### Instructions for filling the Emission Test Template
This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. Constituents of concern are: Carbon Monoxide, Formaldehyde, Methane, Speciated Volatile Hazardous Air Pollutants (HAPs), Speciated Semi HAPs, Sulfer Dioxide, Oxygen, Carbon Dioxide, Hydrogen Cyanide, Nitrogen Oxides, Total Dissolved Solids (TDS), and Total Suspended Solids (TSS). You must complete 3 separate sampling events for each of the requested constituents. spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. Fields shaded in yellow are required. All cells that are shaded in light green are populated using drop

- down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. Please Do Not modify the structure of this spreadsheet by adding or subtracting rows, columns, cells. Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls (example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet
1. Please enter the the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet. 2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family requred for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constiuent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg Hg +2 

### , or if the Ontario

- Hydro Method was used, you would need to enter Hg 0

### , Hg P

### , and Hg Specieated Volatile Organic HAP and Speciated Semi

-Volatile Organic HAP worksheets allow you to use a drop provided in the Constituent field to define as many records as needed to record each HAP that you have results for. General instructions follow for these worksheets:
Boiler Operation Information
1. Please determine which units of measure (acfm or dscfm) were used for Exhaust Flow Rate and which units of measure (deg C or deg F) were used for Exhaust Temperature. Fill these units of measure into the Units of Measure field. 2. Please provide the values of all requested parameters for each of the 3 sample testing periods in the Sample 1, Sample 2, and Sample 3 fields

. 3. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information

1. Please enter what types of fuel are being used in your boiler using the drop

- downs in the Fuel Type Selection field. You may enter up to 4 fuel types. Then, enter the input rate of each fuel in the Sample 1, Sample 2, and Sample 3 fields. If you are not burning one or more of the fuel types entered in one or more samples, then enter an input rate of zero.

### If you are not burning one or more of the fuel types entered in one or more samples, then enter an input rate of zero. 2. Please enter the unit of measure using the drop down provided. 3. Please enter the test method used to determine the fuel input rate. 4. Please provide any other information that you feel may be important in the Other Supporting Information field.

Emission Data
1. Some constituents ask for the emission rate results of each of the 3 samples in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and ppmvd @ 7% O2 (parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field.

### This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. Constituents of concern are: Carbon Monoxide, Formaldehyde, Methane, Speciated Volatile Hazardous Air Pollutants (HAPs), Speciated Semi

-Volatile Organic HAPs, Sulfer Dioxide, Oxygen, Carbon Dioxide, Hydrogen Cyanide, Nitrogen Oxides, Total Dissolved Solids (TDS), and Total Suspended Solids (TSS). You must complete 3 separate sampling events for each of the requested constituents. This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using Fields shaded in yellow are required. All cells that are shaded in light green are down lists. You do not need to populate cells shaded in gray, as they are automatically populated

Please Do Not modify the structure of this spreadsheet by adding or subtracting Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls (example: 8100_Unit_2_EmisTestMethods.xls).

1. Please enter the the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet.

The emission data worksheets are provided for each constituent or constituent family requred for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constiuent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg 0 

### and , and Hg +2 

### . However, both the Volatile Organic HAP worksheets allow you to use a drop

- down provided in the Constituent field to define as many records as needed to record each HAP that you have results for.

1. Please determine which units of measure (acfm or dscfm) were used for Exhaust Flow Rate and which units of measure (deg C or deg F) were used for Exhaust Temperature. Fill these units of measure into the Units of Measure field. 2. Please provide the values of all requested parameters for each of the 3 sample testing periods in the Sample 1, Sample
3. Please provide any other supporting information or comments in the Other Supporting Information field.

downs in the Fuel Type Selection field. You may enter up to 4 fuel types. Then, enter the input rate of each fuel in the Sample 1, Sample 2, and Sample 3 fields. If you are not burning one or more of the fuel types entered in one or more samples, then enter an input rate of zero.

### If you are not burning one or more of the fuel types entered in one or more samples, then enter an input rate of zero.

