### Name: Fred Walsh

Title: Environmental Manager Company: Mt. Carmel Cogen Inc. Sign Date: 9/29/2010 Name: Stephen Schell Title: President Company: Air Analysis, LLC Sign Date: 9/29/2010 Permitted Facility Representative / Date Testing Company Representative / Date 

## Mount Carmel Cogen - ICR Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Sunday, January 30, 2011 Page 1 of 12

### Mount Carmel Cogen - ICR 9/29/2010 Facility Information: Foster Wheeler Mt. Carmel Cogen P.O. Box 409

Marion Heights PA 17832 Contact: Fred Walsh Phone: 570 373-3999 Fax: Email: fredwalsh@mtcarmelcogen.com Testing Company: Air Analysis, LLC t/a SGF Consulting Services 189 Hausman Road

Lenhartsville PA 19534 Contact: Stephen Schell Phone: 610 756-3490 Fax: 610 756-3491 Email: sschell@hughes.net

Air Permit Number: 49-00001 Permitted Source ID/Name: Foster Wheeler Mt. Carmel Cogen SG-101 Permitted Maximum Process Rate: Max. Normal Operation Process Rate: 623.5 mmBtu/hr Target Process Test Rate 90% of Maximum Load

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: The Mount Carmel Cogeneration facility typically produces 40 MW of electricity and consists of a 623.5 mmBtu/hr Foster Wheeler brand circulating fluidized bed boiler, which utilizes waste anthracite coal as its main fuel. Emissions are controlled with limestone addition for sulfulr dioxide emissions control and a Joy Environmental Equipment Company fabric filter collector for particulate emissions control. Flue gas emissions are discharged from the fabric filter collector through a Howden I.D. Fan rated at 239,036 cfm and then to the atmosphere through a vertical stack. Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information: AFS #: 4209700067 FRS #: 110007026306

SCC / Description 10102018 External Combustion Boilers - Electric Generation - Waste Coal - Circulating Fluidized Bed Combustion

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Exhaust Duct 0 54 54 4 72.367 3 64.375 82.625 Stack 108 1812 1860 2 108 6 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location Carbon Monoxide Method 10 3 120 0 Exhaust Duct Custom Method 18 3 120 0 Methane Exhaust Duct Total organic compounds

(TOC) as Propane Method 25A 3 120 0 Exhaust Duct

O2 Method 3A O2 0 During each test run Exhaust Duct 

### Sunday, January 30, 2011 Page 2 of 12

### Mount Carmel Cogen - ICR 9/29/2010

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.

Co2 Method 3A CO2 0 During each test run Exhaust Duct Sulfur Dioxide Method 6C 3 120 0 Exhaust Duct Flowrate Method 1 - 4 0 Throughout testing program Stack

% H2O Method 1 - 4 0 During each test run Stack Custom Method 0010 3 120 0 Semi-Volatile Organic HAP Stack Formaldehyde Method 0011 3 120 0 Stack Custom Method 0031 3 120 0 Volatile Organic HAP Stack



### Sunday, January 30, 2011 Page 3 of 12

### Mount Carmel Cogen - ICR 9/29/2010 Sampling / Stack Data Results Summary 

### Location Exhaust Duct - Method 10 Average Run Number 1 2 3 Test Date 6/22/2010 6/22/2010 6/22/2010 Run Start Time 7:30:00 AM 10:33:00 AM 1:44:00 PM

Run Finish Time 9:29:00 AM 12:22:00 PM 3:43:00 PM

Carbon Dioxide, % 12.23 12.64 12.71 12.527 Oxygen, % 8.23 7.72 7.73 7.893 Dry Volumetric Flow Rate, dry scfm 194336 194463 194463 194,420.667 F-Factor, dscfm/MMBtu @ %O2 10865 11255 11255 11,125.000 Moisture, % 7.41 6.87 6.87 7.050 Fuel Type Override Override Override Fw 0 0 0 0.000 Fc 0 0 0 0.000



### Location Exhaust Duct - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type Fw Fc



### Sunday, January 30, 2011 Page 4 of 12

### Mount Carmel Cogen - ICR 9/29/2010 Location Exhaust Duct - Method 6C Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type Fw Fc



### Sunday, January 30, 2011 Page 5 of 12

### Mount Carmel Cogen - ICR 9/29/2010 Emissions Summary

Process Run Data 

### Location: Exhaust Duct - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 lb/mmBtuO2 7.24E-02 8.06E-02 7.92E-02 0.077 ppm 5.56E+01 6.21E+01 6.10E+01 59.567 ppm@7%O2 6.10E+01 6.55E+01 6.44E+01 63.633


