Unassociated Document


Exhibit 4.8.4 - Electronic Catalogue (1,3,4,5) - 39CBF39CBFI




 













  





  











  



















Carrier China


Carrier is affiliated to United Technologies. United Technologies ranks 126 in world’s 500 tops (2006), its business extends to architectural industry and aerospace industry around the world.







In 1902, Professor Carrier invented first set of scientific air-conditioning system. Since then, carrier’s complete series products and system resolution have become first choice of many world-renowned buildings.







In 2007, carrier’s sales revenue reaches 14.6 billion US dollars, leading in the whole industry. Its distributors’ network covers over 170 countries. Carrier is now world’s biggest HVAC manufacturer.







Carrier China has 11 companies, 40 sales service offices and 2,500 employees.







As the world-class factory, Carrier Yileng has several advanced production lines of units and compressors, covering main units of commercial and residential central air-conditioning systems and air terminal products. The various products can meet diversifying demands from different customers.







Index








	
39CBFI Series Modular Air-Conditioning Unit

	
 


	
Mark Method of Unit Type

	
1


	
Air Amount scope

	1
	
Characteristics of Unit

	
2


	
Introduction of software

	
4


	
Control Illusion of Unit

	
5


	
Control

	
6


	
Swift Model Selection

	
7


	
Sketch Map of Function Section

	
8


	
Adjustment of air valve

	9
	
Cold amount and heat amount of unit and pipe coil configuration

	10
	
Weight of Pipe Coil

	12
	
Connection dimension of pipe coil installation

	13
	
Fan section

	16
	
Humidifier Option

	19
	
Silencer

	20
	
Filter

	21
	
Specification and number of Filter

	22
	
Filtering grade of purification needed

	23
	
Electrical heating section

	24
	
Case Weight

	24
	  	  
	
39CBF Series Modular Air-Conditioning Unit

	  
	
Mark Method of 39CBF

	25
	
Air Amount Scope of 39CBF

	
25


	
Characteristics of Unit 39CBF

	
26


	
Swift Model Selection of 39CBF

	
28


	
Other Specification

	
29















  





  











  













Mark Method of Unit Type


 











 


Computing Formula for Unit Modulus and Dimension







39CBFI


 


(1)  Unit Height = Height Modulus × 100 + 100 + 100 (Base)


 


 (2)  Unit Width = Width Modulus× 100 + 100


 


Example:39CBFI 0712


 


07 Height Modulus


 


Height of Unit is:7 × 100 + 100 + 100 (底座) =900mm


 


12 Width Modulus


 


Width of Unit:12 × 100 + 100 =1300mm







Scope of Air Amount


 


39CBFI    2209~57766m3/h










  





1











  













Characteristics of Unit







Double-Panel Structure, Outstanding Heat Prevention


50mm foam panel is light and rigid, and its thermal conductivity is less than 0.0199W/M.°C. The framework and framing strips have been specially treated for insulation, preventing the appearance of cold bridge. Double metal panels are quality color steel sheet and galvanized steel panel, ensuring fire-proof and anti-corrosion performance of the unit. Meanwhile, external panel can be optionally painted by powder of cold-rolled steel sheet, internal panel can be use stainless steel, to satisfy different demand from customers.


 







New sealing material, minimize air leakage


The case of unit includes panel, framework and gland strip. The panel adopts unique embedding method, so that connection points can be connected precisely. The new gland strip is applied between frame and panel, and each access door and pass-through of pipes has been meticulously designed to ensure air tightness of unit. It completely complies with or beyond the GB/T14294-93.


 











Elaborate design of water pan


Water pan shall be galvanized steel panel, and stainless steel water pan is available. The down drain method ensures all the condensed water discharged. The lowest point of pipe coil loop equips a freeing port, which can empty the standing water inside pipe coil. This can avoid frost crack of pipe coil.


 











Cold/Hot water pipe coil, international high-level design



	
l

	
Pipe coil employs Carrier’s latest ripple fins to install on copper pipe by mechanic expansion pipe method, which has excellent heat transfer efficiency. Customers can select hydrophilic aluminum foil to more excellent reach heat transfer performance.







Pipe coil header is steel header, and copper header is available if user has such requirement. The drain valve and air evacuation valve are installed on pipe coil header to ensure no air on loop, meanwhile empty standing water inside pipe coil to avoid frost crack.



	
l

	
When face velocity is more than 2.5m/s, water-dam can be added behind pipe coil, which can effectively separate water from air.







 











Corrugated air damper, flexible adjustment


Handle or electric mode can be selected. Using corrugated link mechanism adjustment, and air damper can open flexibly. Electric remote control device can be installed.


 














  





2











  








 





 


Unit Base


Each section equips unit base to strength whole machine, reduce unit’s vibration, easy for transport and split joint.
















Use optimized “many-swings on front side and curve on back side double intakes centrifugal fan, low noise and high efficiency


Blade wheel and belt pulley have been adjusted by dynamic poise, and whole fan has been regulated by vibration test, so that the whole fan can run smoothly.  The base that fan and motor used together installs shock absorbers, soft connection have been provided between air outlet and chassis, so that operational components can be completely isolated, so does shock. The blade of front section or back section can be selected in accordance with air pressure and air flow rate.


 











Provide all kinds of filers to cater different need



	
l

	
Provide all-level filters, ranging from preliminary filter (board-structure, efficiency can reach G4 level), to medium filter (bag-structure, efficiency can reach F8 level), and high efficiency filter (H13). And provide active carbon filter, filter cartridge filter, antistatic filter and other special filters.





















Modulus design and convenient model selection


The width, height and length of unit add in proportion by modulus of 100mm


Each regulation of flow shall have certain type of unit to match


Modulus products save the material to maximum, control production cost


Standard modules products are convenient and quick for mode shaping and manufacture.
















Easy and Convenient Repair


Parts have strong commonality, very easy to change, and price is cheap. Detachable panel can be installed on one side of unit; furthermore, access doors are set to necessary function setting. It is convenient to maintain fan, pipe coil and filters. Pipe coil is installed on lead rail of water pan, easy to maintain, clean and dismantle.


 





 





  





3











  













Introduction of Software







Computer Model Selection


The company provides swift and précised computer model selection service. Calculate the most idea function configuration and most economic type.







Function Charateristics



·   Project Management





·   Modulus Management





·   Flexible Combination of Functions





·   Provide several configurations according to user’s requirement





·   Sub-Box Section Configuration





·   Unit Performance Calculation





·   Whole-set Quotation





·   Output Drawing and technical specification





·   Chinese Interface, Easy use





















  





4











  













Example of Unit Control








	 	
Control of AC Unit

	 	 
	 	 	 	 
	 	
Monitor Equipment

	 	
Monitor Contents


	 	  	 	  
	 	
AC Unit

	 	

Fan Start stop control; Fan Operation Status, Fault Alarm, Handle and auto status; , Filter silting Alarm; (pipe coil freeze protection Alarm) Cold Water Valve regulation, Hot Water Valve Regulation; Fresh-air Damper Adjustment; recirculation door Adjustment; Himidifier Switch; Supply Temperature; Supply Temperature; recirculation humidity level; indoor temperature and humidity level; outdoor temperature and humidity level




	 	 	 	 
	 	
Schematic diagram of AC unit (Example)






















	
1  humility of return air

	
2  Temperature of Return air

	
3  Damper adjustment of Return air

	
4   Fresh-air damper adjust

	
5  Screen silting Alarm


	
6  Hot Water Valve Adjust  

	
7  Cold Water Valve adjustment

	
8  humidifier Switch

	
9   Fan Operation Status

	
10 Fan Handle or auto Status


	
11 Fan Fault

	
12 Fan Stop Control

	
13 Temperature of Supply Air

	  	  











	 	AC Unit Fresh-Air Control
	 	 	 	 
	 	
Monitor equipment

	 	
monitor content


	 	 	 	 
	 	
Fresh-air Unit

	 	

Fan Start Stop Control; Fan Operational Status, Fault Alarm, Handle and auto status, filter silt alarm; (pipe coil freeze protection Alarm) Cold Water Valve Adjustment, hot water Valve Adjustment, Fresh-air damper adjustment; temperature of supply air, indoor temperature and humidity, outdoor temperature and humidity




	 	 	 	 
	 	
Schematic diagram of Fresh-air unit (Example)






















	
1   Fresh-air Damper openness

	
2   Screen Silting Alarm

	
3   Valve Adjustment

	
4   Fan Operation

	
5   handle – Auto Status


	
6   Fan Fault Alarm

	
7   Fan Start-stop

	
8   temperature of Supply air

	
9   Outdoor Temperature

	  













  





5











  













Control







Realize single machine and network control to AC unit according to customer’s requirement


 


Function


 



	 	
●

	
aim to all kinds of AC unit and terminals, provide all-level control system solution







 




	 	
●

	
Through communication signal line, assemble temperature, humility, valve and damper’s signals on AC unit and terminals, send alarms through internal logical procedure, control valve, damper openness, monitor fan, screen status, auto alarm.







 





	 	
●

	
Equip special system monitor interface, realizing system control of simple AC Unit.












Single Machine Control Module of AC Unit
















 














  





6











  













Quick Model Selection








	
Unit Specification

	 	
Pipe coil in the wind

	 	
Outline Diamension

	 	
Air

	 	
Full Pressure of


	  	 	  	 	  	  	 	
Flow

	 	
External unit


	
39CFI

	 	
Area (m2)

	 	
Height H*

	
Width W

	 	  	 	  	 	  	 	  
	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
0609

	 	
0.24

	 	
700

	
1000

	 	
2008

	 	
2209

	 	
2430

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
0610

	 	
0.34

	 	
700

	
1100

	 	
2755

	 	
3058

	 	
3364

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
0712

	 	
0.49

	 	
800

	
1300

	 	
3979

	 	
4417

	 	
4859

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
0813

	 	
0.70

	 	
900

	
1400

	 	
5663

	 	
6286

	 	
6915

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
0914

	 	
0.81

	 	
1000

	
1500

	 	
6582

	 	
7306

	 	
8037

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
1015

	 	
1.05

	 	
1100

	
1600

	 	
8495

	 	
9429   

	 	
10372

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
1016

	 	
1.15

	 	
1100

	
1700

	 	
9337

	 	
10364

	 	
11400

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
1117

	 	
1.44

	 	
1200

	
1800

	 	
11632

	 	
12912

	 	
14703

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
1317

	 	
1.68

	 	
1400

	
1800

	 	
13623

	 	
15121

	 	
16633

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
1518

	 	
2.07

	 	
1600

	
1900

	 	
16837

	 	
18689

	 	
20558

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
1522

	 	
2.36

	 	
1600

	
2300

	 	
19133

	 	
21238

	 	
23362

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
1622

	 	
2.55

	 	
1700

	
2300

	 	
20664

	 	
22937

	 	
25231

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
1822

	 	
2.93

	 	
1900

	
2300

	 	
23725

	 	
26335

	 	
28968

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
1824

	 	
3.30

	 	
1900

	
2500

	 	
26786

	 	
29733

	 	
32706

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
1825

	 	
3.59

	 	
1900

	
2600

	 	
29082

	 	
32281

	 	
35509

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
2025

	 	
3.96

	 	
2100

	
2600

	 	
30143

	 	
35679

	 	
39247

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
2226

	 	
4.63

	 	
2300

	
2700

	 	
37501

	 	
41626

	 	
45789

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	
2330

	 	
5.48

	 	
2400

	
3100

	 	
44388

	 	
49271

	 	
54198

	 	
200~800


	  	 	  	 	  	  	 	  	 	  	 	  	 	  
	Unit height, not inclusive of base, 100mm	
400

	
3500

	 	
52041

	 	
57766

	 	
63543

	 	  








  





7











  













Function Section Sketch








	
Serial No.

