Name:

Title: Company: Sign Date: Name: Title: Company: Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date 

### Joliet 9 - Midwest Generation EME, LLC

Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Tuesday, February 08, 2011 Page 1 of 42Joliet 9 - Midwest Generation EME, LLC

Facility Information: Joliet 9 - Midwest Generation EME, LLC 1800 Channahon Road

Joliet IL 60436 Contact: Scott B. Miller Phone: 630-771-7859 Fax: 312-788-5219 Email: smiller@mwgen.com Testing Company: Platt Environmental Services, Inc. 1520 Kensington Road Suite 204 Oak Brook IL 60523-2141 Contact: Eric L. Ehlers Phone: 630-699-7690 Fax: Email: eehlers@plattenv.com

Air Permit Number: 95090046 Permitted Source ID/Name: Joliet 9 874 Permitted Maximum Process Rate: 3543 mmBtu/hr Max. Normal Operation Process Rate: 3543 mmBtu/hr Target Process Test Rate 3378 mmBtu/hr

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Joliet Station 9, Unit 6 is a cyclone fired boiler rated at 341 MW (gross) amd 3,543 MMBtu/hr. The single boiler comprising Unit 6 (BLR5) is capable of producing 2,200,000 lbs of steam per hour at 2,100 psia and 1,055 degrees F. The boiler consists of an air supply system, nine cyclone burners, and a convective heat transfer system. (superheater and reheater, economizers and air heaters). Unit 6 utilizes natural gas during startup, for flame stabilization, and for NOx control in the reburn system. Heat produced in the boiler converts water to high-pressure steam in the boiler. Steam is forced through thr turbine, causing the blades and shaft to rotate. The turbine shaft turns the attached generator shaft, which produces electricity. Air emissions from Unit 6 result from combustion of fuel within the boiler. Combustion emissions include, but are not limited to, NOx, CO, particulates including PM/PM10/PM2.5, VOM, SO2, sulfuric acid (H2SO4) mist, lead, and various HAPs, including mercury (Hg) and Hydrochloric Acid (HCl). The emissions generated are controlled (for specific pollutants) through various methods before entering the air via the Unit 6 Stack (ST1). The various methods of control include over-fire air (OFA) technology for NOx control, activated carbon injection (ACI) for mercury control, and electrostatic precipitators (ESP) for particulate control. Additionally, Joliet Station burns low-sulfur coal to minimize SO2 emissions. Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information: AFS #: 171970143 FRS #: 110000432773

SCC / Description 10100223 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous Coal - Cyclone Furnace (Subbituminous Coal)
The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Stack 171 0 0 4 0 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location Tuesday, February 08, 2011 Page 2 of 42Joliet 9 - Midwest Generation EME, LLC

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. None Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location Mercury M30B - Hg 3 120 0 Stack Custom M18 - CH4 3 120 0 Stack Custom M0031-VOHAP 3 120 0 Stack Custom M0010-SVOHAP 3 120 0 Stack Carbon Monoxide Method 10 3 120 0 Stack Formaldehyde Method 0011 3 120 0 Stack Total organic compounds

(TOC) as Propane Method 25A 3 120 0 Stack Hydrogen Fluoride Method 26A 3 180 0 Stack Hydrogen Chloride Method 26A 3 180 0 Stack Organic Condensible

Particulate OTM - 27/28 3 360 0 Stack
Filterable Particulate OTM - 27/28 3 360 0 Stack Total PM2.5 OTM - 27/28 3 360 0 Stack Total Particulate OTM - 27/28 3 360 0 Stack Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 360 0 Stack
Filterable PM2.5 OTM - 27/28 3 360 0 Stack Selenium Method 29 3 240 0 Stack Beryllium Method 29 3 240 0 Stack Antimony Method 29 3 240 0 Stack Arsenic Method 29 3 240 0 Stack Cadmium Method 29 3 240 0 Stack Chromium Method 29 3 240 0 Stack Cobalt Method 29 3 240 0 Stack Lead Method 29 3 240 0 Stack Nickel Method 29 3 240 0 Stack Filterable Particulate Method 29 3 240 0 Stack Manganese Method 29 3 240 0 Stack O2 Method 3A O2 9 120 0 Stack Custom CTM-033 HCN 3 60 0 Stack Co2 Method 3A CO2 9 120 0 Stack

Tuesday, February 08, 2011 Page 3 of 42Joliet 9 - Midwest Generation EME, LLC

Sampling / Stack Data Results Summary Location Stack - Method 0011 Average Run Number M0011-1 M0011-2 M0011-3 Test Date 6/18/2010 6/18/2010 6/18/2010 Run Start Time 8:30:00 AM 11:15:00 AM 1:50:00 PM

Run Finish Time 10:46:00 AM 1:30:00 PM 4:00:00 PM Net Run Time, minutes 120 120 120 Dry Gas Meter Volume Sampled, dscf 95.348 96.587 97.297 96.411 Moisture Content of Stack Gas, % 11.46 12.14 10.47 11.357 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 13.7 13.4 13.6 13.567 Oxygen, % 5.8 5.9 5.8 5.833 Average Stack Gas Temperature, °F 297.21 301.50 303.17 300.627 Dry Volumetric Flow Rate, dry scfm 721,845.2 728,055.4 742,155.9 730,685.500 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,212,979.1 1,239,868.3 1,243,026.1 1,231,957.83 3 Percent Isokinetic of Sampling Rate, % 101.6 102.0 100.8 101.467 F-Factor, dscfm/MMBtu @ %O2 9681 9681 9681 9,681.000 Fw 0 0 0 0.000 Fc 1854 1854 1854 1,854.000

Location Stack - Method 10 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type Fw Fc

Tuesday, February 08, 2011 Page 4 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type Fw Fc

Location Stack - Method 26A Average Run Number Test Date Run Start Time Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2 Fw Fc

Tuesday, February 08, 2011 Page 5 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 29 Average Run Number Test Date Run Start Time Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2 Fw Fc

Location Stack - Method 3A CO2 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type Fw Fc

Tuesday, February 08, 2011 Page 6 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 3A CO2 3 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type Fw Fc

Location Stack - Method 3A CO2 3 6 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type Fw Fc

Tuesday, February 08, 2011 Page 7 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 3A O2 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type Fw Fc

Location Stack - Method 3A O2 3 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type Fw Fc

Tuesday, February 08, 2011 Page 8 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 3A O2 3 6 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type Fw Fc

Location Stack - OTM - 27/28 Average Run Number Test Date Run Start Time Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2 Fw Fc