4. Please provide any other information that you feel may be important in the Other Supporting Information field.

1. Some constituents ask for the emission rate results of each of the 3 samples in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and ppmvd @ 7% O2 (parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). Please provide any other information that you feel may be important in the Other Supporting Information field.EIA

Facility Code Facility Name Boiler ID

8223 Springerville Generating Station 4Control Device Configuraton

Listed (by

boiler) in Question 16 (page 17) of the questionnaireEIA

Facility Code Facility Name Boiler ID 8223 Springerville Generating Station 4

Parameter Sample 1 Sample 2 Sample 3 Date of Testing Steam Output (1000 lb/hr) Total Heat Input (MMBtu/hr) Basis (W et/Dry) Exhaust Steam % Moisture Exhaust Flow Rate (acfm or dscfm) Exhaust Temperature (deg C or deg F)

Fuel Type Selection Fuel Input Rate Sample 1 Fuel Input Rate

Sample 2 Fuel Input Rate

Sample 3 subbituminous

Emission Test Results CO Emission Rate Sample 1 (lb/MMBtu) CO Emission Rate Sample 1 (ppmvd @ 7% O2) CO Emission Rate Sample 2 (lb/MMBtu)Unit of Measure Other Supporting Information

1000 lb/hr MMBtu/hr N/A %

Unit of Measure Fuel Flow Me asurement Method Other Supporting

Information lb/hour Other Facility DMS

CO Emission Rate Sample 2 (ppmvd @ 7% O2) CO Emission Rate Sample 3 (lb/MMBtu) CO Emission Rate Sample 3 (ppmvd @ 7% O2) Test Method Used (ex. U.S. EPA Method 10A) Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 8223 Springerville Generating Station 4

Parameter Sample 1 Sample 2 Date of Testing 5/8/2010 5/9/2010 Steam Output (1000 lb/hr) Total Heat Input (MMBtu/hr) 3910.433 3968.067 Basis (W et/Dry) Wet We t Exhaust Steam % Moisture 15.6 15.6 Exhaust Flow Rate (acfm or dscfm) 834669.1 847024.3 Exhaust Temperature (deg C or deg F) 195.1 195.0

Fuel Type Selection Fuel Input Rate Sample 1 Fuel Input Rate Sample 2 subbituminous 452458.9 453056.7

Emission Test Results Methane Emission Rate Sample 1 (lb/MMBtu) Methane Emission Rate Sample 1 (ppmvd @ 7% O2) 4.335E-05 0.0710Sample 3 Unit of Measure Other Supporting Information 5/9/2010 1000 lb/hr No data available 3888.800 MMBtu/hr Facility process data We t N/A 15.8 % Unit CEMS 832041.0 dscfm Calculated from Facility DMS 192.1 deg F Facility process data
Fuel Input Rate Sample 3 Unit of Measure Fuel Flow Measurement Method Other Supporting Information 458622.2 lb/hour Other Facility DMS

Methane Emission Rate Sample 2 (lb/MMBtu) Methane Emission Rate Sample 2 (ppmvd @ 7% O2) Methane Emission Rate Sample 3 (lb/MMBtu) Methane Emission Rate Sample 3 (ppmvd @ 7% O2) 1.875E-05 0.0307 3.110E-05 0.0509Test Method Used

(ex. U.S. EPA Method 18) Other Supporting Information U.S. EPA Method 18 0.0681,0.0295,0.0489,ADL,Zero gas standards were analy zed with results ranging from -0.20 to 0.30 ppmv and sample concentrations ranged from 0.07 to 0.05 ppmv. The analyte may not actually

be present in the samples.0.0681,0.0295,0.0489,ADL,Zero gas standards were analy zed with results ranging from -0.20 to 0.30 ppmv and sample concentrations ranged from 0.07 to 0.05 ppmv. The analyte may not actually

be present in the samples.0.0681,0.0295,0.0489,ADL,Zero gas standards were analy zed with results ranging from -0.20 to 0.30 ppmv and sample concentrations ranged from 0.07 to 0.05 ppmv. The analyte may not actually

be present in the samples.EIA

Facility Code Facility Name Boiler ID 8223 Springerville Generating Station 4

Parameter Sample 1 Sample 2 Date of Testing 5/7/2010 5/7/2010 Steam Output (1000 lb/hr) Total Heat Input (MMBtu/hr) 3990.166667 3982.633333 Basis (W et/Dry) Wet We t Exhaust Steam % Moisture 15.03333333 15.13333333 Exhaust Flow Rate (acfm or dscfm) 859716.3352 854083.9889 Exhaust Temperature (deg C or deg F) 188.6666667 189.0333333

