Facility _Information facility _id utility

_code legal_owner_name

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 49889 10343 Mt Carmel Cogen Inc Mt Carmel Cogen Inc PO BOX 409 MARION HEIGHTS RD MARION HEIGHTS

PA 17832

Page 1Facility _Information plant_name

physical_address

phyical_city

physical_state

physical_zip

mailing_address

mailing_city

mailing_state

mailing_zip Foster Wheeler Mt Carmel Cogen

Marion Heights Road

MARION HEIGHTS

PA 17832 P.O Box 409 MARION HEIGHTS

PA 17832

Page 2Facility _Information RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas Yes TRUE FALSE TRUE FALSE FALSE TRUE FALSE TRUE

Page 3Facility _Information ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE TRUE Sem iannual monitoring and deviation reports (Title V Permit 49-00001, Section B, Condition #023)Annual compliance certification reports (Title V Permit 49-00001, Section B, Condition #024)Semiannual reports of calculations for VOC emissions (Title V Permit 49-00001, Section C, Condition #022)Notification and reporting of malfunctions (Title V Permit 49-00001, Section C, Condition #023)CEMS sy stem performance/RATA reports (Title V Permit 49-00001, Section D, Souce 031, Condtion #018)Quarterly CEMS data reports for opacity, SO2, Nox, CO, and quartely calculations of emissions of PM, F, Hg, (Title V Permit 49-00001, Section D, Souce 031, Condtion #019) No July 2008 HCl Stack Test - flue gas O2, flue gas CO2, flue gas temperature and flue gas pressure not measured. Also, Chloride in fuel is 83 ug/g (micrograms/gram). Concentrations are in gr/dscf.July 2008 Hg Stack Test - Stack Temps as follows:Run 1 - 312 FRun 2 - 310 FRun 3 - 310 FMercury in fuel is 0.152 ug/g (micrograms/gram)July 2009 Hg Stack Test - Stack temps as follows:Run 1 - 306 FRun 2 - 304 FRun 3 - 305 FUnits for mercury in fuel is ug/g (micrograms/gram)June 2005 PM Stack Test - Stack Temps as follows:Run 1 - 311 FRun 2 - 309 FRun 3 - 318 FParticulate concentrations are in gr/dscf.May 2007 PM Stack Test - Stack Temps as follows:Run 1 - 309 FRun 2 - 321 FRun 3 - 312 FParticulate concentrations are in gr/dscf.May 2009 PM Stack Test - Stack Temps as follows:Run 1 - 301 FRun 2 - 298 FRun 3 - 292 FParticulate concentrations are in gr/dscf.On sampling port tab, S031 Duct port is located in duct work going to stack while S031 stack por

Page 4Facility _Information July

2008 HCl Stack Test - flue gas O2, flue gas CO2, flue gas temperature and flue gas pressure not measured. Also, Chloride in fuel is 83 ug/g (micrograms/gram). Concentrations are in gr/dscf.July 2008 Hg Stack Test - Stack Temps as follows:Run 1 - 312 FRun 2 - 310 FRun 3 - 310 FMercury in fuel is 0.152 ug/g (micrograms/gram)July 2009 Hg Stack Test - Stack temps as follows:Run 1 - 306 FRun 2 - 304 FRun 3 - 305 FUnits for mercury in fuel is ug/g (micrograms/gram)June 2005 PM Stack Test - Stack Temps as follows:Run 1 - 311 FRun 2 - 309 FRun 3 - 318 FParticulate concentrations are in gr/dscf.May 2007 PM Stack Test - Stack Temps as follows:Run 1 - 309 FRun 2 - 321 FRun 3 - 312 FParticulate concentrations are in gr/dscf.May 2009 PM Stack Test - Stack Temps as follows:Run 1 - 301 FRun 2 - 298 FRun 3 - 292 FParticulate concentrations are in gr/dscf.On sampling port tab, S031 Duct port is located in duct work going to stack while S031 stack por

Page 5Facility _Information July

2008 HCl Stack Test - flue gas O2, flue gas CO2, flue gas temperature and flue gas pressure not measured. Also, Chloride in fuel is 83 ug/g (micrograms/gram). Concentrations are in gr/dscf.July 2008 Hg Stack Test - Stack Temps as follows:Run 1 - 312 FRun 2 - 310 FRun 3 - 310 FMercury in fuel is 0.152 ug/g (micrograms/gram)July 2009 Hg Stack Test - Stack temps as follows:Run 1 - 306 FRun 2 - 304 FRun 3 - 305 FUnits for mercury in fuel is ug/g (micrograms/gram)June 2005 PM Stack Test - Stack Temps as follows:Run 1 - 311 FRun 2 - 309 FRun 3 - 318 FParticulate concentrations are in gr/dscf.May 2007 PM Stack Test - Stack Temps as follows:Run 1 - 309 FRun 2 - 321 FRun 3 - 312 FParticulate concentrations are in gr/dscf.May 2009 PM Stack Test - Stack Temps as follows:Run 1 - 301 FRun 2 - 298 FRun 3 - 292 FParticulate concentrations are in gr/dscf.On sampling port tab, S031 Duct port is located in duct work going to stack while S031 stack por

