Process Information

1Name of legal owner of facility:

Alabama Power Company 2Name of legal operator of facility, if different from legal owner:

3Address of _X__ legal owner or ____ operator:

600 North 18th Street Birmingham, AL 35291-0830 4aPlant Name (as reported on U.S. DOE/EIA Form-860 (2007), "Annual Electric Generator Report", schedule 2, line 1, page 37, question 1) OR Plant Name (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report", schedule 2, page 1, question 1):

Barry 4bEIA Plant Code (as reported on U.S. DOE/EIA Form-860 (2007), schedule 2, line 1, page 37, question 2) OR Plant ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), schedule 2, page 1, question 2):

Plant Code - 3 5Complete street address of facility (physical location):

15300 Highway 43 North Bucks, Alabama 36512-0070 6Provide mailing address if different:

600 North 18th Street Birmingham, AL 35291-0830 7Name and title of contact(s) able to answer technical questions about the completed survey:

Sarah Markham, Engineer II 8Contact(s) telephone number(s):

(205) 257-6780 and e-mail address(es):

sasander@southernco.com 9Is this facility considered to be owned or operated by a small entity as defined by the Regulatory Flexibility Act? ____ Yes

_X__ No____ Don't know

10Which of the following fossil fuels or other material(s) are fired in any steam generating unit at this facility?

_X__ coal ____ oil (including pet coke)

_X__ natural gas

_X__ other (specify in question 14 below)

11Which of the following fossil fuel or other material(s) are permitted1to be fired in any steam generating unit at this facility?

_X__ coal

_X__ oil (including pet coke)

_X__ natural gas

_X__ other (specify in question 14 below) Note: These are the anticipated fuels; however, the permit and design are not necessarily restricted to these fuels.

12If coal or solid fuel, as described below, derived from a fossil source is fired, indicate which rank of coal or solid fuel was utilized during the previous 12 months prior to the receipt of this ICR:2,3 ____ lignite (% _____) ____ subbituminous (% _____)

_X__ bituminous (% _100_) ____ anthracite (% _____) ____ coal refuse (including gob, culm, and subbituminous-derived coal refuse) (% _____) ____ synfuel (including, but not limited to, briquettes, pellets, or extrusions which are formed by binding materials, or processes that recycle materials) (%_____) (please specify the type or form of synfuel used ___________________________________________) ____ petroleum coke (% _____)

1"Permitted" in this context, refers to the fuels that the permit anticipates will be combusted at the facility.

2If the boiler is fired by a blend of coal ranks, please specify percentage (separately, on both a mass and on a Btu basis) of each coal rank (e.g., 85% subbituminuous/15% bituminous).

3In reference to footnote 1, if necessary, a notation can be added to a utilized fuel type that is not listed in the operating permit noting the reason the fuel type was combusted (e.g., "the permitting agency allowed this fuel to be combusted for special testing and research purposes").13If oil is fired, indicate which type of oil was utilized during the previous 12 months prior to the receipt of this ICR:4

____ distillate (% _____)

_ _ __ other (specify __________) (% _____) ____ residual or bunker C (% _____)

14aIf "other" was checked in questions 10 or 11 above indicating that any non-fossil fuel or other material (including, but not limited to, plastics, treated wood, rubber belting or gaskets, whole tires, tire-derived fuel, boiler cleaning solutions, animal wastes, etc.) is either utilized or permitted to be used, please indicate below what materials are combusted in the boiler and in what quantities (specify whether this quantity is on a weight percentage or heat [Btu] basis). Also indicate (yes/no) whether you are permitted5to burn non-fossil fuel(s) or other material(s) even if you do not actually burn them.

1The permitting agency allowed this fuel to be combusted for special testing and research purposes.

14bIf "other" was checked in questions 10 or 11 above indicating that any non-fossil fuel or other material (including, but not limited to, plastics, treated wood, rubber belting or gaskets, whole tires, tire-derived fuel, boiler cleaning solutions, animal wastes, etc.) is either utilized or permitted to be used, were such material to be classified as "solid waste" under the Resource Conservation and Recovery Act and, thus make the utilizing unit subject to CAA section 129, would you continue to utilize (i.e., use as a fuel) the material?____ Yes____ No

_X__ Neither Explain:Until the regulations are finalized, we cannot determine with certainty whether we would use these other materials.

4If the boiler is fired by a blend of fuel oil ranks, please specify percentage (separately, on both a volume and on a Btu basis) of each fuel oil rank (e.g., 85% residual oil/15% distillate).

5If necessary, a notation can be added to a utilized fuel type that is not listed in the operating permit noting the reason the fuel was combusted (e.g., "the permitting agency allowed this fuel to be combusted for special testing and research purposes"). 1210.4 tons Quantity/year

none

65,000 gallons used oil was burned; no used-oil contaminated waste was

burned Other Material Boiler cleaning wastes that are not hazardous wastes as defined in 40 CFR Part 261, Subpart B and ADEM Admin. Code R. 335-14-2 may be combusted in these units for energy
recovery.
Used oil that is not hazardous waste as defined in 40 CFR Part 279 and ADEM Admin. Code R. 335-14-17, and which is generated at Alabama Power facilities in the state of Alabama my be combusted in these units for energy recovery. This includes non-hazardous waste residue that is contaminated with used oil and used oil that is generated by Alabama Power employees who are household used oil generators. Biomass (wood chips) Actually burn
No

Yes

Yes Permitted to burn
Yes

Yes

No115Identification (or designation) of all coal- and oil-fired steam generating units (boilers) (as defined by Clean Air Act section 112(a)(8))

located at this facility.Boiler ID6Original design fuel (i.e.,coal rank or type of oil)Design heat input,(MMBtu/hr)7Present maximum heatinput, (MMBtu/hr)8MWe Gross capacitysummerMWe Net CapacitysummerOriginal design grossefficiency (%, HHV)Present operating grossefficiency (%, HHV)Design steam pressure(psig)Operating steam pressure(psig)Design steam temperature(oF)Operating steamtemperature (oF)Design steam reheattemperature (oF)9Operating steam reheattemperature (oF)10Fuel11Hours/year operated12Average annual capacityfactor for the past 3 yearsApplicable NSPSEstimated year ofretirement13

1 coal CBI CBI 145 138 88.5 N/A 1800 1820 1000 998 1000 988bituminous coal, natural gas, used oil, biomass CBI CBI none not available

2 coal CBI CBI 145 137 88.5 N/A 1800 1820 1000 997 1000 982bituminous coal, natural gas, used oil, biomass CBI CBI none not available

3 bituminous CBI CBI 263 249 89.7 87.95 2000 1990 1000 992 1000 988bituminous coal, natural gas, used oil CBI CBI none not available

4 bituminous CBI CBI 376 362 89.06 87.9 2400 2393 1000 959 1000 998bituminous coal, natural gas, used oil, biomass CBI CBI none not available

5 bituminous CBI CBI 772 734 89.1 88.9 3500 3502 1000 986 1000 952bituminous coal, natural gas, used oil CBI CBI none not available

NOTES "N/A" means not available. Original design fuel.Based on the original contract boiler data sheet; only the primary fuel is listed if multiple fuels were included on the data sheet. See also text to previous response (Part I, No. 11), which indicates that the design fuel simply means the fuel for which the boiler is optimized to operate at maximum possible efficiency, but that the boiler was designed to handle and burn a range of fuels. MWe Gross Capacity Summer.Identifies the gross normal full load as of May 2009. Alabama Power does not change unit capacities from season to season. MWe Net Capacity Summer.Identifies the net normal full load as of May 2009; taken directly from the 2009 installed and authorized document. Alabama Power does not change unit capacities from season to season. Original design gross efficiency (%, HHV).Taken directly from the original contract boiler data sheet. Present operating gross efficiency (%, HHV).Based on the most recent actual test of the boiler efficiency, unless no recent boiler efficiency test was available. Where no recent test was available, that status is indicated. Design steam pressure (psig).Based on the thermal design of the unit as represented on the turbine heat balance sheet. Operating steam pressure (psig).Represents the average throttle pressure when the unit operated at gross normal full load over a three year period (January 2007 to December 2009). Design steam temperature.Based on the thermal design of the unit as represented on the turbine heat balance sheet. Operating steam temperature.Represents the average steam temperature when the unit operated at gross normal full load over a three year period (January 2007 to December 2009). Design steam reheat temperature.Based on the thermal design of the unit as represented on the turbine heat balance sheet. Operating steam reheat temperature.Represents the average reheat steamtemperature when the unit operated at gross normal full load over a three year period (January 2007 to December 2009). Fuel.Indicates the fuels burned in the previous calendar year (January to December 2009). NSPS.Where no NSPS is identified, the unit is not currently subject to any NSPS. Retirement.Alabama Power has not committed to actual retirement dates for Barry Units 1 - 5. Alabama Power continually evaluates retirement scenarios with respect to its generating units for a variety of planning purposes, taking into account a wide range of variables. While the company assumes financial "retirement dates" for accounting purposes, for example, for depreciation schedules or for FERC or Public Service Commission uses, these dates are not indicative of the unit's actual retirement date.

6Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, [for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW]) OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

7Per fuel burned in the boiler. Report this based on higher heating value (HHV).

8Per fuel burned in the boiler. Report this based on higher heating value (HHV).

9Please indicate if more than one steam reheat cycle is utilized, and, if so, please provide information for both.

10Please indicate if more than one steam reheat cycle is utilized, and, if so, please provide information for both.

11Indicate the fuels utilized for the indicated boiler, and percentages, as indicated in questions 11 - 13.

12The "hours/year operated" would be the average of the actual number of hours the unit operated in 1 year based on the last 3 years of operation.

13This can be treated as CBI and can be submitted through the proper CBI procedure if desired.16For each boiler noted in Part I, question 15, provide the following information for each current emission control device installed

and operating and/or planned (please designate the order of the emission controls - 1 for the first control following the boiler, 2 for the second control following the boiler, etc.):

Boiler ID14 Type15 NOx control16 SO2 control17 PM control18 Other control19

1 tangential-fired (1) low-NOx burners + closecoupled OFA (11/08/2002) (2) SNCR (05/01/2006) N/A (3) flue gas conditioning -
CaCO3injection1(1988) (4) hot-side ESP (07/17/1976) N/A

2 tangential-fired (1) low-NOx burners + closecoupled OFA (05/30/2003) (2) SNCR (07/01/2006) N/A (3) flue gas conditioning -
CaCO3injection1(1988) (4) hot-side ESP (05/01/1976) N/A

3 tangential-fired (1) low-NOx burners + closecoupled OFA (03/10/1996) (2) SNCR (07/28/2006) N/A (3) flue gas conditioning -
CaCO3injection1(1988) (4) hot-side ESP (01/03/1976) N/A

4 tangential-fired (1) low-NOx burners + separated OFA (03/16/1998) (2) SNCR (05/01/2006) N/A (3) flue gas conditioning - SO3 injection (1979)2 (4) cold-side ESPs arranged in parallel (03/29/1976 and 1985) N/A

5 tangential-fired (1) low-NOx burners + separated OFA (05/28/1998) (3) SCR (05/01/2008) - the SCR uses a titania-vanadia based ceramic catalyst and anhydrous ammonia as the reductant; the catalyst is designed to minimize SO3 formation3 (5) calcium-based wet flue gas desulfurization (01/21/2010)(2) flue gas conditioning - SO3 injection (1979) (4) cold-side ESPs arranged in series (10/19/1971 and 06/06/1976) N/A

Note: "N/A" means not applicable.

1Units 1, 2, and 3 still have the capability for CaCO3injection, but the plant has not used it in several years.

2SO3injection on Unit 4 was not operated during 2009.

3When making catalyst decisions, the primary goal is to achieve the desired NOx performance, with a secondary goal of minimizing SO3formation.

14Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, [for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW]) OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

15Examples: tangential-fired; cyclone; wall-fired; circulating fluidized bed (CFB)

16Examples: low-NOx burners; selective catalytic reduction (SCR); selective non-catalytic reduction (SNCR); over-fire air (OFA). Include specific date that control went online or planned operational date for new installation. If this boiler's control configuration utilizes a SCR, please include the type of material from which the catalyst is manufactured and the type of reductant used in with the SCR (e.g., anhydrous ammonia, urea, other). Also, please note if the catalyst is specifically designed to reduce SO3 formation?

17Examples: wet flue gas desulfurization (FGD; any type); dry scrubbing (any type); specify whether calcium- or sodium-based. Include specific date that control went online or planned operational date for new installation.

18Examples: fabric filter; cold-side electrostatic precipitator (ESP); hot-side ESP; cyclone or multiclone; venturi scrubber. Include specific date that control went online or planned operational date for new installation.

19Please indicate systems installed specifically to control any other pollutants (e.g., Hg, SO3, etc.). Examples: activated carbon injection (ACI); Powerspan ECO®; dry sorbent injection or wet ESP for SO3 control; flue gas conditioning to control opacity (e.g., SO3 injection, ammonia, other); additive use for mercury control (e.g., bromine; scrubber additives). Include specific date that control went online or planned operational date for new installation. Also include any pollutants controlled by this technology (e.g., control technology [pollutant controlled]).

### 17For each boiler noted in Part I, question 15, provide the company (prime vendor) name and company contact information for each

HAP-specific (e.g., mercury, hydrogen chloride) control technology that you have either contracted for, are installing, or have installed for the purpose of participating in a control technology demonstration project20

### (e.g., U.S. Department of Energy program, consent decree, etc.).

Name Telephone Address 1 N/A N/A N/A N/A 2 N/A N/A N/A N/A 3 N/A N/A N/A N/A 4 N/A N/A N/A N/A 5 N/A N/A N/A N/A

Note: "N/A" means not applicable.

20A control technology demonstration project is defined as a U.S. Government (e.g., U.S. Department of Energy program) sponsored (in whole or in part) project or mandate (e.g., as a result of a consent decree) that adds a HAP control technology to a facility's unit to demonstrate the technology's HAP removal performance.

21Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, [for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW]) OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8). 

### Company (vendor) contact information Boiler ID21

### Company (vendor) name

### 18For the control technologies identified in Part I, question 17, provide the date of actual start-up of the demonstration (if the control

is currently operating), the date of expected or projected start-up, the date the demonstration was completed, the type of HAP control installed (e.g., sorbent and type; pre-combustion boiler chemical additive; combustion boiler chemical additive), the desired HAP emission reduction or rate (if any), and the coal rank(s) upon which the demonstration was conducted. Please specify the format of the target HAP emission reduction rate (e.g., lb/MWh, lb/TBtu, percent reduction, etc.). If the format of the target end-point is percent reduction, provide (1) an estimate of what an equivalent emission rate would be (and specify the format of the equivalent emission rate), and (2) the basis for calculating the percent reduction (i.e., where the "inlet" and "outlet" are).

Boiler ID22

### Demonstration

activity actual startup date Demonstration

activity projected start-up date Demonstration

activity end-date or projected end-dateType of control (e.g.,

sorbent and type; chemical additive23

### )Desired HAP emission reduction (%) or emission rate Coal rank(s) in use

1 N/A N/A N/A N/A N/A N/A 2 N/A N/A N/A N/A N/A N/A 3 N/A N/A N/A N/A N/A N/A 4 N/A N/A N/A N/A N/A N/A 5 N/A N/A N/A N/A N/A N/A

Note: "N/A" means not applicable.

22Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, [for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW]) OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

23If additive is used, please indicate injection point.

### 19For each boiler noted in Part I, question 15, provide the company (prime vendor) name and company contact information for each

HAP-specific (e.g., mercury, hydrogen chloride) control technology that you have either contracted for, are installing, or have installed for the purpose of provide a non-demonstration, full-scale operating system.

Name Telephone Address 1 N/A N/A N/A N/A 2 N/A N/A N/A N/A 3 N/A N/A N/A N/A 4 N/A N/A N/A N/A 5 N/A N/A N/A N/A

Note: "N/A" means not applicable.

24Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, [for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW]) OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8). 

### Company (vendor) contact information Boiler ID24

### Company (vendor) name

### 20For the control technologies identified in Part I, question 19, provide the date of actual start-up (if the control is currently operating), the

date of expected or projected start-up, the type of HAP control installed (e.g., sorbent and type; pre-construction boiler chemical additive; combustion of boiler chemical additive), the guaranteed HAP emission reduction or emission rate, the sorbent feed rate upon which the guarantee is based, and the coal rank(s) upon which the guarantee is based. Please specify the format of the guarantee (e.g., lb/MWh, lb/TBtu, percent reduction, etc.). If the format of the guarantee is percent reduction, provide (1) an estimate of what an equivalent emission rate would be (and specify the format of the equivalent emission rate), and (2) the basis for calculating the percent reduction (i.e., where the "inlet" and "outlet" are).

Boiler ID25

### Actual start-up dateExpected or projected start-up date Type of control (e.g.,

sorbent and type; chemical additive)26

### Guaranteed HAP

emission reduction (%) or emission rateSorbent or additive

feed rate on which guarantee is basedCoal rank(s) upon

which guarantee is based

1 N/A N/A N/A N/A N/A N/A 2 N/A N/A N/A N/A N/A N/A 3 N/A N/A N/A N/A N/A N/A 4 N/A N/A N/A N/A N/A N/A 5 N/A N/A N/A N/A N/A N/A

Note: "N/A" means not applicable.

25Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, [for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW]) OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

26If additive is used, please indicate injection point.

### 21For each boiler noted in Part I, question 15, provide the following information:

PM28 

### PM10(29)

### PM2.5(30) 

### SO2 HCl and/or HF HCN Metal

HAP31 

### Hg CO Other organics (specify)Other

pollutant (specify)
1 0.12 lb/MMBtu (Title V permit; annual Reference Method 5 or 17) N/A N/A1.8 lb/MMBtu (Title V permit; 24-hour rolling average) N/A N/A N/A N/A N/A N/A N/A

2 0.12 lb/MMBtu (Title V permit; annual Reference Method 5 or 17) N/A N/A1.8 lb/MMBtu (Title V permit; 24-hour rolling average) N/A N/A N/A N/A N/A N/A N/A

3 0.12 lb/MMBtu (Title V permit; annual Reference Method 5 or 17) N/A N/A1.8 lb/MMBtu (Title V permit; 24-hour rolling average) N/A N/A N/A N/A N/A N/A N/A

4 0.12 lb/MMBtu (Title V permit; annual Reference Method 5 or 17) N/A N/A1.8 lb/MMBtu (Title V permit; 24-hour rolling average) N/A N/A N/A N/A N/A N/A N/A

5 0.12 lb/MMBtu (Title V permit; annual Reference Method 5 or 17) N/A N/A1.8 lb/MMBtu (Title V permit; 24-hour rolling average) N/A N/A N/A N/A N/A N/A N/A

Note: "N/A" means not applicable.

27Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, [for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW]) OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

28If the boiler has separate permitted emission limits for filterable and condensable PM, respectively, please indicate those separate limits. Also include the compliance test method utilized.

29List the compliance test method utilized.

30List the compliance test method utilized.

31Metal HAP include compounds of antimony, arsenic, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, phosphorus, and selenium; indicate permit level for all metal HAP for which a permit level has been developed. 

### Permitted emission limit (indicate type of permit and format of emission limit)

Boiler ID27

### 22For each boiler noted in Part I, question 15, provide the following information:

PM33 

### PM10 

### PM2.5 

### SO2 HCl and/or HF HCN Metal HAP34 

### Hg CO Other organics (specify) Other

pollutant (specify)

1 ESP: 99.0% collection efficiency guarantee (expired in 1976) N/A N/A N/A N/A N/A N/A N/A N/A N/A N/A

2 ESP: 99.0% collection efficiency guarantee (expired in 1976) N/A N/A N/A N/A N/A N/A N/A N/A N/A N/A

3 ESP: 0.09 lb/MMBtu, filterable (expired in 1999) N/A N/A N/A N/A N/A N/A N/A N/A N/A N/A

4 ESP: 0.06 lb/MMBtu, filterable (expired in 1998) N/A N/A N/A N/A N/A N/A N/A N/A N/A N/A

5 ESP: 0.05 lb/MMBtu, filterable (expired in 2007); FGD: CBI N/A N/A FGD: 98% instantaneous removal efficiency to meet a 95% 30-day rolling average removal efficiency1 N/A N/A N/A N/A N/A N/A N/A

Note: "N/A" means not applicable.

1These values are not vendor guaranteed rates, but are the performance expectations for the FGD provided by our internal engineering group. Like vendor guarantees, these performance expectations are dependent on specific operating conditions.



### 23Was any other guarantee level sought or offered? ____ Yes

_X__ No Please elaborate.

32Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, [for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW]) OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

33If the boiler has separate guaranteed emission rate for filterable and condensable PM, respectively, please indicate those separate emission rates.

34Metal HAP include compounds of antimony, arsenic, beryllium, cadmium, cobalt, lead, manganese, nickel, phosphorus, and selenium; indicate permit level for all metal HAP for which a permit level has been developed. 

### Most recent guaranteed emission rate for each pollutant for which there is a permitted emission limit

Boiler ID32

### 24For each boiler noted in Part I, question15, provide the following information:

PM36 

### PM10

### PM2.5 

### SO2 HCl and/or HF HCN Metal

HAP37 

### Hg CO Other organics (specify)
1 Emission tests for particulate matter will be conducted annually. Consecutive tests will not be conducted sooner than six months apart or later than eighteen months apart unless approved by the director. Results will be reported to the Director within thirty days of completion of testing. The Director must be notified at least ten days in advance of all emission tests that will be conducted and submitted as proof of compliance with ADEM Rules and Regulations. Submission of an annual particulate matter testing schedule with periodic updates as changes occur will satisfy the 10-day notification requirement. All records must be maintained for 5 years. N/A N/AThe installed Continuous Sulfur Dioxide Emissions Monitor will be operated, maintained, and certified using 40 CFR Part 75 procedures. Data from this monitor will also be used to provide an indication of the sulfur dioxide emissions from these units, using pounds per million Btu computed on a 24- hour rolling average. A summary emission report will be submitted to ADEM within thirty days of the end of each calendar quarter. Deviations from permit requirements shall be reported within 48 hours or 2 working days of such deviations, including those attributable to upset conditions as defined in the permit. The report will include the probably cause of said deviations, and any corrective actions or preventative measures that were taken. All records must be maintained for 5 years. N/A N/A N/A N/A N/A N/A

2 Emission tests for particulate matter will be conducted annually. Consecutive tests will not be conducted sooner than six months apart or later than eighteen months apart unless approved by the director. Results will be reported to the Director within thirty days of completion of testing. The Director must be notified at least ten days in advance of all emission tests that will be conducted and submitted as proof of compliance with ADEM Rules and Regulations. Submission of an annual particulate matter testing schedule with periodic updates as changes occur will satisfy the 10-day notification requirement. All records must be maintained for 5 years. N/A N/AThe installed Continuous Sulfur Dioxide Emissions Monitor will be operated, maintained, and certified using 40 CFR Part 75 procedures. Data from this monitor will also be used to provide an indication of the sulfur dioxide emissions from these units, using pounds per million Btu computed on a 24- hour rolling average. A summary emission report will be submitted to ADEM within thirty days of the end of each calendar quarter. Deviations from permit requirements shall be reported within 48 hours or 2 working days of such deviations, including those attributable to upset conditions as defined in the permit. The report will include the probably cause of said deviations, and any corrective actions or preventative measures that were taken. All records must be maintained for 5 years. N/A N/A N/A N/A N/A N/A

3 Emission tests for particulate matter will be conducted annually. Consecutive tests will not be conducted sooner than six months apart or later than eighteen months apart unless approved by the director. Results will be reported to the Director within thirty days of completion of testing. The Director must be notified at least ten days in advance of all emission tests that will be conducted and submitted as proof of compliance with ADEM Rules and Regulations. Submission of an annual particulate matter testing schedule with periodic updates as changes occur will satisfy the 10-day notification requirement. All records must be maintained for 5 years. N/A N/AThe installed Continuous Sulfur Dioxide Emissions Monitor will be operated, maintained, and certified using 40 CFR Part 75 procedures. Data from this monitor will also be used to provide an indication of the sulfur dioxide emissions from these units, using pounds per million Btu computed on a 24- hour rolling average. A summary emission report will be submitted to ADEM within thirty days of the end of each calendar quarter. Deviations from permit requirements shall be reported within 48 hours or 2 working days of such deviations, including those attributable to upset conditions as defined in the permit. The report will include the probably cause of said deviations, and any corrective actions or preventative measures that were taken. All records must be maintained for 5 years. N/A N/A N/A N/A N/A N/A 

### Required monitoring, recordkeeping, and reporting requirements for each pollutant for which there is a permitted emission limit

Boiler ID35

### PM36 

### PM10

### PM2.5 

### SO2 HCl and/or HF HCN Metal

HAP37 

### Hg CO Other organics (specify) Required monitoring, recordkeeping, and reporting requirements for each pollutant for which there is a permitted emission limit

Boiler ID35

4 Emission tests for particulate matter will be conducted annually. Consecutive tests will not be conducted sooner than six months apart or later than eighteen months apart unless approved by the director. Results will be reported to the Director within thirty days of completion of testing. The Director must be notified at least ten days in advance of all emission tests that will be conducted and submitted as proof of compliance with ADEM Rules and Regulations. Submission of an annual particulate matter testing schedule with periodic updates as changes occur will satisfy the 10-day notification requirement. All records must be maintained for 5 years. N/A N/AThe installed Continuous Sulfur Dioxide Emissions Monitor will be operated, maintained, and certified using 40 CFR Part 75 procedures. Data from this monitor will also be used to provide an indication of the sulfur dioxide emissions from these units, using pounds per million Btu computed on a 24- hour rolling average. A summary emission report will be submitted to ADEM within thirty days of the end of each calendar quarter. Deviations from permit requirements shall be reported within 48 hours or 2 working days of such deviations, including those attributable to upset conditions as defined in the permit. The report will include the probably cause of said deviations, and any corrective actions or preventative measures that were taken. All records must be maintained for 5 years. N/A N/A N/A N/A N/A N/A

5 Emission tests for particulate matter will be conducted annually. Consecutive tests will not be conducted sooner than six months apart or later than eighteen months apart unless approved by the director. Results will be reported to the Director within thirty days of completion of testing. The Director must be notified at least ten days in advance of all emission tests that will be conducted and submitted as proof of compliance with ADEM Rules and Regulations. Submission of an annual particulate matter testing schedule with periodic updates as changes occur will satisfy the 10-day notification requirement. All records must be maintained for 5 years. N/A N/AThe installed Continuous Sulfur Dioxide Emissions Monitor will be operated, maintained, and certified using 40 CFR Part 75 procedures. Data from this monitor will also be used to provide an indication of the sulfur dioxide emissions from these units, using pounds per million Btu computed on a 24- hour rolling average. A summary emission report will be submitted to ADEM within thirty days of the end of each calendar quarter. Deviations from permit requirements shall be reported within 48 hours or 2 working days of such deviations, including those attributable to upset conditions as defined in the permit. The report will include the probably cause of said deviations, and any corrective actions or preventative measures that were taken. All records must be maintained for 5 years. N/A N/A N/A N/A N/A N/A

Note: "N/A" means not applicable.

35Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, [for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW]) OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

36If the boiler's monitoring, recordkeeping, and reporting requirements require your company to monitoring, keep records, and report filterable and condensable PM separately, please describe the separate actions required.