	 	
Description

	 	
Simple Graph

	 	  	 	
Note


	  	 	  	 	  	 	  	 	  
	
1

	 	
Combined Section

	 	


	 	
(0609~0813) 5M


0914~1317) 6M


(1518~1622) 8M


(1822~2025) 9M


(2226~2334) 11M

	 	  
	  	 	  	 	  	 	  	 	  
	
2

	 	
Bag Filter Section

	 	


	 	
6M

	 	
The function section is recommended to set repair section


	  	 	  	 	  	 	  	 	  
	
3

	 	
Comprehensive Filter Section

	 	


	 	
6M

	 	
The function section is recommended to set repair section


	  	 	  	 	  	 	  	 	  
	
4

	 	
Surface Cold Section

	 	


	 	
6M

	 	
Include water-dam


	  	 	  	 	  	 	  	 	  
	
5

	 	
Hot Water pipe coil section

	 	


	 	
3M

	 	
When surface cold section did not include wet film humidifier and water-dam, can be installed with cold water pan


	  	 	  	 	  	 	  	 	  
	
6

	 	
Steam pipe coil section

	 	


	 	
3M

	 	  
	  	 	  	 	  	 	  	 	  
	
7

	 	
Electricity Heat Section

	 	


	 	
3M

	 	  
	  	 	  	 	  	 	  	 	  
	
8

	 	
Steam Humidifier Section

	 	


	 	
6M

	 	  
	  	 	  	 	  	 	  	 	  
	
9

	 	
Wet Film Humidifying Section

	 	


	 	
3M

	 	
Can directly install with pipe coil, water pan, no space Demand


	  	 	  	 	  	 	  	 	  
	
10

	 	
High Pressure Spray humidifying Section

	 	


	 	
6M

	 	
Can be neighbor with surface cold machine, use water-dam


	  	 	  	 	  	 	  	 	  
	
11

	 	
Fan Section

	 	


	 	  	 	
Fan has four air-out directions


	  	 	  	 	  	 	  	 	  
	
12

	 	
Fresh-air return air section

	 	


	 	
(0609~0813) 10M


(0914~1825) 12M


(2025~2334) 18M

	 	  
	  	 	  	 	  	 	  	 	  
	
13

	 	
Silencing Section

	 	


	 	
6M, 12M

	 	
The function section is recommended to set repair section


	  	 	  	 	  	 	  	 	  
	
14

	 	
Air Outlet Section

	 	


	 	
(0609~0813) 5M


(0914~1317) 6M


(1518~1622) 8M


(1822~2025) 9M


(2226~2334) 11M

	 	
The outlet can be on the side or on the top


	  	 	  	 	  	 	  	 	  
	
15

	 	
Empty Section

	 	


	 	
3M, 6M

	 	  
	  	 	  	 	  	 	  	 	  
	
16

	 	
High Efficient filter section

	 	


	 	
9M

	 	  










注:以上模数长度仅限于 0609~2334 机组。












  





8











  








Sketch Map Identification of Unit Direction


 








	
Direction of unit: 

	
favorable current direction, pipe coil in/out water pipe those the access door on the left are left side door, and verse vise.







 










Adjustment Air Valve







It combines return air valve side rod drive openness ripple valve, which is light and flexible to operate, air resistance small, good sealant. It can be hand control, or electronic executor control. The dimension of adjustable air valve shows as follows:








	  	
39CBFI


	
Unit Spec

	
L × H

	
Weight


	
39CBFI

	
mm

	
kg


	
0609

	
848.0 × 420.5

	
19.7


	
0610

	
948.0 × 420.5

	
20.9


	
0712

	
1148.0 × 420.5

	
23.8


	
0813

	
1248.0 × 420.5

	
25.3


	
0914

	
1348.0 × 578.0

	
36.7


	
1015

	
1448.0 × 578.0

	
38.5


	
1016

	
1548.0 × 578.0

	
40.0


	
1117

	
1648.0 × 578.0

	
42.7


	
1317

	
1648.0 × 578.0

	
42.7


	
1518

	
1748.0 × 735.0

	
46.0


	
1522

	
2148.0 × 735.5

	
62.4


	
1622

	
2148.0 × 735.5

	
62.4


	
1822

	
2148.0 × 893.0

	
72.0


	
1824

	
2348.0 × 893.0

	
76.8


	
1825

	
2448.0 × 893.0

	
79.5


	
2025

	
2448.0 × 893.0

	
79.5


	
2226

	
2548.0 × 1050.5

	
89.7


	
2330

	
2948.0 × 1050.5

	
100.7


	
2334

	
3348.0 × 1050.5

	
111.0















 




  





9











  






 


Cold Amount and heat amount of unit, and configuration of pipe coil







Unit equipped with cold/hot water pipe coil and heat pipe coil. The cold/hot water pipe coil can use cold water and hot water in winter and summer in turn. Heat pipe coil is heated by special hot water, or select steam pipe coil.








	  	  	
4 Row

	
6 Row


	
Unit Spec

	
air volume

	
Total cold

	
A. cold

	
Air .resist.

	
Water Flow

	
Water Resis

	
Loop

	
Total C

	
A. cold

	
Air Resist


	
39CBFI

	
(CMH)

	
(kW)

	
(kW)

	
(Pa)

	
(L/s)

	
(kPa)

	  	
(kW)

	
(kW)

	
(Pa)


	
0609

	
2209

	
12.1

	
9.12

	
128

	
0.58

	
7.9

	
HF

	
17.16

	
11.75

	
196


	
0610

	
3058

	
16.58

	
11.90

	
124

	
0.79

	
12.4

	
HF

	
24.69

	
16.65

	
188


	
0712

	
4417

	
23.92

	
17.11

	
126

	
1.1

	
17.1

	
HF

	
36.07

	
24.24

	
192


	
0813

	
6286

	
35.39

	
25.27

	
126

	
1.7

	
34.6

	
HF

	
48.28

	
33.18

	
191


	
0914

	
7306

	
40.83

	
29.04

	
128

	
1.96

	
39.5

	
HF

	
55.62

	
38.37

	
192


	
1015

	
9429

	
53.41

	
38.08

	
127

	
2.6

	
46.9

	
HF

	
72.84

	
49.96

	
191


	
1016

	
10364

	
59.51

	
42.16

	
128

	
2.85

	
55.8

	
HF

	
81.18

	
55.39

	
191


	
1117

	
12912

	
79.53

	
58.65

	
125

	
3.8

	
17.8

	
FL

	
103.39

	
69.97

	
191


	
1317

	
15121

	
93.44

	
68.79

	
126

	
4.5

	
20.8

	
FL

	
121.26

	
82.01

	
192


	
1518

	
18689

	
116.43

	
85.41

	
127

	
5.6

	
26.7

	
FL

	
150.61

	
101.68

	
193


	
1522

	
21238

	
135.61

	
98.38

	
127

	
6.5

	
25.2

	
FL

	
173.71

	
116.64

	
192


	
1622

	
22937

	
145.83

	
105.99

	
127

	
7

	
27.7

	
FL

	
187.1

	
125.76

	
192


	
1822

	
26335

	
167.58

	
121.76

	
127

	
8

	
28.1

	
FL

	
214.93

	
144.44

	
192


	
1824

	
29733

	
193.22

	
139.09

	
128

	
9.2

	
35.6

	
FL

	
245.77

	
164.41

	
193


	
1825

	
32281

	
212.52

	
152.13

	
128

	
10.2

	
45

	
FL

	
257.06

	
174.31

	
191


	
2025

	
35679

	
234.3

	
167.90

	
128

	
11.2

	
44.8

	
FL

	
283.45

	
192.37

	
191


	
2226

	

41628



	
275.39

	
196.72

	
129

	
13.2

	
51.8

	
FL

	
332.93

	
225.39

	
191


	
2330

	
49271

	
331.15

	
234.96

	
129

	
15.8

	
69.5

	
FL

	
399.05

	
268.91

	
192


	
2334

	
57766

	
*371.14

	
*268.51

	
*129

	
*14.1

	
*68.9

	
FL

	
*450.89

	
*308.05

	
*193












Standard operation





	  	  	
6 Row

	
8 row


	  	
Air

	  	  	  	  	  	  	  	  	  
	
Unit Spec

	
volume

	
W Flow

	
Water Resis

	
Loop

	
Total Cold

	
A. Cold

	
Air Resistant

	
Water Fl

	
Water Resis

	
Loop


	
39CBFI

	
(CMH)

	
(L/s)

	
(kPa)

	  	
(kW)

	
(kW)

	
(Pa)

	
(L/s)

	
(kPa)

	  
	
0609

	
2209

	
0.8

	
16.1

	
HF

	
19.7

	
12.91

	
264

	
0.9

	
26.6

	
HF


	
0610

	
3058

	
1.2

	
40.2

	
HF

	
27.73

	
18.07

	
253

	
1.3

	
64.2

	
HF


	
0712

	
4417

	
1.7

	
43.58

	
HF

	
37.96

	
25.18

	
254

	
1.8

	
14.8

	
FL


	
0813

	
6286

	
2.3

	
19.1

	
FL

	
55.05

	
36.28

	
257

	
2.6

	
29.2

	
FL


	
0914

	
7306

	
2.7

	
19.6

	
FL

	
63.8

	
42.09

	
258

	
3.1

	
29.5

	
FL


	
1015

	
9429

	
3.5

	
18.6

	
FL

	
83.77

	
54.95

	
256

	
4

	
29.5

	
FL


	
1016

	
10364

	
3.9

	
24.1

	
FL

	
92.6

	
60.76

	
257

	
4.4

	
38

	
FL


	
1117

	
12912

	
4.9

	
37.7

	
FL

	
116.72

	
76.14

	
256

	
5.6

	
57.8

	
FL


	
1317

	
15121

	
5.8

	
43.1

	
FL

	
136.75

	
89.19

	
257

	
6.5

	
64.6

	
FL


	
1518

	
18689

	
7.2

	
41.8

	
FL

	
169.37

	
110.39

	
259

	
8.1

	
65.2

	
FL


	
1522

	
21238

	
8.3

	
54.1

	
FL

	
182.96

	
121.25

	
256

	
8.7

	
22.6

	
DB


	
1622

	
22937

	
8.9

	
58.1

	
FL

	
196.83

	
130.62

	
256

	
9.4

	
23.8

	
DB


	
1822

	
26335

	
10.3

	
59.5

	
FL

	
226.3

	
150.1

	
256

	
10.8

	
18.8

	
DB


	
1824

	
29733

	
11.8

	
75.8

	
FL

	
258.44

	
170.76

	
257

	
12.4

	
25.8

	
DB


	
1825

	
32281

	
12.3

	
36.6

	
DB

	
282.03

	
186.02

	
258

	
13.5

	
31.4

	
DB


	
2025

	
35679

	
13.6

	
37.8

	
DB

	
311.39

	
205.46

	
258

	
14.9

	
33.5

	
DB


	
2226

	
41628

	
15.9

	
43.7

	
DB

	
364.32

	
240.16

	
258

	
17.4

	
38.5

	
DB


	
2330

	
49271

	
19.1

	
57.7

	
DB

	
433.94

	
285.45

	
259

	
20.8

	
49.8

	
DB


	
2334

	
57766

	
18

	
56.8

	
DB

	
521.38

	
340.26

	
259

	
24.9

	
76.1

	
DB







 


