Name: Steven Smokey

Title: Senior Generation Engineer

Company: Great River Energy

Sign Date: 9/2/2010

Name: George Lipinski, PE

Title: Source Testing Unit Leader

Company: URS Corporation

Sign Date: 9/2/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 03, 2011 Page 1 of 25
9/2/2010

Facility Information:

Stanton

4001 Hwy. 200A

Stanton ND 58571

Contact: Steve Smokey

Phone: 701 745-5204

Fax: Of above person

Email: ssmokey@grenergy.com

Testing Company:

URS Corporation

9400 Amberglen Boulevard

P.O. Box 201088

Austin TX 78729

Contact:Meggan DeLollis

Phone: 512 454-4797

Fax: Of above person

Email: Of above person

Air Permit Number:

2824

Permitted Source ID/Name:

1 Enter the Boiler ID of the tested boiler (left)

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

This description should describe the process and associated controls to differentiate this facility from, or document 

similarity with others of same SCC.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: Enter ARS ID FRS #: Enter FRS ID

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 

ESP1a

0 0 0 11.17 0 0 4 3

Stack Exit 

ESP2b

0 0 0 11.17 0 0 4 3

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 180 0

ESP1a

Stack Exit Carbon Monoxide Method 10 3 120 0

ESP1a

Thursday, February 03, 2011 Page 2 of 25
9/2/2010

Stack Exit Formaldehyde Method 0011 3 120 0

ESP1a

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

ESP1a

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

ESP1a

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

ESP1a

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

ESP1a

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

ESP1a

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

ESP1a

Stack Exit OCDD Method 23 3 480 0

ESP1a

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

ESP1a

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

ESP1a

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

ESP1a

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

ESP1a

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

ESP1a

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

ESP1a

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

ESP1a

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

ESP1a

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

ESP1a

Stack Exit OCDF Method 23 3 480 0

ESP1a

Stack Exit Other TCDD Method 23 0

ESP1a

Stack Exit Other PeCDD Method 23 0

ESP1a

Stack Exit Other HxCDD Method 23 0

ESP1a

Stack Exit Other HpCDD Method 23 0

ESP1a

Stack Exit Other TCDF Method 23 0

ESP1a

Stack Exit Other PeCDF Method 23 0

ESP1a

Stack Exit Other HxCDF Method 23 0

ESP1a

Stack Exit Other HpCDF Method 23 0

ESP1a

Stack Exit Total Dioxins Method 23 3 480 0

ESP1a

Stack Exit Total Furans Method 23 3 480 0

ESP1a

Thursday, February 03, 2011 Page 3 of 25
9/2/2010

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

ESP1a

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

ESP1a

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

ESP1a

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

ESP1a

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

ESP1a

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

ESP1a

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

ESP1a

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

ESP1a

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

ESP1a

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

ESP1a

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

ESP1a

Stack Exit Total PCBs Method 23 3 480 0

ESP1a

Stack Exit Total TEQ Method 23 3 480 0

ESP1a

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

ESP1a

Stack Exit Hydrogen Chloride Method 26 3 180 0

ESP1a

Stack Exit Hydrogen Fluoride Method 26 3 180 0

ESP1a

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

ESP1a

Stack Exit Hydrogen Chloride Method 26A 3 180 0

ESP1a

Filterable Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit 

ESP1a

Total Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit 

ESP1a

Total PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit 

ESP1a

Filterable PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit 

ESP1a

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit 

ESP1a

Organic Condensible 

Particulate

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit 

ESP1a

Stack Exit Cadmium Method 29 3 240 0

ESP1a

Thursday, February 03, 2011 Page 4 of 25
9/2/2010

Stack Exit Selenium Method 29 3 240 0

ESP1a

Stack Exit Nickel Method 29 3 240 0

ESP1a

Stack Exit Mercury Method 29 3 240 0

ESP1a

Stack Exit Manganese Method 29 3 240 0

ESP1a

Stack Exit Beryllium Method 29 3 240 0

ESP1a

Stack Exit Filterable Particulate Method 29 3 240 0

ESP1a

Stack Exit Chromium Method 29 3 240 0

ESP1a

Stack Exit Lead Method 29 3 240 0

ESP1a

Stack Exit Magnesium Method 29 3 240 0

ESP1a

Stack Exit Arsenic Method 29 3 240 0

ESP1a

Stack Exit Antimony Method 29 3 240 0

ESP1a

Stack Exit Co2 Method 3A CO2 3 120 0

ESP1a

Stack Exit O2 Method 3A O2 3 480 0

ESP1a

Stack Exit Co2 Method 3A CO2 3 480 0

ESP1a

Stack Exit O2 Method 3A O2 3 240 0

ESP1a

Stack Exit Co2 Method 3A CO2 3 240 0

ESP1a

Stack Exit O2 Method 3A O2 3 120 0

ESP1a

Total Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit 

ESP1a

Inorganic (Aqueous) 

Condensible Part.

