Unassociated Document












 























 





 





Exhibit 4.8.89 - Quotations Specifications and Other Info (REDACTED)












Cleanroom system quotation summary sheet








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Former quotation

	
New quotation

	
Price difference

	  	
Remark


	
1

	
Equipment cost (1) (attached quotation detail list)

	
***

	
***

	
***

	  	
1. Becoming large of process water main machine, pumps, and water tanks


2. The adding cold storage humidity requirements


3. K15, K25 need to add direct expansion section.


	  	
Equipment cost (2) (attached quotation detail list)

	
***

	
***

	
***

	  	
1. Parts of power distribution boxes are provided by owners, so the correspondent main materials need to be deducted.


	
2

	
Cleanroom maintenance (first floor&second floor)

	
***

	
***

	
***

	
***

	
1. According to the requirements of the owner, increase the windows


2. Part of the floor change the materials from pvc to epoxy color sand


3. Adding the floor drain


4. Parts of differential pressure sensor need to be changed with LCD


	
3

	
HVAC system

	
***

	
***

	
***

	  	
None


	
4

	
Fire protection and smoke evacuation smoke system

	
***

	
***

	
***

	  	
None


	
5

	
Technology chilled water system

	
***

	
***

	
***

	  	
1. According to the changes of end use equipments, pipe diameter becomes larger


2. Change the materials of pipe material from the steel to stainless steel


	
6

	
Air-conditioning water pipeline system

	
***

	
***

	
***

	  	
None


	
7

	
Circulating water system

	
***

	
***

	
***

	  	
1. Because the cooling tower becomes large, circulating pumps and other equipment become larger


2. Pipeline systems are also large


	
8

	
Air-conditioning AHU steam pipeline system

	
***

	
***

	
***

	  	
None


	
9

	
Technology steam piping system

	
***

	
***

	
***

	  	
None


	
10

	
Tap-water CWS system

	
***

	
***

	
***

	  	
Increase the water distribution points of 2F


	
11

	
Fire protection and smoke evacuation pipeline system

	
***

	
***

	
***

	  	
Change the box surface of fire protection and smoke evacuation from the aluminum and glass to stainless steel wire drawing surface


	
12

	
Electrical system

	
***

	
***

	
***

	  	
1. The main HVAC equipment becomes larger and more, the cable shall be adjusted


	
13

	
Automatic control system

	
***

	
***

	
***

	  	
1. Adding room differential pressure sensor control system


2. Pipeline becomes large, automatic control valve also becomes large


3. Wires become more


	
14

	
The third party testing and verification. Verification service cost

	
***

	
***

	
***

	  	
None













	
Quotation summary sheet

	
1/90

	
2009-6-19











  





  











  



















Cleanroom system quotation summary sheet








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Former quotation

	
New quotation

	
Price difference

	  	
Remark


	
15

	
Maintenance cost

	
***

	
***

	
***

	  	
None


	
16

	
Spare parts

	
***

	
***

	
***

	  	
None


	
17

	
Transportation cost

	
***

	
***

	
***

	  	
None


	
18

	
Cleaning telephone

	
820yuan/piece

	  	  	  	
This contract includes cleaning telephone supply and installation


	  	  	  	  	  	  	  
	
First

	
Total

	
***

	
***

	
***

	
***

	  
	  	  	  	  	  	  	  
	
Second

	
Preferential price

	
***

	  	  	  	  
	  	  	  	  	  	  	  
	
Third

	
Contract price

	  	  	  	
***

	  
	  	  	  	  	  	  	  
	  	
Including:

	  	  	  	  	  
	  	  	
Equipment part

	  	  	
***

	  
	  	  	
Installation part

	  	  	
***

	  











	
Quotation summary sheet

	
2/90

	
2009-6-19











  





  











  






 










Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Price


difference

	
Remark

	
Changing reasons


	
First

	
Air-conditioning


equipment

	  	  	
Former

	
Now

	  	
Former

	
Now

	
Former

	
Now

	  	  	  
	
Kaili 39 CBF

	  
	
1

	
K1X

	
Horizontal indoor combined type

	
Air quantity: 18000m3/h; ext. Static pressure:


200Pa; fresh air heat: 80Kw; fresh air cold: 130Kw; motor power: 22Kw

	
1

	  	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: air blower section, new air cold retaining water section, new air steam heating section, in effect filter section F6, coarse filter section G3, the fresh air section.

	  	  	  	  	  	  
	
2

	
K11

	
Horizontal indoor combined type

	
Air quantity: 60500m3/h; ext. Static pressure:


950Pa; new return air cold: 60Kw; steam heating power: 55Kw; dry steam humidifier: 15Kg / h; motor power: 45Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  	  
	
3

	
K12

	
Horizontal indoor combined type

	
Air quantity: 25100m3/h; ext. Static pressure


950Pa; new return air cold: 10Kw; steam heating power: 15Kw; dry steam humidifier: 13Kg / h; motor power: 22Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air

	  	  	  	  	  	  	  
	
4

	
K13

	
Horizontal indoor combined type

	
Air quantity: 50000m3/h; ext. Static pressure:


950Panew return air cold: 100Kw; steam heating power: 90Kw; dry steam humidifier: 24Kg / h; motor power: 37Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  	  
	
5

	
K14

	
Horizontal indoor combined type

	
Air quantity: 12000m3/h; ext. Static pressure:


950Pa; new return air cold: 25Kw; steam heating power: 25Kw; dry steam humidifier: 10.5Kg / h; motor power: 11Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  	  
	
6

	
K15

	
Horizontal indoor combined type

	
Air quantity: 9000m3/h; ext. Static pressure:


850Pa; new wind heating: 8Kw; new return wind cold: 51Kw; wheel dehumidifier:


Larger than 14Kg / h; wheel regenerative steam consumption: 75Kg / h; motor power: 11Kw; regenerative blower motor power: 1.1kw; dry steam humidifier: 3.5Kg / h

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili, direct-expansion

	
Increasing direct expansion cooling section


	  	  	
Unit section: wind section, in effect filter section F7, humididier section, fresh return air cooling, wind section, middle section, desiccant wheel Section

	  	  	  	  	  
	  	  	
New wind steam heating section, in effect filter section F6, filter section G3, fresh wind section

	  	  	  	  	  	  	  	  
	
7

	
K2X

	
Horizontal indoor combined type

	
Air quantity: 18000m3/h; ext. Static pressure:


200Pa; fresh air heat: 80Kw; fresh air cold: 130Kw; motor power: 22Kw


fresh air cold: 130Kw; motor power: 15Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: wind section, new air cold retaining water section, fresh wind steam heating section, in effect filter section F6, filter section G3

	  	  	  	  	  	  	  
	
8

	
K21

	
Horizontal indoor combined type

	
Air quantity: 32100m3/h; ext. Static pressure:


950Pa; New return air cold: 65Kw; steam heating power: 60Kw; dry steam humidifier: 15Kg / h; motor power: 22Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	  	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air

	  	  	  	  	  	  	  











	
Quotation summary sheet

	
3/90

	
2009-6-19
















  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
     Equipment No.     

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Price difference

	
Remark

	
Changing


	
First

	
Air-conditioning

equipment

	  	  	
Former

	
Now

	  	
Former

	
Now

	
Former

	
Now

	  	  	  
	
9

	
K22

	
Horizontal indoor combined type

	
Air quantity: 50000m3/h; ext. Static pressure


950Pa; New return air cold: 100Kw; steam heating power: 90Kw; dry steam humidifier: 24Kg / h; motor power rate: 37Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  	  
	
10

	
K23

	
Horizontal indoor combined type

	
Air quantity: 13100m3/h; ext. Static pressure


950Pa; New return air cold: 30Kw; steam heating power: 28Kw; dry steam humidifier: 9Kg / h; motor power: 11Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  	  
	
11

	
K24

	
Horizontal indoor combined type

	
Air quantity: 5100m3/h; ext. Static pressure


950Pa; New return air cold: 10Kw; steam heating power: 15Kw; dry steam humidifier: 13Kg / h; motor power: 4Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  	  
	
12

	
K25

	
Horizontal indoor combined type

	
Air quantity: 19000m3/h; ext. Static pressure


850Pa; fresh air heating: 8Kw; new return air cold: 51Kw; wheel dehumidification capacity: more than 14Kg / h; wheel regenerative steam consumption: 75Kg / h; motor power: 11Kw; renewable fan motor power: 1.1kw; dry steam humidification: 3.5Kg / h

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili, direct-expansion

	
Increasing direct expansion cooling section


	  	  	
Unit section: wind section, in effect filter section F7, humididier section, fresh return air cooling, wind section, middle section, desiccant wheel section (with regenerative heater)

	  	  	  	  	  
	  	  	
New wind steam heating section, in effect filter section F6, filter section G3, fresh wind section

	  	  	  	  	  	  	  	  
	
13

	
K3X

	
Horizontal indoor combined type

	
Air quantity: 8800m3/h; ext. Static pressure


200Pa; New return air cold: 140Kw; new form of cold air: 85Kw; motor power rate: 4Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: wind section, new air cold retaining water section, fresh wind steam heating section, in effect filter section F6, filter section G3,wind section

	  	  	  	  	  	  
	
14

	
K31

	
Horizontal indoor combined type

	
Air quantity: 12600m3/h; ext. Static pressure


950Pa; New return air cold: 30Kw; steam heating power: 25Kw; dry steam humidifier: 8Kg / h; motor power: 11Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  	  
	
15

	
K32

	
Horizontal indoor combined type

	
Air quantity: 20300m3/h; ext. Static pressure


950Pa; New return air cold: 40Kw; steam heating power: 52Kw; dry steam humidifier: 37Kg / h; motor power: 15Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  	  
	
16

	
K33

	
Horizontal indoor combined type

	
Air quantity: 15500m3/h; ext. Static pressure


950Pa; New return air cold: 35Kw; steam heating power: 35Kw; dry steam humidifier: 22.5Kg / h; motor power: 11Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  	  











	
Quotation summary sheet

	
4/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	

     Equipment No.     



	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Price difference

	
Remark

	
Changing


	
First.

	
Air-conditioning

equipment

	  	  	
Former

	
Now

	  	
Former

	
Now

	
Former

	
Now

	  	  	  
	
17

	
K34

	
Horizontal indoor combined type

	
Air quantity: 8000m3/h; ext. Static pressure


950Pa; new return air cold: 18Kw; steam heating power: 16Kw; dry steam humidifier: 6Kg / h; motor power: 5.5Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
0

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  	  
	
18

	
K41

	
Horizontal indoor combined type

	
Air quantity: 19500m3/h; ext. Static pressure


550Pa; fresh air heating: 35Kw; new return air cold: 110Kw; steam heating: 75Kw; dry steam humidifier: 38Kg / h; motor power: 15Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
0

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  
	  	  	
New air steam heating section, in effect filter section F6, coarse filter section G3, the fresh air section.

	  	  	  	  	  	  	  	  
	
19

	
K51

	
Horizontal indoor combined type

	
Air quantity: 7000m3/h; ext. Static pressure


550Pa; fresh air heating: 15Kw; new return air cold: 40Kw; steam heating: 20Kw; dry steam humidifier: 14Kg / h; motor power: 7.5Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
0

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  
	  	  	
New air steam heating section, in effect filter section F6, coarse filter section G3, the fresh air section.

	  	  	  	  	  	  	  	  
	
20

	
K52

	
Horizontal indoor combined type

	
Air quantity: 7650m3/h; ext. Static pressure


550Pa; fresh air heating: 20Kw; new return air cold: 50Kw; steam heating: 30Kw; dry steam humidifier: 20Kg / h; motor power: 5.5Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
0

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  	  	  	  
	  	  	
New air steam heating section, in effect filter section F6, coarse filter section G3, the fresh air section.

	  	  	  	  	  	  	  	  
	
21

	
K61

	
Horizontal indoor combined type

	
Air quantity: 3000m3/h; ext. Static pressure


850Pa; fresh air heating: 10Kw; new return air cold: 20Kw; steam heating: 10Kw; dry steam humidifier: 9Kg / h; motor power: 3Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
0

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  
	  	  	
New air steam heating section, in effect filter section F6, coarse filter section G3, the fresh air section.

	  	  	  	  	  	  	  	  
	
22

	
K62

	
Horizontal indoor combined type

	
Air quantity: 21000m3/h; ext. Static pressure


500Pa; fresh air heating: 35Kw; new return air cold: 90Kw; steam heating: 20Kw; dry steam humidifier: 30Kg / h; motor power: 15Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
0

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  
	  	  	
New air steam heating section, in effect filter section F6, coarse filter section G3, the fresh air section.

	  	  	  	  	  	  	  	  
	
23

	
K71

	
Horizontal indoor combined type

	
Air quantity: 11500m3/h; ext. Static pressure


950Pa; fresh air heating: 20Kw; new return air cold: 60Kw; steam heating: 25Kw; dry steam humidifier: 17Kg / h; motor power: 11Kw

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
0

	
Kaili

	  
	  	  	
Unit section: wind section, in effect filter section F7, middle section, air blower section, humididier section, heating section, fresh return air cooling section, return air combined section.

	  	  	  	  	  
	  	  	
New air steam heating section, in effect filter section F6, coarse filter section G3, the fresh air section.

	  	  	  	  	  	  	  	  











	
Quotation summary sheet

	
5/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	

     Equipment No.     



	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Price difference

	
Remark

	
Changing


	
First.

	
Air-conditioning

equipment

	  	  	
Former

	
Now

	  	
Former

	
Now

	
Former

	
Now

	  	  	  
	
24

	
XH71

	
Closet-type energy-saving air conditioner fresh air ventilation (with transitional season pass and the new air humidification function)

	
Air quantity: 8000m3/h; wind side ext. Static pressure: 270Pa; exhaust side of the outside than the outside pressure: 230Pa; blower power: 3Kw; exhaust fan power: 3Kw; rated heat recovery efficiency: ≥ 60%; rated cooling capacity table: 120Kw; rated Add heat: 115Kw; dry steam humidifier: 70Kg / h

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
SUNTEC

	  
	
25

	
XH72

	
Closet-type energy-saving air conditioner fresh air ventilation (with transitional season pass and the new air humidification function)

	
Air quantity: 3000m3/h; wind side ext. Static pressure: 180Pa; exhaust side of the outside than the outside pressure: 230Pa; blower power: 1Kw; exhaust fan power: 1Kw; rated heat recovery efficiency: ≥ 60%; rated cooling capacity table: 45Kw; Rated Add heat: 43Kw; dry steam humidifier: 25Kg / h

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
SUNTEC

	  
	
26

	
XH73

	
Closet-type energy-saving air conditioner fresh air ventilation (with transitional season pass and the new air humidification function)

	
Air quantity: 5000m3/h; wind side ext. Static pressure: 250Pa; exhaust side of the outside than the outside pressure: 250Pa; blower power: 2.2Kw; exhaust fan power: 2.2Kw; rated heat recovery efficiency: ≥ 60%; rated cooling capacity table: 75Kw ; rated heat flux: 72Kw; dry steam humidifier: 40Kg / h

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
SUNTEC

	  
	
27

	
FCU-1

	
Horizontal concealed fan coil (high static)

	
Air quantity:410m3/h,ext. Static pressure:50pa, rated cooling capacity: 2.05Kw, rated heat: 3.48Kw, motor power: 49w/220V (high level)

	
7

	
7

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	
28

	
FCU-2

	
Horizontal concealed fan coil (high static)

	
Air quantity:750m3/h,ext. Static pressure:50pa, rated cooling capacity: 3.74Kw, rated heat: 6.26Kw, motor power: 84w/220V. (high level)

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	
29

	
FCU-3

	
Horizontal concealed fan coil (high static)

	
Air quantity:900m3/h,ext. Static pressure:50pa, rated cooling capacity: 4.5Kw, Rated calories: 7.5Kw, motor power: 105w/220V (high level)

	
4

	
4

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	
30

	
FCU-4

	
Horizontal concealed fan coil (high static)

	
Air quantity:1060m3/h,ext. Static pressure:50pa,rated cooling capacity: 5.23Kw, rated heat: 8.72Kw, motor power: 122w/220V. (high level)

	
16

	
16

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	
31

	
FCU-5

	
Horizontal concealed fan coil (high static)

	
Air quantity:1430m3/h,ext. Static pressure:50pa,rated cooling capacity: 7.5Kw, Rated calories: 12.49Kw, motor power rate: 184w/220V. (high level)

	
34

	
34

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	
32

	
FCU-6

	
Horizontal concealed fan coil (high static)

	
Air quantity:2110m3/h,ext. Static pressure:50pa,rated cooling capacity: 10.35Kw, rated heat: 17.25Kw, motor power rate: 248w/220V.(high level)

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	
33

	
FCU-7

	
Horizontal surface mounted fan coil

	
Air quantity:1020m3/h,ext. Static pressure:12pa, rated cooling capacity: 5.23kw, rated heat: 8.72kw, motor power: 87w/220v. (High level)

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili (1st floor 1# stairs) addition

	  
	
34

	
FCU-8

	
Horizontal surface mounted fan coil

	
Air quantity:1360m3/h,ext. Static pressure:12pa,rated cooling capacity: 7.68kw, rated heat: 12. 9kw, motor power: 100w/220v

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili (1st floor 2#3# stairs) addition

	  











	
Quotation summary sheet

	
6/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Price difference

	
Remark

	
Changing


	
First.

	
Air-conditioning

equipment

	  	  	
Former

	
Now

	  	
Former

	
Now

	
Former

	
Now

	  	  	  
	
35

	
L1-1~ 2

	
LSLG

	
Cooling capacity: 790 kw, water flow rate: 136m3 / h (5-10 °C), cooling water flow: 169m3 / h (32-37 °C), the compressor input power: 189kw, (refrigerant HCF-134a)

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	  
	
36

	
L1-3~ 5

	
Horizontal centrifugal pump

	
Flow: 131 ~ 225m3 / h, head: 29.5 ~ 24.5 m, rpm: 1480rpm, input power: 22 kw.