Tuesday, February 08, 2011 Page 9 of 42Joliet 9 - Midwest Generation EME, LLC

Emissions Summary Location: Stack - Method 0011 Compound: Formaldehyde Average RunNumber M0011-1 M0011-2 M0011-3 Mass_mg 0.018 0.011 0.023 0.017 lb/mmBtuO2 5.58E-06 3.39E-06 6.98E-06 0.000 ppm 5.34E-03 3.22E-03 6.69E-03 0.005 ppm@7%O2 4.92E-03 2.98E-03 6.16E-03 0.005
Location: Stack - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 lb/mmBtuO2 1.32E-01 1.09E-01 1.53E-01 0.131 ppm 1.36E+02 1.12E+02 1.57E+02 135.000 ppm@7%O2 1.25E+02 1.04E+02 1.45E+02 124.667
Location: Stack - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 0.00E+00 3.47E-05 8.48E-05 0.000 ppm 0.00E+00 2.25E-02 5.53E-02 0.026 ppm@7%O2 0.00E+00 2.09E-02 5.09E-02 0.024
Location: Stack - Method 26A Compound: Hydrogen Chloride Average RunNumber M26A-1 M26A-2 M26A-3 Mass_mg 2.7 3 3.6 3.100 lb/mmBtuO2 4.80E-04 5.40E-04 6.04E-04 0.001 Compound: Hydrogen Fluoride Average RunNumber M26A-1 M26A-2 M26A-3 Mass_mg 2.6 3 2.5 2.700 lb/mmBtuO2 4.62E-04 5.40E-04 4.20E-04 0.000
Location: Stack - Method 29 Compound: Antimony Average RunNumber M5/29-1 M5/29-2 M5/29-3 Mass_mg 0.0052 0.0044 0.004 0.005 lb/mmBtuO2 8.71E-07 6.85E-07 5.45E-07 0.000 Compound: Arsenic Average RunNumber M5/29-1 M5/29-2 M5/29-3 Mass_mg 0.0224 0.0181 0.0141 0.018
Tuesday, February 08, 2011 Page 10 of 42Joliet 9 - Midwest Generation EME, LLC

lb/mmBtuO2 3.75E-06 2.82E-06 1.92E-06 0.000 Compound: Beryllium Average RunNumber M5/29-1 M5/29-2 M5/29-3 Mass_mg 0.00179 0.00145 0.00131 0.002 lb/mmBtuO2 3.00E-07 2.26E-07 1.79E-07 0.000 Compound: Cadmium Average RunNumber M5/29-1 M5/29-2 M5/29-3 Mass_mg 0.00438 0.0032 0.00321 0.004 lb/mmBtuO2 7.34E-07 4.98E-07 4.38E-07 0.000 Compound: Chromium Average RunNumber M5/29-1 M5/29-2 M5/29-3 Mass_mg 0.04161 0.02992 0.02051 0.031 lb/mmBtuO2 6.97E-06 4.66E-06 2.80E-06 0.000 Compound: Cobalt Average RunNumber M5/29-1 M5/29-2 M5/29-3 Mass_mg 0.0111 0.00905 0.00719 0.009 lb/mmBtuO2 1.86E-06 1.41E-06 9.80E-07 0.000 Compound: Filterable Particulate Average RunNumber M5/29-1 M5/29-2 M5/29-3 Mass_mg 451.7 315.5 237.9 335.033 lb/mmBtuO2 7.57E-02 4.91E-02 3.24E-02 0.052 Compound: Lead Average RunNumber M5/29-1 M5/29-2 M5/29-3 Mass_mg 0.05394 0.03849 0.02849 0.040 lb/mmBtuO2 9.04E-06 5.99E-06 3.88E-06 0.000 Compound: Manganese Average RunNumber M5/29-1 M5/29-2 M5/29-3 Mass_mg 0.09789 0.06799 0.04819 0.071 lb/mmBtuO2 1.64E-05 1.06E-05 6.57E-06 0.000 Compound: Nickel Average RunNumber M5/29-1 M5/29-2 M5/29-3 Mass_mg 0.03297 0.02132 0.01492 0.023 lb/mmBtuO2 5.53E-06 3.32E-06 2.03E-06 0.000 Compound: Selenium Average RunNumber M5/29-1 M5/29-2 M5/29-3 Mass_mg 0.0245 0.0187 0.018 0.020 Tuesday, February 08, 2011 Page 11 of 42Joliet 9 - Midwest Generation EME, LLC

Process Run Data lb/mmBtuO2 4.11E-06 2.91E-06 2.45E-06 0.000
Location: Stack - OTM - 27/28 Compound: Filterable Particulate Average RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2 MOTM27/OTM28-3 Mass_mg 344.9 255.9 229.5 276.767 lb/mmBtuO2 8.75E-02 6.07E-02 4.67E-02 0.065 Compound: Filterable PM2.5 Average RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2 MOTM27/OTM28-3 Mass_mg 79.4 78.6 52.3 70.100 lb/mmBtuO2 2.02E-02 1.87E-02 1.06E-02 0.017 Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2 MOTM27/OTM28-3 Mass_mg 25 13.3 12.1 16.800 lb/mmBtuO2 6.34E-03 3.16E-03 2.46E-03 0.004 Compound: Organic Condensible Particulate Average RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2 MOTM27/OTM28-3 Mass_mg 4.3 0.7 1.1 2.033 lb/mmBtuO2 1.09E-03 1.66E-04 2.24E-04 0.000 Compound: Total Particulate Average RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2 MOTM27/OTM28-3 Mass_mg 374.2 269.9 242.7 295.600 lb/mmBtuO2 9.50E-02 6.41E-02 4.94E-02 0.070 Compound: Total PM2.5 Average RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2 MOTM27/OTM28-3 Mass_mg 108.7 92.6 65.5 88.933 lb/mmBtuO2 2.76E-02 2.20E-02 1.33E-02 0.021

Tuesday, February 08, 2011 Page 12 of 42Joliet 9 - Midwest Generation EME, LLC

Process Run Data

Run Name Value UOM Comments Target Value 1 Coal Firing Rate 399.5 1000 lb/hr Test 1, 6/15/10, OTM27/OTM28, 8:41-14:45 0