37Metal HAP include compounds of antimony, arsenic, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, phosphorus, and selenium; indicate permit level for all metal HAP for which a permit level has been developed.

### 25For the control technologies identified in Part I, questions 17 and 19, provide the cost information requested.38



### Facility Name/Unit No.: N/A Retrofit to existing boiler? Installation on a new boiler? Total Capital Investment:

- $ Total Operating Costs:

- $(Include base year for operating costs [e.g., 2006]

26Are any other means of emission control (for any pollutant) employed on any boiler noted in Part I, question 15 (e.g., low-ash coal, coal or oil with low trace constituents, etc.)? Please specify. No.

38This can be treated as CBI and can be submitted through the proper CBI procedure if desired.

Note: "N/A" means not applicable.

### Fuel Analysis39



### 1aPlant or facility name from Part I, question 4a:

Barry 1bPlant or facility code from Part I, question 4b:

Plant Code - 3

39The respondent should reply to this ICR with separate pages 18 through 24 (Part II) for each of their facilities.

### 2For each individual coal and oil shipment received during the preceding 12 calendar months, provide the following information,

as available (indicated N/A if not available; use additional pages, as necessary):

D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 1,248 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.4413,149 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.27 13,283 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.43 6.21 13,224 1,277 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.3013,160 1,344 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 5.95 13,242 1,238 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.09 13,273 1,309 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.45 13,181 1,319 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 5.68 13,308 1,258 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 5.91 13,237 1,358 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 7.26 12,948 1,265 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.2413,168 1,272 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.23 13,153 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.27 13,194 1,231 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.22 13,106 1,300 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.2013,208 1,387 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.05 13,303 1,270 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.26 13,235 1,334 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.97 13,119 1,298 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.71 13,063 1,187 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 7.22 13,042 1,269 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 7.21 13,023 1,353 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.66 7.33 13,033 1,205 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.7013,043 1,153 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.97 13,016 1,291 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.63 13,006 1,368 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.96 13,059 1,223 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 7.02 13,032 1,271 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.99 13,024 1,417 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.66 6.85 13,099 1,315 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 7.05 12,971 1,372 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.64 6.66 13,056 1,259 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.67 7.0413,026 1,384 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.89 12,980 1,287 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.7412,998 1,378 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.64 6.71 13,045 1,327 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.64 6.96 13,035 1,369 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.66 7.28 12,982 1,281 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 6.71 13,072 1,364 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.37 13,097 1,289 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 6.57 13,074 1,247 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.39 13,053 1,295 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 6.77 13,038 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor AnalysesD.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,360 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.5013,089 1,344 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 6.4413,088 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.77 13,019 1,278 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.66 13,092 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 7.1413,000 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.41 13,066 1,380 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.61 6.77 13,027 1,253 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 6.75 13,024 1,306 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.82 13,019 1,352 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 7.02 12,880 1,166 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.1412,992 1,369 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.92 13,035 1,332 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.7413,042 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 6.65 13,059 1,415 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.71 13,018 1,261 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.87 12,990 1,226 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 6.8413,064 1,309 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.49 13,041 1,210 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 7.15 12,865 1,181 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 6.56 13,107 1,226 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 6.18 13,158 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.51 13,044 1,324 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.48 13,064 1,270 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.6413,020 1,331 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.5413,055 1,304 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.63 13,074 1,330 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.57 13,010 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.93 12,990 1,307 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.71 13,009 1,271 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.7013,054 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.93 12,993 1,306 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 7.25 12,984 1,304 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 7.8012,891 1,314 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.63 13,119 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.62 13,081 1,234 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.36 13,130 1,249 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 5.76 13,226 1,317 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.63 7.11 13,034 1,277 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.93 13,013 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.61 7.3412,960 1,307 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.23 13,079 1,276 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.0013,160 1,349 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 7.1012,923 1,422 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.7413,075D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,325 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.65 13,103 1,425 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 6.19 13,144 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.28 13,088 1,394 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 7.06 12,981 1,420 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.05 13,158 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.7413,023 1,275 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.65 13,065 1,333 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.65 13,067 1,419 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.37 13,086 1,360 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.75 12,997 1,267 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.68 13,070 1,247 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.9012,964 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.59 13,045 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.6013,024 1,341 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.66 13,083 1,250 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.76 12,990 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.59 13,044 1,397 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.82 13,056 1,338 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.48 13,099 1,345 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.2413,125 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.41 5.96 13,116 1,380 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 6.06 13,093 1,394 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.55 13,049 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.3413,085 1,268 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.35 6.1413,009 1,333 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.40 6.21 13,080 1,260 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.38 5.88 13,140 1,311 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.44 6.0413,146 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.43 6.15 13,089 1,360 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.36 5.69 13,162 1,403 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.45 6.57 13,040 1,398 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.36 6.02 13,073 1,259 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.38 6.06 13,137 1,283 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.37 6.11 13,021 1,348 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 7.11 12,874 1,284 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.43 6.41 13,087 1,305 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.46 6.11 13,137 1,288 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.46 6.51 13,069 1,396 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.34 6.07 13,040 1,253 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.87 13,055 1,420 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.42 6.05 13,114 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 6.27 13,076 1,331 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 6.19 13,126 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 6.46 13,056D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,226 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.46 6.55 13,070 1,381 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.36 13,069 1,362 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.49 13,063 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.49 13,102 1,377 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.93 13,085 1,359 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.46 6.3413,100 1,303 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.45 6.25 13,138 1,416 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 7.0013,040 1,387 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.69 13,069 1,281 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.41 13,111 1,246 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.5013,024 1,194 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.46 6.46 13,058 1,259 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 6.2013,136 1,353 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.18 13,166 1,141 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 6.36 13,109 1,257 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.38 13,177 1,302 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.76 13,001 1,168 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.7013,059 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.31 13,113 1,349 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.59 13,034 1,195 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.61 13,092 1,123 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 7.15 13,015 1,162 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.91 13,115 1,043 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.57 13,061 1,117 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.51 13,067 1,160 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.72 13,078 1,422 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.48 13,054 1,139 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.55 12,995 1,138 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 7.15 12,986 1,123 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.66 12,993 1,119 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.7013,021 1,157 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.52 13,047 1,229 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.35 5.83 13,065 1,194 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.35 5.99 13,170 1,234 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.73 12,971 1,105 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.36 6.13 13,080 1,203 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.01 13,151 1,132 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 7.05 13,001 1,225 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.32 5.71 13,087 1,350 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.38 6.5412,980 1,231 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 6.89 12,977 1,336 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.27 13,051 1,260 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.37 5.93 13,124 1,197 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.16 13,143D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,324 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.36 5.86 13,085 1,258 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.22 13,107 1,256 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.38 5.95 13,089 1,357 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.35 6.55 12,997 1,333 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.41 6.42 13,010 1,267 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.34 5.86 12,993 1,267 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.36 5.93 13,070 1,214 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.34 5.72 13,083 1,232 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.33 5.95 13,071 1,119 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.35 6.18 13,047 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.36 6.02 13,116 1,182 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 5.99 13,108 1,233 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.07 13,091 1,268 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.07 13,084 1,262 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.35 6.27 12,989 1,213 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.35 5.81 13,130 1,264 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.26 13,148 1,252 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.35 13,171 1,238 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.21 13,124 1,122 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.36 5.8013,160 1,283 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.59 13,087 1,168 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.43 6.32 13,070 1,138 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.08 13,105 1,259 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.2013,133 1,176 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.48 13,038 1,244 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.36 5.92 13,058 1,082 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.57 13,040 1,120 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 7.43 12,915 1,259 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.72 13,027 1,177 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.19 13,071 1,237 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.32 13,063 1,091 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.23 13,172 1,146 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.38 13,058 1,229 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.46 6.21 13,134 1,234 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.6013,044 1,211 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.56 13,015 1,098 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.38 6.51 13,074 1,163 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.36 6.06 13,115 1,177 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.40 6.7013,150 1,092 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.40 7.21 13,057 1,044 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.40 6.41 13,037 1,078 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.41 6.93 13,009 732 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.44 6.72 13,060 933 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.44 6.72 13,060D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

968 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.41 7.18 13,019 823 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.37 6.27 13,066 1,143 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.40 6.61 13,090 801 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.38 6.41 13,066 1,250 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.41 6.78 13,090 1,235 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.40 6.89 12,998 1,217 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.39 6.39 13,011 1,092 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 6.35 13,064 1,346 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.40 6.52 12,996 1,222 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.45 7.3413,022 1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.64 7.52 13,119 1,299 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 7.16 13,096 1,320 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 7.07 13,132 1,143 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.39 6.26 13,075 1,091 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.40 6.31 13,022 1,338 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.40 6.66 13,002 1,292 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.53 13,037 1,400 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.61 7.95 13,014 1,238 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 7.31 12,901 1,429 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.71 13,037 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 6.71 13,084 1,233 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 7.69 13,003 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.2413,074 1,301 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.22 13,018 1,350 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.40 6.22 13,056 1,317 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.31 13,062 1,249 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 7.22 13,089 1,235 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 7.33 13,090 1,189 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.93 6.8413,048 1,304 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.93 7.2012,900 1,266 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 6.88 13,065 1,325 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.49 13,055 225 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 6.98 13,066 1,418 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 7.07 13,067 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.63 6.6413,066 1,220 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.75 7.07 12,970 1,368 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.67 6.81 13,090 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.70 6.45 13,093 1,278 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.80 7.19 12,949 1,284 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 6.77 13,052 1,394 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.75 6.56 13,032 1,385 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 6.43 13,078 1,189 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.74 6.2413,180 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.68 6.67 13,034D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,271 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.70 6.39 13,093 1,345 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.67 6.42 13,057 1,433 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 6.68 13,005 1,276 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.74 6.53 13,020 1,379 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.71 6.39 13,082 1,322 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.73 6.37 13,109 1,381 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.36 13,143 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.71 6.23 13,127 1,421 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 6.32 13,134 1,402 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.81 6.59 13,108 1,396 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.70 6.56 13,007 1,417 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.36 13,087 1,402 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.75 6.4413,100 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.88 6.78 12,995 1,231 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 6.57 13,069 1,355 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.29 13,077 1,382 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.70 6.77 13,028 1,327 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 6.82 13,007 1,259 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.62 13,076 1,343 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.86 6.73 13,033 1,320 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.82 6.73 13,012 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 6.15 13,054 1,340 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.72 6.89 12,999 1,279 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 6.56 13,059 1,264 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.70 6.49 13,034 1,363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.64 6.55 13,042 1,350 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.72 6.26 13,157 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.66 6.63 13,066 1,281 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 6.5013,047 1,360 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.33 13,131 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 6.55 13,019 1,310 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 6.63 13,075 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.69 6.77 13,033 1,389 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 6.69 13,026 307 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.83 6.76 12,978 1,340 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 6.61 13,012 1,289 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.80 6.8412,954 1,348 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.87 6.7412,966 1,378 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.77 6.52 13,025 1,312 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.82 6.21 13,100 1,223 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.72 6.23 13,074 1,386 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.81 6.71 13,026 1,273 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.74 6.56 13,072 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.75 6.5013,057D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,394 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.86 6.86 12,979 1,350 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.75 6.13 13,115 1,323 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.79 7.0012,962 1,344 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.68 6.08 13,085 1,417 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.68 6.19 13,142 1,321 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 6.8013,023 1,398 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.84 6.82 12,999 1,258 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.77 6.66 12,997 1,250 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.73 6.7012,964 1,250 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 6.77 12,965 1,299 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 6.1413,128 1,394 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 5.79 13,183 1,348 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.73 5.92 13,160 1,191 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.77 6.73 13,003 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.90 7.01 12,925 1,342 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.71 6.36 13,081 1,380 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.70 6.26 13,112 1,407 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.83 6.56 13,017 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.80 6.48 13,034 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.68 6.06 13,092 1,380 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.83 6.76 12,997 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.84 6.77 13,018 1,423 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.84 6.71 13,053 1,450 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.7013,006 1,454 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 6.45 13,080 1,358 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 6.91 13,030 1,474 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 6.41 13,025 1,483 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.63 6.5013,066 1,436 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 6.51 13,065 1,272 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.66 6.58 13,103 1,465 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.68 6.41 13,141 1,415 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.66 6.3013,157 1,398 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.69 6.39 13,091 1,377 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.67 6.29 13,171 1,431 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 6.42 13,133 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.3013,233 1,360 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 6.28 13,129 1,392 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.21 13,133 1,410 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 6.23 13,168 1,367 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.66 6.21 13,187 1,281 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.31 13,087 1,373 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.88 13,003 1,319 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.41 13,075 1,177 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.37 13,162D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,312 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.0413,161 1,336 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.17 13,169 1,415 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.4413,105 1,267 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.61 13,185 1,426 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.4413,105 1,168 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.88 13,060 1,373 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.5013,163 1,292 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.23 13,121 1,224 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.49 13,058 1,326 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.26 13,137 1,411 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 5.79 13,156 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.4413,105 1,360 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.4413,105 1,483 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.4413,105 1,395 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.64 6.69 13,075 1,425 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.77 13,050 1,428 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.66 6.59 13,078 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.7413,088 1,161 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.57 13,025 1,174 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.89 12,995 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.45 13,052 1,410 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.72 13,117 1,428 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 6.3013,120 1,430 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.6013,054 1,353 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.29 13,152 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.31 13,103 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.15 13,154 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.67 6.4013,065 1,437 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.45 13,147 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.43 13,158 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.63 6.3413,061 1,209 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.39 13,092 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 5.98 13,047 1,297 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 5.81 13,124 1,224 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 5.39 13,148 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.11 13,056 1,256 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.46 5.65 13,136 1,381 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 5.62 13,184 1,459 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 5.62 13,090 1,388 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 5.73 13,100 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 5.55 13,131 1,300 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.46 5.28 13,202 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.1413,124 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 5.96 13,180D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,265 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 5.88 13,125 1,254 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 5.9013,138 1,191 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.61 6.5413,047 1,267 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 5.98 13,108 1,199 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 6.19 13,119 1,173 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 5.72 13,175 1,254 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.45 5.1413,169 1,283 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 6.33 13,070 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 5.96 13,137 1,267 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.12 13,102 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.02 13,113 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.03 13,114 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.4013,045 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.26 13,094 1,443 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 5.97 13,151 1,425 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.3013,115 1,462 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.0013,093 1,236 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.66 13,009 1,401 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 5.75 13,172 1,247 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.49 13,023 1,268 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.43 13,086 1,386 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.03 13,071 1,323 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.08 13,055 1,293 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.37 13,069 1,213 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.4013,117 1,349 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.46 13,105 1,354 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 5.86 13,116 1,221 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.73 13,033 1,182 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 5.98 13,194 1,330 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.41 13,113 1,370 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.2013,076 1,412 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 5.93 13,139 1,267 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.3413,073 1,278 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.6013,074 1,295 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.46 5.67 13,096 1,418 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.36 13,004 1,436 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 5.92 13,130 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.05 13,140 1,297 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.07 13,124 1,414 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.45 5.9413,061 1,381 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 5.93 13,135 1,390 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.01 13,068 1,227 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.45 5.9413,110 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 5.82 13,173D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,393 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.46 5.7013,124 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 5.57 13,086 1,144 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 6.12 13,043 1,252 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.45 5.69 13,124 1,424 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.45 5.72 13,064 1,326 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.45 5.93 13,124 1,176 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.01 13,053 1,412 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.18 13,112 1,348 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 5.58 13,147 1,456 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 5.86 13,171 1,177 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.08 13,138 1,368 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.29 13,092 1,322 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.3013,163 1,407 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 6.03 13,090 1,432 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 5.91 13,155 1,243 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.43 13,071 1,332 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.37 13,111 1,320 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.25 13,214 1,429 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 5.78 13,241 1,257 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.42 13,019 1,289 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 5.38 13,233 1,330 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 5.97 13,174 1,341 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.3013,064 1,441 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 5.99 13,141 1,460 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.1413,146 1,193 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.23 13,081 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 6.12 13,149 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.0013,149 1,359 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.32 13,044 1,228 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.4413,099 1,309 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.15 13,163 1,371 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.1413,083 1,311 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.3413,066 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 5.95 13,100 1,260 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.39 13,142 1,118 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.6013,154 1,392 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.51 13,118 1,253 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.45 13,121 1,026 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.73 13,084 1,378 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.31 13,108 1,199 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.36 13,120 1,178 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.38 13,121 1,352 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.5013,093 1,324 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.5013,171D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,349 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.39 13,117 1,204 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.28 13,134 1,355 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.1413,136 1,353 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.45 13,045 1,287 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 6.29 13,138 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 6.56 13,051 1,336 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 6.48 13,103 1,330 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.81 13,035 1,220 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 6.59 13,145 1,441 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.85 13,000 1,306 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 7.16 12,965 1,320 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 7.22 12,984 1,278 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.49 13,086 1,309 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.52 13,109 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.27 13,132 1,395 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.35 13,075 1,132 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.63 13,052 1,394 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.43 13,085 1,285 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.5413,064 1,293 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.16 13,174 1,299 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.45 13,110 1,317 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.25 13,177 1,494 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.4013,052 1,322 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.68 13,002 1,212 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.64 6.27 13,095 1,348 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.29 13,127 1,271 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.61 6.06 13,119 1,377 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.28 13,133 1,341 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.11 13,085 1,309 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.63 6.22 13,089 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 5.92 13,164 1,245 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 5.86 13,130 1,260 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 5.9413,186 1,322 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 7.02 12,997 1,228 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.88 13,016 1,337 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 7.3012,969 1,305 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 6.66 13,089 1,358 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 7.57 12,983 1,340 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.76 13,068 1,193 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.68 6.77 13,077 1,288 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.64 6.63 13,082 1,282 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 6.92 13,050 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.63 6.92 13,011 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.67 6.98 13,016D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,439 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 6.17 13,142 1,279 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.64 6.72 12,965 1,367 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 6.23 13,052 1,419 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 6.3013,082 1,216 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 6.41 13,083 1,300 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.63 6.0013,044 1,186 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.64 6.25 13,089 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.61 6.67 13,017 1,204 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 6.49 13,098 1,281 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.63 6.1413,109 1,390 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 7.07 13,015 1,325 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.02 13,118 1,262 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.63 6.6013,052 1,314 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 5.91 13,125 1,314 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 6.39 13,085 1,367 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.32 13,002 1,352 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 5.88 13,181 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.12 13,073 1,451 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 6.28 13,093 1,407 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 6.8013,044 1,445 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 5.7413,110 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 6.19 13,088 1,271 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 5.1013,197 1,353 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 5.87 13,148 1,071 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 6.2413,164 1,176 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.2013,190 1,191 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 6.2013,136 1,115 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 5.69 13,211 1,165 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 5.97 13,128 1,198 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 5.5013,268 1,116 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 5.55 13,227 1,071 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 5.52 13,165 1,173 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 5.4013,249 1,202 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 5.41 13,203 1,227 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 5.48 13,255 1,112 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 5.97 13,161 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.61 6.5013,036 1,355 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.26 13,105 1,142 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.51 13,064 1,323 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.61 6.56 13,079 1,246 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 6.35 13,104 1,273 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 6.45 13,060 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 5.97 13,155 1,443 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.16 13,127D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,304 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.13 13,116 1,379 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.62 6.09 13,046 1,387 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.60 6.37 13,078 1,168 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 6.5413,052 1,368 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 6.33 13,073 1,243 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.22 13,055 1,436 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.59 6.1413,052 1,262 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.27 13,090 1,343 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.56 6.45 13,034 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.73 6.98 13,018 1,310 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 6.58 13,007 1,376 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.56 13,024 363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.73 6.98 13,018 1,240 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.54 6.28 13,110 1,283 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.57 6.2413,111 1,292 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 7.4012,956 1,394 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.75 7.86 12,981 1,194 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 7.45 13,017 1,422 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 8.32 12,868 1,378 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.75 8.17 13,014 1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 8.11 12,963 1,209 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.80 7.47 12,967 1,288 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.80 7.06 12,995 1,256 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.81 7.39 12,981 1,310 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 7.76 12,908 1,192 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 6.86 13,026 1,244 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.81 7.43 12,866 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 7.0413,023 1,223 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.79 7.1412,990 1,380 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 7.1412,947 1,246 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.80 7.0412,993 1,300 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.77 6.9413,036 1,305 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.77 6.87 13,062 1,416 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.79 6.93 12,965 1,186 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.77 6.75 13,079 1,182 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.81 7.0412,968 1,390 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.82 7.19 12,980 1,314 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.77 6.77 12,979 1,351 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 7.06 13,037 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.81 6.98 13,031 1,348 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 7.09 12,998 1,397 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.77 7.31 13,006 1,436 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.80 6.8013,106 1,334 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 6.98 13,020D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,263 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.75 7.05 13,011 1,276 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 6.82 13,024 1,376 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 6.79 13,056 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 6.66 13,109 1,435 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.80 6.8413,014 1,401 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.77 6.86 13,071 1,244 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 7.08 13,013 1,280 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.75 7.26 13,042 1,315 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.74 6.81 13,066 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 6.37 13,139 1,295 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.75 6.67 13,071 1,309 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.73 6.62 13,079 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.72 6.52 13,094 1,327 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.71 6.59 13,120 1,334 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.75 6.52 13,096 1,314 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 7.45 12,974 1,291 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 5.93 13,090 1,375 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.78 6.91 13,037 1,288 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.73 7.27 13,004 1,400 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.76 6.93 13,070 1,387 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 7.4012,987 1,480 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.64 6.56 13,105 1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.4413,175 1,143 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.65 6.91 13,118 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.73 6.88 13,037 1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.48 6.1013,166 1,315 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.51 6.81 13,027 1,438 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.61 13,047 1,400 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.45 13,133 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.8413,060 1,229 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.43 6.22 13,110 1,345 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.40 6.4013,093 1,215 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.42 5.99 13,163 1,317 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.44 6.21 13,113 1,333 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.52 6.55 13,125 1,247 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.55 6.66 13,097 1,377 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 6.17 13,091 1,441 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.46 5.78 13,214 1,341 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.42 6.36 13,102 1,337 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.53 6.26 13,115 1,416 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.40 6.01 13,128 1,341 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.29 13,163 1,310 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.47 6.2013,118 1,274 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.58 6.78 12,923D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,337 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.2413,139 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.44 6.03 13,108 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.50 6.29 13,091 1,353 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.1413,236 1,215 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE BARGE 0.49 6.2013,128 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,332 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,359 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,269 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,287 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,281 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,272 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,360 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,311 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,244 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,386 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,334 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,331 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,214 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,183 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,330 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,298 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,241 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,306 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,182 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,293 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,312 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,315 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,334 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,209 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,336 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,254 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,251 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,275 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,271 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,336 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,133 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,167 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,197 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,233 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,295 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,319 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,220 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,235 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,227 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,155 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,234 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,089 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,199 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,291 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,257 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,221 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,263 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,152 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,041 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,178 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,120 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,151 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,196 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,087 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,273 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,208 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,182 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,419 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,225 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,249 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,301 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,232 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,197 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,275 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,211 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,228 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,312 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,256 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,265 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,319 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,177 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,387 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,334 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,297 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,340 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,353 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,301 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,336 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,302 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,211 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,316 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,285 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,279 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,245 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,258 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,275 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,342 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,320 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,298 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,232 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,299 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,267 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,367 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,326 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,192 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,248 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,370 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,354 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,400 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,342 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,360 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,268 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,413 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,293 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,315 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,291 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,336 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,427 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,340 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,282 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,274 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,324 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,265 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,231 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,291 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,321 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,367 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,205 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,388 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,297 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,292 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,406 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,367 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,352 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,289 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,320 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,419 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,322 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,258 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,384 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,270 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,336 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,275 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,401 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,355 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,330 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,393 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,351 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,406 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,405 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.75 13,044 1,350 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,346 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,265 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,337 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,315 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,340 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,334 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,367 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,387 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,376 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,279 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,278 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,315 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,146 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,338 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,350 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,298 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,332 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,260 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,274 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,269 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,186 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,350 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,314 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,305 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,398 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,348 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,351 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,342 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,277 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,316 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,210 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,316 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,214 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,259 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,437 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,380 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,366 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,319 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,369 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,269 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,321 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,348 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,298 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,262 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,342 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,229 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,306 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,284 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,393 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,354 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,219 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,372 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,253 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,293 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,352 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,354 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,337 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,342 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,237 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,311 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,342 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,300 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,248 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,306 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,269 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,371 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,187 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,342 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,385 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,197 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,194 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,310 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,362 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,376 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,206 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,400 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,375 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,319 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,228 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,302 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,270 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,416 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,280 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,422 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,420 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,377 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,237 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,357 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,333 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,358 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,326 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,359 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,301 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,337 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,238 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,300 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,287 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,227 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,360 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,326 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,319 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,273 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,208 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,370 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,327 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,245 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,277 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,385 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,220 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,283 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,283 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,282 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,325 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,448 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,317 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,285 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,304 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,340 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,292 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,261 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,297 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,331 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,305 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,307 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,264 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,389 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,334 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,323 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,355 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,288 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,234 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,310 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.56 6.6013,070 1,253 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,382 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,233 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,252 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,267 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,210 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,252 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,158 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,256 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,198 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,341 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,135 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,311 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,133 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 962 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,120 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,033 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,229 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,081 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,183 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,148 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,155 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,168 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,087 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 878 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,303 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,196 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,157 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,269 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,244 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,309 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,416 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,258 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,427 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,128 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,239 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 719 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,283 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,316 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,229 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,268 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,265 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,316 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,343 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,284 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,145 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,243 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,376 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,087 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,176 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,251 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,109 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,289 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,197 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,291 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,165 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,187 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,304 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,227 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,174 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,243 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,302 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,217 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 895 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,257 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 801 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,214 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,223 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,223 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,283 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,233 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,122 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,273 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,245 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,221 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,201 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,268 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,256 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,251 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,106 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,266 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,349 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,217 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,293 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,272 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,327 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 955 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,214 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,146 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,166 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,148 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,111 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,191 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,187 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,141 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,041 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,074 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,131 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,142 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,276 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,008 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,168 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,081 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,362 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,275 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,013 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,091 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,345 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,146 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,264 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,165 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,307 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 912 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,118 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,020 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,026 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,252 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,410 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,200 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,174 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,410 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,379 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,297 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,350 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,265 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,188 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,212 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.58 6.6413,097 1,218 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,299 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,208 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,357 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,221 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,253 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,176 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,157 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,344 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,242 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,109 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,108 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,019 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,106 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,307 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,194 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,226 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,240 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,278 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,293 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,105 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,115 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,288 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,264 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,275 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,305 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,304 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,323 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,381 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,221 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,439 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,222 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,180 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,330 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,375 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,457 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,146 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,204 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,423 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,341 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,260 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,304 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,418 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,413 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,196 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,441 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,527 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,441 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,397 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,468 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,197 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,478 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,301 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,109 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,425 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,410 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,204 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,367 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,327 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,247 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,293 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,314 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,344 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,424 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,346 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,360 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,156 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,326 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,312 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,320 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,451 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,489 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,204 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,450 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,234 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,345 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,265 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,254 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,389 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,362 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,370 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,468 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,228 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,464 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,247 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,396 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,402 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,478 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,359 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,387 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,423 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,390 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,324 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,285 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,413 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,463 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,472 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,392 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,251 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,197 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,418 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,427 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,369 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,395 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,448 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,419 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,392 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,367 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,346 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,270 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,298 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,428 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,373 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,321 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,258 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,254 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,297 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,292 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,527 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,137 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,437 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,321 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,324 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,297 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,326 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,326 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,470 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,353 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,401 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,258 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,241 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,375 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,350 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,404 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,434 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,345 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,397 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,380 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,320 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,395 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,239 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,511 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,393 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.68 6.5413,047 1,377 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,370 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,388 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,444 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,281 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,266 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,439 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,281 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,346 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,302 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,373 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,274 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,352 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,023 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,299 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,364 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,238 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,487 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,353 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,346 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,387 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,207 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,410 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,382 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,349 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,384 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,393 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,345 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,371 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,381 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,420 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,409 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,341 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,453 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,306 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,397 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,331 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,288 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,386 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,211 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,380 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,423 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,359 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,422 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,445 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,433 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,407 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,449 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,447 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,341 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,266 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,255 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,375 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,366 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,393 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,236 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,309 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,258 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,366 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,436 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,400 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,323 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,412 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,400 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,264 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,372 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,393 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,419 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,404 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,368 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,381 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,440 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,406 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,440 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,382 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,191 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,498 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,500 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,418 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,378 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,386 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,400 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,415 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,423 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,448 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,401 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,442 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,398 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,285 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,432 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,247 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,332 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,415 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,445 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,392 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,317 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,401 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,331 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,433 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,351 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,330 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,358 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,309 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,371 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,370 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,393 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,355 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,466 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,210 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,360 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,325 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,264 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,364 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,405 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,282 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,409 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,415 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,362 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,307 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,325 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,373 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,295 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,288 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,288 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,184 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,379 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,297 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,334 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,087 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,407 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,472 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,385 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,434 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,354 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,387 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,324 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,376 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,370 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,350 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,478 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,357 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,459 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,245 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,444 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,367 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,437 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,404 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,377 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,333 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,370 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,441 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,368 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,442 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,299 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,036 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,387 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,436 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,298 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,362 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,346 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,279 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,233 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.62 6.66 13,059 1,354 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,407 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,306 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,315 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,262 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,371 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,370 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,368 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,459 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,495 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,432 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,395 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,405 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,411 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,395 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,403 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,398 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,402 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,336 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,372 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,501 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,241 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,404 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,165 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,389 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,364 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,461 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,330 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,373 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,321 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,454 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,409 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,367 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,406 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,400 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,364 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,419 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,235 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,366 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,279 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,327 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,381 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,357 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,418 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,421 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,385 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,323 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,338 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,369 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,424 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,334 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,337 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,416 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,397 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,357 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,354 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,322 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,477 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,323 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,438 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,419 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,377 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,246 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,385 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,369 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,323 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,433 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,340 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,351 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,352 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,268 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,444 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,304 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,232 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,392 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,375 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,437 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,400 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,343 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,362 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,395 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,442 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,401 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,451 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,322 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,412 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,418 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,379 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,417 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,415 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,424 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,264 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,304 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,404 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,413 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,355 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,418 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,413 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,432 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,386 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,443 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,358 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,246 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,281 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,324 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,398 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,261 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,358 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,370 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,344 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,345 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,325 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,442 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,353 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,138 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,292 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,312 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,266 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,271 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,172 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,469 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,349 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,389 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,299 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,238 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,477 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,423 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.50 5.98 13,125 1,333 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,238 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,245 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,371 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,372 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,348 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,186 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,340 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,274 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,215 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,423 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,269 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,352 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,260 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,147 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,385 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,168 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,412 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,453 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,397 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,428 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,317 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,426 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,414 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,242 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,242 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,348 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,351 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,410 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,368 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,306 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,379 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,332 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,278 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,430 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,189 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,248 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,403 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,315 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,080 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,350 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,327 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,367 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,285 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,248 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,219 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,231 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,265 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,224 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,320 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,460 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,167 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,125 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,220 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,197 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,229 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,289 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,417 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,475 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,343 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,430 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,376 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,310 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,410 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,412 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,300 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,306 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,291 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,282 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,303 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,197 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,438 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,401 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,333 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,447 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,365 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,394 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,429 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,268 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,385 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,352 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,189 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,431 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,327 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,394 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,436 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,244 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,415 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,341 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,271 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,443 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,317 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,388 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,418 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,274 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,222 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,442 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,189 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,371 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,402 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,447 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,239 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,412 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,342 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,352 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,340 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,237 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,430 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,174 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,423 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,248 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,239 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,362 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,229 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,438 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,386 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,494 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,385 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.51 6.19 13,166 1,382 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,422 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,382 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,464 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,353 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,473 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,205 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,088 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,292 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,325 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,405 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,466 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,146 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,403 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,379 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,397 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,320 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,248 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,460 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,404 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,402 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,421 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,190 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,344 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,389 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,418 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,349 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,264 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,377 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,358 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,395 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,342 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,194 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,208 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,354 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,408 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,344 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,337 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,291 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,451 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,298 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,297 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,342 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,419 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,420 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,480 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,343 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,431 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,218 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,531 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,420 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,440 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,358 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,324 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,376 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,378 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,450 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,376 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,422 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,443 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,378 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,422 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,241 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,351 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,489 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,337 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,379 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,369 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,406 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,050 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,362 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,411 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,429 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,449 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,351 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,434 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,231 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,424 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,396 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,270 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,394 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,321 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,219 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,215 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,398 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,351 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,446 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,480 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,411 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,195 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,386 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,407 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,280 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,378 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,324 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,405 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,380 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,381 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,381 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,387 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,413 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,224 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,248 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,327 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,270 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,350 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,364 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,300 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,349 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,450 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,403 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,351 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,370 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,422 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,431 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,419 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,199 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,277 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,409 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,392 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,286 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,430 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,393 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,300 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,381 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,145 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,226 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,377 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,429 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,309 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,298 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,314 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,274 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,242 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,255 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,123 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,337 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.54 6.28 13,097 1,317 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,282 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,178 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,421 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,325 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,393 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,288 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,427 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,148 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,232 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,220 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,315 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,395 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,233 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,306 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,300 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,156 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,275 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,149 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,256 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,155 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,298 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,279 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,382 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,426 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,159 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,394 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,314 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,359 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,349 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,362 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,341 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,141 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,286 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,169 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,320 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,346 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,324 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,398 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,283 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,349 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,216 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,325 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,330 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,468 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,421 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,416 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,417 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,473 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,382 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,486 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,411 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,344 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,409 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,393 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,423 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,297 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,256 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,340 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,458 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,373 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,384 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,296 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,277 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,463 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,469 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,409 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,386 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,386 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,431 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,355 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,415 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,458 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,491 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,331 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,347 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,322 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,478 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,452 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,148 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,352 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,430 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,389 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,380 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,263 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,286 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,125 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,487 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,430 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,322 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,267 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,349 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,384 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,310 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,286 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,223 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,166 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,239 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,192 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,406 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,068 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,186 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,209 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,223 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,176 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,213 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,091 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,186 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,218 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,232 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,289 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,278 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,134 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,231 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,195 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,268 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,237 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,100 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,195 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,197 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,134 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,292 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,348 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,412 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,425 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,255 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,284 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,291 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,346 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,396 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,443 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,372 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,386 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,278 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,412 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,332 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,382 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,369 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.67 6.97 12,963 1,327 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,364 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,393 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 743 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,303 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,195 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,206 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,366 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,249 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,303 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,391 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,467 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,254 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,374 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,299 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,462 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,226 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,332 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,229 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,425 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,394 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,254 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,398 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,271 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,369 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,355 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,422 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,450 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,428 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,428 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,387 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,407 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,403 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,397 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,305 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,324 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,305 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,423 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,364 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,332 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,122 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,307 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,330 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,456 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,388 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,235 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,336 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,321 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,407 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,137 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,325 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,314 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,281 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,232 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,244 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,314 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,453 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,035 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,265 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,268 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,167 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,020 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,113 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,247 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,286 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,261 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,300 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,297 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,371 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,133 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,259 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,252 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,281 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,212 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,314 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,234 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,308 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,300 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,248 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,175 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,301 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,225 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,032 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,283 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,264 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,363 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,485 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,368 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,305 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,282 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,305 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,399 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,364 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,213 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,343 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,328 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,235 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,340 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,372 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,373 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,372 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,381 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,299 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,336 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,351 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,241 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,144 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,329 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,353 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.71 7.1412,967 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,338 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,311 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,335 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,412 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,370 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,318 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,319 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,331 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,336 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,311 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,355 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,288 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,383 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,214 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,397 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,260 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,414 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,310 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,273 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,274 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,288 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,423 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,356 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,197 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,266 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,459 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,190 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,290 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,311 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,372 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,322 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,403 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,289 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,325 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,341 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,285 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,346 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,339 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,357 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,361 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,433 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,313 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,263 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,281 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,294 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,287 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,295 1, 2, 3, 4, 5 COLOMBIA N/A GRAN MADRE SHIP 0.57 7.2412,939 1,477 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.05 14.32 12,853 1,438 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.18 14.53 12,922 1,484 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.11 14.55 12,778 1,455 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.13 16.0412,469 1,462 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.02 13.41 13,013 1,443 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.05 13.29 13,032 1,536 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.22 16.73 12,421 1,414 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.26 16.38 12,456 1,395 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.17 16.1012,477 1,362 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.34 15.19 12,736 1,385 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.17 17.26 12,411 1,442 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.27 16.59 12,517 1,390 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.02 15.96 12,454 1,297 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.10 16.69 12,325 1,395 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.13 16.2012,388 1,416 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.15 17.37 12,229 1,351 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.03 15.61 12,450 1,448 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.13 16.69 12,350 1,344 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.10 16.11 12,516 1,397 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.03 14.09 12,913 1,332 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.16 16.25 12,469 1,394 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.17 17.9012,177 1,452 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.27 16.67 12,328 1,442 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.23 16.23 12,480 1,382 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.14 15.58 12,570 1,448 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.23 16.2012,402 1,406 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.12 14.53 12,773D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,264 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.17 15.17 12,575 1,384 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.18 16.1012,456 1,419 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.24 16.21 12,472 1,413 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.93 16.3012,367 1,412 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.02 15.76 12,480 1,397 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.09 19.35 11,792 1,408 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.06 17.15 12,212 1,410 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.09 19.71 11,767 1,397 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.96 17.69 12,149 1,011 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.05 15.0012,761 1,270 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.13 18.05 12,071 1,205 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.95 18.02 12,043 1,186 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.00 18.12 12,048 1,254 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.12 16.16 12,424 1,170 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.97 17.0412,179 1,370 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.01 14.89 12,677 1,404 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.22 14.78 12,729 1,249 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.95 15.82 12,474 1,322 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.02 14.99 12,681 1,290 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.95 14.79 12,716 783 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.95 13.9412,830 793 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.87 15.07 12,646 1,144 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.97 15.68 12,484 1,185 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.04 14.88 12,726 1,105 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.97 15.1412,569 0 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.97 15.68 12,484 1,195 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.93 14.31 12,737 1,121 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.96 15.55 12,556 1,137 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.88 15.4012,565 1,043 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.97 15.21 12,671 1,079 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.94 14.35 12,786 1,313 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.89 15.13 12,578 1,093 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.95 14.81 12,684 1,278 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.97 15.99 12,500 1,412 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.06 16.75 12,375 1,372 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.96 16.7412,412 1,398 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.98 15.88 12,507 1,406 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.06 14.23 12,794 1,350 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.05 15.0412,684 1,403 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.97 15.06 12,648 1,407 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.97 14.92 12,544 1,464 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.02 12.79 13,109 1,430 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.96 15.91 12,497 1,409 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.03 16.52 12,327D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,399 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.96 15.66 12,418 1,407 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.94 15.9012,437 1,498 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.93 14.59 12,695 1,420 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.99 14.5012,763 1,419 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.94 13.9412,751 1,455 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.92 14.58 12,678 1,456 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.00 15.76 12,444 1,408 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.07 15.48 12,531 1,419 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.96 14.75 12,705 1,411 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.00 16.07 12,425 1,408 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.96 14.81 12,726 1,324 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.00 15.76 12,485 1,472 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.99 15.93 12,489 1,396 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.00 16.22 12,384 1,333 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.06 14.6012,726 1,380 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.98 14.87 12,755 1,343 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.95 14.22 12,825 1,371 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.96 15.75 12,419 1,428 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.04 16.12 12,488 1,387 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.06 12.87 13,157 1,360 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.85 14.42 12,795 1,348 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.03 14.16 12,819 1,376 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.85 14.11 12,834 1,327 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.89 14.91 12,648 1,374 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.86 14.78 12,712 1,369 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.86 13.5012,981 1,394 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.92 14.81 12,745 1,384 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.90 14.78 12,770 1,370 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.94 15.25 12,695 1,314 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.89 14.5012,759 1,434 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.99 12.09 13,322 1,324 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.90 14.0412,796 1,495 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.94 15.03 12,566 1,310 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.91 14.76 12,673 1,366 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.95 14.79 12,684 1,388 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.01 15.3012,581 1,413 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.96 14.32 12,765 1,421 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.90 15.18 12,698 1,436 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.86 15.95 12,468 1,399 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.95 15.47 12,587 1,374 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.92 16.43 12,440 1,366 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.90 15.61 12,550 1,330 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.90 14.91 12,696 1,393 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.96 18.17 12,091D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,279 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.12 17.01 12,257 1,308 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.10 14.57 12,703 1,345 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.10 14.88 12,682 1,323 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.13 14.19 12,992 1,355 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.09 17.58 12,182 1,340 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.10 14.0412,843 1,334 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.04 13.87 12,915 1,348 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.09 14.13 12,880 1,286 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.01 14.79 12,646 1,240 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.97 14.73 12,682 1,276 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.05 14.2012,802 1,283 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.02 15.09 12,732 1,258 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.88 14.76 12,562 1,314 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.19 21.63 11,283 1,244 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.92 15.16 12,598 1,340 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.89 14.39 12,713 1,233 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.99 14.07 12,835 1,332 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.06 15.81 12,431 1,231 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.97 15.3412,454 1,359 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.94 14.0012,726 1,371 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.00 13.78 12,879 1,322 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.98 14.58 12,650 1,412 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.97 14.69 12,630 1,414 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.98 14.52 12,636 1,287 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.98 14.37 12,750 1,277 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.95 15.43 12,606 1,465 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.94 13.18 13,050 1,355 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.01 15.4412,568 1,423 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.93 14.13 12,830 1,264 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.92 13.67 12,871 1,339 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.05 15.48 12,495 1,312 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.07 15.61 12,505 1,370 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.02 14.69 12,676 1,362 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.02 15.53 12,474 1,317 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.98 16.36 12,361 1,378 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.00 14.86 12,652 1,320 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.95 14.06 12,687 1,405 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.93 14.09 12,703 1,361 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.91 13.93 12,673 1,405 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.99 13.2012,866 1,249 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.91 14.08 12,698 1,302 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.91 13.73 12,708 1,339 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.92 13.89 12,757 1,269 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 1.01 14.08 12,715D.B. D.B. D.B. 

