(918) 307-8865 or (888) 461-8778 

www.airhygiene.com 

Corporate Headquarters

5634 S. 122nd E. Ave. Ste. F 

Tulsa, Oklahoma 74146 

Las Vegas Office

5925 E. Lake Mead Blvd. 

Las Vegas, Nevada 89156 

Philadelphia Office

8900 State Road 

Philadelphia, Pennsylvania 19136 

Houston Office 

1920 Treble Drive 

Humble, Texas 77338 
STACK EMISSIONS STUDY 

FROM THE 

CATERPILLAR G3520C 

UNITS 1 - 6 

PREPARED FOR 

ENERGY DEVELOPMENTS 

COVEL GARDENS LANDFILL GAS 

POWER STATION 

REGULATED ENTITY #: RN104156062 

CUSTOMER REFERENCE #: CN601527534 

SAN ANTONIO, TEXAS 

AUGUST 29-30, 2007 

Prepared and Reviewed by: 

 

 

 John M. Plummer, Project Manager Quinn A. Bierman, President 

TABLE OF CONTENTS 

1.0 INTRODUCTION ______________________________________________________ 1

1.1 TEST PURPOSE AND OBJECTIVES __________________________________ 1

1.2 SUMMARY OF TEST PROGRAM _____________________________________ 1

1.2.1 Participating Organizations__________________________________________ 1 

1.2.2 Industry _________________________________________________________ 1 

1.2.3 Plant Location ____________________________________________________ 1 

1.2.4 Equipment Tested _________________________________________________ 1 

1.2.5 Emission Points___________________________________________________ 1 

1.2.6 Pollutants Measured _______________________________________________ 1 

1.2.7 Dates of Emission Test _____________________________________________ 1 

1.3 KEY PERSONNEL __________________________________________________ 2

2.0 SUMMARY OF TEST RESULTS ________________________________________ 2

2.1 EMISSION TEST RESULTS __________________________________________ 2

3.0 SOURCE OPERATION_________________________________________________ 9

3.1 PROCESS DESCRIPTION____________________________________________ 9

4.0 SAMPLING AND ANALYTICAL PROCEDURES __________________________ 9

4.1 TEST METHODS ____________________________________________________ 9

4.2 INSTRUMENT CONFIGURATION AND OPERATIONS __________________ 9

APPENDICES 

Appendix A Results and Calculations 

Appendix B Quality Assurance Activities 

Appendix C Calibration Gas Certifications 
ed-07-sanantonio-tx-ecom#3-rpt Page 1 

Stack Emissions Study 

from the 

Caterpillar G3520C, Units 1 - 6 

prepared for 

Energy Developments 

San Antonio, Texas 

August 29-30, 2007 

1.0 INTRODUCTION 

Air Hygiene International, Inc. (Air Hygiene) has completed the stack sampling survey for nitrogen 

oxides (NOx), carbon monoxide (CO), and oxygen (O2) from the exhausts of the Caterpillar G3520C, 

Units 1 - 6 at Energy Developments’ Covel Gardens Landfill Gas Power Station near San Antonio, 

Texas. This report details the background information, test results, process description, 

sampling/analysis methodology, and quality control/assurance activities of the stack sampling survey 

conducted on August 29-30, 2007. 

1.1 TEST PURPOSE AND OBJECTIVES

The purpose of the test was to conduct the quarterly emission tests to document emission levels of 

selected pollutants at normal operation levels of the designated engines. The information will be used 

to confirm compliance with the air quality permit requirements. The specific objective was to 

determine the emission concentration of NOx, CO, and O2 from the exhausts of Energy Developments’ 

Caterpillar G3520C, Units 1 - 6 during normal operating conditions. 