	
3

	
3

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Grundfos, 2 use 1 reserve

	  
	
37

	
L1-6

	
Ground expansion tank

	
Single tank dual pump, water pump parameters are as follows: Flow: 7.5 ~ 13.8m3 / h, Head: 37 ~ 34 m, input power: 3 kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
NZP1.2x1-50x2x1

	  
	
38

	
L1-7

	
Rectangular water tank

	
1800x1200x1200

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Stainless steel water tank

	  
	  	  	  	  	  	  	  	
***

	
***

	
***

	
***

	
***

	  	  
	
Second.

	
Process refrigeration equipment

	  	  	  	  	  	
***

	
***

	
***

	
***

	
***

	  	  
	
1

	
L2-1LSLG

	
LSLG

	
Cooling capacity: 1355 kw, water flow rate: 233m3 / h (7-12 °C), cooling water flow: 283m3 / h (32-37 °C), compression


Machine input power: 288kw, (refrigerant HCF-134a)

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Kaili

	
Capacity of the original host — cold: 456 kw


	
2

	
L2-2~ 4horizontal centrifugal pump

	
Horizontal centrifugal pump

	
Flow: 112 ~ 192m3 / h, Head: 34 ~ 28m, rpm: 1480rpm, input power: 22kw

	
2

	
3

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Grundfos, two uses one reserve

	
The original water pump: flow: 28 ~ 56m3 / h, head: 29.6 ~ 26.1


	
3

	
L2-4 steel cold water tank

	
Rectangular water tank

	
3000x2000x3300

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Stainless steel tank 150mm outside the tank centrifugal glass wool insulation

	
The original tank: 2500x1800x2000


	
Second.

	
Ventilation equipment

	  	  	  	  	  	
***

	
***

	
***

	
***

	
***

	  	  
	
1

	
PBJ11-1 PBJ21-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 750m3/h, total pressure: 400pa, motor power: 0.37kw.

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
2

	
PB63-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 1500m3/h, total pressure: 200pa,motor power: 0.25kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
3

	
PB53-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 3000m3/h, total pressure: 200pa,motor power: 0.55kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
4

	
PJ11-1 PJ21-1 PJ31-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 1350m3/h, total pressure: 400pa,motor power: 0.55kw.

	
3

	
3

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
5

	
PJ12-1 PJ24-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 750m3/h, total pressure: 400pa, motor power: 0.37kw.

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
6

	
PJ13-1 PJ22-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 1900m3/h, total pressure: 400pa,motor power: 0.55kw.

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
7

	
PJ14-1 PJ23-1 PJ34-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 1450m3/h, total pressure: 400pa,motor power: 0.55kw.

	
3

	
3

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
8

	
PJ15-1 PJ25-1 PJ61-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 550m3/h, total pressure: 400pa, motor power 0.37kw.

	
3

	
3

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
9

	
PJ32-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 2200m3/h, total pressure: 400pa,motor power: 0.55kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
10

	
PJ33-1 PJ71-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 1100m3/h, total pressure: 400pa,motor power: 0.37kw.

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
11

	
PJ41-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 2200m3/h, total pressure: 300pa,motor power: 0.55kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
12

	
PJ41-2

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 1850m3/h, total pressure: 300pa,motor power: 0.37kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
13

	
PJ41-3

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 800m3/h, total pressure: 300pa, motor power 0.18kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  











	
Quotation summary sheet

	
7/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	

     Equipment No.     



	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Price difference

	
Remark

	
Changing


	
First.

	
Air-conditioning

equipment

	  	  	
Former

	
Now

	  	
Former

	
Now

	
Former

	
Now

	  	  	  
	
14

	
PJ41-4

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 900m3/h, total pressure: 300pa, motor power: 0.18kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
15

	
PJ51-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 800m3/h, total pressure: 400pa, motor power: 0.25kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
16

	
P62-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 3300m3/h, total pressure: 300pa,


Motor power: 0.75kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
17

	
P41-4

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 900m3/h, total pressure: 300pa, motor power: 0.18kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
18

	
P41-3

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 800m3/h, total pressure: 300pa, motor power: 0.18kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
19

	
P41-2

	
Low noise intermediate- efficacy explosion-proof exhaust

	
Air quantity: 1850m3/h, total pressure: 300pa,


Motor power: 0.37kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
20

	
P41-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 2200m3/h, total pressure: 300pa,


Motor power: 0.55kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
21

	
P63-1

	
Low noise intermediate- efficacy explosion-proof exhaust fan

	
Air quantity: 2200m3/h, total pressure: 300pa,


Motor power: 0.55kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
22

	
P73-1~ 3

	
Low noise intermediate- efficacy explosion-proof exhaust fan nox

	
Air quantity: 1650m3/h, total pressure: 500pa,


Motor power: 0.55kw.

	
3

	
3

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
23

	
PJ52-1 P73-7~8

	
Coarse clean ventilation

	
Air quantity:800m3/h,static pressure:140pa, rpm:


2500rpm,fan power: 0.17 Kw/220V.

	
3

	
3

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	
24

	
PJ52-2~3 P73-4~6 P73-9~10

	
Coarse clean ventilation

	
Air quantity:500m3/h,static pressure:160pa, rpm:


2500rpm, fan power:0.13kw/220V.

	
7

	
7

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	
25

	
P63-2

	
Coarse clean ventilation

	
Air quantity:300m3/h,static pressure:100pa, rpm:


2500rpm, fan power:0.08kw/220V.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	
26

	
P53-1

	
Wall-type exhaust fan

	
Air quantity:1500m3/h,static pressure:45pa, rpm:


1380rpm,fan power:0.09kw.

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	
27

	
P53-2-1~ 4 P53-3-1~ 3

	
Wall-type exhaust fan

	
Air quantity:2400m3/h,static pressure:60pa, rpm:


1380rpm,fan power:0.15kw.

	
7

	
7

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	
28

	
IU1-1~ 20

	
Induction fan

	
Air quantity:650~850m3/h, export wind


Speed:11~15m/s,motor power rate:120w/220V,nozzle type:Φ100x2

	
0

	
0

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Here canceled according to the meeting of Suntec

	  
	
Third.

	
Laminar hood equipment

	  	  	  	  	  	  	  	  	  	  	  	  
	
1

	
CL11 CL13 CL21 CL23

	
Rack stainless steel laminar flow hood (local A-zone use) Dimensions: (length x width x high) 2000x1000x550

	
Air quantity:3600m3/h,average surface wind speed:0.5m/s,ext. Static pressure:50~100Pa, power:0.6Kw/220V,high filtration efficiency: ≥ 99.995% at MPPS ( H14)

	
4

	
4

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
2

	
CL12 CL22 CL52

	
Rack stainless steel laminar flow hood (local A-zone use) Dimensions: (length x width x high)1600x800x550

	
Air quantity:2300m3/h,average surface wind speed:0.5m/s,ext. Static pressure:50~100Pa, power:0.4Kw/220V,high filtration efficiency: ≥ 99.995% at MPPS ( H14)

	
3

	
3

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
3

	
CL31-1 CL31-2 CL34 CL35CL51

	
Rack stainless steel laminar flow hood (local A-zone use) Dimensions: (length x width x high) 1200x600x550

	
Air quantity:1300m3/h, average surface wind speed:0.5m/s,ext. Static pressure:50~100Pa, power:0.2Kw/220V,high filtration efficiency: ≥ 99.995% at MPPS ( H14)

	
5

	
5

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  











	
Quotation summary sheet

	
8/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	

     Equipment No.     



	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Price difference

	
Remark

	
Changing


	
First.

	
Air-conditioning

equipment

	  	  	
Former

	
Now

	  	
Former

	
Now

	
Former

	
Now

	  	  	  
	
4

	
CL32-1

	
Rack stainless steel laminar flow hood (local A-zone use) Dimensions: (length x width x high) 3300x1000x550

	
Air quantity:6500m3/h,average surface wind speed: 0.55m/s, ext. Static pressure: 50~100Pa, power: 1Kw/220V, high filtration efficiency>99.995% at MPPS (H14)

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
5

	
CL32-1

	
Rack stainless steel laminar flow hood (local A-zone use) Dimensions: (length x width x high) 1250x1000x550

	
Air quantity:2500m3/h,average surface wind speed: 0.5m/s, ext. Static pressure: 50~100Pa, power: 0.4Kw/220V, high filtration efficiency>99.995% at MPPS (H14)

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
6

	
CL33

	
Rack stainless steel laminar flow hood (local A-zone use) Dimensions: (length x width x high) 1600x1200x550

	
Air quantity:3450m3/h,average surface wind speed: 0.5m/s, ext. Static pressure: 50~100Pa, power: 0.6Kw/220V, high filtration efficiency>99.995% at MPPS (H14)

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
7

	
CL36-1

	
Rack stainless steel laminar flow hood (local A-zone use) Dimensions: (length x width x high) 600x550x550

	
Air quantity:600m3/h,average surface wind speed: 0.5m/s, ext. Static pressure: 50~100Pa, power: 0.2Kw/220V, high filtration efficiency>99.995% at MPPS (H14)

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	
8

	
CL36-2

	
Rack stainless steel laminar flow hood (local A-zone use) Dimensions: (length x width x high) 1100x1000x550

	
Air quantity:2000m3/h,average surface wind speed: 0.5m/s, ext. Static pressure: 50~100Pa, power: 0.4Kw/220V, high filtration efficiency>99.995% at MPPS (H14)

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Suntec

	  
	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
9

	
1

	
Delivery

	
1000X1000X1500

	
4

	
4

	
Sets.

	
***

	
***

	
***

	
***

	
***

	
Suntec

	
according to 4/30 meeting re-adjust


	  	
2

	
Delivery

	
600X600X600

	
0

	
1

	
Sets.

	
***

	
***

	
***

	
***

	
***

	
With purification function


	  	
3

	
Delivery

	
600X600X600

	
3

	
2

	
Sets.

	
***

	
***

	
***

	
***

	
***

	
Suntec


	  	
4

	
Delivery

	
800X800X800

	
15

	
8

	
Sets.

	
***

	
***

	
***

	
***

	
***

	
Suntec


	  	
5

	
Delivery

	
800X800X800

	
3

	
10

	
Sets.

	
***

	
***

	
***

	
***

	
***

	
With purification function


	
Forth

	
Combined icehouse

	  	  	  	  	  	  	  	  	  	  	  	  
	
1

	
LK71

	
Combined icehouse(2-8°C,35-75%)

	
Icehouse volume:100m3, icehouse height:3m, icehouse door with air curtain

	
1

	
1

	
Sets.

	
***

	
***

	
***

	
***

	
***

	
Hongwei

	
requirements of adding humidity


	  	  	
LK71-b

	
Air-cooled and temperature semi-hermetic condensing units LCU-42FJ one

	  	  	  	  	  	  	  	  	  	  
	  	  	
LK71-a

	
Cooler CC-CV9000H one

	  	  	  	  	  	  	  	  	  	  
	
2

	
LK61

	
Combined icehouse(2-8 °C,35-75%)

	
Icehouse volume:28m3, icehouse height:3m, icehouse door with air curtain

	
1

	
1

	
Sets.

	
***

	
***

	
***

	
***

	
***

	
Hongwei

	
requirements of adding humidity


	  	  	
LK61-b

	
Air-cooled and temperature semi-hermetic condensing units LCU-72FJ one

	  	  	  	  	  	  	  	  	  	  
	  	  	
LK61-a1~2

	
Cooler CC-CV9000H two

	  	  	  	  	  	  	  	  	  	  
	
3

	
LK62

	
Combined icehouse(2-8 °C,35-75%)

	
Icehouse volume:100m3, icehouse height:3m, icehouse door with air curtain

	
1

	
1

	
Sets.

	
***

	
***

	
***

	
***

	
***

	
Hongwei

	
requirements of adding humidity


	  	  	
LK61-b

	
Air-cooled and temperature semi-hermetic condensing units LCU-42FJ one

	  	  	  	  	  	  	  	  	  	  
	  	  	
LK61-a

	
Cooler CC-CV9000H one

	  	  	  	  	  	  	  	  	  	  
	
4

	
LK63

	
Combined icehouse(2-8 °C,35-75%)

	
Air-cooled and temperature semi-hermetic condensing units LCU-42FJ one

	
1

	
1

	
Sets.

	
***

	
***

	
***

	
***

	
***

	
Hongwei

	
requirements of adding humidity













	
Quotation summary sheet

	
9/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Price difference

	
Remark

	
Changing


	
First.

	
Air-conditioning equipment

	  	  	
Former

	
Now

	  	
Former

	
Now

	
Former

	
Now

	
First.

	
Air-conditioning equipment

	  
	  	  	
LK63-b

	
Air-cooled and temperature semi-hermetic condensing units LCU-72FJ one

	  	  	  	  	  	  	  	  	  	  
	  	  	
LK63-a1~2

	
Cooler CC-CV9000H two

	  	  	  	  	  	  	  	  	  	  
	
5

	
LK64

	
Combined icehouse(2-8°C,35-75%)

	
Icehouse volume: 220m3, icehouse height:3m, icehouse door with air curtain

	
1

	
1

	
sets.

	
***

	
***

	
***

	
***

	
***

	
Hongwei

	
requirements of adding humidity


	  	  	
LK64-b

	
Air-cooled and temperature semi-hermetic condensing units LCU-62FJ one

	  	  	  	  	  	  	  	  	  	  
	  	  	
LK64a1~2

	
Cooler CC-CV9000H two

	  	  	  	  	  	  	  	  	  	  
	
6

	
LK65

	
Combined icehouse(-20°C)

	
Icehouse volume: 60m3, icehouse height:3m, icehouse door with air curtain

	
1

	
1

	
sets.

	
***

	
***

	
***

	
***

	
***

	
Hongwei

	  
	  	  	
LK65-b

	
Air-cooled and temperature semi-hermetic condensing units LCU-72FJ one

	  	  	  	  	  	  	  	  	  	  
	  	  	
LK65-a

	
Cooler CC-CV9000H one

	  	  	  	  	  	  	  	  	  	  
	
7

	  	
process equipment in place

	  	  	  	  	  	  	
***

	
***

	
***

	  	  
	
Fifth

	
Cleanroom equipment

	  	  	  	  	  	  	  	  	  	  	  	  
	
1

	
Stainless steel clean wash-basin

	  	
Stainless steel

	
16

	
17

	
sets.

	
***

	
***

	
***

	
***

	
***

	  	
according to 4/30 meeting re-adjust


	  	
Inductive water faucet

	  	
ToTo DLE102BSK

	
0

	
16

	
sets.

	
***

	
***

	
***

	
***

	
***


	  	
Stainless steel clean basin

	  	  	
24

	
19

	
sets.

	
***

	
***

	
***

	
***

	
***


	  	
Locker

	  	
adjust in accordance with 100 persons

	
16

	
16

	
sets.

	
***

	
***

	
***

	
***

	
***


	  	
Stainless steel cabinet for shoes

	  	
adjust in accordance with 100 persons

	
8

	
8

	
sets.

	
***

	
***

	
***

	
***

	
***


	  	
Hand dryer

	  	  	
9

	
10

	
sets.

	
***

	
***

	
***

	
***

	
***


	  	
Hand sanitizer

	  	
Wuhan Lihui

	
7

	
20

	
sets

	
***

	
***

	
***

	
***

	
***


	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	
Sixth

	
Fixed air flow valve

	  	  	  	  	  	  	  	  	  	  	  	  
	  	
1

	
Air quantitycav

	  	  	  	  	  	  	  	  	  	
Tuosi

	  
	  	  	  	
EN200x100

	
31

	
31

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	  	  	  	
EN300x100

	
75

	
75

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	  	  	  	
EN300x150

	
182

	
182

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	  	  	  	
EN300x200

	
67

	
67

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	  	  	  	
EN300x100

	
14

	
14

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	  	  	  	
EN300x200

	
7

	
7

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	  	
2

	
Air quantity VAV

	  	  	  	
Piece

	
***

	
***

	
***

	
***

	
***

	
Tuosi

	  
	  	  	  	
TVJ200x100

	
14

	
14

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	  	  	  	
TJ300x100

	
12

	
12

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	  	  	  	
TVJ200x100

	
4

	
4

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	  	  	  	
TVJ300x100

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	  	  	  	
TVR100

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	
***

	  	  
	  	  	  	  	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  	
Former quotation

	
Now quotation

	
Price difference

	  	  
	  	
Subtotal

	  	  	  	  	  	  	  	
***

	
***

	
***

	  	  
	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  	  	  	  	  	  











	
Quotation summary sheet

	
10/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Price difference

	
Remark

	
changing


	
First、

	
Air-conditioning equipment

	  	  	
Former

	
Now

	  	
Former

	
Now

	
Former

	
Now

	  	  	  
	  	
Subtotal 1

	  	  	  	  	  	  	  	
***

	
***

	
***

	  	  
	  	
Installation and accessories

	  	  	
5%

	  	  	  	  	
***

	
***

	
***

	  	  
	  	
Subtotal 2

	  	  	  	  	  	  	  	
***

	
***

	
***

	  	  
	  	
Tax

	  	  	
4.33%

	  	  	  	  	
***

	
***

	
***

	  	  
	  	
Total

	  	  	  	  	  	  	  	
***

	
***

	
***

	  	  
	  	  	  	  	  	  	  	  	  	  	  	  	  	  





Note: the words in yellow are the changing part.








