Unassociated Document




Exhibit 4.8.48 - Self-Control Components - SQS Series

















4573         







SQS35...         


SQS65...         


SQS85...         







Electrically Operated Valve Actuator


 


Stroke 5.5mm








	


	
  

	














	
SQS35.50, SQS35.53

	 	
SQS35.00, SQS35.03, SQS65, SQS65.2


	
SQS65.5

	 	
SQS85.00, SQS85.03


	 	 	 
	
With spring-return/

	 	
without spring-return/


	
Without manual adjustment

	 	
with manual adjustment







Electrically Operated Valve (EOV)



	
l

	
SQS35...AC 220V working voltage, receiving three-position control signal








	
l

	
SQS85...AC 24V working voltage, receiving three-position control signal








	
l

	
SQS65...AC 24V working voltage, receiving DC 0...10V or DC 2...10V control signal








	
l

	
Adjustment power can reach 400N








	
l

	
0.5mm Stroke








	
l

	
Directly installing onto valve body without other facility








	
l

	
SQS35.00, SQS35.03, SQS85.00 and SQS85.03 have additional auxiliary switch function








	
l

	
meeting Standard of DIN 32 730, the actuator with/without spring return








	
l

	
Actuator without spring return has functions of manual adjustment and position display








	
l

	
Spring-return actuator with function of position display but without manual adjustment








	
Usage







Valve actuator is used for serial types of two-way valve, three-way valve, VVG44...,VVG45...,VVP45..., VMP43..., VMP44..., VMP45..., VXG44..., VXP45... and VV152..., and the drive stoke is 5.5mm.








	
Siemens Building Technologies

	  
	
HVAC Products

	
CM1N4573C/03.2003   











  





  











  












	
l

	
Applicable area adheres to IEC 721-3-3 (Regulation 721-3-3 by International Electro-technical Commission ) Grade 3K5








	
l

	
Environmental temperature: -5...+50°C








	
l

	
Valve inner medium temperature: +2...+130°C








	
l

	
Using installation fittings ASK30 can drive the following 4mm or 5.5mm turn valves: X3i..., WG45..., VXG45..., VXG46... and VVI51...








	
Function Three-position or ratio control signal







Revisable synchro motor adopts three-way control signals (SQS35 and SQS85) or ratio control signal DC 0...10V (SQS65 and SQS65.5) or DC 2...10V (SQS65.2) for driving. It makes corresponding valve way through anti-lock gear mechanism.







Three-position control of Terminal Y1or Y2:



	
l

	
Y1 has voltage: valve rod contracts and valve gate opens








	
l

	
Y2 has voltage: valve rod extends and valve gate closes








	
l

	
Y1 or Y2 has no voltage: valve rod keeps in current position












SQS65...       Flow Characteristics Selection


Repositioning connection S1 (under cap/under print circuit board) can change the flow characteristics of 5.5mm turn valve (from “equal proportion” to “linear”). In any case, flow characteristics relate to valve way.



	
l

	
S1 connecting A and C can produce equal-proportion flow characteristics (factory set), which is mainly used for heating application.








	
l

	
S1 connecting B and C can produce linear flow characteristics, which is mainly used for cooling application.








	
l

	
For automatic operation, S1 connecting A and C or connecting B and C mainly depends on necessary flow characteristic.













	
S1 Position

	  	  
	
S1 connect to: A & C

	  	
S1 connect to: B & C


	
(equal-proportion flow characteristics)

	  	
(Linear flow characteristics)


	  	  	  
	


	
  

	













Flow Characteristics


Relationship between DC 0...10V or DC 2...10V control signal and volume flow control signal:


Y= DC 0...10V or DC 2...10V


R=0...1000Ω








	
Siemens Building Technologies

	  
	
HVAC Products

	
CM1N4573C/03.2003   











  





  











  








Flow Characteristics


Log=equal=proportion valve characteristics (factory set)


Lin-linear valve characteristics


Flow range


K&100=volume flow 100%


K&=volume flow 0%















Type Overview



	
Type No.

	
Working


Voltage

	
Control Mode


(Control Signal)

	
Runtime


(Sec)

	
Spring-return


Function

	
Spring-return


Time(Sec)


	
SQS35.00

	
AC 230 V

	
Three-way

	
150

	
With

	
—


	
SQS35.03

	
35


	
SQS35.50

	
150

	
Without

	
8


	
SQS35.53

	
35


	
SQS65.5

	
AC 24 V

	
DC 0...10 V

	
35

	
with

	
8


	
SQS65

	
without

	
—


	
SQS65.2

	
DC 2...10 V


	
SQS85.00

	
Three-way

	
150


	
SQS85.03

	
35












Accessory



	
Name

	
Type No.

