195) Date: 2/3/2010



# BOP090002



# New Jersey Department of Environmental Protection

Facility Profile (General)

(732) 238-4702 x

( ) - x

chip.bergeron@aes.com AES Red Oak, L.L.C.

Albert Bergeron

President and Facility Manager

(732) 238-1462 x0101 AES Red Oak, L.L.C

832 Red Oak Lane

Sayreville, NJ 08872 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Private

NJ EIN: Contact Type: Operator

( ) - x

( ) - x AES Red Oak, L.L.C.

( ) - x AES Red Oak, L.L.C

832 Red Oak Lane

Sayreville, NJ 08872 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Private

NJ EIN: Contact Type: Owner (Current Primary)

(732) 238-4702 x

( ) - x

chip.bergeron@aes.com AES Red Oak, L.L.C.

Albert Bergeron

President and Facility Manager

(732) 238-1462 x0101 AES Red Oak, L.L.C

832 Red Oak Lane

Sayreville, NJ 08872 Organization: Org. Type:

Name:

Title:

Phone:

Fax: Mailing

Address:

Other:

Type:

Email: Private

NJ EIN: Contact Type: Responsible Official

Page 3 of 3

# AES RED OAK LLC (18195)

BOP090002



# New Jersey Department of Environmental Protection

Reason for Application Date: 2/3/2010



# Permit Being Modified

Permit Class: BOP Number: 60002

Description

of Modifications: 1) Include CAIR permit as an attachment to the operating permit.

2) Update Subchapter 19 and other requirements.

3) Correct emission unit 1 to include PT5, instead of PT3.

4) Update Appendix II: Cooling Tower Chemical Additives by removing several chemicals

currently allowed to be used in the cooling tower and adding sulfuric acid, and depositrol to

the list

5) Update stack testing requirement

Replace with updated stack test language

Correct list of pollutants required to be stack tested to include NOx, CO, VOC, SO2,

TSP, PM-10, Ammonia and (SO3 and H2SO4)

Allow compliance with all NOx, CO, VOC and PM-10 limits to be demonstrated by the

average of three Department approved stack test runs in accordance with current

Department policy.