	
Quotation summary sheet

	
11/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	
Seventh

	
Power distribution cabinet

	  	  	  	  	  	  	  
	  	
1

	
Low pressure power distribution cabinet

	
11KHX

	
1

	
Piece

	
***

	
***

	  
	  	
2

	  	
12KHX

	
1

	  	
***

	
***

	  
	  	
3

	  	
11KX

	
1

	
Piece

	
***

	
***

	  
	  	
4

	  	
12KX

	
1

	
Piece

	
***

	
***

	  
	  	
5

	  	
13KX

	
1

	
Piece

	
***

	
***

	  
	  	
6

	  	
14KX

	
1

	
Piece

	
***

	
***

	  
	  	
7

	  	
15KX

	
1

	
Piece

	
***

	
***

	  
	  	
8

	  	
16KX

	
1

	
Piece

	
***

	
***

	  
	  	
9

	
11ELX/12ELX/13ELX

	
11ELX~20ELX

	
10

	
Piece

	
***

	
***

	  
	  	
10

	  	
21ELX

	
1

	
Piece

	
***

	
***

	  
	  	
11

	  	
22ELX

	
1

	
Piece

	
***

	
***

	  
	  	
12

	  	
110DX

	
1

	
Piece

	
***

	
***

	  
	  	
13

	  	
111DX

	
1

	
Piece

	
***

	
***

	  
	  	
14

	  	
112DX

	
1

	
Piece

	
***

	
***

	  
	  	
15

	  	
113DX

	
1

	
Piece

	
***

	
***

	  











	
Quotation summary sheet

	
12/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
16

	  	
114DX

	
1

	
Piece

	
***

	
***

	  
	  	
17

	  	
115DX

	
1

	
Piece

	
***

	
***

	  
	  	
18

	  	
116DX

	
1

	
Piece

	
***

	
***

	  
	  	
19

	  	
117DX

	
1

	
Piece

	
***

	
***

	  
	  	
20

	  	
117DX

	
1

	
Piece

	
***

	
***

	  
	  	
21

	  	
11MHX

	
1

	
Piece

	
***

	
***

	  
	  	
22

	  	
21MHX

	
1

	
Piece

	
***

	
***

	  
	  	
23

	  	
DGMX

	
1

	
Piece

	
***

	
***

	  
	  	
24

	
11MX

	
DGMX

	
1

	
Piece

	
***

	
***

	  
	  	
25

	  	
12MX

	
1

	
Piece

	
***

	
***

	  
	  	
26

	  	
13MX,14MX

	
2

	
Piece

	
***

	
***

	  
	  	
27

	  	
15MX

	
1

	
Piece

	
***

	
***

	  
	  	
28

	  	
16MX

	
1

	
Piece

	
***

	
***

	  
	  	
29

	  	
21MX

	
1

	
Piece

	
***

	
***

	  
	  	
30

	  	
22MX

	
1

	
Piece

	
***

	
***

	  
	  	
31

	  	
23MX

	
1

	
Piece

	
***

	
***

	  











	
Quotation summary sheet

	
13/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
32

	  	
01JX~06JX,11JX~14JX

	
10

	
Piece

	
***

	
***

	  
	  	
33

	  	
11DX

	
1

	
Piece

	
***

	
***

	  
	  	
34

	  	
12DX

	
1

	
Piece

	
***

	
***

	  
	  	
35

	  	
13DX

	
1

	
Piece

	
***

	
***

	  
	  	
36

	  	
14DX

	
1

	
Piece

	
***

	
***

	  
	  	
37

	  	
15DX

	
1

	
Piece

	
***

	
***

	  
	  	
38

	  	
16DX

	
1

	
Piece

	
***

	
***

	  
	  	
39

	  	
17DX

	
1

	
Piece

	
***

	
***

	  
	  	
40

	  	
18DX

	
1

	
Piece

	
***

	
***

	  
	  	
41

	  	
19DX

	
1

	
Piece

	
***

	
***

	  
	  	
42

	  	
22DX

	
1

	
Piece

	
***

	
***

	  
	  	
43

	  	
23DX

	
1

	
Piece

	
***

	
***

	  
	  	
44

	  	
11EX

	
1

	
Piece

	
***

	
***

	  
	  	
45

	  	
12EX

	
1

	
Piece

	
***

	
***

	  
	  	
46

	  	
13EX

	
1

	
Piece

	
***

	
***

	  
	  	
47

	  	
14EX

	
1

	
Piece

	
***

	
***

	  











	
Quotation summary sheet

	
14/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
48

	  	
15EX

	
1

	
Piece

	
***

	
***

	  
	  	
49

	  	
16EX

	
1

	
Piece

	
***

	
***

	  
	  	
50

	  	
17EX

	
1

	
Piece

	
***

	
***

	  
	  	
51

	  	
21EX

	
1

	
Piece

	
***

	
***

	  
	  	
52

	  	
22EX

	
1

	
Piece

	
***

	
***

	  
	  	
53

	  	
23EX

	
1

	
Piece

	
***

	
***

	  
	  	
54

	  	
24EX

	
1

	
Piece

	
***

	
***

	  
	  	
55

	  	
21HX

	
1

	
Piece

	
***

	
***

	  
	  	
56

	  	
11CX~18CX

	
8

	
Piece

	
***

	
***

	  
	  	
57

	  	
11LX

	
1

	
Piece

	
***

	
***

	  
	  	
58

	  	
12LX

	
1

	
Piece

	
***

	
***

	  
	  	
59

	  	
13LX

	
1

	
Piece

	
***

	
***

	  
	  	
60

	  	
14LX

	
1

	
Piece

	
***

	
***

	  
	  	
61

	  	
11HX

	
1

	
Piece

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  
	  	  	
Total (1) — Former quotation

	  	  	  	  	
***

	  











	
Quotation summary sheet

	
15/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  
	
Seventh

	
Power distribution cabinet

	  	  	  	  	  	  	  
	  	
1

	
Switch cabinet

	
11KHX

	
1

	
Piece

	
***

	
***

	
Clean space ( machine room )


	  	
2

	
Switch cabinet

	
12KHX

	
1

	
Piece

	
***

	
***

	
Clean space ( machine room )


	  	
3

	
Air-conditioning cabinet

	
11KX

	
1

	
Piece

	
***

	
***

	
Clean space ( machine room )


	  	
4

	
Air-conditioning cabinet

	
12KX

	
1

	
Piece

	
***

	
***

	
Clean space ( machine room )


	  	
5

	
Air-conditioning cabinet

	
13KX

	
1

	
Piece

	
***

	
***

	
Clean space ( machine room )


	  	
6

	
Air-conditioning cabinet

	
14KX

	
1

	
Piece

	
***

	
***

	
Clean space ( machine room )


	  	
7

	
Air-conditioning cabinet

	
15KX

	
1

	
Piece

	
***

	
***

	
Clean space ( machine room )


	  	
8

	
Air-conditioning cabinet

	
16KX

	
1

	
Piece

	
***

	
***

	
Clean space ( machine room )


	  	
9

	
The second type loading power cabinet

	
21ELX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
10

	
The second type loading power cabinet

	
22ELX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
11

	
Power box

	
110DX

	
1

	
Piece

	
***

	
***

	
Clean space













	
Quotation summary sheet

	
16/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
12

	
Power box

	
111DX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
13

	
Power box

	
112DX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
14

	
Power box

	
117DX

	
1

	
Piece

	
***

	
***

	
Only for installation


	  	
15

	
Maintenance box

	
21JX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
16

	
Maintenance box

	
22JX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
17

	
Maintenance box

	
23JX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
18

	
Maintenance box

	
24JX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
19

	
Maintenance box

	
25JX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
20

	
Maintenance box

	
26JX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
21

	
Lighting box

	
12MX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
22

	
Lighting box

	
13MX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
23

	
Lighting box

	
14MX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
24

	
Lighting box

	
22MX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
25

	
Power box

	
11DX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
26

	
Power box

	
12DX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
27

	
Power box

	
13DX

	
1

	
Piece

	
***

	
***

	
Clean space













	
Quotation summary sheet

	
17/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
28

	
Power box

	
14DX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
29

	
Power box

	
15DX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
30

	
Power box

	
16DX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
31

	
Power box

	
17DX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
32

	
Power box

	
18DX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
33

	
Power box

	
19DX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
34

	
The second type loading power cabinet

	
11EX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
35

	
The second type loading power cabinet

	
12EX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
36

	
The second type loading power cabinet

	
13EX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
37

	
The second type loading power cabinet

	
14EX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
38

	
The second type loading power cabinet

	
15EX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
39

	
The second type loading power cabinet

	
16EX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
40

	
The second type loading power cabinet

	
17EX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
41

	
The second type loading power cabinet

	
21EX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
42

	
The second type loading power cabinet

	
22EX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
43

	
The second type loading power cabinet

	
23EX

	
1

	
Piece

	
***

	
***

	
Clean space













	
Quotation summary sheet

	
18/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
44

	
The second type loading power cabinet

	
24EX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
45

	
Plugging box

	
11CX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
46

	
Plugging box

	
12CX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
47

	
Plugging box

	
13CX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
48

	
Plugging box

	
14CX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
49

	
Plugging box

	
15CX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
50

	
Plugging box

	
16CX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
51

	
Plugging box

	
17CX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
52

	
Plugging box

	
18CX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	
53

	
Power cabinet

	
21LX

	
1

	
Piece

	
***

	
***

	
Clean space


	  	  	
Total (2) —now quotation

	  	  	  	  	
***

	  
	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	
Total (2)

	
Total (1)

	
Total ( 2) -Total ( 1)

	  
	  	
Subtotal

	  	  	  	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  











	
Quotation summary sheet

	
19/90

	
2009-6-19











  





  











  



















Quotation sheet of equipment department








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  
	  	
Subtotal 1

	  	  	  	
***

	
***

	
***

	  
	  	
Installation and accessories

	  	  	
5%

	
***

	
***

	
***

	  
	  	
Subtotal 2

	  	  	  	
***

	
***

	
***

	  
	  	
Tax

	  	  	
4.33%

	
***

	
***

	
***

	  
	  	
Total

	  	  	  	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  



















	
Quotation summary sheet

	
20/90

	
2009-6-19











  





  











  



















Quotation sheet of retaining project








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and


specification

	
Unit

	
Quantity

	  	
Unit price

	
Unit price of

stainless steel

	
Total

	
Total price of

stainless steel

	
Price


difference

	
Price difference of


stainless steel

	
Remark

	
Reasons of addition


	  	  	  	  	
Former

	
Now

	
2009.6.17

	
Former

	
Now

	  	
Former

	
Now

	  	  	  	  	  
	
1

	
100hollow color steel partition wall

	
100mm

	
m2

	
2478

	
2478

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
5% exhaustion, SUNTEC

	  
	  	
50 rockwool color steel clad plate

	
50mm

	
m2

	
4113

	
4335

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
5% exhaustion, SUNTEC

	
Adding suspended ceiling to water producing plant


 


	  	
50 rockwool color steel clad plate (one side magnesium oxide)

	
50mm

	
m2

	
706

	
706

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
5% exhaustion, SUNTEC

	  
	  	
Aluminium alloy connecting piece

	  	
m2

	
7297

	
7519

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	  	
Horizontal adjustment system

	  	
m2

	
7297

	  	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	  	
Treated joint

	  	
m2

	
7297

	
0

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	
2

	
55 magnesium


 Rockwool color steel clad plate

	
55mm

	
m2

	
5059

	
5059

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
5% exhaustion, SUNTEC

	  
	  	
Aluminium alloy connecting piece

	  	
m2

	
5059

	
5059

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	  	
Hanger of drop ceiling tiles

	  	
m2

	
5059

	
5059

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	  	
Treated joint

	  	
m2

	
5059

	
5059

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	
3

	
Double window

	
1200×1000

	
Sets.

	
13

	
86

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
Glass thickness 5mm,SUNTEC

	
Adding according to requirements of proprietor


	
4

	
Swing in

	
800X2100

	
Sets.

	
128

	
127

	
15

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
With windows,SUNTEC

	  
	  	
Stainless steel swing in

	
800X2100

	
Sets.

	  	  	
112

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
With windows,SUNTEC

	  
	  	
Swing in

	
900X2100

	
Sets.

	
22

	
22

	
6

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
With windows,SUNTEC

	  
	  	
Stainless steel swing in

	
900X2100

	
Sets.

	  	  	
16

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
With windows,SUNTEC

	  
	  	
Swing in

	
1000X2100

	
Sets.

	
0

	
0

	
0

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
With windows,SUNTEC

	  
	  	
Large-small door

	
1200X2100

	
Sets.

	
10

	
10

	
10

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
With windows,SUNTEC

	  
	  	
Double door

	
1200X2100

	
Sets.

	
28

	
28

	
5

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
With windows,SUNTEC

	  
	  	
Stainless steel double door

	
1200X2100

	
Sets.

	  	  	
23

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
With windows,SUNTEC

	  
	  	
Double door (push-pull type)

	
1200X2100

	
Sets.

	
4

	
5

	
1

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
Safety gate . With windows, SUNTEC

	  
	  	
Stainless steel double door (push-pull type)

	
1200X2100

	
Sets.

	  	  	
4

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
Safety gate . With windows, SUNTEC

	  
	  	
Double door

	
1500X2100

	
Sets.

	
3

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
With windows,SUNTEC

	  
	  	
Stainless steel double door

	
1500X2100

	
Sets.

	  	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
With windows,SUNTEC

	  
	  	
Stainless steel double door (push-pull type)

	
1200X2100

	
Sets.

	
7

	
7

	
7

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
Safety gate, SUNTEC

	  
	  	
Stainless steel double door

	
1200X2100

	
Sets.

	
4

	
4

	
4

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
SUNTEC

	  
	  	
Stainless steel swing in

	
800X2100

	
Sets.

	
19

	
19

	
19

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
With windows,SUNTEC

	  
	  	
Stainless steel swing in (push-pull type)

	
800X2100

	
Sets.

	
1

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
***

	
Safety gate, SUNTEC

	  
	  	
Side-hung door induction system

	  	
Sets.

	
0

	
4

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	
Used in cold house


	
6

	
Earth round corner

	  	
m

	
4800

	
4800

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
SUNTEC

	  











	
Cleanroom retaining

	
21/90

	
2009-6-19











  





  











  



















Quotation sheet of retaining project








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and


specification

	
Unit

	
Quantity

	  	
Unit price

	
Unit price of

stainless steel

	
Total

	
Total price of

stainless steel

	
Price


difference

	
Price difference of

stainless steel

	
Remark

	
Reasons of addition


	  	
Top round corner

	  	
m

	
4800

	
4800

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
SUNTEC

	  
	  	
Wall round corner

	  	
m

	
6500

	
6500

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
SUNTEC

	  
	  	
Round corner piece

	  	
Pcs

	
2000

	
2000

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
SUNTEC

	  
	
7

	
Epoxy color sand ground

	
4 mm

	
m2

	
3245

	
3523

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
Zhuanghe -Yingcai

	
Changing the former PVC floor to the oxygen color sands floor


	
8

	
PVC coiled material

	
Columbia

	
m2

	
1875

	
1263

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
Nera


	
9

	
Hole binding blowing in and out

	  	
Sets.

	
498

	
498

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	  	
Hole binding of lamps and lanterns

	  	
Sets.

	
840

	
840

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	  	
Hole binding of switch and plug

	  	
Sets.

	
660

	
660

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	  	
Precast line pipe

	  	
Sets.

	
660

	
660

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	
10

	
Stainless steel cleaning floor drain

	  	
Sets.

	
26

	
29

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	  	
Stainless steel common floor drain

	  	
Sets.

	
0

	
26

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	
11

	
Two-door air brake controller


 

	  	
Sets.

	
44

	
44

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
Suntec

	  
	
12

	
Three-door air brake controller


 

	  	
Sets.

	
5

	
5

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
Suntec

	  
	  	
Four-door air brake controller


 

	  	
Sets.

	
6

	
6

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
Suntec

	  
	  	
Five-door air brake controller


 

	  	
Sets.

	
1

	
1

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
Suntec

	  
	
13

	
Dial differential pressure instruments


 

	  	
Piece

	
198

	
90

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
DWYER

	
Changing parts of dial differential pressure instruments to differential pressure sensor with LCD


	  	
Differential pressure sensor with LCD


 

	  	
Piece

	  	
83

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	
DWYER


	
14

	
Crash barrier

	  	
m

	
103

	
103

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	  
	
15

	
Access control

	  	
Set

	
0

	
8

	  	
***

	
***

	  	
***

	
***

	  	
***

	  	  	
Adding according to the meeting requirement


	  	  	  	  	  	  	  	
***

	
***

	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	
***

	
***

	  	
Former


quotation

	
Now


quotation

	
Stainless steel quotation

	
Price difference of former and now quotation

	
Price difference of former and now stainless steel quotation

	  	  
	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  
	  	
Subtotal 1

	  	  	  	  	  	  	  	  	
5,879,595

	
6,036,637

	
809,000

	
157,042

	
177,650

	  	  
	  	
Installation cost and management cost

	  	  	  	
15%

	  	  	  	  	
881,939

	
905,496

	
121,350

	
23,556

	
26,648

	  	  
	  	
Subtotal 2

	  	  	  	  	  	  	  	  	
6,761,534

	
6,942,133

	
930,350

	
180,599

	
204,298

	  	  
	  	
Tax

	  	  	  	
4.33%

	  	  	  	  	
292,774

	
300,594

	
40,284

	
7,820

	
8,846

	  	  
	  	
Total

	  	  	  	  	  	  	  	  	
¥7,054,309

	
¥7,242,727

	
¥970,634

	
¥188,419

	
¥213,144

	  	  
	
Note: Words in yellow color are the changed part.

