CHAPTER 1. INTRODUCTION

TABLE OF CONTENTS

1.1	 PURPOSE OF THE DOCUMENT ................................................................................. 1­1
 

1.2	 OVERVIEW OF ASHRAE STANDARD 90.1 COMMERCIAL EQUIPMENT

ENERGY CONSERVATION STANDARDS ................................................................ 1­1

1.3	 OVERVIEW OF THE ENERGY CONSERVATION STANDARDS AND ASHRAE

STANDARD 90.1­2007 FOR COMMERCIAL PACKAGED BOILERS ..................... 1­2

1.4	 STRUCTURE OF THE DOCUMENT............................................................................ 1­3
 

1­i

EERE-2008-BT-STD-0013 COMMENT 06
    

     

                       

                             

                   

                     

                 

                 

                   

       

         

                           

                             

                       

                           

                     

                       

                           

   

                 

                     

                       

                     

                         

                         

                               

                           

                 

                         

                           

                           

                             

                         

                         

                       

                                                

         

CHAPTER 1. INTRODUCTION
 

1.1 PURPOSE OF THE DOCUMENT
 

This technical support document (TSD) is a stand­alone report that documents the

technical analyses and results in support of the information presented in the Notice of Proposed

Rulemaking (NOPR) for establishing amended energy conservation standards for certain

commercial and industrial equipment covered by the American National Standards Institute

(ANSI)/ American Society of Heating, Refrigerating and Air­Conditioning Engineers

(ASHRAE) /Illuminating Engineering Society of North America (IESNA) Standard 90.1­2007

Energy Standard for Buildings Except Low­Rise Residential Buildings (ASHRAE Standard 90.1­

2007),a including commercial packaged boilers.

1.2	 OVERVIEW OF ASHRAE STANDARD 90.1 COMMERCIAL EQUIPMENT

ENERGY CONSERVATION STANDARDS

Title III of the Energy Policy and Conservation Act (EPCA), Pub. L. 94­163, as

amended, sets forth a variety of provisions concerning energy efficiency. Part A­1 of Title III

created the energy conservation program for certain industrial equipment. (42 U.S.C. 6311­6317)

In general, this program addresses the energy efficiency of certain types of commercial and

industrial equipment. Part A­1 specifically includes definitions (42 U.S.C. 6311), energy

conservation standards (42 U.S.C. 6313), test procedures (42 U.S.C. 6314), labeling provisions

(42 U.S.C. 6315), and the authority to require information and reports from manufacturers (42

U.S.C. 6316).

EPCA contains mandatory energy conservation standards for commercial heating, airconditioning, and water­heating equipment. (42 U.S.C. 6313(a)) Specifically, the statute sets

standards for small, large, and very large commercial package air­conditioning and heating

equipment, packaged terminal air conditioners (PTACs) and packaged terminal heat pumps

(PTHPs), warm air furnaces, packaged boilers, storage water heaters, and unfired hot water

storage tanks. Id. In doing so, EPCA established Federal energy conservation standards that

generally correspond to the levels in ASHRAE Standard 90.1, as in effect on October 24, 1992

(i.e., ASHRAE Standard 90.1­1989), for each type of covered equipment listed in 42 U.S.C.

6313(a).

In acknowledgement of technological changes that yield energy efficiency benefits,

Congress further directed DOE through EPCA to consider amending the existing Federal energy

conservation standard for each type of equipment listed, each time ASHRAE Standard 90.1 is

amended with respect to such equipment. (42 U.S.C. 6313(a)(6)(A)) For each type of equipment,

EPCA directs that if ASHRAE Standard 90.1 is amended, DOE must adopt amended standards at

the new efficiency level in ASHRAE Standard 90.1, unless clear and convincing evidence

supports a determination that adoption of a more stringent level would produce significant

additional energy savings and be technologically feasible and economically justified. (42 U.S.C.

a For more information see www.ashrae.org

1­1

EERE-2008-BT-STD-0013 COMMENT 06
                           

                             

                   

                         

                       

                     

                           

                     

                              

                         

         

             

         

                           

                         

                         

                             

                                 

                               

        

                     

                                   

                         

                       

                             

                             

                         

                         

                               

   

                             

                     

                    

                       

                          

                           

                 

                             

                             

6313(a)(6)(A)(ii)) If DOE decides to adopt as a national standard the efficiency levels specified

in the amended ASHRAE Standard 90.1, DOE must establish such standard not later than 18

months after publication of the amended industry standard. (42 U.S.C. 6313(a)(6)(A)(ii)(I))

However, if DOE determines that a more­stringent standard is justified under 42 U.S.C.

6313(a)(6)(A)(ii)(II), then it must establish such more­stringent standard not later than 30

months after publication of the amended ASHRAE Standard 90.1. (42 U.S.C. 6313(a)(6)(B))

DOE considers stakeholder participation to be a very important part of the process for

setting energy conservation standards. DOE actively encourages the participation and interaction

of all stakeholders during the comment period in each stage of the rulemaking. During comment

periods, interactions among stakeholders provide a balanced discussion of the information that is

required for the standards rulemaking.

1.3	 OVERVIEW OF THE ENERGY CONSERVATION STANDARDS AND ASHRAE

STANDARD 90.1­2007 FOR COMMERCIAL PACKAGED BOILERS

EPCA defines a “packaged boiler” as “a boiler that is shipped complete with heating

equipment, mechanical draft equipment, and automatic controls; usually shipped in one or more

sections.” (42 U.S.C. 6311(11)(B)) In its regulations, DOE further refined the “packaged boiler”

definition to exclude a boiler that is custom designed and field constructed. 10 CFR 431.102.