### State/Country County42 

### Coal seam43 % Sulf% A shBtu/lb 

### Fuel source Amount received, dry basis, short tons40

### ID # of boiler(s) firing fuel41 

### Fuel shipment method Vendor Analyses

1,315 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.95 13.11 12,850 1,338 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.92 14.16 12,644 1,335 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.99 13.69 12,728 1,348 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.92 13.95 12,702 1,327 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.94 14.9412,599 1,360 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.89 14.01 12,776 1,371 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.91 13.7412,783 1,369 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.92 13.91 12,772 1,306 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.86 13.69 12,658 1,344 1, 2, 3, 4, 5 ALABAMA BIBB, JEFFERSON, TUSCALOOSA, WALKER AMERICAN #1 BARGE 0.91 14.15 12,728 11,361 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.51 9.61 13,089 11,171 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.45 6.3013,743 11,197 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.45 8.5413,398 11,420 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.45 8.45 13,335 11,456 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.43 12.9012,650 11,536 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.45 9.88 13,234 11,022 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.51 12.1012,805 10,494 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.58 10.65 12,737 10,704 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.57 10.02 12,903 10,852 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.52 10.43 12,872 11,066 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.54 7.93 13,227 11,107 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.51 9.06 13,121 11,034 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.53 12.03 12,723 11,007 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.53 9.9012,999 10,731 1, 2, 3, 4, 5 COLORADO GUNNISON D SEAM BARGE 0.52 10.36 12,925

Note: "N/A" means not available. 

### Note: The information being provided is on a shipment by shipment basis. Alabama Power cannot guarantee that what was shipped in the preceding 12 calendar months is what was burned in the preceding 12 calendar months. Multiple seams may be listed to account for the flexibility written into the purchase orders. Actual shipments may not have originated from each seam listed.

40EPA recognizes that facilities have (sometimes) several months inventory and that the amount received is not necessarily the same as the amount fired.

41Boiler ID (as reported on U.S. DOE/EIA Form EIA-860 (2007), "Annual Electric Generating Report," schedule 6, part A, line 1, page 53, [for plants equal to or greater than 10 MW but less than 100 MW] or on schedule 6, part B, line 1, page 54, [for plants greater than 100 MW]) OR Generator ID (as reported on U.S. DOE/EIA Form EIA-923 (2008), "Power Plant Operations Report," schedule 5, part A, page 8).

42If known.

43If known.3For each individual coal and oil shipment received during the preceding 12 calendar months, provide the following information44, as

available (dry basis) (indicate N/A if not available):

AntimonyArsenicBerylliumCadmiumChromiumCobaltLeadManganeseSelenium 09-701 1,541 0.54 6.58 13,057 0.052 38 50 4.4 <1 2.8 0.3 <0.02 5.5 1.8 1.9 14.7 5.5Colombia Cesar / La Loma Gran Madre Barge 09-703 79,623 0.73 6.67 13,115 0.05 47 88 6.4 1.3 7.2 0.5 0.17 6.9 2.5 3.0 22.4 5.3Colombia Cesar / La Loma Gran Madre Ship
09-306 11,746 0.55 10.55 12,773 0.028 76 59 4 <1 0.9 0.7 0.06 5.3 2.3 6.0 13.2 1.0Colorado Gunnison D Train 09-608 7,123 0.94 14.35 12,829 0.078 435 61 12.4 1.9 12.5 1.7 0.04 18.1 7.6 5.4 38.5 1.3Alabama Jefferson, Walker Mary Lee, Top American, American #1Train
09-619 7,123 0.94 14.49 12,653 0.096 481 82 21 2.1 16.5 1.7 0.04 21.5 11.8 7.3 76.3 1.1Alabama Jefferson, Walker Blue Creek, Top American, Bear Creek, Black Creek, Blue Creek, Bear Creek High Ash Train

09-319 12,281 0.57 9.66 12,894 0.03 131 56 3.7 <1 1 0.6 0.03 5 2.1 5.4 21.7 0.9Colorado Gunnison D Train 09-713 1,471 0.73 6.50 12,989 0.086 46 39 4.9 <1 6.6 0.4 0.16 5.5 1.9 2.2 13.5 5.4Colombia Cesar / La Loma Gran Madre Barge 09-333 12,286 0.53 10.91 13,086 0.033 231 57 4 <1 1 0.7 0.03 5.9 2.2 5.6 13.7 0.9Colorado Gunnison D Train 09-719 1,441 0.54 6.30 13,080 0.059 67 31 5.5 <1 4.5 0.3 0.12 5.9 2.2 2.9 20.5 5.2Colombia Cesar / La Loma Gran Madre Barge 09-633 8,864 0.90 15.40 12,534 0.105 337 62 17.4 2.2 16.9 2.3 0.04 22.5 11.2 9.9 76.2 1.1Alabama Jefferson, Walker, Franklin Blue Creek, Bear Creek, Black Creek, America #1, Mary Lee, Top America, Nickle Plate Barge

09-727 1,493 0.60 6.42 13,019 0.068 41 32 4.9 <1 6.1 0.3 0.15 6.0 2.2 3.1 16.4 5.6Colombia Cesar / La Loma Gran Madre Barge 09-338 12,197 0.46 9.97 13,087 0.032 266 56 4.1 <1 1.1 0.6 0.05 6.4 2.9 6.5 16.9 0.9Colorado Gunnison D Train

Note: Alabama Power collects this information on select coal shipments, but does not have this information available on a shipment by shipment basis. The information Alabama Power provides in this response cannot be linked to the information in Part II, Question 2 because the information comes from two separate databases. Thus, the information provided in this response represents only a very small portion of our actual shipments.

44To the extent that a vendor provides these data or that a facility is required by State or local agency to analyze its fuel for HAP constituents (e.g., Cl, F), and any metallic HAP (e.g., Hg, Pb, As, Se, etc.), EPA wishes the responding facility to provide those fuel analyses results. Otherwise, this 12-month fuel analysis requirement can be bypassed by the respondent.

45Metal HAP includes compounds of antimony, arsenic, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, phosphorus, and selenium. Sample ID # State/Country County Coal Seam Fuel Shipment Method Total amount of fuel represented byTotal Sulfur,

% Ash Content, %Heating Value,

Btu/lb Mercury,

ppmChlorine,

ppmFluorine,

ppm Nickel,

ppm Other Trace Metal HAP, ppm4Were the data provided in Part II, question 3 above, acquired pursuant to:

____ permit requirements ____ contractual obligations ____ standard operational procedures

_X__ other (please specifyto support R&D projects, plant performance, and TRI reporting)

5Analyses provided in Part II, question 3 above, supplied by ____ Fuel supplier (name and address)

_X__ Other (name and address) Analytical services are conducted by Alabama Power Company's in-house laboratory. Alabama Power Company, General Services Laboratory 744 Highway 87, GSC #8 Calera, AL 35040 6Name and address of laboratory performing analyses: Alabama Power Company, General Services Laboratory 744 Highway 87, GSC #8 Calera, AL 35040 7In addition to the analyses required in Part II, question 3 above, for samples for which analyses of chlorine and/or any of the HAP metals were conducted, please provide copies of any analyses conducted over the preceding 12 calendar months for (a) complete proximate and ultimate analyses, (b) additional trace metals, and (c) the mineralogy of the ash that are readily available for the oil(s) or coal(s) listed in Part II, question 2 above. The Agency is requesting these data only as they may already be available; no additional sampling or analyses are required to provide these data.

Total

MoistureVolatilesAsh Fixed CarbonCarbonHydrogenNitrogenTotal SulfurOxygenBariumCopperMagnesiumSodiumVanadiumZinc Al2O3Fe2O3 CaO MgO MnO2P2O5 K2O SiO2 Na2O SO3 TiO2

09-701 12.26 38.50 6.58 54.92 76.99 4.59 1.52 0.54 9.78 250 6.0 0.066 0.107 16.8 7.2 21.62 7.76 3.65 1.660.03535 0.26 1.60 54.80 2.20 4.88 1.01 09-703 11.02 38.68 6.67 54.65 76.80 4.67 1.19 0.73 9.94 190 7.8 0.050 0.096 20.5 8.5 23.49 8.11 2.70 1.250.05311 0.29 1.50 54.73 1.94 4.54 1.02 09-306 8.80 38.09 10.55 51.36 74.14 4.84 1.54 0.55 8.38 240 8.5 0.081 0.050 15.5 11.0 27.37 5.02 3.32 1.270.01981 0.62 1.35 55.88 0.63 3.30 0.86 09-608 4.50 30.23 14.35 55.42 72.93 4.65 1.72 0.94 5.41 250 17.8 0.110 0.047 34.9 14.9 26.72 6.50 1.88 1.270.04251 0.38 2.94 56.61 0.44 1.77 1.24 09-619 7.30 31.30 14.49 54.21 72.21 4.60 1.67 0.94 6.09 300 20.4 0.107 0.032 40.7 18.3 27.15 7.12 1.98 1.230.08333 0.71 3.03 55.36 0.30 1.58 1.23 09-319 8.81 37.86 9.66 52.48 72.92 5.03 1.64 0.5710.18 250 8.2 0.075 0.051 14.2 14.4 25.88 6.26 4.06 1.300.03550 0.68 1.37 54.60 0.72 3.76 0.90 09-713 14.87 39.18 6.50 54.32 75.07 4.96 1.67 0.7311.07 260 6.7 0.059 0.105 18.83 8.6 20.42 9.25 3.57 1.510.03288 0.32 1.44 53.70 2.17 6.04 0.99 09-333 7.58 36.91 10.91 52.18 73.35 5.03 1.34 0.53 8.84 240 9.0 0.079 0.074 15.5 10.6 23.62 5.05 3.01 1.200.01991 0.52 1.83 59.66 0.92 2.96 0.89 09-719 16.43 38.29 6.30 55.41 75.13 5.00 1.43 0.5411.60 230 5.7 0.059 0.100 17.3 8.9 21.25 7.84 3.74 1.560.05153 0.30 1.36 54.93 2.15 5.44 0.93 09-633 6.39 30.25 15.40 54.35 71.39 4.55 1.55 0.90 6.21 250 21.3 0.117 0.034 41.5 22.3 26.33 6.69 1.54 1.260.07830 0.45 2.93 57.39 0.30 1.64 1.22 09-727 16.30 38.85 6.42 54.73 74.62 5.02 1.58 0.6011.76 250 6.5 0.058 0.100 18.8 8.9 20.71 8.31 3.65 1.510.04046 0.30 1.35 55.79 2.09 4.71 0.99 09-338 7.80 37.33 9.97 52.70 73.85 5.15 1.71 0.46 8.86 220 9.9 0.078 0.071 17.6 13.6 24.33 5.36 4.07 1.300.02690 0.54 1.55 56.81 0.96 3.78 0.93 Sample ID # Proximate Analyses, % by wt Ultimate Analyses, % by wt Ash Mineralogy, % by wt Other Trace Metals, ppm

### 8aWhat emission test report(s), parametric monitoring data, and other data or monitoring are available for the boilers noted in Part I,

question 15, for tests conducted since January 1, 2005. Please consider reports prepared for all testing and monitoring programs, for all pollutants, including (but not limited to) those required under Title V, compliance with State or local requirements, fulfillment of contractual obligations, U.S. Department of Energy (DOE) programs, etc. (NOTE: EPA is not requesting copies of the test reports or data at this time; however we may request actual copies in the future.) Use additional pages as necessary.