	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  



















	
Cleanroom retaining

	
22/90

	
2009-6-19











  





  











  



















Quotation sheet of retaining project








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	
Fifth

	
Air duct accessory

	  	  	  	  	  	  	  
	  	  	
Zinc coated steel air duct

	  	  	  	  	  	  
	  	  	  	
Δ=1.2mm

	
60

	  	
***

	
***

	  
	  	  	  	
Δ=1.0mm

	
3882

	
m2

	
***

	
***

	  
	  	  	  	
Δ=0.75mm

	
5040

	
m2

	
***

	
***

	  
	  	  	  	
Δ=0.6mm

	
5920

	
m2

	
***

	
***

	  
	  	  	  	
Δ=0.5mm

	
2532

	
m2

	
***

	
***

	  
	  	  	
Aluminium plate (explosion-proof)

	
Δ=2.0mm

	
1

	
m2

	  	
***

	  
	  	  	  	
Δ=1.5mm

	
30

	
m2

	  	
***

	  
	  	  	  	
Δ=1.0mm

	
30

	
m2

	  	
***

	  
	  	  	
Rubber heat preservation

	
Dt=25mm

	
392.2

	
m3

	
***

	
***

	
Huamei, B1


	  	  	  	
Dt=20mm

	
48

	
m3

	
***

	
***

	
Huamei, B1


	  	  	
Microperforated panel hend muffler

	  	  	  	  	  	
Yingda


	  	  	  	
2000x800

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
2000x700

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
1600x630

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
1250x320

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
1100x630

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
1100x500

	
5

	
Piece

	
***

	
***

	  
	  	  	  	
1000x630

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
1000x500

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
800x400

	
6

	
Piece

	
***

	
***

	  
	  	  	  	
700x320

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
630x320

	
3

	
Piece

	
***

	
***

	  
	  	  	  	
500x320

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
500x250

	
4

	
Piece

	
***

	
***

	  











	
Cleanroom retaining

	
23/90

	
2009-6-19











  





  











  



















Quotation sheet of retaining project








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	  	  	
400x250

	
6

	
Piece

	
***

	
***

	  
	  	  	  	
400x200

	
3

	
Piece

	
***

	
***

	  
	  	  	  	
320x200

	
5

	
Piece

	
***

	
***

	  
	  	  	
Microperforated panel pipeline hend muffler

	  	  	  	  	  	
Yingda


	  	  	  	
400x200x1000

	
1

	
Piece

	
***

	
***

	  
	  	  	
ZW type hend muffler

	  	  	  	  	  	
Yingda


	  	  	  	
1250x630

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
1000x400

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
800x400

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
700x400

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
500x320

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
400x250

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
320x200

	
3

	
Piece

	
***

	
***

	  
	  	  	  	
250x200

	
1

	
Piece

	
***

	
***

	  
	  	  	
ZP type finnedmuffler

	  	  	  	  	  	
Yingda


	  	  	  	
800x250x1000

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
500x250x1000

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
400x250x1000

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
320x400x1000

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
320x200x1000

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
320x160x1000

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
250x200x1000

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
200x160x1000

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
200x120x1000

	
1

	
Piece

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  
	  	  	
Sofe fabrie joining

	  	
535

	
m2

	
***

	
***

	  
	  	  	
Support of air duct

	  	
17375

	
m2

	
***

	
***

	  











	
Cleanroom retaining

	
24/90

	
2009-6-19











  





  











  



















Quotation sheet of retaining project








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	  	
Universal port of wind

	  	  	  	  	  	  
	  	  	  	  	
350

	
Piece

	
***

	
***

	  
	
Sixth

	
Valve

	  	  	  	  	  	  	  
	  	  	
Rectangle spring loaded fire damper (70°C)

	  	  	  	  	  	
Yingda


	  	  	  	
2000x800

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
2000x700

	
0

	
Piece

	
***

	
***

	  
	  	  	  	
1600x630

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
1250x630

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
1250x400

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
1250x320

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
1100x630

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
1100x500

	
3

	
Piece

	
***

	
***

	  
	  	  	  	
1000x630

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
1000x550

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
1000x500

	
7

	
Piece

	
***

	
***

	  
	  	  	  	
1000x400

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
800x400

	
8

	
Piece

	
***

	
***

	  
	  	  	  	
800x320

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
700x400

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
700x320

	
0

	
Piece

	
***

	
***

	  
	  	  	  	
630x320

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
630x250

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
500x320

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
500x250

	
3

	
Piece

	
***

	
***

	  
	  	  	  	
400x250

	
6

	
Piece

	
***

	
***

	  
	  	  	  	
400x200

	
3

	
Piece

	
***

	
***

	  
	  	  	  	
320x400

	
1

	
Piece

	
***

	
***

	  











	
Cleanroom retaining

	
25/90

	
2009-6-19











  





  











  



















Quotation sheet of retaining project








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	  	  	
320x200

	
7

	
Piece

	
***

	
***

	  
	  	  	  	
250x200

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
250x160

	
1

	
Piece

	
***

	
***

	  
	  	  	
Power-driven airtight valve

	  	  	  	  	  	
Yingda


	  	  	  	
1250x400

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
1000x500

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
1000x400

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
1000x320

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
800x400

	
3

	
Piece

	
***

	
***

	  
	  	  	  	
800x320

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
630x400

	
0

	
Piece

	
***

	
***

	  
	  	  	  	
630x250

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
500x250

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
500x200

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
400x400

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
400x200

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
320x200

	
1

	
Piece

	
***

	
***

	  
	  	  	
Sealed bisect multi-vane regulating valve

	  	  	  	  	  	
Yingda


	  	  	  	
1250x500

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
1100x500

	
3

	
Piece

	
***

	
***

	  
	  	  	  	
1000x500

	
10

	
Piece

	
***

	
***

	  
	  	  	  	
1000x400

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
1000x320

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
900x400

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
900x250

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
800x500

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
800x400

	
11

	
Piece

	
***

	
***

	  











	
Cleanroom retaining

	
26/90

	
2009-6-19











  





  











  



















Quotation sheet of retaining project








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	  	  	
800x360

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
800x320

	
11

	
Piece

	
***

	
***

	  
	  	  	  	
800x250

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
700x400

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
700x320

	
3

	
Piece

	
***

	
***

	  
	  	  	  	
630x400

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
630x320

	
9

	
Piece

	
***

	
***

	  
	  	  	  	
630x250

	
3

	
Piece

	
***

	
***

	  
	  	  	  	
550x320

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
500x320

	
3

	
Piece

	
***

	
***

	  
	  	  	  	
500x250

	
14

	
Piece

	
***

	
***

	  
	  	  	  	
400x400

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
400x320

	
5

	
Piece

	
***

	
***

	  
	  	  	  	
400x250

	
8

	
Piece

	
***

	
***

	  
	  	  	  	
400x200

	
5

	
Piece

	
***

	
***

	  
	  	  	  	
320x400

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
320x320

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
320x200

	
12

	
Piece

	
***

	
***

	  
	  	  	  	
320x160

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
250x200

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
250x160

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
200x200

	
1

	
Piece

	
***

	
***

	  
	  	  	
Bisect multi-vane regulating valve

	  	  	  	  	  	
Yingda


	  	  	  	
200x200

	
37

	
Piece

	
***

	
***

	  
	  	  	  	
320x200

	
243

	
Piece

	
***

	
***

	  
	  	  	  	
400x200

	
90

	
Piece

	
***

	
***

	  











	
Cleanroom retaining

	
27/90

	
2009-6-19











  





  











  



















Quotation sheet of retaining project








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	  	  	
500x200

	
30

	
Piece

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  
	
Seventh.

	
Air opening

	  	  	  	  	  	  	  
	  	  	
Aluminum monolayer shutter tuyere

	  	  	  	  	  	
Yingda


	  	  	
Air distribution quantity regulating valve

	
200x200

	
12

	
Piece

	
***

	
***

	  
	  	  	  	
250x250

	
8

	
Piece

	
***

	
***

	  
	  	  	  	
300x300

	
16

	
Piece

	
***

	
***

	  
	  	  	  	
400x400

	
21

	
Piece

	
***

	
***

	  
	  	  	  	
500x500

	
7

	
Piece

	
***

	
***

	  
	  	  	  	
800x600

	
4

	
Piece

	
***

	
***

	  
	  	  	
Aluminum monolayer shutter tuyere

	  	  	  	  	  	
Yingda


	  	  	
The filtration net of the thick result

	
600x300

	
7

	
Piece

	
***

	
***

	  
	  	  	  	
800x300

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
900x300

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
1000x300

	
16

	
Piece

	
***

	
***

	  
	  	  	  	
1300x300

	
34

	
Piece

	
***

	
***

	  
	  	  	
Monolayer shutter tuyere (explosion-proof type )

	  	  	  	  	  	
Yingda


	  	  	
Air distribution quantity regulating valve

	
400x200

	
6

	
Piece

	
***

	
***

	  
	  	  	  	
400x300

	
6

	
Piece

	
***

	
***

	  
	  	  	
Orientation adjustable diffuser


 

	  	  	  	  	  	
Yingda


	  	  	  	
FDK3030 (300x300)

	
12

	
Piece

	
***

	
***

	  
	  	  	  	
FDK4040 (400x400)

	
133

	
Piece

	
***

	
***

	  
	  	  	  	
FDK5040 (500x500)

	
17

	
Piece

	
***

	
***

	  
	  	  	
Fan coil return air plenum chamber

	  	  	  	  	  	
Suntec


	  	  	  	  	
63

	
Piece

	
***

	
***

	  
	  	  	
Return air unit plenum chamber

	  	  	  	  	  	
Suntec













	
Cleanroom retaining

	
28/90

	
2009-6-19











  





  











  



















Quotation sheet of retaining project








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	  	  	
Latrolet size 320x200

	
253

	
Piece

	
***

	
***

	
(Used for return

air wall)


	  	  	
Aluminum fixed louvre

	  	  	  	  	  	
Yingda


	  	  	  	
2400x600

	
3

	
Piece

	
***

	
***

	  
	  	  	  	
2200x600

	
10

	
Piece

	
***

	
***

	  
	  	  	  	
2000x500

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
1800x400

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
1400x500

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
1250x600

	
5

	
Piece

	
***

	
***

	  
	  	  	  	
1200x500

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
1000x600

	
22

	
Piece

	
***

	
***

	  
	  	  	  	
1000x500

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
600x500

	
4

	
Piece

	
***

	
***

	  
	  	  	
Efficient incubation air outlet

	  	  	  	  	  	
AAF


	  	  	
With regulating valve, fluid bath sealing and leakage test, pressure differential detection interface, and efficient filter with the filter efficiency H14

	
RFM-1000, rated air flowrate 500m3/h

	
31

	
Piece

	
***

	
***

	
AAF


	  	  	
RFM-1000, rated air flowrate 1000m3/h

	
75

	
Piece

	
***

	
***

	
AAF


	  	  	
RFM-1250, rated air flowrate 1250m3/h

	
44

	
Piece

	
***

	
***

	
AAF


	  	  	
RFM-1500, rated air flowrate 1500m3/h

	
138

	
Piece

	
***

	
***

	
AAF


	  	  	
RFM-2000, rated air flowrate 2000m3/h

	
67

	
Piece

	
***

	
***

	
AAF


	  	  	  	  	  	  	  	  	  
	  	  	
Equipment stainless steel exhaust hood

	  	  	  	  	  	  
	  	  	  	
D=1000x500/d=500x250

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
D=800x600/d=400x250

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
D=600x600/d=250x200

	
2

	
Piece

	
***

	
***

	  
	  	  	  	
D=600x400/d=320x200

	
1

	
Piece

	
***

	
***

	  
	  	  	  	
D=500x500/d=250x250

	
2

	
Piece

	
***

	
***

	  











	
Cleanroom retaining

	
29/90

	
2009-6-19











  





  











  



















Quotation sheet of retaining project








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	  	  	
D=250x250/d=160x160

	
1

	
piece

	
***

	
***

	  
	  	  	
Ceiling air diffuser (with air regulation)

	  	  	  	  	  	
Yingda


	  	  	  	
Valve pit 120x120

	
28

	
Piece

	
***

	
***

	  
	  	  	  	
Valve pit 180x180

	
76

	
Piece

	
***

	
***

	  
	  	  	  	
Valve pit 240x240

	
120

	
Piece

	
***

	
***

	  
	  	  	  	
Valve pit 300x300

	
34

	
Piece

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  
	  	
Subtotal

	  	  	  	  	  	
***

	  
	  	  	  	  	  	  	  	  	  
	  	
Subtotal 1

	  	  	  	  	  	
***

	  
	  	
Installation cost and management cost

	  	  	
15%

	  	  	
***

	  
	  	
Subtotal 2

	  	  	  	  	  	
***

	  
	  	
Tax

	  	  	
33%

	  	  	
***

	  
	  	
Total

	  	  	  	  	  	
***

	  
	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  



















	
Cleanroom retaining

	
30/90

	
2009-6-19











  





  











  



















Quotation sheet of fire protection and smoke evacuation system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	
First.

	
Fire protection and smoke evacuation equipments

	  	  	  	  	  	  	  
	
 


1

	
PY11 PY21 PY31

	
Low noise fire protection and smoke evacuation centrifugal air blower

	
Air quantity: 13500m3/h, total pressure:


800pa, rpm: 952rpm,motor power: 5.5kw.

	
 


3

	
 


Piece

	
***

	
***

	  
	
 


2

	
PY41 PY71

	
Low noise fire protection and smoke evacuation centrifugal air blower

	
Air quantity: 18000m3/h, total pressure:


1000pa, rpm: 978rpm,motor power: 11kw.

	
2

	  	
***

	
***

	  
	  	  	  	  	  	  	  	  	  
	
Second.

	
Air duct accessory

	  	  	  	  	  	  	  
	  	  	
Zinc coated steel air duct

	  	  	  	  	  	  
	  	  	  	
Δ=1.0mm

	
725

	
m2

	
***

	
***

	  
	  	  	  	
Δ=0.75mm

	
773

	
m2

	
***

	
***

	  
	  	  	
Sofe fabrie joining

	  	
100

	
m2

	
***

	
***

	  
	  	  	
Support of air duct

	  	
1498

	
m2

	
***

	
***

	  
	  	  	
Universal port of wind

	  	  	  	  	  	  
	  	  	  	  	
20

	
Piece

	
***

	
***

	  
	
Third.

	
Valve

	  	  	  	  	  	  	  
	  	  	
Fire protection and smoke evacuation valve (normal close, 280°C, with signal access point)

	  	  	  	  	
Yingda


	  	  	  	
630x250

	
8

	
Piece

	
***

	
***

	  
	  	  	  	
630x320

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
800x320

	
4

	
Piece

	
***

	
***

	  
	  	  	  	
800x400

	
3

	
Piece

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  
	
Fourth.

	
Tuyere

	  	  	  	  	  	  	  
	  	  	
Leafiness exhaust port (normal close )

	  	  	  	  	  	
Yingda


	  	  	  	
500x500

	
11

	
Piece

	
***

	
***

	  
	  	  	
Plate-type exhaust port (normal close )

	  	  	  	  	  	
Yingda













	
Fire protection and smoke evacuation

	
31/90

	
2009-6-19











  





  











  



















Quotation sheet of fire protection and smoke evacuation system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Equipment No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	  	  	
630x630

	
4

	  	
Piece

	
***

	  
	  	  	
Louvre

	  	  	  	  	  	
Yingda


	  	  	  	
1250x600

	
5

	  	
Piece

	
***

	  
	  	  	  	  	  	  	  	  	  
	  	
Subtotal

	  	  	  	  	  	
***

	  
	  	  	  	  	  	  	  	  	  
	  	
Subtotal 1

	  	  	  	  	  	
***

	  
	  	
Accessories

	  	  	
3%

	  	  	
***

	  
	  	
Installation cost and management cost

	  	  	
15%

	  	  	
***

	  
	  	
Subtotal 2

	  	  	  	  	  	
***

	  
	  	
Tax

	  	  	
4.33%

	  	  	
***

	  
	  	
Total

	  	  	  	  	  	
***

	  
	  	  	  	  	  	  	  	  	  



















	
Fire protection and smoke evacuation

	
32/90

	
2009-6-19











  





  











  



















Quotation sheet of technology chilled water system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	
First.

	
Technology chilled water system

	  	  	  	  	  	  
	
1

	
Stainless steel seamless steel pipe

	  	  	  	  	  	  
	  	  	
DN250

	
60

	
m

	  	
***

	  
	  	  	
DN200

	
66

	
m

	
***

	
***

	  
	  	  	
DN125

	
24

	
m

	
***

	
***

	  
	  	  	
DN100

	
72

	
m

	
***

	
***

	  
	  	  	
DN80

	
12

	
m

	
***

	
***

	  
	  	  	
DN65

	
6

	
m

	
***

	
***

	  
	  	  	
DN50

	
24

	
m

	
***

	
***

	  
	  	  	
DN40

	
12

	
m

	
***

	
***

	  
	  	  	
DN15

	
12

	
m

	
***

	
***

	  
	
2

	
Stainless steel bend

	  	  	  	  	  	  
	  	  	
DN250

	
30

	
Piece

	
***

	
***

	  
	  	  	
DN200

	
15

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
12

	
Piece

	
***

	
***

	  
	  	  	
DN100

	
16

	
Piece

	
***

	
***

	  
	  	  	
DN80

	
8

	
Piece

	
***

	
***

	  
	  	  	
DN50

	
8

	
Piece

	
***

	
***

	  











	
Technology chilled water part

	
33/90

	
2009-6-19











  





  











  



















Quotation sheet of technology chilled water system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	
First.

	
Technology chilled water system

	  	  	  	  	  	  
	  	  	
DN40

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN15

	
20

	
Piece

	
***

	
***

	  
	
3

	
Stainless steel tee

	  	  	  	  	  	  
	  	  	
DN250x200

	
10

	
Piece

	
***

	
***

	  
	  	  	
DN250x150

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN200x200

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN100x50

	
4

	
Piece

	
***

	
***

	  
	
4

	
Stainless steel reducer

	  	  	  	  	  	  
	  	  	
DN250x100

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN250x200

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN200x150

	
8

	
Piece

	
***

	
***

	  
	  	  	
DN200x125

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN125x100

	
10

	
Piece

	
***

	
***

	  
	  	  	
DN100x80

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN80x65

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN50x40

	
2

	
Piece

	
***

	
***

	  
	
5

	
Stainless steel butterfly valve

	  	  	  	  	  	  











	
Technology chilled water part

	
34/90

	
2009-6-19











  





  











  



















Quotation sheet of technology chilled water system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	
First.

	
Technology chilled water system

	  	  	  	  	  	  
	  	  	
DN250

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN200

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN150

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
8

	
Piece

	
***

	
***

	  
	
6

	
Stainless steel Y type filter

	  	  	  	
***

	
***

	  
	  	  	
DN200

	
3

	
Piece

	
***

	
***

	  
	
7

	
Stainless steel check valve

	  	  	  	
***

	
***

	  
	  	  	
DN200

	
3

	
Piece

	
***

	
***

	  
	
8

	
Stainless steel soft connecting

	  	  	  	
***

	
***

	  
	  	  	
DN200

	
8

	
Piece

	
***

	
***

	  
	
9

	
Stainless steel automatic air valve

	  	  	  	
***

	
***

	  
	  	  	
DN20

	
10

	
Piece

	
***

	
***

	  
	
10

	
Pipe fitting

	  	
1

	
Sets.

