Name: Julie Metts

Title: Director - Air Quality

Company: Santee Cooper

Sign Date: 9/2/2010

Name: Craig McKenzie

Title: Senior Project Manager

Company: GEL, Engineering

Sign Date: 9/2/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Santee Cooper - Jefferies Generating Station Unit #2

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 03, 2011 Page 1 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Facility Information:

Santee Cooper - Jefferies Generating Station

463 Powerhouse Road

Monks Corner SC 29461

Contact: Julie Metts, P.E.

Phone: 843-761-800, ext. 4688

Fax: 843-761-4156

Email: jjmetts@santeecooper.com

Testing Company:

GEL Engineering, LLC

2040 Savage Road

Charleston SC 29407

Contact:Craig McKenzie, QSTI

Phone: 843-769-7378

Fax: 843-769-7397

Email: cam2@gel.com

Air Permit Number:

TV-0420-0003

Permitted Source ID/Name:

Unit #2

Permitted Maximum Process Rate:

598 MMBtu/hr

Max. Normal Operation Process Rate:

598 MMBtu/hr

Target Process Test Rate

598 MMBtu/hr

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 4501500003 FRS #: 4911

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exhaust 78 0 0 78 300 560 4 48

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exhaust Carbon Monoxide Method 10 3 180 0

Stack Exhaust 2,3,7,8-TCDD Method 23 3 480 0

Stack Exhaust 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exhaust 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exhaust 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Stack Exhaust 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Regulation Description Compound Limit Unit

NA 0

Thursday, February 03, 2011 Page 2 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Stack Exhaust 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exhaust OCDD Method 23 3 480 0

Stack Exhaust 2,3,7,8-TCDF Method 23 3 480 0

Stack Exhaust 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exhaust 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exhaust 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exhaust 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exhaust 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exhaust 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exhaust 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exhaust 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exhaust OCDF Method 23 3 480 0

Stack Exhaust Other TCDD Method 23 3 480 0

Stack Exhaust Other PeCDD Method 23 3 480 0

Stack Exhaust Other HxCDD Method 23 3 480 0

Stack Exhaust Other HpCDD Method 23 3 480 0

Stack Exhaust Other TCDF Method 23 3 480 0

Stack Exhaust Other PeCDF Method 23 3 480 0

Stack Exhaust Other HxCDF Method 23 3 480 0

Stack Exhaust Other HpCDF Method 23 3 480 0

Stack Exhaust 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exhaust 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exhaust 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exhaust 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exhaust 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exhaust 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exhaust 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exhaust Method 23 3 480 0

Stack Exhaust 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exhaust 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exhaust Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Stack Exhaust Method 25A 3 180 0

Stack Exhaust Hydrogen Fluoride Method 26A 3 180 0

Stack Exhaust Hydrogen Chloride Method 26A 3 180 0

Stack Exhaust Manganese Method 29 3 240 0

Stack Exhaust Chromium Method 29 3 240 0

Stack Exhaust Cadmium Method 29 3 240 0

Stack Exhaust Beryllium Method 29 3 240 0

Stack Exhaust Cobalt Method 29 3 240 0

Stack Exhaust Lead Method 29 3 240 0

Stack Exhaust Antimony Method 29 3 240 0

Stack Exhaust Nickel Method 29 3 240 0

Stack Exhaust Mercury Method 29 3 240 0

Stack Exhaust Selenium Method 29 3 240 0

Stack Exhaust Phosphorus (yellow or white) Method 29 3 240 0

Stack Exhaust Arsenic Method 29 3 240 0

Organic Condensible 

Particulate

Stack Exhaust Method 5/OTM-28 3 240 0

Inorganic (Aqueous) 

Condensible Part.

Stack Exhaust Method 5/OTM-28 3 240 0

Thursday, February 03, 2011 Page 3 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

NA

Stack Exhaust Filterable Particulate Method 5/OTM-28 3 240 0

Stack Exhaust Sulfur Dioxide Method 6C 3 180 0

Thursday, February 03, 2011 Page 4 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Sampling / Stack Data Results Summary

Location Stack Exhaust - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exhaust - Method 23

Average

Run Number 1 2 3

Test Date 7/14/2010 7/15/2010 7/16/2010

Run Start Time 8:00:00 AM 10:15:00 

AM

7:55:00 AM

Run Finish Time 3:50:00 PM 6:05:00 PM 3:45:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 252.340 254.224 248.516 251.693