Page 6Facility _Information July

2008 HCl Stack Test - flue gas O2, flue gas CO2, flue gas temperature and flue gas pressure not measured. Also, Chloride in fuel is 83 ug/g (micrograms/gram). Concentrations are in gr/dscf.July 2008 Hg Stack Test - Stack Temps as follows:Run 1 - 312 FRun 2 - 310 FRun 3 - 310 FMercury in fuel is 0.152 ug/g (micrograms/gram)July 2009 Hg Stack Test - Stack temps as follows:Run 1 - 306 FRun 2 - 304 FRun 3 - 305 FUnits for mercury in fuel is ug/g (micrograms/gram)June 2005 PM Stack Test - Stack Temps as follows:Run 1 - 311 FRun 2 - 309 FRun 3 - 318 FParticulate concentrations are in gr/dscf.May 2007 PM Stack Test - Stack Temps as follows:Run 1 - 309 FRun 2 - 321 FRun 3 - 312 FParticulate concentrations are in gr/dscf.May 2009 PM Stack Test - Stack Temps as follows:Run 1 - 301 FRun 2 - 298 FRun 3 - 292 FParticulate concentrations are in gr/dscf.On sampling port tab, S031 Duct port is located in duct work going to stack while S031 stack por

Page 7Facility _Information July

2008 HCl Stack Test - flue gas O2, flue gas CO2, flue gas temperature and flue gas pressure not measured. Also, Chloride in fuel is 83 ug/g (micrograms/gram). Concentrations are in gr/dscf.July 2008 Hg Stack Test - Stack Temps as follows:Run 1 - 312 FRun 2 - 310 FRun 3 - 310 FMercury in fuel is 0.152 ug/g (micrograms/gram)July 2009 Hg Stack Test - Stack temps as follows:Run 1 - 306 FRun 2 - 304 FRun 3 - 305 FUnits for mercury in fuel is ug/g (micrograms/gram)June 2005 PM Stack Test - Stack Temps as follows:Run 1 - 311 FRun 2 - 309 FRun 3 - 318 FParticulate concentrations are in gr/dscf.May 2007 PM Stack Test - Stack Temps as follows:Run 1 - 309 FRun 2 - 321 FRun 3 - 312 FParticulate concentrations are in gr/dscf.May 2009 PM Stack Test - Stack Temps as follows:Run 1 - 301 FRun 2 - 298 FRun 3 - 292 FParticulate concentrations are in gr/dscf.On sampling port tab, S031 Duct port is located in duct work going to stack while S031 stack por

Page 8Facility _Information July

2008 HCl Stack Test - flue gas O2, flue gas CO2, flue gas temperature and flue gas pressure not measured. Also, Chloride in fuel is 83 ug/g (micrograms/gram). Concentrations are in gr/dscf.July 2008 Hg Stack Test - Stack Temps as follows:Run 1 - 312 FRun 2 - 310 FRun 3 - 310 FMercury in fuel is 0.152 ug/g (micrograms/gram)July 2009 Hg Stack Test - Stack temps as follows:Run 1 - 306 FRun 2 - 304 FRun 3 - 305 FUnits for mercury in fuel is ug/g (micrograms/gram)June 2005 PM Stack Test - Stack Temps as follows:Run 1 - 311 FRun 2 - 309 FRun 3 - 318 FParticulate concentrations are in gr/dscf.May 2007 PM Stack Test - Stack Temps as follows:Run 1 - 309 FRun 2 - 321 FRun 3 - 312 FParticulate concentrations are in gr/dscf.May 2009 PM Stack Test - Stack Temps as follows:Run 1 - 301 FRun 2 - 298 FRun 3 - 292 FParticulate concentrations are in gr/dscf.On sampling port tab, S031 Duct port is located in duct work going to stack while S031 stack por

Page 9Facility _Information July

2008 HCl Stack Test - flue gas O2, flue gas CO2, flue gas temperature and flue gas pressure not measured. Also, Chloride in fuel is 83 ug/g (micrograms/gram). Concentrations are in gr/dscf.July 2008 Hg Stack Test - Stack Temps as follows:Run 1 - 312 FRun 2 - 310 FRun 3 - 310 FMercury in fuel is 0.152 ug/g (micrograms/gram)July 2009 Hg Stack Test - Stack temps as follows:Run 1 - 306 FRun 2 - 304 FRun 3 - 305 FUnits for mercury in fuel is ug/g (micrograms/gram)June 2005 PM Stack Test - Stack Temps as follows:Run 1 - 311 FRun 2 - 309 FRun 3 - 318 FParticulate concentrations are in gr/dscf.May 2007 PM Stack Test - Stack Temps as follows:Run 1 - 309 FRun 2 - 321 FRun 3 - 312 FParticulate concentrations are in gr/dscf.May 2009 PM Stack Test - Stack Temps as follows:Run 1 - 301 FRun 2 - 298 FRun 3 - 292 FParticulate concentrations are in gr/dscf.On sampling port tab, S031 Duct port is located in duct work going to stack while S031 stack por