	
***

	
***

	  
	
11

	
Centrifugal glass wool insulation

	
D=60mm, 40mm

	
14

	
m3

	
***

	
***

	
Cornposite alumininm foil maskant outpackage outside


	
12

	
Thermometer

	  	
8

	
Piece

	
***

	
***

	
Tianchuan


	
13

	
Pressure gauge

	  	
14

	
Piece

	
***

	
***

	
Tianchuan


	
14

	
Stainless steel flange

	  	  	  	  	  	  











	
Technology chilled water part

	
35/90

	
2009-6-19











  





  











  



















Quotation sheet of technology chilled water system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	
First

	
Technology chilled water system

	  	  	  	  	  	  
	  	  	
DN250

	
8

	
Piece

	
***

	
***

	  
	  	  	
DN200

	
48

	
Piece

	
***

	
***

	  
	  	  	
DN150

	
16

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
24

	
Piece

	
***

	
***

	  
	  	  	
DN100

	
10

	
Piece

	
***

	
***

	  
	  	  	
DN80

	
16

	
Piece

	
***

	
***

	  
	  	  	
DN65

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN50

	
6

	
Piece

	
***

	
***

	  
	  	
Subtotal 1

	  	  	  	  	
***

	  
	  	
Accessories

	  	
5%

	  	  	
***

	  
	  	
Installation cost and management cost

	  	
12%

	  	  	
***

	  
	  	
Subtotal 2

	  	  	  	  	
***

	  
	  	
Tax

	  	
4.33%

	  	  	
***

	  
	  	
Total

	  	  	  	  	
***

	  
	  	  	  	  	  	  	  	  
	
Note:

	  	  	  	  	  	  
	
Technology chilled water pipes only include the visible in the plant and integrated drawing, and exclude the parts entering into the cleanroom.

	  	  	  
	  	  	  	  	  	  	  	  



















	
Technology chilled water part

	
36/90

	
2009-6-19











  





  











  



















Quotation sheet of technology chilled water system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	
First

	
Technology chilled water system

	  	  	  	  	  	  





Note: technology chilled water re-design and quotation








	
Technology chilled water part

	
37/90

	
2009-6-19











  





  











  



















Quotation of circulating water system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	
First.

	
Circulating water system

	  	  	  	  	  	  
	
1

	
Seamless steel pipe

	  	  	  	  	  	  
	  	  	
DN400

	
28

	
m

	  	
***

	  
	  	  	
DN300

	
30

	
m

	
***

	
***

	  
	  	  	
DN250

	
78

	
m

	
***

	
***

	  
	  	  	
DN200

	
15

	
m

	
***

	
***

	  
	
2

	
Bend

	  	  	  	  	  	  
	  	  	
DN400

	
8

	
Piece

	
***

	
***

	  
	  	  	
DN300

	
12

	
Piece

	
***

	
***

	  
	  	  	
DN250

	
28

	
Piece

	
***

	
***

	  
	
3

	
Tee

	  	  	  	  	  	  
	  	  	
DN400/200

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN400/250

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN400/300

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN300/300

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN300/250

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN250/250

	
2

	
Piece

	
***

	
***

	  
	
4

	
Reducer

	  	  	  	  	  	  











	
Circulating water part

	
38/90

	
2009-6-19











  





  











  



















Quotation of circulating water system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	
First.

	
Circulating water system

	  	  	  	  	  	  
	  	  	
DN300/250

	
9

	
Piece

	
***

	
***

	  
	
2

	
Butterfly valve

	  	  	  	  	  	  
	  	  	
DN300

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN250

	
14

	
Piece

	
***

	
***

	  
	  	  	
DN200

	
4

	
Piece

	
***

	
***

	  
	
3

	
Y TYPE FILTER

	  	  	  	  	  	  
	  	  	
DN300

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN250

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN200

	
2

	
Piece

	
***

	
***

	  
	
4

	
Ball valve

	  	  	  	  	  	  
	  	  	
DN20

	
16

	
Piece

	
***

	
***

	  
	
5

	
Soft connecting

	  	  	  	  	  	  
	  	  	
DN250

	
10

	
Piece

	
***

	
***

	  
	  	  	
DN200

	
4

	
Piece

	
***

	
***

	  
	
6

	
Check valve

	  	  	  	  	  	  
	  	  	
DN250

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN200

	
2

	
Piece

	
***

	
***

	  











	
Circulating water part

	
39/90

	
2009-6-19











  





  











  



















Quotation of circulating water system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	
First.

	
Circulating water system

	  	  	  	  	  	  
	
7

	
Pipe fitting

	  	
1

	
Sets.

	
***

	
***

	  
	
8

	
Water pump

	
Q=187m3/h,H=24m

	
2

	
Piece

	
***

	
***

	
Grundfos


	  	  	
Q=280m3/h,H=24m

	
2

	
Piece

	
***

	
***

	  
	
9

	
Thermometer

	  	
10

	
Piece

	
***

	
***

	
Tianchuan


	
10

	
Pressure gauge

	  	
10

	
Piece

	
***

	
***

	
Tianchuan


	
11

	
Flange

	
DN400

	
12

	
Piece

	
***

	
***

	  
	  	  	
DN300

	
16

	
Piece

	
***

	
***

	  
	  	  	
DN250

	
76

	
Piece

	
***

	
***

	  
	  	  	
DN200

	
36

	
Piece

	
***

	
***

	  
	  	  	  	  	  	  	  	  
	  	
Subtotal 1

	  	  	  	  	
***

	  
	  	
Accessories

	  	
5%

	  	  	
***

	  
	  	
Installation cost and management cost

	  	
12%

	  	  	
***

	  
	  	
Subtotal 2

	  	  	  	  	
***

	  
	  	
Tax

	  	
4.33%

	  	  	
***

	  
	  	
Total

	  	  	  	  	
***

	  
	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  



















	
Circulating water part

	
40/90

	
2009-6-19











  





  











  



















Quotation of circulating water system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	
First.

	
Circulating water system

	  	  	  	  	  	  
	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  





Note: due to the change of cooling tower. Circulating water pump. And technology chilled water, chilled water pipe needs re-quote.








	
Circulating water part

	
41/90

	
2009-6-19











  





  











  



















Quotation sheet of technology steam piping system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Technology steam piping system

	  	  	  	  	  	  
	
1

	
Seamless steel pipe

	  	  	  	  	  	  
	  	  	
DN150

	
22

	
m

	  	
***

	  
	  	  	
DN125

	
7

	
m

	
***

	
***

	  
	  	  	
DN100

	
7

	
m

	
***

	
***

	  
	  	  	
DN65

	
35

	
m

	
***

	
***

	  
	  	  	
DN50

	
38

	
m

	
***

	
***

	  
	  	  	
DN32

	
4

	
m

	
***

	
***

	  
	  	  	
DN25

	
21

	
m

	
***

	
***

	  
	  	  	
DN20

	
112

	
m

	
***

	
***

	  
	
2

	
Bend

	  	  	  	  	  	  
	  	  	
DN150

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN100

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN65

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN50

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN40

	
5

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
15

	
Piece

	
***

	
***

	  











	
Technology steam piping system

	
42/90

	
2009-6-19











  





  











  



















Quotation sheet of technology steam piping system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Technology steam piping system

	  	  	  	  	  	  
	  	  	
DN20

	
17

	
Piece

	
***

	
***

	  
	
3

	
Reducer

	  	  	  	  	  	  
	  	  	
DN150/125

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN125/100

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN100/65

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN65/50

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN50/20

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN40/20

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN32/20

	
1

	
Piece

	
***

	
***

	  
	
4

	
Tee

	  	  	  	  	  	  
	  	  	
DN150/100

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN100/40

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN65/32

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN65/20

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN50/20

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN40/25

	
1

	
Piece

	
***

	
***

	  











	
Technology steam piping system

	
43/90

	
2009-6-19











  





  











  



















Quotation sheet of technology steam piping system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Technology steam piping system

	  	  	  	  	  	  
	  	  	
DN32/20

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
6

	
Piece

	
***

	
***

	  
	
5

	
Flange

	  	  	  	  	  	  
	  	  	
DN150

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
8

	
Piece

	
***

	
***

	  
	  	  	
DN100

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN80

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
26

	
Piece

	
***

	
***

	  
	  	  	
DN20

	
20

	
Piece

	
***

	
***

	  
	
6

	
Cut-off valve

	  	  	  	  	  	  
	  	  	
DN150

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN100

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
10

	
Piece

	
***

	
***

	  
	  	  	
DN20

	
10

	
Piece

	
***

	
***

	  
	
7

	
Y type filter

	  	  	  	  	  	  
	  	  	
DN125

	
1

	
Piece

	
***

	
***

	  











	
Technology steam piping system

	
44/90

	
2009-6-19











  





  











  



















Quotation sheet of technology steam piping system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Technology steam piping system

	  	  	  	  	  	  
	
8

	
Drain valve

	  	  	  	  	  	  
	  	  	
DN25

	
3

	
Piece

	
***

	
***

	  
	
9

	
Safety valve

	  	  	  	  	  	  
	  	  	
DN80

	
1

	
Piece

	
***

	
***

	  
	
10

	
Pressure reducing valve

	  	  	  	  	  	
Spiraxsarco


	  	  	
DN100

	
1

	
Piece

	
***

	
***

	  
	
11

	
Gas-liquid separator

	  	  	  	  	  	  
	  	  	
DN150

	
1

	
Piece

	
***

	
***

	  
	
12

	
Pipe fitting

	  	
1

	
Sets.

	
***

	
***

	  
	
13

	
Centrifugal glass wool insulation

	
D=50mm

	
4.5

	
m3

	
***

	
***

	
Huamei


	
14

	
Iron sheet outside protection

	
D=0.5mm

	
120

	
m2

	
***

	
***

	  
	  	
Water room stainless steel set pipe insulation

	  	
50

	
m

	
***

	
***

	  
	
15

	
Pressure gauge

	  	
2

	
Piece

	
***

	
***

	
Tianchuan


	  	  	  	  	  	  	  	  
	  	
Subtotal 1

	  	  	  	  	
***

	  
	  	
Accessories

	  	
3%

	  	  	
***

	  
	  	
Installation cost and management cost

	  	
15%

	  	  	
***

	  











	
Technology steam piping system

	
45/90

	
2009-6-19











  





  











  








 


 










Quotation sheet of technology steam piping system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
 No.

	
Name

	
Model and specification 

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Technology steam piping system

	  	  	  	  	  	  
	  	
Subtotal 2

	  	  	  	  	
***

	  
	  	
Tax

	  	
4.33%

	  	  	
***

	  
	  	
Total

	  	  	  	  	
***

	  
	
Note:

	  	  	  	  	  	  	  
	
Technology steam piping pipe can be seen in the integrated drawing, and can not be seen in the cleanroom.

	  	  	  	  
	  	  	  	  	  	  	  	  





 





 



	
Technology steam piping system

	
46/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning water pipeline system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification 

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning water pipeline system

	  	  	  	  	  	  
	
1

	
Seamless steel pipe

	  	  	  	  	  	  
	  	  	
DN250

	
250

	
m

	  	
***

	  
	  	  	
DN200

	
60

	
m

	
***

	
***

	  
	  	  	
DN150

	
220

	
m

	
***

	
***

	  
	  	  	
DN125

	
170

	
m

	
***

	
***

	  
	  	  	
DN100

	
300

	
m

	
***

	
***

	  
	  	  	
DN80

	
254

	
m

	
***

	
***

	  
	  	  	
DN65

	
320

	
m

	
***

	
***

	  
	  	  	
DN50

	
191

	
m

	
***

	
***

	  
	  	  	
DN40

	
115

	
m

	
***

	
***

	  
	  	  	
DN32

	
250

	
m

	
***

	
***

	  
	  	  	
DN15

	
68

	
m

	
***

	
***

	  
	
2

	
Galvanized steel pipe

	  	  	  	  	  	  
	  	  	
DN40

	
500

	
m

	
***

	
***

	  
	  	  	
DN32

	
745

	
m

	
***

	
***

	  
	  	  	
DN25

	
240

	
m

	
***

	
***

	  
	  	  	
DN20

	
78

	
m

	
***

	
***

	  











	
Air-conditioning water system

	
47/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning water pipeline system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification 

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning water pipeline system

	  	  	  	  	  	  
	  	  	
DN15

	
55

	
m

	
***

	
***

	  
	
3

	
Bend

	  	  	  	  	  	  
	  	  	
DN250

	
14

	
Piece

	
***

	
***

	  
	  	  	
DN200

	
16

	
Piece

	
***

	
***

	  
	  	  	
DN150

	
18

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
8

	
Piece

	
***

	
***

	  
	  	  	
DN100

	
8

	
Piece

	
***

	
***

	  
	  	  	
DN80

	
12

	
Piece

	
***

	
***

	  
	  	  	
DN65

	
22

	
Piece

	
***

	
***

	  
	  	  	
DN50

	
37

	
Piece

	
***

	
***

	  
	  	  	
DN40

	
16

	
Piece

	
***

	
***

	  
	  	  	
DN32

	
45

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
18

	
Piece

	
***

	
***

	  
	  	  	
DN20

	
25

	
Piece

	
***

	
***

	  
	  	  	
DN15

	
80

	
Piece

	
***

	
***

	  
	
4

	
Reducer

	  	  	  	  	  	  
	  	  	
DN100/80

	
4

	
Piece

	
***

	
***

	  











	
Air-conditioning water system

	
48/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning water pipeline system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification 

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning water pipeline system

	  	  	  	  	  	  
	  	  	
DN80/65

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN65/50

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN65/40

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN50/40

	
4

	
Piece

	
***

	
***

	  
	
5

	
Tee

	  	  	  	  	  	  
	  	  	
DN250/200

	
18

	
Piece

	
***

	
***

	  
	  	  	
DN250/150

	
8

	
Piece

	
***

	
***

	  
	  	  	
DN250/100

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN250/50

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN150/80

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN150/50

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN150/40

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN150/32

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN125/100

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN125/80

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN125/65

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN125/50

	
4

	
Piece

	
***

	
***

	  











	
Air-conditioning water system

	
49/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning water pipeline system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification 

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning water pipeline system

	  	  	  	  	  	  
	  	  	
DN125/40

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN100/80

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN100/65

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN100/40

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN100/32

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN80/65

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN80/50

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN80/40

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN80/32

	
8

	
Piece

	
***

	
***

	  
	  	  	
DN80/25

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN80/20

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN65/20

	
34

	
Piece

	
***

	
***

	  
	  	  	
DN50/50

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN50/32

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN50/20

	
12

	
Piece

	
***

	
***

	  
	  	  	
DN40/20

	
27

	
Piece

	
***

	
***

	  
	  	  	
DN32/25

	
2

	
Piece

	
***

	
***

	  











	
Air-conditioning water system

	
50/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning water pipeline system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification 

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning water pipeline system

	  	  	  	  	  	  
	  	  	
DN32/20

	
32

	
Piece

	
***

	
***

	  
	  	  	
DN25/20

	
6

	
Piece

	
***

	
***

	  
	
6

	
Butterfly valve

	  	  	  	  	  	  
	  	  	
DN250

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN200

	
14

	
Piece

	
***

	
***

	  
	  	  	
DN150

	
7

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN100

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN80

	
7

	
Piece

	
***

	
***

	  
	
7

	
Cut-off valve

	  	  	  	  	  	  
	  	  	
DN250

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN100

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN80

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN50

	
9

	
Piece

	
***

	
***

	  
	  	  	
DN40

	
14

	
Piece

	
***

	
***

	  
	  	  	
DN32

	
16

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
5

	
Piece

	
***

	
***

	  





 




	
Air-conditioning water system

	
51/90

	
2009-6-19









 




  





  











  














 


Quotation sheet of air-conditioning water pipeline system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification 

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning water pipeline system

	  	  	  	  	  	  
	  	  	
DN20

	
154

	
Piece

	
***

	
***

	  
	  	  	
DN15

	
66

	
Piece

	
***

	
***

	  
	
8

	
Y type filter

	  	  	  	  	  	  
	  	  	
DN200

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN80

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN65

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN50

	
5

	
Piece

	
***

	
***

	  
	  	  	
DN40

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN32

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
14

	
Piece

	
***

	
***

	  
	  	  	
DN20

	
40

	
Piece

	
***

	
***

	  
	  	  	
DN15

	
37

	
Piece

	
***

	
***

	  
	
9

	
Static balanced valve

	  	  	  	  	  	  
	  	  	
DN200

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN150

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN100

	
2

	
Piece

	
***

	
***

	  





 



	
Air-conditioning water system

	
52/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning water pipeline system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification 

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning water pipeline system

	  	  	  	  	  	  
	  	  	
DN80

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN65

	
5

	
Piece

	
***

	
***

	  
	  	  	
DN50

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN32

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN20

	
1

	
Piece

	
***

	
***

	  
	
10

	
Check valve

	  	  	  	
***

	
***

	  
	  	  	
DN200

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN150

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN50

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN32

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN20

	
16

	
Piece

	
***

	
***

	  
	  	  	
DN15

	
32

	
Piece

	
***

	
***

	  
	
11

	
Drain valve

	  	  	  	  	  	  
	  	  	
DN32

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
3

	
Piece

	
***

	
***

	  





 



	
Air-conditioning water system

	
53/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning water pipeline system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification 

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning water pipeline system

	  	  	  	  	  	  
	  	  	
DN20

	
17

	
Piece

	
***

	
***

	  
	  	  	
DN15

	
32

	
Piece

	
***

	
***

	  
	
12

	
Automatic air valve

	  	  	  	
***

	
***

	  
	  	  	
DN20

	
45

	
Piece

	
***

	
***

	  
	
13

	
Pipe fitting

	  	
1

	
Sets.

