Unassociated Document


 



Exhibit 4.8.3 - Electronic Catalogue (1,3,4,5) - 30HXC









 




  





  











  






 


 




	  	  	
 


Carrier China


 


Carrier is affiliated to United Technologies. United Technologies ranks 126 in world’s 500 tops (2006), its business extends to architectural industry and aerospace industry around the world.


 


In 1902, Professor Carrier invented first set of scientific air-conditioning system. Since then, carrier’s complete series products and system resolution have become first choice of many world-renowned buildings.


 


In 2007, carrier’s sales revenue reaches 14.6 billion US dollars, leading in the whole industry. Its distributors’ network covers over 170 countries. Carrier is now world’s biggest HVAC manufacturer.


 


Carrier China has 11 companies, 40 sales service offices and 2,500 employees.


 


As the world-class factory, Carrier Yileng has several advanced production lines of units and compressors, covering main units of commercial and residential central air-conditioning systems and air terminal products. The various products can meet diversifying demands from different customers.









 



	
Index

	 	  
	  	 	  
	
Type Explanation

	 	1
	
Specification

	 	1
	
Cooling Capacity

	 	1
	  	 	  
	
Characteristics of units

	 	2
	  	 	  
	
Performance Table

	 	4
	  	 	  
	
Outline Dimensions

	 	8
	  	 	  
	
Unit Hoisting

	 	12
	
Foundation Dimensions

	 	12
	  	 	  
	
Ice Storage Application Performance Table

	 	13
	
Option Explanation

	 	13
	
On-site Wiring Diagram

	 	13





 




  





  











  






 


Type Explanation


 





 


Specification




	 	 	 	 	 	 	 	 	 
	  	 	  	 	  	 	
30HXY

	 	30HXC
	Type	 	
110B

	 	
130B

	 	
165B

	 	
200B

	 	
250B

	 	
300B

	 	
350B

	 	
400B


	
Nominal Cooling Capacity

	 	
kW

	 	
329

	 	
455

	 	
574

	 	
686

	 	
875

	 	
1027

	 	
1204

	 	
1366


	
Cold Amount Regulation Number

	 	
104kcal/h

	 	
30

	 	
40

	 	
50

	 	
60

	 	
75

	 	
90

	 	
105

	 	
120


	  	 	  	 	  	 	
3

	 	
6

	 	
6

	 	
6

	 	
8

	 	
8

	 	
10

	 	
10


	
Minimum Cold Amount

	 	
%

	 	
40

	 	
19

	 	
19

	 	
21

	 	
14

	 	
14

	 	
10

	 	
10


	
Compressor

	 	
Loop A

	 	
No

	 	
1

	 	
2

	 	
2

	 	
2

	 	
2

	 	
2

	 	
2

	 	
2


	  	 	
Loop B

	 	
No

	 	
-

	 	
-

	 	
-

	 	
-

	 	
1

	 	
1

	 	
2

	 	
2


	  	 	
In/out Water Temperature

	 	
°C

	 	  	 	  	 	  	 	12/7	 	  	 	  	 	  
	Evaporatorr	 	
Flow Rate

	 	
m3/h

	 	
57

	 	
78

	 	
99

	 	
118

	 	
150

	 	
177

	 	
207

	 	
235


	  	 	
Water Pressure Drop

	 	
kPa

	 	
65

	 	
45

	 	
50

	 	
66

	 	
66

	 	
73

	 	
74

	 	
75


	  	 	
In/out Diameter

	 	
Dg

	 	
100

	 	
125

	 	
125

	 	
125

	 	
150

	 	
150

	 	
200

	 	
200


	  	 	
In/out Water Temperature

	 	
°C

	 	  	 	  	 	  	 	30/35	 	  	 	  	 	  
	Condenser	 	Flow Rate	 	
m3/h

	 	
69

	 	
95

	 	
120

	 	
143

	 	
182

	 	
214

	 	
251

	 	
284


	  	 	
Water Pressure Drop

	 	
kPa

	 	
63

	 	
83

	 	
77

	 	
69

	 	
68

	 	
59

	 	
68

	 	
69


	  	 	
In/out Diameter

	 	
Dg

	 	
125

	 	
125

	 	
125

	 	
125

	 	
200

	 	
200

	 	
200

	 	
200


	  	 	
Power Supply

	 	  	 	  	 	  	 	  	 	
380V-3Ph-50Hz

	 	  	 	  	 	  
	
Motor

	 	
Input Power Rated operational

	 	
kW

	 	
71

	 	
98

	 	
122

	 	
144

	 	
186

	 	
217

	 	
256

	 	
288


	  	 	
power

	 	
A

	 	
134

	 	
172

	 	
214

	 	
253

	 	
218/108

	 	
254/127

	 	
225/225

	 	
253/253


	  	 	
(Star /Triangle ) Max

	 	  	 	  	 	  	 	  	 	  	 	  	 	  	 	  	 	  
	  	 	
Current for Start Up

	 	
A

	 	
328

	 	
314

	 	
374

	 	
465

	 	
443/288

	 	
510/351

	 	
443/443

	 	
510/510


	HFC-134a	 	Loop A	 	kg	 	
78

	 	
90

	 	
102

	 	
130

	 	
107

	 	
120

	 	
90

	 	
110


	Filling Amount	 	Loop B	 	
kg

	 	
-

	 	
-

	 	
-

	 	
-

	 	
75

	 	
80

	 	
109

	 	
137


	
Unit Weight(Include Refrigerant)

	 	
kg

	 	
1929

	 	
2446

	 	
2520

	 	
2957

	 	
4258

	 	
4378

	 	
5055

	 	
5223


	Operational Weight	 	
kg

	 	
2089

	 	
2589

	 	
2685

	 	
3153

	 	
4618

	 	
4738

	 	
5518

	 	
5686


	
Outline Dimensions

	 	
Length

	 	
mm

	 	
2556

	 	
2988

	 	
2988

	 	
2988

	 	
3512

	 	
3512

	 	
4021

	 	
4021


	  	 	
Width

	 	
mm

	 	
980

	 	
980

	 	
980

	 	
980

	 	
1015

	 	
1015

	 	
1015

	 	
1015


	  	 	
Height

	 	
mm

	 	
1910

	 	
1816

	 	
1816

	 	
1921

	 	
2060

	 	
2060

	 	
2112

	 	
2112









 


Note:


1. The standard design pressure of units is 1.0MPa


2. 110B-200B is single-channel power supply, 250B-400B is double-channel power supply, above current parameters please refer to loop marks.