Moisture Content of Stack Gas, % 9.63 9.49 9.48 9.533

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 8.49 7.89 8.44 8.273

Oxygen, % 9.38 10.29 9.61 9.760

Average Stack Gas Temperature, °F 408.75 411.04 414.17 411.320

Dry Volumetric Flow Rate, dry scfm 89,608.2 89,016.7 91,821.8 90,148.900

Actual Wet Volumetric Flue Gas Flow Rate, acfm 164,136.4 162,683.0 168,337.4 165,052.267

Percent Isokinetic of Sampling Rate, % 98.9 100.3 95.0 98.067

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 03, 2011 Page 5 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Location Stack Exhaust - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exhaust - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 03, 2011 Page 6 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Location Stack Exhaust - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exhaust - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 03, 2011 Page 7 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Location Stack Exhaust - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, February 03, 2011 Page 8 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Emissions Summary

Location: Stack Exhaust - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

Elb/hr 1.09E+00 6.57E-01 7.22E-02 0.606

lb/mmBtuO2 3.30E-03 1.93E-03 2.13E-04 0.002

ppm 2.71E+00 1.59E+00 1.77E-01 1.492

ppm@7%O2 3.28E+00 1.91E+00 2.13E-01 1.801

Location: Stack Exhaust - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000201 0.000000142 0.0000000216 0.000

Elb/hr 9.44E-10 6.58E-09 1.06E-09 0.000

lb/mmBtuO2 2.93E-12 2.23E-11 3.26E-12 0.000

ng/dscm 2.81E-03 1.97E-02 3.07E-03 0.009

ng/dscm@7%O2 3.39E-03 2.58E-02 3.78E-03 0.011

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000137 0.0000000258 0.0000000104 0.000

Elb/hr 6.44E-10 1.19E-09 5.08E-10 0.000

lb/mmBtuO2 2.00E-12 4.05E-12 1.57E-12 0.000

ng/dscm 1.92E-03 3.58E-03 1.48E-03 0.002

ng/dscm@7%O2 2.32E-03 4.69E-03 1.82E-03 0.003

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000398 0.00000000572 0.00000000179 0.000

Elb/hr 1.87E-10 2.65E-10 8.75E-11 0.000

lb/mmBtuO2 5.80E-13 8.98E-13 2.70E-13 0.000

ng/dscm 5.57E-04 7.95E-04 2.54E-04 0.001

ng/dscm@7%O2 6.72E-04 1.04E-03 3.13E-04 0.001

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000352 0.000000005 0.00000000296 0.000

Elb/hr 1.65E-10 2.32E-10 1.45E-10 0.000

lb/mmBtuO2 5.13E-13 7.85E-13 4.47E-13 0.000

ng/dscm 4.93E-04 6.95E-04 4.21E-04 0.001

ng/dscm@7%O2 5.95E-04 9.11E-04 5.18E-04 0.001

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000768 0.00000000944 0.000000007 0.000

Elb/hr 3.61E-10 4.37E-10 3.42E-10 0.000

Thursday, February 03, 2011 Page 9 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

lb/mmBtuO2 1.12E-12 1.48E-12 1.06E-12 0.000

ng/dscm 1.07E-03 1.31E-03 9.95E-04 0.001

ng/dscm@7%O2 1.29E-03 1.72E-03 1.23E-03 0.001

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000056 0.0000000174 0.00000000488 0.000

Elb/hr 2.63E-10 8.06E-10 2.39E-10 0.000

lb/mmBtuO2 8.16E-13 2.73E-12 7.36E-13 0.000

ng/dscm 7.84E-04 2.42E-03 6.94E-04 0.001

ng/dscm@7%O2 9.46E-04 3.17E-03 8.54E-04 0.002

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000548 0.00000000996 0.00000000636 0.000

Elb/hr 2.57E-10 4.61E-10 3.11E-10 0.000

lb/mmBtuO2 7.98E-13 1.56E-12 9.60E-13 0.000

ng/dscm 7.67E-04 1.38E-03 9.04E-04 0.001

ng/dscm@7%O2 9.25E-04 1.81E-03 1.11E-03 0.001

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000388 0.0000000096 0.00000000316 0.000

Elb/hr 1.82E-10 4.45E-10 1.54E-10 0.000

lb/mmBtuO2 5.65E-13 1.51E-12 4.77E-13 0.000

ng/dscm 5.43E-04 1.33E-03 4.49E-04 0.001

ng/dscm@7%O2 6.55E-04 1.74E-03 5.53E-04 0.001

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000364 0.00000000572 0.00000000228 0.000

Elb/hr 1.71E-10 2.65E-10 1.11E-10 0.000

lb/mmBtuO2 5.30E-13 8.98E-13 3.44E-13 0.000

ng/dscm 5.09E-04 7.95E-04 3.24E-04 0.001

ng/dscm@7%O2 6.14E-04 1.04E-03 3.99E-04 0.001

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000436 0.00000000544 0.00000000332 0.000