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit 

ESP1a

Stack Exit Filterable Particulate Method 5 3 240 0

ESP1a

Organic Condensible 

Particulate

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit 

ESP1a

Filterable Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit 

ESP1a

Stack Exit Sulfur Dioxide Method 6C 3 180 0

ESP1a

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

ESP1a

Stack Exit 2,3,7,8-TCDD Method 23 3 16 0

ESP2b

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 16 0

ESP2b

Thursday, February 03, 2011 Page 5 of 25
9/2/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Method 23- 5/25/95

Method 3B - 2/2000

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 16 0

ESP2b

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 16 0

ESP2b

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 16 0

ESP2b

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 16 0

ESP2b

Stack Exit OCDD Method 23 3 16 0

ESP2b

Stack Exit 2,3,7,8-TCDF Method 23 3 16 0

ESP2b

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 16 0

ESP2b

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 16 0

ESP2b

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 16 0

ESP2b

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 16 0

ESP2b

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 16 0

ESP2b

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 16 0

ESP2b

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 16 0

ESP2b

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 16 0

ESP2b

Stack Exit OCDF Method 23 3 16 0

ESP2b

Thursday, February 03, 2011 Page 6 of 25
9/2/2010

Sampling / Stack Data Results Summary

Location Stack Exit ESP1a - Method 23

Average

Run Number 1 2 3

Test Date 6/30/2010 7/1/2010 7/2/2010

Run Start Time 8:50:00 AM 8:15:00 

AM

8:05:00 AM

Run Finish Time 5:25:00 PM 3:57:00 PM 3:44:00 PM

Net Run Time, minutes 485 475 475

Dry Gas Meter Volume Sampled, dscf 289.421 294.307 284.849 289.526

Moisture Content of Stack Gas, % 11.36 11.32 11.78 11.487

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11.37 12.83 12.87 12.357

Oxygen, % 8.57 6.97 6.9 7.480

Average Stack Gas Temperature, °F 304.92 299.08 316.42 306.807

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 82.8 85.9 86.0 84.900

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1840 1840 1840 1,840.000

Thursday, February 03, 2011 Page 7 of 25
9/2/2010

Location Stack Exit ESP2b - Method 23

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 03, 2011 Page 8 of 25
9/2/2010

Emissions Summary

Location: Stack Exit ESP1a - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000037 0.0000000096 0.0000000051 0.000

lb/mmBtuO2 4.67E-12 1.06E-12 5.76E-13 0.000

ng/dscm 4.52E-03 1.15E-03 6.32E-04 0.002

ng/dscm@7%O2 5.10E-03 1.15E-03 6.27E-04 0.002

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000014 0.000000032 0.000000021 0.000

lb/mmBtuO2 1.77E-11 3.52E-12 2.37E-12 0.000

ng/dscm 1.71E-02 3.84E-03 2.60E-03 0.008

ng/dscm@7%O2 1.93E-02 3.83E-03 2.58E-03 0.009

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000022 0.0000000078 0.0000000044 0.000

lb/mmBtuO2 2.78E-12 8.57E-13 4.97E-13 0.000

ng/dscm 2.68E-03 9.36E-04 5.46E-04 0.001

ng/dscm@7%O2 3.02E-03 9.34E-04 5.42E-04 0.001

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000065 0.0000000029 0.0000000038 0.000

lb/mmBtuO2 8.21E-13 3.19E-13 4.29E-13 0.000

ng/dscm 7.93E-04 3.48E-04 4.71E-04 0.001

ng/dscm@7%O2 8.94E-04 3.47E-04 4.68E-04 0.001

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000082 0.000000017 0.000000011 0.000

lb/mmBtuO2 1.04E-11 1.87E-12 1.24E-12 0.000

ng/dscm 1.00E-02 2.04E-03 1.36E-03 0.004

ng/dscm@7%O2 1.13E-02 2.04E-03 1.35E-03 0.005

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000058 0.0000000028 0.0000000036 0.000