 


Cooling Capacity


329~1355kW


 




  





1











  






 


Characteristics of Units







Carrier 30HXY/HXC Screw Chiller has no Chloride (no consumption to ozonosphere), and is efficient (consume less power, making contribution to reduce greenhouse effect), stable, easy to maintain, and low operation cost, which is the first choice of central air conditioning system for hotel, restaurant, office, school, hospital and industrial and mining establishments.







Structural Characteristics of Units



	
1.

	
Powerful Pro-Dialog control system, direct-viewing display, and simple operation








	
2.

	
Full-liquid evaporator with reinforced heat-transfer pipes, featuring high heat transfer efficiency








	
3.

	
Electronic expansion valve is agilely controllable.








	
4.

	
Stop valve equipped with refrigerants is easy for maintenance.








	
5.

	
External second-stage oil separator conceal installed inside evaporator by Carrier’s patent technology has high efficiency of separation








	
6.

	
When releasing from factory, evaporator and condenser are fitted with connection pipes and clamps, which are easy for installation.












Characteristics of Compressor



	
1.

	
The compressor can be repaired on-site and Carrier designs dual-screw compressor for HFC-134a








	
2.

	
Semi-closed motor is parallel with compressor, which gears up the system, so that compact structure can be realized.








	
3.

	
Use aerospace gear AGMA12 (the highest grade of American Gear Manufacturer's Association), which runs quietly and is sturdy and durable.








	
4.

	
Employing computer optimization design to produce completely ne w concept tooth of rotor, machining precision of major components can reach micro-size, as a result, compressor is efficient and leakage rate is tiny.








	
5.

	
Use refrigerants to cool motor, and motor can work reliably under low temperature.








	
6.

	
Plunger type unloading device, simple and reliable structure, no internal loss








	
7.

	
Unique design internal silencer reduces gas pulsation of exhaust gas efficiently












Simple and Easy Installation



	
l

	
Compact structure, less space demand, save machine room’s space








	
l

	
The maximum width of units is only 1015mm, which can easily pass through door frame








	
l

	
Whole set of units releases from factory, and the cooling medium has been filled inside








	
l

	
When installing, only need connect water pipe and power supply of evaporator and condenser












Low Operation and Maintenance Cost



	
l

	
The unit is driven by several sets of compressor, wide adjustment scope of refrigerating capacity, high efficient partial loading








	
l

	
The units adopts double-loop design, stable and low maintenance cost












Low Noise (Three-stage noise elimination)


Internal silencer: rational stream guidance of exhaust air, efficiently reduce noise caused by gas pulsation of high pressure exhaust gas


Silencer of gas exhaust pipeline: transform part of sound energy into heat energy, reducing the noise of units


Mute chassis: addition of another noise barrier, significantly reduce noise’s transfer to the machine room


(Refer to the following pictures)


 




  





2











  






 


Microcomputer control system has user-friendly interface and clear flow chart display, which is easy to instruct and operate by powerful diagnosis, security protection and communication functions. It employs PID control to keep stable water temperature from evaporator, effectively keep the units in operation and its stability and economy efficiency.







Friendly Human-Computer Interface



	
l

	
Colorful user panel, provide LED digital display of operation and control parameters, direct-viewing








	
l

	
The unit flow chart clearly displays on user panel, providing immediate access to major operation parameters such as suction/exhaust gas, temperature, running hours of compressor








	
l

	
Quick access to and modify all operation and control parameters by menu operations












Advanced Control Function



	
l

	
Provide local, remote and CCN network to control units start or stop.








	
l

	
Advanced EXV electronic expansion valve is driven by 1500-stage stepper motor, which matches screw compressor and full-liquid evaporator, ensuring stable and efficient operation under full or partial loading.








	
l

	
Automatically control each refrigeration loops, and start stop of each compressor in each loop, as well as up/down load, in order to balance the operation time of each loop and compressor.








	
l

	
Realize interlock control between units and cold water and chilled water to assure units run under efficient and secure conditions.








	
l

	
Provide “requirement limitation” function that limits the maximum refrigerating capacity of units through power control. The function can be used for energy management of multi-units, realizing the optimization of whole system operation efficiency by limiting the cold amount of individual unit.








	
l

	
When unit starts up, it will reduce flow rate to control water temperature within adjustable scope (0.1-1.1/min), in order to avoid energy loss caused by low temperature water. It will promote energy efficiency ratio of unit, prolong unit’s lifetime.








	
l

	
It offers “Energy save Restoration” function, which will settle a negative correction of cold capacity in accordance with variation tendency of outdoor temperature or return water temperature (provide users with temperature signals), so that unnecessary energy waste can avoid. And it immediately matches the external reducing fluctuation tendency to raise the operation efficiency of units.







 


Strong diagnosis function



	
l

	
Before starting up the unit, the function will quickly confirm every switch, sensor, voltage and compressor by analog inspection.








	
l

	
During its operation, human-computer interface will display a variety of setting points and real operation parameters, monitoring units’ operation. When it is necessary, the system will alarm.








	
l

	
The unit may provide more than 140 display and alarm information. The operator can resort to relevant solution to remove faults by alarm information.












