Unassociated Document







Exhibit 4.8.64 -Design Drawings - Components in Distribution Box

















 


List of Components in Distribution Box








	
Owner Name: Shenyang Sunshine

	
P554


	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10








	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand


	  	
Lighting Distribution Box

	  	
Ampere(A)

	  	  	  
	
1

	
11MX(1st Floor)

	
XSAII-18

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C20/3P

	
20

	
1

	
D-11MX

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
8

	
MX11-1~8

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX11-9~10

	
Schneider


	
2

	
12MX(1st Floor)

	
XSAII-24

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C20/3P

	
20

	
1

	
D-12MX

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
12

	
MX12-1~12

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX12-13~14

	
Schneider


	
3

	
13MX(1st Floor)

	
XSAII-24

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-13MX

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
15

	
MX13-1~15

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX13-16~17

	
Schneider


	
4

	
14MX(1st Floor)

	
XSAII-24

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-14MX

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
15

	
MX14-1~15

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX14-16~17

	
Schneider


	
5

	
15MX(1st Floor)

	
XSAII-18

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C20/3P

	
20

	
1

	
D-15MX

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
8

	
MX15-1~8

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX15-9~10

	
Schneider


	
6

	
16MX(Half Floor)

	
XSAII-24

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C20/3P

	
20

	
1

	
D-16MX

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
14

	
MX16-1~14

	
Schneider







 



	
SUNTEC

	
Page 1 of 8

	
   







 




  





 











  














 


List of Components in Distribution Box








	
Owner Name: Shenyang Sunshine

	
P554


	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10








	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand


	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX16-15~16

	
Schneider


	
7

	
21MX(2nd Floor)

	
XSAII-24

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-21MX

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
10

	
MX21-1~10

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
5

	
MX21-11~15

	
Schneider


	
8

	
22MX(2nd Floor)

	
XSAII-24

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-22MX

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
3

	
MX22-1~3

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
10

	
MX22-4~13

	
Schneider


	
9

	
23MX(2nd Floor)

	
XSAII-24

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C25/3P

	
25

	
1

	
D-23MX

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
14

	
MX23-1~14

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C16/1P

	
16

	
2

	
MX23-15~16

	
Schneider


	
10

	
11MHX (1st Floor Evacuation)

	
XSAII-72

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C25/3P

	
25

	
1

	
D-11MHX

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
17

	
MHX11-1~17

	
Schneider


	
11

	
21MHX(2nd FloorEvacuation)

	
XSAII-72

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C25/3P

	
25

	
1

	
D-21MHX

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
10

	
MHX21-1~10

	
Schneider


	  	
Power Supply Box

	  	  	  	  	  
	
1

	
11DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-11DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
11DX-1~5

	
Schneider







 



	
SUNTEC

	
Page 2 of 8

	
   





 




  





 











  














 


List of Components in Distribution Box








	
Owner Name: Shenyang Sunshine

	
P554


	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10








	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand


	  	
Leakage Protection Breaker

	
DPNVigiC32

	
32+30mA

	
1

	
11DX-6

	
Schneider


	
2

	
12DX(1st Floor)

	
XSAII-36(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-12DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
12DX-1~5

	
Schneider


	
3

	
13DX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C25/3P

	
25

	
1

	
D-13DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
13DX-1~5

	
Schneider


	
4

	
14DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-14DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
14DX-1~5

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C20/1P

	
20

	
1

	
14DX-6

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
1

	
14DX-7

	
Schneider


	
5

	
15DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-15DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
6

	
15DX-1~6

	
Schneider


	
6

	
16DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-16DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
16DX-1~5

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
4

	
16DX-6~9

	
Schneider


	
7

	
17DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C40/3P

	
32

	
1

	
D-17DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
16DX-1~5

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
2

	
16DX-6~7

	
Schneider


	
8

	
18DX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality







 



	
SUNTEC

	
Page 3 of 8

	
   





 




  





 











  














 


List of Components in Distribution Box








	
Owner Name: Shenyang Sunshine

	
P554


	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10








	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand


	  	
Circuit Breaker

	
C65H-63/C25/3P

	
25

	
1

	
D-18DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
3

	
16DX-1~3

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
2

	
16DX-4~5

	
Schneider


	
8

	
19DX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C50/3P

	
50

	
1

	
D-18DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
18DX-1~5

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
3

	
18DX-6~8

	
Schneider


	
9

	
110DX(1st Floor)

	
XSAII-12(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C25/3P

	
25

	
1

	
D-110DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC16

	
16+30mA

	
3

	
110DX-1~3

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
3

	
110DX-4~6

	
Schneider


	
10

	
111DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-111DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
4

	
111DX-1~4

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
3

	
111DX-5~7

	
Schneider


	
11

	
112DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-112DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
112DX-1~5

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
1

	
112DX-6

	
Schneider


	
12

	
113DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-113DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
5

	
113DX-1~5

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
4

	
113DX-6~9

	
Schneider


	
14

	
114DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality







 



	
SUNTEC

	
Page 4 of 8

	
   





 




  





 











  














 


List of Components in Distribution Box








	
Owner Name: Shenyang Sunshine

	
P554


	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10








	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand


	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-114DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
1

	
114DX-1

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
4

	
114DX-2~5

	
Schneider


	
15

	
115DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-115DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
7

	
115DX-1~7

	
Schneider


	
16

	
116DX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C63/3P

	
63

	
1

	
D-116DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC32

	
32+30mA

	
3

	
116DX-1~3

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C63/1P

	
63

	
2

	
116DX-4~5

	
Schneider


	
17

	
117DX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-117DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20-+30mA