lb/mmBtuO2 7.32E-13 3.08E-13 4.07E-13 0.000

ng/dscm 7.08E-04 3.36E-04 4.46E-04 0.000

ng/dscm@7%O2 7.98E-04 3.35E-04 4.43E-04 0.001

Compound: 1,2,3,6,7,8-HxCDF

Average

Thursday, February 03, 2011 Page 9 of 25
9/2/2010

RunNumber 1 2 3

Mass_mg 0.000000012 0.000000006 0.0000000054 0.000

lb/mmBtuO2 1.52E-12 6.60E-13 6.10E-13 0.000

ng/dscm 1.46E-03 7.20E-04 6.70E-04 0.001

ng/dscm@7%O2 1.65E-03 7.18E-04 6.65E-04 0.001

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000012 0.0000000029 0.0000000037 0.000

lb/mmBtuO2 1.52E-12 3.19E-13 4.18E-13 0.000

ng/dscm 1.46E-03 3.48E-04 4.59E-04 0.001

ng/dscm@7%O2 1.65E-03 3.47E-04 4.56E-04 0.001

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000015 0.000000002 0.0000000024 0.000

lb/mmBtuO2 1.89E-13 2.20E-13 2.71E-13 0.000

ng/dscm 1.83E-04 2.40E-04 2.98E-04 0.000

ng/dscm@7%O2 2.06E-04 2.39E-04 2.96E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000034 0.0000000037 0.0000000048 0.000

lb/mmBtuO2 4.29E-13 4.07E-13 5.42E-13 0.000

ng/dscm 4.15E-04 4.44E-04 5.95E-04 0.000

ng/dscm@7%O2 4.68E-04 4.43E-04 5.91E-04 0.001

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000014 0.000000006 0.0000000041 0.000

lb/mmBtuO2 1.77E-12 6.60E-13 4.63E-13 0.000

ng/dscm 1.71E-03 7.20E-04 5.08E-04 0.001

ng/dscm@7%O2 1.93E-03 7.18E-04 5.04E-04 0.001

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.000000012 0.000000014 0.000000014 0.000

lb/mmBtuO2 1.52E-12 1.54E-12 1.58E-12 0.000

ng/dscm 1.46E-03 1.68E-03 1.74E-03 0.002

ng/dscm@7%O2 1.65E-03 1.68E-03 1.73E-03 0.002

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.0000001 0.000000082 0.000000083 0.000

lb/mmBtuO2 1.26E-11 9.01E-12 9.38E-12 0.000

ng/dscm 1.22E-02 9.84E-03 1.03E-02 0.011

ng/dscm@7%O2 1.38E-02 9.82E-03 1.02E-02 0.011

Thursday, February 03, 2011 Page 10 of 25
9/2/2010

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.00000038 0.00000039 0.000000332 0.000

lb/mmBtuO2 4.80E-11 4.29E-11 3.75E-11 0.000

ng/dscm 4.64E-02 4.68E-02 4.12E-02 0.045

ng/dscm@7%O2 5.23E-02 4.67E-02 4.09E-02 0.047

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.000000032 0.000000017 0.000000024 0.000

lb/mmBtuO2 4.04E-12 1.87E-12 2.71E-12 0.000

ng/dscm 3.91E-03 2.04E-03 2.98E-03 0.003

ng/dscm@7%O2 4.41E-03 2.04E-03 2.96E-03 0.003

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.000000022 0.000000025 0.000000016 0.000

lb/mmBtuO2 2.78E-12 2.75E-12 1.81E-12 0.000

ng/dscm 2.68E-03 3.00E-03 1.98E-03 0.003

ng/dscm@7%O2 3.02E-03 2.99E-03 1.97E-03 0.003

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.00000115 0.00000112 0.000000906 0.000

lb/mmBtuO2 1.45E-10 1.23E-10 1.02E-10 0.000

ng/dscm 1.40E-01 1.34E-01 1.12E-01 0.129

ng/dscm@7%O2 1.58E-01 1.34E-01 1.11E-01 0.134

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.000000018 0.000000022 0.000000018 0.000

lb/mmBtuO2 2.27E-12 2.42E-12 2.03E-12 0.000

ng/dscm 2.20E-03 2.64E-03 2.23E-03 0.002

ng/dscm@7%O2 2.48E-03 2.63E-03 2.21E-03 0.002

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000012 0.0000000064 0.0000000054 0.000

lb/mmBtuO2 1.52E-12 7.03E-13 6.10E-13 0.000

ng/dscm 1.46E-03 7.68E-04 6.70E-04 0.001

ng/dscm@7%O2 1.65E-03 7.66E-04 6.65E-04 0.001

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000014 0.0000000079 0.0000000042 0.000

lb/mmBtuO2 1.77E-12 8.68E-13 4.75E-13 0.000

Thursday, February 03, 2011 Page 11 of 25
9/2/2010

ng/dscm 1.71E-03 9.48E-04 5.21E-04 0.001

ng/dscm@7%O2 1.93E-03 9.46E-04 5.17E-04 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000038 0.0000000078 0.0000000096 0.000