Elb/hr 2.05E-10 2.52E-10 1.62E-10 0.000

lb/mmBtuO2 6.35E-13 8.54E-13 5.01E-13 0.000

ng/dscm 6.10E-04 7.56E-04 4.72E-04 0.001

ng/dscm@7%O2 7.36E-04 9.90E-04 5.81E-04 0.001

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000194 0.0000000088 0.0000000139 0.000

Elb/hr 9.11E-10 4.08E-10 6.79E-10 0.000

Thursday, February 03, 2011 Page 10 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

lb/mmBtuO2 2.83E-12 1.38E-12 2.10E-12 0.000

ng/dscm 2.72E-03 1.22E-03 1.98E-03 0.002

ng/dscm@7%O2 3.28E-03 1.60E-03 2.44E-03 0.002

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000005 0.0000005 0.0000005 0.000

Elb/hr 2.35E-08 2.32E-08 2.44E-08 0.000

lb/mmBtuO2 7.28E-11 7.85E-11 7.55E-11 0.000

ng/dscm 7.00E-02 6.95E-02 7.11E-02 0.070

ng/dscm@7%O2 8.45E-02 9.11E-02 8.75E-02 0.088

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.000001 0.000001 0.000001 0.000

Elb/hr 4.70E-08 4.63E-08 4.89E-08 0.000

lb/mmBtuO2 1.46E-10 1.57E-10 1.51E-10 0.000

ng/dscm 1.40E-01 1.39E-01 1.42E-01 0.140

ng/dscm@7%O2 1.69E-01 1.82E-01 1.75E-01 0.175

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.00000134 0.00000143 0.00000106 0.000

Elb/hr 6.29E-08 6.62E-08 5.18E-08 0.000

lb/mmBtuO2 1.95E-10 2.24E-10 1.60E-10 0.000

ng/dscm 1.88E-01 1.99E-01 1.51E-01 0.179

ng/dscm@7%O2 2.27E-01 2.61E-01 1.86E-01 0.225

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000005 0.0000005 0.0000005 0.000

Elb/hr 2.35E-08 2.32E-08 2.44E-08 0.000

lb/mmBtuO2 7.28E-11 7.85E-11 7.55E-11 0.000

ng/dscm 7.00E-02 6.95E-02 7.11E-02 0.070

ng/dscm@7%O2 8.45E-02 9.11E-02 8.75E-02 0.088

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.0000005 0.0000005 0.0000005 0.000

Elb/hr 2.35E-08 2.32E-08 2.44E-08 0.000

lb/mmBtuO2 7.28E-11 7.85E-11 7.55E-11 0.000

ng/dscm 7.00E-02 6.95E-02 7.11E-02 0.070

ng/dscm@7%O2 8.45E-02 9.11E-02 8.75E-02 0.088

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.00000338 0.00000348 0.00000257 0.000

Elb/hr 1.59E-07 1.61E-07 1.26E-07 0.000

Thursday, February 03, 2011 Page 11 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

lb/mmBtuO2 4.92E-10 5.46E-10 3.88E-10 0.000

ng/dscm 4.73E-01 4.83E-01 3.65E-01 0.440

ng/dscm@7%O2 5.71E-01 6.33E-01 4.49E-01 0.551

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.0000005 0.0000005 0.0000005 0.000

Elb/hr 2.35E-08 2.32E-08 2.44E-08 0.000

lb/mmBtuO2 7.28E-11 7.85E-11 7.55E-11 0.000

ng/dscm 7.00E-02 6.95E-02 7.11E-02 0.070

ng/dscm@7%O2 8.45E-02 9.11E-02 8.75E-02 0.088

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000664 0.0000000142 0.00000000624 0.000

Elb/hr 3.12E-10 6.58E-10 3.05E-10 0.000

lb/mmBtuO2 9.67E-13 2.23E-12 9.42E-13 0.000

ng/dscm 9.29E-04 1.97E-03 8.87E-04 0.001

ng/dscm@7%O2 1.12E-03 2.58E-03 1.09E-03 0.002

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000192 0.0000000102 0.0000000082 0.000

Elb/hr 9.02E-10 4.72E-10 4.01E-10 0.000

lb/mmBtuO2 2.80E-12 1.60E-12 1.24E-12 0.000

ng/dscm 2.69E-03 1.42E-03 1.17E-03 0.002

ng/dscm@7%O2 3.25E-03 1.86E-03 1.44E-03 0.002

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000692 0.00000000362 0.00000000716 0.000