	
Applicative Actuator

	
Used Space


	
Auxiliary Switch

	
ASC9.6

	
SQS35.00,SQS35.03


SQS85.00,SQS85.03

	
1 x ASC9.6












Order


Please indicate quality, product name, type No. and accessory when ordering goods.


e.g.: 1 actuator, Type No. SQS35.00, 1 auxiliary switch, Type No. ASC9.6








	
Siemens Building Technologies

	  
	
HVAC Products

	
CM1N4573C/03.2003   











  





  











  











Transportation


Actuator, valve and accessory are packed separately and not put together before dispatch.



	  
	
Capability







The following 5.5mm return, thread two-way and three-way valve can be driven by electric actuators SQS35..., SQS65... and SQS85....



	
Type No.

	
DN[mm]

	
PN[Bar]

	
Technical Material


	
Two-way valve


	
VVG44...


VVP45...


VMP43...(2)


VMP44...(2)


VVG55...


VVI52...

	
15...40


10...20


15, 20


15, 20


15...25


15

	
16


16


16


16


25


25

	
N4364


N4845


N4841


N4844


N4379


N4377


	
Three-way valve


	
VXG44...


VXP45....


XMP43...

	
15...40


10...20


15, 20

	
16


16


16

	
N4464


N4845


N4841


	
Three-way valve with T bypass


	
VMP45...


VMP43...(4)


VMP44...(4)

	
10...20


15, 20


15, 20

	
16


16


16

	
N4845


N4841


N4844







Allowable pressure differentials of valve ΔPmax and ΔPa are listed in relevant valve technical material data sheet.



	
Machine Design








	
l

	
Electric actuator, maintenance free








	
l

	
Reversible synchro motor








	
l

	
Anti-lock gear mechanism








	
l

	
SQS35.50, SQS35.53 and SQS65.5 meet spring-return function of DIN 32730 Standard








	
l

	
Load switch is on stroke limit








	
l

	
Optional flow characteristics: It is equal-proportion or linear when SQS65... actuator connects valve type WG44..., VVI52... and VXG44...








	
l

	
Direct-pressure manual adjustment is used for all actuators without spring return: SQS35.00, SQS35.03, SQS65, SQS65.2 AND SQS85...








	
l

	
All actuators SQS35..., SQS65... AND SQS85... have position indicators








	
l

	
Auxiliary switch Type No. ASC9.6 applies to actuators SQS35.00, SQS35.03, SQS85.00 AND SQS85.03. Actuator Type No. SQS65.50 and SQS35.53 installs auxiliary switch witin the standard (not ASC9.6)













	
Siemens Building Technologies

	  
	
HVAC Products

	
CM1N4573C/03.2003   











  





  











  











Manual Adjustment















SQS35.00, SQS35.03


 


SQS65, SQS65.2


 


SQS85...


 



	
1.

	
Manual adjustment


	 	 






	
2.

	
Position indicator


	 	 






	
3.

	
Connecting bolt of valve neck












Terminal Strip and Auxiliary Switch, etc








	


	 	



	  	 	  
	
SQS35..., SQS85...

	 	
SQS65...













	
5    terminal Strip

	 	
5     terminal Strip


	 	 	 
	
6    auxiliary switch of SQS35.50 and

	 	
6   《lin》/《log》connection


	 	 	 
	
       SQS35.53 within the standard

	 	
7      electrical bridge













	
Accessory

	
ASC9.6 auxiliary switch


	  	
Applying to actuators with Type No.SQS35.00, SQS35.03, SQS85.00 and SQS85.03


	  	
Switching point can be adjusted in the stroke range of 0...100%


	  	
Prefer “Technical Data” for accessory detail


	  	  
	
Disposal

	
actuator must be splitted into constructional elements before disposal.
















 








 





	
Siemens Building Technologies

	  
	
HVAC Products

	
CM1N4573C/03.2003   











  





  











  












	
Project

	
Actuator must be install electrical connection according to local regulations and connection diagram


	  	  
	
Notes:

	
It must adhere to regulations and requirements for personal and property safety at any time.


	
SQS65...