lb/mmBtuO2 4.80E-13 8.57E-13 1.08E-12 0.000

ng/dscm 4.64E-04 9.36E-04 1.19E-03 0.001

ng/dscm@7%O2 5.23E-04 9.34E-04 1.18E-03 0.001

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000018 0.0000000051 0.0000000041 0.000

lb/mmBtuO2 2.27E-12 5.61E-13 4.63E-13 0.000

ng/dscm 2.20E-03 6.12E-04 5.08E-04 0.001

ng/dscm@7%O2 2.48E-03 6.11E-04 5.04E-04 0.001

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.000000014 0.000000018 0.00000002 0.000

lb/mmBtuO2 1.77E-12 1.98E-12 2.26E-12 0.000

ng/dscm 1.71E-03 2.16E-03 2.48E-03 0.002

ng/dscm@7%O2 1.93E-03 2.16E-03 2.46E-03 0.002

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.000000025 0.000000023 0.000000022 0.000

lb/mmBtuO2 3.16E-12 2.53E-12 2.49E-12 0.000

ng/dscm 3.05E-03 2.76E-03 2.73E-03 0.003

ng/dscm@7%O2 3.44E-03 2.75E-03 2.71E-03 0.003

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.00000004 0.000000039 0.000000024 0.000

lb/mmBtuO2 5.05E-12 4.29E-12 2.71E-12 0.000

ng/dscm 4.88E-03 4.68E-03 2.98E-03 0.004

ng/dscm@7%O2 5.50E-03 4.67E-03 2.96E-03 0.004

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.000000016 0.000000021 0.000000024 0.000

lb/mmBtuO2 2.02E-12 2.31E-12 2.71E-12 0.000

ng/dscm 1.95E-03 2.52E-03 2.98E-03 0.002

ng/dscm@7%O2 2.20E-03 2.51E-03 2.96E-03 0.003

Compound: OCDD

Average

RunNumber 1 2 3

Thursday, February 03, 2011 Page 12 of 25
9/2/2010

Mass_mg 0.000000049 0.000000025 0.000000016 0.000

lb/mmBtuO2 6.19E-12 2.75E-12 1.81E-12 0.000

ng/dscm 5.98E-03 3.00E-03 1.98E-03 0.004

ng/dscm@7%O2 6.74E-03 2.99E-03 1.97E-03 0.004

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000025 0.00000015 0.000000082 0.000

lb/mmBtuO2 3.16E-11 1.65E-11 9.27E-12 0.000

ng/dscm 3.05E-02 1.80E-02 1.02E-02 0.020

ng/dscm@7%O2 3.44E-02 1.80E-02 1.01E-02 0.021

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000034 0.0000000094 0.0000000049 0.000

lb/mmBtuO2 4.29E-12 1.03E-12 5.54E-13 0.000

ng/dscm 4.15E-03 1.13E-03 6.08E-04 0.002

ng/dscm@7%O2 4.68E-03 1.13E-03 6.04E-04 0.002

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000021 0.0000000132 0.0000000056 0.000

lb/mmBtuO2 2.65E-11 1.45E-12 6.33E-13 0.000

ng/dscm 2.56E-02 1.58E-03 6.94E-04 0.009

ng/dscm@7%O2 2.89E-02 1.58E-03 6.89E-04 0.010

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000757 0.0000000194 0.0000000109 0.000

lb/mmBtuO2 9.56E-12 2.13E-12 1.23E-12 0.000

ng/dscm 9.24E-03 2.33E-03 1.35E-03 0.004

ng/dscm@7%O2 1.04E-02 2.32E-03 1.34E-03 0.005

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000001525 0.0000000236 0.000000017 0.000

lb/mmBtuO2 1.93E-11 2.59E-12 1.92E-12 0.000

ng/dscm 1.86E-02 2.83E-03 2.11E-03 0.008

ng/dscm@7%O2 2.10E-02 2.82E-03 2.09E-03 0.009

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000306 0.0000000046 0.0000000048 0.000

lb/mmBtuO2 3.86E-12 5.06E-13 5.42E-13 0.000

ng/dscm 3.73E-03 5.52E-04 5.95E-04 0.002

ng/dscm@7%O2 4.20E-03 5.51E-04 5.91E-04 0.002

Thursday, February 03, 2011 Page 13 of 25
9/2/2010

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000162 0.0000000791 0.0000000757 0.000