Report 1Unit 1 Particulate Emissions Test (April 26, 2005) Report 2Unit 2 Particulate Emissions Test (March 24, 2005) Report 3Unit 3 Particulate Emissions Test (February 15, 2005) Report 4Unit 4 Particulate Emissions Test (March 25, 2005) Report 5Unit 5 Particulate Emissions Test (May 19, 2005) Report 6Unit 1 Particulate Emissions Test (June 21, 2006) Report 7Unit 2 Particulate Emissions Test (August 21, 2006) Report 8Unit 3 Particulate Emissions Test (July 25, 2006) Report 9Unit 4 Particulate Emissions Test (April 27, 2006) Report 10Unit 5 Particulate Emissions Test (June 6, 2006) Report 11Unit 1 Particulate Emissions Test (May 22, 2007) Report 12Unit 2 Particulate Emissions Test (May 22, 2007) Report 13Unit 3 Particulate Emissions Test (May 23, 2007) Report 14Unit 4 Particulate Emissions Test (February 22, 2007) Report 15Unit 5 Particulate Emissions Test (May 30, 2007) Report 16Unit 1 Particulate Emissions Test (June 19, 2008) Report 17Unit 2 Particulate Emissions Test (May 21, 2008) Report 18Unit 3 Particulate Emissions Test (May 22, 2008) Report 19Unit 4 Particulate Emissions Test (April 9, 2008) Report 20Unit 5 Particulate Emissions Test (May 20, 2008) Report 21Unit 1 Particulate Emissions Test (June 2, 2009) Report 22Unit 2 Particulate Emissions Test (August 13, 2009) Report 23Unit 3 Particulate Emissions Test (July 16, 2009) Report 24Unit 4 Particulate Emissions Test (June 3, 2009) Report 25Unit 5 Particulate Emissions Test (May 13, 2009) Report 26Unit 1 Compliance Assurance Monitoring Test (June 22, 2006) Report 27Unit 2 Compliance Assurance Monitoring Test (August 22, 2006) Report 28Unit 3 Compliance Assurance Monitoring Test (July 26, 2006) Report 29Unit 4 Compliance Assurance Monitoring Test (April 28, 2006) Report 30Unit 5 Compliance Assurance Monitoring Test (May 31, 2007) Report 31Unit 1 Compliance Assurance Monitoring Test (December 6, 2005) Report 32Unit 2 Engineering Particulate Tests as Part of the Switch Mode Power Supply Test (January 23-24, 2007) Report 33Unit 2 Engineering Particulate Test as Part of the Switch Mode Power Supply Test (July 24, 2007) Report 34Unit 2 Engineering Particulate Test as Part of the Switch Mode Power Supply Test (July 27, 2007) Report 35Unit 5 APC Air-Preheater Performance Test (September 5-6, 2007)

8bPlease indicate the date(s) and types (e.g., stack, fuel, parametric, etc.) of the test(s) and the constituents (including criteria and hazardous air pollutants) sampled for: Report 1 Date: 4/26/2005 Type: duct Constituents: PM Report 2 Date: 3/24/2005 Type: duct Constituents: PM Report 3 Date: 2/15/2005 Type: duct Constituents: PM Report 4 Date: 3/25/2005 Type: duct Constituents: PM

### Report 5 Date: 5/19/2005 Type: duct Constituents: PM

Report 6 Date: 6/21/2006 Type: duct Constituents: PM Report 7 Date: 8/21/2006 Type: duct Constituents: PM Report 8 Date: 7/25/2006 Type: duct Constituents: PM Report 9 Date: 4/27/2006 Type: duct Constituents: PM Report 10 Date: 6/6/2006 Type: duct Constituents: PM Report 11 Date: 5/22/2007 Type: duct Constituents: PM Report 12 Date: 5/22/2007 Type: duct Constituents: PM Report 13 Date: 5/23/2007 Type: duct Constituents: PM Report 14 Date: 2/22/2007 Type: duct Constituents: PM Report 15 Date: 5/30/2007 Type: duct Constituents: PM Report 16 Date: 6/19/2008 Type: duct Constituents: PM Report 17 Date: 5/21/2008 Type: duct Constituents: PM Report 18 Date: 5/22/2008 Type: duct Constituents: PM Report 19 Date: 4/9/2008 Type: duct Constituents: PM Report 20 Date: 5/20/2008 Type: duct Constituents: PM Report 21 Date: 6/2/2009 Type: duct Constituents: PM Report 22 Date: 8/13/2009 Type: duct Constituents: PM Report 23 Date: 7/16/2009 Type: duct Constituents: PM Report 24 Date: 6/3/2009 Type: duct Constituents: PM Report 25 Date: 5/13/2009 Type: duct Constituents: PM Report 26 Date: 6/22/2006 Type: duct Constituents: PM Report 27 Date: 8/22/2006 Type: duct Constituents: PM Report 28 Date: 7/26/2006 Type: duct Constituents: PM Report 29 Date: 4/28/2006 Type: duct Constituents: PM Report 30 Date: 5/31/2007 Type: duct Constituents: PM Report 31 Date: 12/6/2005 Type: duct Constituents: PM Report 32 Date: 1/23 -1/24/2007 Type: duct Constituents: PM Report 33 Date: 7/24/2007 Type: duct Constituents: PM Report 34 Date: 7/27/2007 Type: duct Constituents: PM Report 35 Date: 9/5 - 9/6/2007 Type: duct Constituents: CO, NOx, CO2

8cDo any of these test reports reflect testing at a location before any emission control devices? Yes _X

__No _

_ __If yes, please note which reports and provide a detailed description of the location of the emissions sampling point(s). Reports 32, 33, and 34 contain test results for testing that was conducted at the inlet to the ESP and the outlet of the ESP. Report 35 tests for CO were conducted at the economizer outlet.

8dWere any of these test reports conducted when use of other material(s) or non-fossil fuels were fired in the boiler? Yes ____No _X

__If yes, please not which reports and identify the other material(s) or non-fossil fuels used.

8eDo any of these test reports reflect testing during periods of startup, shutdown, and malfunction? Yes ____No _X

__If yes, please note which reports.

### 8fDid the unit's control configuration differ from that shown in Part I, question 16, at the time of these test results?

Yes _X

__No ____If yes, please list the unit's complete control configuration at time of testing in a similar format to Part I, question 16. The control configuration shown below is representative of the conditions present during Reports 1, 2, 3, 4, 5, 9, 10, 14, 15, 29, 30, and 35 (no SNCRs were installed on Units 1-4, and no SCR or FGD was installed on Unit 5).

Boiler ID
1

2

3

4

5

Note: "N/A" means not applicable.

1Units 1, 2, and 3 still have the capability for CaCO3injection, but the plant has not used it in several years.

2SO3injection on Unit 4 was not operated during 2009.

tangential-fired 

### Type tangential-fired

tangential-fired

tangential-fired

tangential-fired 

### NOx control SO2 control PM control Other control

(1) low-NOx burners + closecoupled OFA (05/30/2003) (2) flue gas conditioning -
CaCO3injection (1988)1 (3) hot-side ESP (07/17/1976)

(2) flue gas conditioning -
CaCO3injection (1988)1 (3) hot-side ESP (05/01/1976)

(1) low-NOx burners + closecoupled OFA (03/10/1996)

(1) low-NOx burners + separated OFA (03/16/1998)

(1) low-NOx burners + separated OFA (05/28/1998) N/A

N/A

N/A

N/A

N/A(1) low-NOx burners + closecoupled OFA (11/08/2002)

(2) flue gas conditioning -
CaCO3injection (1988)1 (3) hot-side ESP (01/03/1976)

(2) flue gas conditioning -
SO3injection (1979)2 (3) two cold-side ESPs arranged in parallel (03/29/1976 and 1985)

(2) flue gas conditioning - SO3injection (1979) (3) two cold-side ESPs arranged in series (10/19/1971 and 06/06/1976) N/A

N/A

N/A

N/A

N/A

### The control configuration shown below is representative of the conditions present on Units 1-4 during Reports 7, 11, 12, 13, 16, 17, 18, 21, 22, 23,

and 24 (no sodium carbonate operating on Units 1-3, no SO3

### injection on Unit 4).

Boiler ID
1

2

3

4

Note: "N/A" means not applicable.



### The control configuration shown below is representative of the conditions present on Units 1-4 during Reports 8, 19, 26, 27, 28, 31, and 32 (no sodium carbonate or SNCRs operating on Units 1-3, no SO3

### injection or SNCR operating on Unit 4).

Boiler ID
1

2

3

4

Note: "N/A" means not applicable.



### Type NOx control SO2 control PM control Other control tangential-fired (1) low-NOx burners + closecoupled OFA (11/08/2002) (2) SNCR (05/01/2006) N/A (3) hot-side ESP (07/17/1976) N/A

tangential-fired (1) low-NOx burners + closecoupled OFA (05/30/2003) (2) SNCR (07/01/2006) N/A (3) hot-side ESP (05/01/1976) N/A

tangential-fired (1) low-NOx burners + closecoupled OFA (03/10/1996) (2) SNCR (07/28/2006) N/A (3) hot-side ESP (01/03/1976) N/A

tangential-fired (1) low-NOx burners + separated OFA (03/16/1998) (2) SNCR (05/01/2006) N/A (3) two cold-side ESPs arranged in parallel (03/29/1976 and 1985) N/A



### Type NOx control SO2 control PM control Other control tangential-fired (1) low-NOx burners + closecoupled OFA (11/08/2002) (2) SNCR (05/01/2006) N/A (3) hot-side ESP (07/17/1976) N/A

tangential-fired (1) low-NOx burners + closecoupled OFA (05/30/2003) (2) SNCR (07/01/2006) N/A (3) hot-side ESP (05/01/1976) N/A

tangential-fired (1) low-NOx burners + closecoupled OFA (03/10/1996) (2) SNCR (07/28/2006) N/A (3) hot-side ESP (01/03/1976) N/A

tangential-fired (1) low-NOx burners + separated OFA (03/16/1998) N/A (2) two cold-side ESPs arranged in parallel (03/29/1976 and 1985) N/A

### The control configuration shown below is representative of the conditions present on Unit 5 during Reports 20 and 25 (no FGD installed).

Boiler ID
5

Note: "N/A" means not applicable.

1When making catalyst decisions, the primary goal is to achieve the desired NOx performance, with a secondary goal of minimizing SO3formation.



### 8gDo any of these test reports reflect testing at a location before a post combustion SO2 emission control device (e.g., FGD, SDA, Dry Scrubber)? Yes ____No _X

__If yes, please note which reports and, in addition to the detailed description of the location of the sampling point(s) (question 8c above), include detail about how much, if any, bypass of unscrubbed flue gas was utilized at at the time of testing (including percentage of total scrubber flue gas flow). Note by diagram where sampling ports were located in relation to the bypass ductwork.

Type NOx control SO2 control PM control Other control tangential-fired (1) low-NOx burners + separated OFA (05/28/1998) (3) SCR (05/01/2008) - the SCR uses a titania-vanadia based ceramic catalyst and anhydrous ammonia as the reductant; the catalyst is designed to minimize SO3 formation1 N/A (2) flue gas conditioning - SO3injection (1979) (4) two cold-side ESPs arranged in series (10/19/1971 and 06/06/1976) N/A

### 9What type of deviation reporting is required for violations of permit requirements? Deviations from permit requirements shall be reported within 48 hours or 2 working days of such deviations, including those attributable to upset conditions as defined in the permit. The report will include the probable cause of said deviations, and any corrective actions or preventative measures that were taken. The date, time, duration, magnitude, cause and corrective action taken for each excess emission are also include in the quarterly reports submitted to ADEM. Note: Not all reported deviations are considered violations of permit requirements. 10Are deviation reports available for malfunctions or other periods of noncompliance with permit terms and conditions? Yes _X

__No ____If yes, please note which reports.

Deviation cause and corrective action reports are also available in each quarterly report submitted to ADEM. Additionally, all deviations from permit terms and conditions are reported in the annual Title V compliance certifications, submitted to both ADEM and EPA. Note: A malfunction is not necessarily a period of non-compliance with permit terms and conditions. Not all reported deviations are considered violations of permit requirements. 11Are continuous emissions monitoring system (CEMS) data available (e.g., mercury, continuous opacity monitoring systems) that are not already being provided to the U.S. EPA, even if from short-term testing? Yes _X

__No ____If yes46

### , please note for which pollutants CEMS data are available and the period of time (both total period and calendar period) for which the data are available. If CEM data are being provided to EPA, please note to which Office the data are being provided.

Mercury CEMS data are available1

### for the following periods of time:

Units 1-3:December 3, 2008 - December 31, 2009 Unit 4A:June 24, 2009 - December 31, 2009 Unit 4B:December 15, 2009 - December 31, 2009 Unit 5:June 17, 2009 - September 21, 2009

COMS data are available for the following periods of time:

Unit 1-3:October 1, 1993 - December 31, 2009 Unit 4A:October 1, 1993 - December 31, 2009 Unit 4B:October 1, 1993 - December 31, 2009 Unit 5A:October 1, 1993 - March 28, 2008 Unit 5B:October 1, 1993 - March 28, 2008 Unit 5:March 29, 2008 - December 31, 2009

1

### Alabama Power considers CEMS data "available" only if it is maintained and subject to quality assurance/quality control procedures that meet the requirements of 40 CFR Part 75.

46Where units are monitored by CEMS (either following CAMR, State, or NIST QA/QC procedures), and where data are available, EPA requests that this CEMS data be submitted by the respondent. The respondent should also mark the periods of start up, shut down and malfunction events (SSM) in the data sets.12For each boiler noted in Part I, question 15, provide the following information:

Test ReportDate of test PM49 SO2 HCl/HF/HCN Metal HAP50 Hg51 CO Other organics (specify) 1 Report 1 4/26/2005See Attachment 1 N/A N/A N/A N/A N/A N/A 2 Report 2 3/24/2005See Attachment 2 N/A N/A N/A N/A N/A N/A 3 Report 3 2/15/2005See Attachment 3 N/A N/A N/A N/A N/A N/A 4 Report 4 3/25/2005See Attachment 4 N/A N/A N/A N/A N/A N/A 5 Report 5 5/19/2005See Attachment 5 N/A N/A N/A N/A N/A N/A 1 Report 6 6/21/2006See Attachment 6 N/A N/A N/A N/A N/A N/A 2 Report 7 8/21/2006See Attachment 7 N/A N/A N/A N/A N/A N/A 3 Report 8 7/25/2006See Attachment 8 N/A N/A N/A N/A N/A N/A 4 Report 9 4/27/2006See Attachment 9 N/A N/A N/A N/A N/A N/A 5 Report 10 6/6/2006See Attachment 10 N/A N/A N/A N/A N/A N/A 1 Report 11 5/22/2007See Attachment 11 N/A N/A N/A N/A N/A N/A 2 Report 12 5/22/2007See Attachment 12 N/A N/A N/A N/A N/A N/A 3 Report 13 5/23/2007See Attachment 13 N/A N/A N/A N/A N/A N/A 4 Report 14 2/22/2007See Attachment 14 N/A N/A N/A N/A N/A N/A 5 Report 15 5/30/2007See Attachment 15 N/A N/A N/A N/A N/A N/A 1 Report 16 6/19/2008See Attachment 16 N/A N/A N/A N/A N/A N/A 2 Report 17 5/21/2008See Attachment 17 N/A N/A N/A N/A N/A N/A 3 Report 18 5/22/2008See Attachment 18 N/A N/A N/A N/A N/A N/A 4 Report 19 4/9/2008See Attachment 19 N/A N/A N/A N/A N/A N/A 5 Report 20 5/20/2008See Attachment 20 N/A N/A N/A N/A N/A N/A 1 Report 21 6/2/2009See Attachment 21 N/A N/A N/A N/A N/A N/A 2 Report 22 8/13/2009See Attachment 22 N/A N/A N/A N/A N/A N/A 3 Report 23 7/16/2009See Attachment 23 N/A N/A N/A N/A N/A N/A 4 Report 24 6/3/2009See Attachment 24 N/A N/A N/A N/A N/A N/A 5 Report 25 5/13/2009See Attachment 25 N/A N/A N/A N/A N/A N/A 1 Report 26 6/22/2006See Attachment 26 N/A N/A N/A N/A N/A N/A 2 Report 27 8/22/2006See Attachment 27 N/A N/A N/A N/A N/A N/A 3 Report 28 7/26/2006See Attachment 28 N/A N/A N/A N/A N/A N/A 4 Report 29 4/28/2006See Attachment 29 N/A N/A N/A N/A N/A N/A 5 Report 30 5/31/2007See Attachment 30 N/A N/A N/A N/A N/A N/A 1 Report 31 12/6/2005See Attachment 31 N/A N/A N/A N/A N/A N/A 2 Report 321/23 - 1/24/2007See Attachments 32 & 33 N/A N/A N/A N/A N/A N/A 2 Report 33 7/24/2007See Attachment 34 N/A N/A N/A N/A N/A N/A 2 Report 34 7/27/2007See Attachment 35 N/A N/A N/A N/A N/A N/A 5 Report 35 9/5 - 9/6/2007 N/A N/A N/A N/A N/A See Attachment 36 N/A

Note: "N/A" means not applicable.

47Provide emission test data for all tests conducted since January 1, 2005. Please indicate test data acquired both before and after any control device. Use additional pages as necessary. EPA may, at some future date, request a copy of one or more emission test reports. Data generated to fulfill both Federal and State requirements must be provided. Note that data generated pursuant to CAA Title V must be maintained and available for 5 years. Also include averaging times and measurement units for all pollutants.

48For each emissions test run the respondent should provide the following process information: Unit Load (MW), Net generation during run (MWh net), Flue gas moisture content (%), Flue gas flow rate (dscfm or Nm3/hr), Flue gas oxygen content (%, dry), Flue gas carbon dioxide content (%, dry), Flue gas temperature at sampling point (oF), Flue gas pressure at sampling point (atm), Standard temperature (oF), Standard pressure (atm).

49If emission testing recorded the emissions of filterable and condensable PM, separately, please include those separate emission results. Also, please include separate emission results for total PM, PM10, and PM2.5. 50Metal HAP include compounds of antimony, arsenic, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, phosphorus, and selenium; indicate emission level for all metal HAP for which an emission test has been conducted.

51Please provide separate results for total Hg, elemental Hg, oxidized Hg, and particulate Hg, as available. If the emissions testing recorded the amount of unburned carbon in fly ash (as reflected by the "Loss of Ignition" [L.O.I]) at the time of any Hg testing, please include these data. Boiler ID Emissions test results (indicate format of emission data)47,48

### ATTACHMENT 1 - Barry Report 1 Test Results

Title of Run RUN 1 RUN 2 RUN 3
Date Month/Day/Year 4/26/20054/26/20054/26/2005 Sampling Time -Start Military 0920 1126 1324 Sampling Time -Stop Military 1044 1250 1448 Number of Ports dimensionless 16 16 16 Number of Points per Port dimensionless 3 3 3 Heat Input Million Btu per Hour 1444 1457 1425 Stack Static Pressure Inches Water -11.00 -11.00 -11.00 Barometric Pressure Inches Mercury 30.05 30.05 30.05 Meter Correction Factor dimensionless 1.011 1.011 1.011 Oxygen Concentration Mole Percent O2 7.5 7.0 7.0 Carbon Dioxide Concentration Mole Percent CO2 12.0 12.5 12.5 Volume of Gas Metered Actual Cubic Feet 51.150 51.370 50.332 Volume of Water Collected Milliliters 91.00 103.00 99.00 Sampling Time Minutes 96 96 96 Nozzle Diameter Inches 0.240 0.240 0.240 Weight of Solids Collected Milligrams 58.0 32.1 55.6 Area of Stack Square Feet 180.000180.000180.000 Avg. Sqr. Root Velocity Pressure Inches Water 0.7781 0.7863 0.7691 Average Orifice Pressure(DH) Inches Water 1.3 1.4 1.3 Average Stack Temperature Degrees F 597 604 608 Average Meter Temperature Degrees F 74 81 82 Average Generation MW 143 143 143

3 Runs
RUN 1 RUN 2 RUN 3Average

Volume of Gas Sampled Standard Dry 51.532 51.124 49.95750.871 Cubic Feet Molecular Wt. of Stack Gas LB/LB-MOLE 29.28 29.22 29.2329.24

Water vapor in Stack Gas Percent 7.7 8.7 8.5 8.3

Average Stack Gas Velocity Feet per second 62.1 63.0 61.7 62.3

Stack Gas Flow Rate Actual Cubic 670,291680,505666,690672,495 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 327,181329,847321,948326,326 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 302,073301,277294,479299,276 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 22,625 22,566 22,05622,416 Per Minute Particulate Concentration Grains per Standard 0.0173 0.0097 0.01710.0147 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0078 0.0043 0.00760.0066 Cubic Foot Particulate Emission Rate Pounds per Hour 44.9 25.0 43.3 37.7

Particulate Emission Rate Pounds per Million 0.031 0.017 0.0300.026 Allowable Particulate Emission RateBtu (Heat Input) 0.12 0.12 0.120.12 Isokinetic Rate Percent 101.8 101.3 101.2101.4

TABLE I. SUMMARY OF PARTICULATE EMISSIONS TEST RESULTS

ALABAMA POWER COMPANY BARRY STEAM PLANT, UNIT 1 4/26/2005

Calculations

### ATTACHMENT 2 - Barry Report 2 Test Results

Title of Run RUN 1 RUN 2 RUN 3
Date Month/Day/Year 3/24/20053/24/20053/24/2005 Sampling Time -Start Military 0830 1042 1226 Sampling Time -Stop Military 0936 1146 1328 Number of Ports dimensionless 5 5 5 Number of Points per Port dimensionless 6 6 6 Heat Input Million Btu per Hour 1,687 1,696 1,646 Stack Static Pressure Inches Water -7.50 -7.50 -7.50 Barometric Pressure Inches Mercury 30.35 30.35 30.35 Meter Correction Factor dimensionless 1.0410 1.0410 1.0410 Oxygen Concentration Mole Percent O2 5.5 5.5 5.0 Carbon Dioxide ConcentrationMole Percent CO2 14.5 14.5 15.0 Volume of Gas Metered Actual Cubic Feet 36.020 35.818 35.705 Volume of Water Collected Milliliters 60 70 73 Sampling Time Minutes 60.00 60.00 60.00 Nozzle Diameter Inches 0.252 0.252 0.252 Weight of Solids Collected Milligrams 88.7 26.0 51.6 Area of Stack Square Feet 180.0000180.0000180.0000 Avg. Sqr. Root Velocity PressureInches Water 0.8182 0.8215 0.8018 Average Orifice Pressure(DH)Inches Water 1.5 1.5 1.4 Average Stack Temperature Degrees F 592 597 594 Average Meter Temperature Degrees F 62 68 77 Average Generation MW 145 145 145

3 Runs RUN 1 RUN 2 RUN 3Average

Volume of Gas Sampled Standard Dry 38.629 37.953 37.19537.926 Cubic Feet Molecular Wt. of Stack Gas LB/LB-MOLE 29.69 29.54 29.5329.59

Water vapor in Stack Gas Percent 6.8 8.0 8.5 7.8

Average Stack Gas Velocity Feet per second 64.1 64.6 63.0 63.9

Stack Gas Flow Rate Actual Cubic 691,769698,041680,427690,079 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 345,825347,210339,327344,120 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 322,264319,474310,630317,456 Feet Per Minute Particulate Concentration Grains per Standard 0.0354 0.0105 0.02140.0224 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0165 0.0048 0.00980.0104 Cubic Foot Particulate Emission Rate Pounds per Hour 97.7 28.9 56.9 61.2

Particulate Emission Rate Pounds per Million 0.058 0.017 0.0350.036 Btu (Heat Input) Allowable 0.12 Isokinetic Rate Percent 103.8 102.9 103.7103.5



### TABLE I. SUMMARY OF PARTICULATE EMISSIONS TEST RESULTS

ALABAMA POWER COMPANY BARRY STEAM PLANT, UNIT 2 3/24/2005

Calculations

## ATTACHMENT 3 - Barry Report 3 Test Results

Indicator\Label Side A Side A Side A Side B Side B Side B Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 2/15/20052/15/20052/15/2005 2/15/20052/15/20052/15/2005 Sampling Time -Start Military 0820 0950 1120 0820 0950 1120 Sampling Time -Stop Military 0920 1050 1220 0920 1050 1220 Heat Input Million Btu per Hour 2,591 2,675 2,751 2,591 2,675 2,751 Stack Static Pressure Inches Water -10.00 -10.00 -10.00 -10.00 -10.00 -10.00 Barometric Pressure Inches Mercury 30.20 30.20 30.20 30.20 30.20 30.20 Meter Correction Factor dimensionless 1.011 1.011 1.011 1.041 1.041 1.041 Oxygen Concentration Mole Percent O2 6.0 6.5 6.0 6.0 6.0 5.5 Carbon Dioxide Concentration Mole Percent CO2 13.5 13.0 14.0 15.0 15.0 15.0 Volume of Gas Metered Actual Cubic Feet 39.610 39.625 40.467 40.805 39.467 41.755 Volume of Water Collected Milliliters 82 86 84 77 82 84 Sampling Time Minutes 60.00 60.00 60.00 60.00 60.00 60.00 Nozzle Diameter Inches 0.275 0.275 0.275 0.275 0.275 0.275 Weight of Solids Collected Milligrams 28.0 19.2 28.5 25.8 18.3 19.0 Area of Stack Square Feet 174.500174.500174.500 174.500174.500174.500 Avg. Sqr. Root Velocity Pressure Inches Water 0.7798 0.7643 0.7866 0.7630 0.7639 0.7880 Average Orifice Pressure(DH) Inches Water 1.5 1.5 1.6 1.8 1.8 1.9 Average Stack Temperature Degrees F 589 599 599 600 611 612 Average Meter Temperature Degrees F 60 63 66 64 67 70 Average Generation MW 259 259 259 259 259 259

Side A Side A Side A3 Runs Side B Side B Side B3 Runs RUN 1 RUN 2 RUN 3Average RUN 1 RUN 2 RUN 3Average

Volume of Gas Sampled Standard Dry 41.221 40.963 41.60441.262 43.428 41.772 43.89743.032 Cubic Feet Molecular Wt. of Stack Gas LB/LB-MOLE 29.34 29.23 29.40 29.32 29.67 29.57 29.5829.60

Water vapor in Stack Gas Percent 8.6 9.0 8.7 8.7 7.7 8.5 8.3 8.1

Average Stack Gas Velocity Feet per second 61.7 60.9 62.5 61.7 60.3 60.8 62.7 61.3

Stack Gas Flow Rate Actual Cubic 645,819637,105653,954645,626631,533636,592656,964641,696 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 319,988312,767320,867317,874309,788309,061318,584312,478 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 292,591284,639293,019290,083285,926282,919292,259287,035 Feet Per Minute Particulate Concentration Grains per Standard 0.0105 0.0072 0.01050.0094 0.0091 0.0067 0.00670.0075 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0047 0.0032 0.00470.0042 0.0041 0.0030 0.00300.0034 Cubic Foot Particulate Emission Rate Pounds per Hour 26.2 17.6 26.5 23.4 22.4 16.4 16.7 18.5

Particulate Emission Rate Pounds per Million 0.0101 0.0066 0.00960.0088 0.0087 0.0061 0.00610.0069 Btu (Heat Input) Combined Particulate Emission RatePounds per Million 0.0188 0.0127 0.01570.0157 Allowable Particulate Emission RateBtu (Heat Input) 0.12 0.12 0.12 0.12