Complete Security Protection Function



	
l

	
The system provides functions such as temperature of cold water is too low, oil pressure is low, pressure of refrigerating fluid is too high, leak current, motor overload, voltage too high or too low, open-phase protection and many others.












Advanced Group Control Function


Every set of unit can provide RS485 Standard serial interface, with which can realize group control to multiple-units, if through CNN network (need phase). The system can connect with the counterparts of other buildings; the standard protocol includes BACnet/Modbus/Lonwork.


 




  





3











  






 


Performance Table


 



30HXY110B



	 	 	 	 	 	 	 	 	 	 	 
	
Ref. Capacity

	 	
Input Power

	 	
Evaporator

	 	
Condenser


	  	 	  	 	
Cold water

	 	
Cold Water

	 	
Flow Rate

	 	
Chill Water

	 	
Chill Water

	 	
Chill Water


	
(kW)

	 	
(kW)

	 	
out Tep(°C)

	 	
in Tep(°C)

	 	
(m3 / h)

	 	
Out Tep(°C)

	 	
In Tep(°C)

	 	
(m3 / h)


	
316

	 	
64

	 	  	 	  	 	
54

	 	
31

	 	
26

	 	
65


	
312

	 	
67

	 	5	 	10	 	
54

	 	
33

	 	
28

	 	
65


	
308

	 	
70

	 	  	 	  	 	
53

	 	
35

	 	
30

	 	
65


	
305

	 	
74

	 	  	 	  	 	
52

	 	
37

	 	
32

	 	
65


	
326

	 	
64

	 	  	 	  	 	
56

	 	
31

	 	
26

	 	
67


	
322

	 	
67

	 	 6	 	11	 	
55

	 	
33

	 	
28

	 	
67


	
319

	 	
70

	 	  	 	  	 	
55

	 	
35

	 	
30

	 	
67


	
315

	 	
74

	 	  	 	  	 	
54

	 	
37

	 	
32

	 	
67


	
336

	 	
65

	 	  	 	  	 	
58

	 	
31

	 	
26

	 	
69


	
333

	 	
68

	 	7	 	
12

	 	
57

	 	
33

	 	
29

	 	
69


	
329

	 	
71

	 	  	 	  	 	
57

	 	
35

	 	
30

	 	
69


	
325

	 	
74

	 	  	 	  	 	
56

	 	
37

	 	
32

	 	
69


	
347

	 	
65

	 	  	 	  	 	
60

	 	
31

	 	
26

	 	
71


	
343

	 	
68

	 	8	 	13	 	
59

	 	
33

	 	
28

	 	
71


	
339

	 	
71

	 	  	 	  	 	
58

	 	
35

	 	
30

	 	
70


	
335

	 	
75

	 	  	 	  	 	
58

	 	
37

	 	
32

	 	
70


	
357

	 	
65

	 	  	 	  	 	
61

	 	
31

	 	
26

	 	
73


	
353

	 	
68

	 	
9

	 	14	 	
61

	 	
33

	 	
28

	 	
73


	
349

	 	
72

	 	  	 	  	 	
60

	 	
35

	 	
30

	 	
72


	
345

	 	
75

	 	  	 	  	 	
59

	 	
37

	 	
32

	 	
72


	
367

	 	
65

	 	  	 	 	 	
63

	 	
31

	 	
26

	 	
74


	
363

	 	
68

	 	10	 	15	 	
62

	 	
33

	 	
28

	 	
74


	
360

	 	
72

	 	  	 	  	 	
62

	 	
38

	 	
30

	 	
74


	
355

	 	
75

	 	  	 	  	 	
61

	 	
37

	 	
32

	 	
74












30HXC130B





	 	 	 	 	 	 	 	 	 	 	 
	
Ref. Capacity

	 	
Input Power

	 	
Evaporator

	 	
Condenser


	  	 	  	 	
Cold water

	 	
Cold Water

	 	
Flow Rate

	 	
Chill Water

	 	
Chill Water

	 	
Chill Water


	
(kW)

	 	
(kW)

	 	
out Tep(°C)

	 	
in Tep(°C)

	 	
(m3 / h)

	 	
Out Tep(°C)

	 	
In Tep(°C)

	 	
(m3 / h)


	
439

	 	
89

	 	  	 	  	 	
76

	 	
31

	 	
26

	 	
91


	
431

	 	
93

	 	5	 	10	 	
74

	 	
33

	 	
28

	 	
90


	
424

	 	
98

	 	  	 	  	 	
73

	 	
35

	 	
30

	 	
90


	
416

	 	
102

	 	  	 	  	 	
72

	 	
37

	 	
32

	 	
89


	
456

	 	
89

	 	  	 	  	 	
78

	 	
31

	 	
26

	 	
94


	
448

	 	
93

	 	6	 	
11

	 	
77

	 	
33

	 	
28

	 	
93


	
439

	 	
98

	 	  	 	  	 	
76

	 	
35

	 	
30

	 	
92


	
430

	 	
103

	 	  	 	  	 	
74

	 	
37

	 	
32

	 	
92


	
473

	 	
90

	 	  	 	  	 	
81

	 	
31

	 	
26

	 	
97


	
464

	 	
94

	 	
7

	 	12	 	
80

	 	
33

	 	
28

	 	
96


	
455

	 	
98

	 	  	 	  	 	
78

	 	
35

	 	
30

	 	
95


	
447

	 	
103

	 	  	 	  	 	
77

	 	
37

	 	
32

	 	
95


	
488

	 	
90

	 	  	 	  	 	
84

	 	
31

	 	
26

	 	
99


	
480

	 	
94

	 	8	 	13	 	
82

	 	
33

	 	
28

	 	
99


	
472

	 	
99

	 	  	 	  	 	
81

	 	
35

	 	
30

	 	
98


	
462

	 	
103

	 	  	 	  	 	
79

	 	
37

	 	
32

	 	
97


	
505

	 	
90

	 	  	 	  	 	
87

	 	
31

	 	
26

	 	
102


	
495

	 	
95

	 	9	 	14	 	
85

	 	
33

	 	
28

	 	
101


	
486

	 	
99

	 	  	 	  	 	
84

	 	
35

	 	
30

	 	
101


	
478

	 	
104

	 	  	 	  	 	
82

	 	
37

	 	
32

	 	
100


	
521

	 	
91

	 	  	 	  	 	
90

	 	
31

	 	
6

	 	
105


	
512

	 	
95

	 	
10

	 	15	 	
88

	 	
33

	 	
28

	 	
104


	
503

	 	
99

	 	  	 	  	 	
87

	 	
35

	 	
30

	 	
104


	
493

	 	
104

	 	  	 	  	 	
85

	 	
37

	 	
32

	 	
103







 