HF—Semi loop  FL—Full Loop  DB—Double Loop  Standard Operation Condition:inlet dry bulb temperature —27oC  inlet wet bulb temperature —19.5oC  inlet water —7oC Note:* refers to control refrigerating water pipe pressure drop , differential return water temperature is  5oC



 




  





10











  






 


Cold Amount and heat amount of unit, and configuration of pipe coil




 




	
Unit Cold

	  
	
Amount

	
Fresh-air


	  	
Operational


	  	
Condition










	
Unit spec

	
Air volume

	
4 Row

	
6 Row


	
39CBFI

	
(CMH)

	
Total Cold

	
A. Cold

	
Air Resist

	
Water Res

	
Water Flow

	
Loop

	
T Cold

	
A Cold

	
Air Consist


	  	  	
(kW)

	
(kW)

	
(Pa)

	
(L/s)

	
(kPa)

	  	
(kW)

	
(kW)

	
(Pa)


	
0609

	
2209

	
31.55

	
13.66

	
134

	
1.5

	
27

	
HF

	
39.51

	
16.75

	
201


	
0610

	
3058

	
45.81

	
19.63

	
128

	
2.2

	
59.4

	
HF

	
51.03

	
21.75

	
193


	
0712

	
4417

	
59.83

	
26.18

	
130

	
2.9

	
15.1

	
FL

	
76.05

	
32.32

	
195


	
0813

	
6286

	
87.31

	
38.01

	
131

	
4.2

	
28

	
FL

	
109.86

	
46.64

	
197


	
0914

	
7306

	
102.48

	
44.53

	
132

	
4.9

	
49.2

	
FL

	
128.37

	
54.48

	
198


	
1015

	
9429

	
133.99

	
58.08

	
130

	
6.4

	
52.5

	
FL

	
160.2

	
68.89

	
195


	
1016

	
10364

	
*149.59

	
64.66

	
131

	
7.2

	
59.0

	
FL

	
177.02

	
76.12

	
196


	
1117

	
12912

	
*183.57

	
*79.32

	
*131

	
*7.3

	
*60.1

	
FL

	
*214.73

	
*92.33

	
*196


	
1317

	
15121

	
*215.15

	
*92.94

	
*132

	
*8.6

	
*70.3

	
FL

	
*253.28

	
108.91

	
*197


	
1518

	
18689

	
*261.47

	
*113.29

	
*132

	
*9.6

	
*62

	
FL

	
*314.54

	
*135.25

	
*197


	
1522

	
21238

	
*296.3

	
*128.45

	
*131

	
*10.1

	
*63.6

	
FL

	
*348.73

	
*149.95

	
*196


	
1622

	
22937

	
*318.64

	
*138.24

	
*132

	
*10.9

	
*62.9

	
FL

	
*379.61

	
*163.23

	
*196


	
1822

	
26335

	
*366.3

	
*158.88

	
*132

	
*12.5

	
*65.3

	
FL

	
*435.05

	
*187.07

	
*196


	
1824

	
29733

	
*412.33

	
*178.94

	
*133

	
*13.1

	
*57.4

	
FL

	
*490.59

	
*210.96

	
*197


	
1825

	
32281

	
*443.04

	
*192.65

	
*133

	
*313.2

	
*61.6

	
FL

	
*531.97

	
*226.88

	
*197


	
2025

	
35679

	
*488.74

	
*212.6

	
*133

	
*14.6

	
*68

	
FL

	
*585.95

	
*250

	
*197


	
2226

	
41628

	
*561.78

	
*245.1

	
*134

	
*15.8

	
*69.8

	
FL

	
*675.37

	
*288.55

	
*198


	
2330

	
49271

	  	  	  	  	  	  	
*795.42

	
*340.05

	
*198


	
2334

	
57766

	  	  	  	  	  	  	
*916.95

	
*392.85

	
*198












Fresh-air operation condition





	  	  	
6 Row

	
8 Row


	
Unit Spec

	
Air

	  	  	  	  	  	  	  	  	  
	
39CBFI

	
Volume

	
W Flow

	
Flow Resist

	
Loop

	
T. Cold

	
A. Cold

	
Air Resis

	
W Flow

	
Water Resi

	
Loop


	  	
(CMH)

	
(L/s)

	
(kPa)

	  	
(kW)

	
(kW)

	
(Pa)

	
(L/s)

	
(kPa)

	  
	
0609

	
2209

	
1.9

	
63

	
HF

	
41.12

	
17.41

	
268

	
2

	
12.7

	
FL


	
0610

	
3058

	
2.4

	
18.8

	
FL

	
57.83

	
24.48

	
257

	
2.8

	
20.6

	
FL


	
0712

	
4417

	
3.6

	
31.6

	
FL

	
85.25

	
36.09

	
260

	
4.1

	
40.3

	
FL


	
0813

	
6286

	
5.3

	
52.6

	
FL

	
119.37

	
50.14

	
267

	
5.7

	
28.47

	
DB


	
0914

	
7306

	
6.1

	
64.9

	
FL

	
138.16

	
58.03

	
268

	
6.6

	
31.08

	
DB


	
1015

	
9429

	
7.7

	
36.15

	
DB

	
177.27

	
75.45

	
266

	
8.5

	
34.2

	
DB


	
1016

	
10364

	
8.5

	
38.88

	
DB

	
192.67

	
80.92

	
267

	
9.2

	
34.88

	
DB


	
1117

	
12912

	
*8.5

	
*40.12

	
DB

	
*241.20

	
*101.30

	
*266

	
*9.6

	
*37.91

	
DB


	
1317

	
15121

	
*10.1

	
*38.93

	
DB

	
*283.07

	
*118.89

	
*267

	
*11.3

	
*38.25

	
DB


	
1518

	
18689

	
*11.6

	
*41.76

	
DB

	
*349.11

	
*146.63

	
*269

	
*12.8

	
*38.88

	
DB


	
1522

	
21238

	
*11.9

	
*51.7

	
DB

	
*389.59

	
*165.04

	
*268

	
*13.3

	
*41.3

	
DB


	
1622

	
22937

	
*13

	
*53.9

	
DB

	
*418.82

	
*177.46

	
*267

	
*14.3

	
*50

	
DB


	
1822

	
26335

	
*14.8

	
*52.36

	
DB

	
*481.33

	
*203.93

	
*267

	
*16.4

	
*52.8

	
DB


	
1824

	
29733

	
*15.6

	
*57.6

	
DB

	
*542.69

	
*229.64

	
*268

	
*17.3

	
*48

	
DB


	
1825

	
32281

	
*15.9

	
*58.7

	
DB

	
*584.99

	
*247.94

	
*268

	
*17.5

	
*50.9

	
DB


	
2025

	
35679

	
*17.5

	
*60.6

	
DB

	
*645.87

	
*273.76

	
*269

	
*19.3

	
*54.5

	
DB


	
2226

	
41628

	
*19

	
*60.4

	
DB

	
*745.61

	
*316.21

	
*269

	
*21

	
*54.5

	
DB


	
2330

	
49271

	
*21.9

	
*69.2

	
DB

	
*879.19

	
*372.94

	
*269

	
*23.4

	
*61.9

	
DB


	
2334

	
57766

	
*21.9

	
*76.7

	
DB

	
*1016.91

	
*431.73

	
*269

	
*24.3

	
*72

	
DB







 


HF—Semi loop  FL—Full Loop  DB—Double Loop  Standard Operation Condition:inlet dry bulb temperature —35oC  inlet wet bulb temperature —28oC  inlet water —7oC Note:* refers to control refrigerating water pipe pressure drop , differential return water temperature is  5oC


 




  





11











  






 


Cold Amount and heat amount of unit, and configuration of pipe coil







Unit Heat Energy:(2 Row)








	  	
Inlet temperature of hot water


	
Unit Spec

	
60 °C

	
70 °C

	
80°C


	
39CBFI

	
Heat

	
air resist

	
w resist

	
w Flow

	
Heat

	
air resist

	
w resist

	
w Flow

	
Heat

	
air resist

	
w resist

	
w Flow


	  	
(kW)

	
(Pa)

	
(kPa)

	
(L/s)

	
(kW)

	
(Pa)

	
(kPa)

	
(L/s)

	
(kW)

	
(Pa)

	
(kPa)

	
(L/s)