1.2 SUMMARY OF TEST PROGRAM

The following list details pertinent information related to this specific project: 

1.2.1 Participating Organizations: 

3⁄4 Energy Developments 

3⁄4 Air Hygiene 

1.2.2 Industry: 

3⁄4 Electric Utility 

1.2.3 Plant Location: 

3⁄4 Covel Gardens Landfill Gas Power Station near San Antonio, Texas 

1.2.4 Equipment Tested: 

3⁄4 Caterpillar G3520C, Units 1 - 6, Emission Point Numbers E1 - E6 

1.2.5 Emission Points: 

3⁄4 Exhausts of the Caterpillar G3520C, Units 1 - 6 

1.2.6 Pollutants Measured: 

3⁄4 NOx 

3⁄4 CO 

3⁄4 O2

1.2.7 Date of Emission Test: 

3⁄4 August 29-30, 2007 
ed-07-sanantonio-tx-ecom#3-rpt Page 2 

1.3 KEY PERSONNEL

Energy Developments: Liza Mireles 713-300-3323 

Air Hygiene: Mike Plummer 918-307-8865

2.0 SUMMARY OF TEST RESULTS 

2.1 EMISSION TEST RESULTS 

Results from the sampling conducted at Covel Gardens Landfill Gas Power Station from the 

Caterpillar G3520C, Units 1 - 6 exhausts on August 29-30, 2007 are summarized in the following 

tables. 
ed-07-sanantonio-tx-ecom#3-rpt Page 3 

TABLE 2.1 

UNIT 1 EMISSIONS REPORT 

Company: Date:

 Engine Tested: Location:

Stack Gas Flow Rate: Method 2

Test # Brake 

Horsepower O2 Conc. (%) Fuel Heating Value 

(Btu/SCF) [HHV]

F Factor-Dry Oxy.

(DSCFex/MMBtu)

Fuel Flow

(SCF/hr)

Stack Flow

(SCF/hr)

1 2,172.0 7.8 474.54 9,444.22 N/A 250,000.00

2 2,172.0 7.9 474.54 9,444.22 N/A 250,000.00

3 2,172.0 7.8 474.54 9,444.22 N/A 250,000.00

Average 2,172.0 7.9 474.54 9,444.22 N/A 250,000.00

NOx Mass Emission Rate

Test # Brake 

Horsepower 

NOx Conc. 

(ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr)

1 2,172.0 69.0 46.01 0.43 2.06 9.02

2 2,172.0 68.0 46.01 0.42 2.03 8.89

3 2,172.0 63.0 46.01 0.39 1.88 8.24

Average 2,172.0 66.7 46.01 0.42 1.99 8.72

CO Mass Emission Rate

Test # Brake 

Horsepower 

CO Conc. 

(ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr)

1 2,172.0 658.0 28.00 2.50 11.96 52.37

2 2,172.0 652.0 28.00 2.47 11.85 51.89

3 2,172.0 672.3 28.00 2.55 12.22 53.51

Average 2,172.0 660.8 28.00 2.51 12.01 52.59

Energy Development August 29, 2007

Caterpillar G3520 C, Unit #1 Covel Gardens Power Station
ed-07-sanantonio-tx-ecom#3-rpt Page 4 

TABLE 2.2 

UNIT 2 EMISSIONS REPORT 

Company: Date:

 Engine Tested: Location:

Stack Gas Flow Rate: Method 2

Test # Brake 

Horsepower O2 Conc. (%) Fuel Heating Value 

(Btu/SCF) [HHV]

F Factor-Dry Oxy.

(DSCFex/MMBtu)

Fuel Flow

(SCF/hr)

Stack Flow

(SCF/hr)

1 2,172.0 8.0 474.54 9,637.46 N/A 250,000.00

2 2,172.0 8.1 474.54 9,637.46 N/A 250,000.00

3 2,172.0 8.0 474.54 9,637.46 N/A 250,000.00

Average 2,172.0 8.1 474.54 9,637.46 N/A 250,000.00

NOx Mass Emission Rate

Test # Brake 

Horsepower 

NOx Conc. 

(ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr)

1 2,172.0 82.7 46.01 0.52 2.47 10.81

2 2,172.0 71.7 46.01 0.45 2.14 9.37

3 2,172.0 67.7 46.01 0.42 2.02 8.85

Average 2,172.0 74.0 46.01 0.46 2.21 9.68

CO Mass Emission Rate

Test # Brake 

Horsepower 

CO Conc. 

(ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr)

1 2,172.0 730.7 28.00 2.77 13.28 58.15

2 2,172.0 724.3 28.00 2.75 13.16 57.65

3 2,172.0 747.0 28.00 2.83 13.57 59.45

Average 2,172.0 734.0 28.00 2.79 13.34 58.42

Energy Development August 29, 2007

Caterpillar G3520 C, Unit #2 Covel Gardens Power Station
ed-07-sanantonio-tx-ecom#3-rpt Page 5 

TABLE 2.3 

UNIT 3 EMISSIONS REPORT 

Company: Date:

 Engine Tested: Location:

Stack Gas Flow Rate: Method 2

Test # Brake 

Horsepower O2 Conc. (%) Fuel Heating Value 

(Btu/SCF) [HHV]

F Factor-Dry Oxy.

(DSCFex/MMBtu)

Fuel Flow

(SCF/hr)

Stack Flow

(SCF/hr)

1 2,172.0 7.8 474.54 9,637.46 N/A 250,000.00

2 2,172.0 7.9 474.54 9,637.46 N/A 250,000.00

3 2,172.0 7.9 474.54 9,637.46 N/A 250,000.00

Average 2,172.0 7.9 474.54 9,637.46 N/A 250,000.00

NOx Mass Emission Rate

Test # Brake 

Horsepower 

NOx Conc. 

(ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr)

1 2,172.0 75.0 46.01 0.47 2.24 9.81

2 2,172.0 69.7 46.01 0.43 2.08 9.11

3 2,172.0 71.0 46.01 0.44 2.12 9.29

Average 2,172.0 71.9 46.01 0.45 2.15 9.40

CO Mass Emission Rate

Test # Brake 

Horsepower 

CO Conc. 

(ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr)

1 2,172.0 732.3 28.00 2.78 13.31 58.29

2 2,172.0 730.3 28.00 2.77 13.27 58.13

3 2,172.0 730.3 28.00 2.77 13.27 58.13

Average 2,172.0 731.0 28.00 2.77 13.28 58.18

Energy Development August 29, 2007

Caterpillar G3520 C, Unit #3 Covel Gardens Power Station
ed-07-sanantonio-tx-ecom#3-rpt Page 6 

TABLE 2.4 

UNIT 4 EMISSIONS REPORT 

Company: Date:

 Engine Tested: Location:

Stack Gas Flow Rate: Method 2

Test # Brake 

Horsepower O2 Conc. (%) Fuel Heating Value 

(Btu/SCF) [HHV]

F Factor-Dry Oxy.

(DSCFex/MMBtu)

Fuel Flow

(SCF/hr)

Stack Flow

(SCF/hr)

1 2,172.0 8.3 474.54 9,637.46 N/A 250,000.00

2 2,172.0 8.0 474.54 9,637.46 N/A 250,000.00

3 2,172.0 7.8 474.54 9,637.46 N/A 250,000.00

Average 2,172.0 8.0 474.54 9,637.46 N/A 250,000.00

NOx Mass Emission Rate

Test # Brake 

Horsepower 

NOx Conc. 

(ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr)

1 2,172.0 77.0 46.01 0.48 2.30 10.07

2 2,172.0 77.7 46.01 0.48 2.32 10.16

3 2,172.0 77.7 46.01 0.48 2.32 10.16

Average 2,172.0 77.4 46.01 0.48 2.31 10.13

CO Mass Emission Rate

Test # Brake 

Horsepower 

CO Conc. 

(ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr)

1 2,172.0 733.3 28.00 2.78 13.33 58.37

2 2,172.0 730.0 28.00 2.77 13.26 58.10

3 2,172.0 734.0 28.00 2.79 13.34 58.42

Average 2,172.0 732.4 28.00 2.78 13.31 58.29

Energy Development August 30, 2007

Caterpillar G3520 C, Unit #4 Covel Gardens Power Station
ed-07-sanantonio-tx-ecom#3-rpt Page 7 

TABLE 2.5 

UNIT 5 EMISSIONS REPORT 

Company: Date:

 Engine Tested: Location:

Stack Gas Flow Rate: Method 2

Test # Brake 

Horsepower O2 Conc. (%) Fuel Heating Value 

(Btu/SCF) [HHV]

F Factor-Dry Oxy.

(DSCFex/MMBtu)

Fuel Flow

(SCF/hr)

Stack Flow

(SCF/hr)

1 2,172.0 7.9 474.54 9,637.46 N/A 250,000.00

2 2,172.0 7.9 474.54 9,637.46 N/A 250,000.00

3 2,172.0 7.9 474.54 9,637.46 N/A 250,000.00

Average 2,172.0 7.9 474.54 9,637.46 N/A 250,000.00

NOx Mass Emission Rate

Test # Brake 

Horsepower 

NOx Conc. 

(ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr)

1 2,172.0 76.7 46.01 0.48 2.29 10.03

2 2,172.0 68.7 46.01 0.43 2.05 8.98

3 2,172.0 76.7 46.01 0.48 2.29 10.03

Average 2,172.0 74.0 46.01 0.46 2.21 9.68

CO Mass Emission Rate

Test # Brake 

Horsepower 

CO Conc. 

(ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr)

1 2,172.0 725.3 28.00 2.75 13.18 57.73

2 2,172.0 725.7 28.00 2.75 13.19 57.75

3 2,172.0 727.7 28.00 2.76 13.22 57.91

Average 2,172.0 726.2 28.00 2.76 13.20 57.80

Energy Development August 29, 2007

Caterpillar G3520 C, Unit #5 Covel Gardens Power Station
ed-07-sanantonio-tx-ecom#3-rpt Page 8 

TABLE 2.6 

UNIT 6 EMISSIONS REPORT 

Company: Date:

 Engine Tested: Location:

Stack Gas Flow Rate: Method 2

Test # Brake 

Horsepower O2 Conc. (%) Fuel Heating Value 

(Btu/SCF) [HHV]

F Factor-Dry Oxy.

(DSCFex/MMBtu)

Fuel Flow

(SCF/hr)

Stack Flow

(SCF/hr)

1 2,172.0 8.3 474.54 9,637.46 N/A 250,000.00

2 2,172.0 8.3 474.54 9,637.46 N/A 250,000.00

3 2,172.0 8.3 474.54 9,637.46 N/A 250,000.00

Average 2,172.0 8.3 474.54 9,637.46 N/A 250,000.00

NOx Mass Emission Rate

Test # Brake 

Horsepower 

NOx Conc. 

(ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr)

1 2,172.0 58.0 46.01 0.36 1.73 7.59

2 2,172.0 49.3 46.01 0.31 1.47 6.45

3 2,172.0 52.0 46.01 0.32 1.55 6.80

Average 2,172.0 53.1 46.01 0.33 1.59 6.95

CO Mass Emission Rate

Test # Brake 

Horsepower 

CO Conc. 

(ppmvd) MW E (g/hp*hr) E (lb/hr) E (ton/yr)

1 2,172.0 725.3 28.00 2.75 13.18 57.73

2 2,172.0 690.3 28.00 2.62 12.54 54.94

3 2,172.0 699.3 28.00 2.65 12.71 55.66

Average 2,172.0 705.0 28.00 2.68 12.81 56.11

Energy Development August 29, 2007

Caterpillar G3520 C, Unit #6 Covel Gardens Power Station
ed-07-sanantonio-tx-ecom#3-rpt Page 9 

3.0 SOURCE OPERATION

3.1 PROCESS DESCRIPTION

The units tested were Caterpillar G3520C, Units 1 - 6. The engines are rated at 2,172 horsepower. 

The engines emissions are vented to the atmosphere through an exhaust system extending from the 

engine. The sample ports were located on the exhaust stack. All exhaust samples were continuously 

drawn from the exhaust stack at the sample ports. 

4.0 SAMPLING AND ANALYTICAL PROCEDURES

4.1 TEST METHODS 

The emission tests on the Caterpillar G3520C, Units 1 - 6 at the Covel Gardens Landfill Gas Power 

Station was performed following EPA methods described by the Code of Federal Regulations (CFR), 

Title 40, Part 60, Appendix A and Title 40, Part 63, Appendix A, Conditional Test Method (CTM)-

034. Table 4.1 below outlines the specific methods performed on August 29-30, 2007. 

TABLE 4.1 

SUMMARY OF SAMPLING METHODS

Pollutant or Parameter Sampling 

Method Analysis Method 

Stack Flow Rate EPA Method 2 S-type Pitot Tube 

O2, NOx, CO EPA CTM-034 Electrochemical Cell 

4.2 INSTRUMENT CONFIGURATION AND OPERATIONS FOR GAS ANALYSIS

The sampling and analysis procedures used during these tests conform in principle with the methods 

outlined in the Code of Federal Regulations (CFR), Title 40, Part 60, Appendix A, Methods 2, and 

CFR, Title 40, Part 63, Appendix A, Conditional Test Method (CTM)-034. 