Elb/hr 3.25E-10 1.68E-10 3.50E-10 0.000

lb/mmBtuO2 1.01E-12 5.68E-13 1.08E-12 0.000

ng/dscm 9.69E-04 5.03E-04 1.02E-03 0.001

ng/dscm@7%O2 1.17E-03 6.59E-04 1.26E-03 0.001

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000346 0.0000000556 0.000000303 0.000

Elb/hr 1.63E-08 2.58E-09 1.48E-08 0.000

lb/mmBtuO2 5.04E-11 8.73E-12 4.57E-11 0.000

ng/dscm 4.84E-02 7.72E-03 4.31E-02 0.033

ng/dscm@7%O2 5.84E-02 1.01E-02 5.31E-02 0.041

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.0000005 0.0000005 0.0000005 0.000

Elb/hr 2.35E-08 2.32E-08 2.44E-08 0.000

Thursday, February 03, 2011 Page 12 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

lb/mmBtuO2 7.28E-11 7.85E-11 7.55E-11 0.000

ng/dscm 7.00E-02 6.95E-02 7.11E-02 0.070

ng/dscm@7%O2 8.45E-02 9.11E-02 8.75E-02 0.088

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000005 0.0000005 0.0000005 0.000

Elb/hr 2.35E-08 2.32E-08 2.44E-08 0.000

lb/mmBtuO2 7.28E-11 7.85E-11 7.55E-11 0.000

ng/dscm 7.00E-02 6.95E-02 7.11E-02 0.070

ng/dscm@7%O2 8.45E-02 9.11E-02 8.75E-02 0.088

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.000000809 0.000000711 0.000000503 0.000

Elb/hr 3.80E-08 3.29E-08 2.46E-08 0.000

lb/mmBtuO2 1.18E-10 1.12E-10 7.59E-11 0.000

ng/dscm 1.13E-01 9.88E-02 7.15E-02 0.094

ng/dscm@7%O2 1.36E-01 1.29E-01 8.80E-02 0.118

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.0000005 0.0000005 0.0000005 0.000

Elb/hr 2.35E-08 2.32E-08 2.44E-08 0.000

lb/mmBtuO2 7.28E-11 7.85E-11 7.55E-11 0.000

ng/dscm 7.00E-02 6.95E-02 7.11E-02 0.070

ng/dscm@7%O2 8.45E-02 9.11E-02 8.75E-02 0.088

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000048 0.000000209 0.000000042 0.000

Elb/hr 2.25E-09 9.68E-09 2.05E-09 0.000

lb/mmBtuO2 6.99E-12 3.28E-11 6.34E-12 0.000

ng/dscm 6.72E-03 2.90E-02 5.97E-03 0.014

ng/dscm@7%O2 8.11E-03 3.80E-02 7.35E-03 0.018

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000118 0.0000000178 0.00000000604 0.000

Elb/hr 5.54E-10 8.24E-10 2.95E-10 0.000

lb/mmBtuO2 1.72E-12 2.79E-12 9.12E-13 0.000

ng/dscm 1.65E-03 2.47E-03 8.58E-04 0.002

ng/dscm@7%O2 1.99E-03 3.24E-03 1.06E-03 0.002

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000206 0.000000143 0.0000000196 0.000

Elb/hr 9.68E-10 6.62E-09 9.58E-10 0.000

Thursday, February 03, 2011 Page 13 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

lb/mmBtuO2 3.00E-12 2.24E-11 2.96E-12 0.000

ng/dscm 2.88E-03 1.99E-02 2.79E-03 0.009

ng/dscm@7%O2 3.48E-03 2.61E-02 3.43E-03 0.011

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000137 0.000000015 0.00000000184 0.000

Elb/hr 6.44E-10 6.95E-10 8.99E-11 0.000

lb/mmBtuO2 2.00E-12 2.35E-12 2.78E-13 0.000

ng/dscm 1.92E-03 2.08E-03 2.62E-04 0.001

ng/dscm@7%O2 2.32E-03 2.72E-03 3.23E-04 0.002

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000782 0.000000255 0.0000000904 0.000

Elb/hr 3.67E-09 1.18E-08 4.42E-09 0.000

lb/mmBtuO2 1.14E-11 4.00E-11 1.36E-11 0.000

ng/dscm 1.09E-02 3.54E-02 1.28E-02 0.020

ng/dscm@7%O2 1.32E-02 4.64E-02 1.58E-02 0.025

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000282 0.0000000692 0.0000000366 0.000

Elb/hr 1.32E-09 3.21E-09 1.79E-09 0.000

lb/mmBtuO2 4.11E-12 1.09E-11 5.52E-12 0.000

ng/dscm 3.95E-03 9.61E-03 5.20E-03 0.006

ng/dscm@7%O2 4.77E-03 1.26E-02 6.40E-03 0.008

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000108 0.00000018 0.00000012 0.000