Page 10Facility _Information July

2008 HCl Stack Test - flue gas O2, flue gas CO2, flue gas temperature and flue gas pressure not measured. Also, Chloride in fuel is 83 ug/g (micrograms/gram). Concentrations are in gr/dscf.July 2008 Hg Stack Test - Stack Temps as follows:Run 1 - 312 FRun 2 - 310 FRun 3 - 310 FMercury in fuel is 0.152 ug/g (micrograms/gram)July 2009 Hg Stack Test - Stack temps as follows:Run 1 - 306 FRun 2 - 304 FRun 3 - 305 FUnits for mercury in fuel is ug/g (micrograms/gram)June 2005 PM Stack Test - Stack Temps as follows:Run 1 - 311 FRun 2 - 309 FRun 3 - 318 FParticulate concentrations are in gr/dscf.May 2007 PM Stack Test - Stack Temps as follows:Run 1 - 309 FRun 2 - 321 FRun 3 - 312 FParticulate concentrations are in gr/dscf.May 2009 PM Stack Test - Stack Temps as follows:Run 1 - 301 FRun 2 - 298 FRun 3 - 292 FParticulate concentrations are in gr/dscf.On sampling port tab, S031 Duct port is located in duct work going to stack while S031 stack por

Page 11Facility _Information July

2008 HCl Stack Test - flue gas O2, flue gas CO2, flue gas temperature and flue gas pressure not measured. Also, Chloride in fuel is 83 ug/g (micrograms/gram). Concentrations are in gr/dscf.July 2008 Hg Stack Test - Stack Temps as follows:Run 1 - 312 FRun 2 - 310 FRun 3 - 310 FMercury in fuel is 0.152 ug/g (micrograms/gram)July 2009 Hg Stack Test - Stack temps as follows:Run 1 - 306 FRun 2 - 304 FRun 3 - 305 FUnits for mercury in fuel is ug/g (micrograms/gram)June 2005 PM Stack Test - Stack Temps as follows:Run 1 - 311 FRun 2 - 309 FRun 3 - 318 FParticulate concentrations are in gr/dscf.May 2007 PM Stack Test - Stack Temps as follows:Run 1 - 309 FRun 2 - 321 FRun 3 - 312 FParticulate concentrations are in gr/dscf.May 2009 PM Stack Test - Stack Temps as follows:Run 1 - 301 FRun 2 - 298 FRun 3 - 292 FParticulate concentrations are in gr/dscf.On sampling port tab, S031 Duct port is located in duct work going to stack while S031 stack por

Page 12Facility _Information July

2008 HCl Stack Test - flue gas O2, flue gas CO2, flue gas temperature and flue gas pressure not measured. Also, Chloride in fuel is 83 ug/g (micrograms/gram). Concentrations are in gr/dscf.July 2008 Hg Stack Test - Stack Temps as follows:Run 1 - 312 FRun 2 - 310 FRun 3 - 310 FMercury in fuel is 0.152 ug/g (micrograms/gram)July 2009 Hg Stack Test - Stack temps as follows:Run 1 - 306 FRun 2 - 304 FRun 3 - 305 FUnits for mercury in fuel is ug/g (micrograms/gram)June 2005 PM Stack Test - Stack Temps as follows:Run 1 - 311 FRun 2 - 309 FRun 3 - 318 FParticulate concentrations are in gr/dscf.May 2007 PM Stack Test - Stack Temps as follows:Run 1 - 309 FRun 2 - 321 FRun 3 - 312 FParticulate concentrations are in gr/dscf.May 2009 PM Stack Test - Stack Temps as follows:Run 1 - 301 FRun 2 - 298 FRun 3 - 292 FParticulate concentrations are in gr/dscf.On sampling port tab, S031 Duct port is located in duct work going to stack while S031 stack por

Page 13Facility _Information July

2008 HCl Stack Test - flue gas O2, flue gas CO2, flue gas temperature and flue gas pressure not measured. Also, Chloride in fuel is 83 ug/g (micrograms/gram). Concentrations are in gr/dscf.July 2008 Hg Stack Test - Stack Temps as follows:Run 1 - 312 FRun 2 - 310 FRun 3 - 310 FMercury in fuel is 0.152 ug/g (micrograms/gram)July 2009 Hg Stack Test - Stack temps as follows:Run 1 - 306 FRun 2 - 304 FRun 3 - 305 FUnits for mercury in fuel is ug/g (micrograms/gram)June 2005 PM Stack Test - Stack Temps as follows:Run 1 - 311 FRun 2 - 309 FRun 3 - 318 FParticulate concentrations are in gr/dscf.May 2007 PM Stack Test - Stack Temps as follows:Run 1 - 309 FRun 2 - 321 FRun 3 - 312 FParticulate concentrations are in gr/dscf.May 2009 PM Stack Test - Stack Temps as follows:Run 1 - 301 FRun 2 - 298 FRun 3 - 292 FParticulate concentrations are in gr/dscf.On sampling port tab, S031 Duct port is located in duct work going to stack while S031 stack por

Page 14Facility _Information July

2008 HCl Stack Test - flue gas O2, flue gas CO2, flue gas temperature and flue gas pressure not measured. Also, Chloride in fuel is 83 ug/g (micrograms/gram). Concentrations are in gr/dscf.July 2008 Hg Stack Test - Stack Temps as follows:Run 1 - 312 FRun 2 - 310 FRun 3 - 310 FMercury in fuel is 0.152 ug/g (micrograms/gram)July 2009 Hg Stack Test - Stack temps as follows:Run 1 - 306 FRun 2 - 304 FRun 3 - 305 FUnits for mercury in fuel is ug/g (micrograms/gram)June 2005 PM Stack Test - Stack Temps as follows:Run 1 - 311 FRun 2 - 309 FRun 3 - 318 FParticulate concentrations are in gr/dscf.May 2007 PM Stack Test - Stack Temps as follows:Run 1 - 309 FRun 2 - 321 FRun 3 - 312 FParticulate concentrations are in gr/dscf.May 2009 PM Stack Test - Stack Temps as follows:Run 1 - 301 FRun 2 - 298 FRun 3 - 292 FParticulate concentrations are in gr/dscf.On sampling port tab, S031 Duct port is located in duct work going to stack while S031 stack por