	
0609

	
12.79

	
55

	
1.0

	
0.3

	
20.22

	
56

	
2.2

	
0.5

	
22.92

	
57

	
2.8

	
0.5


	
0610

	
20.42

	
56

	
2.8

	
0.5

	
78.58

	
60

	
4.8

	
0.7

	
32.38

	
54

	
6.4

	
0.8


	
0712

	
32.34

	
58

	
4.2

	
0.8

	
41.72

	
58

	
6.6

	
1.0

	
47.19

	
55

	
8.6

	
1.1


	
0813

	
43.34

	
54

	
7.0

	
1.0

	
60.47

	
57

	
8.7

	
1.3

	
72.16

	
62

	
10.1

	
1.4


	
0914

	
54.38

	
61

	
7.5

	
1.2

	
69.91

	
58

	
11.8

	
1.6

	
83.63

	
62

	
12.8

	
1.7


	
1015

	
70.73

	
60

	
10.4

	
1.6

	
90.73

	
61

	
16.4

	
2.1

	
108.46

	
61

	
17.7

	
2.2


	
1016

	
78.40

	
55

	
13.2

	
1.8

	
92.25

	
60

	
17.8

	
2.1

	
119.29

	
61

	
18.8

	
2.2


	
1117

	
91.03

	
55

	
17.4

	
2.1

	
115.38

	
56

	
24.1

	
2.5

	
137.06

	
55

	
24.6

	
2.5


	
1317

	
114.81

	
61

	
21.3

	
2.5

	
134.37

	
55

	
26.9

	
2.8

	
160.37

	
55

	
28.7

	
3.0


	
1518

	
141.54

	
62

	
25.5

	
3.0

	
166.57

	
62

	
34.5

	
3.5

	
198.72

	
56

	
36.9

	
3.7


	
1522

	
151.63

	
58

	
16.0

	
3.2

	
196.27

	
59

	
26.0

	
4.1

	
235.90

	
61

	
29.5

	
4.3


	
1622

	
162.63

	
58

	
17.4

	
3.4

	
211.41

	
59

	
29.2

	
4.4

	
258.37

	
61

	
36.4

	
5.2


	
1822

	
186.85

	
55

	
22.1

	
3.9

	
242.87

	
60

	
37.3

	
5.1

	
291.96

	
61

	
42.4

	
5.4


	
1824

	
214.15

	
59

	
29.2

	
4.5

	
276.48

	
58

	
47.2

	
5.7

	
333.27

	
55

	
50.9

	
6.1


	
1825

	
233.49

	
61

	
33.7

	
4.8

	
302.41

	
60

	
56.8

	
6.2

	
363.08

	
61

	
64.7

	
6.6


	
2025

	
257.75

	
57

	
40.1

	
5.3

	
333.67

	
58

	
67.4

	
6.8

	
398.91

	
61

	
70.7

	
7.1


	
2226

	
320.56

	
58

	
55.7

	
6.6

	
374.32

	
57

	
70.5

	
7.5

	
445.08

	
55

	
72.8

	
7.6


	
2330

	
348.95

	
60

	
58.4

	
7.0

	
461.95

	
60

	
71.1

	
9.0

	
530.27

	
55

	
75.8

	
11.5


	
2334

	
446.20

	
58

	
66.2

	
9.7

	
553.49

	
58

	
74.4

	
11.3

	
660.44

	
61

	
79.8

	
11.7







 


Note: Inlet dry bulb temperature —15oC; from 0609 to 1518 unit employs semi-loop, from 1522 to  2334 unit employs full loop。







Weight of pipe coil section




 


(单位: kg)



	
Unit Number

	
Pipe Coil Number


	
39CBFI

	
2 Row

	
4 Row

	
6 Row

	
8 Row


	
0609

	
35.30

	
73.16

	
77.70

	
83.92


	
0610

	
40.30

	
78.42

	
84.62

	
92.77


	
0712

	
42.60

	
89.86

	
98.80

	
104.68


	
0813

	
47.36

	
97.27

	
108.26

	
122.00


	
0914

	
51.30

	
103.46

	
115.90

	
131.38


	
1015

	
54.00

	
114.76

	
131.21

	
151.08


	
1016

	
56.36

	
119.38

	
137.55

	
159.12


	
1117

	
64.01

	
131.26

	
153.89

	
180.26


	
1317

	
69.90

	
142.88

	
169.35

	
187.94


	
1518

	
75.53

	
160.33

	
193.00

	
230.45


	
1522

	
111.54

	
178.95

	
217.85

	
256.74


	
1622

	
116.32

	
187.78

	
228.89

	
271.11


	
1822

	
124.14

	
204.02

	
252.26

	
300.51


	
1824

	
128.02

	
226.15

	
273.16

	
327.49


	
1825

	
129.86

	
228.14

	
288.05

	
347.01


	
2025

	
136.98

	
254.93

	
319.51

	
384.74


	
2226

	
166.16

	
284.69

	
359.83

	
435.83


	
2330

	
188.06

	
323.33

	
412.93

	
504.93


	
2334

	
206.11

	
363.44

	
468.24

	
576.24







 


Note:The weight on the chart only refers to the weight of pipe coil, exclusive of weight of box.


 




  





12











  






 


Connection dimension of installation of pipe coil


 





 



* MPT- outside thread




 



	
39CBFI

	
A

	
B

	
øC

	
F


	
0609

	
800

	
357

	
1—  ′′

	
233


	  	  	  	
1/2 MPT

	  
	
0610

	
800

	
421

	
1—  ′′

	
233


	  	  	  	
1/2 MPT

	  
	
0712

	
900

	
484

	
1—  ′′

	
233


	  	  	  	
1/2 MPT

	  
	
0813

	
1000

	
611

	
1—  ′′

	
233


	
0914

	
1100

	
675

	
1/2 MPT

	
233


	
1015

	
1200

	
802

	
1—  ′′

	
233


	  	  	  	
1/2 MPT

	  
	
1016

	
1200

	
802

	
1—  ′′

	
233


	  	  	  	
1/2 MPT

	  
	
1117

	
1300

	
917

	
1—  ′′

	
240


	  	  	  	
1/2 MPT

	  
	
1317

	
1500

	
1107

	
1—  ′′

	
240


	  	  	  	
1/2 MPT

	  
	
1518

	
1700

	
1298

	  	
240













	
39CBFI

	
D

	
E

	
øC


	
2 排   热水

	
55

	
138

	
1-1/2′′


	
4 排

	
91

	
173

	  
	
6 排

	
63

	
201

	
见上表


	
8 排

	
88

	
226

	  





 





 



	
39CBFI

	
A

	
B

	
øC

	
F


	
1522

	
1700

	
1298

	
2′′ MPT

	
240


	
1622

	
1800

	
1361

	
2′′ MPT

	
240


	
1822

	
2000

	
1523

	
3′′ MPT

	
254


	
1824

	
2000

	
1523

	
3′′ MPT

	
254


	
1825

	
2000

	
1523

	
3′′ MPT

	
254













	
39CBFI

	
D

	
E

	
øC


	
2 row hot water

	
55

	
138

	
1-1/2′′


	
4 row(diameter 2′′ MPT)

	
116

	
198

	
Refer to


	
4 row(diameter 3′′ MPT)

	
88

	
226

	
above chart


	
6 row、8 row

	
88

	
226

	  





 




  





13











  






 


Connection dimension of installation of pipe coil
















	
39CBFI

	
A

	
B

	
øC

	
øF


	
2025

	
2200

	
982

	
2′′ MPT

	
3′′ MPT


	
2226

	
2400

	
1173

	
2′′ MPT

	
3′′ MPT


	
2330

	
2500

	
1300

	
2′′ MPT

	
3′′ MPT


	
2334

	
2500

	
1300

	
2′′ MPT

	
3′′ MPT













	
39CBFI

	
D1

	
D2

	
E1

	
E2

	
øC


	
2 row hot

	
55

	
138

	
1-1/2” MPT


	
4 row

	
116

	
88

	
198

	
226

	
Refer to above


	
6 row 8 Row

	
88

	
226

	
chart avove












Steam pipe coil Section







(Unit: kW)





	
Unit Spec

	
Pipe Coil

	
Steam

	
Weight


	
39CBFI

	
Type

	
Pressure(MPa)

	
kg


	
0609

	
(GL-2R-09-06)× 1

	
28.3

	
32.6

	
36.2

	
45


	
0610

	
(GL-2R-09-07)× 1

	
38.2

	
44.2

	
49.1

	
48


	
0712

	
(GL-2R-11-09)× 1

	
53.9

	
62.3

	
69.1

	
57


	
0813

	
(GL-2R-15-10)× 1

	
76.4

	
88.3

	
97.9

	
80


	
0914

	
(GL-2R-17-11)× 1

	
92.1

	
106.5

	
118.1

	
98


	
1015

	
(GL-2R-19-12)× 1

	
115.9

	
136.7

	
151.5

	
107


	
1016

	
(GL-2R-19-13)× 1

	
129.6

	
149.9

	
166.2

	
114


	
1117

	
(GL-2R-22-14)× 1

	
161.1

	
186.4

	
206.7

	
126


	
1317

	
(GL-2R-13-14)× 2

	
188.5

	
217.9

	
241.6

	
167


	
1518

	
(GL-2R-15-15)× 2

	
234.9

	
271.6

	
301.3

	
212


	
1522

	
(GL-2R-15-19)× 2

	
271.4

	
313.8

	
348.1

	
243


	
1622

	
(GL-2R-17-19)× 2

	
298.9

	
345.7

	
382.8

	
269


	
1822

	
(GL-2R-19-19)× 2

	
345.6

	
399.4

	
442.7

	
286


	
1824

	
(GL-2R-19-21)× 2

	
387.4

	
448.1

	
496.3

	
303


	
1825

	
(GL-2R-19-22)× 2

	
416.6

	
481.7

	
533.0

	
320


	
2025

	
(GL-2R-22-22)× 2

	
464.8

	
537.8

	
595.5

	
354


	
2226

	
(GL-2R-22-23)× 2

	
525.6

	
607.3

	
672.5

	
374


	
2330

	
(GL-2R-22-27)× 2

	
620.7

	
717.4

	
795.9

	
413


	
2334

	
(GL-2R-22-31)× 2

	
724.0

	
835.8

	
927.9

	
471







 



	
注: Inlet Day-bulb temperature is 7oC .the weight on the chart only refers to the weight of pipe coil, exclusive of weight of box.














  





14











  






 





 



	
39CBFI

	
A

	
B

	
øC

	
F


	
0609

	
800

	
287

	
2′′ MPT

	
278


	
0610

	
800

	
287

	
2′′ MPT

	
278


	
0712

	
900

	
358

	
2′′ MPT

	
278


	
0813

	
1000

	
500

	
2′′ MPT

	
278


	
0914

	
1100

	
571

	
2′′ MPT

	
278


	
1015

	
1200

	
678

	
2′′ MPT

	
278


	
1016

	
1200

	
678

	
2′′ MPT

	
278


	
1117

	
1300

	
784

	
2′′ MPT

	
278













	
39CBFI

	
D

	
E


	
2 排

	
80

	
154







 





 



	
39CBFI

	
A

	
B

	
øC

	
F


	
1317

	
1500

	
429

	
2′′ MPT

	
278


	
1518

	
1700

	
500

	
2′′ MPT

	
278


	
1522

	
1700

	
500

	
2′′ MPT

	
278


	
1622

	
1800

	
571

	
2′′ MPT

	
278


	
1822

	
2000

	
678

	
2′′ MPT

	
278


	
1824

	
2000

	
678

	
2′′ MPT

	
278


	
1825

	
2000

	
678

	
2′′ MPT

	
278


	
2025

	
2200

	
784

	
2′′ MPT

	
278


	
2226

	
2400

	
784

	
2′′ MPT

	
478


	
2330

	
2500

	
784

	
2′′ MPT

	
478


	
2334

	
2500

	
784

	
2′′ MPT

	
478













	
39CBFI

	
D

	
E


	
2 排

	
80

	
154







 




  





15











  






 


Fan Section







Configuration of fan and motor








	
Unit Spec 39CBFI

	
Fitting Fan

	
Max Power of


Fan


(kW)

	
Max seat of Fan

	
Length of Fan 


Section(mm)


HorizontaVertical

	
Weight(kg)