Elb/hr 5.07E-09 8.34E-09 5.86E-09 0.000

lb/mmBtuO2 1.57E-11 2.83E-11 1.81E-11 0.000

ng/dscm 1.51E-02 2.50E-02 1.71E-02 0.019

ng/dscm@7%O2 1.82E-02 3.28E-02 2.11E-02 0.024

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000903 0.000000134 0.000000103 0.000

Elb/hr 4.24E-09 6.21E-09 5.03E-09 0.000

lb/mmBtuO2 1.32E-11 2.10E-11 1.55E-11 0.000

ng/dscm 1.26E-02 1.86E-02 1.46E-02 0.015

ng/dscm@7%O2 1.52E-02 2.44E-02 1.80E-02 0.019

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000198 0.00000035 0.000000223 0.000

Elb/hr 9.30E-09 1.62E-08 1.09E-08 0.000

Thursday, February 03, 2011 Page 14 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

lb/mmBtuO2 2.88E-11 5.49E-11 3.37E-11 0.000

ng/dscm 2.77E-02 4.86E-02 3.17E-02 0.036

ng/dscm@7%O2 3.34E-02 6.37E-02 3.90E-02 0.045

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000757 0.000000341 0.000000739 0.000

Elb/hr 3.56E-08 1.58E-08 3.61E-08 0.000

lb/mmBtuO2 1.10E-10 5.35E-11 1.12E-10 0.000

ng/dscm 1.06E-01 4.74E-02 1.05E-01 0.086

ng/dscm@7%O2 1.28E-01 6.21E-02 1.29E-01 0.106

Location: Stack Exhaust - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

Elb/hr 6.93E-01 9.02E-01 6.90E-01 0.762

lb/mmBtuO2 2.09E-03 2.64E-03 2.04E-03 0.002

ppm 1.09E+00 1.39E+00 1.07E+00 1.183

ppm@7%O2 1.32E+00 1.67E+00 1.29E+00 1.427

Location: Stack Exhaust - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 79.326 71.616 52.952 67.965

Elb/hr 9.71E+00 8.61E+00 6.43E+00 8.250

lb/mmBtuO2 2.89E-02 2.65E-02 1.92E-02 0.025

mg/dscm 2.77E+01 2.56E+01 1.86E+01 23.967

mg/dscm@7%O2 3.35E+01 3.08E+01 2.23E+01 28.867

ppm 1.83E+01 1.69E+01 1.22E+01 15.800

ppm@7%O2 2.22E+01 2.03E+01 1.47E+01 19.067

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 7.827 6.508 4.3 6.212

Elb/hr 9.58E-01 7.82E-01 5.22E-01 0.754

lb/mmBtuO2 2.85E-03 2.41E-03 1.56E-03 0.002

mg/dscm 2.73E+00 2.33E+00 1.51E+00 2.190

mg/dscm@7%O2 3.31E+00 2.80E+00 1.81E+00 2.640

ppm 3.28E+00 2.80E+00 1.81E+00 2.630

ppm@7%O2 3.97E+00 3.37E+00 2.17E+00 3.170

Location: Stack Exhaust - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.31129 0.33357 0.1606 0.268

Elb/hr 2.87E-02 3.45E-02 1.49E-02 0.026

lb/mmBtuO2 8.66E-05 1.02E-04 4.91E-05 0.000

Thursday, February 03, 2011 Page 15 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

mg/dscm 8.31E-02 8.94E-02 4.35E-02 0.072

mg/dscm@7%O2 1.00E-01 1.18E-01 5.69E-02 0.092

ppm 1.64E-02 1.77E-02 8.60E-03 0.014

ppm@7%O2 1.98E-02 2.35E-02 1.12E-02 0.018

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.021075 0.03341 0.01639 0.024

Elb/hr 1.94E-03 3.46E-03 1.52E-03 0.002

lb/mmBtuO2 5.86E-06 1.02E-05 5.01E-06 0.000

mg/dscm 5.63E-03 8.95E-03 4.44E-03 0.006

mg/dscm@7%O2 6.80E-03 1.19E-02 5.81E-03 0.008

ppm 1.81E-03 2.87E-03 1.43E-03 0.002

ppm@7%O2 2.19E-03 3.80E-03 1.87E-03 0.003

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.000094 0.000075 0.00005 0.000

Elb/hr 8.66E-06 7.77E-06 4.64E-06 0.000

lb/mmBtuO2 2.62E-08 2.30E-08 1.53E-08 0.000

mg/dscm 2.51E-05 2.01E-05 1.36E-05 0.000

mg/dscm@7%O2 3.03E-05 2.66E-05 1.78E-05 0.000

ppm 6.70E-05 5.36E-05 3.62E-05 0.000

ppm@7%O2 8.10E-05 7.10E-05 4.73E-05 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00746 0.0074 0.00399 0.006