Page 15facility _contacts facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 49889 1 Environmental Manager Fred Walsh570373399925 fredwalsh@mtcarmelcogen.com TRUE

Page 16facility _coal_utilized facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note 49889 coal refuse 100 100

Page 17facility _oil_utilized facility _id oil_type percentage_volume percentage_btu

other_type

Page 18facility _other_materials facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain 49889 Propane TRUE FALSE 0 tons/year Propane use in boiler has been discontinued - propane lines capped off to discontinue use. No

Page 19facility _other_materials rcra_explain

Page 20boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuelheat_input max_heat_input MWe_capacity 49889 SG-101 Fluidized bed firing Dry Bottom waste coal 623.5 505 139913

Page 21boiler_information

MWe_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 123100 91 88 1125 940 910 900 FALSE

Page 22boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 7843 83.65 Subpart Da(1) FALSE

Page 23boiler_information

NOx_control

SO2_control

combustion_additives No Yes No

Page 24boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 49889 SG-101 coal refuse 2007 99 96 49889 SG-101 coal refuse 2008 99 96 49889 SG-101 coal refuse 2009 99 94 49889 SG-101 natural gas 2007 1 4 49889 SG-101 natural gas 2008 1 4 49889 SG-101 natural gas 2009 1 6 49889 SG-101 other fossil fuel (specify) 2007 0 0 propane 49889 SG-101 other fossil fuel (specify) 2008 0 0 propane 49889 SG-101 other fossil fuel (specify) 2009 0 0 propane

Page 25boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online

Page 26boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online 49889 SG-101 Limestone injection to fluidized bed-fired furnace 1/1/1990

Page 27boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 28facility _units facility _id unit_id 49889 SG-101

Page 29unit_boilers

facility _id unit_id boiler_id 49889 SG-101 SG-101

Page 30facility _controls facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 49889 C031 PM control Fabric Filter, reverse air FALSE 1/1/1990

Page 31facility _controls reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

Page 32facility _sampling_ports facility _id sampling_port_id 49889 S031 Duct Port 49889 S031 Stack Port

Page 33facility _stacks facility _id stack_id stack_height stack_diameter

sack_gas_velocity 49889 S031 306 9 60.269

Page 34configurations

facility _id configuration_id 49889 SG-101

Page 35configuration_components

facility _id configuration_id

component_id

order component_type port_near 49889 SG-101 C031 3 PM control 49889 SG-101 S031 6 Stack 49889 SG-101 S031 Duct Port 5 Sam pling Port pevious 49889 SG-101 S031 Stack Port 4 Sam pling Port next 49889 SG-101 SG-101 1 Unit

Page 36configuration_pollutants1

facility _id configuration_id

pollutant_name

permit_type_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 49889 SG-101 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.3 pound per million British Thermal Unit (lb/MMBtu)

30 days 0.6 pound per million British Thermal Unit (lb/MMBtu) 49889 SG-101 Total Suspended Particulates (TSP) Federal - Title V Operating Permit

0.03 pound per million British Thermal Unit (lb/MMBtu) 17 pound per hour (lb/hr) 49889 SG-101 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

0.24 pound per million British Thermal Unit (lb/MMBtu)

24 hours 136 pound per hour (lb/hr) 49889 SG-101 Carbon Monoxide (CO) Federal - Title V Operating Permit

0.5 pound per million British Thermal Unit (lb/MMBtu)

24 hours 283.3 pound per hour (lb/hr) 49889 SG-101 Hydrogen Fluoride (HF) Federal - Title V Operating Permit

3.5 pound per hour (lb/hr) 49889 SG-101 Total Mercury (Hgt) Federal - Title V Operating Permit

0.164 pound per hour (lb/hr) 49889 SG-101 VOCs Federal - Title V Operating Permit 49 tons per year (tons/yr)

Page 37configuration_pollutants1

avg_period_2

em lim it_3 emlim it_units_3 avg_period_3

em lim it_4 em lim it_units_4 avg_period_4

em lim it_details

test_method 24 hours 340 pound per hour (lb/hr) 24 hours pound per hour (lb/hr)

24 hours 24 hours Lim it on combined VOC emissions from all combustion sources at the facility
.

Page 38configuration_pollutants1

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping

req_reporting No guaranteed emission rate available.

CEMS CEMS DAHS Quarterly

CEMS Data submittals to PA DEP and EPA Yes 99.97% removal efficiency of baghouse. Stack testing every

odd year. Calculations used to verify compliance with PM limit. Subm it calculations used to verify compliance quarterly

to PA DEP. No guaranteed emission rate available.

CEMS CEMS DAHS Quarterly

CEMS Data submittals to PA DEP and EPA No guaranteed emission rate available.

CEMS CEMS DAHS Quarterly

CEMS Data submittals to PA DEP and EPA No guaranteed emission rate available.

Recordkeeping

Calculations used to verify compliance with HF limit Subm it calculations used to verify compliance quarterly

to PA DEP. No guaranteed emission rate available.