	
***

	
***

	  
	
14

	
Centrifugal glass wool insulation

	
D=70. 60. 50. 4

	
83

	
m3

	
***

	
***

	
Cornposite alumininm foil maskant outside/Huamei


	
15

	
Soft connecting joint

	  	  	  	
***

	
***

	  
	  	  	
DN200

	
14

	
Piece

	
***

	
***

	  
	  	  	
DN150

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
4

	
Piece

	
***

	
***

	  
	
16

	
Thermometer

	  	
8

	
Piece

	
***

	
***

	
Tianchuan


	
17

	
Pressure gauge

	  	
14

	
Piece

	
***

	
***

	
Tianchuan


	  	  	  	  	  	  	  	  
	  	
Subtotal 1

	  	  	  	  	
***

	  
	  	
Accessories

	  	
3%

	  	  	
***

	  
	  	
Installation cost and management cost

	  	
15%

	  	  	
***

	  
	  	
Subtotal 2

	  	  	  	  	
***

	  













 



	
Air-conditioning water system

	
54/90

	
2009-6-19














  





  











  














 


Quotation sheet of air-conditioning water pipeline system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning water pipeline system

	  	  	  	  	  	  
	  	
Tax

	  	
4.33%

	  	  	
***

	  
	  	
Total

	  	  	  	  	
***

	  
	  	  	  	  	  	  	  	  
	
Note:

	  	  	  	  	  	  	  
	
It just includes the pipeline in the drawing, that pipelines in the process of construction not seen in the drawing shall be added, and the quotation of electric control valve is in the automatic control part

	  	  
	  	  	  	  	  	  	  	  





 





 



	
Air-conditioning water system

	
55/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning steam piping system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning steam piping system

	  	  	  	  	  	  
	
1

	
Seamless steel tube

	  	  	  	  	  	  
	  	  	
DN150

	
122

	
m

	  	
***

	  
	  	  	
DN125

	
13

	
m

	
***

	
***

	  
	  	  	
DN100

	
16

	
m

	
***

	
***

	  
	  	  	
DN80

	
30

	
m

	
***

	
***

	  
	  	  	
DN65

	
24

	
m

	
***

	
***

	  
	  	  	
DN50

	
96

	
m

	
***

	
***

	  
	  	  	
DN40

	
90

	
m

	
***

	
***

	  
	  	  	
DN32

	
90

	
m

	
***

	
***

	  
	  	  	
DN25

	
192

	
m

	
***

	
***

	  
	  	  	
DN20

	
112

	
m

	
***

	
***

	  
	
2

	
Bend

	  	  	  	  	  	  
	  	  	
DN150

	
8

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN100

	
5

	
Piece

	
***

	
***

	  
	  	  	
DN80

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN65

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN50

	
14

	
Piece

	
***

	
***

	  











	
Air-conditioning steam piping system

	
56/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning steam piping system


 



	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	  	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning steam piping system

	  	  	  	  	  	  
	  	  	
DN40

	
48

	
Piece

	
***

	
***

	  
	  	  	
DN32

	
32

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
112

	
Piece

	
***

	
***

	  
	  	  	
DN20

	
82

	
Piece

	
***

	
***

	  
	
3

	
Reducer

	  	  	  	  	  	  
	  	  	
DN150/125

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN150/25

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN125/100

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN100/65

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN100/50

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN80/65

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN80/50

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN80/32

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN65/40

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN65/50

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN65/25

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN50/40

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN50/32

	
4

	
Piece

	
***

	
***

	  





 



	
Air-conditioning steam piping system

	
57/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning steam piping system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning steam piping system

	  	  	  	  	  	  
	  	  	
DN50/25

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN40/32

	
7

	
Piece

	
***

	
***

	  
	  	  	
DN40/25

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN32/25

	
10

	
Piece

	
***

	
***

	  
	  	  	
DN32/20

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN25/25

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN25/20

	
15

	
Piece

	
***

	
***

	  
	
4

	
Tee

	  	  	  	  	  	  
	  	  	
DN150/150

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN150/125

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN150/25

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN150/20

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN125/80

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN125/40

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN100/80

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN100/32

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN80/40

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN65/40

	
1

	
Piece

	
***

	
***

	  





 



	
Air-conditioning steam piping system

	
58/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning steam piping system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning steam piping system

	  	  	  	  	  	  
	  	  	
DN65/20

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN50/50

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN50/40

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN32/20

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN25/25

	
27

	
Piece

	
***

	
***

	  
	  	  	
DN20/20

	
20

	
Piece

	
***

	
***

	  
	
5

	
Flange

	  	  	  	  	  	  
	  	  	
DN150

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN125

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN80

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN50

	
8

	
Piece

	
***

	
***

	  
	  	  	
DN40

	
54

	
Piece

	
***

	
***

	  
	  	  	
DN32

	
36

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
120

	
Piece

	
***

	
***

	  
	  	  	
DN20

	
90

	
Piece

	
***

	
***

	  
	
6

	
Cut-off valve

	  	  	  	  	  	  
	  	  	
DN125

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN150

	
1

	
Piece

	
***

	
***

	  





 



	
Air-conditioning steam piping system

	
59/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning steam piping system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning steam piping system

	  	  	  	  	  	  
	  	  	
DN80

	
2

	
Piece

	
***

	
***

	  
	  	  	
DN50

	
4

	
Piece

	
***

	
***

	  
	  	  	
DN40

	
18

	
Piece

	
***

	
***

	  
	  	  	
DN32

	
13

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
40

	
Piece

	
***

	
***

	  
	  	  	
DN20

	
30

	
Piece

	
***

	
***

	  
	
7

	
Ytype filter

	  	  	  	  	  	  
	  	  	
DN50

	
1

	
Piece

	
***

	
***

	  
	  	  	
DN40

	
6

	
Piece

	
***

	
***

	  
	  	  	
DN32

	
3

	
Piece

	
***

	
***

	  
	  	  	
DN25

	
13

	
Piece

	
***

	
***

	  
	  	  	
DN20

	
10

	
Piece

	
***

	
***

	  
	
8

	
Water pipe accessories

	  	
1

	
Sets.

	
***

	
***

	  
	
9

	
Centrifugal glass wool insulation

	
D=50mm

	
15

	
m3

	
***

	
***

	
Cornposite alumininm foil maskant outside /Huamei


	  	
Galvanized steelcontainment vessel

	  	
380

	
m2

	
***

	
***

	  
	
10

	
Pressure gage

	  	
33

	
Piece

	
***

	
***

	
Tianchuan


	  	  	  	  	  	  	  	  
	  	
Subtotal 1

	  	  	  	  	
***

	  
	  	
Accessories

	  	
3%

	  	  	
***

	  





 



	
Air-conditioning steam piping system

	
60/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of air-conditioning steam piping system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Remark


	  	
Air-conditioning steam piping system

	  	  	  	  	  	  
	  	
Installation cost and management cost

	  	
15%

	  	  	
***

	  
	  	
Subtotal 2

	  	  	  	  	
***

	  
	  	
Tax

	  	
4.33%

	  	  	
***

	  
	  	
Total

	  	  	  	  	
***

	  
	  	  	  	  	  	  	  	  
	
Note:

	  	  	  	  	  	  	  
	
It just includes the pipeline in the drawing, that pipelines in the process of construction not seen in the drawing shall be added,and the quotation of electric control valve is in the automatic control part

	  	  	  
	  	  	  	  	  	  	  	  













 



	
Air-conditioning steam piping system

	
61/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of tap-water CWS system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Price difference

	
Remark


	  	
Tap-water CWS system 304

	  	
Former

	
Now

	  	  	
Former

	
Now

	  	  
	
1

	
Stainless steel sanitary tube

	  	  	  	  	  	  	  	  	  
	  	  	
DN50

	
78

	
78

	  	
***

	
***

	
***

	
***

	  
	  	  	
DN40

	
81

	
81

	
m

	
***

	
***

	
***

	
***

	  
	  	  	
DN32

	
84

	
84

	
m

	
***

	
***

	
***

	
***

	  
	  	  	
DN25

	
26

	
78

	
m

	
***

	
***

	
***

	
***

	  
	  	  	
DN15

	
189

	
295

	
m

	
***

	
***

	
***

	
***

	  
	
2

	
Stainless steel bend

	  	  	  	  	  	  	  	  	  
	  	  	
DN50

	
7

	
7

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN40

	
5

	
5

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN25

	
10

	
10

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN20

	
5

	
38

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN15

	
41

	
63

	
Piece

	
***

	
***

	
***

	
***

	  
	
3

	
Stainless steel reducer

	  	  	  	  	  	  	  	  	  
	  	  	
DN50/40

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN50/25

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN40/15

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN25/15

	
2

	
8

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN20/15

	
4

	
16

	
Piece

	
***

	
***

	
***

	
***

	  
	
4

	
Stainless steel tee

	  	  	  	  	  	  	  	  	  
	  	  	
DN50/40

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN50/25

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	  





 




	
Tap-water CWS system

	
62/90

	
2009-6-19









 




  





  











  






 










Quotation sheet of tap-water CWS system


 



	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and


specification

	
Quantity

	
Unit

	
Unit


price

	
Total

	
Price


difference

	
Remark


	  	
Tap-water CWS system 304

	  	
Former

	
Now

	  	  	
Former

	
Now

	  	  
	  	  	
DN50/20

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN50/15

	
7

	
7

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN40/25

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN40/15

	
10

	
10

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN25/25

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN25/15

	
15

	
15

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN25/20

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN20/20

	
1

	
1

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN20/25

	
3

	
3

	
Piece

	
***

	
***

	
***

	
***

	  
	
5

	
stainless steel all-inclusive clamp ball valve

	  	  	  	  	  	  	  	  	  
	  	  	
DN50

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN20

	
2

	
2

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	
DN15

	
45

	
57

	
Piece

	
***

	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	
Former


quotation

	
Now


quotation

	
Price


difference

	  
	  	  	  	  	  	  	  	  	  	  	  
	  	
Subtotal 1

	  	  	  	  	  	
***

	
***

	
***

	  
	  	
Accessories

	  	  	
3%

	  	  	
***

	
***

	
***

	  
	  	
Installation cost and management cost

	  	  	
15%

	  	  	
***

	
***

	
***

	  
	  	
Subtotal 2

	  	  	  	  	  	
***

	
***

	
***

	  
	  	
Tax

	  	  	
4.33%

	  	  	
***

	
***

	
***

	  





 



	
Tap-water CWS system

	
63/90

	
2009-6-19







 




  





  











  



















Quotation sheet of tap-water CWS system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and


specification

	
Quantity

	
Unit

	
Unit 


price

	
Total

	
Price


difference

	
Remark


	  	
Tap-water CWS system 304

	  	
Former

	
Now

	  	  	
Former

	
Now

	  	  
	  	
Total

	  	  	  	  	  	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  
	
Note:

	  	  	  	  	  	  	  	  	  	  
	
Water pipe can be seen in the package drawing only, the part into the clean room is not included.

	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  	  	  





 



	
Tap-water CWS system

	
64/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of fire services pipe system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Price


difference

	
Remark


	  	
Fire services pipe system

	  	
Former

	
Now

	  	  	
Former

	
Now

	  	  
	
1

	
Galvanized welded steel pipe

	  	  	  	  	  	  	  	  	  
	  	  	
DN65

	
244

	
m

	  	
***

	
***

	
***

	
***

	  
	
2

	
Bend

	  	  	  	  	  	  	  	  	  
	  	  	
DN65

	
106

	
Piece

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
Fire hydrant of cleanroom

	  	
27

	
Piece

	
***

	
***

	
***

	
***

	
***

	
Changing the fire box material from aluminum and glass to stainless steel


	  	
Including the fire hydrant with 25cm fire hose, C19 water gun, pump starting button, and three MF/ABC4 dry-chemical fire extinguisher.

	  	  	  	  
	  	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	
Former quotation

	
Now


quotation

	
Price difference

	  
	  	
Subtotal 1

	  	  	  	  	  	
***

	
***

	
***

	  
	  	
Accessories

	  	
3%

	  	  	  	
***

	
***

	
***

	  
	  	
Installation cost and management cost

	  	
15%

	  	  	  	
***

	
***

	
***

	  
	  	
Subtotal 2

	  	  	  	  	  	
***

	
***

	
***

	  
	  	
Tax

	  	
4.33%

	  	  	  	
***

	
***

	
***

	  
	  	
Total

	  	  	  	  	  	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  
	
Note:

	  	  	  	  	  	  	  	  	  	  
	
Pipeline just includes the pipelines of cleanroom, Branch pipe valve is reserved by proprietor,and our company calculates from the branch pipe valve.

	  	  	  	  	  
	  	  	  	  	  	  	  	  	  	  	  











	
Fire services pipe system

	
65/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of fire services pipe system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Quantity

	
Unit

	
Unit price

	
Total

	
Price difference

	
Remark


	  	
Fire services pipe system

	  	
Former

	
Now

	  	  	
Former

	
Now

	  	  





Note: the words in yellow are the addition part.


 



	
Fire services pipe system

	
66/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of electrical system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
First

	
Lighting part

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
1

	
Double tube fluorescent lamp

	
2*28 W

	
Set

	
100

	
100

	
***

	
***

	
***

	
***

	
***

	
T5 tube


	
2

	
Double tube fluorescent lamp(with emergency)

	
2*28 W

	
Set

	
28

	
28

	
***

	
***

	
***

	
***

	
***

	
T5tube


	
3

	
Three-tube fluorescent lamp

	
3*18 W

	
Set

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
T5tube


	
4

	
Three-tube fluorescent lamp (with emergency)

	
3*28 W

	
Set

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
T5tube


	
5

	
Double tube clean fluorescent lamp

	
2*28 W

	
Set

	
245

	  	
***

	
***

	
***

	
***

	
***

	
T5tube


	
6

	
Double tube clean fluorescent lamp(emergency)

	
2*28 W

	
Set

	
183

	
183

	
***

	
***

	
***

	
***

	
***

	
T5tube


	
7

	
Wether fluorescent lamp

	
2*28 W

	
Set

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
T5tube


	
8

	
Boom fluorescent lamp

	
2*28 W

	
Set

	
39

	
39

	
***

	
***

	
***

	
***

	
***

	
T5tube


	
9

	
Double tube explosion-proof fluorescent lamp

	
2*28 W

	
Set

	
9

	
9

	
***

	
***

	
***

	
***

	
***

	
Xinliming


	
10

	
Three-tube clean fluorescent lamp

	
3*28 W

	
Set

	
260

	
260

	
***

	
***

	
***

	
***

	
***

	
T5tube


	
11

	
Three-tube clean fluorescent lamp (emergency)

	
3*28 W

	
Set

	
102

	
102

	
***

	
***

	
***

	
***

	
***

	
T5tube


	
12

	
Four-tube clean fluorescent lamp

	
4*28 W

	
Set

	
122

	
122

	
***

	
***

	
***

	
***

	
***

	
T5tube


	
13

	
Four-tube clean fluorescent lamp (emergency)

	
4*28 W

	
Set

	
42

	
42

	
***

	
***

	
***

	
***

	
***

	
T5tube


	
14

	
Circular fluorescent lamp

	
1*32 W

	
Set

	
26

	
26

	
***

	
***

	
***

	
***

	
***

	
Qiaoguang


	
15

	
Three-tube grille lamp

	
3*14 W

	
Set

	
56

	
56

	
***

	
***

	
***

	
***

	
***

	
Qiaoguang


	
16

	
Standard dome lighting factory lamp

	
1*100 W

	
Set

	
86

	
86

	
***

	
***

	
***

	
***

	
***

	
Qiaoguang


	
17

	
Automatic sensor light

	
2*10 W

	
Set

	
26

	
26

	
***

	
***

	
***

	
***

	
***

	
Qiaoguang


	
18

	
Factory energy saving lamp

	
1*55 W

	
Set

	
102

	
102

	
***

	
***

	
***

	
***

	
***

	
Qiaoguang


	
19

	
Damp proof ceiling-mounted luminaire

	
1*100 W

	
Set

	
87

	
87

	
***

	
***

	
***

	
***

	
***

	
Qiaoguang


	
20

	
Dyd. Exit light

	
1*8 W

	
Set

	
103

	
103

	
***

	
***

	
***

	
***

	
***

	
Qiaoguang


	
21

	
Single rocker flush type switch

	
250V 10A

	
Piece

	
157

	
157

	
***

	
***

	
***

	
***

	
***

	
TCL


	
22

	
Double rocker flush type switch

	
250V 10A

	
Piece

	
36

	
36

	
***

	
***

	
***

	
***

	
***

	
TCL


	
23

	
Triple rocker flush type switch

	
250V 10A

	
Piece

	
17

	
17

	
***

	
***

	
***

	
***

	
***

	
TCL


	
24

	
Four-rocker flush type switch

	
250V 10A

	
Piece

	
15

	
15

	
***

	
***

	
***

	
***

	
***

	
TCL


	
25

	
Single flame-proof switch

	
250V 10A

	
Piece

	
4

	
4

	
***

	
***

	
***

	
***

	
***

	
TCL


	
26

	
Open mounted single double control switch

	
250V 10A

	
Piece

	
40

	
40

	
***

	
***

	
***

	
***

	
***

	
TCL


	
27

	
Light distribution box

	
PZ-30

	
Set

	
11

	
11

	
***

	
***

	
***

	
***

	
***

	  
	
28

	
Source automatic transfer box

	  	
Set

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	  











	
Electrical part

	
67/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of electrical system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
First

	
Lighting part

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
Second

	
Lighting wire. Spool

	  	  	  	  	  	  	  	  	  	  
	
1

	
Galvanizing KBG electric spool

	
¢20

	
m

	
8600

	
8600

	
***

	
***

	
***

	
***

	
***

	  
	
2

	
Common overline box

	
86 type

	
Piece

	
4120

	
4120

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
Wire

	
ZB-BV750-2

	
m

	
37890

	
37890

	
***

	
***

	
***

	
***

	
***

	  
	
Third

	
Power section

	  	  	  	  	  	  	  	  	  	  
	
1

	
Power box

	
XSAII-

	
Piece

	
0

	
0

	
***

	
***

	
***

	
***

	
***

	  
	
2

	
Plugging box

	
XSAII-

	
Piece

	
0

	
0

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
Overhauling power box

	
XSMII-

	
Piece

	
0

	
0

	
***

	
***

	
***

	
***

	
***

	  
	
4

	
Single two-level and three level phase socket


(five holes)

	
250V 10A

	
Piece

	
82

	
82

	
***

	
***

	
***

	
***

	
***

	
TCL


	
5

	
Duplex single four-level socket

	
250V 10A

	
Piece

	
455

	
455

	
***

	
***

	
***

	
***

	
***

	
TCL


	
6

	
Triphase four-level socket

	
440V 25A

	
Piece

	
6

	
6

	
***

	
***

	
***

	
***

	
***

	
TCL


	
7

	
Air-conditioning socket

	
250V 15A

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
TCL


	
8

	
Mud saver

	
T223V/KG

	
Piece

	
481

	
481

	
***

	
***

	
***

	
***

	
***

	  
	  	