### Location: Exhaust Duct - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 1.14E-03 6.11E-04 7.49E-04 0.001 ppm 5.56E-01 2.99E-01 3.66E-01 0.407 ppm@7%O2 6.10E-01 3.15E-01 3.86E-01 0.437



### Location: Exhaust Duct - Method 6C Compound: Sulfur Dioxide Average Run 1 2 3 lb/mmBtuO2 8.65E-02 1.30E-01 1.09E-01 0.109 ppm 2.90E+01 4.38E+01 3.68E+01 36.533 ppm@7%O2 3.18E+01 4.62E+01 3.88E+01 38.933



### Sunday, January 30, 2011 Page 6 of 12

### Mount Carmel Cogen - ICR 9/29/2010 Process Run Data



### Run Name Value UOM Comments Target Value 1 Anthracite Waste (Culm) Fuel Feed 78.33 TPH Run 1 M0011, 6/21/10 13:22- 15:29 0

1 Steam Flow 420 klbs/hr 0 1 Mega Watt output 40.09 MW 0 

### 1 Stack Moisture 5.79 % 0 1 Stack Flow Rate 191177 scfm 0 1 Stack Temperature 318 F 0 

### 1 Stack O2 7.86 % 0 1 Stack CO2 12.46 % 0 2 Anthracite Waste (Culm) Fuel Feed 75 TPH Run 2 M0011, Run 1 M25A, M10 & M6C, 6/22/10 7:30-9:35 0

2 Steam Flow 420 klbs/hr 0 

### 2 Mega Watt output 40.73 MW 0 2 Stack Moisture 7.41 % 0 2 Stack Flow Rate 194336 scfm 0 

### 2 Stack Temperature 315 F 0 2 Stack O2 8.23 % 0 2 Stack CO2 12.23 % 0 

### 3 Anthracite Waste (Culm) Fuel Feed 78.33 TPH Run 3 M0011, Run 2 M25A, M10 & M6C - 6/22/10 10:20-12:27 0

3 Steam Flow 420 klbs/hr 0 3 Mega Watt output 40.56 MW 0 3 Stack Moisture 6.87 % 0 

### 3 Stack Flow Rate 194463 scfm 0 3 Stack Temperature 316 F 0 

### 3 Stack O2 7.72 % 0 3 Stack CO2 12.64 % 0 4 Anthracite Waste (Culm) Fuel Feed 78.3 TPH Run 3 M25A, M10 & M6C - 6/22/10 13:44-15:43 0

4 Steam Flow 420 klbs/hr 0 4 Mega Watt output 40.94 MW 0



### Sunday, January 30, 2011 Page 7 of 12

### Mount Carmel Cogen - ICR 9/29/2010

APCD Run Data 4 Stack Moisture 6.87 % 0 

### 4 Stack Flow Rate 194463 scfm 0 4 Stack Temperature 316 F 0 4 Stack O2 7.73 % 0 

### 4 Stack CO2 12.71 % 0 5 Anthracite Waste (Culm) Fuel Feed 72.7 TPH Run 1 M0010 & M0031 - 6/23/10 7:17-9:25 0



### 5 Steam Flow 420 klbs/hr 0 5 Mega Watt output 40.27 MW 0 

### 5 Stack Moisture 6.54 % 0 5 Stack Flow Rate 185535 scfm 0 5 Stack Temperature 318 F 0 

### 5 Stack O2 8.08 % 0 5 Stack CO2 12.27 % 0 6 Anthracite Waste (Culm) Fuel Feed 71 TPH Run 2 M0010 & M0031 - 6/23/10 10:50 - 12:58 0

6 Steam Flow 419 klbs/hr 0 6 Mega Watt output 39.91 MW 0 

### 6 Stack Moisture 7.19 % 0 6 Stack Flow Rate 188154 scfm 0 6 Stack Temperature 312 F 0 

### 6 Stack O2 8.06 % 0 6 Stack CO2 12.25 % 0 7 Anthracite Waste (Culm) Fuel Feed 66.8 TPH Run 3 M0010 & M0031 - 6/24/10 7:55-10:25 0