Recordkeeping

Calculations used to verify compliance with Hg limit Subm it calculations used to verify compliance quarterly

to PA DEP. Lim it on combined VOC emissions from all combustion sources at the facility
. No guaranteed emission rate available.

Recordkeeping and stack testing every odd year. Calculations used to verify compliance with VOC limit on all combustion units in plant Subm it calculations used to verify compliance semiannually to PA DEP.

Page 39configuration_pollutants1 Quarterly

CEMS Data submittals to PA DEP and EPA Subm it calculations used to verify compliance quarterly

to PA DEP. Quarterly

CEMS Data submittals to PA DEP and EPA Quarterly

CEMS Data submittals to PA DEP and EPA Subm it calculations used to verify compliance quarterly

to PA DEP. Subm it calculations used to verify compliance quarterly

to PA DEP. Subm it calculations used to verify compliance semiannually to PA DEP.

Page 40control_technologies

facility _id configuration_id

component_id

control_id project_titleproject_type vendor_name

vndor_contact

vendor_phone

Page 41control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 42control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 43control_technologies feed_rate_units

Page 44control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 45control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_name

Page 46control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investment

total_operating_costs

base_year

Page 47control_costs

CBI

Page 48misc_controls

facility _id misc_control_id

control_description

Page 49misc_control_configurations

facility _id misc_control_id

configuration_id

Page 50fuel_shipments

facility _id shipment_id

shipment_date

amount_received

amount_units

fuel_type state_country other_country

county 49889 Apr 2009 4/1/2009 40256 short tons (2000 lbs) coal PA PA - Northumberland 49889 Aug 2009 8/1/2009 47230 short tons (2000 lbs) coal PA PA - Northumberland 49889 Dec 2009 12/1/2009 32204 short tons (2000 lbs) coal PA PA - Northumberland 49889 Feb 2009 2/1/2009 54600 short tons (2000 lbs) coal PA PA - Northumberland 49889 Jan 2009 1/1/2009 51575 short tons (2000 lbs) coal PA PA - Northumberland 49889 Jul 2009 7/1/2009 43656 short tons (2000 lbs) coal PA PA - Northumberland 49889 Jun 2009 6/1/2009 36797 short tons (2000 lbs) coal PA PA - Northumberland 49889 Mar 2009 3/1/2009 49658 short tons (2000 lbs) coal PA PA - Northumberland 49889 May

2009 5/1/2009 21953 short tons (2000 lbs) coal PA PA - Northumberland 49889 Nov 2009 11/1/2009 30122 short tons (2000 lbs) coal PA PA - Northumberland 49889 Oct 2009 10/1/2009 41705 short tons (2000 lbs) coal PA PA - Northumberland 49889 Sep 2009 9/1/2009 37071 short tons (2000 lbs) coal PA PA - Northumberland

Page 51fuel_shipments

coal_seam shipment_method NA - waste coal

Trucks NA - waste coal

Trucks NA - waste coal

Trucks NA - waste coal

Trucks NA - coal refuse

Trucks NA - waste coal

Trucks NA - waste coal

Trucks NA - waste coal

Trucks NA - waste coal

Trucks NA - waste coal

Trucks NA - waste coal

Trucks NA - waste coal

Trucks

Page 52fuel_shipment_configurations

facility _id shipment_id

configuration_id 49889 Apr 2009 SG-101 49889 Aug 2009 SG-101 49889 Dec 2009 SG-101 49889 Feb 2009 SG-101 49889 Jan 2009 SG-101 49889 Jul 2009 SG-101 49889 Jun 2009 SG-101 49889 Mar 2009 SG-101 49889 May

2009 SG-101 49889 Nov 2009 SG-101 49889 Oct 2009 SG-101 49889 Sep 2009 SG-101

Page 53fuel_shipment_samples

facility _id shipment_id

sample_id amount_fuel amount_fuel_units

total_sulfur ash_content heating_value

hating_units

Page 54fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address

Page 55fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_name lab_address lab_city lab_state lab_zip analysis_copies

Page 56fuel_shipment_samples analysis_copies

Page 57fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL

Page 58test_reports

facility _id report_id report_typeother_type report_description report_begin_date

report_end_date

before_control

during_deviation 49889 HCl 2008 other em ission factor determination HCl - CFB Exhaust Stack 2008

7/10/2008 7/10/2008 No No 49889 Hg 2008 compliance Hg - CFB Exhaust Stack 2008 7/8/2008 7/9/2008 No No 49889 Hg 2009 compliance Hg - CBF Exhaust Stack 2009 7/27/2009 7/28/2009 No No 49889 PM 2005 compliance PM - CFB Exhaust Stack 2005 6/1/2005 6/1/2005 No No 49889 PM 2007 compliance PM - CFB Exhaust Stack 2007 5/29/2007 5/30/2007 No No 49889 PM 2009 compliance PM - CFB Exhaust Stack 2009 6/8/2009 6/10/2009 No No 49889 VOC 2005 compliance VOC - CFB Exhaust Stack 2005 6/1/2005 6/1/2005 No No 49889 VOC 2007 compliance VOC - CFB Exhaust Stack 2007 5/29/2007 5/29/2007 No No 49889 VOC 2009 compliance VOC - CFB Exhaust Stack 2009 6/8/2009 6/8/2009 No No