Elb/hr 6.87E-04 7.66E-04 3.70E-04 0.001

lb/mmBtuO2 2.08E-06 2.27E-06 1.22E-06 0.000

mg/dscm 1.99E-03 1.98E-03 1.08E-03 0.002

mg/dscm@7%O2 2.41E-03 2.62E-03 1.41E-03 0.002

ppm 4.26E-04 4.24E-04 2.31E-04 0.000

ppm@7%O2 5.15E-04 5.62E-04 3.02E-04 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.07541 0.07212 0.0408 0.063

Elb/hr 6.95E-03 7.47E-03 3.79E-03 0.006

lb/mmBtuO2 2.10E-05 2.21E-05 1.25E-05 0.000

mg/dscm 2.01E-02 1.93E-02 1.11E-02 0.017

mg/dscm@7%O2 2.43E-02 2.56E-02 1.45E-02 0.021

ppm 9.31E-03 8.94E-03 5.12E-03 0.008

ppm@7%O2 1.13E-02 1.18E-02 6.70E-03 0.010

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.0168 0.01351 0.01003 0.013

Elb/hr 1.55E-03 1.40E-03 9.31E-04 0.001

Thursday, February 03, 2011 Page 16 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

lb/mmBtuO2 4.67E-06 4.14E-06 3.07E-06 0.000

mg/dscm 4.48E-03 3.62E-03 2.72E-03 0.004

mg/dscm@7%O2 5.41E-03 4.80E-03 3.56E-03 0.005

ppm 1.83E-03 1.48E-03 1.11E-03 0.001

ppm@7%O2 2.21E-03 1.96E-03 1.45E-03 0.002

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 2.12194 1.93573 1.052 1.703

Elb/hr 1.95E-01 2.00E-01 9.77E-02 0.164

lb/mmBtuO2 5.90E-04 5.93E-04 3.22E-04 0.001

mg/dscm 5.66E-01 5.19E-01 2.85E-01 0.457

mg/dscm@7%O2 6.84E-01 6.88E-01 3.73E-01 0.582

ppm 6.57E-02 6.02E-02 3.31E-02 0.053

ppm@7%O2 7.94E-02 7.98E-02 4.33E-02 0.068

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.17013 0.22343 0.1063 0.167

Elb/hr 1.57E-02 2.31E-02 9.87E-03 0.016

lb/mmBtuO2 4.73E-05 6.84E-05 3.25E-05 0.000

mg/dscm 4.54E-02 5.99E-02 2.88E-02 0.045

mg/dscm@7%O2 5.49E-02 7.94E-02 3.77E-02 0.057

ppm 1.99E-02 2.62E-02 1.26E-02 0.020

ppm@7%O2 2.41E-02 3.47E-02 1.65E-02 0.025

Compound: Mercury

Average

RunNumber 1 2 3

Mass_mg 0.00178 0.00127 0.00232 0.002

Elb/hr 1.64E-04 1.32E-04 2.15E-04 0.000

lb/mmBtuO2 4.95E-07 3.89E-07 7.09E-07 0.000

mg/dscm 4.75E-04 3.40E-04 6.29E-04 0.000

mg/dscm@7%O2 5.74E-04 4.51E-04 8.22E-04 0.001

ppm 5.70E-05 4.08E-05 7.54E-05 0.000

ppm@7%O2 6.89E-05 5.41E-05 9.86E-05 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.22283 0.22515 0.109 0.186

Elb/hr 2.05E-02 2.33E-02 1.01E-02 0.018

lb/mmBtuO2 6.20E-05 6.89E-05 3.33E-05 0.000

mg/dscm 5.95E-02 6.03E-02 2.96E-02 0.050

mg/dscm@7%O2 7.19E-02 7.99E-02 3.87E-02 0.064

ppm 2.44E-02 2.47E-02 1.21E-02 0.020

ppm@7%O2 2.95E-02 3.27E-02 1.58E-02 0.026

Compound: Phosphorus (yellow or white)