	
3

	
117DX-1~3

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
2

	
117DX-4~5

	
Schneider


	
18

	
21DX(2nd Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-21DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20-+30mA

	
6

	
21DX-1~6

	
Schneider


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
2

	
21DX-7~8

	
Schneider


	
19

	
22DX(2nd Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-22DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20-+30mA

	
6

	
22DX-1~6

	
Schneider


	
20

	
23DX(2nd Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-23DX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20-+30mA

	
6

	
23DX-1~5

	
Schneider







 



	
SUNTEC

	
Page 5 of 8

	
   





 




  





 











  














 


List of Components in Distribution Box








	
Owner Name: Shenyang Sunshine

	
P554


	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10








	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand


	  	
Circuit Breaker

	
C65H-63/C10/1P

	
10

	
2

	
23DX-6~7

	
Schneider


	  	
Power Supply Box

	  	  	  	  	  
	
1

	
11EX(1st Floor)

	
XSAII-84(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C50/3P

	
50

	
1

	
D-11EX

	
Schneider


	  	
Leakage Protection Breaker

	
C65H/63/16/4+VigiC65ELE

	
16+30mA

	
5

	
11EX-1~5

	
Schneider


	
2

	
12EX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C50/3P

	
50

	
1

	
D-12EX

	
Schneider


	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
7

	
11EX-1~7

	
Schneider


	
3

	
13EX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C63/3P

	
63

	
1

	
D-13EX

	
Schneider


	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
9

	
11EX-1~9

	
Schneider


	
4

	
14EX(1st Floor)

	
XSAII-48(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C50/3P

	
50

	
1

	
D-14EX

	
Schneider


	  	
Leakage Protection Breaker

	
C65H/63/16/4+VigiC65ELE

	
16+30mA

	
6

	
14EX-1~6

	
Schneider


	
6

	
15EX(1st Floor)

	
XSAII-18(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C50/3P

	
50

	
1

	
D-15EX

	
Schneider


	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
7

	
15EX-1~7

	
Schneider


	
7

	
16EX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C63/3P

	
63

	
1

	
D-16EX

	
Schneider


	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
9

	
16EX-1~9

	
Schneider


	
8

	
17EX(1st Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-17EX

	
Schneider


	  	
Leakage Protection Breaker

	
C65H/63/D10/3P

	
10

	
7

	
17EX-1~7

	
Schneider


	
9

	
21EX(2nd Floor)

	
XSAII-24(Concealed Installation)

	  	  	  	
High Quality







 



	
SUNTEC

	
Page 6 of 8

	
   





 




  





 











  














 


List of Components in Distribution Box








	
Owner Name: Shenyang Sunshine

	
P554


	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10








	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand


	  	
Circuit Breaker

	
C65H-63/C50/3P

	
50

	
1

	
D-21EX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC32

	
32+30mA

	
7

	
21EX-1~7

	
Schneider


	
10

	
22EX(2nd Floor)

	
XSAII-36(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C63/3P

	
63

	
1

	
D-22EX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
10

	
22EX-1~10

	
Schneider


	
11

	
23EX(2nd Floor)

	
XSAII-36(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C40/3P

	
40

	
1

	
D-23EX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
8

	
23EX-1~8

	
Schneider


	
12

	
24EX(2nd Floor)

	
XSAII-36(Concealed Installation)

	  	  	  	
High Quality


	  	
Circuit Breaker

	
C65H-63/C32/3P

	
32

	
1

	
D-24EX

	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC20

	
20+30mA

	
6

	
24EX-1~6

	
Schneider


	  	
Maintenance Power Box (1st Floor)

	  	  	  	  	  
	
1

	
Maintenance Power Box

	
Non-Standard

	  	
4

	  	
High Quality


	  	
11JX、12JX、13JX、14JX

	  	  	  	  	  
	  	
Circuit Breaker

	
C65H/63/D63/3P

	
63

	
16

	
Incoming Line

	
Schneider


	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
16

	  	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC16

	
16+30mA

	
48

	  	
Schneider


	
1

	
Maintenance Power Box (Trench)

	
Non-Standard

	  	
6

	  	
High Quality


	  	
01JX、02JX、03JX、04JX、05JX、06JX

	  	  	  	  	  
	  	
Circuit Breaker

	
C65H/63/D63/3P

	
63

	
16

	
Incoming Line

	
Schneider


	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
16

	  	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC16

	
16+30mA

	
48

	  	
Schneider







 



	
SUNTEC

	
Page 7 of 8

	
   





 




  





 











  














 


List of Components in Distribution Box








	
Owner Name: Shenyang Sunshine

	
P554


	 	 
	
Project Name: Clean-room Installation Project

	
2009-2-10








	
Serial

	
Description

	
Specification

	
Circuit Cap.

	
Qty.

	
Circuit No.

	
Brand


	
1

	
Maintenance Power Box (Half Floor)

	
Non-Standard

	  	
6

	  	
High Quality


	  	
21JX、22JX、23JX、24JX、25JX、26JX

	  	  	  	  	  
	  	
Circuit Breaker

	
C65H/63/D63/3P

	
63

	
16

	
Incoming Line

	
Schneider


	  	
Leakage Protection Breaker

	
C65H/63/32/4+VigiC65ELE

	
32+30mA

	
16

	  	
Schneider


	  	
Leakage Protection Breaker

	
DPNVigiC16

	
16+30mA

	
48

	  	
Schneider


	
1

	
Socket Box (Seed Proliferation)

	
Non-Standard

	  	
8

	  	  
	  	
Socket

	  	  	  	  	
Schneider


	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  
	  	  	  	  	  	  	  





 



	
SUNTEC

	
Page 8 of 8