	
When using Actuator SQS65..., valves with Types VVG55..., VMP..., VVP... and VXP... must be connected onto “lin” for connectors of selected flow characteristics.


	  	
It must obey allowable temperature (see “Application” and “technical Data”). It must be illustrated in Facility Diagram if auxiliary switch is needed.








Installation





Direction










	


	 	



	  	 	  
	
Allowed

	 	
Not allowed













	  	
Valve Installation Handbook is printed on the back of actuator. Accessory Guide is put in corresponding accessory package box.


	
Debugging

	
Connection and function is inspected when debugging, in addition, auxiliary or auxiliary switch are also inspected and set necessarily.













	


	



	  	  
	
Stroke《0》= valve door close

	
Stoke 《1》=valve door open













	  	
Manual Regulator: Manual regulator is rotated clockwise to close Siemens 5.5mm Stroke Valve (=0% stroke)


	  	  
	
SQS35.../SQS85...

	
The flow characteristics of these actuators are linear when connecting to Valves of Type No. VVG44..., VVI52... or VXG444...


	  	  
	
SQS65...

	
The flow characteristics of these actuators are equal-proportion (factory sets) by electrical assembly when connecting to Valves of Type No. VVG44..., VVI52... or VXG44.... The flow characteristics can turn to “linear” through relocating connectors.













	
Siemens Building Technologies

	  
	
HVAC Products

	
CM1N4573C/03.2003   











  





  











  












	
Guarantee

	
Actuator Technical Date (Δpmax, ΔPs, leak rate, noise level and working life) apply to Siemens valves listed in matched “Compatibility” only.


	  	
Siemens neither guarantee nor promise if SQS... actuators are connected to third-party valve doors.


	
Maintain

	
When repairing valves: turn off pump and power source, turn off main stop valve on pipes, release pressure in pipes and cool it down completely. If necessary, electrical connection from terminal should be disconnected.


	  	  
	  	
Actuator must be installed correctly with valve door, then restarting can be done.







 


Technical Data



 


Power Source





Working Voltage







	
SQS35...

	
AC230 V ± 15 % , 50 / 60 Hz


	
SQS65...

	
AC 24 V ± 20 % , 50 / 60 Hz


	
SQS85...

	
AC24 V ± 20 % , 50 / 60 Hz












Power consumption








	
SQS35.00

	
2.5 VA


	
SQS35.03

	
3.5 VA


	
SQS35.50

	
5 VA


	
SQS35.53

	
6 VA


	
SQS65, SQS65.2

	
4.5 VA


	
SQS65.5

	
7 VA


	
SQS85.00

	
2 VA


	
SQS85.03

	
2 VA












Limiting converting volume of converting terminal 11 or 12



	
SQS35..., SQS85...

	
AC 250 V, 6A resistance/2.5A inductance












Working Parameter


Control Pattern (Control Signal)



	
SQS85...

	
three-position


	
SQS65, SQS65.5

	
DC 0...10V (in proportion)


	
SQS65.2

	
DC 210V (in proportion)













	
Runtime

	
On or Off


	
SQS35.00, SQS35.50, SQS85.00

	
50Hz, 150 s


	
SQS35.03, SQS35.53, SQS85.03

	
50Hz, 35 s


	
SQS65, SQS65.2, SQS65.5

	
50Hz, 35 s













	
Siemens Building Technologies

	  
	
HVAC Products

	
CM1N4573C/03.2003   











  





  











  












	
Spring Return Characteristics

	  
	
SQS35.50, SQS35.53, SQS65.5

	
turn-off time 8 s


	
Adjustment Force

	
400 N


	
Stroke

	
5.5 mm












Input Signal



	
Terminal Y (SQS65, SQS65.5)

	
DC 0...10V, Max 0.1 mA


	
Terminal Y (SQS65.2)

	
DC 2...10V, Max 0.1 mA


	 	 
	
Terminal R (SQS65, SQS65.5, SQS65.2)

	
resistance 0...1000Ω













	
Output Signal

	  
	
Terminal U (SQS65, SQS65.5, SQS65.2)

	
DC 0...10V, Max 0.5 mA













	
Enclosure Protection Standard

	  
	
Enclosure Protection Standard

	
EN 60529, IP54


	
Cable bushing

	
Pg11 (2x)













	
Environment Condition

	  
	
Valve inner medium temperature

	
+2...+130°C


	  	  
	
Operation

	
IEC 721-3-3


	
Environmental Condition

	
Grade 3K5


	 	 
	