Average

RunNumber 1 2 3

Mass_mg 48.9427 51.4225 31.42 43.928

Thursday, February 03, 2011 Page 17 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Elb/hr 4.51E+00 5.33E+00 2.92E+00 4.253

lb/mmBtuO2 1.36E-02 1.57E-02 9.61E-03 0.013

mg/dscm 1.31E+01 1.38E+01 8.52E+00 11.807

mg/dscm@7%O2 1.58E+01 1.83E+01 1.11E+01 15.067

ppm 1.01E+01 1.07E+01 6.62E+00 9.140

ppm@7%O2 1.22E+01 1.42E+01 8.66E+00 11.687

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0081 0.00524 0.01191 0.008

Elb/hr 7.46E-04 5.43E-04 1.11E-03 0.001

lb/mmBtuO2 2.25E-06 1.60E-06 3.64E-06 0.000

mg/dscm 2.16E-03 1.40E-03 3.23E-03 0.002

mg/dscm@7%O2 2.61E-03 1.86E-03 4.22E-03 0.003

ppm 6.59E-04 4.28E-04 9.84E-04 0.001

ppm@7%O2 7.97E-04 5.67E-04 1.29E-03 0.001

Location: Stack Exhaust - Method 5/OTM-28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 463.7 527.3 509.9 500.300

Elb/hr 4.46E+01 5.19E+01 5.08E+01 49.100

lb/mmBtuO2 1.39E-01 1.70E-01 1.40E-01 0.150

mg/dscm 1.33E+02 1.49E+02 1.24E+02 135.333

mg/dscm@7%O2 1.61E+02 1.97E+02 1.62E+02 173.333

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 29.2 23.9 123.7 58.933

Elb/hr 2.81E+00 2.35E+00 1.23E+01 5.820

lb/mmBtuO2 8.72E-03 7.72E-03 3.40E-02 0.017

mg/dscm 8.37E+00 6.75E+00 3.02E+01 15.107

mg/dscm@7%O2 1.01E+01 8.94E+00 3.95E+01 19.513

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 7.5 15.9 6.8 10.067

Elb/hr 7.22E-01 1.56E+00 6.78E-01 0.987

lb/mmBtuO2 2.24E-03 5.14E-03 1.87E-03 0.003

mg/dscm 2.15E+00 4.49E+00 1.66E+00 2.767

mg/dscm@7%O2 2.60E+00 5.95E+00 2.17E+00 3.573

Location: Stack Exhaust - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

Elb/hr 9.19E+01 1.15E+02 7.81E+01 95.000

lb/mmBtuO2 2.78E-01 3.38E-01 2.31E-01 0.282

ppm 9.99E+01 1.22E+02 8.35E+01 101.800

Thursday, February 03, 2011 Page 18 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Process Run Data

ppm@7%O2 1.21E+02 1.47E+02 1.00E+02 122.667

Thursday, February 03, 2011 Page 19 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input Million Btus/million BTU using O2 335.6 Methods 6C, 10, 

25A, & 26A

598

1 Net megawatts 39.5 MW Methods 6C, 10, 

25A, & 26A

46

1 Steam 40000 kpph Methods 6C, 10, 

25A, & 26A

48200

1 Fuel rate 28141 lb/hr Methods 6C, 10, 

25A, & 26A

28000

2 Heat Input Million Btus/million BTU using O2 335.6 Run 2 - Methods 

6C, 10, 25A, & 

26A

598

2 Net megawatts 39 MW Run 2 - Methods 

6C, 10, 25A, & 

26A

46

2 Steam 40000 kpph Run 2 - Methods 

6C, 10, 25A, & 

26A

48200

2 Fuel rate 27983 lb/hr Run 2 - Methods 

6C, 10, 25A, & 

26A

28000

3 Heat Input Million Btus/million BTU using O2 334 Run 3 - Methods 

6C, 10, 25A, & 

26A

598

3 Net megawatts 39 MW Run 3 - Methods 

6C, 10, 25A, & 

26A

46

3 Steam 40000 kpph Run 3 - Methods 

6C, 10, 25A, & 

26A

48200

3 Fuel rate 27992 lb/hr Run 3 - Methods 

6C, 10, 25A, & 

26A

28000

4 Heat Input Million Btus/million BTU using O2 330.9 Run 1- Methods 

29 & 5 / OTM28

598

4 Net megawatts 38 MW Run 1- Methods 

29 & 5 / OTM28

46

4 Steam 46500 kpph Run 1- Methods 

29 & 5 / OTM28

48200

4 Fuel rate 28165 lb/hr Run 1- Methods 

29 & 5 / OTM28

28000

5 Heat Input Million Btus/million BTU using O2 338 Run 2- Methods 

29 & 5 / OTM28

598

5 Net megawatts 35 MW Run 2- Methods 

29 & 5 / OTM28

46

Thursday, February 03, 2011 Page 20 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