Socket wire. Spool

	  	  	  	  	  	  	  	  	  	  
	
1

	
Galvanizing KBG electric spool

	
¢25

	
m

	
7650

	
7650

	
***

	
***

	
***

	
***

	
***

	  
	
2

	
Common overline box

	
86 type

	
Piece

	
3980

	
3980

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
Wire

	
ZB-BV750-2

	
m

	
18700

	
18700

	
***

	
***

	
***

	
***

	
***

	  
	
4

	
Wire

	
ZB-BV750-2

	
m

	
4890

	
4890

	
***

	
***

	
***

	
***

	
***

	  
	  	
Cable bridge

	  	  	  	  	  	  	  	  	  	  
	
1

	
Common cable bridge

	
800*200

	
m

	
107

	
107

	
***

	
***

	
***

	
***

	
***

	  
	
2

	
Common cable bridge

	
600*200

	
m

	
209

	
209

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
Common cable bridge

	
400*200

	
m

	
23

	
23

	
***

	
***

	
***

	
***

	
***

	  
	
4

	
Common cable bridge

	
300*100

	
m

	
81

	
81

	
***

	
***

	
***

	
***

	
***

	  
	
5

	
Fireproof cable bridge

	
300*150

	
m

	
159

	
159

	
***

	
***

	
***

	
***

	
***

	  





 



	
Electrical part

	
68/90

	
2009-6-19







 




  





  











  






 










Quotation sheet of electrical system


 



	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
First

	
Lighting part

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
6

	
Common bridge bend

	
800*200

	
Piece

	
4

	
4

	
***

	
***

	
***

	
***

	
***

	  
	
7

	
Common bridge tee

	
800*200

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	  
	
8

	
Common bridge cross tee

	
800*200

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	  
	
9

	
Common bridge bend

	
600*200

	
Piece

	
4

	
4

	
***

	
***

	
***

	
***

	
***

	  
	
10

	
Common bridge tee

	
600*200

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	  
	
11

	
Common bridge bend

	
400*200

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	  
	
12

	
Common bridge bend

	
300*100

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	  
	
13

	
Fireproof bridge bend

	
300*150

	
Piece

	
4

	
4

	
***

	
***

	
***

	
***

	
***

	  
	
14

	
Derrick

	
M10

	
m

	
1650

	
1650

	
***

	
***

	
***

	
***

	
***

	  
	
15

	
4# angle steel

	
40*40*4

	
m

	
730

	
730

	
***

	
***

	
***

	
***

	
***

	  
	  	
Cable

	  	  	  	  	
***

	
***

	
***

	
***

	
***

	  
	
1

	
ZR-YJV-5x6

	
Power box power distribution

	
m

	
1425

	
1425

	
***

	
***

	
***

	
***

	
***

	  
	
2

	
ZR-YJV-5x4

	
Power box power distribution

	
m

	
409

	
409

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
ZR-YJV-5x10

	
Power box power distribution

	
m

	
350

	
350

	
***

	
***

	
***

	
***

	
***

	  
	
4

	
ZR-YJV-5x16

	
Power box power distribution

	
m

	
92

	
92

	
***

	
***

	
***

	
***

	
***

	  
	
5

	
ZR-YJV-3x25+2x16

	
Cleaning unit

	
m

	
243

	
243

	
***

	
***

	
***

	
***

	
***

	  
	
5

	
ZR-YJV-3x25+2x16

	
Power cabinet

	
m

	
220

	
220

	
***

	
***

	
***

	
***

	
***

	  
	
6

	
ZR-YJV-5x6

	
Cleaning unit

	
m

	
687

	
687

	
***

	
***

	
***

	
***

	
***

	  
	
7

	
ZR-YJV-5x6

	
Cleaning machine 3501/2

	
m

	
246

	
246

	
***

	
***

	
***

	
***

	
***

	  
	
8

	
ZR-YJV-5x6

	
Autoclave cabinet 3503

	
m

	
93

	
93

	
***

	
***

	
***

	
***

	
***

	  
	
9

	
ZR-YJV-5x10

	
Drying cabinet 5104

	
m

	
84

	
84

	
***

	
***

	
***

	
***

	
***

	  
	
10

	
ZR-YJV-5x6

	
Switching box 21HX

	
m

	
27

	
27

	
***

	
***

	
***

	
***

	
***

	  
	
11

	
ZR-YJV-3x50+2x25

	
Switching box 11HX

	
m

	
177

	
177

	
***

	
***

	
***

	
***

	
***

	  
	
12

	
ZR-YJV-3x240+2x120

	
Refrigerator L1-1

	
m

	
152

	
152

	
***

	
***

	
***

	
***

	
***

	  





 



	
Electrical part

	
69/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of electrical system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price


difference

	
Remark


	
First

	
Lighting part

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
13

	
ZR-YJV-3x240+2x120

	
Refrigerator L1-2

	
m

	
152

	
152

	
***

	
***

	
***

	
***

	
***

	  
	
14

	
ZR-YJV-3x150+2x70

	
Refrigerator L2-1

	
m

	
152

	
0

	
***

	
***

	
***

	
***

	
***

	  
	
15

	
ZR-YJV-3x300+2x150

	
Refrigerator L2-1

	
m

	
0

	
152

	
***

	
***

	
***

	
***

	
***

	  
	
16

	
ZR-YJV-5x10

	
Power boxex

	
m

	
946

	
946

	
***

	
***

	
***

	
***

	
***

	  
	
17

	
ZR-YJV-5x16

	
Power boxex

	
m

	
1270

	
1270

	
***

	
***

	
***

	
***

	
***

	  
	
18

	
ZR-YJV-5x6

	
Power boxex

	
m

	
89

	
89

	
***

	
***

	
***

	
***

	
***

	  
	
19

	
ZR-YJV-3x35+2x16

	
Tunnel drying oven

	
m

	
112

	
112

	
***

	
***

	
***

	
***

	
***

	  
	
20

	
ZR-YJV-3x35+2x16

	
Power cabinet

	
m

	
252

	
252

	
***

	
***

	
***

	
***

	
***

	  
	
21

	
ZR-YJV-3x70+2x35

	
Power cabinet KHX

	
m

	
140

	
140

	
***

	
***

	
***

	
***

	
***

	  
	
22

	
ZR-YJV-3x95+2x50

	
Power cabinet LX

	
m

	
167

	
167

	
***

	
***

	
***

	
***

	
***

	  
	
19

	
ZR-YJV-5x6

	
Capping machine

	
m

	
112

	
112

	
***

	
***

	
***

	
***

	
***

	  
	  	
Power cabinet LX. ELX. HX power distribution cable (bottom end)

	  	  	  	  	  	  	  	  	  	  
	
1

	
ZR-YJV-3x25+2x16

	  	
m

	
49

	
49

	
***

	
***

	
***

	
***

	
***

	  
	
2

	
ZR-YJV-3x35+2x16

	  	
m

	
87

	
87

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
ZR-VV-1.0, 5x4

	  	
m

	
153

	
153

	
***

	
***

	
***

	
***

	
***

	  
	
4

	
ZR-VV-1.0, 4x4

	  	
m

	
56

	
56

	
***

	
***

	
***

	
***

	
***

	  
	
5

	
ZR-VV-1.0, 4x6

	  	
m

	
199

	
218

	
***

	
***

	
***

	
***

	
***

	  
	
6

	
ZR-VV-1.0, 4x16

	  	
m

	
207

	
301

	
***

	
***

	
***

	
***

	
***

	  
	
7

	
ZR-VV-1.0, 5x10

	  	
m

	
132

	
132

	
***

	
***

	
***

	
***

	
***

	  
	
8

	
ZR-kvv-1.0, 5x2.5

	  	
m

	
156

	
156

	
***

	
***

	
***

	
***

	
***

	  
	
9

	
ZR-kvv-1.0, 4x2.5

	  	
m

	
724

	
724

	
***

	
***

	
***

	
***

	
***

	  
	
10

	
ZR-BV-1.0, 2.5

	  	
m

	
2170

	
2170

	
***

	
***

	
***

	
***

	
***

	  
	
11

	
ZR-BV-1.0, 4.0

	  	
m

	
1679

	
1679

	
***

	
***

	
***

	
***

	
***

	  





 



	
Electrical part

	
70/90

	
2009-6-19







 




  





  











  






 










Quotation sheet of electrical system


 



	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
First

	
Lighting part

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
12

	
NH-VV-1.0, 4x2.5

	  	
m

	
387

	
387

	
***

	
***

	
***

	
***

	
***

	  
	
13

	
NH-VV-1.0, 4x4

	  	
m

	
579

	
579

	
***

	
***

	
***

	
***

	
***

	  
	
14

	
NH-VV-1.0, 4x10

	  	
m

	
398

	
398

	
***

	
***

	
***

	
***

	
***

	  
	
15

	
NH-KVV-0.5, 14x1.5

	  	
m

	
368

	
368

	
***

	
***

	
***

	
***

	
***

	  
	
16

	
NH-BV-0.5, 2.5

	  	
m

	
3267

	
3267

	
***

	
***

	
***

	
***

	
***

	  
	
17

	
NH-BV-0.5, 4.0

	  	
m

	
2100

	
2100

	
***

	
***

	
***

	
***

	
***

	  
	  	
Air-conditioning cabinet KX below

	  	  	  	  	
***

	
***

	
***

	
***

	
***

	  
	
1

	
ZR-VV-1.0, 4x16

	  	
m

	
390

	
390

	
***

	
***

	
***

	
***

	
***

	  
	
2

	
ZR-VV-1.0, 4x10

	  	
m

	
430

	
430

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
ZR-KVV-0,5, 2x1.5

	  	
m

	
3100

	
3100

	
***

	
***

	
***

	
***

	
***

	  
	
4

	
ZR-KVV-0,5, 7x1.5

	  	
m

	
2524

	
2524

	
***

	
***

	
***

	
***

	
***

	  
	
5

	
ZR-KVV-0,5, 4x2.5

	  	
m

	
1824

	
1824

	
***

	
***

	
***

	
***

	
***

	  
	
6

	
ZR-KVV-0,5, 5x2.5

	  	
m

	
112

	
112

	
***

	
***

	
***

	
***

	
***

	  
	
7

	
ZR-KVV-0,5, 2x4

	  	
m

	
824

	
824

	
***

	
***

	
***

	
***

	
***

	  
	
8

	
ZR-KVV-0,5, 2x6

	  	
m

	
179

	
179

	
***

	
***

	
***

	
***

	
***

	  
	
9

	
ZR-KVV-0,5, 3x1.5

	  	
m

	
635

	
635

	
***

	
***

	
***

	
***

	
***

	  
	
10

	
ZR-VV-1.0, 3x50+1x25

	  	
m

	
65

	
65

	
***

	
***

	
***

	
***

	
***

	  
	
11

	
ZR-VV-1.0, 3x35+1x16

	  	
m

	
65

	
65

	
***

	
***

	
***

	
***

	
***

	  
	
12

	
ZR-VV-1.0, 4x4

	  	
m

	
585

	
585

	
***

	
***

	
***

	
***

	
***

	  
	  	
Direct-expansion air conditioning unit power distribution

	  	  	  	  	  	  	  	  	  	  
	
1

	
ZR-VV-1.0, 5x10

	  	
m

	
0

	
132

	
***

	
***

	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	
Cable pipe

	  	  	  	  	  	  	  	  	  	  





 



	
Electrical part

	
71/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of electrical system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
First

	
Lighting part

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
1

	
Galvanized steel pipe

	
SC125

	
m

	
456

	
456

	
***

	
***

	
***

	
***

	
***

	  
	
2

	
Galvanized steel pipe

	
SC70

	
m

	
194

	
194

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
Galvanized steel pipe

	
SC50

	
m

	
355

	
355

	
***

	
***

	
***

	
***

	
***

	  
	
4

	
Galvanized steel pipe

	
SC40

	
m

	
1287

	
1287

	
***

	
***

	
***

	
***

	
***

	  
	
5

	
Galvanized steel pipe

	
SC32

	
m

	
2940

	
2940

	
***

	
***

	
***

	
***

	
***

	  
	
Fourth

	
Ground part

	  	  	  	  	
***

	
***

	
***

	
***

	
***

	  
	
1

	
Equal potential connecting box

	  	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	  
	
2

	
Galvanized flat steel

	
40mmx4m

	
m

	
818

	
818

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
Galvanized flat steel

	
80mmx8m

	
m

	
45

	
45

	
***

	
***

	
***

	
***

	
***

	  
	
4

	
Galvanized round steel

	
¢12

	
m

	
650

	
650

	
***

	
***

	
***

	
***

	
***

	  
	
5

	
Connecting line

	
BV-0.5-1x95mm

	
m

	
360

	
360

	
***

	
***

	
***

	
***

	
***

	  
	
6

	
Connecting line

	
BV-0.5-1x35mm

	
m

	
1890

	
1890

	
***

	
***

	
***

	
***

	
***

	  
	
7

	
Connecting line

	
BV-0.5-1x16mm

	
m

	
1200

	
1200

	
***

	
***

	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  	  
	
Fifth

	
Interlocking part

	  	  	  	  	  	  	  	  	  	  
	  	
Two doors interlocking

	  	  	  	  	  	  	  	  	  	  
	
1

	
Two doors interlocking controls

	
T108

	
Set

	
44

	
44

	  	  	  	  	  	
In the structure quotation


	
2

	
RVV-4*1.0

	  	
m

	
902

	
902

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
KBG pipe

	
¢15

	
m

	
780

	
780

	
***

	
***

	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	
Three doors interlocking

	  	  	  	  	  	  	  	  	  	  
	
1

	
Interlocking controls

	  	
Set

	
5

	
5

	  	  	  	  	  	
In the structure quotation


	
2

	
RVV-4*1.0

	  	
m

	
166

	
166

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
KBG pipe

	
¢15

	
m

	
200

	
200

	
***

	
***

	
***

	
***

	
***

	  





 



	
Electrical part

	
72/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of electrical system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
First

	
Lighting part

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	
Four doors interlocking

	  	  	  	  	  	  	  	  	  	  
	
1

	
Interlocking controls

	  	
Set

	
6

	
6

	  	  	  	  	  	
In the structure quotation


	
2

	
RVV-4*1.0

	  	
m

	
240

	
240

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
KBG pipe

	
¢15

	
m

	
240

	
240

	
***

	
***

	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	
Five doors interlocking

	  	  	  	  	  	  	  	  	  	  
	
1

	
Interlocking controls

	  	
Set

	
1

	
1

	  	  	  	  	  	
In the structure quotation


	
2

	
RVV-4*1.0

	  	
m

	
40

	
40

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
KBG pipe

	
¢15

	
m

	
40

	
40

	
***

	
***

	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	
Former


quotation

	
Now


quotation

	
Price difference

	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	
Subtotal

	  	  	  	  	  	  	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	
Subtotal 1

	  	  	  	  	  	  	
***

	
***

	
***

	  
	  	
Accessories

	  	  	  	
3%

	  	  	
***

	
***

	
***

	  
	  	
Installation cost and management cost

	  	  	  	
15%

	  	  	
***

	
***

	
***

	  
	  	
Subtotal 2

	  	  	  	  	  	  	
***

	
***

	
***

	  
	  	
Tax

	  	  	  	
4.33%

	  	  	
***

	
***

	
***

	  
	  	
Total

	  	  	  	  	  	  	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	  	  	  	  













 



	
Electrical part

	
73/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of electrical system








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
First

	
Lighting part

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  





Remark: the words in yellow are the quantity additional part.