10 Coal Firing Rate 398.4 1000 lb/hr Test 1, 6/15/10, M26A, 12:28- 15:38 0

11 Coal Firing Rate 399.4 1000 lb/hr Test 2, 6/16/10, M26A, 12:10- 14:20 0

12 Coal Firing Rate 403.8 1000 lb/hr Test 3, 6/17/10, M26A, 12:15- 15:27 0

13 Coal Firing Rate 397.8 1000 lb/hr Test 1, 6/15/10, CTM033, 15:25- 16:40 0

14 Coal Firing Rate 399.8 1000 lb/hr Test 2, 6/16/10, CTM033, 14:25- 15:40 0

15 Coal Firing Rate 322.2 1000 lb/hr Test 3, 6/17/10, CTM033, 14:20- 15:40 0

16 Coal Firing Rate 399.5 1000 lb/hr Test 1, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 8:30- 10:46 0

17 Coal Firing Rate 398.2 1000 lb/hr Test 2, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 11:15- 13:30 0

18 Coal Firing Rate 396.2 1000 lb/hr Test 3, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 13:50- 16:00 0

2 Coal Firing Rate 397.2 1000 lb/hr Test 2, 6/16/10, OTM27/OTM28, 7:45-13:46 0

3 Coal Firing Rate 398.8 1000 lb/hr Test 3, 6/17/10, OTM27/OTM28, 7:45-13:56 0

4 Coal Firing Rate 399.1 1000 lb/hr Test 1, 6/15/10, M5/29, 8:00-12:10 0

5 Coal Firing Rate 396.6 1000 lb/hr Test 2, 6/16/10, M5/29, 7:45-11:54 0

6 Coal Firing Rate 396.8 1000 lb/hr Test 3, 6/17/10, M5/29, 7:45-11:55 0

Tuesday, February 08, 2011 Page 13 of 42Joliet 9 - Midwest Generation EME, LLC

7 Coal Firing Rate 396.9 1000 lb/hr Test 1, 6/15/10, M30B, 8:00-10:00 0

8 Coal Firing Rate 395.9 1000 lb/hr Test 2, 6/16/10, M30B, 7:45-9:45 0

9 Coal Firing Rate 397.5 1000 lb/hr Test 3, 6/17/10, M30B, 10:10- 12:10 0

1 Sorbent Type and Sorbent Injection Rate 378.4 lb/hr Test 1, 6/15/10, OTM27/OTM28, 8:41-14:45 0

10 Sorbent Type and Sorbent Injection Rate 367.3 lb/hr Test 1, 6/15/10, M26A, 12:28- 15:38 0

11 Sorbent Type and Sorbent Injection Rate 366.8 lb/hr Test 2, 6/16/10, M26A, 12:10- 14:20 0

12 Sorbent Type and Sorbent Injection Rate 244.6 lb/hr Test 3, 6/17/10, M26A, 12:15- 15:27 0

13 Sorbent Type and Sorbent Injection Rate 195.6 lb/hr Test 1, 6/15/10, CTM033, 15:25- 16:40 0

14 Sorbent Type and Sorbent Injection Rate 367.3 lb/hr Test 2, 6/16/10, CTM033, 14:25- 15:40 0

15 Sorbent Type and Sorbent Injection Rate 354.8 lb/hr Test 3, 6/17/10, CTM033, 14:20- 15:40 0

16 Sorbent Type and Sorbent Injection Rate 374.6 lb/hr Test 1, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 8:30- 10:46 0

17 Sorbent Type and Sorbent Injection Rate 376.5 lb/hr Test 2, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 11:!5- 13:30 0

18 Sorbent Type and Sorbent Injection Rate 374.6 lb/hr Test 3, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 13:50- 16:00 0