Page 59test_reports

deviation_reports No No No No No No No No No

Page 60test_report_configurations

facility _id report_id configuration_id 49889 HCl 2008 SG-101 49889 Hg 2008 SG-101 49889 Hg 2009 SG-101 49889 PM 2005 SG-101 49889 PM 2007 SG-101 49889 PM 2009 SG-101 49889 VOC 2005 SG-101 49889 VOC 2007 SG-101 49889 VOC 2009 SG-101

Page 61test_report_fuels

facility _id report_id fuel_id 49889 HCl 2008 anthracite culm 49889 Hg 2008 antracite culm 49889 Hg 2009 antrhacite culm 49889 PM 2005 anthracite culm 49889 PM 2007 anthracite culm 49889 PM 2009 antracite culm 49889 VOC 2005 antracite culm 49889 VOC 2007 antracite culm 49889 VOC 2009 antracite culm

Page 62test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 49889 HCl 2008 anthracite culm coal refuse 100 100 49889 Hg 2008 antracite culm coal refuse 100 100 49889 Hg 2009 antrhacite culm coal refuse 100 100 49889 PM 2005 anthracite culm coal refuse 100 100 49889 PM 2007 anthracite culm coal refuse 100 100 49889 PM 2009 antracite culm coal refuse 100 100 49889 VOC 2005 antracite culm coal refuse 100 100 49889 VOC 2007 antracite culm coal refuse 100 100 49889 VOC 2009 antracite culm coal refuse 100 100

Page 63cem_data

facility _id time_period

cem_period_description

Page 64cem_data_pollutants1

facility _id time_period

pollutant_name

Page 65test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent 49889 HCl 2008 S031 Stack Port No CFB stack No 49889 Hg 2008 S031 Stack Port No Test perfomed with two sample trains (A&B) Run results reported are average of two trains. No 49889 Hg 2009 S031 Stack Port No Test perfomed with two sample trains (A&B). Results for each run are average of two trains. No 49889 PM 2005 S031 Stack Port No CFB stack No 49889 PM 2007 S031 Stack Port No CFB stack No 49889 PM 2009 S031 Stack Port No CFB stack No 49889 VOC 2005 S031 Duct Port No VOC stack inlet duct No 49889 VOC 2007 S031 Duct Port No CFB stack inlet duct No 49889 VOC 2009 S031 Duct Port No CFB stack inlet duct No

Page 66test_report_sampling

fg_fraction 100% of flue gas flow to stack S031 100% of flue gas flow to stack S031 100% of flue gas flow to stack S031 100% of flue gas flow to stack S031 100% of flue gas flow to stack S031 100% of flue gas flow to stack S031 100% of flue gas flow to stack S031 100% of flue gas flow to stack S031 100% of flue gas flow to stack S031

Page 67sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetime

unit_load net_generation fg_moisture_content 49889 HCl 2008 S031 Stack Port 1 7/10/2008 7/10/2008 46.1 41 8.5 49889 HCl 2008 S031 Stack Port 2 7/10/2008 7/10/2008 45 61 7.2 49889 HCl 2008 S031 Stack Port 3 7/10/2008 7/10/2008 44.7 40 7.3 49889 Hg 2008 S031 Stack Port 1 7/8/2008 7/8/2008 44.7 160 7.3 49889 Hg 2008 S031 Stack Port 2 7/9/2008 7/9/2008 44.4 100 7.6 49889 Hg 2008 S031 Stack Port 3 7/9/2008 7/9/2008 44.7 130 7.7 49889 Hg 2009 S031 Stack Port 1 7/27/2009 7/27/2009 45 89 7.3 49889 Hg 2009 S031 Stack Port 2 7/28/2009 7/28/2009 45.9 82 6.9 49889 Hg 2009 S031 Stack Port 3 7/28/2009 7/28/2009 44.9 89 7.2 49889 PM 2005 S031 Stack Port 1 6/1/2005 6/1/2005 46.5 62 4.5 49889 PM 2005 S031 Stack Port 2 6/1/2005 6/1/2005 45.7 62 5.9 49889 PM 2005 S031 Stack Port 3 6/1/2005 6/1/2005 45.3 62 5.8 49889 PM 2007 S031 Stack Port 1 5/29/2007 5/29/2007 44.1 80 6.4 49889 PM 2007 S031 Stack Port 2 5/29/2007 5/29/2007 43.9 79 6.4 49889 PM 2007 S031 Stack Port 3 5/30/2007 5/30/2009 44 80 6.7 49889 PM 2009 S031 Stack Port 1 6/8/2009 6/8/2009 44.2 79 6.1 49889 PM 2009 S031 Stack Port 2 6/8/2009 6/8/2009 44.1 77 6.3 49889 PM 2009 S031 Stack Port 3 6/10/2009 6/10/2009 44.2 79 6.2 49889 VOC 2005 S031 Duct Port 1 6/1/2005 6/1/2005 46.5 62 4.5 49889 VOC 2005 S031 Duct Port 2 6/1/2005 6/1/2005 45.7 41 5.9 49889 VOC 2005 S031 Duct Port 3 6/1/2005 6/1/2005 45.3 41 5.8 49889 VOC 2007 S031 Duct Port 1 5/29/2007 5/29/2007 44.1 40 6.4 49889 VOC 2007 S031 Duct Port 2 5/29/2007 5/29/2007 44.2 40 6.4 49889 VOC 2007 S031 Duct Port 3 5/29/2007 5/29/2007 44.1 40 6.4 49889 VOC 2009 S031 Duct Port 1 6/8/2009 6/8/2009 44.2 39 6.1 49889 VOC 2009 S031 Duct Port 2 6/8/2009 6/8/2009 43.7 38 6.3 49889 VOC 2009 S031 Duct Port 3 6/8/2009 6/8/2009 44.6 39 6.3