  





4











  






 


Performance Table


 


30HXC165B



	 	 	 	 	 	 	 
	
Ref. Capacity

	 	
Input Power

	 	
evaporator

	 	
Condenser


	  	 	  	 	
Cold water

	 	
Cold Water

	 	
Flow Rate

	 	
Chill Water

	 	
Chill Water

	 	
Chill Water


	
(kW)

	 	
(kW)

	 	
out Tep(°C)

	 	
in Tep(°C)

	 	
(m3 / h)

	 	
Out Tep(°C)

	 	
In Tep(°C)

	 	
(m3 / h)


	
554

	 	
110

	 	  	 	  	 	
95

	 	
31

	 	
26

	 	
114


	
544

	 	
115

	 	5	 	10	 	
94

	 	
33

	 	
28

	 	
113


	
533

	 	
122

	 	  	 	  	 	
92

	 	
35

	 	
30

	 	
113


	
524

	 	
127

	 	  	 	  	 	
90

	 	
37

	 	
32

	 	
112


	
575

	 	
111

	 	  	 	  	 	
99

	 	
31

	 	
26

	 	
118


	
564

	 	
117

	 	
6

	 	11	 	
97

	 	
33

	 	
28

	 	
117


	
554

	 	
122

	 	  	 	  	 	
95

	 	
35

	 	
30

	 	
116


	
543

	 	
128

	 	  	 	  	 	
93

	 	
37

	 	
32

	 	
115


	
595

	 	
111

	 	 	 	  	 	
102

	 	
31

	 	
26

	 	
121


	
586

	 	
117

	 	
7

	 	12	 	
101

	 	
33

	 	
28

	 	
121


	
574

	 	
122

	 	  	 	  	 	
99

	 	
35

	 	
30

	 	
120


	
563

	 	
128

	 	  	 	  	 	
97

	 	
37

	 	
32

	 	
119


	
617

	 	
111

	 	  	 	  	 	
106

	 	
31

	 	
29

	 	
125


	
606

	 	
117

	 	
8

	 	13	 	
104

	 	
33

	 	
28

	 	
124


	
594

	 	
123

	 	  	 	  	 	
102

	 	
35

	 	
30

	 	
123


	
584

	 	
128

	 	  	 	  	 	
100

	 	
37

	 	
32

	 	
122


	
637

	 	
111

	 	  	 	  	 	
110

	 	
31

	 	
26

	 	
129


	
626

	 	
117

	 	
9

	 	14	 	
108

	 	
33

	 	
28

	 	
128


	
615

	 	
123

	 	  	 	  	 	
106

	 	
35

	 	
30

	 	
127


	
604

	 	
129

	 	  	 	  	 	
104

	 	
34

	 	
32

	 	
126


	
658

	 	
112

	 	  	 	  	 	
113

	 	
31

	 	
26

	 	
132


	
646

	 	
118

	 	
10

	 	
15

	 	
111

	 	
33

	 	
28

	 	
131


	
635

	 	
123

	 	  	 	  	 	
109

	 	
35

	 	
30

	 	
130


	
622

	 	
129

	 	  	 	  	 	
107

	 	
37

	 	
32

	 	
129












30HXC200B





	  	 	  	 	  	 	  	 	  	 	  	 	  	 	  
	
Ref. Capacity

	 	
Input Power

	 	
evaporator

	 	
Condenser


	  	 	  	 	
Cold water

	 	
Cold Water

	 	
Flow Rate

	 	
Chill Water

	 	
Chill Water

	 	
Chill Water


	
(kW)

	 	
(kW)

	 	
out Tep(°C)

	 	
in Tep(°C)

	 	
(m3 / h)

	 	
Out Tep(°C)

	 	
In Tep(°C)

	 	
(m3 / h)