 



	
Electrical part

	
74/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of automatic-control engineering








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X. K2X system )

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
1

	
Control

	
CPU315-2DP

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
2

	
Touch screen

	
TP177A

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
3

	
Analog quantity input module

	
Em331(8AI)

	
Piece

	
8

	
8

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
4

	
Analog quantity output module

	
Em332(8AO)

	
Piece

	
8

	
8

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
5

	
Digital quantity input module

	
Em321(16DI)

	
Piece

	
5

	  	
***

	
***

	
***

	
***

	
-12670

	
SIEMENS


	
6

	
Digital quantity output module

	
Em322(16DO)

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
7

	
Communication module

	
CPU343-1

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
8

	
Power module (5A)

	
PS307

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
9

	
Backboard bus connecting module

	
Im360

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
10

	
Backboard bus connecting module

	
Im361

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
11

	
40pins connector

	
Connector

	
Piece

	
23

	
23

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
12

	
Program mmc

	
512K

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
13

	
Tragschiene

	
530M

	
Piece

	
3

	
3

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
14

	
PLC control cabinet

	
1000*1800*400

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
Customized


	
15

	
24VAC/DC transformer

	  	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
First

	
K1X

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
HUBA


	
4

	
Electric switch valve (two-way)DN32

	
VVI41.32+SQX82

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN65

	
VVF31.65+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
6

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
Second

	
K11

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
Setrea













	
Automatic-control part

	
75/90

	
2009-6-19







 




  





  











  



















Quotation sheet of automatic-control engineering


 



	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X. K2X system)

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
HUBA


	
4

	
Electric regulating valve (two-way) DN50

	
VVF31 . 50+S Q X62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN25

	
VVG44.25+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
7

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
Third

	
K12

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
HUBA


	
4

	
Electric regulating valve (two-way) DN25

	
VVG44.25+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN15

	
VVG44.15+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
7

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
Fourth

	
K13

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
HUBA


	
4

	
Electric regulating valve (two-way) DN65

	
VVF31.65+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN32

	
VVI41.32+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN20

	
VVG41.20+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
7

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
Fifth

	
K14

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
HUBA







 



	
Automatic-control part

	
76/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of automatic-control engineering








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X. K2X system)

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
4

	
Electric regulating valve (two-way) DN32

	
VVI41.32+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
5

	
Electric regulating valve (two-way)DN20

	
VVG44 . 20+S Q S65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
7

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
Sixth

	
K15

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
3

	
3

	
***

	
***

	
***

	
***

	
0

	
HUBA


	
4

	
Electric switch valve (two-way)DN20

	
VVG44.20+SQS85

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
5

	
Electric switch valve (two-way)DN65

	
VVF31.65+SQX82

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN25

	
VVG44.25+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
7

	
Electric regulating valve (two-way) DN50

	
VVI41.50+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
8

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
9

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
Seventh

	
K2X-1

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
HUBA


	
4

	
Electric switch valve (two-way)DN32

	
VVI41.32+SQX82

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN65

	
VVF31.65+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
6

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
SIEMENS


	
Eighth

	
K21

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
0

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
0

	
HUBA







 



	
Automatic-control part

	
77/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of automatic-control engineering








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X. K2X system)

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
4

	
Electric regulating valve (two-way) DN50

	
VVF31.50+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way)DN25

	
VVG44 . 25+S Q S65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Ninth

	
K22

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric regulating valve (two-way) DN50

	
VVF31.50+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN25

	
VVG44.25+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Tenth

	
K23

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric regulating valve (two-way) DN32

	
VVI41.32+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN20

	
VVG44.20+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Eleventh

	
K2X-2

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric switch valve (two-way)DN25

	
VVG44.25+SQS85

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS







 



	
Automatic-control part

	
78/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of automatic-control engineering








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X. K2X system)

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
5

	
Electric switch valve (two-way)DN65

	
VVF31.65+SQX82

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric switch valve (two-way) DN25

	
VVG41 . 25+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Twelveth

	
K24

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric regulating valve (two-way) DN40

	
VVI41.40+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Thirteen

	
K25

	  	  	  	  	  	  	  	  	
***

	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric regulating valve (two-way) DN40

	
VVI41.40+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
(Second)

	
PLCP-02 (K3X, K4X, K5X, K6X,


K7X, L1, L2 system)

	  	  	  	  	  	  	  	  	  	  
	
1

	
Control

	
CPU315-2DP

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
2

	
Touch screen

	
TP177A

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
3

	
Analog quantity input module

	
Em331(8AI)

	
Piece

	
8

	
8

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
4

	
Analog quantity output module

	
Em332(8AO)

	
Piece

	
6

	
6

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Digital quantity input module

	
Em321(16DI)

	
Piece

	
5

	
5

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Digital quantity output module

	
Em322(16DO)

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
SIEMENS







 



	
Automatic-control part

	
79/90

	
2009-6-19







 




  





  











  






 










Quotation sheet of automatic-control engineering


 



	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X. K2X system )

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
7

	
Communication module

	
CPU343-1

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
8

	
Power module (5A)

	
PS307

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
9

	
Backboard bus connecting module

	
Im360

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
10

	
Backboard bus connecting module

	
Im361

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
11

	
40pins connector

	
Connector

	
Piece

	
21

	
21

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
12

	
Program mmc

	
512K

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
13

	
Tragschiene

	
530M

	
Piece

	
3

	
3

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
14

	
Plccontrol cabinet

	
1000*1800*400

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Customized


	
15

	
24VAC/dctransformer

	  	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Fourteenth

	
K3X

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric switch valve (two-way)DN32

	
VVI41.32+SQX82

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN65

	
VVF31.65+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Fifteenth

	
K31

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric regulating valve (two-way) DN32

	
VVI41.32+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN20

	
VVG44.20+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Sixteenth

	
K32

	  	  	  	  	  	  	  	  	  	  





 



	
Automatic-control part

	
80/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of automatic-control engineering








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X. K2X system )

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266 . X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric regulating valve (two-way) DN40

	
VVI41.40+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN25

	
VVG44.25+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN20

	
VVG41.20+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Seventeenth

	
K33

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric regulating valve (two-way) DN40

	
VVI41.40+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN20

	
VVG44.20+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN20

	
VVG41.20+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Eighteenth

	
K34

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric regulating valve (two-way) DN25

	
VVG44.25+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN15

	
VVG44.15+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN20

	
VVG41.20+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Nineteen

	
K41

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
E+E







 



	
Automatic-control part

	
81/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of automatic-control engineering








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X. K2X system )

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604 . X

	
Piece

	
3

	
3

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric switch valve (two-way)DN25

	
VVG44.25+SQS85

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN65

	
VVF31.65+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN25

	
VVG44.25+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Electric regulating valve (two-way) DN20

	
VVG41.20+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
8

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Twentyth

	
K51

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
3

	
3

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric switch valve (two-way)DN20

	
VVG44.20+SQS85

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN40

	
VVI41.40+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN15

	
VVG44.15+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
8

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Twenty-first

	
K52

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric switch valve (two-way)DN20

	
VVG44.20+SQS85

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN40

	
VVI41.40+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN20

	
VVG44.20+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
8

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS







 



	
Automatic-control part

	
82/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of automatic-control engineering








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X. K2X system )

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
Twenty-second

	
K61

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
3

	
3

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric switch valve (two-way)DN20

	
VVG44.20+SQS85

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN25

	
VVG44.25+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN15

	
VVG44.15+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
8

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Twenty-third

	
K62

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric switch valve (two-way)DN25

	
VVG44.25+SQS85

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN65

	
VVF31.65+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN15

	
VVG44.15+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Electric regulating valve (two-way) DN20

	
VVG41.20+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
8

	
Wind valve actuator

	
GDB161.1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
Twenty-fourth

	
K71

	  	  	  	  	  	  	  	  	  	  
	
1

	
Air duct temperature humidity sensor

	
EE16

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Air duct pressure sensor

	
266.X

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Setrea


	
3

	
Pressure difference switch

	
604.X

	
Piece

	
3

	
3

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
4

	
Electric switch valve (two-way)DN20

	
VVG44.20+SQS85

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Electric regulating valve (two-way) DN50

	
VVF31.50+SQX62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Electric regulating valve (two-way) DN20

	
VVG44.20+SQS65

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS







 



	
Automatic-control part

	
83/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of automatic-control engineering








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X. K2X system )

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
7

	
Electric regulating valve (two-way) DN15

	
VVG41.15+SKD62

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
8

	
Wind valve actuator

	
GDB161 . 1E

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	  
	  	
L1

	  	  	  	  	
***

	
***

	
***

	
***

	
***

	  
	
1

	
Level switch

	  	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Collihigh


	
2

	
Waterpipe pressure differential sensor

	
692.x

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
3

	
Electric switch valve (two-way)DN32

	
VVI41.32+SQX82

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
4

	
Electric regulating valve (two-way) DN150

	
VVF31.150+SKC60

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	  	
L2

	  	  	  	  	  	  	  	  	  	  
	
1

	
Level switch

	  	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Collihigh


	
2

	
Waterpipe pressure differential sensor

	
692.x

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
3

	
Electric switch valve (two-way)DN32

	
VVI41.32+SQX82

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	  	
Electric switch valve (two-way) DN80

	
VVF31.80+SKC60

	
Piece

	
1

	
0

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
4

	
Electric regulating valve (two-way) DN125

	
VVF31.125+SKC60

	
Piece

	
0

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	  	  	  	  	  	  	  	  	  	  	  	  
	
1

	
Evaporimeter butterfly valve DN 200

	
VKF46.200+SQL36E 65

	
Piece

	
2

	
0

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
2

	
Condenserbutterfly valve DN200

	
VKF46.200+SQL36E 65

	
Piece

	
2

	
0

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
3

	
Evaporimeter butterfly valve DN250

	
VKF46.200+SQL36E 65

	
Piece

	
0

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
4

	
Condenserbutterfly valve DN250

	
VKF46.200+SQL36E 65

	
Piece

	
0

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	  	  	  	  	  	  	  	  	  	  	  	  
	
(Third)

	
PLCP-03 (temperature and humidity control system )

	  	  	  	  	  	  	  	  	  	  
	
1

	
Control

	
CPU315-2DP

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
2

	
Touch screen

	
TP177A

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS







 



	
Automatic-control part

	
84/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of automatic-control engineering








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X. K2X system )

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
3

	
Analog quantity input module

	
Em331(8AI)

	
Piece

	
16

	
16

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
4

	
Communication module

	
CPU343-1

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Power module (5A)

	
PS307

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
Backboard bus connecting module

	
Im360

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Backboard bus connecting module

	
Im361

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
8

	
40pins connector

	
Connector

	
Piece

	
16

	
16

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
9

	
Program mmc

	
512K

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
10

	
Tragschiene

	
530M

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
11

	
Plccontrol cabinet

	
1000*1800*400

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Customized


	
12

	
24VAC/dctransformer

	  	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	  	
Temperature and humidity control 1

	  	  	  	  	  	  	  	  	  	  
	
1

	
Indoor temperature humidity sensor

	
EE10

	
Piece

	
13

	
13

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Differential pressure sensor

	
266.x

	
Piece

	
13

	
13

	
***

	
***

	
***

	
***

	
***

	
HUBA


	  	
Temperature and humidity control 2

	  	
Piece

	  	  	  	  	  	  	  	  
	
1

	
Indoor temperature humidity sensor

	
EE10

	
Piece

	
13

	
13

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Differential pressure sensor

	
266.x

	
Piece

	
13

	
13

	
***

	
***

	
***

	
***

	
***

	
HUBA


	  	
Temperature and humidity control 3

	  	
Piece

	  	  	  	  	  	  	  	  
	
1

	
Indoor temperature humidity sensor

	
EE10

	
Piece

	
14

	
14

	
***

	
***

	
***

	
***

	
***

	
E+E


	
2

	
Differential pressure sensor

	
266.x

	
Piece

	
14

	
14

	
***

	
***

	
***

	
***

	
***

	
HUBA


	
(Fourth)

	
PLCP-03 (room differential pressure sensor controlSystem)

	 	 	 	 	 	 	 	 	 	 
	
1

	
Control

	
CPU315-2DP

	
Piece

	
0

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
2

	
Touch screen

	
TP177A

	
Piece

	
0

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
3

	
Analog quantity input module

	
Em331(8AI)

	
Piece

	
0

	
16

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
4

	
Communication module

	
CPU343-1

	
Piece

	
0

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
5

	
Power module (5A)

	
PS307

	
Piece

	
0

	
2

	
***

	
***

	
***

	
***

	
***

	
SIEMENS









	
Automatic-control part

	
85/90

	
2009-6-19














  





  











  














 


Quotation sheet of automatic-control engineering


 



	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X, K2X system)

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
6

	
Backboard bus connecting module

	
IM360

	
Piece

	
0

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
7

	
Backboard bus connecting module

	
IM361

	
Piece

	
0

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
8

	
40pins connector

	
connector

	
Piece

	
0

	
16

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
9

	
Program mmc

	
512K

	
Piece

	
0

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
10

	
Tragschiene

	
530M

	
Piece

	
0

	
2

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
11

	
PLC control cabinet

	
1000*1800*400

	
Piece

	
0

	
1

	
***

	
***

	
***

	
***

	
***

	
Customized


	
12

	
24VAC/DC transformer

	  	
Piece

	
0

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	  	
Room differential pressure continuous record and show

	  	
Piece

	  	  	  	  	  	  	  	  
	
1

	
Pressure differential sensor with LCD

	
DM-2012-LCD (±60PA)

	
Piece

	
0

	
83

	
***

	
***

	
***

	
***

	
***

	
See the structure quotation


	  	  	  	
Piece

	  	  	  	  	  	  	  	  
	
Fifteenth

	
Centralized system

	  	  	  	  	  	  	  	  	  	  
	
1

	
Monitoring host

	
Lenovo YT

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Lenovo YT


	
2

	
Printer

	
EPSON

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
EPSON


	
3

	
Uninterruptable power supply 10 min

	
3KVA

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Santak


	
4

	
Communication connector

	
A53

	
Piece

	
2

	
2

	
***

	
***

	
***

	
***

	
***

	
Moxa


	
5

	
Centralized software

	
WINCC

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
SIEMENS


	
6

	
SIMATIC electronic signature

	
6ES7 658-

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Siemens


	
7

	
Wincc flexible/Audit

	
(Operation edition)

	
Piece

	
1

	
1

	
***

	
***

	
***

	
***

	
***

	
Siemens


	  	
In accordance with 21CFR (Code of Federal Regulations) Part 11 of the pharmaceutical industry, neet the requirements proposed by wincc flexible / Audit GMP (Good Manufacturing Practice) and FDA (Food and Drug Administration). Version and changing tracking using wincc fl exible / changing control options may collect and record any changes in the configuration. This can meet the GMP requirements of the changing control. Within the data of 512 can be traced back.


	
Sixteenth

	
Fan coil part

	  	  	  	  	  	  	  	  	  	  
	  	
FCU control

	
WI46.20/SUA21/R

	
Piece

	
66

	
66

	
***

	
***

	
***

	
***

	
***

	
SIEMENS







 



	
Automatic-control part

	
86/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of automatic-control engineering








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Price difference

	
Remark


	
(First)

	
PLCP-01 (K1X、K2X system)

	  	  	
Former

	
Now

	
Former

	
Now

	
Former

	
Now

	  	  
	
Seventeenth

	
Control cable

	  	  	  	  	  	  	  	  	  	  
	
1

	
RVVP4*1.0

	  	
m

	
5430

	
5430

	
***

	
***

	
***

	
***

	
***

	  
	
2

	
RVVP3*1.0

	  	
m

	
4050

	
4050

	
***

	
***

	
***

	
***

	
***

	  
	
3

	
RVV3*1.0

	  	
m

	
1350

	
1350

	
***

	
***

	
***

	
***

	
***

	  
	
4

	
RVVP2*1.0

	  	
m

	
4050

	
7250

	
***

	
***

	
***

	
***

	
***

	  
	
5

	
RVV2*1.0

	  	
m

	
3280

	
3280

	
***

	
***

	
***

	
***

	
***

	  
	
6

	
Galvanized spool

	
JDG20

	
m

	
6780

	
6780

	
***

	
***

	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  	
Former


quotation

	
Now


quotation

	
Price difference

	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	
Subtotal

	  	  	  	  	  	  	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  	  
	  	
Subtotal 1

	  	  	  	  	  	  	
***

	
***

	
***

	  
	  	
Accessories

	  	  	  	
3%

	  	  	
***

	
***

	
***

	  
	  	
Installation cost and management cost

	  	  	  	
12%

	  	  	
***

	
***

	
***

	  
	  	
Subtotal 2

	  	  	  	  	  	  	
***

	
***

	
***

	  
	  	
Tax

	  	  	  	
4.33%

	  	  	
***

	
***

	
***

	  
	  	
Total

	  	  	  	  	  	  	
***

	
***

	
***

	  
	  	  	  	  	  	  	  	  	  	  	  	  





Remark: the words in yellow are the additional quantity.


 



	
Automatic-control part

	
87/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of test and validation








	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18













	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Remark


	  	
The third party testing

	  	  	  	  	  	  
	
1

	
Filter integrity testing

	
PAO testing

	
Piece

	
356.00

	
***

	
***

	
Shangke Suzhou


	
2

	
Differential pressure testing

	  	
Set

	
1

	
***

	
***

	
Shangke Suzhou


	
3

	
Air changes

	  	
Set

	
1

	
***

	
***

	
Shangke Suzhou


	
4

	
Temperature

	  	
Set

	
1

	
***

	
***

	
Shangke Suzhou


	
5

	
Humidity

	  	
Set

	
1

	  	
-

	
Shangke Suzhou


	
6

	
Clarity (dust particle number)

	  	
Set

	
1

	
***

	
***

	
Shangke Suzhou


	
7

	
Air pattern

	  	
Set

	
1

	
***

	
***

	
Shangke Suzhou


	
8

	
Self-purification

	  	
Set

	
1

	
***

	
***

	
Shangke Suzhou


	  	  	  	  	  	  	
-

	  
	
9

	
Room differential pressure verification certificate

	  	
Piece

	
198

	
***

	
***

	
Bureau of weights and measures


	
10

	
Temperature humidity sensor verification certificate

	  	
Piece

	
75

	
***

	
***

	
Bureau of weights and measures


	
11

	
Differential pressure sensor verification certificate

	  	
Piece

	
70

	
***

	
***

	
Bureau of weights and measures


	  	  	  	  	  	  	  
	  	
Automatic control system computer validation

	  	  	  	  	  
	  	
By valuedata pte ltd, Singapore

	  	  	  	  	  
	
1

	
Document: Validation Master Plan

	
Set

	
1

	
***

	
***

	  











	
Test and verification

	
88/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of test and validation


 



	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Remark


	  	
The third party testing

	  	  	  	  	  	  
	
2

	
Document: User Requirement Specification

	
Set

	
1

	
***

	
***

	  
	
3

	
Document: Quality Plan - Functional Design Specification - Acceptance Test Specification - Hardware Design Specification - Hardware Test Specification - Software Module Test Specifications - Software Module Testing - Integration Testing

	
Set

	
1

	
***

	
***

	  
	
4

	
Document: System Impact Assessment and


Risk Assessment

	
Set

	
1

	
***

	
***

	  
	
5

	
 


Document: Design Qualification

	
Set

	
1

	
***

	
***

	  
	
6

	
 


Document: Installation Qualification Protocol

	
Set

	
1

	
***

	
***

	  
	
7

	
 


Document: Operation Qualification Protocol

	
Set

	
1

	
***

	
***

	  
	
8

	
On Site Support: Operation Qualification


Execution with report

	
Set

	
1

	
***

	
***

	  





 



	
Test and verification

	
89/90

	
2009-6-19







 




  





  











  














 


Quotation sheet of test and validation


 



	
Proprietor name: Shenyang SUNSHINE Pharmaceutical Co., Ltd

	
No.: Q558-B


	
Project name: Cleanroom project of production department New factory

	
Date: 2009-6-18







 



	
No.

	
Name

	
Model and specification

	
Unit

	
Quantity

	
Unit price

	
Total

	
Remark


	  	
The third party testing

	  	  	  	  	  	  
	  	  	  	  	  	  	  	  
	  	
Subtotal 1

	  	  	  	  	
***

	  
	  	
Tax

	  	  	
4.33%

	  	
***

	  
	  	
Total

	  	  	  	  	
***

	  
	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  
	  	  	  	  	  	  	  	  













 



	
Test and verification

	
90/90

	
2009-6-19