Additionally, if the boiler is shipped in more than one section, the sections may be produced by

more than one manufacturer, and may be originated or shipped at different times and from more

than one location. Id.

The current Federal energy conservation standards separate commercial packaged boilers

only by the type of fuel used by the boiler, creating two equipment classes: (1) gas­fired, and (2)

oil­fired. (42 U.S.C. 6313(a)(4)(C)­(D); 10 CFR 431.87) As set forth below, EPCA specified

minimum Federal standards for commercial packaged boilers manufactured on or after January

1, 1994. Id. The minimum combustion efficiency at the maximum rated capacity of a gas­fired

packaged boiler with capacity of 300,000 Btu/h (British thermal units per hour) (300 kBtu/h) or

more must be 80 percent. (42 U.S.C. 6313(a)(4)(C); 10 CFR 431.87(a)) The minimum

combustion efficiency at the maximum rated capacity of an oil­fired packaged boiler with

capacity of 300,000 Btu/h or more must be 83 percent. (42 U.S.C. 6313 (a)(4)(D); 10 CFR

431.87(b))

On January 9, 2008, the ASHRAE Board of Directors gave final approval to ASHRAE

Standard 90.1­2007, which ASHRAE officially released on January 10, 2008. ASHRAE

Standard 90.1­2007 addresses efficiency levels for several equipment classes of commercial

packaged boilers. The amended ASHRAE Standard 90.1 (ASHRAE Standard 90.1­2007)

revised the efficiency levels for commercial packaged boilers specified in ASHRAE Standard

90.1­2007. ASHRAE Standard 90.1­2007 divides boilers into 10 equipment classes (in place of

the two specified in EPCA), and changes the efficiency metric from combustion efficiency to

thermal efficiency for 8 of the 10 equipment classes.

On July 16, 2008, DOE published a notice of data availability (July 2008 NODA) and

request for public comment in the Federal Register as a preliminary step pursuant to EPCA’s

1­2

EERE-2008-BT-STD-0013 COMMENT 06
                         

                         

                           

                       

                       

                         

                       

                 

                           

                         

                             

                       

                               

  

     

                          

       

                       

                     

         

                   

                       

               

     

                       

                     

               

                       

                     

                       

   

                     

               

               

         

requirements for DOE to consider amended energy conservation standards for certain types of

commercial equipment covered by ASHRAE Standard 90.1. 73 FR 40770 (July 16, 2008).

Specifically, the July 2008 NODA presented for public comment DOE’s analysis of the potential

energy savings estimates for amended national energy conservation standards for types of

commercial equipment based on: (1) the modified efficiency levels contained within ASHRAE

Standard 90.1­2007; and (2) more­stringent efficiency levels. Id. at 40772. DOE has described

these analyses and preliminary conclusions and sought input from interested parties, including

the submission of data and other relevant information. Id.

After receiving public comment on the July 2008 NODA, DOE revised its analysis for

commercial packaged boilers used in the NODA and summarized the assumptions and presents

the results in this TSD. In addition, DOE conducted several other analyses in preparation for

publishing this notice of proposed rulemaking (NOPR) and TSD for commercial packaged

boilers. A list of the analyses and the corresponding Chapter number is presented in the next

section.

1.4 STRUCTURE OF THE DOCUMENT

This NOPR TSD outlines the analytical approaches used in this rulemaking. The TSD

consists of seven chapters.

Chapter 1	 Introduction: provides an overview of the appliance standards program

and how it applies to the ASHRAE equipment rulemaking, and outlines

the structure of the document.

Chapter 2	 Market Assessment: characterizes the commercial packaged boiler

market.

Chapter 3	 Engineering Analysis: discusses the methods used for developing the

relationship incremental contractor cost and increased efficiency for

commercial packaged boilers.

Chapter 4	 Energy Use Characterization: discusses the process used for generating

energy use estimates of commercial packaged boilers for a variety of

equipment classes, climate locations, and potential amended standard

levels.

Chapter 5	 Life­Cycle Cost and Payback Period Analyses: discusses the economic

effects of standards on commercial customers and users of the equipment

and compares the LCC and PBP of equipment with and without higher

energy conservation standards.

Chapter 6	 Shipments Analysis: discusses the methods used for forecasting

shipments with and without higher energy conservation standards,

including how equipment purchase decisions are economically influenced

and modeled with econometric equations.

1­3

EERE-2008-BT-STD-0013 COMMENT 06
                       

                 

                 

                 

                

               

                   

       

                  

               

Chapter 7 National Impact Analysis: discusses the methods used for forecasting

national energy consumption and national economic impacts based on

annual equipment shipments and estimates of future equipment efficiency

distributions in the absence and presence of higher energy conservation

standards.

Chapter 8 Environmental Assessment: discusses the environmental effects of

amended energy conservation standards, including the impact on

emissions of three pollutants: sulfur dioxide (SO2), nitrogen oxides (NOX),

and carbon dioxide (CO2).

Chapter 9 Emissions Monetization: discusses the monetization analysis of potential

emissions reductions resulting from higher energy conservation standards.

1­4

EERE-2008-BT-STD-0013 COMMENT 06