	
658

	 	
129

	 	  	 	  	 	
113

	 	
31

	 	
26

	 	
135


	
651

	 	
137

	 	
5

	 	
10

	 	
112

	 	
33

	 	
28

	 	
135


	
644

	 	
143

	 	  	 	  	 	
111

	 	
35

	 	
30

	 	
135


	
636

	 	
150

	 	  	 	  	 	
109

	 	
37

	 	
32

	 	
135


	
680

	 	
130

	 	  	 	  	 	
117

	 	
31

	 	
26

	 	
139


	
672

	 	
137

	 	
6

	 	
11

	 	
116

	 	
33

	 	
28

	 	
139


	
664

	 	
143

	 	  	 	  	 	
114

	 	
35

	 	
30

	 	
139


	
657

	 	
151

	 	  	 	  	 	
113

	 	
37

	 	
32

	 	
139


	
701

	 	
130

	 	  	 	  	 	
121

	 	
31

	 	
26

	 	
143


	
694

	 	
138

	 	
7

	 	
12

	 	
119

	 	
33

	 	
28

	 	
143


	
686

	 	
144

	 	  	 	  	 	
118

	 	
35

	 	
30

	 	
143


	
678

	 	
151

	 	  	 	  	 	
117

	 	
37

	 	
32

	 	
143


	
723

	 	
131

	 	  	 	  	 	
124

	 	
31

	 	
26

	 	
147


	
715

	 	
138

	 	
8

	 	13	 	
123

	 	
33

	 	
28

	 	
147


	
708

	 	
144

	 	  	 	  	 	
122

	 	
35

	 	
30

	 	
146


	
699

	 	
152

	 	  	 	  	 	
120

	 	
37

	 	
32

	 	
146


	
744

	 	
131

	 	  	 	  	 	
128

	 	
31

	 	
26

	 	
151


	
737

	 	
139

	 	9	 	14	 	
127

	 	
33

	 	
28

	 	
151


	
728

	 	
145

	 	  	 	  	 	
125

	 	
35

	 	
30

	 	
150


	
720

	 	
152

	 	  	 	  	 	
124

	 	
37

	 	
32

	 	
150


	
766

	 	
134

	 	  	 	  	 	
64

	 	
31

	 	
26

	 	
155


	
758

	 	
139

	 	10	 	
15

	 	
64

	 	
33

	 	
28

	 	
154


	
750

	 	
145

	 	  	 	  	 	
63

	 	
35

	 	
30

	 	
154


	
741

	 	
153

	 	  	 	  	 	
62

	 	
37

	 	
32

	 	
154







 




  





5











  






 


Performance Table

 


30HXC250B





	 	 	 	 	 	 	 
	
Ref. Capacity

	 	
Input Power

	 	
evaporator

	 	
Condenser


	  	 	  	 	
Cold water

	 	
Cold Water

	 	
Flow Rate

	 	
Chill Water

	 	
Chill Water

	 	
Chill Water


	
(kW)

	 	
(kW)

	 	
out Tep(°C)

	 	
in Tep(°C)

	 	
(m3 / h)

	 	
Out Tep(°C)

	 	
In Tep(°C)

	 	
(m3 / h)


	
845

	 	
168

	 	  	 	  	 	
145

	 	
31

	 	
29

	 	
174


	
829

	 	
176

	 	
5

	 	
10

	 	
143

	 	
33

	 	
28

	 	
173


	
813

	 	
185

	 	  	 	  	 	
140

	 	
35

	 	
30

	 	
172


	
797

	 	
193

	 	  	 	  	 	
137

	 	
37

	 	
32

	 	
170


	
877

	 	
169

	 	  	 	  	 	
151

	 	
31

	 	
26

	 	
180


	
860

	 	
177

	 	6	 	11	 	
148

	 	
33

	 	
28

	 	
178


	
844

	 	
185

	 	  	 	  	 	
145

	 	
35

	 	
30

	 	
177


	
827

	 	
193

	 	  	 	  	 	
142

	 	
37

	 	
32

	 	
175


	
909

	 	
170

	 	  	 	  	 	
156

	 	
31

	 	
26

	 	
186


	
892

	 	
178

	 	
7

	 	12	 	
153

	 	
33

	 	
28

	 	
184


	
875

	 	
186

	 	  	 	  	 	
150

	 	
35

	 	
30

	 	
182


	
858

	 	
194

	 	  	 	  	 	
148

	 	
37

	 	
32

	 	
181


	
941

	 	
170

	 	  	 	  	 	
162

	 	
31

	 	
26

	 	
191


	
924

	 	
178

	 	8	 	13	 	
159

	 	
33

	 	
28

	 	
190


	
906

	 	
187

	 	  	 	  	 	
156

	 	
35

	 	
30

	 	
188


	
889

	 	
195

	 	  	 	  	 	
153

	 	
37

	 	
32

	 	
186


	
974

	 	
171

	 	  	 	  	 	
167

	 	
31

	 	
26

	 	
197


	
956

	 	
179

	 	9	 	14	 	
164

	 	
33

	 	
28

	 	
195


	
937

	 	
187

	 	  	 	  	 	
161

	 	
35

	 	
30

	 	
193


	
920

	 	
195

	 	  	 	  	 	
158

	 	
37

	 	
32

	 	
192


	
1005

	 	
172

	 	  	 	  	 	
173

	 	
31

	 	
26

	 	
202


	
988

	 	
180

	 	10	 	
15

	 	
170

	 	
33

	 	
28

	 	
201


	
969

	 	
188

	 	  	 	  	 	
167

	 	
35

	 	
30

	 	
199


	
950

	 	
196

	 	  	 	  	 	
163

	 	
37

	 	
32

	 	
197












30HXC300B





	 	 	 	 	 	 	 
	
Ref. Capacity

	 	
Input Power

	 	
evaporator

	 	
Condenser


	  	 	  	 	
Cold water

	 	
Cold Water

	 	
Flow Rate

	 	
Chill Water

	 	
Chill Water

	 	
Chill Water


	
(kW)

	 	
(kW)

	 	
out Tep(°C)

	 	
in Tep(°C)

	 	
(m3 / h)

	 	
Out Tep(°C)

	 	
In Tep(°C)

	 	
(m3 / h)