	
0609

	
ADZ180

	
1.5

	
Y90

	
600

	
900

	
20.55


	
0610

	
ADZ180

	
2.2

	
Y100

	
600

	
900

	
20.55


	
ADZ200

	
700

	
900

	
23.21


	
0712

	
ADZ225

	
3.7

	
Y112

	
700

	
900

	
32.98


	
ADZ/RDZ250

	
700

	
900

	
34.98/37.08


	
0813

	
ADZ/RDZ280

	
5.5

	
Y132

	
800

	
900

	
41.44/43.64


	
ADZ/RDZ315

	
800

	
900

	
46.44/47.64


	
0914

	
ADZ/RDZ315

	
5.5

	
Y132

	
800

	
900

	
46.44/47.64


	
ADZ/RDZ355

	
900

	
900

	
60.41/64.41


	
1015

	
ADZ/RDZ355

	
7.5

	
Y132

	
900

	
900

	
60.41/64.41


	
ADZ/RDZ400

	
900

	
900

	
73.48/76.48


	
1016

	
ADZ/RDZ355

	
7.5

	
Y132

	
900

	
900

	
64.21/68.21


	
ADZ/RDZ400

	
900

	
900

	
77.21/80.21


	
1117

	
ADZ/RDZ400

	
11

	
Y160

	
900

	
900

	
79.02/82.02


	
ADZ/RDZ450

	
1100

	
1100

	
88.02/97.52


	
1317

	
ADZ/RDZ400

	
15

	
Y160

	
900

	
900

	
79.02/82.02


	
ADZ/RDZ450

	
1100

	
1100

	
88.02/97.52


	
1518

	
ADZ/RDZ450

	
15

	
Y160

	
1100

	
1100

	
88.02/97.52


	
ADZ/RDZ500

	
1100

	
1100

	
97.16/108.16


	
1522

	
ADZ/RDZ500

	
18.5

	
Y180

	
1100

	
1100

	
97.16/108.16


	
ADZ/RDZ560

	
1300

	
1300

	
186.0/195.0


	
1622

	
ADZ/RDZ560

	
18.5

	
Y180

	
1300

	
1300

	
186.0/195.0


	
ADZ/RDZ630

	
1400

	
1400

	
250.0/253.0


	
1822

	
ADZ/RDZ560

	
18.5

	
Y180

	
1300

	  	
186.0/195.0


	
ADZ/RDZ630

	
1400

	  	
250.0/253.0


	
1824

	
ADZ/RDZ560

	
22

	
Y180

	
1300

	  	
186.0/195.0


	
ADZ/RDZ630

	
1400

	  	
250.0/253.0


	
1825

	
ADZ/RDZ630

	
30

	
Y200

	
1400

	  	
250.0/253.0


	
ADZ/RDZ710

	
1500

	  	
281.0/323.0


	
2025

	
ADZ/RDZ630

	
30

	
Y200

	
1400

	  	
250.0/253.0


	
ADZ/RDZ710

	
1500

	  	
281.0/323.0


	
2226

	
ADZ/RDZ710

	
30

	
Y200

	
1500

	  	
281.0/323.0


	
ADZ/RDZ800

	
1700

	  	
370.0/405.0


	
2330

	
ADZ/RDZ800

	
37

	
Y225

	
1700

	  	
370.0/405.0


	
ADZ/RDZ900

	
1900

	  	
442.0/490.0


	
2334

	
ADZ/RDZ800

	
45

	
Y225

	
1700

	  	
370.0/405.0


	
ADZ/RDZ900

	
1900

	  	
442.0/490.0












Note: The weight on the chart only refers to the weight of pipe coil, exclusive of weight of box.,


 




  





16











  






 



Fan Section









Outlet direction of horizontal unit and flange size


 










(单位:mm)




	
Unit Spec


39CBFI

	
Fitting Fan

	
A

	
D

	
E


	
THF

	
BHF

	
UBF

	
UBR


	
0609

	
ADZ180

	
289.5

	
229

	
290.5

	
193.5

	
125

	
222


	
0610

	
ADZ180

	
314.5

	
229

	
290.5

	
193.5

	
125

	
222


	
ADZ200

	
312.5

	
256

	
298.5

	
192.5

	
125

	
231


	
0712

	
ADZ/RDZ225

	
411.5

	
288

	
312.5

	
192.5

	
125

	
268


	
ADZ/RDZ250

	
411.5

	
322

	
324.0

	
192.0

	
125

	
257


	
0813

	
ADZ/RDZ280

	
392.5

	
361

	
340.5

	
193.5

	
125

	
306


	
ADZ/RDZ315

	
349.5

	
404

	
359.5

	
191.5

	
125

	
293


	
0914

	
ADZ/RDZ315

	
399.5

	
404

	
359.5

	
191.5

	
125

	
293


	
ADZ/RDZ355

	
391.5

	
453

	
384.5

	
194.5

	
125

	
315


	
1015

	
ADZ/RDZ355

	
441.5

	
453

	
384.5

	
194.5

	
125

	
315


	
ADZ/RDZ400

	
391.5

	
507

	
413.0

	
193.0

	
125

	
345


	
1016

	
ADZ/RDZ355

	
491.5

	
453

	
384.5

	
194.5

	
125

	
315


	
ADZ/RDZ400

	
491.5

	
507

	
413.0

	
193.0

	
125

	
345


	
1117

	
ADZ/RDZ400

	
541.5

	
507

	
413.0

	
193.0

	
125

	
345


	
ADZ/RDZ450

	
424.5

	
569

	
441.5

	
193.5

	
125

	
373


	
1317

	
ADZ/RDZ400

	
541.5

	
507

	
413.0

	
193.0

	
125

	
345


	
ADZ/RDZ450

	
379.5

	
569

	
441.5

	
193.5

	
125

	
373


	
1518

	
ADZ/RDZ450

	
429.5

	
569

	
441.5

	
193.5

	
125

	
373


	
ADZ/RDZ500

	
410.5

	
638

	
463.5

	
193.5

	
125

	
395


	
1522

	
ADZ/RDZ500

	
610.5

	
638

	
463.5

	
193.5

	
125

	
395


	
ADZ/RDZ560

	
617.5

	
715

	
554.5

	
253.5

	
125

	
426


	
1622

	
ADZ/RDZ560

	
617.5

	
715

	
554.5

	
253.5

	
125

	
426


	
ADZ/RDZ630

	
531.5

	
801

	
596.5

	
252.5

	
125

	
469


	
1822

	
ADZ/RDZ560

	
617.5

	
715

	
554.5

	
253.5

	
125

	
426


	
ADZ/RDZ630

	
531.5

	
801

	
596.5

	
252.5

	
125

	
469


	
1824

	
ADZ/RDZ560

	
717.5

	
715

	
554.5

	
253.5

	
125

	
426


	
ADZ/RDZ630

	
691.5

	
801

	
596.5

	
252.5

	
125

	
469


	
1825

	
ADZ/RDZ630

	
741.5

	
801

	
596.5

	
252.5

	
125

	
469


	
ADZ/RDZ710

	
629.5

	
898

	
644.5

	
253.5

	
125

	
516


	
2025

	
ADZ/RDZ630

	
741.5

	
801

	
596.5

	
252.5

	
125

	
469


	
ADZ/RDZ710

	
629.5

	
898

	
644.5

	
253.5

	
125

	
516


	
2226

	
ADZ/RDZ710

	
679.5

	
898

	
644.5

	
253.5

	
125

	
516


	
ADZ/RDZ800

	
620.0

	
1007

	
713.5

	
266.5

	
125

	
572


	
2330

	
ADZ/RDZ800

	
820.0

	
1007

	
713.5

	
266.5

	
125

	
572


	
ADZ/RDZ900

	
792.0

	
1130

	
770.5

	
266.5

	
125

	
629


	
2334

	
ADZ/RDZ800

	
1020.0

	
1007

	
713.5

	
266.5

	
125

	
572


	
ADZ/RDZ900

	
1167.0

	
1130

	
770.5

	
266.5

	
125

	
629









 




  





17











  






 



Fan Section









Outlet direction of vertical unit and flange size


 











(单位:mm)







	
Unit Spec


39CBFI

	
Fitting Fan

	
A

	
D

	
E


	
THF

	
BHF

	
UBF

	
UBR


	
0609

	
ADZ180

	
289.5

	
229

	
940.5

	
843.5

	
125

	
222


	
0610

	
ADZ180

	
339.5

	
229

	
940.5

	
843.5

	
125

	
222


	
ADZ200

	
312.5

	
256

	
948.5

	
842.5

	
125

	
231


	
0712

	
ADZ/RDZ225

	
411.5

	
288

	
1062.5

	
842.5

	
125

	
268


	
ADZ/RDZ250

	
411.5

	
322

	
1074.0

	
942.0

	
125

	
257


	
0813

	
ADZ/RDZ280

	
392.5

	
361

	
1190.5

	
1043.5

	
125

	
306


	
ADZ/RDZ315

	
349.5

	
404

	
1209.5

	
1041.5

	
125

	
293


	
0914

	
ADZ/RDZ315

	
399.5

	
404

	
1309.5

	
1141.5

	
125

	
293


	
ADZ/RDZ355

	
391.5

	
453

	
1334.5

	
1144.5

	
125

	
315


	
1015

	
ADZ/RDZ355

	
441.5

	
453

	
1434.5

	
1244.5

	
125

	
315


	
ADZ/RDZ400

	
391.5

	
507

	
1463.0

	
1243.0

	
125

	
345


	
1016

	
ADZ/RDZ355

	
491.5

	
453

	
1434.5

	
1244.5

	
125

	
315


	
ADZ/RDZ400

	
491.5

	
507

	
1463.0

	
1243.0

	
125

	
345


	
1117

	
ADZ/RDZ400

	
541.5

	
507

	
1563.0

	
1343.0

	
125

	
345


	
ADZ/RDZ450

	
424.5

	
569

	
1591.5

	
1343.5

	
125

	
373


	
1317

	
ADZ/RDZ400

	
541.5

	
507

	
1763.0

	
1543.0

	
125

	
345


	
ADZ/RDZ450

	
379.5

	
569

	
1791.5

	
1543.5

	
125

	
373


	
1518

	
ADZ/RDZ450

	
429.5

	
569

	
1991.5

	
1743.5

	
125

	
373


	
ADZ/RDZ500

	
410.5

	
638

	
2013.5

	
1743.5

	
125

	
395


	
1522

	
ADZ/RDZ500

	
610.5

	
638

	
2013.5

	
1743.5

	
125

	
395


	
ADZ/RDZ560

	
617.5

	
715

	
2104.5

	
1803.5

	
125

	
426


	
1622

	
ADZ/RDZ460

	
617.5

	
715

	
2204.5

	
1903.5

	
125

	
426


	
ADZ/RDZ5630

	
531.5

	
801

	
2246.5

	
1902.5

	
125

	
469


















  





18











  






 


Selection Humidifier







The unit humidifier can add dry steam humidifier, or high pressure spray humidifier and wet film humidifier.


