Emission testing results for Windhager BioWIN and BioWIN-XL

BioWIN260 - TUV Test report H-C3 1190-01/08, 2008-03-15

High Load

Measured flue gas parameters Steady State

CO-content ppm 68 Test report page 4/6

mg/m3 78 calculated @ 7.2% O2

CO (related to 10% O2) mg/m3 62 Test report page 5/6

CO (related to 13% O2) mg/m3 45 Test report page 5/6

Calculated

CO (related to 7% O2) mg/m3 79

CO-content ppm 69

Measured Dust

Dust particulites mg/m3 15

Calculated with CO molar mass of 28.01 gr/mol

Dust particulites (related to 10% O2) mg/m3 11

Dust particulites (related to 13% O2) mg/m3 8

Dust particulites mg/MJ 5

Calculated Lbs/MMBTU 0.01

Pellet boiler efficiency

Effifency LHV, measured % 93

Efficiency HHV, calculated % 87

Moisture content pellets 6.40%
BioWIN210 - TUV Test report NA

High Load

Measured flue gas parameters Steady State

CO-content ppm Test report page 4/6

mg/m3 calculated @ 7.2% O2

CO (related to 10% O2) mg/m3 Test report page 5/6

CO (related to 13% O2) mg/m3 Test report page 5/6

Calculated

CO (related to 7% O2) mg/m3

CO-content ppm

Measured Dust

Dust particulites mg/m3

Calculated with CO molar mass of 28.01 gr/mol

Dust particulites (related to 10% O2) mg/m3

Dust particulites (related to 13% O2) mg/m3

Dust particulites mg/MJ

Calculated Lbs/MMBTU

Pellet boiler efficiency

Effifency LHV, measured %

Efficiency HHV, calculated %

Moisture content pellets 
BioWIN150 - TUV Test report H-C2 1190-02/12, 2012-05-23

High Load

Measured flue gas parameters Steady State

CO-content ppm 52 Test report page 4/6

mg/m3 60 calculated @ 6% O2

CO (related to 10% O2) mg/m3 21 Test report page 5/6

CO (related to 13% O2) mg/m3 15 Test report page 5/6

Calculated

CO (related to 7% O2) mg/m3 17

CO-content ppm 15

Measured Dust

Dust particulites mg/m3 18

Calculated with CO molar mass of 28.01 gr/mol

Dust particulites (related to 10% O2) mg/m3 14

Dust particulites (related to 13% O2) mg/m3 15

Dust particulites mg/MJ 6

Calculated Lbs/MMBTU 0.014

Pellet boiler efficiency

Effifency LHV, measured % 92.7

Efficiency HHV, calculated % 87

Moisture content pellets 6.40%
BioWIN100 - TUV Test report H-C1 1190-03/12, 2012-05-23

High Load

Measured flue gas parameters Steady State

CO-content ppm 60 Test report page 4/6

mg/m3 69 calculated @ 8% O2

CO (related to 10% O2) mg/m3 59 Test report page 5/6

CO (related to 13% O2) mg/m3 43 Test report page 5/6

Calculated

CO (related to 7% O2) mg/m3 75

CO-content ppm 65

Measured Dust

Dust particulites mg/m3 17

Calculated with CO molar mass of 28.01 gr/mol

Dust particulites (related to 10% O2) mg/m3 13

Dust particulites (related to 13% O2) mg/m3 9

Dust particulites mg/MJ 6

Calculated Lbs/MMBTU 0.014

Pellet boiler efficiency

Effifency LHV, measured % 93.2

Efficiency HHV, calculated % 87

Moisture content pellets 6.40%
BioWIN350 - TUV Test report H-C4 1190-00/11, 2011-02-09