2 Sorbent Type and Sorbent Injection Rate 364 lb/hr Test 2, 6/16/10, OTM27/OTM28, 7:45-13:46 0

3 Sorbent Type and Sorbent Injection Rate 319.3 lb/hr Test 3, 6/17/10, OTM27/OTM28, 7:45-13:56 0

4 Sorbent Type and Sorbent Injection Rate 376.4 lb/hr Test 1, 6/15/10, M5/29, 8:00-12:10 0

Tuesday, February 08, 2011 Page 14 of 42Joliet 9 - Midwest Generation EME, LLC

5 Sorbent Type and Sorbent Injection Rate 363.3 lb/hr Test 2, 6/16/10, M5/29, 7:45-11:54 0

6 Sorbent Type and Sorbent Injection Rate 365.2 lb/hr Test 3, 6/17/10, M5/29, 7:45-11:55 0

7 Sorbent Type and Sorbent Injection Rate 373.9 lb/hr Test 1, 6/15/10, M30B, 8:00-10:00 0

8 Sorbent Type and Sorbent Injection Rate 362.4 lb/hr Test 2, 6/16/10, M30B, 7:45-9:45 0

9 Sorbent Type and Sorbent Injection Rate 365.8 lb/hr Test 3, 6/17/10, M30B, 10:10- 12:10 0

1 Average Heat Input 3385.3 mmBtu/hr Test 1, 6/15/10, OTM27/OTM28, 8:41-14:45 0

10 Average Heat Input 3376.2 mmBtu/hr Test 1, 6/15/10, M26A, 12:28- 15:38 0

11 Average Heat Input 3384.2 mmBtu/hr Test 2, 6/16/10, M26A, 12:10- 14:20 0

12 Average Heat Input 3422.2 mmBtu/hr Test 3, 6/17/10, M26A, 12:15- 15:27 0

13 Average Heat Input 3371.2 mmBtu/hr Test 1, 6/15/10, CTM033, 15:25- 16:40 0

14 Average Heat Input 3388.1 mmBtu/hr Test 2, 6/16/10, CTM033, 14:25- 15:40 0

15 Average Heat Input 3417.7 mmBtu/hr Test 3, 6/17/10, CTM033, 14:20- 15:40 0

16 Average Heat Input 3385.5 mmBtu/hr Test 1, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 8:30- 10:46 0

17 Average Heat Input 3374.3 mmBtu/hr Test 2, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 11:15- 13:30 0

18 Average Heat Input 3357.6 mmBtu/hr Test 3, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 13:50- 16:00 0

2 Average Heat Input 3366.2 mmBtu/hr Test 2, 6/16/10, OTM27/OTM28, 7:45-13:46 0

Tuesday, February 08, 2011 Page 15 of 42Joliet 9 - Midwest Generation EME, LLC

3 Average Heat Input 3379.1 mmBtu/hr Test 3, 6/17/10, OTM27/OTM28, 7:45-13:56 0

4 Average Heat Input 3382 mmBtu/hr Test 1, 6/15/10, M5/29, 8:00-12:10 0

5 Average Heat Input 3360.9 mmBtu/hr Test 2, 6/16/10, M5/29, 7:45-11:54 0

6 Average Heat Input 3362.2 mmBtu/hr Test 3, 6/17/10, M5/29, 7:45-11:55 0

7 Average Heat Input 3363.5 mmBtu/hr Test 1, 6/15/10, M30B, 8:00-10:00 0

8 Average Heat Input 3354.6 mmBtu/hr Test 2, 6/16/10, M30B, 7:45-9:45 0

9 Average Heat Input 3368.5 mmBtu/hr Test 3, 6/17/10, M30B, 10:10- 12:10 0

1 Steam Output 2303 1000 lb steam/hr Test 1, 6/15/10, OTM27/OTM28, 8:41-14:45 0

10 Steam Output 2306.4 1000 lb steam/hr Test 1, 6/15/10, M26A, 12:28- 15:38 0

11 Steam Output 2229.9 1000 lb steam/hr Test 2, 6/16/10, M26A, 12:10- 14:20 0

12 Steam Output 2252.4 1000 lb steam/hr Test 3, 6/17/10, M26A, 12:15- 15:27 0

13 Steam Output 2304.7 1000 lb steam/hr Test 1, 6/15/10, CTM033, 15:25- 16:40 0

14 Steam Output 2241.8 1000 lb steam/hr Test 2, 6/16/10, CTM033, 14:25- 15:40 0

15 Steam Output 2253.3 1000 lb steam/hr Test 3, 6/17/10, CTM033, 14:20- 15:40 0

16 Steam Output 2287.1 1000 lb steam/hr Test 1, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 8:30- 10:46 0

17 Steam Output 2265.0 1000 lb steam/hr Test 2, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 11:15- 13:30 0

18 Steam Output 2254.8 1000 lb steam/hr Test 3, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 13:50- 16:00 0

Tuesday, February 08, 2011 Page 16 of 42Joliet 9 - Midwest Generation EME, LLC

2 Steam Output 2229 1000 lb steam/hr Test 2, 6/16/10, OTM27/OTM28, 7:45-13:45 0

3 Steam Output 2239.4 1000 lb steam/hr Test 3, 6/17/10, OTM27/OTM28, 7:45-13:56 0

4 Steam Output 2298.9 1000 lb steam/hr Test 1, 6/15/10, M5/29, 8:00-12:10 0

5 Steam Output 2227.9 1000 lb steam/hr Test 2, 6/16/10, M5/29, 7:45-11:54 0

6 Steam Output 2234.9 1000 lb steam/hr Test 3, 6/17/10, M5/29, 7:45-11:55 0

7 Steam Output 2304.0 1000 lb steam/hr Test 1, 6/15/10, M30B, 8:00-10:00 0

8 Steam Output 2231.1 1000 lb steam/hr Test 2, 6/16/10, M30B, 7:45-9:45 0

9 Steam Output 2239.0 1000 lb steam/hr Test 3, 6/17/10, M30B, 10:10- 12:10 0

1 Synfuel Firing Rate 0 0 10 Synfuel Firing Rate 0 0 11 Synfuel Firing Rate 0 0 12 Synfuel Firing Rate 0 0 13 Synfuel Firing Rate 0 0 14 Synfuel Firing Rate 0 0 15 Synfuel Firing Rate 0 0 16 Synfuel Firing Rate 0 0 17 Synfuel Firing Rate 0 0 18 Synfuel Firing Rate 0 0 2 Synfuel Firing Rate 0 0 3 Synfuel Firing Rate 0 0 4 Synfuel Firing Rate 0 0 5 Synfuel Firing Rate 0 0 6 Synfuel Firing Rate 0 0 7 Synfuel Firing Rate 0 0 8 Synfuel Firing Rate 0 0 9 Synfuel Firing Rate 0 0 1 Petroleum Coke Firing Rate 0 0 10 Petroleum Coke Firing Rate 0 0 11 Petroleum Coke Firing Rate 0 0

Tuesday, February 08, 2011 Page 17 of 42Joliet 9 - Midwest Generation EME, LLC

12 Petroleum Coke Firing Rate 0 0 13 Petroleum Coke Firing Rate 0 0 14 Petroleum Coke Firing Rate 0 0 15 Petroleum Coke Firing Rate 0 0 16 Petroleum Coke Firing Rate 0 0 17 Petroleum Coke Firing Rate 0 0 18 Petroleum Coke Firing Rate 0 0 2 Petroleum Coke Firing Rate 0 0 3 Petroleum Coke Firing Rate 0 0 4 Petroleum Coke Firing Rate 0 0 5 Petroleum Coke Firing Rate 0 0 6 Petroleum Coke Firing Rate 0 0 7 Petroleum Coke Firing Rate 0 0 8 Petroleum Coke Firing Rate 0 0 9 Petroleum Coke Firing Rate 0 0 1 Coal Gas Firing Rate 0 0 10 Coal Gas Firing Rate 0 0 11 Coal Gas Firing Rate 0 0 12 Coal Gas Firing Rate 0 0 13 Coal Gas Firing Rate 0 0 14 Coal Gas Firing Rate 0 0 15 Coal Gas Firing Rate 0 0 16 Coal Gas Firing Rate 0 0 17 Coal Gas Firing Rate 0 0 18 Coal Gas Firing Rate 0 0 2 Coal Gas Firing Rate 0 0 3 Coal Gas Firing Rate 0 0 4 Coal Gas Firing Rate 0 0 5 Coal Gas Firing Rate 0 0 6 Coal Gas Firing Rate 0 0 7 Coal Gas Firing Rate 0 0 8 Coal Gas Firing Rate 0 0 9 Coal Gas Firing Rate 0 0 1 Fuel Oil Firing Rate 0 0 10 Fuel Oil Firing Rate 0 0 11 Fuel Oil Firing Rate 0 0

Tuesday, February 08, 2011 Page 18 of 42Joliet 9 - Midwest Generation EME, LLC

12 Fuel Oil Firing Rate 0 0 13 Fuel Oil Firing Rate 0 0 14 Fuel Oil Firing Rate 0 0 15 Fuel Oil Firing Rate 0 0 16 Fuel Oil Firing Rate 0 0 17 Fuel Oil Firing Rate 0 0 18 Fuel Oil Firing Rate 0 0 2 Fuel Oil Firing Rate 0 0 3 Fuel Oil Firing Rate 0 0 4 Fuel Oil Firing Rate 0 0 5 Fuel Oil Firing Rate 0 0 6 Fuel Oil Firing Rate 0 0 7 Fuel Oil Firing Rate 0 0 8 Fuel Oil Firing Rate 0 0 9 Fuel Oil Firing Rate 0 0 1 Flue Gas Flowrate 754355 dscfm Test 1, 6/15/10, OTM27/OTM28, 8:41-14:45 0