Figure 4.1 depicts the sample system used for the NOx, CO, and O2 tests. A stainless steel probe was 

inserted into the sample port of the stack to extract gas measurements from the emission stream. The 

gas sample was continuously pulled through the probe and transported via heat-traced Teflon® tubing 

to the ECOM-AC portable gas analyzer. 

Gaseous calibration standards were provided in aluminum cylinders with the concentrations certified 

by the vendor. EPA Protocol No. 1 was used to determine the cylinder concentrations where 

applicable (i.e. NOx calibration gases). 
ed-07-sanantonio-tx-ecom#3-rpt Page 10 

Table 4.2 provides a description of the analyzer used for the instrument portion of the tests. All data 

from the continuous monitoring instrument was recorded using the Advanced DAS ECOM Software. 

Data records can be found in Appendix A of this report. 

Three test runs of approximately 10 minutes each were conducted on the engines in the “as found” 

operating condition of the Caterpillar G3520C, Units 1 - 6 for NOx, CO, and O2. 

Exhaust flow rates were measured on Unit 2 at high load during the May 9, 2006 initial compliance 

demonstration. The Unit 2 exhaust flow rate determined in accordance with EPA Method 2 is 

representative of all units and is used to calculate emission rates. 

The stack gas analysis for O2, NOx, and CO concentrations was performed in accordance with the 

procedures set forth in EPA CTM-034. The analyzer uses an electrochemical cell. 

TABLE 4.2 

 ANALYTICAL INSTRUMENTATION 

Parameter Model & 

Manufacturer 

Max. 

Ranges Sensitivity Detection Principle 

O2, NOx, and 

CO 

Telegan, 

Tempest 100 

21%, 

4000 

ppm, 

40,000 

ppm 

0.1 ppm 

or % Electrochemical Cell 

 
E:\SHARED\DRAWINGS\ECOM SCHEMATIC.PPT 04/04/06 DRAWING:06-001 TKG COPYRIGHT 

© 2006 

56

STACK flow

sampleconfiguration

SAMPLE LINE

GAS CONDITIONER

CALIBRATION/DRIFTGAS BOTTLES

calibration/

drift line

O2ANALYZER

COANALYZERNOxANALYZERTHCANALYZERSO2

ANALYZER (optional)

calibrationconfiguration

PROBE

PROBE

ELECTROCHEMICAL CELL
APPENDIX A 

Results and Calculations 
123456

Air Fuel Ratio 26.8 27 26.4 26.7 26.8 27.1

Engine Speed in RPM 1200 1200 1200 1200 1200 1200

Load in KW 1600 1600 1600 1600 1600 1600

Exhaust Temperature 968 966 961 950 958 957

UNIT #

ENGINE OPERATING DATA 8-29-07
App. A 

EMISSION CALCULATIONS 

Mass Emission Rate Calculations

G

CRA Q MW E lb hr S × = × 6 10 ( / )

CRA = corrected raw average 

Qs = stack gas flow rate (Method 19) 

MW = molecular weight (lb/lb-mol) 

G = ideal gas conversion factor 

bhp

E

E g hp hr lb hr 453.6 ( / ) / × ⋅ =

bhp = brake horsepower 

2000 ( / )

