Unassociated Document








Exhibit 4.8.66 -Design Drawings - Power Consumption – Workshop





















	
Bill of Power Consumption in Production Workshop








	
Serial No.

	
Description

	
Unit(KW)

	
Calculating Power(KW)

	
Calculating Current after Compensation

	
Cable Type

	
Remarks


	
A

	
Gross Installed Capacity of Workshop Power

	
1831

	
999

	
1597.75

	
ZR-YJV22-1.0,3x300+1x150

	
Compliance with Actual Needs


	
1

	
Power Supply Box11DX

	
15

	
11

	
20.89

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
2

	
Power Supply Box12DX

	
18

	
13

	
24.69

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
3

	
Power Supply Box13DX

	
13

	
9

	
17.09

	
ZR-YJV22-1.0,5x4

	
Compliance with Actual Needs


	
4

	
Maintanence Box21,22JX

	
20

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
5

	
Power Supply Box15DX

	
15

	
11

	
20.89

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
6

	
Power Supply Box16DX

	
18

	
13

	
24.69

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
7

	
Maintanence Box23,24JX

	
20

	
16

	
30.39

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs


	
8

	
Power Supply Box18DX

	
13

	
9

	
17.09

	
ZR-YJV22-1.0,5x4

	
Compliance with Actual Needs


	
9

	
Power Supply Box19DX

	
28

	
21

	
39.88

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs


	
10

	
Power Supply Box110DX

	
7

	
7

	
13.29

	
ZR-YJV22-1.0,5x4

	
Compliance with Actual Needs


	
11

	
Power Supply Box111DX

	
20

	
15

	
28.49

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
12

	
Power Supply Box112DX

	
12

	
10

	
18.99

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
13

	
Power Supply Box113DX

	
77

	
49

	
93.06

	
ZR-YJV22-1.0,3x35+2x16

	
Compliance with Actual Needs


	
14

	
Power Supply Box114DX

	
20

	
15

	
28.49

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
15

	
Power Supply Box116DX

	
54

	
19

	
36.09

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs


	
16

	
Power Supply Box117DX

	
14

	
11

	
20.89

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
17

	
Power Supply Box21DX

	
20

	
15

	
28.49

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
18

	
Power Supply Box22DX

	
18

	
14

	
26.59

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
19

	
Power Supply Box23DX

	
22

	
12

	
22.79

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
20

	
Power Cabinet11LX

	
38

	
32

	
60.78

	
ZR-YJV22-1.0,3x25+2x16

	
Compliance with Actual Needs


	
21

	
Power Cabinet12LX

	
115

	
97

	
184.23

	
ZR-YJV22-1.0,3x95+2x50

	
Compliance with Actual Needs


	
22

	
Power Cabinet13LX

	
35

	
26

	
49.38

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs


	
23

	
Power Cabinet21LX

	
103

	
87

	
165.23

	
ZR-YJV22-1.0,3x95+2x50

	
Compliance with Actual Needs


	
24

	
Maintanence Box25,26JX

	
20

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
25

	
CIP Washing Unit

	
28.5

	
28.5

	
54.13

	
ZR-YJV22-1.0,3x25+2x16

	
Compliance with Actual Needs


	
26

	
CIP Washing Unit

	
15.5

	
15.5

	
29.44

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
27

	
Cleaning Machine of Instruments

	
10.65

	
10.65

	
20.23

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
28

	
Sterilizing Cabinet

	
9

	
8

	
15.19

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
29

	
Sterilizing Cabinet

	
9

	
8

	
15.19

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
30

	
Cleaning Machine

	
10.65

	
15.5

	
29.44

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
31

	
Cleaning Machine

	
10.65

	
15.5

	
29.44

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
32

	
Sterilizing Cabinet

	
11.5

	
10.35

	
19.66

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
33

	
Drying Box

	
20

	
18

	
34.19

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs


	
34

	
Elevator

	
7.5

	
7.5

	
14.24

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs













  





第 1 页,共 3 页










 




 




 