10 Flue Gas Flowrate 755783 dscfm Test 1, 6/15/10, M26A, 12:28- 15:38 0

11 Flue Gas Flowrate 737695 dscfm Test 2, 6/16/10, M26A, 12:10- 14:20 0

12 Flue Gas Flowrate 746162 dscfm Test 3, 6/17/10, M26A, 12:15- 15:27 0

13 Flue Gas Flowrate 759040 dscfm Test 1, 6/15/10, CTM033, 15:25- 16:40 0

14 Flue Gas Flowrate 737989 dscfm Test 2, 6/16/10, CTM033, 14:25- 15:40 0

15 Flue Gas Flowrate 746499 dscfm Test 3, 6/17/10, CTM033, 14:20- 15:40 0

16 Flue Gas Flowrate 749379 dscfm Test 1, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 8:30- 10:46 0

17 Flue Gas Flowrate 749066 dscfm Test 2, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 11:15- 13:30 0

Tuesday, February 08, 2011 Page 19 of 42Joliet 9 - Midwest Generation EME, LLC

18 Flue Gas Flowrate 745125 dscfm Test 3, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 13:50- 16:00 0

2 Flue Gas Flowrate 734204 dscfm Test 2, 6/16/10, OTM27/OTM28, 7:45-13:46 0

3 Flue Gas Flowrate 738359 dscfm Test 3, 6/17/10, OTM27/OTM28, 7:45-13:56 0

4 Flue Gas Flowrate 752383 dscfm Test 1, 6/15/10, M5/29, 8:00-12:10 0

5 Flue Gas Flowrate 733349 dscfm Test 2, 6/16/10, M5/29, 7:45-11:54 0

6 Flue Gas Flowrate 735965 dscfm Test 3, 6/17/10, M5/29, 7:45-11:55 0

7 Flue Gas Flowrate 749794 dscfm Test 1, 6/15/10, M30B, 8:00-10:00 0

8 Flue Gas Flowrate 732043 dscfm Test 2, 6/16/10, M30B, 7:45-9:45 0

9 Flue Gas Flowrate 736895 dscfm Test 3, 6/17/10, M30B, 10:10- 12:10 0

1 Pressure Drop Across FGD (if applicable) 0 in H2O 0 10 Pressure Drop Across FGD (if applicable) 0 in H2O 0 11 Pressure Drop Across FGD (if applicable) 0 in H2O 0 12 Pressure Drop Across FGD (if applicable) 0 in H2O 0 13 Pressure Drop Across FGD (if applicable) 0 in H2O 0 14 Pressure Drop Across FGD (if applicable) 0 in H2O 0 15 Pressure Drop Across FGD (if applicable) 0 in H2O 0 16 Pressure Drop Across FGD (if applicable) 0 in H2O 0 17 Pressure Drop Across FGD (if applicable) 0 in H2O 0 18 Pressure Drop Across FGD (if applicable) 0 in H2O 0 2 Pressure Drop Across FGD (if applicable) 0 in H2O 0 3 Pressure Drop Across FGD (if applicable) 0 in H2O 0 4 Pressure Drop Across FGD (if applicable) 0 in H2O 0 5 Pressure Drop Across FGD (if applicable) 0 in H2O 0 6 Pressure Drop Across FGD (if applicable) 0 in H2O 0 7 Pressure Drop Across FGD (if applicable) 0 in H2O 0 8 Pressure Drop Across FGD (if applicable) 0 in H2O 0 9 Pressure Drop Across FGD (if applicable) 0 in H2O 0 1 FGD Scrubber Liquor Flow Rate 0 gal/min 0
Tuesday, February 08, 2011 Page 20 of 42Joliet 9 - Midwest Generation EME, LLC

10 FGD Scrubber Liquor Flow Rate 0 gal/min 0 11 FGD Scrubber Liquor Flow Rate 0 gal/min 0 12 FGD Scrubber Liquor Flow Rate 0 gal/min Test 3, 6/17/10, M26A, 12:15- 15:27 0

13 FGD Scrubber Liquor Flow Rate 0 gal/min 0 14 FGD Scrubber Liquor Flow Rate 0 gal/min 0 15 FGD Scrubber Liquor Flow Rate 0 gal/min 0 16 FGD Scrubber Liquor Flow Rate 0 gal/min 0 17 FGD Scrubber Liquor Flow Rate 0 gal/min 0 18 FGD Scrubber Liquor Flow Rate 0 gal/min 0 2 FGD Scrubber Liquor Flow Rate 0 gal/min 0 3 FGD Scrubber Liquor Flow Rate 0 gal/min 0 4 FGD Scrubber Liquor Flow Rate 0 gal/min 0 5 FGD Scrubber Liquor Flow Rate 0 gal/min 0 6 FGD Scrubber Liquor Flow Rate 0 gal/min 0 7 FGD Scrubber Liquor Flow Rate 0 gal/min 0 8 FGD Scrubber Liquor Flow Rate 0 gal/min 0 9 FGD Scrubber Liquor Flow Rate 0 gal/min 0 1 Unit Net Electric Generation 286.06 MWh Test 1, 6/15/10, OTM27/OTM28, 8:41-14:45 0