Isokinetic Rate Percent 99.3 101.5 100.1 100.3 107.1 104.1 105.9105.7 

### TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 3

Calculations

### ATTACHMENT 4 - Barry Report 4 Test Results

Side A Side A Side A Side B Side B Side B

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 3/25/20053/25/20053/25/2005 3/25/20053/25/20053/25/2005 Sampling Time -Start Military 0824 0948 1122 0824 0948 1122 Sampling Time -Stop Military 0928 1054 1220 0924 1048 1222 Heat Input Million Btu per Hour 3466 3456 3466 3466 3456 3466 Plant Load Megawatts 376 375 376 376 375 376 Stack Static Pressure Inches Water 1.50 1.50 1.50 1.40 1.40 1.40 Barometric Pressure Inches Mercury 29.90 29.90 29.90 29.90 29.90 29.90 Meter Correction Factor dimensionless 1.041 1.041 1.041 1.052 1.052 1.052 Oxygen Concentration Mole Percent O2 4.0 4.0 4.0 6.0 5.5 4.5 Carbon Dioxide Concentration Mole Percent CO2 15.0 15.0 15.0 13.5 15.0 14.5 Volume of Gas Metered Actual Cubic Feet 35.815 32.510 36.820 39.955 36.990 37.960 Volume of Water Collected Milliliters 66.00 71.0 86.0 74.0 76.0 79.0 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.237 0.222 0.237 0.240 0.240 0.240 Weight of Solids Collected Milligrams 15.9 15.0 24.2 23.9 17.6 22.9 Number of Points Sampled 30 30 30 30 30 30 Area of Stack Square Feet 183.7500183.7500183.7500 183.7500183.7500183.7500 Avg. Sqr. Root Velocity Pressure Inches Water 0.8157 0.8348 0.8460 0.8534 0.7960 0.8286 Average Orifice Pressure(DH) Inches Water 1.8 1.4 1.9 2.0 1.7 1.9 Average Stack Temperature Degrees F 281.2 283.8 291.8 295.1 302.2 302.9 Average Meter Temperature Degrees F 73.0 71.8 74.8 60.7 63.6 66.0 Average Generation MW 376 375 376 376 375 376

Side A Side A Side A3 Runs Side B Side B Side B3 RunsTotal RUN 1 RUN 2 RUN 3Average RUN 1 RUN 2 RUN 3AverageA & B Sides

Volume of Gas Sampled Standard Dry 37.077 33.703 38.00036.260 42.817 39.383 40.25136.260 Cubic Feet Molecular Wt. of Stack Gas LB/LB-MOLE 29.589 29.427 29.35129.456 29.467 29.569 29.44329.456

Water vapor in Stack Gas Percent 7.7 9.0 9.6 8.8 7.5 8.3 8.5 8.8

Average Stack Gas Velocity Feet per second 53.50 55.00 56.11 54.87 56.63 52.97 55.28 54.87

Stack Gas Flow Rate Actual Cubic 589,869606,404618,650604,974624,325583,989609,510604,9741,209,949 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 421,387431,688435,717429,597437,665405,591422,946429,597 859,194 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 388,809392,743393,770391,774404,740371,818387,177391,774 783,548 Feet Per Minute Stack Gas Flow Rate Pounds Dry Air 1,754,2911,772,0401,776,6711,767,6671,826,1681,677,6251,746,9261,767,6673,535,335 per Hour Particulate Concentration Grains per Standard 0.006600.006850.009810.007760.008600.006880.008760.00776 Dry Cubic Foot Particulate Concentration Grains per Actual 0.004350.004440.006240.005010.005570.004380.005570.00501 Cubic Foot Particulate Emission Rate Pounds per Hour 22.01 23.07 33.10 26.06 29.82 21.93 29.08 26.06 52.12

Particulate Emission Rate Pounds per 0.0063 0.0067 0.00960.0075 0.0086 0.0063 0.00840.00778 Million Btu Combined Particulate Emission RatePounds per 0.0150 0.0130 0.01790.0153 Allowable Particulate Emission RateMillion Btu 0.12 0.12 0.12 0.12

Isokinetic Rate Percent 95.3 97.7 96.5 96.5 103.1 103.2 101.3 96.5 TABLE I. SUMMARY OF PARTICULATE EMISSIONS TEST RESULTS

ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 4

Calculations

### ATTACHMENT 5 - Barry Report 5 Test Results

Indicator\Label SIDE A SIDE A SIDE A SIDE B SIDE B SIDE B Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 5/19/20055/19/20055/19/2005 5/19/20055/19/20055/19/2005 Sampling Time -Start Military 0814 0950 1115 0814 0950 1108 Sampling Time -Stop Military 0922 1058 1226 0920 1059 1212 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 8,007 7,995 7,924 8,007 7,995 7,924 Stack Static Pressure Inches Water -0.60 -0.60 -0.60 -0.40 -0.40 -0.40 Barometric Pressure Inches Mercury 29.95 29.95 29.95 29.95 29.95 29.95 Meter Correction Factor dimensionless 1.051 1.051 1.051 1.011 1.011 1.011 Oxygen Concentration Mole Percent O2 5.5 6.5 6.5 5.0 5.5 6.0 Carbon Dioxide Concentration Mole Percent CO2 15.0 13.0 13.0 16.0 14.0 13.5 Volume of Gas Metered Actual Cubic Feet 36.771 40.986 42.101 40.605 40.702 38.503 Volume of Water Collected Milliliters 71.00 96.00 92.00 77.00 81.00 85.00 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.209 0.211 0.212 0.222 0.220 0.215 Weight of Solids Collected Milligrams 19.9 21.1 26.7 28.6 20.7 41.4 Area of Stack Square Feet 287.500287.500287.500 287.500287.500287.500 Avg. Sqr. Root Velocity Pressure Inches Water 1.0459 1.1467 1.1431 1.0736 1.0888 1.0771 Average Orifice Pressure(DH) Inches Water 1.5 1.9 1.9 1.7 1.7 1.5 Average Stack Temperature Degrees F 321 323 326 317 322 325 Average Meter Temperature Degrees F 82 86 90 75 81 84 Average Generation MW 776 776 776 776 776 776

SIDE A SIDE BTotal Unit RUN 1 RUN 2 RUN 3Average RUN 1 RUN 2 RUN 3Average

Volume of Gas Sampled Standard Dry 37.816 41.870 42.69240.793 40.726 40.396 37.97039.697 Cubic Feet Molecular Wt. of Stack Gas LB/LB-MOLE 29.60 29.14 29.20 29.31 29.72 29.39 29.22 29.4429.41

Water vapor in Stack Gas Percent 8.1 9.7 9.2 9.0 8.2 8.6 9.5 8.88.8

Average Stack Gas Velocity Feet per second 70.5 78.1 77.9 75.5 72.0 73.7 73.3 73.073.5

Stack Gas Flow Rate Actual Cubic 1,216,7091,346,5531,343,3181,302,1931,242,7611,271,3821,263,9901,259,3772,561,571 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 822,150906,944901,427876,840844,567858,782850,161851,1701,728,010 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 755,393818,599818,411797,468775,547784,718769,119776,4611,573,929 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 56,579 61,313 61,29959,730 58,088 58,775 57,60758,157117,887 Per Minute Particulate Concentration Grains per Standard 0.0081 0.0078 0.00960.0085 0.0108 0.0079 0.01680.01180.0112 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0050 0.0047 0.00590.0052 0.0067 0.0049 0.01020.00730.0069 Cubic Foot Particulate Emission Rate Pounds per Hour 52.5 54.5 67.6 58.2 71.9 53.1 110.7 78.6136.7

Particulate Emission Rate Pounds per Million 0.007 0.007 0.009 0.007 0.009 0.007 0.014 0.0100.017 Allowable Particulate Emission Rate Btu (Heat Input) 0.12

Isokinetic Rate Percent 100.7 100.9 101.9 101.2 93.6 93.4 93.8 93.6 

### TABLE I. SUMMARY OF PARTICULATE EMISSIONS TEST RESULTS

ALABAMA POWER COMPANY BARRY STEAM PLANT, UNIT 5 5/19/2005

Calculations

### ATTACHMENT 6 - Barry Report 6 Test Results

Title of Run RUN 1 RUN 2 RUN 3 Date Month/Day/Year 6/21/20066/21/20066/21/2006 Sampling Time -Start Military 0723 0923 1108 Sampling Time -Stop Military 0847 1047 1232 Number of Ports dimensionless 14 14 14 Number of Points per Port dimensionless 3 3 3 Heat Input Million Btu per Hour 1,428 1,455 1,466 Stack Static Pressure Inches Water -11.00 -11.00 -11.00 Barometric Pressure Inches Mercury 30.18 30.18 30.18 Standard Orifice PressureDH@ Inches Water 2.378 2.378 2.378 Meter Correction Factor dimensionless 0.938 0.938 0.938 Oxygen Concentration Mole Percent O2 7.0 6.5 6.5 Carbon Dioxide Concentration Mole Percent CO2 12.0 12.5 12.5 Volume of Gas Metered Actual Cubic Feet 52.582 54.600 54.475 Volume of Water Collected Milliliters 120 129 119 Sampling Time Minutes 84 84 84 Nozzle Diameter Inches 0.240 0.240 0.240 Weight of Solids Collected Milligrams 65.9 67.5 47.0 Area of Stack Square Feet 180.0 180.0 180.0 Avg. Sqr. Root Velocity Pressure Inches Water 0.8360 0.8731 0.8702 Average Orifice Pressure(DH) Inches Water 1.6 1.7 1.7 Average Stack Temperature Degrees F 595 598 596 Average Meter Temperature Degrees F 80 86 91 Average Generation MW 143 143 143

RUN 1 RUN 2 RUN 3AVERAGE

Volume of Gas Sampled Standard Dry 48.877 50.130 49.63749.548 Cubic Feet Molecular Wt. of Stack Gas (wet)LB/LB-MOLE 28.94 28.94 29.02 28.96

Water vapor in Stack Gas Percent 10.4 10.8 10.1 10.4

Average Stack Gas Velocity Feet per second 66.9 69.9 69.5 68.8

Stack Gas Flow Rate Actual Cubic 722,369755,266751,001742,879 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 354,656369,990368,664364,436 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 317,916330,016331,280326,404 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 23,812 24,718 24,81324,448 Per Minute Particulate Concentration Grains per Standard 0.0208 0.0207 0.01460.0187 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0091 0.0091 0.00640.0082 Cubic Foot Particulate Emission Rate Pounds per Hour 56.6 58.7 41.4 52.2

Particulate Emission Rate Pounds per Million 0.040 0.040 0.028 0.036 Btu (Heat Input) 0.12 0.12 0.12 0.12 Isokinetic Rate Percent 104.8 103.6 102.2 103.5

Post Test Meter Correction Factordimensionless 0.98 0.99 0.99 0.99

Percent Difference Allowed 5% 3.84 4.91 5.40 4.72 Calculations TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 1

### ATTACHMENT 7 - Barry Report 7 Test Results

Title of Run RUN 1 RUN 2 RUN 3 Date Month/Day/Year 8/21/20068/21/20068/21/2006 Sampling Time -Start Military 0852 1025 1152 Sampling Time -Stop Military 0952 1125 1252 Number of Ports dimensionless 5 5 5 Number of Points per Port dimensionless 6 6 6 Heat Input Million Btu per Hour 1,450 1,451 1,451 Stack Static Pressure Inches Water -7.50 -7.50 -7.50 Barometric Pressure Inches Mercury 30.05 30.05 30.05 Standard Orifice PressureDH@ Inches Water 2.020 2.020 2.020 Meter Correction Factor dimensionless 0.974 0.974 0.974 Oxygen Concentration Mole Percent O2 4.0 3.5 3.5 Carbon Dioxide Concentration Mole Percent CO2 12.5 14.0 14.5 Volume of Gas Metered Actual Cubic Feet 36.150 36.655 37.810 Volume of Water Collected Milliliters 96 100 99 Sampling Time Minutes 60 60 60 Nozzle Diameter Inches 0.252 0.252 0.252 Weight of Solids Collected Milligrams 50.7 36.8 33.1 Area of Stack Square Feet 180.000180.000180.000 Avg. Sqr. Root Velocity PressureInches Water 0.7589 0.8012 0.7859 Average Orifice Pressure(DH) Inches Water 1.4 1.5 1.5 Average Stack Temperature Degrees F 576 577 577 Average Meter Temperature Degrees F 91 98 102 Average Generation MW 145 145 145

RUN 1 RUN 2 RUN 3Average

Volume of Gas Sampled Standard Dry 34.013 34.074 34.89234.327 Cubic Feet Molecular Wt. of Stack Gas (wet)LB/LB-MOLE 28.73 28.88 28.9928.87

Water vapor in Stack Gas Percent 11.7 12.1 11.8 11.9

Average Stack Gas Velocity Feet per second 60.2 63.5 62.1 61.9

Stack Gas Flow Rate Actual Cubic 650,565685,362671,119669,015 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 326,844344,027336,769335,880 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 288,514302,271297,092295,959 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 21,610 22,640 22,25222,167 Per Minute Particulate Concentration Grains per Standard 0.0230 0.0166 0.01460.0181 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0102 0.0073 0.00650.0080 Cubic Foot Particulate Emission Rate Pounds per Hour 56.8 43.1 37.2 45.7

Particulate Emission Rate Pounds per Million 0.039 0.030 0.0260.031 Allowable Btu (Heat Input) 0.12 0.12 0.120.12 Isokinetic Rate Percent 102.1 97.6 101.7100.5



### TABLE I. PARTICULATE EMISSIONS TEST RESULTS

ALABAMA POWER COMPANY BARRY STEAM PLANT, UNIT 2 8/21/2006

Calculations

### ATTACHMENT 8 - Barry Report 8 Test Results

Title of Run RUN 1ARUN 2ARUN 3A RUN 1BRUN 2BRUN 3B Date Month/Day/Year 7/25/20067/25/20067/25/2006 7/25/20067/25/20067/25/2006 Sampling Time -Start Military 0915 1052 1222 0915 1052 1222 Sampling Time -Stop Military 1015 1152 1322 1015 1152 1322 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 2,488 2,479 2,488 2,488 2,479 2,488 Stack Static Pressure Inches Water -10.00 -10.00 -10.00 -10.00 -10.00 -10.00 Barometric Pressure Inches Mercury 29.95 29.95 29.95 29.95 29.95 29.95 Standard Orifice PressureDH@ Inches Water 1.882 1.882 1.882 2.087 2.087 2.087 Meter Correction Factor dimensionless 0.995 0.995 0.995 0.966 0.966 0.966 Oxygen Concentration Mole Percent O2 4 5 4.5 5 6 5.25 Carbon Dioxide Concentration Mole Percent CO2 15 15 15 15 15 15 Volume of Gas Metered Actual Cubic Feet 41.599 42.464 42.796 43.600 43.350 43.484 Volume of Water Collected Milliliters 98.00 88.00 74.00 95.00 84.00 100.00 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.265 0.265 0.265 0.265 0.265 0.265 Weight of Solids Collected Milligrams 34.8 23.8 17.2 19.9 25.4 11.2 Area of Stack Square Feet 174.500174.500174.500 174.500174.500174.500 Avg. Sqr. Root Velocity Pressure Inches Water 0.8283 0.8423 0.8453 0.8241 0.8151 0.8362 Average Orifice Pressure(DH) Inches Water 1.650 1.678 1.740 1.924 1.878 1.955 Average Stack Temperature Degrees F 595 603 606 608 611 612 Average Meter Temperature Degrees F 83 88 93 97 104 108 Average Generation MW 254 253 253 254 253 253

RUN 1ARUN 2ARUN 3AAVERAGERUN 1BRUN 2BRUN 3BAVERAGE

Volume of Gas Sampled Standard Dry 40.440 40.912 40.89940.750 40.137 39.419 39.29339.616 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.56 30.60 30.5830.580 30.60 30.64 30.6130.617

Water vapor in Stack Gas Percent 10.2 9.2 7.89.094 10.0 9.1 10.79.946

Average Stack Gas Velocity Feet per second 66.1 67.2 67.466.891 66.0 65.2 67.266.169

Stack Gas Flow Rate Actual Cubic 691,675703,780705,606700,353691,416683,072703,870692,786 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 337,836341,364341,190340,130333,765328,854338,455333,691 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 303,245309,980314,413309,213300,308298,875302,248300,477 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 22,713 23,217 23,55023,160 22,493 22,386 22,63822,506 Per Minute Particulate Concentration Grains per Standard 0.0133 0.0090 0.00650.010 0.0076 0.0099 0.00440.007 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0058 0.0039 0.00290.004 0.0033 0.0043 0.00190.003 Cubic Foot Particulate Emission Rate Pounds per Hour 34.4 23.8 17.525.234 19.7 25.4 11.418.816

Particulate Emission Rate Pounds per Million 0.0138 0.0096 0.00700.010 0.0079 0.0103 0.00460.008 Btu (Heat Input) Combined Particulate Emission RatePounds per Million 0.0217 0.0199 0.01160.0177 Allowable Particulate Emission RateBtu (Heat Input) 0.12 0.12 0.12 0.12 Isokinetic Rate Percent 101.2 100.2 98.8 100.1 101.5 100.1 98.7 100.1

Post Test Meter Correction Factor dimensionless 0.999 0.990 1.0050.998 0.989 0.988 1.0090.995

Percent Difference Allowed 5% 0.4 -0.5 1.0 0.3 2.3 2.2 4.3 2.9 Calculations TABLE I. SUMMARY OF PARTICULATE EMISSIONS TEST RESULTS

ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 3 Tuesday, July 25, 2006

### ATTACHMENT 9 - Barry Report 9 Test Results

Side A Side A Side A Side B Side B Side B

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 4/27/20064/27/20064/27/2006 4/27/20064/27/20064/27/2006 Sampling Time -Start Military 1006 1146 1312 1006 1146 1312 Sampling Time -Stop Military 1106 1246 1412 1106 1246 1412 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 3,198 3,214 3,270 3,198 3,214 3,270 Stack Static Pressure Inches Water 1.50 1.50 1.50 1.50 1.50 1.50 Barometric Pressure Inches Mercury 30.40 30.40 30.40 30.30 30.30 30.30 Standard Orifice PressureDH@ Inches Water 1.960 1.960 1.960 2.311 2.311 2.311 Meter Correction Factor dimensionless 1.011 1.011 1.011 0.978 0.978 0.978 Oxygen Concentration Mole Percent O2 6 6 6 6 5.5 5.5 Carbon Dioxide Concentration Mole Percent CO2 14 13 13 11 13 13 Volume of Gas Metered Actual Cubic Feet 38.220 40.940 41.940 44.585 42.445 42.650 Volume of Water Collected Milliliters 68 82 70 79 73 75 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.237 0.237 0.237 0.237 0.237 0.237 Weight of Solids Collected Milligrams 26.50 20.20 26.90 48.50 32.10 35.10 Area of Stack Square Feet 183.75 183.75 183.75 183.75 183.75 183.75 Avg. Sqr. Root Velocity Pressure Inches Water 0.7627 0.8635 0.8559 0.9485 0.8955 0.9447 Average Orifice Pressure(DH) Inches Water 1.6 2.1 2.5 2.7 2.5 2.3 Average Stack Temperature Degrees F 289 295 300 289 291 295 Average Meter Temperature Degrees F 66 70 73 68 68 73 Average Generation MW 376 375 376 376 375 376

Side A Side A Side A Side B Side B Side B RUN 1 RUN 2 RUN 3Average RUN 1 RUN 2 RUN 3Average

Volume of Gas Sampled Standard Dry 39.581 42.120 42.94141.547 44.494 42.269 42.06342.942 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 29.55 29.29 29.4429.42 29.07 29.38 29.3529.27

Water vapor in Stack Gas Percent 7.5 8.4 7.1 7.7 7.7 7.5 7.7 7.7

Average Stack Gas Velocity Feet per second 49.9 57.0 56.5 54.5 62.7 59.0 62.4 61.3

Stack Gas Flow Rate Actual Cubic 550,416628,321623,183600,640691,190650,034687,805676,343 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 395,417447,914441,348428,226494,920464,211488,734482,622 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 365,833410,315409,896395,348456,748429,312450,892445,650 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 27,401 30,733 30,70129,612 34,210 32,155 33,77233,379 Per Minute Particulate Concentration Grains per Standard 0.0103 0.0074 0.00960.0091 0.0168 0.0117 0.01290.0138 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0069 0.0048 0.00630.0060 0.0111 0.0077 0.00840.0091 Cubic Foot Particulate Emission Rate Pounds per Hour 32.3 26.0 33.9 30.7 65.7 43.0 49.7 52.8

Particulate Emission Rate Pounds per Million 0.010 0.008 0.0100.010 0.021 0.013 0.0150.016 Btu (Heat Input) Isokinetic Rate Percent 108.1 102.6 104.7105.1 97.4 98.4 93.2 96.3

Combined Particulate Emission RatePounds per Million 0.031 0.021 0.0260.026 Allowable Particulate Emission RateBtu (Heat Input) 0.12 0.12 0.12 0.12 Calculations TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 4

### ATTACHMENT 10 - Barry Report 10 Test Results

Side ASide ASide A Side B Side B Side B

Title of Run RUN 1 RUN 2 RUN 3 RUN 4 RUN 5 RUN 6 Date Month/Day/Year 6/6/20066/6/20066/6/2006 6/6/20066/6/20066/6/2006 Sampling Time -Start Military 0828 1000 1121 0828 1000 1121 Sampling Time -Stop Military 0938 1110 1229 0094 1109 1229 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 7,003 7,003 7,003 7,003 7,003 7,003 Stack Static Pressure Inches Water -0.70 -0.70 -0.70 -0.70 -0.70 -0.70 Barometric Pressure Inches Mercury 30.15 30.15 30.15 30.15 30.15 30.15 Standard Orifice PressureDH@ Inches Water 1.960 1.960 1.960 2.084 2.084 2.084 Meter Correction Factor dimensionless 1.011 1.011 1.011 0.957 0.957 0.957 Oxygen Concentration Mole Percent O2 6 5.5 5.5 6.5 6 6 Carbon Dioxide Concentration Mole Percent CO2 12 12 12 12 12 12 Volume of Gas Metered Actual Cubic Feet 37.52538.80536.010 39.10046.35040.900 Volume of Water Collected Milliliters 72 76 86 69 78 74 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.215 0.215 0.210 0.210 0.215 0.208 Weight of Solids Collected Milligrams 13.1 21.0 41.5 31.0 30.7 29.2 Area of Stack Square Feet 287.500287.500287.500 287.500287.500287.500 Avg. Sqr. Root Velocity Pressure Inches Water 1.08131.06071.0504 1.05651.12981.0873 Average Orifice Pressure(DH) Inches Water 1.8 1.7 1.6 1.6 2.0 1.6 Average Stack Temperature Degrees F 329 332 334 320 318 315 Average Meter Temperature Degrees F 75 83 85 82 88 94 Average Generation MW 774 774 774 774 774 774

TOTAL Side ASide ASide ASide A Side B Side B Side B Side B UNIT RUN 1 RUN 2 RUN 3AVERAGE RUN 4 RUN 5 RUN 6AVERAGEAVERAGE

Volume of Gas Sampled Standard Dry 37.91638.59235.70137.40336.88243.32837.78439.33138.387 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.16 30.14 30.14 30.15 30.18 30.16 30.16 30.17 30.16

Water vapor in Stack Gas Percent 8.2 8.5 10.2 9.0 8.1 7.8 8.4 8.1 8.5

Average Stack Gas Velocity Feet per second 73.4 72.2 71.8 72.4 71.3 76.1 73.1 73.5 73.0

Stack Gas Flow Rate Actual Cubic 1,265,4561,244,9311,238,0821,249,4901,229,1491,312,7031,261,6341,267,8292,517,318 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 852,190834,978828,083838,417836,799895,712865,054865,8551,704,272 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 782,268764,145743,751763,388769,075825,741792,038795,6181,559,006 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 58,59257,23455,70757,17857,60461,84859,32459,59258,410 Per Minute Particulate Concentration Grains per Standard 0.00530.00840.01790.01050.01290.01090.01190.01190.0112 Dry Cubic Foot Particulate Concentration Grains per Actual 0.00330.00510.01080.00640.00810.00690.00750.00750.0069 Cubic Foot Particulate Emission Rate Pounds per Hour 35.7 54.9 114.1 68.2 85.3 77.2 80.8 81.1 149

Particulate Emission Rate Pounds per Million 0.005 0.008 0.016 0.010 0.012 0.011 0.012 0.012 0.021 Btu (Heat Input) Isokinetic Rate Percent 92.1 96.0 95.6 94.6 95.5 99.7 96.9 97.4 96.0

Combined Particulate Emission RatePounds per Million 0.017 0.019 0.028 0.021 Allowable Btu (Heat Input) 0.12 0.12 0.12 0.12 TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 5

Calculations

### ATTACHMENT 11 - Barry Report 11 Test Results

Title of Run RUN 1 RUN 2 RUN 3 Date Month/Day/Year 5/22/20075/22/20075/22/2007 Sampling Time -Start Military 0730 0927 1115 Sampling Time -Stop Military 0854 1051 1239 Number of Ports dimensionless 14 14 14 Number of Points per Port dimensionless 3 3 3 Heat Input Million Btu per Hour 1,411 1,408 1,424 Stack Static Pressure Inches Water -9.00 -9.00 -9.00 Barometric Pressure Inches Mercury 30.05 30.05 30.05 Standard Orifice PressureDH@ Inches Water 2.418 2.418 2.418 Meter Correction Factor dimensionless 0.939 0.939 0.939 Oxygen Concentration Mole Percent O2 4.0 4.5 5.0 Carbon Dioxide Concentration Mole Percent CO2 15.5 15.5 15.0 Volume of Gas Metered Actual Cubic Feet 51.150 49.900 49.800 Volume of Water Collected Milliliters 112 118 107 Sampling Time Minutes 84 84 84 Nozzle Diameter Inches 0.236 0.236 0.236 Weight of Solids Collected Milligrams 113.0 85.3 83.8 Area of Stack Square Feet 180.000180.000180.000 Avg. Sqr. Root Velocity Pressure Inches Water 0.8702 0.8483 0.8492 Average Orifice Pressure(DH) Inches Water 1.5 1.4 1.4 Average Stack Temperature Degrees F 590 595 591 Average Meter Temperature Degrees F 75 84 89 Average Generation MW 143 143 143

RUN 1 RUN 2 RUN 3Average

Volume of Gas Sampled Standard Dry 47.763 45.887 45.32146.323 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.64 30.66 30.6030.63

Water vapor in Stack Gas Percent 9.9 10.8 10.0 10.2

Average Stack Gas Velocity Feet per second 68.9 67.4 67.3 67.9

Stack Gas Flow Rate Actual Cubic 744,136728,363726,912733,137 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 367,404357,783358,705361,297 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 330,883319,152322,829324,288 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 24,783 23,904 24,18024,289 Per Minute Particulate Concentration Grains per Standard 0.036 0.029 0.0280.031 Dry Cubic Foot Particulate Concentration Grains per Actual 0.016 0.013 0.0130.014 Cubic Foot Particulate Emission Rate Pounds per Hour 103.3 78.3 78.8 86.8

Particulate Emission Rate Pounds per Million 0.073 0.056 0.0550.061 Allowable Btu (Heat Input) 0.12 0.12 0.120.12 Isokinetic Rate Percent 101.8 101.4 99.0100.7