Page 1 of 1AES RED OAK LLC (18195)BOP090002New Jersey Department of Environmental ProtectionNon-Source Fugitive EmissionsDate:02/03/2010FGNJIDDescription ofActivity CausingEmissionLocationDescriptionReasonable Estimate of Emissions (tpy)VOC(Total)NOxCOSOTSP(Total)PM-10PbHAPS(Total)Other(Total)FG1Total0.0000.0000.0000.0000.0000.0000.0000.000000000.000Page 1 of 1AES RED OAK LLC (18195)BOP090002New Jersey Department of Environmental ProtectionInsignificant Source Emissions2/3/2010Date:ISNJIDSource/GroupDescriptionEquipment TypeLocationDescriptionEstimate of Emissions (tpy)VOC(Total)NOxCOSOTSPPM-10PbHAPS(Total)Other(Total)IS1Total0.0000.0000.0000.0000.0000.0000.0000.000000000.000Page 1 of 1Equip.NJIDFacility'sDesignationEquipmentDescriptionEquipment TypeCertificateNumberInstallDateGrandFatheredLast Mod.(Since 1968)Equip.Set IDNew Jersey Department of Environmental ProtectionEquipment InventoryBOP090002AES RED OAK LLC (18195)2/3/2010Date:E1Combine Cyc1CPCP0200011/31/2000NoCombined Cycle Unit No. 1SWPC 501FCombustion TurbineE2Combine Cyc2CPCP0200011/31/2000NoCombined Cycle Unit No. 2SWPC 501FCombustion TurbineE3Combine Cyc3CPCP0200011/31/2000NoCombined Cycle Unit No. 3SWPC 501FCombustion TurbineE4CoolingTowerOPCP0200011/31/2000NoTen Cell Cooling TowerOther EquipmentE5NH3 TankSPCP0200011/31/2000No20,000 Gallon AmmoniaStorage TankStorage VesselE10HeaterBPCP0200011/31/2000NoFuel Gas HeaterBoilerPage 1 of 1AES RED OAK LLC (18195)Date:2/3/2010New Jersey Department of Environmental ProtectionControl Device InventoryCDNJIDFacility'sDesignationDescriptionCD TypeInstallDateGrandFatheredLast Mod.(Since 1968)CDSet IDBOP090002CD1Combined Cycle Unit No. 1Selective Catalytic ReductionSystem1/31/2000NoSCR1Selective CatalyticReductionCD2Combined Cycle Unit No. 1Oxidation Catalyst1/31/2000NoOxCat1OtherCD3Combined Cycle Unit No. 2Selective Catalytic ReductionSystem1/31/2000NoSCR2Selective CatalyticReductionCD4Combined Cycle Unit No. 2Oxidation Catalyst1/31/2000NoOxCat2OtherCD5Combined Cycle Unit No. 3Selective Catalytic ReductionSystem1/31/2000NoSCR3Selective CatalyticReductionCD6Combined Cycle Unit No. 3Oxidation Catalyst1/31/2000NoOxCat3OtherPage 1 of 1AES RED OAK LLC (18195)Date:2/3/2010New Jersey Department of Environmental ProtectionEmission Points InventoryPTNJIDFacility'sDesignationDescriptionConfig.Equiv.Diam.(in.)Height(ft.)Dist. toProp.Line (ft)Exhaust Temp. (deg. F)Exhaust Vol. (acfm)Avg.Min.Max.Avg.Min.Max.DischargeDirectionPTSet IDBOP090002PT1Stack Unit 1Stack for Combined CycleUnit 1Round228150250225.0172.0245.0UpR1,344,000.01,070,000.0798,000.0PT2Stack Unit 2Stack for Combined CycleUnit 2Round228150250225.0172.0245.0UpR1,344,000.01,070,000.0798,000.0PT3Stack Unit 3Stack for Combined CycleUnit 3Round228150250225.0172.0245.0UpR1,344,000.01,070,000.0798,000.0PT4Cooling ToweCooling TowerRound8454650100.032.0125.0UpR137,216.9102,912.050,000.0PT5NH3 TankAqueous Ammonia TankRound62225055.00.095.0UpR20.010.00.0PT7Heater StackStack 1 for Fuel Gas HeaterRound1630200559.0300.0818.0UpR3,905.92,437.3968.6PT8Heater StackStack 2 for Fuel Gas HeaterRound1630200559.0300.0818.0UpR3,905.92,437.3968.6Page 1 of 1New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryAES RED OAK LLC (18195)BOP090002Date:2/3/2010U 1 Elec Gen Combined Cycle Units - Threeturbines each with a heat input of 2180 MMBtu/hrUOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1501F1-NormalCombined Cycle Unit No.1-Normal OperationsNormal - SteadyStateE1CD1 (P)CD2 (P)PT12-01-002-010.08,760.0OS2501F1-SUCombined Cycle Unit No.1-StartupStartupE1PT12-01-002-010.08,760.0OS3501F1-SDCombined Cycle Unit No.1-ShutdownShutdownE1PT12-01-002-010.08,760.0OS4501F2-NormalCombined Cycle Unit No.2-Normal OperationsNormal - SteadyStateE2CD3 (P)CD4 (P)PT22-01-002-010.08,760.0OS5501F2-SUCombined Cycle Unit No.2-StartupStartupE2PT22-01-002-010.08,760.0OS6501F2-SDCombined Cycle Unit No.2-ShutdownShutdownE2PT22-01-002-010.08,760.0OS7501F3-NormalCombined Cycle Unit No.3-Normal OperationsNormal - SteadyStateE3CD5 (P)CD6 (P)PT32-01-002-010.08,760.0OS8501F3-SUCombined Cycle Unit No.3-StartupStartupE3PT32-01-002-010.08,760.0OS9501F3-SDCombined Cycle Unit No.3-ShutdownShutdownE3PT32-01-002-010.08,760.0Page 1 of 3New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryAES RED OAK LLC (18195)BOP090002Date:2/3/2010U 2 Cooling Towe Ten Cell Cooling Tower (200,000 gal/min capacity)UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1Cool TowerTen Cell Cooling Tower -Normal OperationNormal - SteadyStateE4PT43-02-999-990.08,760.0U 3 NH3 Tank 20,000 Gallon Ammonia Storage TankUOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1NH3 Tank20,000 Gallon AmmoniaStorage Tank - NormalOperationsNormal - SteadyStateE5PT54-03-011-970.08,760.0Page 2 of 3New Jersey Department of Environmental ProtectionEmission Unit/BatchProcess InventoryAES RED OAK LLC (18195)BOP090002Date:2/3/2010U 7 Heater Fuel Gas Heater (16 MMBTU/hr)UOSNJIDFacility'sDesignationUOSDescriptionOperationTypeSignif.Equip.ControlDevice(s)EmissionPoint(s)SCC(s)Flow(acfm)Temp.(deg F)Min.Max.Min.Max.AnnualOper. HoursMin.Max.VOCRangeOS1Heater-GasFuel Gas Heater NormalNormal - SteadyStateE10PT7PT80.08,760.0968.03,905.9300.0818.0Page 3 of 3Date:2/3/2010New Jersey Department of Environmental ProtectionSubject Item Group InventoryGR1 FacilityGroup NJID:Members:TypeIDOSStepUU 1OS0 SummaryUU 2OS0 SummaryUU 3OS0 SummaryUU 7OS0 SummaryFormal Reason(s) for Group/Cap:9OtherOther (explain):To restrict facility's total emissionsCondition/Requirements that will be complied with or are no longerapplicable as a result of this Group:Operating Circumstances:Page 1 of 1