Bill of Power Consumption in Production Workshop





	
35

	
Switching Cabinet11HX

	
46

	
46

	
87.36

	
ZR-YJV22-1.0,3x50+2x25

	
Compliance with Actual Needs


	
36

	
Switching Cabinet21HX

	
10

	
10

	
18.99

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
37

	
Freezing Machine

	
189

	
189

	
358.96

	
ZR-YJV22-1.0,3x240+2x120

	
Compliance with Actual Needs


	
38

	
Freezing Machine

	
189

	
189

	
358.96

	
ZR-YJV22-1.0,3x240+2x120

	
Compliance with Actual Needs


	
39

	
Freezing Machine

	
98

	
98

	
186.12

	
ZR-YJV22-1.0,3x150+2x70

	
Compliance with Actual Needs


	
40

	
Process Second-Class Load

	
442

	  	  	  	  
	
B

	
Gross Capacity of Second-Class Load in Process

	
442

	
276

	
530.82

	
ZR-YJV22-1.0,3x150+1x70

	
Compliance with Actual Needs


	
1

	
Power Supply Box11EX

	
24

	
18

	
34.18

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs


	
2

	
Power Supply Box12EX

	
27

	
20

	
37.98

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs


	
3

	
Power Supply Box13EX

	
33

	
25

	
47.48

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs


	
4

	
Power Supply Box14EX

	
24

	
20

	
37.98

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs


	
5

	
Power Supply Box15EX

	
27

	
20

	
37.98

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs


	
6

	
Power Supply Box16EX

	
33

	
25

	
47.48

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs


	
7

	
Power Supply Box17EX

	
16

	
14

	
26.59

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs


	
8

	
Power Supply Box21EX

	
24

	
18

	
34.18

	
ZR-YJV22-1.0,5x10

	
Compliance with Actual Needs


	
9

	
Power Supply Box22EX

	
33

	
25

	
47.48

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs


	
10

	
Power Supply Box23EX

	
22

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
11

	
Power Supply Box24EX

	
12

	
12

	
22.79

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
12

	
Power Cabinet11~13ELX

	
21

	
17

	
32.29

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs


	
13

	
Power Cabinet21ELX

	
2

	
2

	
3.8

	
ZR-YJV22-1.0,5x4

	
Compliance with Actual Needs


	
14

	
Power Cabinet22ELX

	
23

	
23

	
43.68

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs


	
15

	
Tunnel Oven

	
33

	
33

	
62.67

	
ZR-YJV22-1.0,3x35+2x16

	
Compliance with Actual Needs


	
16

	
Capping Machine

	
10

	
10

	
18.99

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
17

	
Power Supply Box14DX

	
22

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
18

	
Power Supply Box17DX

	
22

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
19

	
HPLC

	
17

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
20

	
HPLC

	
17

	
17

	
32.29

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
C

	
Gross Capacity of Air Conditioning Load in Workshop

	
316

	
253

	
480.51

	
ZR-YJV22-1.0,3x240+2x120

	
Compliance with Actual Needs


	
1

	
Power Cabinet11KX

	
26

	
26

	
49.38

	
ZR-YJV22-1.0,5x16

	
Compliance with Actual Needs


	
2

	
Power Cabinet12KX

	
33

	
33

	
62.67

	
ZR-YJV22-1.0,3x25+2x16

	
Compliance with Actual Needs


	
3

	
Power Cabinet13KX

	
30

	
30

	
56.98

	
ZR-YJV22-1.0,3x25+2x16

	
Compliance with Actual Needs


	
4

	
Power Cabinet14KX

	
48

	
48

	
91.16

	
ZR-YJV22-1.0,3x35+2x16

	
Compliance with Actual Needs


	
5

	
Power Cabinet15KX

	
41

	
41

	
77.87

	
ZR-YJV22-1.0,3x35+2x16

	
Compliance with Actual Needs


	
6

	
Power Cabinet16KX

	
40

	
40

	
75.97

	
ZR-YJV22-1.0,3x35+2x16

	
Compliance with Actual Needs


	
7

	
Power Cabinet11KHX

	
30

	
30

	
56.98

	
ZR-YJV22-1.0,3x25+2x16

	
Compliance with Actual Needs


	
8

	
Power Cabinet12KHX

	
68

	
68

	
129.15

	
ZR-YJV22-1.0,3x70+2x35

	
Compliance with Actual Needs
















  