Post Test Meter Correction Factordimensionless 0.95 0.95 0.96 0.95

Percent Difference Allowed 5% 0.8 1.4 1.9 1.3

TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 1

CalculationsATTACHMENT 12 - Barry Report 12 Test Results

Title of Run RUN 1 RUN 2 RUN 3
Date Month/Day/Year 5/22/20075/22/20075/22/2007 Sampling Time -Start Military 0722 0858 1023 Sampling Time -Stop Military 0822 0958 1123 Number of Ports dimensionless 5 5 5 Number of Points per Port dimensionless 6 6 6 Heat Input Million Btu per Hour 1,419 1,408 1,424 Stack Static Pressure Inches Water -7.50 -7.50 -7.50 Barometric Pressure Inches Mercury 30.05 30.05 30.05 Standard Orifice PressureDH@ Inches Water 1.939 1.939 1.939 Meter Correction Factor dimensionless 0.981 0.981 0.981 Oxygen Concentration Mole Percent O2 5.0 4.0 3.5 Carbon Dioxide Concentration Mole Percent CO2 14.5 14.0 13.0 Volume of Gas Metered Actual Cubic Feet 37.615 33.800 33.243 Volume of Water Collected Milliliters 129 78 124 Sampling Time Minutes 60 60 60 Nozzle Diameter Inches 0.254 0.254 0.254 Weight of Solids Collected Milligrams 28.0 32.2 30.7 Area of Stack Square Feet 180.000180.000180.000 Avg. Sqr. Root Velocity Pressure Inches Water 0.8031 0.7475 0.7083 Average Orifice Pressure(DH) Inches Water 1.4 1.2 1.2 Average Stack Temperature Degrees F 578 579 582 Average Meter Temperature Degrees F 67 75 82 Average Generation MW 143 143 143

RUN 1 RUN 2 RUN 3Average

Volume of Gas Sampled Standard Dry 37.253 32.982 31.99134.075 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.52 30.40 30.2230.38

Water vapor in Stack Gas Percent 14.0 10.0 15.4 13.2

Average Stack Gas Velocity Feet per second 63.8 59.0 56.8 59.9

Stack Gas Flow Rate Actual Cubic 688,907637,060613,397646,455 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 345,295319,134306,248323,559 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 296,902287,168258,995281,022 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 22,238 21,509 19,39921,049 Per Minute Particulate Concentration Grains per Standard 0.012 0.015 0.0150.014 Dry Cubic Foot Particulate Concentration Grains per Actual 0.005 0.007 0.0060.006 Cubic Foot Particulate Emission Rate Pounds per Hour 29.5 37.0 32.8 33.1

Particulate Emission Rate Pounds per Million 0.021 0.026 0.0230.023 Allowable Btu (Heat Input) 0.12 0.12 0.120.12 Isokinetic Rate Percent 107.0 97.9 105.3103.4

Post Test Meter Correction Factor dimensionless 0.99 1.03 1.05 1.02

Percent Difference Allowed 5% 0.9 4.7 6.6 4.1

TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 2

Calculations

### ATTACHMENT 13 - Barry Report 13 Test Results

Side A Side A Side A Side B Side B Side B

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 5/23/20075/23/20075/23/2007 5/23/20075/23/20075/23/2007 Sampling Time -Start Military 0735 0919 1102 0735 0919 1102 Sampling Time -Stop Military 0835 1019 1202 0835 1019 1202 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 2,526 2,526 2,548 2,526 2,526 2,548 Stack Static Pressure Inches Water -10.00 -10.00 -10.00 -10.00 -10.00 -10.00 Barometric Pressure Inches Mercury 30.15 30.15 30.15 30.15 30.15 30.15 Standard Orifice PressureDH@ Inches Water 2.418 2.418 2.418 1.939 1.939 1.939 Meter Correction Factor dimensionless 0.939 0.939 0.939 0.981 0.981 0.981 Oxygen Concentration Mole Percent O2 4.0 4.5 5.0 4.0 4.5 4.0 Carbon Dioxide Concentration Mole Percent CO2 15.0 15.0 14.0 13.0 13.0 14.0 Volume of Gas Metered Actual Cubic Feet 44.914 43.924 45.122 41.417 41.875 42.143 Volume of Water Collected Milliliters 103 102 105 83 92 91 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.274 0.274 0.274 0.274 0.274 0.274 Weight of Solids Collected Milligrams 47.9 42.7 25.2 45.0 56.0 56.1 Area of Stack Square Feet 174.500174.500174.500 174.500174.500174.500 Avg. Sqr. Root Velocity Pressure Inches Water 0.8067 0.8050 0.8186 0.7848 0.7944 0.8046 Average Orifice Pressure(DH) Inches Water 2.3 2.2 2.3 1.7 1.7 1.8 Average Stack Temperature Degrees F 612 616 620 626 627 631 Average Meter Temperature Degrees F 81 85 89 74 79 84 Average Generation MW 253 253 253 253 253 253

Side A Side A Side ASide A Side B Side B Side BSide B Combined RUN 1 RUN 2 RUN 3Average RUN 1 RUN 2 RUN 3AverageAverage/Total

Volume of Gas Sampled Standard Dry 41.729 40.471 41.30741.169 40.674 40.724 40.62440.674 40.922 Cubic Feet Molecular Wt. of Stack Gas (dry)LB/LB-MOLE 30.56 30.58 30.4430.53 30.24 30.26 30.4030.30 30.413

Water vapor in Stack Gas Percent 10.4 10.6 10.7 10.6 8.8 9.6 9.5 9.3 9.936

Average Stack Gas Velocity Feet per second 64.7 64.7 66.0 65.1 63.4 64.3 65.1 64.3 64.686

Stack Gas Flow Rate Actual Cubic 676,887676,958691,116681,654663,779673,244681,599672,874 1,354,528 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 327,648326,342332,046328,679317,199321,327324,092320,872 649,551 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 293,543291,733296,563293,946289,401290,442293,180291,007 584,954 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 21,986 21,851 22,21322,017 21,676 21,754 21,95921,796 43,813 Per Minute Particulate Concentration Grains per Standard 0.018 0.016 0.0090.014 0.017 0.021 0.0210.020 0.017 Dry Cubic Foot Particulate Concentration Grains per Actual 0.008 0.007 0.0040.006 0.007 0.009 0.0090.009 0.007 Cubic Foot Particulate Emission Rate Pounds per Hour 44.5 40.6 23.9 36.3 42.3 52.7 53.449.5 85.8

Particulate Emission Rate Pounds per Million 0.018 0.016 0.0090.014 0.017 0.021 0.0210.020 0.034 Allowable Btu (Heat Input) 0.12 0.12 0.120.12 0.12 0.12 0.120.12 0.12 Isokinetic Rate Percent 100.9 98.5 98.9 99.5 99.8 99.6 98.499.3 99.4

Post Test Meter Correction Factordimensionless 0.95 0.97 0.97 0.96 1.01 1.00 1.01 1.01 0.98

Percent Difference Allowed 5% 0.8 3.1 3.1 2.3 2.9 2.1 2.9 2.6 2.5 TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 3

Calculations

### ATTACHMENT 14 - Barry Report 14 Test Results

Side A Side A Side A Side B Side B Side B

Title of Run RUN 1 RUN 2 RUN 3 RUN 4 RUN 5 RUN 6 Date Month/Day/Year 2/22/20072/22/20072/22/20072/22/20072/22/20072/22/2007 Sampling Time -Start Military 1210 1340 1502 1210 1340 1502 Sampling Time -Stop Military 1312 1440 1602 1310 1440 1602 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 3,195 3,213 3,230 3,195 3,213 3,230 Stack Static Pressure Inches Water 1.50 1.50 1.50 1.50 1.50 1.50 Barometric Pressure Inches Mercury 30.16 30.16 30.16 30.16 30.16 30.16 Standard Orifice PressureDH@ Inches Water 2.418 2.418 2.418 1.939 1.939 1.939 Meter Correction Factor dimensionless 0.939 0.939 0.939 0.981 0.981 0.981 Oxygen Concentration Mole Percent O2 5.3 5.0 5.0 4.0 4.5 4.0 Carbon Dioxide Concentration Mole Percent CO2 13.3 14.0 13.8 14.0 14.0 14.0 Volume of Gas Metered Actual Cubic Feet 42.898 42.785 43.253 37.554 38.624 35.891 Volume of Water Collected Milliliters 68 85 75 105 63 69 Sampling Time Minutes 60 60 60 60.0 60.0 60.0 Nozzle Diameter Inches 0.236 0.234 0.237 0.232 0.236 0.235 Weight of Solids Collected Milligrams 16.5 22.8 19.7 34.7 36.3 37.9 Area of Stack Square Feet 183.750183.750183.750183.750183.750183.750 Avg. Sqr. Root Velocity Pressure Inches Water 0.8321 0.8502 0.8311 0.8018 0.8103 0.7511 Average Orifice Pressure(DH) Inches Water 2.3 2.2 2.2 1.5 1.6 1.4 Average Stack Temperature Degrees F 314 317 327 289 293 292 Average Meter Temperature Degrees F 79 83 85 72 78 80 Average Generation MW 376 375 375 376 375 375

Side A Side A Side A Side B Side B Side BAverageAverage RUN 1 RUN 2 RUN 3 RUN 4 RUN 5 RUN 6Side ASide B

Volume of Gas Sampled Standard Dry 40.015 39.573 39.874 37.020 37.670 34.81939.82136.503 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.33 30.44 30.40 30.40 30.42 30.4030.3930.41

Water vapor in Stack Gas Percent 7.4 9.2 8.1 11.8 7.3 8.5 8.2 9.2

Average Stack Gas Velocity Feet per second 55.7 57.1 56.1 53.2 53.4 49.6 56.3 52.1

Stack Gas Flow Rate Actual Cubic 614,136629,978618,647586,659588,643547,048620,920574,117 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 423,712432,963419,913418,567417,748388,488425,529408,268 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 392,330393,208385,760369,267387,263355,342390,433370,624 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 29,386 29,451 28,893 27,658 29,006 26,61529,24327,760 Per Minute Particulate Concentration Grains per Standard 0.006 0.009 0.008 0.014 0.015 0.0170.0080.015 Dry Cubic Foot Particulate Concentration Grains per Actual 0.004 0.006 0.005 0.009 0.010 0.0110.0050.010 Cubic Foot Particulate Emission Rate Pounds per Hour 21.4 29.9 25.2 45.7 49.3 51.1 25.5 48.7

Particulate Emission Rate Pounds per Million 0.007 0.009 0.008 0.014 0.015 0.0160.0080.015 Btu (Heat Input) Isokinetic Rate Percent 102.8 103.2 103.3 104.6 98.0 99.6103.1100.7

Post Test Meter Correction Factor dimensionless 1.00 0.99 0.99 1.02 1.04 1.03 0.99 1.03

Percent Difference Allowed (Average 5% ) 6.1 4.6 5.0 5.2 6.1 5.2 5.2 5.5

Combined Particulate Emission RatePounds per Million 0.021 0.025 0.024 0.023 Allowable Btu (Heat Input) 0.12 0.12 0.12 0.12 TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 4

Calculations

### ATTACHMENT 15 - Barry Report 15 Test Results

Side A Side A Side A Side B Side B Side B

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 5/30/20075/30/20075/30/2007 5/30/20075/30/20075/30/2007 Sampling Time -Start Military 0842 1034 1218 0842 1034 1218 Sampling Time -Stop Military 1002 1148 1332 1002 1148 1332 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 7,241 7,317 7,378 7,241 7,317 7,378 Stack Static Pressure Inches Water -1.00 -1.00 -1.00 -1.00 -1.00 -1.00 Barometric Pressure Inches Mercury 30.10 30.10 30.10 30.10 30.10 30.10 Standard Orifice PressureDH@ Inches Water 1.858 1.858 1.858 2.258 2.258 2.258 Meter Correction Factor dimensionless 0.978 0.978 0.978 0.982 0.982 0.982 Oxygen Concentration Mole Percent O2 6.5 6 5 6.0 6.0 4.5 Carbon Dioxide Concentration Mole Percent CO2 13.5 13 13 14.00 13.50 14.5 Volume of Gas Metered Actual Cubic Feet 40.245 40.620 43.115 41.206 41.895 46.176 Volume of Water Collected Milliliters 84 83 78 91 74 98 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.209 0.211 0.220 0.211 0.214 0.218 Weight of Solids Collected Milligrams 15.4 16.1 13.5 20.2 17.6 21.5 Area of Stack Square Feet 287.500287.500287.500 287.500287.500287.500 Avg. Sqr. Root Velocity Pressure Inches Water 1.0784 1.0680 1.0408 1.1244 1.1147 1.1388 Average Orifice Pressure(DH) Inches Water 1.6 1.6 1.8 2.1 2.2 2.5 Average Stack Temperature Degrees F 309 313 317 326 327 329 Average Meter Temperature Degrees F 75 78 82 71 74 76 Average Generation MW 772 772 772 772 772 772

Side A Side A Side ASide A Side B Side B Side B Side BCombined RUN 1 RUN 2 RUN 3AVERAGE RUN 1 RUN 2 RUN 3AVERAGEAVERAGE

Volume of Gas Sampled Standard Dry 39.241 39.408 41.52940.059 40.723 41.173 45.20042.36541.212 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.42 30.32 30.28 30.34 30.48 30.40 30.50 30.46 30.40

Water vapor in Stack Gas Percent 9.2 9.0 8.1 8.8 9.5 7.8 9.3 8.9 8.8

Average Stack Gas Velocity Feet per second 72.4 72.0 70.2 71.5 76.3 75.5 77.4 76.4 74.0

Stack Gas Flow Rate Actual Cubic 1,249,0641,241,6911,211,5541,234,1031,316,3351,302,4691,334,8811,317,8952,551,998 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 860,386851,137826,273845,932887,409877,167896,108886,8951,732,827 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 781,629774,367759,157771,718802,951808,748813,126808,2751,579,993 Feet Per Minute Particulate Concentration Grains per Standard 0.006 0.006 0.005 0.006 0.008 0.007 0.007 0.007 0.006 Dry Cubic Foot Particulate Concentration Grains per Actual 0.004 0.004 0.003 0.004 0.005 0.004 0.004 0.004 0.004 Cubic Foot Particulate Emission Rate Pounds per Hour 40.5 41.8 32.6 38.3 52.6 45.6 51.1 49.8 88.0

Particulate Emission Rate Pounds per Million 0.006 0.006 0.004 0.005 0.007 0.006 0.007 0.007 0.012 Btu (Heat Input) Isokinetic Rate Percent 101.0 100.4 99.3 100.2 100.1 97.6 102.7 100.1 100.2

Combined Particulate Emmision Rate 0.013 0.012 0.011 0.012 Allowable 0.12 0.12 0.12 0.12 Post Test Meter Cal Check (Yqa) dimensionless 1.00 1.01 1.01 1.01 1.03 1.04 1.01 1.02 1.01

Percent Difference Allowed 5% 2.4 2.9 3.2 2.8 4.3 5.3 2.9 4.2 3.5 TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT - UNIT 5 Wednesday, May 30, 2007

Calculations

### ATTACHMENT 16 - Barry Report 16 Test Results

Title of Run RUN 1 RUN 2 RUN 3 Date Month/Day/Year 6/19/20086/19/20086/19/2008 Sampling Time -Start Military 0755 0950 1150 Sampling Time -Stop Military 0919 1114 1314 Number of Ports dimensionless 14 14 14 Number of Points per Port dimensionless 3 3 3 Heat Input Million Btu per Hour 1,288 1,363 1,402 Stack Static Pressure Inches Water -9.50 -9.50 -9.50 Barometric Pressure Inches Mercury 29.94 29.94 29.94 Standard Orifice Pressure DH@ Inches Water 1.939 1.939 1.939 Meter Correction Factor dimensionless 0.981 0.981 0.981 Oxygen Concentration Mole Percent O2 7.0 5.5 6.0 Carbon Dioxide Concentration Mole Percent CO2 14.0 14.5 13.5 Volume of Gas Metered Actual Cubic Feet 53.472 52.704 51.953 Volume of Water Collected Milliliters 137 127 113 Sampling Time Minutes 84 84 84 Nozzle Diameter Inches 0.250 0.250 0.250 Weight of Solids Collected Milligrams 37.7 47.2 44.0 Area of Stack Square Feet 180.000180.000180.000 Avg. Sqr. Root Velocity Pressure Inches Water 0.8209 0.8242 0.8151 Average Orifice Pressure (DH) Inches Water 1.4 1.4 1.4 Average Stack Temperature Degrees F 587 590 592 Average Meter Temperature Degrees F 76 82 88 Average Generation MW 144 144 144

RUN 1 RUN 2 RUN 3AVERAGE

Volume of Gas Sampled Standard Dry 51.939 50.557 49.30750.601 Cubic Feet Molecular Wt. of Stack Gas (dry)LB/LB-MOLE 30.52 30.54 30.40 30.49

Water vapor in Stack Gas Percent 11.0 10.6 9.7 10.5

Average Stack Gas Velocity Feet per second 65.3 65.6 65.0 65.3

Stack Gas Flow Rate Actual Cubic 705,710708,664701,840705,405 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 347,662348,065344,026346,584 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 309,264311,261310,529310,351 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 23,164 23,313 23,25923,245 Per Minute Particulate Concentration Grains per Standard 0.011 0.014 0.0140.013 Dry Cubic Foot Particulate Concentration Grains per Actual 0.005 0.006 0.006 0.006 Cubic Foot Particulate Emission Rate Pounds per Hour 29.63 38.36 36.58 34.86

Particulate Emission Rate Pounds per Million 0.023 0.028 0.026 0.026 Allowable Btu (Heat Input) 0.12 0.12 0.12 0.12 Isokinetic Rate Percent 105.6 102.1 99.8 102.5

Post Test Meter Correction Checkdimensionless 0.98 0.99 1.01 0.99

Percent Difference Allowed 5% Average 0.1 1.0 2.4 1.2

TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 1

Calculations

### ATTACHMENT 17 - Barry Report 17 Test Results

Title of Run RUN 1 RUN 2 RUN 3 Date Month/Day/Year 5/21/20085/21/20085/21/2008 Sampling Time -Start Military 0840 1045 1222 Sampling Time -Stop Military 1012 1145 1322 Number of Ports dimensionless 5 5 5 Number of Points per Port dimensionless 6 6 6 Heat Input Million Btu per Hour 1,621 1,716 1,712 Stack Static Pressure Inches Water -7.30 -7.30 -7.30 Barometric Pressure Inches Mercury 29.92 29.92 29.92 Standard Orifice Pressure DH@ Inches Water 2.040 2.040 2.040 Meter Correction Factor dimensionless 0.975 0.975 0.975 Oxygen Concentration Mole Percent O2 7.0 6.5 5.5 Carbon Dioxide Concentration Mole Percent CO2 14.0 15.0 16.0 Volume of Gas Metered Actual Cubic Feet 41.967 41.296 42.715 Volume of Water Collected Milliliters 95.9 91.6 101.0 Sampling Time Minutes 60 60 60 Nozzle Diameter Inches 0.263 0.263 0.263 Weight of Solids Collected Milligrams 16.7 25.8 16.7 Area of Stack Square Feet 180.000180.000180.000 Avg. Sqr. Root Velocity Pressure Inches Water 0.8270 0.8360 0.8373 Average Orifice Pressure(DH) Inches Water 1.8 1.8 1.8 Average Stack Temperature Degrees F 599 601 604 Average Meter Temperature Degrees F 78 82 87 Averager Generation MW 145 145 145

RUN 1 RUN 2 RUN 3AVERAGE

Volume of Gas Sampled Standard Dry 40.357 39.382 40.36740.035 Cubic Feet Molecular Wt. of Stack Gas (dry)LB/LB-MOLE 30.52 30.66 30.78 30.65

Water vapor in Stack Gas Percent 10.1 9.9 10.5 10.2

Average Stack Gas Velocity Feet per second 65.9 66.5 66.7 66.4

Stack Gas Flow Rate Actual Cubic 711,615718,182720,359716,719 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 348,402350,998350,794350,065 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 313,353316,362313,833314,516 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 23,470 23,696 23,50623,557 Per Minute Particulate Concentration Grains per Standard 0.0064 0.0101 0.00640.0076 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0028 0.0044 0.00280.0033 Cubic Foot Particulate Emission Rate Pounds per Hour 17.1 27.4 17.1 20.5

Particulate Emission Rate Pounds per Million 0.011 0.016 0.010 0.012 Allowable Btu (Heat Input) 0.12 0.12 0.12 0.12 Isokinetic Rate Percent 102.4 99.0 102.3

Post Test Meter Correction Checkdimensionless 0.978 1.001 0.976 0.985

Percent Difference Allowed 5% Average 0.3 2.6 0.1 1.0

TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 2

Calculations

### ATTACHMENT 18 - Barry Report 18 Test Results

SIDE A SIDE A SIDE A SIDE B SIDE B SIDE B

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 5/22/20085/22/20085/22/20085/22/20085/22/20085/22/2008 Sampling Time -Start Military 0745 0916 1038 0745 0916 1038 Sampling Time -Stop Military 0845 1016 1138 0845 1016 1138 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 2,730 2,770 2,795 2,730 2,770 2,795 Stack Static Pressure Inches Water -10.00 -10.00 -10.00 -10.00 -10.00 -10.00 Barometric Pressure Inches Mercury 29.74 29.74 29.74 29.74 29.74 29.74 Standard Orifice Pressure DH@ Inches Water 2.040 2.040 2.040 2.139 2.139 2.139 Meter Correction Factor dimensionless 0.975 0.975 0.975 0.988 0.988 0.988 Oxygen Concentration Mole Percent O2 5.5 5.0 3.5 5.0 4.5 3.5 Carbon Dioxide Concentration Mole Percent CO2 15.0 14.0 14.5 15.0 14.5 14.0 Volume of Gas Metered Actual Cubic Feet 45.413 45.292 46.276 48.855 43.920 45.870 Volume of Water Collected Milliliters 108.7 110.4 129.5 92.2 97.2 122.2 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.275 0.275 0.275 0.275 0.275 0.275 Weight of Solids Collected Milligrams 10.9 15.4 42.2 11.4 15.8 18.0 Area of Stack Square Feet 174.500174.500174.500174.500174.500174.500 Avg. Sqr. Root Velocity PressureInches Water 0.8420 0.8508 0.8583 0.8404 0.8337 0.8647 Average Orifice Pressure (DH) Inches Water 2.1 2.1 2.1 2.2 2.1 2.2 Average Stack Temperature Degrees F 607 607 611 606 608 611 Average Meter Temperature Degrees F 77 81 85 78 83 88 Average Generation MW 258 257 258 258 257 258 Flowrate Side ASide BWeighted 3 Runs3 RunsTOTAL or RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3AVERAGEAVERAGEAVERAGE

Volume of Gas Sampled Standard Dry 43.522 43.069 43.669 47.308 42.146 43.64943.42044.36887.788 Cubic Feet Molecular Wt. of Stack Gas (dry)LB/LB-MOLE 30.62 30.44 30.46 30.60 30.50 30.3830.51 30.49 30.50

Water vapor in Stack Gas Percent 10.5 10.8 12.2 8.4 9.8 11.6 11.2 9.9 10.6

Average Stack Gas Velocity Feet per second 67.7 68.7 69.6 67.3 67.1 70.1 68.7 68.2 68.4

Stack Gas Flow Rate Actual Cubic 709,309718,971728,895704,527702,747734,331719,058713,8691,432,926 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 340,217344,937348,240338,283336,828350,794344,465341,968686,433 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 304,428307,800305,585309,858303,843309,949305,938307,883613,821 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 22,802 23,054 22,888 23,208 22,758 23,21522,91523,06045,975 Per Minute Particulate Concentration Grains per Standard 0.004 0.006 0.015 0.004 0.006 0.0060.0080.005 0.007 Dry Cubic Foot Particulate Concentration Grains per Actual 0.002 0.002 0.006 0.002 0.002 0.0030.0030.002 0.003 Cubic Foot Particulate Emission Rate Pounds per Hour 10.1 14.5 39.0 9.9 15.0 16.9 21.2 13.9 35.1

Particulate Emission Rate Pounds per Million 0.004 0.005 0.014 0.004 0.005 0.0060.0080.005 0.013 Allowable Btu (Heat Input) 0.12 0.12 0.12 0.12 0.12 0.12 0.12 0.12 0.12 Isokinetic Rate Percent 100.8 98.6 100.7 107.6 97.8 99.3 100.1 101.6

Post Test Meter Correction Checkdimensionless 0.98 1.00 0.99 0.91 1.00 0.99 0.99 0.97

Percent Difference Allowed 5% Average 0.3 2.5 1.4 -7.6 1.0 0.0 1.4 -2.2 TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 3

Calculations

### ATTACHMENT 19 - Barry Report 19 Test Results

SIDE ASIDE ASIDE ASIDE BSIDE BSIDE B

Title of Run RUN 1RUN 2RUN 3RUN 1RUN 2RUN 3 Date Month/Day/Year 4/9/20084/9/20084/9/20084/9/20084/9/20084/9/2008 Sampling Time -Start Military 0813 0948 1121 0813 0948 1121 Sampling Time -Stop Military 0919 1055 1226 0919 1055 1226 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 3,180 3,178 3,246 3,180 3,178 3,246 Stack Static Pressure Inches Water 1.50 1.50 1.50 1.50 1.50 1.50 Barometric Pressure Inches Mercury 30.10 30.10 30.10 30.10 30.10 30.10 Standard Orifice Pressure DH@ Inches Water 2.258 2.258 2.258 1.858 1.858 1.858 Meter Correction Factor dimensionless 0.982 0.982 0.982 0.978 0.978 0.978 Oxygen Concentration Mole Percent O2 6.0 6.0 5.5 5.0 5.5 4.0 Carbon Dioxide Concentration Mole Percent CO2 13.5 13.5 14.0 14.0 14.0 15.0 Volume of Gas Metered Actual Cubic Feet 41.04039.13839.77545.09544.10041.905 Volume of Water Collected Milliliters 81 83 83 89 96 89 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.242 0.236 0.233 0.246 0.245 0.240 Weight of Solids Collected Milligrams 23.2 19.9 21.3 22.1 23.6 21.9 Area of Stack Square Feet 183.750183.750183.750183.750183.750183.750 Avg. Sqr. Root Velocity Pressure Inches Water 0.87270.85350.88910.87210.88110.8512 Average Orifice Pressure (DH) Inches Water 2.5 2.2 2.3 2.1 2.0 1.8 Average Stack Temperature Degrees F 287 294 297 303 299 296 Average Meter Temperature Degrees F 65 72 75 66 70 72 Average Generation MW 376 376 376 376 376 376

SIDE ASIDE B RUN 1RUN 2RUN 3RUN 1RUN 2RUN 3AVERAGEAVERAGE

Volume of Gas Sampled Standard Dry 41.00038.61639.01644.74943.47441.12239.54443.115 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.40 30.40 30.46 30.44 30.46 30.56 30.42 30.49

Water vapor in Stack Gas Percent 8.5 9.2 9.1 8.6 9.4 9.2 8.9 9.1

Average Stack Gas Velocity Feet per second 57.5 56.6 59.0 58.1 58.6 56.4 57.7 57.7

Stack Gas Flow Rate Actual Cubic 633,918623,799650,581640,020645,881621,658636,099635,853 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 452,598441,195457,989447,245453,721438,304450,594446,423 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 414,091400,660416,303408,960411,001397,780410,351405,914 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 31,01530,00931,18130,63130,78429,79430,73530,403 Per Minute Particulate Concentration Grains per Standard 0.009 0.008 0.008 0.008 0.008 0.008 0.008 0.008 Dry Cubic Foot Particulate Concentration Grains per Actual 0.006 0.005 0.005 0.005 0.005 0.005 0.005 0.005 Cubic Foot Particulate Emission Rate Pounds per Hour 30.9 27.3 30.0 26.7 29.5 28.0 29.4 28.0