	
985

	 	
196

	 	  	 	  	 	
169

	 	
31

	 	
26

	 	
203


	
974

	 	
205

	 	5	 	10	 	
167

	 	
33

	 	
28

	 	
203


	
963

	 	
215

	 	  	 	  	 	
166

	 	
35

	 	
30

	 	
203


	
951

	 	
225

	 	  	 	  	 	
164

	 	
37

	 	
32

	 	
202


	
1017

	 	
197

	 	  	 	  	 	
175

	 	
31

	 	
26

	 	
209


	
1007

	 	
206

	 	
6

	 	11	 	
173

	 	
33

	 	
28

	 	
209


	
996

	 	
216

	 	  	 	  	 	
171

	 	
35

	 	
30

	 	
208


	
983

	 	
226

	 	  	 	  	 	
169

	 	
37

	 	
32

	 	
208


	
1051

	 	
198

	 	  	 	  	 	
181

	 	
31

	 	
26

	 	
215


	
1039

	 	
206

	 	
7

	 	12	 	
179

	 	
33

	 	
28

	 	
214


	
1027

	 	
217

	 	  	 	  	 	
177

	 	
35

	 	
30

	 	
214


	
1014

	 	
227

	 	  	 	  	 	
174

	 	
37

	 	
32

	 	
213


	
1082

	 	
199

	 	  	 	  	 	
186

	 	
31

	 	
26

	 	
220


	
1070

	 	
207

	 	
8

	 	13	 	
184

	 	
33

	 	
28

	 	
220


	
1058

	 	
218

	 	  	 	  	 	
182

	 	
35

	 	
30

	 	
220


	
1046

	 	
228

	 	  	 	  	 	
180

	 	
37

	 	
32

	 	
219


	
1115

	 	
200

	 	  	 	  	 	
192

	 	
31

	 	
26

	 	
226


	
1103

	 	
208

	 	
9

	 	14	 	
190

	 	
33

	 	
28

	 	
225


	
1091

	 	
218

	 	  	 	  	 	
188

	 	
35

	 	
30

	 	
225


	
1078

	 	
229

	 	  	 	  	 	
185

	 	
37

	 	
32

	 	
225


	
1148

	 	
200

	 	  	 	  	 	
197

	 	
31

	 	
26

	 	
232


	
1135

	 	
209

	 	10	 	15	 	
195

	 	
33

	 	
28

	 	
231


	
1122

	 	
219

	 	  	 	  	 	
193

	 	
35

	 	
30

	 	
231


	
1110

	 	
230

	 	  	 	  	 	
191

	 	
37

	 	
32

	 	
230














  





6











  






 






Performance Table








	
30HXC350B

	 	  	 	  
	  	 	  	 	  	 	  
	  	 	  	 	
evaporator

	 	
Condenser


	
Ref. Capacity

	 	
Input Power

	 	
Cold water

	 	
Cold Water

	 	
Flow Rate out

	 	
Chill Water

	 	
Chill Water

	 	
Chill Water


	
(kW)

	 	
(kW)

	 	
Tep( ̊C)

	 	
in Tep( ̊C)

	 	
(m3 / h)

	 	
Out Tep( ̊C)

	 	
In Tep( ̊C)

	 	
(m3 / h)


	
1161


1140


1117


1095

	 	
231


243


254


266

	 	
5

	 	
10

	 	
200


196


192


188

	 	
31


33


35


37

	 	
26


28


30


32

	 	
239


238


236


234


	
1206


1184


1161


1138

	 	
232


255


255


267

	 	
6

	 	
11

	 	
207


200


200


196

	 	
31


35


35


37

	 	
26


30


30


32

	 	
247


243


243


242


	
1250


1227


1204


1180

	 	
233


245


256


267

	 	
7

	 	
12

	 	
215


211


207


203

	 	
31


33


35


37

	 	
26


28


30


32

	 	
255


253


251


249


	
1295


1270


1247


1223

	 	
234


245


257


268

	 	
8

	 	
13

	 	
223


218


215


210

	 	
31


333


35


37

	 	
26


28


30


32

	 	
263


261


259


256


	
1339


1315


1291


1265

	 	
235


246


258


269

	 	
9

	 	
14

	 	
230


226


222


218

	 	
31


33


35


37

	 	
26


28


30


32

	 	
271


268


266


264


	
1382


358


1333


1308

	 	
236


247


258


270

	 	
10

	 	
15

	 	
238


234


229


225

	 	
31


33


35


37

	 	
26


28


30


32

	 	
278


276


274


271







 




	
30HXC400B

	 	  	 	  
	  	 	  	 	  	 	  
	  	 	  	 	
evaporator

	 	
Condenser


	
Ref. Capacity

	 	
Input Power

	 	
Cold water

	 	
Cold Water

	 	
Flow Rate out

	 	
Chill Water

	 	
Chill Water

	 	
Chill Water


	
(kW)

	 	
(kW)

	 	
Tep( ̊C)

	 	
in Tep( ̊C)

	 	
(m3 / h)

	 	
Out Tep( ̊C)

	 	
In Tep( ̊C)

	 	
(m3 / h)


	
1310


1296


1282


1265

	 	
259


273


286


299

	 	
5

	 	
10

	 	
225


223


220


218

	 	
31


33


35


37

	 	
26


28


30


32

	 	
270


270


270


269


	
1353


1339


1324


1308

	 	
261


274


287


301

	 	
6

	 	
11

	 	
233


230


228


225

	 	
31


33


35


37

	 	
26


28


30


32

	 	
278


277


277


277


	
1396


1382


1366


1350

	 	
263


276


288


303

	 	
7

	 	
12

	 	
240


238


235


232

	 	
31


33


35


37

	 	
26


27


30


32

	 	
285


285


284


284


	
1441


1425


1408


1392

	 	
264


277


290


305

	 	
8

	 	
13

	 	
248


245


242


239

	 	
31


33


35


37

	 	
26


28


30


32

	 	
293


293


292


292


	
1484


1468


1451


1435

	 	
265


278


291


306

	 	
9

	 	
14

	 	
255


252


250


247

	 	
31


33


35


37

	 	
26


28


30


32

	 	
301


300


300


299


	
1528


1511


1495


1476

	 	
266


379


292


307

	 	
10

	 	
15

	 	
263


260


257


254

	 	
31


33


35


37

	 	
26


28


30


32

	 	
309


308


307


307













  





7










 






Outline Dimension




 


30HXY110B
















Note:






	
1.

	
picture 1 is space for maintenance, 2 is space for drawn pipe (the drawn pipes on right side and left side can exchange)








	
2.

	
Pi and Pi’ are two sets of holes for stone bolts, which can select one set to install








	
3.

	
On-site water pipe uses clamp connection, clamp and fitting connection pipes are provided randomly (blue section), and the length of connection pipe is 120mm.