Elb / hr hryear E ton yr× =

hryear = hours per year 
Results and Calculations 

Unit 1
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

7.4 121.0 648.0 0.0 114.0 2.5

7.7 99.0 686.0 0.0 114.0 2.5

7.4 86.0 689.0 0.0 114.0 2.5

7.4 78.0 739.0 0.0 115.0 2.5

7.7 69.0 652.0 0.0 115.0 2.5

7.9 68.0 662.0 0.0 115.0 2.5

7.9 70.0 660.0 0.0 115.0 2.5

7.8 69.0 658.0 0.0

1.7% 1.4% 0.9% 0.0%

YES YES YES YES

7.5 70.0 720.0 0.0 115.0 2.5

19.5 51.0 143.0 0.0 115.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

11:15:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

RUN 1

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #1

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

11:07:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

19.5 40.0 56.0 0.0 115.0 2.5

7.5 86.0 628.0 0.0 115.0 2.5

7.7 82.0 685.0 0.0 115.0 2.5

7.8 79.0 665.0 0.0 115.0 2.5

7.9 69.0 649.0 0.0 115.0 2.5

7.9 68.0 655.0 0.0 115.0 2.5

8.0 67.0 652.0 0.0 114.0 2.5

7.9 68.0 652.0 0.0

0.8% 1.5% 0.5% 0.0%

YES YES YES YES

7.9 67.0 652.0 0.0 114.0 2.5

7.8 71.0 678.0 0.0 113.0 2.5

7.8 68.0 675.0 0.0 112.0 2.5

7.8 71.0 700.0 0.0 112.0 2.5

Stop Time: 

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #1

210-623-1314

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

RUN 2

Analyzer Response

t 1

t 2

t 3

11:16:10

8/29/2007

t 4

t 5

t 6

t 7

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

YES YES Sample Flow Rate are within specifications (±10% or as verified)

11:26:10

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

9.5 46.0 109.0 0.0 111.0 2.5

8.1 67.0 632.0 0.0 111.0 2.5

8.0 63.0 637.0 0.0 110.0 2.5

7.9 62.0 639.0 0.0 110.0 2.5

7.8 63.0 667.0 0.0 110.0 2.5

7.8 62.0 674.0 0.0 110.0 2.5

7.8 64.0 676.0 0.0 110.0 2.5

7.8 63.0 672.3 0.0

0.0% 1.6% 0.8% 0.0%

YES YES YES YES

7.9 65.0 691.0 0.0 109.0 2.5

19.8 39.0 76.0 0.0 109.0 2.5

19.8 31.0 42.0 0.0 109.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

11:37:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

RUN 3

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #1

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

11:28:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 
Results and Calculations 

Unit 2 
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

7.6 127.0 720.0 0.0 113.0 2.5

7.9 104.0 762.0 0.0 113.0 2.5

7.5 140.0 766.0 0.0 113.0 2.5

7.6 112.0 821.0 0.0 114.0 2.5

7.9 83.0 724.0 0.0 114.0 2.5

8.1 82.0 735.0 0.0 114.0 2.5

8.1 83.0 733.0 0.0 114.0 2.5

8.0 82.7 730.7 0.0

1.7% 0.8% 0.9% 0.0%

YES YES YES YES

7.7 83.0 800.0 0.0 114.0 2.5

19.9 54.0 159.0 0.0 114.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

10:30:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

RUN 1

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #2

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

10:22:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

19.9 42.0 62.0 0.0 114.0 2.5

7.7 90.0 698.0 0.0 114.0 2.5

7.9 86.0 761.0 0.0 114.0 2.5

8.0 83.0 739.0 0.0 114.0 2.5

8.1 72.0 721.0 0.0 114.0 2.5

8.1 72.0 728.0 0.0 114.0 2.5

8.2 71.0 724.0 0.0 113.0 2.5

8.1 71.7 724.3 0.0

0.8% 0.9% 0.5% 0.0%

YES YES YES YES

8.1 70.0 724.0 0.0 113.0 2.5

8.0 75.0 753.0 0.0 112.0 2.5

8.0 72.0 750.0 0.0 111.0 2.5

8.0 75.0 778.0 0.0 111.0 2.5

Stop Time: 

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #2

210-623-1314

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

RUN 2

Analyzer Response

t 1

t 2

t 3

10:31:10

8/29/2007

t 4

t 5

t 6

t 7

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

YES YES Sample Flow Rate are within specifications (±10% or as verified)

10:41:10

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

9.7 48.0 121.0 0.0 110.0 2.5

8.3 71.0 702.0 0.0 110.0 2.5

8.2 66.0 708.0 0.0 109.0 2.5

8.1 65.0 710.0 0.0 109.0 2.5

8.0 68.0 741.0 0.0 109.0 2.5

8.0 67.0 749.0 0.0 109.0 2.5

8.0 68.0 751.0 0.0 109.0 2.5

8.0 67.7 747.0 0.0

0.0% 1.0% 0.8% 0.0%

YES YES YES YES

8.1 68.0 768.0 0.0 108.0 2.5

20.2 41.0 84.0 0.0 108.0 2.5

20.2 33.0 47.0 0.0 108.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

10:52:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

RUN 3

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #2

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

10:43:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 
Results and Calculations 