10 Unit Net Electric Generation 285.12 MWh Test 1, 6/15/10, M26A, 12:28- 15:38 0

11 Unit Net Electric Generation 278.98 MWh Test 2, 6/16/10, M26A, 12:10- 14:20 0

12 Unit Net Electric Generation 289.7 MWh Test 3, 6/17/10, M26A, 12:15- 15:27 0

13 Unit Net Electric Generation 284.65 MWh Test 1, 6/15/10, CTM033, 15:25- 16:40 0

14 Unit Net Electric Generation 279.02 MWh Test 2, 6/16/10, CTM033, 14:25- 15:40 0

15 Unit Net Electric Generation 289.58 MWh Test 3, 6/17/10, CTM033, 14:20- 15:40 0

Tuesday, February 08, 2011 Page 21 of 42Joliet 9 - Midwest Generation EME, LLC

16 Unit Net Electric Generation 295.92 MWh Test 1, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 8:30- 10:46 0

17 Unit Net Electric Generation 292.41 MWh Test 2, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 11:15- 13:30 0

18 Unit Net Electric Generation 289.79 MWh Test 3, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 13:50- 16:00 0

2 Unit Net Electric Generation 279.41 MWh Test 2, 6/16/10, OTM27/OTM28, 7:45-13:46 0

3 Unit Net Electric Generation 289.82 MWh Test 3, 6/17/10, OTM27/OTM28, 7:45-13:56 0

4 Unit Net Electric Generation 286.58 MWh Test 1, 6/15/10, M5/29, 8:00-12:10 0

5 Unit Net Electric Generation 279.53 MWh Test 2, 6/16/10, M5/29, 7:45-11:54 0

6 Unit Net Electric Generation 289.79 MWh Test 3, 6/17/10, M5/29, 7:45-11:55 0

7 Unit Net Electric Generation 287.65 MWh Test 1, 6/15/10, M30B, 8:00-10:00 0

8 Unit Net Electric Generation 279.55 MWh Test 2, 6/16/10, M30B, 7:45-9:45 0

9 Unit Net Electric Generation 289.63 MWh Test 3, 6/17/10, M30B, 10:10- 12:10 0

1 Flue Gas Oxygen Content 7.3 % Test 1, 6/15/10, OTM27/OTM28, 8:41-14:45 0

10 Flue Gas Oxygen Content 7.36 % Test 1, 6/15/10, M26A, 12:28- 15:38 0

11 Flue Gas Oxygen Content 7 % Test 2, 6/16/10, M26A, 12:10- 14:20 0

12 Flue Gas Oxygen Content 7.01 % Test 3, 6/17/10, M26A, 12:15- 15:27 0

13 Flue Gas Oxygen Content 7.44 % Test 1, 6/15/10, CTM033, 15:25- 16:40 0

14 Flue Gas Oxygen Content 6.98 % Test 2, 6/16/10, CTM033, 14:25- 15:40 0

Tuesday, February 08, 2011 Page 22 of 42Joliet 9 - Midwest Generation EME, LLC

15 Flue Gas Oxygen Content 7.03 % Test 3, 6/17/10, CTM033, 14:20- 15:40 0

16 Flue Gas Oxygen Content 7.21 % Test 1, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 8:30- 10:46 0

17 Flue Gas Oxygen Content 7.25 % Test 2, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 11:15- 13:30 0

18 Flue Gas Oxygen Content 7.24 % Test 3, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 13:50- 16:00 0

2 Flue Gas Oxygen Content 7 % Test 2, 6/16/10, OTM27/OTM28, 7:45-13:46 0

3 Flue Gas Oxygen Content 7.03 % Test 3, 6/17/10, OTM27/OTM28, 7:45-13:56 0

4 Flue Gas Oxygen Content 7.28 % Test 1, 6/15/10, M5/29, 8:00-12:10 0

5 Flue Gas Oxygen Content 7.01 % Test 2, 6/16/10, M5/29, 7:45-11:54 0

6 Flue Gas Oxygen Content 7.05 % Test 3, 6/17/10, M5/29, 7:45-11:55 0

7 Flue Gas Oxygen Content 7.31 % Test 1, 6/15/10, M30B, 8:00-10:00 0

8 Flue Gas Oxygen Content 7.01 % Test 2, 6/16/10, M30B, 7:45-9:45 0

9 Flue Gas Oxygen Content 7.05 % Test 3, 6/17/10, M30B, 10:10- 12:10 0

1 Flue Gas Carbon Dioxide Content 12.42 % Test 1, 6/15/10, OTM27/OTM28, 8:41-14:45 0

10 Flue Gas Carbon Dioxide Content 12.36 % Test 1, 6/15/10, M26A, 12:28- 15:38 0

11 Flue Gas Carbon Dioxide Content 12.69 % Test 2, 6/16/10, M26A, 12:10- 14:20 0

12 Flue Gas Carbon Dioxide Content 12.69 % Test 3, 6/17/10, M26A, 12:15- 15:27 0

13 Flue Gas Carbon Dioxide Content 12.29 % Test 1, 6/15/10, CTM033, 15:25- 16:40 0

Tuesday, February 08, 2011 Page 23 of 42Joliet 9 - Midwest Generation EME, LLC

14 Flue Gas Carbon Dioxide Content 12.71 % Test 2, 6/16/10, CTM033, 14:25- 15:40 0

15 Flue Gas Carbon Dioxide Content 12.67 % Test 3, 6/17/10, CTM033, 14:20- 15:40 0

16 Flue Gas Carbon Dioxide Content 12.5 % Test 1, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 8:30- 10:46 0

17 Flue Gas Carbon Dioxide Content 12.47 % Test 2, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 11:15- 13:30 0

18 Flue Gas Carbon Dioxide Content 12.48 % Test 3, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 13:50- 16:00 0

2 Flue Gas Carbon Dioxide Content 12.69 % Test 2, 6/16/10, OTM27/OTM28, 7:45-13:46 0

3 Flue Gas Carbon Dioxide Content 12.67 % Test 3, 6/17/10, OTM27/OTM28, 7:45-13:56 0

4 Flue Gas Carbon Dioxide Content 12.44 % Test 1, 6/15/10, M5/29, 8:00-12:10 0

5 Flue Gas Carbon Dioxide Content 12.69 % Test 2, 6/16/10, M5/29, 7:45-11:54 0

6 Flue Gas Carbon Dioxide Content 12.64 % Test 3, 6/17/10, M5/29, 7:45-11:55 0

7 Flue Gas Carbon Dioxide Content 12.41 % Test 1, 6/15/10, M30B, 8:00-10:00 0

8 Flue Gas Carbon Dioxide Content 12.69 % Test 2, 6/16/10, M30B, 7:45-9:45 0

9 Flue Gas Carbon Dioxide Content 12.65 % Test 3, 6/17/10, M30B, 10:10- 12:10 0

1 Flue Gas Moisture Content 11 % Test 1, 6/15/10, OTM27/OTM28, 8:41-14:45 0

10 Flue Gas Moisture Content 11 % Test 1, 6/15/10, M26A, 12:28- 15:38 0

11 Flue Gas Moisture Content 11 % Test 2, 6/16/10, M26A, 12:10- 14:20 0

12 Flue Gas Moisture Content 11 % Test 3, 6/17/10, M26A, 12:15- 15:27 0

Tuesday, February 08, 2011 Page 24 of 42Joliet 9 - Midwest Generation EME, LLC

13 Flue Gas Moisture Content 11 % Test 1, 6/15/10, CTM033, 15:25- 16:40 0

14 Flue Gas Moisture Content 11 % Test 2, 6/16/10, CTM033, 14:25- 15:40 0

15 Flue Gas Moisture Content 11 % Test 3, 6/17/10, CTM033, 14:20- 15:40 0

16 Flue Gas Moisture Content 11 % Test 1, 6/18.10, 0010, 0011, 0031, 25A, 18, 10, 8:30- 10:46 0