Particulate Emission Rate Pounds per Million 0.010 0.009 0.009 0.008 0.009 0.009 0.009 0.009 Btu (Heat Input) Isokinetic Rate Percent 94.9 97.1 96.9 101.5 98.9 100.8 96.3 100.4

Combined Particulate Emission RatePounds per Million 0.018 0.018 0.018 0.018 Allowable Btu (Heat Input) 0.12 0.12 0.12 0.12 TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 4

Calculations

### ATTACHMENT 20 - Barry Report 20 Test Results

Title of Run RUN 1 RUN 2 RUN 3 Date Month/Day/Year 5/20/20085/20/20085/20/2008 Sampling Time -Start Military 0900 1036 1205 Sampling Time -Stop Military 1020 1150 1314 Number of Ports dimensionless 6 6 6 Number of Points per Port dimensionless 5 5 5 Heat Input Million Btu per Hour 8,144 8,047 7,955 Stack Static Pressure Inches Water 0.50 0.50 0.50 Barometric Pressure Inches Mercury 30.10 30.10 30.10 Standard Orifice Pressure DH@ Inches Water 2.040 2.040 2.040 Meter Correction Factor dimensionless 0.975 0.975 0.975 Oxygen Concentration Mole Percent O2 8.00 7.50 7.50 Carbon Dioxide Concentration Mole Percent CO2 13.0 13.0 13.0 Volume of Gas Metered Actual Cubic Feet 50.925 44.000 42.910 Volume of Water Collected Milliliters 90.2 75.3 79.5 Sampling Time Minutes 60 60 60 Nozzle Diameter Inches 0.276 0.247 0.245 Weight of Solids Collected Milligrams 30.3 30.9 33.0 Area of Stack Square Feet 886.875886.875886.875 Avg. Sqr. Root Velocity Pressure Inches Water 0.7809 0.8273 0.8366 Average Orifice Pressure (DH) Inches Water 2.8 2.0 2.0 Average Stack Temperature Degrees F 327 333 335 Average Meter Temperature Degrees F 81 87 93 Average Generation MW 773 773 773

RUN 1 RUN 2 RUN 3AVERAGE

Volume of Gas Sampled Standard Dry 49.050 41.875 40.39443.773 Cubic Feet Molecular Wt. of Stack Gas (dry)LB/LB-MOLE 30.40 30.38 30.38 30.39

Water vapor in Stack Gas Percent 8.0 7.8 8.5 8.1

Average Stack Gas Velocity Feet per second 52.8 56.2 57.0 55.3

Stack Gas Flow Rate Actual Cubic 2,811,8362,988,8943,031,6912,944,140 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 1,898,8582,004,6722,027,0671,976,866 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 1,747,5901,848,2331,855,2021,817,008 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 130,894138,433138,955136,094 Per Minute Particulate Concentration Grains per Standard 0.010 0.011 0.013 0.011 Dry Cubic Foot Particulate Concentration Grains per Actual 0.006 0.007 0.008 0.007 Cubic Foot Particulate Emission Rate Pounds per Hour 142.5 180.0 200.1 174.2

Particulate Emission Rate Pounds per Million 0.017 0.022 0.025 0.022 Allowable Btu (Heat Input) 0.12 0.12 0.12 0.12 Isokinetic Rate Percent 99.8 100.6 98.3 99.6

Post Test Meter Correction Checkdimensionless 1.02 1.00 1.04 1.02

Percent Difference Allowed 5% Average 4.1 2.9 6.0 4.4

TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 5

Calculations

### ATTACHMENT 21 - Barry Report 21 Test Results

Title of Run RUN 1RUN 2RUN 3 Date Month/Day/Year 6/2/20096/2/20096/2/2009 Sampling Time -Start Military 0832 1120 1330 Sampling Time -Stop Military 1002 1244 1454 Number of Ports dimensionless 14 14 14 Number of Points per Port dimensionless 3 3 3 Heat Input Million Btu per Hour 1,267 1,353 1,350 Stack Static Pressure Inches Water -9.50 -9.50 -9.50 Barometric Pressure Inches Mercury 30.01 30.01 30.01 Standard Orifice Pressure DH@ Inches Water 1.683 1.683 1.683 Meter Correction Factor dimensionless 0.952 0.952 0.952 Oxygen Concentration Mole Percent O2 6.00 4.50 4.00 Carbon Dioxide Concentration Mole Percent CO2 14.5 13.5 14.0 Volume of Gas Metered Actual Cubic Feet 55.63155.80056.935 Volume of Water Collected Milliliters 97.6 110.6 107.0 Sampling Time Minutes 84 84 84 Nozzle Diameter Inches 0.247 0.247 0.247 Weight of Solids Collected Milligrams 41.8 33.3 29.2 Area of Stack Square Feet 180.000180.000180.000 Avg. Sqr. Root Velocity Pressure Inches Water 0.84780.83630.8423 Average Orifice Pressure (DH) Inches Water 1.2 1.3 1.3 Average Stack Temperature Degrees F 590 595 600 Average Meter Temperature Degrees F 93 104 108 Average Generation MW 142 142 142

RUN 1RUN 2RUN 3AVERAGE

Volume of Gas Sampled Standard Dry 50.89250.06950.71150.557 Cubic Feet Molecular Wt. of Stack Gas (dry)LB/LB-MOLE 30.56 30.34 30.40 30.43

Water vapor in Stack Gas Percent 8.3 9.4 9.0 8.9 0 Average Stack Gas Velocity Feet per second 67.0 66.7 67.2 67.0

Stack Gas Flow Rate Actual Cubic 724,055720,149725,800723,335 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 356,742353,087354,146354,658 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 327,205319,832322,151323,063 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 24,50823,95524,12924,197 Per Minute Particulate Concentration Grains per Standard 0.013 0.010 0.009 0.011 Dry Cubic Foot Particulate Concentration Grains per Actual 0.006 0.005 0.0040.005 Cubic Foot Particulate Emission Rate Pounds per Hour 35.5 28.1 24.5 29.3

Particulate Emission Rate Pounds per Million 0.028 0.021 0.018 0.022 Allowable Btu (Heat Input) 0.12 0.12 0.12 0.12 Isokinetic Rate Percent 100.1 100.8 101.4 100.8

Post Test Meter Correction Checkdimensionless 0.97 0.98 0.99 0.98

Percent Difference Allowed 5% Average 1.5 3.2 3.7 2.8

TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 1

Calculations

### ATTACHMENT 22 - Barry Report 22 Test Results

Title of Run RUN 1 RUN 2 RUN 3 Date Month/Day/Year 8/13/20098/13/20098/13/2009 Sampling Time -Start Military 0653 0822 0955 Sampling Time -Stop Military 0753 0922 1055 Number of Ports dimensionless 5 5 5 Number of Points per Port dimensionless 6 6 6 Heat Input Million Btu per Hour 1,517 1,496 1,474 Stack Static Pressure Inches Water -9.00 -9.00 -9.00 Barometric Pressure Inches Mercury 30.03 30.03 30.03 Standard Orifice Pressure DH@ Inches Water 1.858 1.858 1.858 Meter Correction Factor dimensionless 0.978 0.978 0.978 Oxygen Concentration Mole Percent O2 6.0 5.5 6.0 Carbon Dioxide Concentration Mole Percent CO2 14.5 15.0 14.0 Volume of Gas Metered Actual Cubic Feet 41.005 41.546 41.603 Volume of Water Collected Milliliters 89.3 101.8 87.5 Sampling Time Minutes 60 60 60 Nozzle Diameter Inches 0.265 0.265 0.265 Weight of Solids Collected Milligrams 25.7 21.3 27.0 Area of Stack Square Feet 180.000180.000180.000 Avg. Sqr. Root Velocity Pressure Inches Water 0.7941 0.8058 0.8042 Average Orifice Pressure (DH) Inches Water 1.5 1.6 1.6 Average Stack Temperature Degrees F 588 595 597 Average Meter Temperature Degrees F 74 77 81 Average Generation MW 140 140 140

RUN 1 RUN 2 RUN 3AVERAGE

Volume of Gas Sampled Standard Dry 39.920 40.264 39.99740.060 Cubic Feet Molecular Wt. of Stack Gas (dry)LB/LB-MOLE 30.56 30.62 30.48 30.55

Water vapor in Stack Gas Percent 9.5 10.6 9.3 9.8

Average Stack Gas Velocity Feet per second 62.8 64.1 64.0 63.6

Stack Gas Flow Rate Actual Cubic 678,725692,287690,952687,321 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 335,671339,847338,710338,076 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 303,694303,704307,088304,829 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 22,747 22,747 23,00122,832 Per Minute Particulate Concentration Grains per Standard 0.010 0.008 0.010 0.009 Dry Cubic Foot Particulate Concentration Grains per Actual 0.004 0.004 0.005 0.004 Cubic Foot Particulate Emission Rate Pounds per Hour 25.8 21.2 27.4 24.8

Particulate Emission Rate Pounds per Million 0.017 0.014 0.019 0.017 Allowable Btu (Heat Input) 0.12 0.12 0.12 0.12 Isokinetic Rate Percent 102.9 103.8 102.0 102.9

Post Test Meter Correction Checkdimensionless 0.97 0.97 0.97 0.97

Percent Difference Allowed 5% Average -0.8 -0.9 -0.3 -0.7

TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 2

Calculations

### ATTACHMENT 23 - Barry Report 23 Test Results

SIDE A SIDE A SIDE A SIDE B SIDE B SIDE B

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 7/16/20097/16/20097/16/20097/16/20097/16/20097/16/2009 Sampling Time -Start Military 0805 0945 1115 805 0945 1115 Sampling Time -Stop Military 0905 1045 1215 905 1045 1215 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 2,811 2,820 2,836 2,811 2,820 2,836 Stack Static Pressure Inches Water -10.00 -9.50 -9.50 -10.00 -9.50 -10.00 Barometric Pressure Inches Mercury 29.92 29.92 29.92 29.92 29.92 29.92 Standard Orifice Pressure DH@ Inches Water 2.088 2.088 2.088 1.858 1.858 1.858 Meter Correction Factor dimensionless 0.999 0.999 0.999 0.978 0.978 0.978 Oxygen Concentration Mole Percent O2 3.50 3.50 3.50 5.0 4.5 5.0 Carbon Dioxide Concentration Mole Percent CO2 14.5 14.0 14.0 14.0 14.5 14.5 Volume of Gas Metered Actual Cubic Feet 42.290 45.910 43.435 42.711 42.555 42.599 Volume of Water Collected Milliliters 100.0 117.0 126.0 99.9 93.4 95.4 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.275 0.275 0.275 0.274 0.274 0.274 Weight of Solids Collected Milligrams 31.8 37.7 22.3 19.6 20.6 26.1 Area of Stack Square Feet 174.500174.500174.500174.500174.500174.500 Avg. Sqr. Root Velocity PressureInches Water 0.8147 0.8776 0.8198 0.7855 0.7857 0.7795 Average Orifice Pressure (DH) Inches Water 2.0 2.4 2.1 1.6 1.6 1.6 Average Stack Temperature Degrees F 596 598 602 629 633 635 Average Meter Temperature Degrees F 75 81 87 81 85 89 Average Generation MW 258 257 257 258 257 257 Flowrate Weighted SIDE A SIDE A SIDE A SIDE B SIDE B SIDE BSide ASide BTOTAL or RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3AVERAGEAVERAGEAVERAGE

Volume of Gas Sampled Standard Dry 41.880 45.071 42.119 40.950 40.488 40.25643.02340.56583.588 Cubic Feet Molecular Wt. of Stack Gas (dry)LB/LB-MOLE 30.46 30.38 30.38 30.44 30.50 30.52 30.41 30.49 30.45

Water vapor in Stack Gas Percent 10.1 10.9 12.3 10.3 9.8 10.0 11.1 10.0 10.6

Average Stack Gas Velocity Feet per second 65.1 70.4 66.1 63.8 63.8 63.4 67.2 63.6 65.4

Stack Gas Flow Rate Actual Cubic 681,781736,706691,674667,978667,748663,396703,387666,3741,369,761 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 332,367359,029335,738315,846314,843312,007342,378314,232656,610 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 298,786319,936294,298283,313284,005280,696304,340282,671587,011 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 22,379 23,963 22,043 21,220 21,272 21,02422,79521,17243,967 Per Minute Particulate Concentration Grains per Standard 0.012 0.013 0.008 0.007 0.008 0.0100.0110.008 0.010 Dry Cubic Foot Particulate Concentration Grains per Actual 0.005 0.006 0.003 0.003 0.003 0.0040.0050.004 0.004 Cubic Foot Particulate Emission Rate Pounds per Hour 29.9 35.3 20.6 17.9 19.1 24.0 28.6 20.3 48.9

Particulate Emission Rate Pounds per Million 0.011 0.013 0.007 0.006 0.007 0.0080.0100.007 0.017 Allowable Btu (Heat Input) 0.12 0.12 0.12 0.12 0.12 0.12 0.12 0.12 0.12 Isokinetic Rate Percent 98.8 99.3 100.9 102.6 101.2 101.8 99.7 101.9

Post Test Meter Correction Checkdimensionless 1.02 1.03 1.03 0.97 0.97 0.97 1.03 0.97

Percent Difference Allowed 5% Average 1.6 3.5 3.1 -1.0 -0.6 -0.5 2.7 -0.7 TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 3

Calculations

### ATTACHMENT 24 - Barry Report 24 Test Results

SIDE ASIDE ASIDE ASIDE BSIDE BSIDE B Title of Run RUN 1RUN 2RUN 3RUN 1RUN 2RUN 3 Date Month/Day/Year 6/3/20096/3/20096/3/20096/3/20096/3/20096/3/2009 Sampling Time -Start Military 0828 0952 1114 0828 0952 1,114 Sampling Time -Stop Military 0932 1057 1219 0933 1057 1,219 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 3,229 3,252 3,197 3,229 3,252 3,197 Stack Static Pressure Inches Water 1.10 1.10 1.10 1.60 1.60 1.60 Barometric Pressure Inches Mercury 30.02 30.02 30.02 30.02 30.02 30.02 Standard Orifice Pressure DH@Inches Water 1.683 1.683 1.683 1.907 1.907 1.907 Meter Correction Factor dimensionless 0.952 0.952 0.952 0.980 0.980 0.980 Oxygen Concentration Mole Percent O2 6.00 5.00 6.00 6.50 6.00 6.00 Carbon Dioxide ConcentrationMole Percent CO2 14.0 12.5 13.0 13.5 14.0 14.0 Volume of Gas Metered Actual Cubic Feet 44.78841.69345.26840.96541.56044.390 Volume of Water Collected Milliliters 99.4 99.2 100.3 95.8 89.9 92.9 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.240 0.235 0.237 0.240 0.240 0.243 Weight of Solids Collected Milligrams 13.6 8.2 6.5 11.4 12.5 9.5 Area of Stack Square Feet 183.750183.750183.750183.750183.750183.750 Avg. Sqr. Root Velocity PressureInches Water 0.87980.84160.88800.84410.84580.8773 Average Orifice Pressure (DH) Inches Water 1.9 1.7 1.9 1.9 1.9 2.2 Average Stack Temperature Degrees F 293 291 286 307 309 311 Average Meter Temperature Degrees F 87 97 101 78 81 84 Average Generation MW 376 376 376 376 376 376

Side ASide BTOTAL or RUN 1RUN 2RUN 3RUN 1RUN 2RUN 3AVERAGEAVERAGEAVERAGE

Volume of Gas Sampled Standard Dry 41.46137.92740.89639.68840.08642.59840.09540.79180.885 Cubic Feet Molecular Wt. of Stack Gas (dry)LB/LB-MOLE 30.48 30.20 30.32 30.42 30.48 30.4830.3330.46 30.40

Water vapor in Stack Gas Percent 10.1 11.0 10.3 10.2 9.5 9.3 10.5 9.7 10.1

Average Stack Gas Velocity Feet per second 58.4 56.2 58.9 56.6 56.7 58.8 57.8 57.4 57.6

Stack Gas Flow Rate Actual Cubic 644,396619,338649,427624,348624,729648,658637,720632,5781,270,299 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 454,575438,004462,115432,784432,222447,380451,565437,462889,027 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 408,479389,991414,289388,628390,952405,731404,253395,104799,357 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 30,59529,21031,03029,10829,28230,38930,27929,59359,872 Per Minute Particulate Concentration Grains per Standard 0.005 0.003 0.002 0.004 0.005 0.0030.0040.004 0.004 Dry Cubic Foot Particulate Concentration Grains per Actual 0.003 0.002 0.002 0.003 0.003 0.0020.0020.003 0.002 Cubic Foot Particulate Emission Rate Pounds per Hour 17.7 11.1 8.7 14.7 16.1 11.9 12.5 14.3 26.8

Particulate Emission Rate Pounds per Million 0.00550.00340.00270.00460.00490.00370.00390.00440.0083 Btu (Heat Input) Isokinetic Rate Percent 98.9 98.9 98.7 99.5 99.9 99.8 98.8 99.8 

### TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 4

Calculations

### ATTACHMENT 25 - Barry Report 25 Test Results

Title of Run RUN 1 RUN 2 RUN 3 Date Month/Day/Year 5/13/20095/13/20095/13/2009 Sampling Time -Start Military 0815 1016 1156 Sampling Time -Stop Military 0947 1134 1320 Number of Ports dimensionless 6 6 6 Number of Points per Port dimensionless 6 5 5 Heat Input Million Btu per Hour 7,989 7,968 7,938 Stack Static Pressure Inches Water 0.50 0.50 0.50 Barometric Pressure Inches Mercury 30.01 30.01 30.01 Standard Orifice Pressure DH@ Inches Water 2.211 2.211 2.211 Meter Correction Factor dimensionless 0.927 0.927 0.927 Oxygen Concentration Mole Percent O2 5.0 6.0 6.0 Carbon Dioxide Concentration Mole Percent CO2 13.0 12.0 12.0 Volume of Gas Metered Actual Cubic Feet 53.625 44.689 40.785 Volume of Water Collected Milliliters 91.4 80.8 78.7 Sampling Time Minutes 72 60 60 Nozzle Diameter Inches 0.250 0.250 0.240 Weight of Solids Collected Milligrams 36.3 32.4 33.6 Area of Stack Square Feet 886.875886.875886.875 Avg. Sqr. Root Velocity Pressure Inches Water 0.7800 0.7833 0.7826 Average Orifice Pressure (DH) Inches Water 1.9 2.0 1.7 Average Stack Temperature Degrees F 350 353 357 Average Meter Temperature Degrees F 74 80 83 Average Generation MW 773 773 773

RUN 1 RUN 2 RUN 3AVERAGE

Volume of Gas Sampled Standard Dry 49.498 40.813 37.05142.454 Cubic Feet Molecular Wt. of Stack Gas (dry)LB/LB-MOLE 30.28 30.16 30.16 30.20

Water vapor in Stack Gas Percent 8.0 8.5 9.1 8.5

Average Stack Gas Velocity Feet per second 53.7 54.2 54.4 54.1

Stack Gas Flow Rate Actual Cubic 2,858,5232,884,0712,892,8192,878,471 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 1,870,5641,881,0361,876,5031,876,034 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 1,720,9831,720,6911,705,9401,715,871 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 128,902128,880127,775128,519 Per Minute Particulate Concentration Grains per Standard 0.011 0.012 0.014 0.012 Dry Cubic Foot Particulate Concentration Grains per Actual 0.007 0.007 0.008 0.007 Cubic Foot Particulate Emission Rate Pounds per Hour 166.6 180.3 204.2 183.7

Particulate Emission Rate Pounds per Million 0.021 0.023 0.026 0.023 Allowable Btu (Heat Input) 0.12 0.12 0.12 0.12 Isokinetic Rate Percent 103.9 102.8 102.2 103.0

Post Test Meter Correction Checkdimensionless 0.92 0.94 0.95 0.94

Percent Difference Allowed 5% Average -0.7 0.9 2.4 0.9

TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 5

Calculations

### ATTACHMENT 26 - Barry Report 26 Test Results

Title of Run RUN 1 RUN 2 RUN 3 Date Month/Day/Year 6/22/20066/22/20066/22/2006 Sampling Time -Start Military 0755 0953 1153 Sampling Time -Stop Military 0919 1117 1317 Number of Ports dimensionless 14 14 14 Number of Points per Port dimensionless 3 3 3 Heat Input Million Btu per Hour 1,465 1,470 1,467 Stack Static Pressure Inches Water -11.00 -11.00 -11.00 Barometric Pressure Inches Mercury 30.22 30.22 30.22 Standard Orifice PressureDH@ Inches Water 2.378 2.378 2.378 Meter Correction Factor dimensionless 0.938 0.938 0.938 Oxygen Concentration Mole Percent O2 7.5 7.0 7.0 Carbon Dioxide Concentration Mole Percent CO2 11.0 12.0 12.0 Volume of Gas Metered Actual Cubic Feet 51.287 51.752 52.790 Volume of Water Collected Milliliters 108 116 117 Sampling Time Minutes 84 84 84 Nozzle Diameter Inches 0.240 0.240 0.240 Weight of Solids Collected Milligrams 129.3 159.2 164.9 Area of Stack Square Feet 180.000180.000180.000 Avg. Sqr. Root Velocity PressureInches Water 0.8473 0.8602 0.8575 Average Orifice Pressure(DH) Inches Water 1.6 1.6 1.6 Average Stack Temperature Degrees F 597 593 593 Average Meter Temperature Degrees F 79 87 93

RUN 1 RUN 2 RUN 3Average

Volume of Gas Sampled Standard Dry 47.763 47.565 47.95647.761 Cubic Feet Molecular Wt. of Stack Gas (wet)LB/LB-MOLE 28.90 28.94 28.9428.93

Water vapor in Stack Gas Percent 9.6 10.3 10.3 10.1

Average Stack Gas Velocity Feet per second 67.8 68.7 68.5 68.3

Stack Gas Flow Rate Actual Cubic 732,657742,056739,494738,069 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 359,637365,478364,472363,196 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 325,042327,844326,928326,604 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 24,346 24,555 24,48724,463 Per Minute Particulate Concentration Grains per Standard 0.0417 0.0515 0.05300.0487 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0185 0.0228 0.02340.0216 Cubic Foot Particulate Emission Rate Pounds per Hour 116.2 144.8 148.4136.5

Particulate Emission Rate Pounds per Million 0.079 0.099 0.1010.093 Btu (Heat Input) Isokinetic Rate Percent 100.2 98.9 100.0 99.7



### TABLE I. PARTICULATE EMISSIONS TEST RESULTS

ALABAMA POWER COMPANY BARRY STEAM PLANT, UNIT 1 COMPLIANCE ASSURANCE MONITORING

Calculations

## ATTACHMENT 27 - Barry Report 27 Test Results

Title of Run RUN 1 RUN 2 RUN 3 Date Month/Day/Year 8/22/20068/22/20068/22/2006 Sampling Time -Start Military 0820 1106 1228 Sampling Time -Stop Military 0920 1206 1328 Number of Ports dimensionless 5 5 5 Number of Points per Port dimensionless 6 6 6 Heat Input Million Btu per Hour 1,463 1,467 1,464 Stack Static Pressure Inches Water -7.50 -7.50 -7.50 Barometric Pressure Inches Mercury 30.20 30.20 30.20 Standard Orifice PressureDH@ Inches Water 2.020 2.020 2.020 Meter Correction Factor dimensionless 0.974 0.974 0.974 Oxygen Concentration Mole Percent O2 7.0 6.5 3.5 Carbon Dioxide Concentration Mole Percent CO2 11.0 11.5 13.0 Volume of Gas Metered Actual Cubic Feet 38.855 37.700 36.265 Volume of Water Collected Milliliters 98 99 94 Sampling Time Minutes 60 60 60 Nozzle Diameter Inches 0.252 0.252 0.252 Weight of Solids Collected Milligrams 96.6 83.7 84.1 Area of Stack Square Feet 180.000180.000180.000 Avg. Sqr. Root Velocity PressureInches Water 0.8293 0.7801 0.7370 Average Orifice Pressure(DH) Inches Water 1.7 1.5 1.3 Average Stack Temperature Degrees F 568 574 574 Average Meter Temperature Degrees F 87 95 99

RUN 1 RUN 2 RUN 3Average

Volume of Gas Sampled Standard Dry 37.040 35.408 33.78335.410 Cubic Feet Molecular Wt. of Stack Gas (wet)LB/LB-MOLE 28.71 28.69 28.8028.73

Water vapor in Stack Gas Percent 11.1 11.6 11.6 11.4

Average Stack Gas Velocity Feet per second 65.4 61.7 58.2 61.8

Stack Gas Flow Rate Actual Cubic 706,801666,741628,763667,435 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 359,576337,435318,111338,374 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 319,755298,190281,272299,739 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 23,950 22,334 21,06722,450 Per Minute Particulate Concentration Grains per Standard 0.0402 0.0364 0.03830.0383 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0182 0.0163 0.01720.0172 Cubic Foot Particulate Emission Rate Pounds per Hour 110.1 93.0 92.4 98.5

Particulate Emission Rate Pounds per Million 0.075 0.063 0.0630.067 Btu (Heat Input) Isokinetic Rate Percent 100.3 102.8 104.0102.4



### TABLE I. PARTICULATE EMISSIONS TEST RESULTS

ALABAMA POWER COMPANY BARRY STEAM PLANT, UNIT 2 CAM

8/22/2006

Calculations

### ATTACHMENT 28 - Barry Report 28 Test Results

SIDE A SIDE A SIDE A SIDE B SIDE B SIDE B

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 7/26/2006 7/26/2006 7/26/2006 7/26/20067/26/20067/26/2006 Sampling Time -Start Military 0920 1105 1225 0920 1105 1225 Sampling Time -Stop Military 1020 1205 1325 1020 1205 1325 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 2,473 2,457 2,460 2,473 2,600 2,600 Stack Static Pressure Inches Water -10.00 -10.00 -10.00 -10.00 -10.00 -10.00 Barometric Pressure Inches Mercury 30.11 30.11 30.11 30.11 30.11 30.11 Standard Orifice PressureDH@ Inches Water 1.882 1.882 1.882 2.087 2.087 2.087 Meter Correction Factor dimensionless 0.995 0.995 0.995 0.966 0.966 0.966 Oxygen Concentration Mole Percent O2 5 5 4.5 6 4 4 Carbon Dioxide Concentration Mole Percent CO2 15 15 16 15 15.5 15 Volume of Gas Metered Actual Cubic Feet 40.980 40.387 40.735 42.600 43.615 42.850 Volume of Water Collected Milliliters 108.00 96.00 95.00 85.00 83.00 88.00 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.265 0.265 0.265 0.265 0.265 0.265 Weight of Solids Collected Milligrams 105.2 126.0 110.4 83.3 108.8 104.1 Area of Stack Square Feet 174.500 174.500 174.500 174.500174.500 174.500 Avg. Sqr. Root Velocity Pressure Inches Water 0.8226 0.8167 0.8193 0.8313 0.8399 0.8357 Average Orifice Pressure(DH) Inches Water 1.6303863331.6067003331.618543333 1.8253611.9111351.8978015 Average Stack Temperature Degrees F 603 606 602 618 619 626 Average Meter Temperature Degrees F 83 89 94 98 103 107

SIDE A SIDE A SIDE A 3 runsSIDE B SIDE B SIDE B3 runs RUN 1 RUN 2 RUN 3Average RUN 1 RUN 2 RUN 3Average