Dry Steam Humidifier


The steam pressure scope of dry steam is (0.02 ~ 0.4)MPa


High –pressure Spray Humidifier


When using high pressure humidifier, it should consider humidifying efficiency which is 40-50%. Humidifying number =Spray amount ×humidifying efficiency


Spray water pressure is 0.5MPa


Wet Film Humidifier



Wet Film humidifier is equipment that  water molecule process spontaneous evaporation to wet the air, in which water supply is as 3 folders as humidifying amount.




    





	
Unit Spec 39CBFI

	
Humidifying amount of  day steam kg/h

	
High Pressure spray amount高压喷雾量 kg/h


	
0609

	
6.3~20

	
5~15


	
0610

	
10~40

	
5~15


	
0712

	
25~63

	
11~25


	
0813

	
20~80

	
15~35


	
0914

	
32~80

	
26~45


	
1015

	
40~80

	
36~65


	
1016

	
63~125

	
36~65


	
1117

	
80~160

	
46~80


	
1317

	
125~200

	
46~80


	
1518

	
125~200

	
66~110


	
1522

	
160~200

	
81~130


	
1622

	
160~200

	
81~130


	
1822

	
160~200

	
81~130


	
1824

	
200~315

	
111~140


	
1825

	
200~315

	
111~140


	
2025

	
315~400

	
141~180


	
2226

	
315~500

	
141~180


	
2330

	
315~630

	
150~220


	
2334

	
315~630

	
150~220

















	
Unit Spec39CBFI

	
Humidifying amount of wet film(kg / h)


	
Efficient40%

	
efficient 60%

	
efficient 75%

	
efficient 85%


	
0609

	
5.8

	
8.6

	
10.8

	
11.5


	
0610

	
8.0

	
11.9

	
14.9

	
15.9


	
0712

	
11.5

	
17.2

	
21.5

	
23.0


	
0813

	
16.4

	
24.5

	
30.7

	
32.7


	
0914

	
19.0

	
28.5

	
35.6

	
38.0


	
1015

	
24.5

	
36.8

	
46.0

	
49.0


	
1016

	
27.0

	
40.4

	
50.0

	
53.9


	
1117

	
33.6

	
50.4

	
63.0

	
67.2


	
1317

	
39.3

	
59.0

	
73.8

	
78.7


	
1518

	
48.6

	
72.9

	
91.2

	
97.3


	
1522

	
55.3

	
82.9

	
103.6

	
110.5


	
1622

	
59.7

	
89.5

	
111.9

	
119.3


	
1822

	
68.5

	
102.8

	
128.5

	
137.0


	
1824

	
77.4

	
116.0

	
145.0

	
154.7


	
1825

	
84.0

	
126.0

	
157.5

	
168.0


	
2025

	
92.8

	
139.2

	
174.0

	
185.6


	
2226

	
108.3

	
162.4

	
203.0

	
216.6


	
2330

	
128.2

	
192.3

	
240.3

	
256.4


	
2334

	
150.3

	
225.4

	
281.8

	
300.6







 




  





19











  






 



Silencer


 




Specification and Weight of Silencer










	
Unit Spec

	
First Grade Silencing(6M)

	
Weight


	
39CBFI

	
6M-I

	
7M-I

	
8M-I

	
9M-I

	
10M-I

	
11M-I

	
12M-I

	
6M-II

	
7M-II

	
8M-II

	
9M-II

	
10M-II

	
11M-II

	
12M-II

	
kg


	
0609

	
2

	  	  	  	  	  	  	
2

	  	  	  	  	  	  	
30


	
0610

	
2

	  	  	  	  	  	  	
2

	  	  	  	  	  	  	
30


	
0712

	  	
3

	  	  	  	  	  	  	
2

	  	  	  	  	  	
44


	
0813

	  	  	
3

	  	  	  	  	  	  	
2

	  	  	  	  	
50


	
0914

	  	  	  	
5

	  	  	  	  	  	  	  	  	  	  	
65


	
1015

	  	  	  	  	
4

	  	  	  	  	  	  	
2

	  	  	
74


	
1016

	  	  	  	  	
4

	  	  	  	  	  	  	
2

	  	  	
74


	
1117

	  	  	  	  	  	
6

	  	  	  	  	  	  	  	  	
90


	
1317

	
6

	
6

	  	  	  	  	  	  	  	  	  	  	  	  	
114


	
1518

	  	
5

	
5

	  	  	  	  	  	
2

	
2

	  	  	  	  	
136


	
1522

	  	
6

	
6

	  	  	  	  	  	
2

	
2

	  	  	  	  	
158


	
1622

	  	  	
12

	  	  	  	  	  	  	
4

	  	  	  	  	
170


	
1822

	  	  	  	
12

	  	  	  	  	  	  	
4

	  	  	  	
190


	
1824

	  	  	  	
14

	  	  	  	  	  	  	
4

	  	  	  	
216


	
1825

	  	  	  	
14

	  	  	  	  	  	  	
4

	  	  	  	
216


	
2025

	  	  	  	  	
14

	  	  	  	  	  	  	
4

	  	  	
228


	
2226

	  	  	  	  	  	
14

	  	  	  	  	  	  	  	  	
210


	
2330

	  	  	  	  	  	
9

	
9

	  	  	  	  	  	
2

	
2

	
325


	
2334

	  	  	  	  	  	
10

	
10

	  	  	  	  	  	
2

	
2

	
356

















	
Unit Spec

	
Second Silencing (12M)

	
Weight


	
39CBFI

	
6M-I

	
7M-I

	
8M-I

	
9M-I

	
10M-I

	
11M-I

	
12M-I

	
6M-II

	
7M-II

	
8M-II

	
9M-II

	
10M-II

	
11M-II

	
12M-II

	
kg


	
0609

	
4

	  	  	  	  	  	  	
4

	  	  	  	  	  	  	
60


	
0610

	
4

	  	  	  	  	  	  	
4

	  	  	  	  	  	  	
60


	
0712

	  	
6

	  	  	  	  	  	  	
4

	  	  	  	  	  	
88


	
0813

	  	  	
6

	  	  	  	  	  	  	
4

	  	  	  	  	
100


	
0914

	  	  	  	
10

	  	  	  	  	  	  	  	  	  	  	
130


	
1015

	  	  	  	  	
8

	  	  	  	  	  	  	
4

	  	  	
148


	
1016

	  	  	  	  	
8

	  	  	  	  	  	  	
4

	  	  	
148


	
1117

	  	  	  	  	  	
12

	  	  	  	  	  	  	  	  	
180


	
1317

	
12

	
12

	  	  	  	  	  	  	  	  	  	  	  	  	
228


	
1518

	  	
10

	
10

	  	  	  	  	  	
4

	
4

	  	  	  	  	
272


	
1522

	  	
12

	
12

	  	  	  	  	  	
4

	
4

	  	  	  	  	
316


	
1622

	  	  	
24

	  	  	  	  	  	  	
8

	  	  	  	  	
340


	
1822

	  	  	  	
24

	  	  	  	  	  	  	
8

	  	  	  	
380


	
1824

	  	  	  	
28

	  	  	  	  	  	  	
8

	  	  	  	
432


	
1825

	  	  	  	
28

	  	  	  	  	  	  	
8

	  	  	  	
432


	
2025

	  	  	  	  	
28

	  	  	  	  	  	  	
8

	  	  	
456


	
2226

	  	  	  	  	  	
28

	  	  	  	  	  	  	  	  	
420


	
2330

	  	  	  	  	  	
18

	
18

	  	  	  	  	  	
4

	
4

	
650


	
2334

	  	  	  	  	  	
20

	
20

	  	  	  	  	  	
4

	
4

	
712







 




  





20











  






 



Filter


 




	
Filter

	  	  
	
In accordance with demand of functions, there are several filters can be selected  :


	
1” thk external pump speedy filter

	  	
2” thk external pump low speed filter


	
1” thk internal pump speedy filter

	  	
2” thk internal pump low speed filter


	
Internal preliminary bag filter

	  	
internal sub-efficiency bag filter


	
Preliminary and medial filter performance

	  	
 


	

filter efficiency: Board- preliminary G3 Grade, bag medium F5 Grade



	  	  









 








 




21











  







 


Qualification and Quantity of Filter


  





	
Unit Spec

	
Board Filter External Specification η=G3

	
weight


kg


	
39CBFI

	
392 × 395

	
492 × 395

	
592 × 395

	
692 × 395

	
392 × 495

	
492 × 495

	
592 × 495

	
thk 1”

	
thk 2”


	
0609

	
2

	  	  	  	  	  	  	
2.6

	
3.1


	
0610

	
2

	  	  	  	  	  	  	
2.6

	
3.1


	
0712

	  	  	  	  	  	
2

	  	
3.2

	
3.8


	
0813

	  	  	
3

	  	  	  	  	
4.8

	
5.8


	
0914

	  	  	  	
3

	  	  	  	
5.1

	
6.1


	
1015

	
4

	  	  	  	
2

	  	  	
8.2

	
9.8


	
1016

	
2

	  	  	  	
4

	  	  	
8.6

	
10.3


	
1117

	  	  	  	  	
3

	
3

	  	
9.3

	
11.2


	
1317

	  	  	  	  	  	
3

	
3

	
10.2

	
12.2


	
1518

	
8

	
4

	  	  	  	  	  	
16.4

	
19.7


	
1522

	  	  	  	  	
8

	
4

	  	
18.4

	
22.1


	
1622

	  	  	  	  	
4

	
8

	  	
18.8

	
22.6


	
1822

	  	  	  	  	
4

	  	
8

	
20.4

	
24.5


	
1824

	
3

	  	
6

	  	
2

	  	
4

	
23.7

	
28.4


	
1825

	
2

	  	
4

	  	
3

	  	
6

	
24.3

	
29.2


	
2025

	
4

	
4

	  	  	
6

	
6

	  	
29.8

	
35.8


	
2226

	  	
4

	  	  	  	
16

	  	
31.6

	
37.9


	
2330

	  	
6

	
2

	  	  	
12

	
4

	
38.6

	
46.3


	
2334

	  	
9

	
3

	  	  	
12

	
4

	
44.7

	
53.6













	
Unit Spec

	
Board Internal Filter Specification=G3

	
Weight


kg


	
39CBFI

	
290 × 595

	
390 × 493

	
390 × 595

	
595 × 595

	
thk 1”

	
thk 2”