APCD Run Data

Process Lab Run Data

5 Steam 44000 kpph Run 2- Methods 

29 & 5 / OTM28

48200

5 Fuel rate 26539 lb/hr Run 2- Methods 

29 & 5 / OTM28

28000

6 Heat Input Million Btus/million BTU using O2 303.6 Run 3- Methods 

29 & 5 / OTM28

598

6 Net megawatts 35 MW Run 3- Methods 

29 & 5 / OTM28

46

6 Steam 44500 kpph Run 3- Methods 

29 & 5 / OTM28

48200

6 Fuel rate 25517 lb/hr Run 3- Methods 

29 & 5 / OTM28

28000

7 Heat Input Million Btus/million BTU using O2 322 598 Run 1- Methods 23

7 Net megawatts 38 MW 46 Run 1- Methods 23

7 Steam 46500 kpph 48200 Run 1- Methods 23

7 Fuel rate 27710 lb/hr 28000 Run 1- Methods 23

8 Heat Input Million Btus/million BTU using O2 295 598 Run 2- Methods 23

8 Net megawatts 35 MW 46 Run 2- Methods 23

8 Steam 44500 kpph 48200 Run 2- Methods 23

8 Fuel rate 26512 lb/hr 28000 Run 2- Methods 23

9 Heat Input Million Btus/million BTU using O2 323.9 598 Run 3- Methods 23

9 Net megawatts 41 MW 46 Run 3- Methods 23

9 Steam 49000 kpph 48200 Run 3- Methods 23

9 Fuel rate 29082 lb/hr 28000 Run 3- Methods 23

Run Name Value UOM Comments

Target

Value

1 NA 0 0

Run Name Value UOM Comments

1 NA 0

Thursday, February 03, 2011 Page 21 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Sampling / Stack Data Results Detail

Location Stack Exhaust - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 03, 2011 Page 22 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Location Stack Exhaust - Method 23

Average

Run Number 1 2 3

Test Date 7/14/2010 7/15/2010 7/16/2010

Run Start Time 8:00:00 AM 10:15:00 AM 7:55:00 AM

Run Finish Time 3:50:00 PM 6:05:00 PM 3:45:00 PM

Net Traversing Points 48 48 48

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.19 0.19 0.19 0.190

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9806 0.9806 0.9806 0.981

Barometric Pressure, inches of Mercury 29.83 29.93 29.94 29.900

Average Orifice Meter Differential, inches H2O 1.11 1.09 1.02 1.073

Dry Gas Meter Volume Sampled, cubic feet 275.627 276.137 265.918 272.561

Average Dry Gas Meter Temperature, °F 105.38 104.08 95.77 101.743

Dry Gas Meter Volume Sampled, dscf 252.340 254.224 248.516 251.693

Total Moisture Liquid collected, g 571.5 566 552.7 563.400

Volume of Water Vapor, standard cubic feet 26.90 26.64 26.02 26.520

Moisture Content of Stack Gas, % 9.63 9.49 9.48 9.533

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9037 0.9051 0.9052 0.905

Carbon Dioxide, % 8.49 7.89 8.44 8.273

Oxygen, % 9.38 10.29 9.61 9.760

Carbon Monoxide & Nitrogen, % 82.13 81.82 81.95 81.967

Fuel Factor 1.36 1.34 1.34

Dry Molecular Weight, lb/lb-Mole 29.73 29.67 29.73 29.710

Wet Molecular weight, lb/lb-Mole 28.60 28.56 28.62 28.593

Flue Gas Static Pressure, inches of H2O -1.2 -1.2 -1.2 -1.200

Absolute Flue Gas Pressure, inches of Mercury 29.74 29.84 29.85 29.810

Average Stack Gas Temperature, °F 408.75 411.04 414.17 411.320

Average Velocity Head, inches of H2O 1.2901972774

7154

1.266869258

1042

1.354703479

60919

1.304

Average Stack Gas Velocity, feet/second 82.44 81.71 84.55 82.900

Stack Cross-Sectional Area, square feet 33.183 33.183 33.183 33.183

Dry Volumetric Flow Rate, dry scfm 89,608.2 89,016.7 91,821.8 90,148.900

Actual Wet Volumetric Flue Gas Flow Rate, acfm 164,136.4 162,683.0 168,337.4 165,052.267

Percent Isokinetic of Sampling Rate, % 98.9 100.3 95.0 98.067

Percent Excess Air, % 76.2 91.0 79.9 82.367

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 78 78 78

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 03, 2011 Page 23 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Location Stack Exhaust - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 03, 2011 Page 24 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Location Stack Exhaust - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 03, 2011 Page 25 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Location Stack Exhaust - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 03, 2011 Page 26 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Location Stack Exhaust - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 03, 2011 Page 27 of 28
Santee Cooper - Jefferies Generating Station Unit #2

9/2/2010

Location Stack Exhaust - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 03, 2011 Page 28 of 28