Volume of Gas Sampled Standard Dry 40.053 39.047 39.06939.069 39.397 39.936 38.98438.984 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.60 30.60 30.7430.74 30.64 30.64 30.5630.56

Water vapor in Stack Gas Percent 11.3 10.4 10.3 10.3 9.2 8.9 9.6 9.6

Average Stack Gas Velocity Feet per second 65.8 65.3 65.2 65.2 66.6 67.3 67.3 67.3

Stack Gas Flow Rate Actual Cubic 688,503 683,369 682,679682,679697,339704,460704,893704,893 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 335,793 332,164 333,079333,079335,170338,289336,501336,501 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 297,974 297,711 298,871298,871304,270308,144304,181304,181 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 22,318 22,299 22,38522,385 22,790 23,080 22,78322,783 Per Minute Particulate Concentration Grains per Standard 0.0404 0.0497 0.04350.0435 0.0326 0.0420 0.04110.0411 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0175 0.0216 0.01910.0191 0.0142 0.0184 0.01770.0177 Cubic Foot Particulate Emission Rate Pounds per Hour 103.3 126.8 111.5111.5 84.9 110.8 107.2107.2

Particulate Emission Rate Pounds per Million 0.042 0.052 0.0450.045 0.034 0.043 0.0410.041 Btu (Heat Input) Combined Particulate Emission RatePounds per Million 0.076 0.094 0.0870.087 Allowable Particulate Emission RateBtu (Heat Input) 0.12 0.12 0.120.12

Isokinetic Rate Percent 102.0 99.6 99.2 99.2 98.3 98.4 97.3 97.3

Post Test Meter Correction Factor dimensionless 1.00 1.02 1.01 1.01 0.98 0.99 1.01 1.01

Percent Difference Allowed 5% 0.94 2.22 1.90 1.90 1.68 2.11 3.97 3.97 Calculations TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT - UNIT 3 COMPLIANCE ASSURANCE MONITORING

### ATTACHMENT 29 - Barry Report 29 Test Results

Title of Run RUN 1ARUN 2ARUN 3A RUN 1BRUN 2BRUN 3B Date Month/Day/Year 4/28/20064/28/20064/28/2006 4/28/20064/28/20064/28/2006 Sampling Time -Start Military 0904 1142 1352 0904 1142 1352 Sampling Time -Stop Military 1004 1242 1452 1004 1242 1452 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 3,354 3,355 3,354 3,354 3,355 3,354 Stack Static Pressure Inches Water 1.50 1.50 1.50 1.50 1.50 1.50 Barometric Pressure Inches Mercury 30.50 30.50 30.50 30.50 30.50 30.50 Meter Correction Factor dimensionless 1.011 1.011 1.011 0.978 0.978 0.978 Oxygen Concentration Mole Percent O2 5 4.5 5 6 5 5 Carbon Dioxide Concentration Mole Percent CO2 13 12 12.5 14 13.5 12.5 Volume of Gas Metered Actual Cubic Feet 33.230 34.835 34.610 36.300 36.580 35.800 Volume of Water Collected Milliliters 67.00 58.00 65.00 83.00 61.00 72.00 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.215 0.215 0.215 0.215 0.215 0.215 Weight of Solids Collected Milligrams 79.1 96.2 90.8 82.4 82.5 82.7 Area of Stack Square Feet 183.750183.750183.750 183.750183.750183.750 Avg. Sqr. Root Velocity Pressure Inches Water 0.8391 0.9138 0.8905 0.9286 0.9481 0.9284 Average Orifice Pressure(DH) Inches Water 1.36 1.57 1.52 1.84 1.84 1.78 Average Stack Temperature Degrees F 284 295 294 297 309 302 Average Meter Temperature Degrees F 69 74 79 82 74 77 Volume of Titrant For H2SO4 AloquitMilliliters

Side A Side B RUN 1ARUN 2ARUN 3AAverageRUN 1BRUN 2BRUN 3BAverage

Volume of Gas Sampled Standard Dry 34.325 35.633 35.10735.022 35.431 36.249 35.27735.652 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 29.25 29.24 29.2229.24 29.24 29.45 29.1329.27

Water vapor in Stack Gas Percent 8.4 7.1 8.0 7.8 9.9 7.3 8.8 8.7

Average Stack Gas Velocity Feet per second 54.9 60.3 58.7 58.0 61.3 62.9 61.661.9

Stack Gas Flow Rate Actual Cubic 605,561664,308647,235639,035675,969692,980679,543682,831 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 431,074475,289463,544456,636482,311486,855481,361483,509 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 394,801441,466426,385420,884434,410451,122439,171441,568 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 29,571 33,066 31,93631,524 32,537 33,789 32,89433,073 Per Minute Particulate Concentration Grains per Standard 0.0355 0.0416 0.03980.0390 0.0358 0.0350 0.03610.0357 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0231 0.0276 0.02620.0257 0.0230 0.0228 0.02330.0231 Cubic Foot Particulate Emission Rate Pounds per Hour 120.1 157.3 145.6141.0 133.4 135.5 135.9134.9

Particulate Emission Rate Pounds per Million 0.036 0.047 0.0430.042 0.040 0.040 0.0410.040 Btu (Heat Input) Isokinetic Rate Percent 103.6 98.0 100.0100.5 99.1 97.6 97.698.1 Run 1 Run 2 Run 3Average Particulate Emission Rate Pounds per Million Btu 0.078 0.087 0.0840.082 (Heat Input) (A & B Combined)



### TABLE I. PARTICULATE EMISSIONS TEST RESULTS

ALABAMA POWER COMPANY BARRY STEAM PLANT - UNIT 4 COMPLIANCE ASSURANCE MONITORING

CalculationsATTACHMENT 30 - Barry Report 30 Test Results

Side ASide ASide A Side B Side B Side B

Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 5/31/20075/31/20075/31/2007 5/31/20075/31/20075/31/2007 Sampling Time -Start Military 0845 1126 1300 0845 1126 1300 Sampling Time -Stop Military 0956 1238 1410 0956 1238 1410 Number of Ports dimensionless 6 6 6 6 6 6 Number of Points per Port dimensionless 5 5 5 5 5 5 Heat Input Million Btu per Hour 7,508 7,290 7,270 7,508 7,290 7,270 Stack Static Pressure Inches Water -1.00 -1.00 -1.00 -1.00 -1.00 -1.00 Barometric Pressure Inches Mercury 30.04 30.04 30.04 30.04 30.04 30.04 Standard Orifice PressureDH@ Inches Water 1.858 1.858 1.858 2.258 2.258 2.258 Meter Correction Factor dimensionless 0.978 0.978 0.978 0.982 0.982 0.982 Oxygen Concentration Mole Percent O2 6 6 5.5 6.5 5.75 5.75 Carbon Dioxide Concentration Mole Percent CO2 14.5 14 14 15.5 15 14 Volume of Gas Metered Actual Cubic Feet 37.20240.21039.742 34.51140.63341.980 Volume of Water Collected Milliliters 88.00 82.00 83.00 70.00 97.00 91.00 Sampling Time Minutes 60 60 60 60 60 60 Nozzle Diameter Inches 0.210 0.212 0.213 0.212 0.210 0.212 Weight of Solids Collected Milligrams 48.3 43.2 49.1 56.4 60.1 55.7 Area of Stack Square Feet 287.500287.500287.500 287.500287.500287.500 Avg. Sqr. Root Velocity Pressure Inches Water 1.04681.11201.0993 0.94391.11191.1281 Average Orifice Pressure(DH) Inches Water 1.49 1.65 1.62 1.62 2.09 2.22 Average Stack Temperature Degrees F 311 318 318 326 327 334 Average Meter Temperature Degrees F 74 80 83 79 88 89

Side ASide ASide ASide A Side B Side B Side BSide B RUN 1 RUN 2 RUN 3AVERAGE RUN 1 RUN 2 RUN 3AVERAGE

Volume of Gas Sampled Standard Dry 36.28638.74838.12037.71833.48838.81940.01137.439 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.56 30.48 30.46 30.50 30.74 30.63 30.47 30.61

Water vapor in Stack Gas Percent 10.2 9.1 9.3 9.5 9.0 10.5 9.7 9.7

Average Stack Gas Velocity Feet per second 70.5 75.1 74.3 73.3 63.8 75.6 77.0 72.1

Stack Gas Flow Rate Actual Cubic 1,215,5301,295,2191,281,4551,264,0681,100,1241,303,9751,328,9551,244,351 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 833,374880,281871,002861,552740,482875,647885,483833,871 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 747,988800,539790,033779,520674,151783,494799,855752,500 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 56,02459,96059,17358,38650,49458,68459,90956,362 Per Minute Particulate Concentration Grains per Standard 0.02050.01720.01980.01920.02590.02380.02140.0237 Dry Cubic Foot Particulate Concentration Grains per Actual 0.01260.01060.01220.01180.01590.01430.0129 0.014 Cubic Foot Particulate Emission Rate Pounds per Hour 131.4 117.8 134.3 127.9 149.9 160.1 147.0 152.3

Particulate Emission Rate Pounds per Million 0.01750.01620.01850.01740.02000.02200.02020.0207 Btu (Heat Input) Isokinetic Rate Percent 96.6 94.6 93.4 94.9 97.1 98.7 97.8 97.8

Combined Particulate Emission RatePounds per Million 0.037 0.038 0.039 0.038 Allowable Btu (Heat Input) 0.12 0.12 0.12 0.12 TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT - UNIT 5 COMPLIANCE ASSURANCE MONITORING

Calculations

## ATTACHMENT 31 - Barry Report 31 Test Results

Title of Run RUN 1 RUN 2 Date Month/Day/Year 12/6/200512/6/2005 Sampling Time -Start Military 0841 1016 Sampling Time -Stop Military 0929 1104 Number of Ports dimensionless 8 8 Number of Points per Port dimensionless 3 3 Heat Input Million Btu per Hour 1,429 1,429 Stack Static Pressure Inches Water -10.00 -10.00 Barometric Pressure Inches Mercury 30.30 30.30 Meter Correction Factor dimensionless 1.042 1.042 Oxygen Concentration Mole Percent O2 6.0 5.5 Carbon Dioxide ConcentrationMole Percent CO2 13.0 13.0 Volume of Gas Metered Actual Cubic Feet 26.120 26.600 Volume of Water Collected Milliliters 50.00 48.00 Sampling Time Minutes 48 48 Nozzle Diameter Inches 0.250 0.250 Weight of Solids Collected Milligrams 116.4 177.1 Area of Stack Square Feet 180.000180.000 Avg. Sqr. Root Velocity PressureInches Water 0.8278 0.8240 Average Orifice Pressure(DH) Inches Water 1.1 1.1 Average Stack Temperature Degrees F 589 590 Average Meter Temperature Degrees F 48 50

RUN 1 RUN 2Average

Volume of Gas Sampled Standard Dry 28.725 29.14328.934 Cubic Feet Molecular Wt. of Stack Gas LB/LB-MOLE 29.39 29.4229.40

Water vapor in Stack Gas Percent 7.6 7.2 7.4

Average Stack Gas Velocity Feet per second 65.3 65.0 65.2

Stack Gas Flow Rate Actual Cubic 705,396702,120703,758 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 350,657348,724349,690 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 324,103323,634323,868 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 24,275 24,24024,258 Per Minute Particulate Concentration Grains per Standard 0.0624 0.09360.0780 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0287 0.04310.0359 Cubic Foot Particulate Emission Rate Pounds per Hour 173.4 259.6216.5

Particulate Emission Rate Pounds per Million 0.121 0.1820.151 Btu (Heat Input) Isokinetic Rate Percent 97.5 99.0 98.3



### TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT, UNIT 1 CAM ENGINEERING

12/6/2005

Calculations

## ATTACHMENT 32 - Barry Report 32 Test Results, Part I

INLET INLET INLETOUTLETOUTLETOUTLET Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 1/23/20071/23/20071/23/20071/23/20071/23/20071/23/2007 Sampling Time -Start Military 0922 1034 1144 0920 1036 1144 Sampling Time -Stop Military 1004 1116 1226 1010 1126 1232 Number of Ports dimensionless 7 7 7 5 5 5 Number of Points per Port dimensionless 3 3 3 5 5 5 Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 9,780 9,780 9,780 Stack Static Pressure Inches Water -7.50 -7.50 -7.50 -7.50 -7.50 -7.50 Barometric Pressure Inches Mercury 30.05 30.05 30.05 30.05 30.05 30.05 Standard Orifice PressureDH@ Inches Water 2.258 2.258 2.258 1.858 1.858 1.858 Meter Correction Factor dimensionless 0.982 0.982 0.982 0.978 0.978 0.978 Oxygen Concentration Mole Percent O2 5.5 6.0 6.0 6.0 6.0 6.0 Carbon Dioxide Concentration Mole Percent CO2 14.0 13.5 14.0 14.0 13.5 14.0 Volume of Gas Metered Actual Cubic Feet 23.290 22.740 23.160 32.935 32.520 32.125 Volume of Water Collected Milliliters 23 22 39 55 72 48 Sampling Time Minutes 42 42 42 50 50 50 Nozzle Diameter Inches 0.250 0.246 0.246 0.276 0.276 0.276 Weight of Solids Collected Milligrams 3,006.33,245.43,716.7 27.1 46.6 43.0 Area of Stack Square Feet 180.000180.000180.000180.000180.000180.000 Avg. Sqr. Root Velocity Pressure Inches Water 0.7481 0.7430 0.7556 0.7568 0.7426 0.7386 Average Orifice Pressure(DH) Inches Water 1.3 1.2 1.2 1.6 1.6 1.6 Average Stack Temperature Degrees F 611 627 611 577 576 577 Average Meter Temperature Degrees F 71 77 76 49 49 49

INLET INLET INLETOUTLETOUTLETOUTLETINLETOUTLET RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3AVERAGEAVERAGE

Volume of Gas Sampled Standard Dry 22.917 22.132 22.576 33.695 33.288 32.84322.54133.275 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.46 30.40 30.48 30.48 30.40 30.4830.4530.45

Water vapor in Stack Gas Percent 4.5 4.5 7.5 7.1 9.2 6.4 5.5 7.6

Average Stack Gas Velocity Feet per second 59.2 59.3 60.1 59.2 58.4 57.7 59.5 58.5

Stack Gas Flow Rate Actual Cubic 639,171640,373649,461639,648630,965623,428643,002631,347 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 296,655292,743291,907298,071287,615292,653293,768292,780 Feet Per Minute Particulate Concentration Grains per Standard 2.020 2.258 2.535 0.012 0.022 0.0202.2710.018 Dry Cubic Foot Particulate Concentration Grains per Actual 0.938 1.032 1.140 0.006 0.010 0.009 1.0370.008 Cubic Foot Particulate Emission Rate Pounds per Hour 5,137.05,666.56,343.5 31.6 53.1 50.65,715.6 45.1

Particulate Emission Rate Pounds per Million 3.831 4.426 4.969 0.024 0.042 0.040 Btu (O2 F Factor) Efficiency (based on grains per standardPercent 99.387 99.045 99.205 99.212 dry cubic foot) Isokinetic Rate Percent 97.1 98.1 100.4 97.9 100.3 97.2 98.5 98.5 

### TABLE I. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 2

Calculations

## ATTACHMENT 33 - Barry Report 32 Test Results, Part II

INLET INLETOUTLETOUTLET Title of Run RUN 1 RUN 2 RUN 1 RUN 2 Date Month/Day/Year 1/24/20071/24/20071/24/20071/24/2007 Sampling Time -Start Military 1002 1114 1002 1114 Sampling Time -Stop Military 1044 1156 1052 1204 Number of Ports dimensionless 7 7 5 5 Number of Points per Port dimensionless 3 3 5 5 Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 9,780 Stack Static Pressure Inches Water -7.50 -7.50 -7.50 -7.50 Barometric Pressure Inches Mercury 29.98 29.98 29.98 29.98 Standard Orifice PressureDH@ Inches Water 2.258 2.258 1.858 1.858 Meter Correction Factor dimensionless 0.982 0.982 0.978 0.978 Oxygen Concentration Mole Percent O2 5.0 6.0 5.0 6.0 Carbon Dioxide Concentration Mole Percent CO2 15.0 14.5 15.0 14.5 Volume of Gas Metered Actual Cubic Feet 23.430 23.870 31.062 33.218 Volume of Water Collected Milliliters 62 35 62 63 Sampling Time Minutes 42 42 50 50 Nozzle Diameter Inches 0.246 0.248 0.276 0.276 Weight of Solids Collected Milligrams 2,594.53,800.1 48.0 66.2 Area of Stack Square Feet 180.000180.000180.000180.000 Avg. Sqr. Root Velocity Pressure Inches Water 0.7713 0.7488 0.7382 0.7540 Average Orifice Pressure(DH) Inches Water 1.3 1.3 1.6 1.6 Average Stack Temperature Degrees F 602 597 579 576 Average Meter Temperature Degrees F 78 88 50 51

INLET INLETOUTLETOUTLETINLETOUTLET RUN 1 RUN 2 RUN 1 RUN 2AVERAGEAVERAGE

Volume of Gas Sampled Standard Dry 22.714 22.696 31.622 33.77922.70532.701 Cubic Feet Molecular Wt. of Stack Gas (dry) LB/LB-MOLE 30.60 30.56 30.60 30.5630.5830.58

Water vapor in Stack Gas Percent 11.4 6.8 8.4 8.1 9.1 8.3

Average Stack Gas Velocity Feet per second 61.6 59.1 57.9 59.1 60.4 58.5

Stack Gas Flow Rate Actual Cubic 665,273638,353625,743638,097651,813631,920 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 288,182292,359286,342294,029290,271290,186 Feet Per Minute Particulate Concentration Grains per Standard 1.759 2.578 0.023 0.0302.1690.027 Dry Cubic Foot Particulate Concentration Grains per Actual 0.762 1.181 0.011 0.0140.9710.012 Cubic Foot Particulate Emission Rate Pounds per Hour 4,345.06,461.5 57.4 76.15,403.3 66.7

Particulate Emission Rate Pounds per Million 3.230 5.053 0.043 0.059 Btu (O2 F Factor) Efficiency (based on grains per standardPercent 98.671 98.830 98.750 dry cubic foot) Isokinetic Rate Percent 102.3 99.2 95.7 99.5 100.7 97.6 

### TABLE II. PARTICULATE EMISSIONS TEST RESULTS ALABAMA POWER COMPANY BARRY STEAM PLANT UNIT 2

Calculations

### ATTACHMENT 34 - Barry Report 33 Test Results

OUTLETOUTLETOUTLET INLET INLET INLET Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 7/24/20077/24/20077/24/20077/24/20077/24/20077/24/2007 Sampling Time -Start Military 0918 1030 1200 0918 1030 1200 Sampling Time -Stop Military 1008 1120 1250 1008 1118 1248 Number of Ports dimensionless 5 5 5 8 8 8 Number of Points per Port dimensionless 5 5 5 3 3 3 Oxygen F Factor SDCF/MMBtu 9,780 9,780 9,780 Stack Static Pressure Inches Water -8.00 -8.00 -8.00 -8.00 -8.00 -8.00 Barometric Pressure Inches Mercury 29.95 29.95 29.95 29.95 29.95 29.95 Standard Orifice PressureDH@ Inches Water 1.939 1.939 1.939 2.418 2.418 2.418 Meter Correction Factor dimensionless 0.981 0.981 0.981 0.939 0.939 0.939 Oxygen Concentration Mole Percent O2 5 5 4 4 4 4 Carbon Dioxide Concentration Mole Percent CO2 15 15 16 16 16 15.5 Volume of Gas Metered Actual Cubic Feet 34.945 35.168 35.740 29.248 28.485 28.387 Volume of Water Collected Milliliters 79.00 77.00 78.00 85.00 76.00 82.00 Sampling Time Minutes 50 50 50 48 48 48 Nozzle Diameter Inches 0.275 0.275 0.275 0.265 0.255 0.255 Weight of Solids Collected Milligrams 19.0 18.1 26.24,398.03,005.14,244.7 Area of Stack Square Feet 180.000180.000180.000180.000180.000180.000 Avg. Sqr. Root Velocity PressureInches Water 0.7592 0.7725 0.7686 0.6869 0.6970 0.7042 Average Orifice Pressure(DH) Inches Water 1.8 1.9 1.8 1.7 1.8 1.8 Average Stack Temperature Degrees F 589 587 586 620 616 612 Average Meter Temperature Degrees F 84 87 89 79 85 89

OUTLETOUTLETOUTLET INLET INLET INLETOUTLETINLET RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3AVERAGEAVERAGE

Volume of Gas Sampled Standard Dry 33.446 33.518 33.923 27.053 26.058 25.80033.62926.304 Cubic Feet Molecular Wt. of Stack Gas (dry)LB/LB-MOLE 30.60 30.60 30.72 30.72 30.72 30.6430.64030.693

Water vapor in Stack Gas Percent 10.0 9.8 9.8 12.9 12.1 13.0 9.8 12.7

Average Stack Gas Velocity Feet per second 60.2 61.1 60.7 55.5 56.1 56.7 60.7 56.1

Stack Gas Flow Rate Actual Cubic 649,761660,082655,358599,169605,621612,800655,067605,863 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 320,761326,554324,390287,243291,557296,049323,902291,616 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 288,667294,688292,710250,234256,363257,524292,022254,707 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 21,621 22,072 21,924 18,743 19,202 19,28921,87219,078 Per Minute Particulate Concentration Grains per Standard 0.0087 0.0083 0.0119 2.5036 1.7760 2.5336 0.010 2.271 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0039 0.0037 0.0053 1.0456 0.7518 1.0647 0.0040.954 Cubic Foot Particulate Emission Rate Pounds per Hour 21.6 21.0 29.85,369.93,902.65,592.6 24.24,955.0

Particulate Emission Rate Pounds per Million 0.016 0.015 0.021 0.017 Btu (O2 F Factor) EFFICIENCY (based on grains perPercent 99.651 99.532 99.531 99.571 standard dry cubic foot) Isokinetic Rate Percent 101.1 99.3 101.1 105.8 107.5 105.9 100.5 106.4 TABLE I. PARTICULATE & FLOWRATE TEST RESULTS

ALABAMA POWER COMPANY BARRY UNIT 2 7/24/2007

Calculations

### ATTACHMENT 35 - Barry Report 34 Test Results

OUTLETOUTLETOUTLET INLET INLET INLET Title of Run RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3 Date Month/Day/Year 7/27/20077/27/20077/27/20077/27/20077/27/20077/27/2007 Sampling Time -Start Military 0808 0924 1040 0808 0924 1040 Sampling Time -Stop Military 0854 1014 1128 0850 1006 1022 Number of Ports dimensionless 5 5 5 8 8 8 Number of Points per Port dimensionless 5 5 5 3 3 3 Stack Static Pressure Inches Water -8.00 -8.00 -8.00 -8.00 -8.00 -8.00 Barometric Pressure Inches Mercury 29.90 29.90 29.90 29.90 29.90 29.90 Standard Orifice PressureDH@ Inches Water 1.939 1.939 1.939 2.418 2.418 2.418 Meter Correction Factor dimensionless 0.981 0.981 0.981 0.939 0.939 0.939 Oxygen Concentration Mole Percent O2 5.0 4.0 3.5 4.0 3.0 2.5 Carbon Dioxide Concentration Mole Percent CO2 16.0 16.5 16.0 17.0 17.0 16.0 Volume of Gas Metered Actual Cubic Feet 30.225 28.700 30.040 25.356 25.349 25.999 Volume of Water Collected Milliliters 87.9 86.8 79.1 89.0 78.0 78.0 Sampling Time Minutes 50 50 50 48 48 48 Nozzle Diameter Inches 0.250 0.250 0.250 0.252 0.252 0.252 Weight of Solids Collected Milligrams 32.8 15.9 17.14,400.34,386.94,351.2 Area of Stack Square Feet 180.000180.000180.000180.000180.000180.000 Avg. Sqr. Root Velocity PressureInches Water 0.7729 0.7438 0.7705 0.6860 0.6956 0.6912 Average Orifice Pressure(DH) Inches Water 1.3 1.2 1.3 1.6 1.6 1.6 Average Stack Temperature Degrees F 582 583 586 564 588 573 Average Meter Temperature Degrees F 82 86 90 86 83 91

OUTLETOUTLETOUTLET INLET INLET INLETOUTLETINLET RUN 1 RUN 2 RUN 3 RUN 1 RUN 2 RUN 3AVERAGEAVERAGE

Volume of Gas Sampled Standard Dry 28.943 27.284 28.379 23.118 23.226 23.46128.20223.268 Cubic Feet Molecular Wt. of Stack Gas (dry)LB/LB-MOLE 30.76 30.80 30.70 30.88 30.84 30.6630.75330.793

Water vapor in Stack Gas Percent 12.5 13.0 11.6 15.3 13.7 13.5 12.4 14.2

Average Stack Gas Velocity Feet per second 61.3 59.0 61.1 54.1 55.4 54.8 60.5 54.8

Stack Gas Flow Rate Actual Cubic 661,760637,569660,319584,812598,054591,310653,216591,392 Feet Per Minute Stack Gas Flow Rate Standard Wet Cubic 328,345315,990326,314295,297295,053296,113323,549295,487 Feet Per Minute Stack Gas Flow Rate Standard Dry Cubic 287,277274,834288,468249,995254,778256,044283,526253,606 Feet Per Minute Stack Gas Flow Rate Pounds of Dry Air 21,517 20,585 21,606 18,725 19,083 19,17821,23618,995 Per Minute Particulate Concentration Grains per Standard 0.0175 0.0090 0.0093 2.9313 2.9088 2.85620.012 2.899 Dry Cubic Foot Particulate Concentration Grains per Actual 0.0076 0.0039 0.0041 1.2530 1.2392 1.23680.005 1.243 Cubic Foot Particulate Emission Rate Pounds per Hour 43.0 21.1 22.96,281.16,352.26,268.3 29.06,300.6

Particulate Emission Rate Pounds per Million 0.032 0.016 0.016 0.021 Btu (O2 F Factor) EFFICIENCY (based on grains perPercent 99.405 99.691 99.675 99.590 standard dry cubic foot) Isokinetic Rate Percent 106.4 104.8 103.9 100.1 98.7 99.2 105.0 99.3 

### TABLE II. PARTICULATE EMISSIONS TEST RESULTS

ALABAMA POWER COMPANY BARRY UNIT 2 7/27/2007

Calculations

## ATTACHMENT 36 - Barry Report 35 Test Results

Title of Run Test 1 Test 2 Test 3
Description Full Load, O2 Bias 0Full Load, O2

Bias 0Full Load, O2

Bias 0
Date Month/Day/Year 9/5/20079/6/20079/6/2007 Start Time Military 14:04 14:04 15:55 End Time Military 15:35 15:34 17:25 Test Load MW 773 773 773 Avg. Econ. Gas Outlet CO ppm 82 29 24 Avg. Econ. Gas Outlet O2 % Dry 4.61 4.39 4.38 Avg. Econ. Gas Outlet CO2 % Dry 14.48 14.69 14.68 Avg. Econ. Gas Outlet Temp Deg F 749 760 762 

### BARRY STEAM PLANT UNIT 5 AIR PREHEATER PERFORMANCE TEST RESULTS ALABAMA POWER COMPANY