 



	
Type

	 	
A

	 	 	
B

	 	 	
C

	 	 	
D

	 	 	
E

	 	
S

	 	
R


	
30HXY110B

	 	238	 	 	287	 	 	320	 	 	279	 	 	1910	 	
Dg100

	 	
Dg125







 



	
Loading Distribution(kg)

	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	
Type

	 	
P1

	 	 	
P2

	 	 	
P3

	 	 	
P4

	 	 	
P1’

	 	 	
P2’

	 	 	
P3’

	 	 	
P4’

	 	 	
PT

	 
	
30HXY110B

	 	601	 	 	451	 	 	590	 	 	447	 	 	619	 	 	473	 	 	568	 	 	429	 	 	2089	 









  





8










 




 


30HXC130B~200B
















Note:






	
4.

	
picture 1 is space for maintenance, 2 is space for drawn pipe (the drawn pipes on right side and left side can exchange)








	
5.

	
Pi and Pi’ are two sets of holes for stone bolts, which can select one set to install








	
6.

	
On-site water pipe uses clamp connection, clamp and fitting connection pipes are provided randomly (blue section), and the length of connection pipe is 120mm.
















	
Type

	 	
A

	 	 	
B

	 	 	
C

	 	 	
D

	 	 	
E

	 	 	
S

	 	 	
R

	 
	
30HXC130B


30HXC165B

	 	210	 	 	302	 	 	320	 	 	235	 	 	1816	 	 	
Dg125

	 	 	
Dg125

	 
	
30HXC200B

	 	272	 	 	297	 	 	320	 	 	235	 	 	1921	 	 	
Dg125

	 	 	
Dg125

	 





 



	
Loading Distribution(kg)

	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	
Type

	 	
P1

	 	 	
P2

	 	 	
P3

	 	 	
P4

	 	 	
P1’

	 	 	
P2’

	 	 	
P3’

	 	 	
P4’

	 	 	
PT

	 
	
30HXC130B

	 	804	 	 	543	 	 	741	 	 	501	 	 	840	 	 	506	 	 	773	 	 	470	 	 	2589	 
	
30HXC165B

	 	834	 	 	563	 	 	768	 	 	520	 	 	871	 	 	526	 	 	803	 	 	485	 	 	2685	 
	
30HXC200B

	 	978	 	 	662	 	 	903	 	 	610	 	 	1021	 	 	618	 	 	942	 	 	572	 	 	3153	 











  





9










 






Outline Dimension


 


30HXC250B~300B
















Note:






	
7.

	
picture 1 is space for maintenance, 2 is space for drawn pipe (the drawn pipes on right side and left side can exchange)








	
8.

	
Pi and Pi’ are two sets of holes for stone bolts, which can select one set to install








	
9.

	
On-site water pipe uses clamp connection, clamp and fitting connection pipes are provided randomly (blue section), and the length of connection pipe is 120mm.















	
Type

	 	
A

	 	 	
B

	 	 	
C

	 	 	
D

	 	 	
E

	 	 	
S

	 	 	
R

	 
	
30HXC250B


30HXC300B

	 	306	 	 	340	 	 	357.5	 	 	284	 	 	2060	 	 	
Dg150

	 	 	
Dg200

	 





 



	
Loading Distribution (kg)

	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 
	
type

	 	
P1

	 	 	
P2

	 	 	
P3

	 	 	
P4

	 	 	
P1’

	 	 	
P2’

	 	 	
P3’

	 	 	
P4’

	 	 	
PT

	 
	
30HXC250B

	 	1350	 	 	960	 	 	1355	 	 	953	 	 	1403	 	 	911	 	 	1396	 	 	908	 	 	4618	 
	
30HXC300B

	 	1388	 	 	988	 	 	1380	 	 	982	 	 	1440	 	 	937	 	 	1431	 	 	930	 	 	4738	 









  





10










 




 


30HXC350B~400B
















Note:






	
10.

	
picture 1 is space for maintenance, 2 is space for drawn pipe (the drawn pipes on right side and left side can exchange)








	
11.

	
Pi and Pi’ are two sets of holes for stone bolts, which can select one set to install








	
12.

	
On-site water pipe uses clamp connection, clamp and fitting connection pipes are provided randomly (blue section), and the length of connection pipe is 120mm.















	
type

	 	
A

	 	 	
B

	 	 	
C

	 	 	
D

	 	 	
E

	 	 	
S

	 	 	
R

	 
	
30HXC350B


30HXC400B

	 	290	 	 	379	 	 	340	 	 	309	 	 	2112	 	 	
Dg200

	 	 	
Dg200

	 











	
Loading Distribution (kg)

	 	 	 	 	 	 	 	 	 	 	 	 	 
	
type

	 	
P1

	 	 	
`P2

	 	 	
P3

	 	 	
P4

	 	 	
P1’

	 	 	
P2’

	 	 	
P3’

	 	 	
P4’

	 	 	
PT

	 
	
30HXC350B

	 	1799	 	 	1313	 	 	1391	 	 	1015	 	 	1864	 	 	1249	 	 	1438	 	 	967	 	 	5518	 
	
30HXC400B

	 	1851	 	 	1360	 	 	1432	 	 	1043	 	 	1918	 	 	1287	 	 	1486	 	 	995	 	 	5686	 









  





11










 









Unit Hoisting
















Note:Each supporting chain shall bear whole weight of equipment; the center of unit shall be on the spandrel girder.