High Load

Measured flue gas parameters Steady State

CO-content ppm 39 Test report page 4/6

mg/m3 45 calculated @ 8.4% O2

CO (related to 10% O2) mg/m3 39 Test report page 5/6

CO (related to 13% O2) mg/m3 28 Test report page 5/6

Calculated

CO (related to 7% O2) mg/m3 50

CO-content ppm 44

Measured Dust

Dust particulites mg/m3 21

Calculated with CO molar mass of 28.01 gr/mol

Dust particulites (related to 10% O2) mg/m3 17

Dust particulites (related to 13% O2) mg/m3 12

Dust particulites mg/MJ 8

Calculated Lbs/MMBTU 0.019

Pellet boiler efficiency

Effifency LHV, measured % 91.2

Efficiency HHV, calculated % 86

Moisture content pellets 6.40%
BioWIN450 NA

High Load

Measured flue gas parameters Steady State

CO-content ppm Test report page 4/6

mg/m3 calculated @ 9.5% O2

CO (related to 10% O2) mg/m3 Test report page 5/6

CO (related to 13% O2) mg/m3 Test report page 5/6

Calculated

CO (related to 7% O2) mg/m3

CO-content ppm

Measured Dust

Dust particulites mg/m3

Calculated with CO molar mass of 28.01 gr/mol

Dust particulites (related to 10% O2) mg/m3

Dust particulites (related to 13% O2) mg/m3

Dust particulites mg/MJ

Calculated Lbs/MMBTU

Pellet boiler efficiency

Effifency LHV, measured %

Efficiency HHV, calculated %

Moisture content pellets 
BioWIN600 - TUV Test report H-C5 1190-00/11, 2011-02-09

High Load

Measured flue gas parameters Steady State

CO-content ppm 45 Test report page 4/6

mg/m3 52 calculated @ 9.5% O2

CO (related to 10% O2) mg/m3 43 Test report page 5/6

CO (related to 13% O2) mg/m3 31 Test report page 5/6

Calculated

CO (related to 7% O2) mg/m3 55

CO-content ppm 48

Measured Dust

Dust particulites mg/m3 21

Calculated with CO molar mass of 28.01 gr/mol

Dust particulites (related to 10% O2) mg/m3 16

Dust particulites (related to 13% O2) mg/m3 12

Dust particulites mg/MJ 8

Calculated Lbs/MMBTU 0.019

Pellet boiler efficiency

Effifency LHV, measured % 90.1

Efficiency HHV, calculated % 85

Moisture content pellets 6.40%
FireWIN120 - TUV Test report W-O 1162-00/68, 2008-04-15

High Load

Measured flue gas parameters Steady State

CO-content ppm 72 Test report page 11/15

mg/m3 83 calculated @ 9.5% O2

CO (related to 10% O2) mg/m3 NA

CO (related to 13% O2) mg/m3 48 Test report page 14/15

Calculated

CO (related to 7% O2) mg/m3 108

CO-content ppm 94

Measured Dust

Dust particulites mg/m3 37

Calculated with CO molar mass of 28.01 gr/mol

Dust particulites (related to 10% O2) mg/m3 NA

Dust particulites (related to 13% O2) mg/m3 20

Dust particulites mg/MJ 13

Calculated Lbs/MMBTU 0.030

Pellet boiler efficiency

Effifency LHV, measured % 94.1

Efficiency HHV, calculated % 88

Moisture content pellets 6.40%
FireWIN90 - TUV Test report W-O 1162-00/68, 2008-04-15

High Load

Measured flue gas parameters Steady State

CO-content ppm 74 Test report page 11/15

mg/m3 85 calculated @ 9.3% O2

CO (related to 10% O2) mg/m3 NA

CO (related to 13% O2) mg/m3 55 Test report page 14/15

Calculated

CO (related to 7% O2) mg/m3 103

CO-content ppm 90

Measured Dust

Dust particulites mg/m3 26

Calculated with CO molar mass of 28.01 gr/mol

Dust particulites (related to 10% O2) mg/m3 NA

Dust particulites (related to 13% O2) mg/m3 16

Dust particulites mg/MJ 10

Calculated Lbs/MMBTU 0.023

Pellet boiler efficiency

Effifency LHV, measured % 94.5

Efficiency HHV, calculated % 88

Moisture content pellets 6.40%