Fuel Type Selection Fuel Input Rate Sample 1 Fuel Input Rate Sample 2 subbituminous 455285.5667 455746.6667

Emission Test Results Total Vapor Phase Me rcury Emission Rate Sample 1 (lb/MMBtu) Total Vapor Phase

Me rcury Emission Rate Sample 2 (lb/MMBtu) 2.56809E-06 4.21354E-06Sample 3 Unit of Measure Other Supporting Information 5/7/2010 1000 lb/hr No data available 3927.7 MMBtu/hr Facility process data We t N/A 15.3 % Unit CEMS 846242.4056 dscfm Calculated from Facility DMS 189.3 deg F Facility process data
Fuel Input Rate Sample 3 Unit of Measure Fuel Flow Measurement Method Other Supporting Information 457993.3333 lb/hour Other Facility DMS

Total Vapor Phase Me rcury Emission Rate Sample 3 (lb/MMBtu) Test Method Used

(ex. U.S. EPA

Method 30B) Other Supporting Information 3.96526E-06 U.S. EPA Method 30B 147.25,246.1,233.7,ADL,Met all method QA/QC. See Unit 4 ERT Addendum.147.25,246.1,233.7,ADL,Met all method QA/QC. See Unit 4 ERT Addendum.EIA

Facility Code Facility Name Boiler ID 8223 Springerville Generating Station 4

Parameter Sample 1 Sample 2 Date of Testing Steam Output (1000 lb/hr) Total Heat Input (MMBtu/hr) Basis (W et/Dry) Exhaust Steam % Moisture Exhaust Flow Rate (acfm or dscfm) Exhaust Temperature (deg C or deg F)

Fuel Type Selection Fuel Input Rate Sample 1 Fuel Input Rate Sample 2

Emission Test Results Constituent Consitutent Emission Rate Sample 1 (%) O 2 CO 2Sample 3 Unit of Measure Other Supporting Information

1000 lb/hr MMBtu/hr N/A %

Fuel Input Rate Sample 3 Unit of Measure Fuel Flow Me asurement Method Other Supporting Information

Consitutent Emission Rate

Sample 2 (%) Consitutent Emission Rate Sample 3 (%) Test Method Used

(ex. U.S. EPA

Method 3B) Other Supporting InformationEIA

Facility Code Facility Name Boiler ID 8223 Springerville Generating Station 4

Parameter Sample 1 Sample 2 Date of Testing 5/9/2010 5/9/2010 Steam Output (1000 lb/hr) Total Heat Input (MMBtu/hr) 3819.366667 3833.333333 Basis (W et/Dry) Wet We t Exhaust Steam % Moisture 15.76666667 15.6 Exhaust Flow Rate (acfm or dscfm) 813394.5 818262.7 Exhaust Temperature (deg C or deg F) 185.7 185.3

Fuel Type Selection Fuel Input Rate Sample 1 Fuel Input Rate Sample 2 subbituminous 456845.5667 450080

Emission Test Results Hydroden Cyanide Emission Rate Sample 1 (lb/MMBtu) Hydroden Cyanide Emission Rate Sample 1 (ppmvd @ 7% O2) 7.210E-04 6.994E-01Sample 3 Unit of Measure Other Supporting Information 5/10/2010 1000 lb/hr No data available 4056.033333 MMBtu/hr Facility process data We t N/A

15.43333333 % Unit CEMS 867809.0 dscfm Calculated from Facility DMS 188.8 Facility process data
Fuel Input Rate Sample 3 Unit of Measure Fuel Flow Measurement Method 460234.4333 lb/hour Other