Page 68sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 223519 dscfm 70 1 226852 dscfm 70 1 225916 dscfm 70 1 185372 dscfm 70 1 8.5 11.5 300 190540 dscfm 70 1 8.8 11.5 300 186616 dscfm 70 1 8.9 11.6 300 199761 dscfm 70 1 9 11.5 300 202010 dscfm 70 1 9.8 11.3 300 203266 dscfm 70 1 9.5 11.4 300 182427 dscfm 70 1 9.2 11.8 300 181902 dscfm 70 1 8.5 11.9 300 181566 dscfm 70 1 8.2 12.3 300 170226 dscfm 70 1 7.6 13.1 300 171493 dscfm 7.7 12.9 300 165944 dscfm 70 1 7.8 12.9 300 198403 dscfm 70 1 9.7 10.8 300 196015 dscfm 70 1 9.6 11.2 298 201368 dscfm 70 1 9.7 10.7 292 182427 dscfm 70 1 9.2 11.8 181902 dscfm 8.5 11.9 181566 dscfm 8.2 12.3 170226 dscfm 70 1 7.6 13.1 170226 dscfm 70 1 7.7 12.9 171493 dscfm 70 1 7.8 12.9 198403 dscfm 70 1 9.7 10.8 196015 dscfm 70 1 9.6 11.2 196015 dscfm 70 1 9.7 10.7

Page 69sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value EPA Method 26

NA anthracite culm 45.5 66.4 4571 EPA Method 26

NA anthracite culm 44.7 66.4 4571 EPA Method 26

NA anthracite culm 44.9 66.4 4571 0.97 EPA Method 29 NA antracite culm 44.7 67.87 4287 0.95 Method 29 NA antracite culm 44.4 67.87 4287 0.95 EPA Method 29 NA antracite culm 44.7 67.87 4287 0.94 EPA Method 29 NA antrhacite culm 45 0.94 EPA Method 29 NA antrhacite culm 45.9 0.96 EPA Method 29 NA antrhacite culm 44.9 0.95 Method 5 NA 0.95 Method 5 NA 0.95 Method 5 NA 0.99 Method 5 NA 0.99 Method 5 0.95 Method 5 NA 0.96 Method 5/OTM-28 NA 0.95 Method 5/202 0.95 Method 5/202

Method 25A Method 25A Method 25A Method 25A Method 25A Method 25A Method 25A Method 25 Method 25A

Page 70sampling_runs

fuel_sulfur 0.33 0.33 0.33 0.29 0.29 0.29

Page 71sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_name conc conc_units conc_ND conc_MDL 49889 HCl 2008 S031 Stack Port 1 Hydrogen Chloride (HCl) 0.006 FALSE 49889 HCl 2008 S031 Stack Port 2 Hydrogen Chloride (HCl) 0.0059 FALSE 49889 HCl 2008 S031 Stack Port 3 Hydrogen Chloride (HCl) 0.00649 FALSE 49889 Hg 2009 S031 Stack Port 1 Total Mercury (Hgt) 0.16 microgram per dry standard cubic meter ( FALSE 49889 Hg 2009 S031 Stack Port 2 Total Mercury (Hgt) 0.25 microgram per dry standard cubic meter ( FALSE 49889 Hg 2009 S031 Stack Port 3 Total Mercury (Hgt) 0.18 microgram per dry standard cubic meter ( FALSE 49889 PM 2005 S031 Stack Port 1 PM (Filterable) 0.004 FALSE 49889 PM 2005 S031 Stack Port 2 PM (Filterable) 0.003 FALSE 49889 PM 2005 S031 Stack Port 3 PM (Filterable) 0.003 FALSE 49889 Hg 2008 S031 Stack Port 1 Total Mercury (Hgt) 0.48 microgram per dry standard cubic meter ( FALSE 49889 Hg 2008 S031 Stack Port 2 Total Mercury (Hgt) 0.04 microgram per dry standard cubic meter ( FALSE 49889 Hg 2008 S031 Stack Port 3 Total Mercury (Hgt) 0.04 microgram per dry standard cubic meter ( FALSE 49889 PM 2007 S031 Stack Port 1 PM (Filterable) 0.005 FALSE 49889 PM 2007 S031 Stack Port 2 PM (Filterable) 0.002 FALSE 49889 PM 2007 S031 Stack Port 3 PM (Filterable) 0.002 FALSE 49889 PM 2009 S031 Stack Port 1 PM (Filterable) 0.005 FALSE 49889 PM 2009 S031 Stack Port 1 PM (Condensable) 0.001 FALSE 49889 PM 2009 S031 Stack Port 2 PM (Filterable) 0.002 FALSE 49889 PM 2009 S031 Stack Port 2 PM (Condensable) 0.001 FALSE 49889 PM 2009 S031 Stack Port 3 PM (Filterable) 0.002 FALSE 49889 PM 2009 S031 Stack Port 3 PM (Condensable) 0.001 FALSE 49889 VOC 2005 S031 Duct Port 1 Total Hydrocarbons (THC) (as Methane) 0.06 parts per million by volume (dry) (ppmvd) FALSE 49889 VOC 2005 S031 Duct Port 2 Total Hydrocarbons (THC) (as Methane) 0.13 parts per million by volume (dry) (ppmvd) FALSE 49889 VOC 2005 S031 Duct Port 3 Total Hydrocarbons (THC) (as Methane) 0.7 parts per million by volume (dry) (ppmvd) FALSE 49889 VOC 2007 S031 Duct Port 1 Total Hydrocarbons (THC) (as Methane) 0.12 parts per million by volume (dry) (ppmvd) FALSE 49889 VOC 2007 S031 Duct Port 2 Total Hydrocarbons (THC) (as Methane) 0.12 parts per million by volume (dry) (ppmvd) FALSE 49889 VOC 2007 S031 Duct Port 3 Total Hydrocarbons (THC) (as Methane) 0.07 parts per million by volume (dry) (ppmvd) FALSE 49889 VOC 2009 S031 Duct Port 1 Total Hydrocarbons (THC) (as Methane) 0.9 parts per million by volume (dry) (ppmvd) FALSE 49889 VOC 2009 S031 Duct Port 2 Total Hydrocarbons (THC) (as Methane) 1.21 parts per million by volume (dry) (ppmvd) FALSE 49889 VOC 2009 S031 Duct Port 3 Total Hydrocarbons (THC) (as Methane) 1.13 parts per million by volume (dry) (ppmvd) FALSE