	
0609

	  	
2

	  	  	
2.8

	
3.4


	
0610

	  	
2

	  	  	
2.8

	
3.4


	
0712

	
3

	  	  	  	
3.5

	
4.2


	
0813

	  	  	  	
2

	
5.4

	
6.5


	
0914

	
2

	  	
2

	  	
6.0

	
7.2


	
1015

	
2

	  	  	
2

	
6.4

	
7.7


	
1016

	
3

	  	  	
2

	
7.6

	
9.1


	
1117

	  	  	
3

	
2

	
8.2

	
9.8


	
1317

	
2

	  	  	
4

	
11.0

	
13.2


	
1518

	  	  	
2

	
4

	
11.0

	
13.2


	
1522

	
2

	  	  	
6

	
14.4

	
17.3


	
1622

	
5

	  	  	
6

	
18.0

	
21.6


	
1822

	
5

	  	  	
6

	
18.9

	
22.7


	
1824

	
2

	  	
3

	
6

	
19.5

	
23.4


	
1825

	
4

	  	  	
8

	
22.0

	
26.4


	
2025

	  	  	  	
12

	
24.0

	
28.8


	
2226

	
4

	  	  	
12

	
28.8

	
34.6


	
2330

	
7

	  	  	
12

	
34.5

	
41.4


	
2334

	
8

	  	  	
15

	
39.6

	
47.5














  





22











  







Qualification and Quantity of Filter










	
Unit Spec

	
Bag internal filter Specification η=F5

	
weight


	
kg


	
39CBFI

	
290X595

	
390X493

	
390X595

	
595X595

	
590X290

	
590X390

	
thk 1”

	
thk 2”


	
0609

	  	
2

	  	  	  	  	
2.2

	
2.6


	
0610

	  	
2

	  	  	  	  	
2.2

	
2.6


	
0712

	
3

	  	  	  	  	  	
2.6

	
3.1


	
0813

	  	  	  	
2

	  	  	
5.0

	
6.0


	
0914

	  	  	  	  	
2

	
2

	
5.2

	
6.2


	
1015

	  	  	  	
2

	
2

	  	
5.2

	
6.2


	
1016

	
1

	  	  	
2

	
2

	  	
5.9

	
7.1


	
1117

	  	  	
1

	
2

	  	
2

	
6.5

	
7.8


	
1317

	
2

	  	  	
4

	  	  	
8.0

	
9.6


	
1518

	  	  	
2

	
4

	  	  	
8.0

	
9.6


	
1522

	
2

	  	  	
6

	  	  	
10.6

	
12.7


	
1622

	
2

	  	  	
6

	
3

	  	
14.2

	
17.0


	
1822

	
2

	  	  	
6

	
3

	  	
14.5

	
17.4


	
1824

	
2

	  	  	
6

	  	
3

	
14.7

	
17.6


	
1825

	  	  	  	
8

	
4

	  	
16.4

	
19.7


	
2025

	  	  	  	
12

	  	  	
16.8

	
20.2


	
2226

	  	  	  	
12

	
4

	  	
21.6

	
25.9


	
2330

	
3

	  	  	
12

	
4

	  	
25.6

	
30.7


	
2334

	
3

	  	  	
15

	
5

	  	
30.3

	
36.4













	

机组规格



	
Box Efficient filter Specification η=H11

	
weight


	
kg


	
39CBFI

	
290X595

	
390X

	
493

	
390X595

	
595X595

	
thk 12”


	
0609

	  	
2

	  	  	  	
29.0


	
0610

	  	
2

	  	  	  	
29.0


	
0712

	
3

	  	  	  	  	
39.0


	
0813

	  	  	  	  	
2

	
44.0


	
0914

	
2

	  	  	
2

	  	
61.0


	
1015

	
2

	  	  	  	
2

	
70.0


	
1016

	
3

	  	  	  	
2

	
83.0


	
1117

	  	  	  	
3

	
2

	
96.5


	
1317

	
2

	  	  	  	
4

	
114.0


	
1518

	  	  	  	
2

	
4

	
123.0


	
1522

	
2

	  	  	  	
6

	
158.0


	
1622

	
5

	  	  	  	
6

	
197.0


	
1822

	
5

	  	  	  	
6

	
197.0


	
1824

	
2

	  	  	
3

	
6

	
210.5


	
1825

	
4

	  	  	  	
8

	
228.0


	
2025

	  	  	  	  	
12

	
264.0


	
2226

	
4

	  	  	  	
12

	
316.0


	
2330

	
7

	  	  	  	
12

	
355.0


	
2334

	
8

	  	  	  	
15

	
434.0













	
Purification level

	  	  	  	  	  	  	  	  	  	  
	
US Fed. Std. 209D

	
100,000

	  	
10,000

	
1,000

	
100

	  	
10

	
1

	  	
0.1


	
US Fed. Std. 209E

	
M6.5

	  	
M5.5

	
M4.5

	
M3.5

	  	
M2.5

	
M1.5

	  	
M0.5


	
Purification Level VDI 2083

	
6

	  	
5

	
4

	
3

	  	
2

	
1

	  	
0


	
Flow form

	
Tangled Flow

	
Transitional Flow

	  	  	
horizon Flow

	  	  
	
filter


Filing


Rtae(%)

	
5~10

	  	
10~20

	
30~70

	
>80

	  	  	
>90

	  	  
	
First grade


filteringlevel

	  	
G4

	  	  	
F5

	  	  	  	
F6

	  
	
Second Grade


filtering level


DIN EN 779


DIN 24 183/EN 1822

	  	  	
F7

	  	  	
F9


H10

	  	
H10


H12


H13

	  	
H13


	
Third Grade


Fitering Level

	  	
H12


H13

	  	
H13

	
H14

	  	
H15

	
H16

	  	
H17







 




  





23











  






 



Electrical heating Section










	
Model selection regulation of Electrical heating pipe coil


	Unit Type	
V Area

	
Single row electrical

	
weight

	
Second row electrical

	
Third row electrical Wgt.


	
39CBFI

	
单根最大功率(W)

	
(m2)

	
Heating (kW)

	
kg

	
Heating

	
weight

	
Heating

	  
	
0609

	
810

	
0.26

	
< 5

	
17

	
5~10

	
21.0

	
10~14

	
25.0


	
0610

	
960

	
0.30

	
< 6

	
18

	
6~12

	
22.0

	
12~18

	
26.0


	
0712

	
1260

	
0.48

	
< 8

	
27.5

	
8~16

	
32.5

	
16~22

	
37.5


	
0813

	
1410

	
0.63

	
< 13

	
30.5

	
13~26

	
39.5

	
26~38

	
48.5


	
0914

	
1560

	
0.80

	
< 14.5

	
35

	
14.5~29

	
44.5

	
29~43

	
54.0


	
1015

	
1710

	
1.00

	
< 20.5

	
42

	
20.5~41

	
55.5

	
41~60

	
69.0


	
1016

	
1860

	
1.08

	
< 22.5

	
43.7

	
22.5~45

	
58.2

	
45~65

	
72.7


	
1117

	
2010

	
1.31

	
< 24

	
47.6

	
24~48

	
63.2

	
48~70

	
78.6


	
1317

	
2010

	
1.58

	
< 30

	
56.5

	
30~60

	
76.0

	
60~85

	
95.5


	
1518

	
2360

	
2.00

	
< 36

	
63

	
36~72

	
84.0

	
72~105

	
105.0


	
1522

	
2960

	
2.53

	
< 44

	
70

	
44~88

	
96.0

	
88~130

	
122.0


	
1622

	
2960

	
2.72

	
< 46

	
74

	
46~92

	
100.0

	
92~135

	
126.0


	
1822

	
2960

	
3.10

	
< 53

	
73

	
53~106

	
114.0

	
106~155

	
145.0


	
1824

	
3260

	
3.42

	
< 59

	
95.5

	
59~118

	
130.5

	
118~175

	
165.5


	
1825

	
3410

	
3.59

	
< 61

	
97.2

	
61~122

	
133.2

	
122~180

	
169.2


	
2025

	
3410

	
4.02

	
< 72

	
107

	
72~144

	
149.0

	
144~210

	
191.0


	
2226

	
3560

	
4.66

	
< 85

	
121.5

	
85~170

	
171.5

	
170~250

	
221.5


	
2330

	
4160

	
5.74

	
< 100

	
137

	
100~200

	
196.0

	
200~280

	
255.0


	
2334

	
5360

	
6.61

	
< 125

	
148.5

	
125~250

	
216.5

	
250~340

	
284.5







 



Chassis Weight


 


(单位:kg)










	
Unit Weight

	
39CBFI

	
39CBFI


	
39CBFI

	
3M

	
6M

	
9M

	
12M

	
head Face


	
0609

	
56.7

	
81.3

	
105.6

	
130.7

	
8.4


	
0610

	
60.2

	
86.0

	
111.9

	
138.5

	
9.4


	
0712

	
70.5

	
100.3

	
129.2

	
159.4

	
13.5


	
0813

	
79.4

	
111.0

	
144.5

	
178.1

	
16.9


	
0914

	
84.1

	
119.3

	
155.0

	
190.5

	
20.8


	
1015

	
88.3

	
127.3

	
165.5

	
204.8

	
24.9


	
1016

	
92.1

	
132.2

	
171.3

	
211.5

	
26.6


	
1117

	
97.7

	
140.3

	
182.7

	
224.4

	
31.3


	
1317

	
102.1

	
146.9

	
191.7

	
235.8

	
37.0


	
1518

	
109.9

	
158.2

	
206.7

	
254.4

	
45.5


	
1522

	
143.4

	
198.9

	
253.0

	
307.8

	
55.9


	
1622

	
145.5

	
202.2

	
257.4

	
313.5

	
59.8


	
1822

	
148.8

	
207.8

	
265.3

	
323.7

	
71.4


	
1824

	
159.8

	
221.3

	
283.6

	
346.8

	
73.7


	
1825

	
164.3

	
226.9

	
290.5

	
262.8

	
76.9


	
2025

	
168.5

	
233.6

	
299.4

	
366.0

	
85.6


	
2226

	
177.1

	
245.8

	
315.2

	
385.3

	
98.4


	
2330

	
197.0

	
271.6

	
346.8

	
422.3

	
119.1


	
2334

	
214.0

	
293.2

	
373.4

	
453.6

	
135.3







 


Note: the weight shown on the table include the weight of base


 




  





24











  









Type-Market Method of 39CBF Unit




 





 


Computing Formula for Unit Modulus and Dimension




 


39CBFI


(1)  Unit Height = Height Modulus × 100 + 100 + 100 (Base)


(2)  Unit Width = Width Modulus× 100 + 100


Example:39CBFI 0712


07 Height Modulus


Height of Unit is:7 × 100 + 100 + 100 (底座) =900mm


12 Width Modulus


Width of Unit:12 × 100 + 100 =1300mm


 



Air Flow Scope of 39CBF Unit




 


39CBF      2209~198090m3/h






  





25










 




 



Characteristics of Unit 39CBF




  


Characteristics of Unit


 



	
  

	
·

	
Modules design, parts have strong commonality, easy change







 



	
  

	
·

	
Double panel structure, 50mm foam 50mm foam panel is light and rigid, and its thermal conductivity is less than 0.0199W/M.°C







 



New seal。




 



	
   

	
·

	
The down drain method ensures all the condensed water discharged. 。








·      The lowest point of pipe coil loop equips a freeing port, which can empty the standing water inside pipe coil. This can avoid frost crack of pipe coil.