17 Flue Gas Moisture Content 11 % Test 2, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 11:!5- 13:30 0

18 Flue Gas Moisture Content 11 % Test 3, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 13:50- 16:00 0

2 Flue Gas Moisture Content 11 % Test 2, 6/16/10, OTM27/OTM28, 7:45-13:46 0

3 Flue Gas Moisture Content 11 % Test 3, 6/17/10, OTM27/OTM28, 7:45-13:56 0

4 Flue Gas Moisture Content 11 % Test 1, 6/15/10, M5/29, 8:00-12:10 0

5 Flue Gas Moisture Content 11 % Test 2, 6/16/10, M5/29, 7:45-11:54 0

6 Flue Gas Moisture Content 11 % Test 3, 6/17/10, M5/29, 7:45-11:55 0

7 Flue Gas Moisture Content 11 % Test 1, 6/15/10, M30B, 8:00-10:00 0

8 Flue Gas Moisture Content 11 % Test 2, 6/16/10, M30B, 7:45-9:45 0

9 Flue Gas Moisture Content 11 % Test 3, 6/17/10, M30B, 10:10- 12:10 0

1 Flue Gas Sampling Point Temperature 318.1 Deg F Test 1, 6/15/10, OTM27/OTM28, 8:41-14:45 0

10 Flue Gas Sampling Point Temperature 318.9 Deg F Test 1, 6/15/10, M26A, 12:28- 15:38 0

11 Flue Gas Sampling Point Temperature 314.3 Deg F Test 2, 6/16/10, M26A, 12:10- 14:20 0

Tuesday, February 08, 2011 Page 25 of 42Joliet 9 - Midwest Generation EME, LLC

12 Flue Gas Sampling Point Temperature 320.5 Deg F Test 3, 6/17/10, M26A, 12:15- 15:27 0

13 Flue Gas Sampling Point Temperature 316.7 Deg F Test 1, 6/15/10, CTM033, 15:25- 16:40 0

14 Flue Gas Sampling Point Temperature 313.4 Deg F Test 2, 6/16/10, CTM033, 14:25- 15:40 0

15 Flue Gas Sampling Point Temperature 322.2 Deg F Test 3, 6/17/10, CTM033, 14:20- 15:40 0

16 Flue Gas Sampling Point Temperature 316.1 Deg F Test 1, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 8:30- 10:46 0

17 Flue Gas Sampling Point Temperature 321 Deg F Test 2, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 11:15- 13:30 0

18 Flue Gas Sampling Point Temperature 322.5 Deg F Test 3, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 13:50- 16:00 0

2 Flue Gas Sampling Point Temperature 311.7 Deg F Test 2, 6/16/10, OTM27/OTM28, 7:45-13:46 0

3 Flue Gas Sampling Point Temperature 316.4 Deg F Test 3, 6/17/10, OTM27/OTM28, 7:45-13:56 0

4 Flue Gas Sampling Point Temperature 316.5 Deg F Test 1, 6/15/10, M5/29, 8:00-12:10 0

5 Flue Gas Sampling Point Temperature 310.7 Deg F Test 2, 6/16/10, M5/29, 7:45-11:54 0

6 Flue Gas Sampling Point Temperature 314.9 Deg F Test 3, 6/17/10, M5/29, 7:45-11:55 0

7 Flue Gas Sampling Point Temperature 313.9 Deg F Test 1, 6/15/10, M30B, 8:00-10:00 0

8 Flue Gas Sampling Point Temperature 310.1 Deg F Test 2, 6/16/10, M30B, 7:45-9:45 0

9 Flue Gas Sampling Point Temperature 315.3 Deg F Test 3, 6/17/10, M30B, 10:10- 12:10 0

1 Flue Gas Pressure 0 atm 0 10 Flue Gas Pressure 0 atm 0 11 Flue Gas Pressure 0 atm 0 12 Flue Gas Pressure 0 atm 0

Tuesday, February 08, 2011 Page 26 of 42Joliet 9 - Midwest Generation EME, LLC

13 Flue Gas Pressure 0 atm 0 14 Flue Gas Pressure 0 atm 0 15 Flue Gas Pressure 0 atm 0 16 Flue Gas Pressure 0 atm 0 17 Flue Gas Pressure 0 atm 0 18 Flue Gas Pressure 0 atm 0 2 Flue Gas Pressure 0 atm 0 3 Flue Gas Pressure 0 atm 0 4 Flue Gas Pressure 0 atm 0 5 Flue Gas Pressure 0 atm 0 6 Flue Gas Pressure 0 atm 0 7 Flue Gas Pressure 0 atm 0 8 Flue Gas Pressure 0 atm 0 9 Flue Gas Pressure 0 atm 0 1 Standard Pressure 0 atm 0 10 Standard Pressure 0 atm 0 11 Standard Pressure 0 atm 0 12 Standard Pressure 0 atm 0 13 Standard Pressure 0 atm 0 14 Standard Pressure 0 atm 0 15 Standard Pressure 0 atm 0 16 Standard Pressure 0 atm 0 17 Standard Pressure 0 atm 0 18 Standard Pressure 0 atm 0 2 Standard Pressure 0 atm 0 3 Standard Pressure 0 atm 0 4 Standard Pressure 0 atm 0 5 Standard Pressure 0 atm 0 6 Standard Pressure 0 atm 0 7 Standard Pressure 0 atm 0 8 Standard Pressure 0 atm 0 9 Standard Pressure 0 atm 0 1 Standard Temperature 0 Deg F 0 10 Standard Temperature 0 Deg F 0 11 Standard Temperature 0 Deg F 0 12 Standard Temperature 0 Deg F 0

Tuesday, February 08, 2011 Page 27 of 42Joliet 9 - Midwest Generation EME, LLC

13 Standard Temperature 0 Deg F 0 14 Standard Temperature 0 Deg F 0 15 Standard Temperature 0 Deg F 0 16 Standard Temperature 0 Deg F 0 17 Standard Temperature 0 Deg F 0 18 Standard Temperature 0 Deg F 0 2 Standard Temperature 0 Deg F 0 3 Standard Temperature 0 Deg F 0 4 Standard Temperature 0 Deg F 0 5 Standard Temperature 0 Deg F 0 6 Standard Temperature 0 Deg F 0 7 Standard Temperature 0 Deg F 0 8 Standard Temperature 0 Deg F 0 9 Standard Temperature 0 Deg F 0 1 Unit Gross Electrical Output 331.02 MW Test 1, 6/15/10, OTM27/OTM28, 8:41-14:45 0

10 Unit Gross Electrical Output 330.95 MW Test 1, 6/15/10, M26A, 12:28- 15:38 0

11 Unit Gross Electrical Output 323.80 MW Test 2, 6/16/10, M26A, 12:10- 14:20 0

12 Unit Gross Electrical Output 324.99 MW Test 3, 6/17/10, M26A, 12:15- 15:27 0

13 Unit Gross Electrical Output 330.77 MW Test 1, 6/15/10, CTM033, 15:25- 16:40 0

14 Unit Gross Electrical Output 324.52 MW Test 2, 6/16/10, CTM033, 14:25- 15:40 0

15 Unit Gross Electrical Output 325.16 MW Test 3, 6/17/10, CTM033, 14:20- 15:40 0

16 Unit Gross Electrical Output 329.84 MW Test 1, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 8:30- 10:46 0

17 Unit Gross Electrical Output 326.99 MW Test 2, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 11:15- 13:30 0

Tuesday, February 08, 2011 Page 28 of 42Joliet 9 - Midwest Generation EME, LLC

APCD Run Data 18 Unit Gross Electrical Output 324.80 MW Test 3, 6/18/10, 0010, 0011, 0031, 25A, 18, 10, 13:50- 16:00 0