lb/mmBtuO2 2.05E-11 8.69E-12 8.55E-12 0.000

ng/dscm 1.98E-02 9.49E-03 9.39E-03 0.013

ng/dscm@7%O2 2.23E-02 9.47E-03 9.32E-03 0.014

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000092 0.0000000022 0.0000000096 0.000

lb/mmBtuO2 1.16E-12 2.42E-13 1.08E-12 0.000

ng/dscm 1.12E-03 2.64E-04 1.19E-03 0.001

ng/dscm@7%O2 1.26E-03 2.63E-04 1.18E-03 0.001

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000142 0.0000000949 0.0000000849 0.000

lb/mmBtuO2 1.79E-11 1.04E-11 9.59E-12 0.000

ng/dscm 1.73E-02 1.14E-02 1.05E-02 0.013

ng/dscm@7%O2 1.95E-02 1.14E-02 1.04E-02 0.014

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total PCBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total TEQ

Average

RunNumber 1 2 3

Mass_mg 0.0000000244 0.0000000068 0.0000000023 0.000

lb/mmBtuO2 3.08E-12 7.47E-13 2.60E-13 0.000

Thursday, February 03, 2011 Page 14 of 25
9/2/2010

ng/dscm 2.98E-03 8.16E-04 2.85E-04 0.001

ng/dscm@7%O2 3.36E-03 8.14E-04 2.83E-04 0.001

Location: Stack Exit ESP2b - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000011 0.0000000065 0.0000000058 0.000

ng/dscm 1.26E-03 2.46E-04 6.58E-04 0.001

pg/dscm 1.26E+00 2.46E-01 6.58E-01 0.721

pg/dscm@7%O2 1.23E+00 2.47E-01 6.43E-01 0.707

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000078 0.000000043 0.000000044 0.000

ng/dscm 8.92E-03 1.62E-03 4.99E-03 0.005

pg/dscm 8.92E+00 1.62E+00 4.99E+00 5.177

pg/dscm@7%O2 8.73E+00 1.62E+00 4.87E+00 5.073

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000018 0.0000000094 0.000000013 0.000

ng/dscm 2.06E-03 3.55E-04 1.47E-03 0.001

pg/dscm 2.06E+00 3.55E-01 1.47E+00 1.295

pg/dscm@7%O2 2.02E+00 3.56E-01 1.44E+00 1.272

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.0000000034 0.0000000036 0.000

ng/dscm 3.66E-04 1.28E-04 4.08E-04 0.000

pg/dscm 3.66E-01 1.28E-01 4.08E-01 0.301

pg/dscm@7%O2 3.58E-01 1.28E-01 3.99E-01 0.295

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000012 0.0000000076 0.0000000064 0.000

ng/dscm 1.37E-03 2.87E-04 7.26E-04 0.001

pg/dscm 1.37E+00 2.87E-01 7.26E-01 0.794

pg/dscm@7%O2 1.34E+00 2.88E-01 7.09E-01 0.779

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000031 0.0000000033 0.0000000035 0.000

ng/dscm 3.54E-04 1.25E-04 3.97E-04 0.000

pg/dscm 3.54E-01 1.25E-01 3.97E-01 0.292

pg/dscm@7%O2 3.47E-01 1.25E-01 3.88E-01 0.287

Thursday, February 03, 2011 Page 15 of 25
9/2/2010

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000061 0.000000002 0.0000000041 0.000

ng/dscm 6.97E-04 7.56E-05 4.65E-04 0.000

pg/dscm 6.97E-01 7.56E-02 4.65E-01 0.413

pg/dscm@7%O2 6.82E-01 7.58E-02 4.54E-01 0.404

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.0000000034 0.0000000035 0.000

ng/dscm 3.66E-04 1.28E-04 3.97E-04 0.000

pg/dscm 3.66E-01 1.28E-01 3.97E-01 0.297

pg/dscm@7%O2 3.58E-01 1.28E-01 3.88E-01 0.291

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000027 0.0000000025 0.0000000024 0.000

ng/dscm 3.09E-04 9.45E-05 2.72E-04 0.000

pg/dscm 3.09E-01 9.45E-02 2.72E-01 0.225

pg/dscm@7%O2 3.02E-01 9.47E-02 2.66E-01 0.221

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000046 0.000000005 0.0000000049 0.000

ng/dscm 5.26E-04 1.89E-04 5.56E-04 0.000

pg/dscm 5.26E-01 1.89E-01 5.56E-01 0.424

pg/dscm@7%O2 5.15E-01 1.89E-01 5.43E-01 0.416

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000036 0.0000000037 0.0000000041 0.000