Unit 3 
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

7.6 104.0 871.0 0.0 116.0 2.5

7.9 90.0 728.0 0.0 117.0 2.5

8.0 79.0 733.0 0.0 117.0 2.5

7.8 68.0 734.0 0.0 117.0 2.5

7.7 74.0 735.0 0.0 117.0 2.5

7.8 76.0 731.0 0.0 117.0 2.5

7.9 75.0 731.0 0.0 117.0 2.5

7.8 75.0 732.3 0.0

1.3% 1.3% 0.4% 0.0%

YES YES YES YES

7.9 72.0 736.0 0.0 117.0 2.5

7.9 69.0 728.0 0.0 117.0 2.5

7.9 65.0 746.0 0.0 117.0 2.5

7.8 74.0 752.0 0.0 117.0 2.5

Stop Time: 

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

9:35:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #3

RUN 1

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

9:45:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

7.8 75.0 32.0 0.0 117.0 2.5

7.9 78.0 461.0 0.0 117.0 2.5

8.0 69.0 726.0 0.0 117.0 2.5

7.9 65.0 728.0 0.0 117.0 2.5

7.8 69.0 732.0 0.0 117.0 2.5

7.9 71.0 729.0 0.0 118.0 2.5

7.9 69.0 730.0 0.0 118.0 2.5

7.9 69.7 730.3 0.0

0.8% 1.9% 0.2% 0.0%

YES YES YES YES

7.9 67.0 731.0 0.0 118.0 2.5

19.4 57.0 219.0 0.0 118.0 2.5

Stop Time: 

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

9:59:10

Acceptable "Test Data Phase"

t 8

t 9

t 10

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

t 4

t 5

t 6

t 7

Analyzer Response

t 1

t 2

t 3

9:51:10

8/29/2007

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

RUN 2

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #3

210-623-1314
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

19.8 42.0 177.0 0.0 118.0 2.5

7.9 69.0 509.0 0.0 118.0 2.5

7.9 69.0 725.0 0.0 118.0 2.5

7.9 69.0 732.0 0.0 118.0 2.5

7.9 71.0 731.0 0.0 118.0 2.5

7.9 70.0 730.0 0.0 118.0 2.5

7.9 72.0 730.0 0.0 118.0 2.5

7.9 71.0 730.3 0.0

0.0% 1.4% 0.1% 0.0%

YES YES YES YES

7.9 68.0 731.0 0.0 118.0 2.5

17.9 66.0 411.0 0.0 118.0 2.5

19.8 44.0 104.0 0.0 118.0 2.5

Stop Time: 

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

10:00:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #3

RUN 3

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

10:09:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and
Results and Calculations 

Unit 4 
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

21.2 10.0 112.0 0.0 111.0 2.5

21.2 10.0 342.0 0.0 111.0 2.5

21.1 12.0 712.0 0.0 112.0 2.5

8.5 86.0 735.0 0.0 112.0 2.5

8.4 76.0 735.0 0.0 113.0 2.5

8.4 77.0 732.0 0.0 115.0 2.5

8.2 78.0 733.0 0.0 116.0 2.5

8.3 77.0 733.3 0.0

1.6% 1.3% 0.2% 0.0%

YES YES YES YES

8.0 77.0 736.0 0.0 116.0 2.5

7.9 77.0 733.0 0.0 117.0 2.5

7.9 76.0 735.0 0.0 117.0 2.5

7.8 42.0 729.0 0.0 117.0 2.5

Stop Time: 

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

12:27:10

8/30/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #4

RUN 1

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

12:37:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

8.1 56.0 710.0 0.0 115.0 2.5

8.0 69.0 726.0 0.0 115.0 2.5

8.2 76.0 728.0 0.0 116.0 2.5

8.1 77.0 720.0 0.0 116.0 2.5

8.1 77.0 730.0 0.0 118.0 2.5

8.0 78.0 728.0 0.0 118.0 2.5

7.9 78.0 732.0 0.0 119.0 2.5

8.0 77.7 730.0 0.0

1.3% 0.9% 0.3% 0.0%

YES YES YES YES

7.8 54.0 727.0 0.0 120.0 2.5

19.4 41.0 139.0 0.0 120.0 2.5

19.5 29.0 82.0 0.0 120.0 2.5

Stop Time: 