第 2 页,共 3 页










 




 





 



Bill of Power Consumption in Production Workshop





	
D

	
Gross Capacity of Lighting Load in Workshop

	
122

	
104

	
185.9

	
ZR-YJV22-1.0,3x185+1x95

	
Compliance with Actual Needs


	
1

	
Lighting Box11MHX

	
9

	
9

	
16.09

	
NH-VV-1.0,5x6

	
Compliance with Actual Needs


	
2

	
Lighting Box21MHX

	
6

	
6

	
10.73

	
NH-VV-1.0,5x4

	
Compliance with Actual Needs


	
3

	
Lighting BoxDGMX

	
11

	
11

	
19.66

	
ZR-VV-1.0,5x6

	
Compliance with Actual Needs


	
4

	
Lighting Box11MX

	
5

	
5

	
8.94

	
ZR-VV-1.0,5x4

	
Compliance with Actual Needs


	
5

	
Lighting Box12MX

	
9

	
9

	
16.09

	
ZR-VV-1.0,5x4

	
Compliance with Actual Needs


	
6

	
Lighting Box13MX

	
12

	
12

	
21.15

	
ZR-VV-1.0,5x10

	
Compliance with Actual Needs


	
7

	
Lighting Box14MX

	
12

	
12

	
21.15

	
ZR-VV-1.0,5x10

	
Compliance with Actual Needs


	
8

	
Lighting Box15MX

	
8

	
8

	
14.3

	
ZR-VV-1.0,5x4

	
Compliance with Actual Needs


	
9

	
Lighting Box16MX

	
7

	
7

	
12.51

	
ZR-VV-1.0,5x4

	
Compliance with Actual Needs


	
10

	
Lighting Box21MX

	
16

	
16

	
28.6

	
ZR-VV-1.0,5x10

	
Compliance with Actual Needs


	
11

	
Lighting Box22MX

	
16

	
16

	
28.6

	
ZR-VV-1.0,5x10

	
Compliance with Actual Needs


	
12

	
Lighting Box23MX

	
11

	
11

	
19.66

	
ZR-VV-1.0,5x6

	
Compliance with Actual Needs


	
E

	
Gross Capacity of Second-Class Load in Workshop

	
614

	
425

	
807.17

	
ZR-YJV22-1.0,3x240+1x120

	
Compliance with Actual Needs


	
1

	
Switching Cabinet11HX

	
46

	
46

	
87.36

	
ZR-YJV22-1.0,3x50+2x25

	
Compliance with Actual Needs


	
2

	
Switching Cabinet21HX

	
10

	
10

	
18.99

	
ZR-YJV22-1.0,5x6

	
Compliance with Actual Needs


	
3

	
Lighting Box11MHX

	
9

	
9

	
16.09

	
NH-VV-1.0,5x6

	
Compliance with Actual Needs


	
4

	
Lighting Box21MHX

	
6

	
6

	
10.73

	
NH-VV-1.0,5x4

	
Compliance with Actual Needs


	
5

	
Power Cabinet11KHX

	
30

	
30

	
56.98

	
ZR-YJV22-1.0,3x25+2x16

	
Compliance with Actual Needs


	
6

	
Power Cabinet12KHX

	
68

	
68

	
129.15

	
ZR-YJV22-1.0,3x70+2x35

	
Compliance with Actual Needs


	
7

	
Process Second-Class Load

	
445

	  	  	  	  
	  	  	  	  	  	  	  
	
Note: Gross Capacity of Whole Workshop =A+C+D+E-445=1831+316+122+614-445=2883 KW


	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  





 




  





第 3 页,共 3 页