Hydroden Cyanide Emission Rate Sample 2 (lb/MMBtu) Hydroden Cyanide

Emission Rate Sample 2 (ppmvd @ 7% O2) Hydroden Cyanide Emission Rate Sample 3 (lb/MMBtu) 2.748E-04 2.666E-01 7.911E-04Other Supporting

Information Facility DMS

Hydroden Cyanide Emission Rate Sample 3 (ppmvd @ 7% O2) Test Method Used (ex. U.S. EPA Method 18) Other Supporting Information 7.674E-01 U.S. EPA Method 320 0.7069,0.2697,0.7506,ADLEIA

Facility Code Facility Name Boiler ID 8223 Springerville Generating Station 4

Parameter Sample 1 Sample 2 Date of Testing 5/9/2010 5/9/2010 Steam Output (1000 lb/hr) Total Heat Input (MMBtu/hr) 3819.366667 3833.333333 Basis (W et/Dry) Wet We t Exhaust Steam % Moisture 15.76666667 15.6 Exhaust Flow Rate (acfm or dscfm) 813394.5 818262.7 Exhaust Temperature (deg C or deg F) 185.7 185.3

Fuel Type Selection Fuel Input Rate Sample 1 Fuel Input Rate Sample 2 subbituminous 456845.5667 450080

Emission Test Results Hydroden Chloride Emission Rate Sample 1 (lb/MMBtu) Hydroden Chloride Emission Rate Sample 1 (ppmvd @ 7% O2) 6.582E-03 4.723E+00Sample 3 Unit of Measure Other Supporting Information 5/10/2010 1000 lb/hr No data available 4056.033333 MMBtu/hr Facility process data We t N/A

15.43333333 % Unit CEMS 867809.0 dscfm Calculated from Facility DMS 188.8 Facility process data
Fuel Input Rate Sample 3 Unit of Measure Fuel Flow Measurement Method 460234.4333 lb/hour Other

Hydroden Chloride Emission Rate Sample 2 (lb/MMBtu) Hydroden Chloride

Emission Rate Sample 2 (ppmvd @ 7% O2) Hydroden Chloride Emission Rate Sample 3 (lb/MMBtu) 7.329E-03 5.259E+00 2.850E-05Other Supporting

Information Facility DMS

Hydroden Chloride Emission Rate Sample 3 (ppmvd @ 7% O2) Test Method Used (ex. U.S. EPA Method 18) Other Supporting Information 2.045E-02 U.S. EPA Method 320 4.7734,5.3198,[<0.02],DLLEIA

Facility Code Facility Name Boiler ID 8223 Springerville Generating Station 4

Parameter Sample 1 Sample 2 Date of Testing 5/9/2010 5/9/2010 Steam Output (1000 lb/hr) Total Heat Input (MMBtu/hr) 3819.366667 3833.333333 Basis (W et/Dry) Wet We t Exhaust Steam % Moisture 15.76666667 15.6 Exhaust Flow Rate (acfm or dscfm) 813394.5 818262.7 Exhaust Temperature (deg C or deg F) 185.7 185.3

Fuel Type Selection Fuel Input Rate Sample 1 Fuel Input Rate Sample 2 subbituminous 456845.5667 450080

Emission Test Results Hydroden Floride Emission Rate Sample 1 (lb/MMBtu) Hydroden Floride Emission Rate Sample 1 (ppmvd @ 7% O2) 2.660E-04 3.483E-01Sample 3 Unit of Measure Other Supporting Information 5/10/2010 1000 lb/hr No data available 4056.033333 MMBtu/hr Facility process data We t N/A

15.43333333 % Unit CEMS 867809.0 dscfm Calculated from Facility DMS 188.8 deg F Facility process data
Fuel Input Rate Sample 3 Unit of Measure Fuel Flow Measurement Method 460234.4333 lb/hour Other

Hydroden Floride Emission Rate Sample 2 (lb/MMBtu) Hydroden Floride

Emission Rate Sample 2 (ppmvd @ 7% O2) Hydroden Floride Emission Rate Sample 3 (lb/MMBtu) 2.525E-04 3.307E-01 2.243E-04Other Supporting