7 Steam Flow 418 klbs/hr 0 7 Mega Watt output 39.69 MW 0 

### 7 Stack Moisture 7.07 % 0 7 Stack Flow Rate 189265 scfm 0 7 Stack Temperature 309 F 0 

### 7 Stack O2 8.23 % 0 7 Stack CO2 12.05 % 0

Run Name Value UOM Comments Target Value 

### 1 BAGHOUSE 12 " H2O 0 Sunday, January 30, 2011 Page 8 of 12

### Mount Carmel Cogen - ICR 9/29/2010

Process Lab Run Data 1 12 " H2O 0 

### 2 BAGHOUSE 12 " H2O 0 3 BAGHOUSE 12 " H2O 0 4 BAGHOUSE 12 " H2O 0 

### 5 BAGHOUSE 12 " H2O 0 6 BAGHOUSE 12 " H2O 0 7 BAGHOUSE 12 " H2O 0 

### 1 DRY LIMESTONE INJECTION 6.78 TPH 0 2 DRY LIMESTONE INJECTION 6.22 TPH 0 3 DRY LIMESTONE INJECTION 6.44 TPH 0 

### 4 DRY LIMESTONE INJECTION 7.69 TPH 0 5 DRY LIMESTONE INJECTION 7.13 TPH 0 6 DRY LIMESTONE INJECTION 6.48 TPH 0 

### 7 DRY LIMESTONE INJECTION 7.25 TPH 0

Sunday, January 30, 2011 Page 9 of 12

### Mount Carmel Cogen - ICR 9/29/2010 Sampling / Stack Data Results Detail 

### Location Exhaust Duct - Method 10 Average Run Number 1 2 3 Test Date 6/22/2010 6/22/2010 6/22/2010 Run Start Time 7:30:00 AM 10:33:00 AM 1:44:00 PM Run Finish Time 9:29:00 AM 12:22:00 PM 3:43:00 PM Carbon Dioxide, % 12.23 12.64 12.71 12.527 Oxygen, % 8.23 7.72 7.73 7.893 Fuel Factor 1.04 1.04 1.04 Dry Volumetric Flow Rate, dry scfm 194336 194463 194463 194,420.667 F-Factor, dscfm/MMBtu @ %O2 10865 11255 11255 11,125.000 Moisture, % 7.41 6.87 6.87 7.050 Analyzer Make Thermo Electron Thermo

Electron Thermo

Electron Analyzer Model 48C 48C 48C Analyzer Serial Number 48C-54732- 301 48C-54732-

301 48C-54732-

301 Operating Range 126 126 126 126.000 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 4 5 6 5.000 Calibration Pre Zero Cylinder ID CC133012 CC133012 CC133012 Calibration Pre Zero Cylinder Instrument Response 0.41 0.69 0.15 0.417 Calibration Pre Zero Cylinder Bias 0.19 0.41 -0.02 0.193 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID CC-91200 CC-91200 CC-91200 Calibration Pre High Cylinder Instrument Response 49.78 50.8 48.99 49.857 Calibration Pre High Cylinder Bias 1.97 2.78 1.34 2.030 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID CC133012 CC133012 CC133012 Calibration Post Zero Cylinder Instrument Response 0.69 0.15 -0.5 0.113 Calibration Post Zero Cylinder Bias 0.41 -0.02 -0.53 -0.047 Calibration Post Zero Cylinder Drift 0.22 0.43 0.51 0.387 Calibration Post High Cylinder ID CC-91200 CC-91200 CC-91200 Calibration Post High Cylinder Instrument Response 50.8 48.99 48.73 49.507 Calibration Post High Cylinder Bias 2.78 1.34 1.13 1.750 Calibration Post High Cylinder Drift 0.81 1.44 0.21 0.820 Cavg 56.19 62.24 60.03 59.487 Cavg Units ppmvd ppmvd ppmvd Cgas 55.5953 62.1011 61.0215 59.573 Cgas Units ppmvd ppmvd ppmvd Fuel Type Override Override Override Fw 0 0 0 0.000 Fc 0 0 0 0.000 Cgasw 0 0 0 0.000 Cgasw Units



### Sunday, January 30, 2011 Page 10 of 12

### Mount Carmel Cogen - ICR 9/29/2010 Location Exhaust Duct - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Sunday, January 30, 2011 Page 11 of 12

### Mount Carmel Cogen - ICR 9/29/2010 Location Exhaust Duct - Method 6C Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Sunday, January 30, 2011 Page 12 of 12