ng/dscm 4.12E-04 1.40E-04 4.65E-04 0.000

pg/dscm 4.12E-01 1.40E-01 4.65E-01 0.339

pg/dscm@7%O2 4.03E-01 1.40E-01 4.54E-01 0.332

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.000000015 0.000000012 0.000000013 0.000

ng/dscm 1.71E-03 4.53E-04 1.47E-03 0.001

pg/dscm 1.71E+00 4.53E-01 1.47E+00 1.211

pg/dscm@7%O2 1.67E+00 4.54E-01 1.44E+00 1.188

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.00000003 0.000000063 0.000000041 0.000

ng/dscm 3.43E-03 2.38E-03 4.65E-03 0.003

Thursday, February 03, 2011 Page 16 of 25
9/2/2010

pg/dscm 3.43E+00 2.38E+00 4.65E+00 3.487

pg/dscm@7%O2 3.36E+00 2.39E+00 4.54E+00 3.430

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.000000074 0.00000018 0.000000082 0.000

ng/dscm 8.46E-03 6.80E-03 9.30E-03 0.008

pg/dscm 8.46E+00 6.80E+00 9.30E+00 8.187

pg/dscm@7%O2 8.28E+00 6.81E+00 9.08E+00 8.057

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.000000018 0.000000025 0.000000016 0.000

ng/dscm 2.06E-03 9.45E-04 1.81E-03 0.002

pg/dscm 2.06E+00 9.45E-01 1.81E+00 1.605

pg/dscm@7%O2 2.02E+00 9.47E-01 1.77E+00 1.579

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.000000016 0.000000014 0.000000014 0.000

ng/dscm 1.83E-03 5.29E-04 1.59E-03 0.001

pg/dscm 1.83E+00 5.29E-01 1.59E+00 1.316

pg/dscm@7%O2 1.79E+00 5.30E-01 1.55E+00 1.290

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.000000309 0.000000673 0.000000291 0.000

ng/dscm 3.53E-02 2.54E-02 3.30E-02 0.031

pg/dscm 3.53E+01 2.54E+01 3.30E+01 31.233

pg/dscm@7%O2 3.46E+01 2.55E+01 3.22E+01 30.767

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.000000017 0.000000015 0.000000016 0.000

ng/dscm 1.94E-03 5.67E-04 1.81E-03 0.001

pg/dscm 1.94E+00 5.67E-01 1.81E+00 1.439

pg/dscm@7%O2 1.90E+00 5.68E-01 1.77E+00 1.413

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000023 0.0000000022 0.0000000021 0.000

ng/dscm 2.63E-04 8.31E-05 2.38E-04 0.000

pg/dscm 2.63E-01 8.31E-02 2.38E-01 0.195

pg/dscm@7%O2 2.57E-01 8.33E-02 2.32E-01 0.191

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Thursday, February 03, 2011 Page 17 of 25
9/2/2010

Mass_mg 0.0000000037 0.0000000037 0.0000000042 0.000

ng/dscm 4.23E-04 1.40E-04 4.76E-04 0.000

pg/dscm 4.23E-01 1.40E-01 4.76E-01 0.346

pg/dscm@7%O2 4.14E-01 1.40E-01 4.65E-01 0.340

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000094 0.000000009 0.000000011 0.000

ng/dscm 1.07E-03 3.40E-04 1.25E-03 0.001

pg/dscm 1.07E+00 3.40E-01 1.25E+00 0.887

pg/dscm@7%O2 1.05E+00 3.41E-01 1.22E+00 0.870

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000088 0.00000001 0.000000012 0.000

ng/dscm 1.01E-03 3.78E-04 1.36E-03 0.001

pg/dscm 1.01E+00 3.78E-01 1.36E+00 0.916

pg/dscm@7%O2 9.89E-01 3.79E-01 1.33E+00 0.899

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.000000018 0.000000015 0.000000017 0.000

ng/dscm 2.06E-03 5.67E-04 1.93E-03 0.002

pg/dscm 2.06E+00 5.67E-01 1.93E+00 1.519

pg/dscm@7%O2 2.02E+00 5.68E-01 1.89E+00 1.493

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.00000002 0.000000015 0.000000024 0.000

ng/dscm 2.29E-03 5.67E-04 2.72E-03 0.002

pg/dscm 2.29E+00 5.67E-01 2.72E+00 1.859

pg/dscm@7%O2 2.24E+00 5.68E-01 2.66E+00 1.823

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.000000023 0.000000031 0.00000002 0.000