2 Unit Gross Electrical Output 323.75 MW Test 2, 6/16/10, OTM27/OTM28, 7:45-13:46 0

3 Unit Gross Electrical Output 324.05 MW Test 3, 6/17/10, OTM27/OTM28, 7:45-13:56 0

4 Unit Gross Electrical Output 330.94 MW Test 1, 6/15/10, M5/29, 8:00-12:10 0

5 Unit Gross Electrical Output 323.74 MW Test 2, 6/16/10, M5/29, 7:45-11:54 0

6 Unit Gross Electrical Output 323.68 MW Test 3, 6/17/10, M5/29, 7:45-11:55 0

7 Unit Gross Electrical Output 330.9 MW Test 1, 6/15/10, M30B, 8:00-10:00 0

8 Unit Gross Electrical Output 323.77 MW Test 2, 6/16/10, M30B, 7:45-9:45 0

9 Unit Gross Electrical Output 323.66 MW Test 3, 6/17/10, M30B, 10:10- 12:10 0

1 FGD Scrubber Liquor pH 0 pH 0 10 FGD Scrubber Liquor pH 0 pH 0 11 FGD Scrubber Liquor pH 0 pH 0 12 FGD Scrubber Liquor pH 0 pH 0 13 FGD Scrubber Liquor pH 0 pH 0 14 FGD Scrubber Liquor pH 0 pH 0 15 FGD Scrubber Liquor pH 0 pH 0 16 FGD Scrubber Liquor pH 0 pH 0 17 FGD Scrubber Liquor pH 0 pH 0 18 FGD Scrubber Liquor pH 0 pH 0 2 FGD Scrubber Liquor pH 0 pH 0 3 FGD Scrubber Liquor pH 0 pH 0 4 FGD Scrubber Liquor pH 0 pH 0 5 FGD Scrubber Liquor pH 0 pH 0 6 FGD Scrubber Liquor pH 0 pH 0 7 FGD Scrubber Liquor pH 0 pH 0 8 FGD Scrubber Liquor pH 0 pH 0 9 FGD Scrubber Liquor pH 0 pH 0

Tuesday, February 08, 2011 Page 29 of 42Joliet 9 - Midwest Generation EME, LLC

APCD Run Data

Process Lab Run Data Run Name Value UOM Comments Target Value 1 ACTIVATED CARBON ADSORPTION 0 lb/macf 5 1 ELECTROSTATIC PRECIPITATOR 0 0 1 OVERFIRE AIR 0 0

Run Name Value UOM Comments 1 Fuel Higher Heating Value 0 Btu/lb 1 Fuel Moisture 0 % 1 Fuel Mercury Content 0 ppm 1 Fuel Cadmium Content 0 ppm 1 Ultimate/Proximate Analysis 0 1 Fuel Nickel Content 0 ppm 1 Fuel Arsenic Content 0 ppm 1 Fuel Chromium Content 0 ppm 1 Fuel Beryllium Content 0 ppm 1 Fuel Lead Content 0 ppm 1 Fuel Manganese Content 0 ppm 1 Fuel Chlorine Content 0 ppm 1 Fuel Fluorine Content 0 ppm

Tuesday, February 08, 2011 Page 30 of 42Joliet 9 - Midwest Generation EME, LLC

Sampling / Stack Data Results Detail Location Stack - Method 0011 Average Run Number M0011-1 M0011-2 M0011-3 Test Date 6/18/2010 6/18/2010 6/18/2010 Run Start Time 8:30:00 AM 11:15:00 AM 1:50:00 PM Run Finish Time 10:46:00 AM 1:30:00 PM 4:00:00 PM Net Traversing Points 28 28 28 Net Run Time, minutes 120 120 120 Nozzle Diameter, inches 0.178 0.178 0.178 0.178 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.984 0.984 0.984 0.984 Barometric Pressure, inches of Mercury 28.7 28.7 28.7 28.700 Average Orifice Meter Differential, inches H2O 1.78 1.88 1.89 1.850 Dry Gas Meter Volume Sampled, cubic feet 103.526 106.391 107.248 105.722 Average Dry Gas Meter Temperature, °F 83.58 91.60 92.00 89.060 Dry Gas Meter Volume Sampled, dscf 95.348 96.587 97.297 96.411 Total Moisture Liquid collected, g 262.2 283.7 241.8 262.567 Volume of Water Vapor, standard cubic feet 12.34 13.35 11.38 12.357 Moisture Content of Stack Gas, % 11.46 12.14 10.47 11.357 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8854 0.8786 0.8953 0.886 Carbon Dioxide, % 13.7 13.4 13.6 13.567 Oxygen, % 5.8 5.9 5.8 5.833 Carbon Monoxide & Nitrogen, % 80.5 80.7 80.6 80.600 Fuel Factor 1.10 1.12 1.11 Dry Molecular Weight, lb/lb-Mole 30.42 30.38 30.41 30.403 Wet Molecular weight, lb/lb-Mole 29.00 28.88 29.11 28.997 Flue Gas Static Pressure, inches of H2O 1.9 1.9 1.9 1.900 Absolute Flue Gas Pressure, inches of Mercury 28.84 28.84 28.84 28.840 Average Stack Gas Temperature, °F 297.21 301.50 303.17 300.627 Average Velocity Head, inches of H2O 3.4413763289 9046 3.560501134

59291 3.599691470

82216 3.534 Average Stack Gas Velocity, feet/second 126.76 129.57 129.90 128.743 Stack Cross-Sectional Area, square feet 159.485 159.485 159.485 159.485 Dry Volumetric Flow Rate, dry scfm 721,845.2 728,055.4 742,155.9 730,685.500 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,212,979.1 1,239,868.3 1,243,026.1 1,231,957.8 33 Percent Isokinetic of Sampling Rate, % 101.6 102.0 100.8 101.467 Percent Excess Air, % 37.5 38.3 37.5 37.767 F-Factor, dscfm/MMBtu @ %O2 9681 9681 9681 9,681.000 Round Duct Diameter, inches 171 171 171 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 0 0 0 0.000 Fc 1854 1854 1854 1,854.000

Tuesday, February 08, 2011 Page 31 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 10 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units

Tuesday, February 08, 2011 Page 32 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units

Tuesday, February 08, 2011 Page 33 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 26A Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc

Tuesday, February 08, 2011 Page 34 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 29 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc

Tuesday, February 08, 2011 Page 35 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 3A CO2 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units

Tuesday, February 08, 2011 Page 36 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 3A CO2 3 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units

Tuesday, February 08, 2011 Page 37 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 3A CO2 3 6 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units

Tuesday, February 08, 2011 Page 38 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 3A O2 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units

Tuesday, February 08, 2011 Page 39 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 3A O2 3 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units

Tuesday, February 08, 2011 Page 40 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - Method 3A O2 3 6 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units

Tuesday, February 08, 2011 Page 41 of 42Joliet 9 - Midwest Generation EME, LLC

Location Stack - OTM - 27/28 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc

Tuesday, February 08, 2011 Page 42 of 42