Information Facility DMS

Hydroden Floride Emission Rate Sample 3 (ppmvd @ 7% O2) Test Method Used (ex. U.S. EPA Method 18) Other Supporting Information 2.937E-01 U.S. EPA Method 320 0.352,0.3345,0.2873,ADLEIA

Facility Code Facility Name Boiler ID 8223 Springerville Generating Station 4

Parameter Sample 1 Sample 2 Date of Testing Steam Output (1000 lb/hr) Total Heat Input (MMBtu/hr) Basis (W et/Dry) Exhaust Steam % Moisture Exhaust Flow Rate (acfm or dscfm) Exhaust Temperature (deg C or deg F)

Fuel Type Selection Fuel Input Rate Sample 1 Fuel Input Rate Sample 2

Emission Test Results Constituent Nitrogen Oxides Emission Rate Sample 1 (lb/MMBtu) NO NO 2Sample 3 Unit of Measure Other Supporting Information

1000 lb/hr MMBtu/hr N/A %

Fuel Input Rate Sample 3 Unit of Measure Fuel Flow Measurement Method

Nitrogen Oxides Emission Rate

Sample 1 (ppmvd @ 7% O2) Nitrogen Oxides Emission Rate Sample 2 (lb/MMBtu) Nitrogen Oxides Emission Rate Sample 2 (ppmvd @ 7% O2)Other Supporting Information

Nitrogen Oxides Emission Rate

Sample 3 (lb/MMBtu) Nitrogen Oxides Emission Rate Sample 3 (ppmvd @ 7% O2) Test Method Used (ex. U.S. EPA

Method 7)Other Supporting

InformationEIA

Facility Code Facility Name Boiler ID 8223 Springerville Generating Station 4

Parameter Sample 1 Sample 2 Date of Testing Steam Output (1000 lb/hr) Total Heat Input (MMBtu/hr) Basis (W et/Dry) Exhaust Steam % Moisture Exhaust Flow Rate (acfm or dscfm) Exhaust Temperature (deg C or deg F)

Fuel Type Selection Fuel Input Rate Sample 1 Fuel Input Rate Sample 2

Emission Test Results Constituent Sulfur Dioxide Emission Rate Sample 1 (lb/MMBtu) SO 2Sample 3 Unit of Measure Other Supporting Information

1000 lb/hr MMBtu/hr N/A %

Fuel Input Rate Sample 3 Unit of Measure Fuel Flow Measurement Method

Sulfur Dioxide Emission Rate

Sample 1 (ppmvd @ 7% O2) Sulfur Dioxide Emission Rate Sample 2 (lb/MMBtu) Sulfur Dioxide Emission Rate Sample 2 (ppmvd @ 7% O2)Other Supporting Information

Sulfur Dioxide Emission Rate

Sample 3 (lb/MMBtu) Sulfur Dioxide Emission Rate Sample 3 (ppmvd @ 7% O2) Test Method Used (ex. U.S. EPA

Method 7)Other Supporting

InformationEIA

Facility Code Facility Name Boiler ID 8223 Springerville Generating Station 4

Parameter Sample 1 Sample 2 Date of Testing Steam Output (1000 lb/hr) Total Heat Input (MMBtu/hr) Basis (W et/Dry) Exhaust Steam % Moisture Exhaust Flow Rate (acfm or dscfm) Exhaust Temperature (deg C or deg F)

Fuel Type Selection Fuel Input Rate Sample 1 Fuel Input Rate Sample 2

Emission Test Results Constituent Constituent Emission Rate Sample 1 (mg solids/liter) Total Dissolved Solids (TDS) Total Suspended Solids (TSS)Sample 3 Unit of Measure

1000 lb/hr MMBtu/hr N/A %

Fuel Input Rate Sample 3 Unit of Measure

Constituent Emission Rate

Sample 2 (mg solids/liter) Constituent Emission Rate Sample 3 (mg solids/liter)Other Supporting Information

Fuel Flow Measurement Method

Test Method Used (ex. Standard Test Method for Filterable and Nonfilterable Matter in Water ASTM D5907)Other Supporting

Information

Other Supporting Information