Page 72sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment 11.49 pound per hour (lb/hr)

FALSE 0.018 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 11.47 pound per hour (lb/hr)

FALSE 0.016 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 12.57 pound per hour (lb/hr)

FALSE 0.018 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 0.0001 pound per hour (lb/hr)

FALSE 2E-07 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0002 pound per hour (lb/hr)

FALSE 4.1E-07 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.0001 pound per hour (lb/hr)

FALSE 2E-07 pound per million British Thermal Unit (lb/MMBtu) FALSE 6.39 pound per hour (lb/hr)

FALSE 0.011 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 5.25 pound per hour (lb/hr)

FALSE 0.009 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 5.1 pound per hour (lb/hr)

FALSE 0.008 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 0.00035 pound per hour (lb/hr)

FALSE 5.9E-07 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.000025 pound per hour (lb/hr) FALSE 4.2E-08 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.000025 pound per hour (lb/hr) FALSE 4.3E-08 pound per million British Thermal Unit (lb/MMBtu) FALSE 6.67 pound per hour (lb/hr)

FALSE 0.01 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 3.5 pound per hour (lb/hr)

FALSE 0.006 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 2.65 pound per hour (lb/hr)

FALSE 0.004 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 8.48 pound per hour (lb/hr)

FALSE 0.014 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 1.81 pound per hour (lb/hr)

FALSE 0.004 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 3.24 pound per hour (lb/hr)

FALSE 0.006 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 1.9 pound per hour (lb/hr)

FALSE 0.003 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 3.89 pound per hour (lb/hr)

FALSE 0.006 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 2.26 pound per hour (lb/hr)

FALSE 0.0035 pound per million British Thermal Unit (lb/MMBtu) FALSE gr/dscf 0.08 pound per hour (lb/hr)

FALSE FALSE 0.17 pound per hour (lb/hr)

FALSE FALSE 0.88 pound per hour (lb/hr)

FALSE FALSE 0.14 pound per hour (lb/hr)

FALSE FALSE 0.14 pound per hour (lb/hr)

FALSE FALSE 0.08 pound per hour (lb/hr)

FALSE FALSE 1.22 pound per hour (lb/hr)

FALSE FALSE 1.62 pound per hour (lb/hr)

FALSE FALSE 1.52 pound per hour (lb/hr)

FALSE FALSE

Page 73sampling_run_pollutants1 run_pollutant_comment

Page 74sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL 49889 HCl 2008 S031 Stack Port 1 Chloride (Cl) 83 microgram per gram (dry) (mg/g) FALSE 49889 HCl 2008 S031 Stack Port 2 Chloride (Cl) 83 microgram per gram (dry) (mg/g) FALSE 49889 HCl 2008 S031 Stack Port 3 Chloride (Cl) 83 microgram per gram (dry) (mg/g) FALSE 49889 Hg 2008 S031 Stack Port 1 Mercury

(Hg) 0.152 microgram per gram (dry) (mg/g) FALSE 49889 Hg 2008 S031 Stack Port 2 Mercury

(Hg) 0.152 microgram per gram (dry) (mg/g) FALSE 49889 Hg 2008 S031 Stack Port 3 Mercury

(Hg) 0.152 microgram per gram (dry) (mg/g) FALSE 49889 Hg 2009 S031 Stack Port 1 Mercury

(Hg) 0.16 microgram per gram (dry) (mg/g) FALSE 49889 Hg 2009 S031 Stack Port 2 Mercury

(Hg) 0.14 microgram per gram (dry) (mg/g) FALSE 49889 Hg 2009 S031 Stack Port 3 Mercury

(Hg) 0.14 microgram per gram (dry) (mg/g) FALSE

Page 75sampling_run_fuel fuel_conc_MDL

Page 76