Center of gravity





 




	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	  	
(mm)

	  
	
type

	  	
X

	  	  	
Y

	  	  	
Z

	  	  	
W (Min)

	  	  	
L (Min)

	  	  	
Operation Weight  (kg)

	  
	
30HXY110B

	  	
1156

	  	  	
398

	  	  	
900

	  	  	
1200

	  	  	
1828

	  	  	
2089

	  
	
30HXC130B

	  	
1299

	  	  	
405

	  	  	
892

	  	  	
1200

	  	  	
1828

	  	  	
2589

	  
	
30HXC165B

	  	
2685

	  
	
30HXC200B

	  	
1299

	  	  	
400

	  	  	
870

	  	  	
1200

	  	  	
1828

	  	  	
3153

	  
	
30HXC250B

	  	
1652

	  	  	
426

	  	  	
1031

	  	  	
1200

	  	  	
2515

	  	  	
4618

	  
	
30HXC300B

	  	
4738

	  
	
30HXC350B

	  	
1888

	  	  	
432

	  	  	
1103

	  	  	
1200

	  	  	
3113

	  	  	
5518

	  
	
30HXC400B

	  	
1877

	  	  	
438

	  	  	
1098

	  	  	
1200

	  	  	
3113

	  	  	
5686

	  









Foundation Dimensions





 







Note:




	
1.

	
If unit uses first generation mute chassis, the foundation shall be made as whole, and its surface should be horizontal. The dimensions of foundation is according to the outline dimensions of unit, each side in the length direction shall add more than 250mm, each side in the width direction shall add more than 150mm. The dash dot line shows foundation dimension of unit, after installing mute chassis.








	
2.

	
Four pieces of stone bolts, each one is M20X300








	
3.

	
The position for stone bolts can be 1 2 3 4 or 1' 2’ 3’ 4’ shown on the picture









 



	  	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	 	
(mm)

	 
	
Type

	 	
A

	 	 	
B

	 	 	
C

	 	 	
P

	 	 	
Q

	 	 	
R

	 
	
30HXY110B

	 	468	 	 	1600	 	 	2554	 	 	930	 	 	100	 	 	980	 
	
30HXC130B


30HXC165B


30HXC200B

	 	658	 	 	1546	 	 	2988	 	 	930	 	 	100	 	 	980	 
	
30HXC250B


30HXC300B

	 	650	 	 	2111	 	 	3512	 	 	965	 	 	100	 	 	1015	 
	
30HXC350B


30HXC400B

	 	710	 	 	2503	 	 	4021	 	 	965	 	 	100	 	 	1015	 









  





12










 





 


Ice Storage Application Performance Table








	
type

	 	
30HXY

	 	 	
30HXC

	 
	  	  	  	 	
110B

	 	 	
130B

	 	 	
165B

	 	 	
200B

	 	 	
250B

	 	 	
300B

	 	 	
350B

	 	 	
400B

	 
	
空调

	
制冷量

	
kW

	 	317	 	 	438	 	 	554	 	 	654	 	 	845	 	 	985	 	 	1161	 	 	1307	 
	
工况

	
输入功率

	
kW

	 	71	 	 	98	 	 	122	 	 	144	 	 	185	 	 	215	 	 	254	 	 	287	 
	
蓄冰

	
制冷量

	
kW

	 	211	 	 	270	 	 	336	 	 	436	 	 	509	 	 	656	 	 	699	 	 	869	 
	
工况

	
输入功率

	
kW

	 	69	 	 	94	 	 	119	 	 	140	 	 	179	 	 	207	 	 	246	 	 	277	 
	
额定工况电流

	
A

	 	131	 	 	171	 	 	213	 	 	251	 	 	323	 	 	375	 	 	444	 	 	501	 
	
最大启动电流

	
A

	 	328	 	 	314	 	 	374	 	 	465	 	 	575	 	 	650	 	 	745	 	 	840	 
	
蒸

	
流量

	
m3/h

	 	58	 	 	80	 	 	102	 	 	120	 	 	155	 	 	179	 	 	214	 	 	238	 
	
发

	
空调工况水压降

	
kPa

	 	80	 	 	54	 	 	64	 	 	80	 	 	81	 	 	89	 	 	91	 	 	92	 
	
器

	
蓄冰工况水压降

	
kPa

	 	139	 	 	96	 	 	109	 	 	126	 	 	76	 	 	84	 	 	104	 	 	88	 






 


Note:






	
1.

	
Work condition of air conditioner: cold water in/out temperature is 7/12°C, chilled water in/out temperature 30/35°C








	
2.

	
Work condition of ice storage: cold water outlet temperature is -6°C, chilled water inlet temperature is 30°C.








	
3.

	
refrigerating medium shall be 25%















Option Explanation


 






	
l

	
Interfaces of water room of evaporator and condenser can reverse respectively










Interface of water room of standard unit is on the right side (control cabinet is front side), the option offers left side interface.






	
l

	
Water room of evaporator and condenser can provide 1.6Mpa/2.1Mpa high bearing pressure options








	
l

	
Low temperature unit:










Temperature scope of low temperature ethylene glycol and salting liquid:-6°C~+4°C


Can provide minimum -10°C low temperature option, meeting technological demand






	
l

	
Mute Chassis










First generation mute chassis can denoise the unit over 10dB(A), easy for installation, no effect to maintenance and management of unit, handsome appearance (please see P2)













	
Type

	 	
Size(L x W x H) mm

	 	
Weight (kg)

	 	
Type

	 	
Size(L x W x H) mm

	 	
Weight (kg)


	
30HXY110B

	 	
2867 x 1192 x 2080

	 	
500

	 	
30HXY110B

	 	
When installing second generation

	 	
130


	
30HXC130B~30HXC200B

	 	
3315 x 1192 x 2143

	 	
600

	 	
30HXC130B

	 	
Generation Mute chassis

	 	
130


	
30HXC250B~30HXC300B

	 	
3724 x 1221 x 2212

	 	
700

	 	
30HXC165B

	 	
Chassis, outline is same

	 	
130


	
30HXC350B~30HXC400B

	 	
4333 x 1221 x 2312

	 	
800

	 	
30HXC200B

	 	
to the original set.

	 	
160


	
注:When ordering the equipment, user shall specific the detailed type on the contract.













On-site Wiring Diagram




 









  





13