Temperature

	
-5...+50°C


	 	 
	
Humidity

	
5~95%rh


	  	  
	
Transportation

	
IEC 721-2-3


	
Environmental Condition

	
Grade 2K3


	 	 
	
Temperature

	
-25...+70°C


	 	 
	
Humidity

	
<95%rh


	  	  
	
Storage

	
IEC 721-1-3


	
Environmental Condition

	
Grade 1K3


	 	 
	
Temperature

	
-5...+50°C


	 	 
	
Humidity

	
5~95%rh













	
Industrial Standard

	  
	
Meeting CE Authentication:

	  
	
EMC directive

	
89/336/EEC


	
Low voltage directive

	
73/23/EEC













	
Siemens Building Technologies

	  
	
HVAC Products

	
CM1N4573C/03.2003   











  





  











  












	
Size/Weight

	  
	
Size

	
see “Size”













	
Weight

	  
	
SQS35.00, SQS35.03, SQS65, SQS65.2

	  
	
SQS85.00, SQS85.03

	  
	
Packing not included

	
0.5kg


	
Packing included

	
0.6kg


	  	  
	
SQS35.50, SQ35.53, SQS65.5

	  
	
Packing not included

	
0.6kg


	
Packing included

	
0.7kg


	  	  
	
Material

	  
	
Actuator Shell

	
plastic


	
Luifel & manual regulator

	
plastic


	
Coupling wheel chain & lever

	
platic


	  	  
	
Accessory

	  
	
ASC9.6 auxiliary contact capacity

	  
	
of SQS35... and SQS85...

	AC250V, 10A resistance/3A inductance
	 	 










Connection Diagram


 


SQS35...


 



	


	 	



	  	 	  
	
SQS35.00, SQS35.03

	 	
SQS35.50, SQS35.53


	
AC230V, three-position, no spring return

	 	
AC230V, three-position, spring return





 


	
Cm1 limit switch 100% stroke

	 	
c2 fixedly setting interior auxiliary switch


	
Cm2 limit switch 0% stroke

	 	
(factory installs, without ASC9.6 Accessory)


	
C1 linkable ASC9.6 auxiliary switch

	 	  
	
L threading no-voltage terminal

	 	  











	
Siemens Building Technologies

	  
	
HVAC Products

	
CM1N4573C/03.2003   











  





  











  








SQS85...


 





 


SQS85.00, SQS85.03


 


AC 24V, three-position, no spring return







Cm1 limit switch 100% stroke


Cm2 limit switch 0% stroke


C1 installable ASC9.6 auxiliary switch


L threading no-voltage terminal











Connection Diagram


 


Connecting Terminal


 


SQS65....


 











	
G, G0

	
working voltage AC24 V


	  	
G  System Power line (SP), equivalent to LS on SQS56.2


	  	
G0  System null line (SN), equivalent to NS on SQS56.2


	  	  
	
Input Signal


	
Y

	
SQS65, SQS65.5

	
DC 0...10 V


	  	
SQS65.2

	
DC 2...10 V


	
R

	
SQS65, SQS65.2, SQS65.50...1000 ohms

	  
	
M

	
Detecting element

	  
	
U Output Signal

	  
	  	
SQS65, SQS65.2, SQS65.5

	
DC 0...10 V













	
Siemens Building Technologies

	  
	
HVAC Products

	
CM1N4573C/03.2003   











  





  











  











All connection options are shown on connection diagram. Among these options, how many options and which option used depend on system situation.







Notes: If facility connects onto Terminal R, factory-setting electric bridge through R-M on print circuit board must be punctured.







SQS65, SQS65.5


 


(AC24 V, DC 0...10 V)















SQS65.2


 


(AC24 V, Dc 2...10 V)
















	
Facility


	
F1

	 	
frost detector

	
K1 On/off Switch


	
K1

	 	
On/off Switch

	
N1 typical controller


	
N1

	 	
typical controller

	
P1 position indictor


	
P1

	 	
position indictor

	
R1 position converter


	
R1

	 	
position converter

	
Y1 Actuator













	
Siemens Building Technologies

	  
	
HVAC Products

	
CM1N4573C/03.2003   











  





  











  











Measurement     Unit of measurement: mm


 





 


*    Height after actuator installs on the valve


  > 100mm  minimum distance from wall to cover


 >200mm used for places of installation, connection, operation or maintenance


 




	
Siemens Building Technologies

	  
	
HVAC Products

	
CM1N4573C/03.2003