 



	
  

	
·

	
Using corrugated link mechanism adjustment, and air damper can open flexibly. Electric remote control device can be installed.








·      Each section equips unit base to strength whole machine, reduce unit’s vibration, easy for transport and split joint.




 


Characteristics of performance








	
  

	
·

	
Pipe coil header is steel header, and copper header is available if user has such requirement. The drain valve and air evacuation valve are installed on pipe coil header to ensure no air on loop, meanwhile empty standing water inside pipe coil to avoid frost crack.







·     The case of unit includes panel, framework and gland strip. The panel adopts unique embedding method, so that connection points can be connected precisely. The new gland strip is applied between frame and panel, and each access door and pass-through of pipes has been meticulously designed to ensure air tightness of unit.  When face velocity is more than 2.5m/s, water-dam can be added behind pipe coil, which can effectively separate water from air.


 



	
  

	
·

	
Preliminary  filter is board structure , and efficiency reaches G4 Grade







 


Medium filter is bag structure, efficiency reaches F8 Grade


 



·      Secondary structure is bag structure, its efficiency reach F9. The high efficiency filter’s efficiency reaches H13 Grade.









Computer Model Selection


 


·    The company provides swift and précised computer model selection service. Calculate the most idea function configuration and most economic type.







Easy and Convenient Repair



·   Parts have strong commonality, very easy to change, and price is cheap. Detachable panel can be installed on one side of unit; furthermore, access doors are set to necessary function setting.






·   It is convenient to maintain fan, pipe coil and filters. Pipe coil is installed on lead rail of water pan, easy to maintain, clean and dismantle.











Intelligent Control


 


·   All kinds of sensor structure such as transducer can be installed to realize auto control






  





26










 








Characteristics of Unit 39CBF











EUROVENT Certificate


 



	 	
·

	
The product is China’s first air conditioner to gain EUROVENT. The certificate ensures the real performance is not less than that of sample product.








	 	
·

	
EUROVENT is the professional standard to modular air conditioner, which is widely accepted in the world. The standard is taken charge by France EUROVENT Institute, which is one of international authorized certification authority.








	 	
·

	
EUROVENT includes EN1886 and EN13053








	 	
·

	
EN1886 is for mechanical features of modular air conditioner, including mechanical strength of chassis, cold bridge factor, heat transfer coefficient, air leakage rate, by-pass rate of filter, sound insulation of chassis. EN13053 mainly aims at air conditioners that its whole performance precedes calculated value of model selection program.















 


EN1886: Euro Air Treatment Unit Standard  (39CBF)


 



	
Chassis


Grade

	
Max Re. Deflect


(mm.m-1)

	
Bear Max


Air Press


	
1

	
10

	
No


	
1A

	
10

	
Yes


	
2

	
4

	
No


	
2A

	
4

	
Yes







 



	
Class TB1

	
0.75 < Kb ≤ 1


	
Class TB2

	
0.6 < Kb ≤ 0.75


	
Class TB3

	
0.45 < Kb ≤ 0.6


	
Class TB4

	
0.3 < Kb ≤ 0.45


	
Class TB5

	
No Requirement                  无要求







 



	
Leakage Class

	
Max Air Leak Rate l/sm2                  最大漏风率 l/sm2


	
3A

	
5.70


	
A

	
1.90


	
B

	
0.63


	
C

	
0.21







 


Mechanical strength of chassis


 



Maximum relative deflection refers to max allowable deflection under ±1000Pa.




 



Bearing maximum air pressure of fan refers to the unit shall not be in permanent deformation under ±2500Pa .









Cold Bridge Proof Coefficient


 


The Cold Bridge Proof Coefficient formula Kb=Tmin/ Tair,, tmin is temperature difference between chassis inside and outer layer of chassis, tair is  difference value of temperature between chassis inside and external environment.


Air Leakage Rate


 


The air leakage rate of air treatment unit is measured inside the unit and under sub-pressure 400Pa and positive pressure


 


Outstanding features of 39CBF for industry environment


 



	
  

	
·

	
Excellent air tightness: case of unit consists of panel, frame and gland strip.The panel adopts unique embedding method, so that connection points can be connected precisely. The new gland strip is applied between frame and panel, and each access door and pass-through of pipes has been meticulously designed to ensure air tightness of unit. It completely complies with or beyond the GB/T14294-93.












·    Perfect thermal insulation


 


Between the panels of unit, 50mm thk foam polyurethane is applied as insulation material, which achieves good rigidity. There are even insulation quilt in the frame. Every joint has been treated specially to avoid appearance of cold bridge. Outer surface of panel has been pained specially, to ensure fireproofing and corrosion protection. The application conditions suitable for cold bridge proof, such as tobacco, hospital and electronics.




 


Performance index of box (Euro EN1886 )





 


Box’s  patent number:03270349.X






  





27










 







Quick Model Selection of 39CBF










	  	  	
Outline dimension

	  	  	  	  
	
Unit spec

	
Pipe coil ft.

	  	
Air Volume

	  	
excess pressure of


	
39CBF

	
area(m2)

	
H*

	
W

	
2.25m/s

	
2.5m/s

	
2.75m/s

	
outlet


	  	  	  	  	  	  	  	
Pa


	  	  	  	  	  	  	  	  
	
0609

	
0.24

	
710

	
1010

	
2008

	
2209

	
2430

	
200~800


	  	  	  	  	  	  	  	  
	
0610

	
0.34

	
710

	
1110

	
2755

	
3058

	
3364

	
200~800


	  	  	  	  	  	  	  	  
	
0712

	
0.49

	
810

	
1310

	
3979

	
4417

	
4859

	
200~800


	  	  	  	  	  	  	  	  
	
0813

	
0.70

	
910

	
1410

	
5663

	
6286

	
6915

	
200~800


	  	  	  	  	  	  	  	  
	
0914

	
0.81

	
1010

	
1510

	
6582

	
7306

	
8037

	
200~800


	  	  	  	  	  	  	  	  
	
1015

	
1.05

	
1110

	
1610

	
8495

	
9429

	
10372

	
200~800


	  	  	  	  	  	  	  	  
	
1016

	
1.15

	
1110

	
1710

	
9337

	
10364

	
11400

	
200~800


	  	  	  	  	  	  	  	  
	
1117

	
1.44

	
1210

	
1810

	
11632

	
12912

	
14703

	
200~800


	  	  	  	  	  	  	  	  
	
1317

	
1.68

	
1410

	
1810

	
13623

	
15121

	
16633

	
200~800


	  	  	  	  	  	  	  	  
	
1518

	
2.07

	
1610

	
1910

	
16837

	
18689

	
20558

	
200~800


	  	  	  	  	  	  	  	  
	
1522

	
2.36

	
1610

	
2310

	
19133

	
21238

	
23362

	
200~800


	  	  	  	  	  	  	  	  
	
1622

	
2.55

	
1710

	
2310

	
20664

	
22937

	
25231

	
200~800


	  	  	  	  	  	  	  	  
	
1822

	
2.93

	
1910

	
2310

	
23725

	
26335

	
28968

	
200~800


	  	  	  	  	  	  	  	  
	
1824

	
3.30

	
1910

	
2510

	
26786

	
29733

	
32706

	
200~800


	  	  	  	  	  	  	  	  
	
1825

	
3.59

	
1910

	
2610

	
29082

	
32281

	
35509

	
200~800


	  	  	  	  	  	  	  	  
	
2025

	
3.96

	
2110

	
2610

	
30143

	
35679

	
39247

	
200~800


	  	  	  	  	  	  	  	  
	
2226

	
4.63

	
2310

	
2710

	
37501

	
41626

	
45789

	
200~800


	  	  	  	  	  	  	  	  
	
2330

	
5.48

	
2410

	
3110

	
44388

	
49271

	
54198

	
200~800


	  	  	  	  	  	  	  	  
	
2334

	
6.42

	
2410

	
3510

	
52041

	
57766

	
63543

	
200~800


	  	  	  	  	  	  	  	  
	
2532

	
8.13

	
2610

	
3310

	
65853

	
73170

	
80487

	
200~800


	  	  	  	  	  	  	  	  
	
2832

	
9.01

	
2910

	
3310

	
72973

	
81081

	
89198

	
200~800


	  	  	  	  	  	  	  	  
	
3132

	
9.98

	
3210

	
3310

	
80838

	
89820

	
98802

	
200~800


	  	  	  	  	  	  	  	  
	
3438

	
12.36

	
3510

	
3910

	
100116

	
111240

	
122364

	
200~800


	  	  	  	  	  	  	  	  
	
3841

	
14.69

	
3910

	
4210

	
118989

	
132210

	
145431

	
200~800


	  	  	  	  	  	  	  	  
	
4444

	
17.72

	
4510

	
4510

	
143532

	
159480

	
175428

	
200~800


	  	  	  	  	  	  	  	  
	
4750

	
22.01

	
4810

	
5110

	
178281

	
198090

	
217899

	
200~800







 







注:1、*Height H excludes 100mm thk base and dimension of top wind gap, 2532~4750’s base is 200mm.


2、The length of unit varies in accordance with function configuration.


3、Water Dam should be installed when wind speed is over 2.5m/s.






  





28










 







Other Specification


 




1、 The company can use computer model selection program to design specifically for different operation conditions users provided and select optimized type of unit.


 


2、 Requirement for foundation of unit:


 


·         The base for unit must design in accordance with length and width of unit, which shall level up horizontally.


 


·         The foundation shall be above ground in order to install trap of condensed water. Please refer to the following picture:





 












3、When connecting pipes, please note:


 


·         The working pressure of cold water pipe coil and hot water pipe coil in design shall be 1.6Mpa.


 


·         The maximum pressure of steam pipe coil is no more than 1.4MPa.


 



4、As for fresh-air unit, when temperature of fresh air is below 0°C,operator  turn on device to warm up pipe coil and take other relevant measures before turn on the unit, in order to prevent unit from frozen and burst.




 


5、Flexible joint must be used in the connection section of fan outlet and air duct.


 



6、When stopping  the unit and temperature of pipe coil is lower than freezing temperature, the water inside pipe shall be empty and all standing water shall be blown out. If standing water cannot blow empty, antifreeze shall be added in.




 


7、Insulation measures have been taken into consideration, the surface will not produce dews under normal conditions.


 


8、Please leave sufficient space for routine examination.


 


9、Temperature of supplied air shall not exceed 80°C, if so, user shall raise the requirement that high temperature bearings and special motor will be used.


 


10、If customer has special configuration, such as electric adjustable damper, copper header, stainless steel water pan, high efficient filter and other non-standard requirement, customer shall specify when ordering the purchase.


 



11、If customer needs other requirement such as silencing, secondary air return, purification, adjustment of frequency, recycling of energy, customer shall specify when ordering. Carrier will meet all those requirements. The steam pressure scope needed for humidifying dry steam ranges from 0.02-0.04Mpa.


 




  





29