ng/dscm 2.63E-03 1.17E-03 2.27E-03 0.002

pg/dscm 2.63E+00 1.17E+00 2.27E+00 2.023

pg/dscm@7%O2 2.57E+00 1.17E+00 2.22E+00 1.987

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.000000023 0.000000018 0.00000002 0.000

ng/dscm 2.63E-03 6.80E-04 2.27E-03 0.002

pg/dscm 2.63E+00 6.80E-01 2.27E+00 1.860

pg/dscm@7%O2 2.57E+00 6.81E-01 2.22E+00 1.824

Thursday, February 03, 2011 Page 18 of 25
9/2/2010

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000044 0.000000025 0.000000027 0.000

ng/dscm 5.03E-03 9.45E-04 3.06E-03 0.003

pg/dscm 5.03E+00 9.45E-01 3.06E+00 3.012

pg/dscm@7%O2 4.92E+00 9.47E-01 2.99E+00 2.952

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000049 0.00000025 0.00000027 0.000

ng/dscm 5.60E-02 9.45E-03 3.06E-02 0.032

pg/dscm 5.60E+01 9.45E+00 3.06E+01 32.017

pg/dscm@7%O2 5.48E+01 9.47E+00 2.99E+01 31.390

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000011 0.0000000065 0.0000000058 0.000

ng/dscm 1.26E-03 2.46E-04 6.58E-04 0.001

pg/dscm 1.26E+00 2.46E-01 6.58E-01 0.721

pg/dscm@7%O2 1.23E+00 2.47E-01 6.43E-01 0.707

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000034 0.000000076 0.000000016 0.000

ng/dscm 3.89E-03 2.87E-03 1.81E-03 0.003

pg/dscm 3.89E+00 2.87E+00 1.81E+00 2.857

pg/dscm@7%O2 3.81E+00 2.88E+00 1.77E+00 2.820

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000135 0.0000000169 0.0000000094 0.000

ng/dscm 1.54E-03 6.38E-04 1.07E-03 0.001

pg/dscm 1.54E+00 6.38E-01 1.07E+00 1.083

pg/dscm@7%O2 1.51E+00 6.39E-01 1.05E+00 1.066

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000029 0.000000002 0.0000000021 0.000

ng/dscm 3.31E-04 7.56E-05 2.38E-04 0.000

pg/dscm 3.31E-01 7.56E-02 2.38E-01 0.215

pg/dscm@7%O2 3.24E-01 7.58E-02 2.32E-01 0.211

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000046 0.000000005 0.0000000049 0.000

ng/dscm 5.26E-04 1.89E-04 5.56E-04 0.000

Thursday, February 03, 2011 Page 19 of 25
9/2/2010

pg/dscm 5.26E-01 1.89E-01 5.56E-01 0.424

pg/dscm@7%O2 5.15E-01 1.89E-01 5.43E-01 0.416

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000036 0.0000000037 0.0000000041 0.000

ng/dscm 4.12E-04 1.40E-04 4.65E-04 0.000

pg/dscm 4.12E-01 1.40E-01 4.65E-01 0.339

pg/dscm@7%O2 4.03E-01 1.40E-01 4.54E-01 0.332

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000094 0.000000009 0.000000011 0.000

ng/dscm 1.07E-03 3.40E-04 1.25E-03 0.001

pg/dscm 1.07E+00 3.40E-01 1.25E+00 0.887

pg/dscm@7%O2 1.05E+00 3.41E-01 1.22E+00 0.870

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000088 0.00000001 0.000000012 0.000

ng/dscm 1.01E-03 3.78E-04 1.36E-03 0.001

pg/dscm 1.01E+00 3.78E-01 1.36E+00 0.916

pg/dscm@7%O2 9.89E-01 3.79E-01 1.33E+00 0.899

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

pg/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

pg/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

pg/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

pg/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total PCBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

pg/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

pg/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total TEQ

Average

RunNumber 1 2 3

Thursday, February 03, 2011 Page 20 of 25
9/2/2010

Process Run Data

Mass_mg 0.0000000244 0.0000000068 0.0000000023 0.000

ng/dscm 2.79E-03 2.57E-04 2.61E-04 0.001

pg/dscm 2.79E+00 2.57E-01 2.61E-01 1.103

pg/dscm@7%O2 2.73E+00 2.58E-01 2.55E-01 1.081

Thursday, February 03, 2011 Page 21 of 25
9/2/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Coal Firing Rate 0 0

2 Coal Firing Rate 0 0

3 Coal Firing Rate 0 0

1 Average Heat Input 0 MMBtu/hr 0

2 Average Heat Input 0 MMBtu/hr 0

3 Average Heat Input 0 MMBtu/hr 0

1 Steam Output 0 1000 lb steam/hr 0

2 Steam Output 0 1000 lb steam/hr 0

3 Steam Output 0 1000 lb steam/hr 0

1 Synfuel Firing Rate 0 0

2 Synfuel Firing Rate 0 0

3 Synfuel Firing Rate 0 0

1 Petroleum Coke Firing Rate 0 0

2 Petroleum Coke Firing Rate 0 0

3 Petroleum Coke Firing Rate 0 0

1 Coal Gas Firing Rate 0 0

2 Coal Gas Firing Rate 0 0

3 Coal Gas Firing Rate 0 0

1 Fuel Oil Firing Rate 0 0

2 Fuel Oil Firing Rate 0 0

3 Fuel Oil Firing Rate 0 0

1 Flue Gas Flow Rate 0 dscfm 0

1 Pressure Drop Across FGD (if applicable) 0 in H20 0

1 FGD Scrubber Liquor pH 0 pH 0

1 FGD Scrubber Liquor Flow Rate 0 gal/min 0

1 Sorbent Type and Sorbent Injection Rate (if 

applicable)

0 lb/hr 0

1 Flue Gas Oxygen Content 0 % 0

1 Flue Gas Carbon Dioxide Content 0 % 0

1 Flue Gas Moisture Content 0 % 0

1 Flue Gas Sampling Point Temperature 0 Deg F 0

1 Flue Gas Pressure 0 atm 0

1 Standard Pressure 0 atm 0

1 Standard Temperature 0 Deg F 0

Thursday, February 03, 2011 Page 22 of 25
9/2/2010

APCD Run Data

Process Lab Run Data

1 Unit Gross Electrical Output 0 MW 0

1 Unit Net Electric Generation 0 MWh 0

Run Name Value UOM Comments

Target

Value

1 ELECTROSTATIC PRECIPITATOR 0 percent 99

1 ELECTROSTATIC PRECIPITATOR 0 percent 99

1 0 0

Run Name Value UOM Comments

1 See 4b Comments. 0

Thursday, February 03, 2011 Page 23 of 25
9/2/2010

Sampling / Stack Data Results Detail

Location Stack Exit ESP1a - Method 23

Average

Run Number 1 2 3

Test Date 6/30/2010 7/1/2010 7/2/2010

Run Start Time 8:50:00 AM 8:15:00 AM 8:05:00 AM

Run Finish Time 5:25:00 PM 3:57:00 PM 3:44:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 485 475 475

Nozzle Diameter, inches 0.3 0.3 0.3 0.300

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.998 0.998 0.998 0.998

Barometric Pressure, inches of Mercury 28.32 28.35 28.13 28.267

Average Orifice Meter Differential, inches H2O 1.57 1.69 1.52 1.593

Dry Gas Meter Volume Sampled, cubic feet 316.000 322.000 314.000 317.333

Average Dry Gas Meter Temperature, °F 86.79 88.67 88.29 87.917

Dry Gas Meter Volume Sampled, dscf 289.421 294.307 284.849 289.526

Total Moisture Liquid collected, g 788 798 808 798.000

Volume of Water Vapor, standard cubic feet 37.09 37.56 38.03 37.560

Moisture Content of Stack Gas, % 11.36 11.32 11.78 11.487

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8864 0.8868 0.8822 0.885

Carbon Dioxide, % 11.37 12.83 12.87 12.357

Oxygen, % 8.57 6.97 6.9 7.480

Carbon Monoxide & Nitrogen, % 80.06 80.2 80.23 80.163

Fuel Factor 1.08 1.09 1.09

Dry Molecular Weight, lb/lb-Mole 30.16 30.33 30.34 30.277

Wet Molecular weight, lb/lb-Mole 28.78 28.93 28.89 28.867

Flue Gas Static Pressure, inches of H2O -10.5 -10.5 -10.5 -10.500

Absolute Flue Gas Pressure, inches of Mercury 27.55 27.58 27.36 27.497

Average Stack Gas Temperature, °F 304.92 299.08 316.42 306.807

Average Velocity Head, inches of H2O 0.3790409925

33332

0.378245154

234639

0.367526503

710857

0.375

Average Stack Gas Velocity, feet/second 43.42 43.08 43.15 43.217

Stack Cross-Sectional Area, square feet 0.000 0.000 0.000 0.000

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 82.8 85.9 86.0 84.900

Percent Excess Air, % 68.2 49.1 48.3 55.200

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 0 0 0

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1840 1840 1840 1,840.000

Thursday, February 03, 2011 Page 24 of 25
9/2/2010

Location Stack Exit ESP2b - Method 23

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 03, 2011 Page 25 of 25