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

12:50:10

Acceptable "Test Data Phase"

t 8

t 9

t 10

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

t 4

t 5

t 6

t 7

Analyzer Response

t 1

t 2

t 3

12:41:10

8/30/2007

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

RUN 2

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #4

210-623-1314
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

8.0 47.0 722.0 0.0 120.0 2.5

8.0 61.0 729.0 0.0 121.0 2.5

8.1 76.0 724.0 0.0 121.0 2.5

7.9 76.0 733.0 0.0 121.0 2.5

7.9 78.0 734.0 0.0 121.0 2.5

7.7 77.0 735.0 0.0 121.0 2.5

7.7 78.0 733.0 0.0 122.0 2.5

7.8 77.7 734.0 0.0

1.7% 0.9% 0.1% 0.0%

YES YES YES YES

7.7 77.0 735.0 0.0 122.0 2.5

19.3 58.0 115.0 0.0 122.0 2.5

19.4 32.0 79.0 0.0 122.0 2.5

Stop Time: 

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

12:51:10

8/30/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #4

RUN 3

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

13:00:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and
Results and Calculations 

Unit 5 
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

8.0 71.0 724.0 0.0 105.0 2.5

8.0 72.0 726.0 0.0 105.0 2.5

8.0 78.0 726.0 0.0 105.0 2.5

8.0 72.0 726.0 0.0 106.0 2.5

7.9 77.0 724.0 0.0 107.0 2.5

7.9 77.0 725.0 0.0 107.0 2.5

7.9 76.0 727.0 0.0 108.0 2.5

7.9 76.7 725.3 0.0

0.0% 0.9% 0.2% 0.0%

YES YES YES YES

7.8 76.0 725.0 0.0 109.0 2.5

7.9 75.0 725.0 0.0 109.0 2.5

7.9 75.0 726.0 0.0 109.0 2.5

7.8 72.0 727.0 0.0 110.0 2.5

Stop Time: 

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

8:22:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #5

RUN 1

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

8:32:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

20.1 25.0 34.0 0.0 110.0 2.5

8.0 70.0 721.0 0.0 110.0 2.5

7.9 66.0 724.0 0.0 110.0 2.5

7.9 66.0 727.0 0.0 111.0 2.5

7.9 69.0 726.0 0.0 111.0 2.5

7.9 68.0 725.0 0.0 111.0 2.5

7.9 69.0 726.0 0.0 111.0 2.5

7.9 68.7 725.7 0.0

0.0% 1.0% 0.1% 0.0%

YES YES YES YES

7.8 68.0 727.0 0.0 111.0 2.5

7.8 69.0 729.0 0.0 112.0 2.5

7.9 70.0 730.0 0.0 112.0 2.5

19.8 42.0 322.0 0.0 112.0 2.5

Stop Time: 

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

8:45:10

Acceptable "Test Data Phase"

t 8

t 9

t 10

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

t 4

t 5

t 6

t 7

Analyzer Response

t 1

t 2

t 3

8:35:10

8/29/2007

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

RUN 2

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #5

210-623-1314
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

20.0 26.0 19.0 0.0 112.0 2.5

8.2 49.0 207.0 0.0 112.0 2.5

7.9 75.0 720.0 0.0 112.0 2.5

7.8 75.0 724.0 0.0 112.0 2.5

7.9 77.0 726.0 0.0 112.0 2.5

7.9 76.0 727.0 0.0 112.0 2.5

7.8 77.0 730.0 0.0 112.0 2.5

7.9 76.7 727.7 0.0

0.8% 0.9% 0.3% 0.0%

YES YES YES YES

7.8 79.0 731.0 0.0 113.0 2.5

7.9 75.0 732.0 0.0 113.0 2.5

7.8 75.0 730.0 0.0 113.0 2.5

7.8 77.0 731.0 0.0 113.0 2.5

Stop Time: 

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

8:49:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #5

RUN 3

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

8:59:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and
Results and Calculations 

Unit 6 
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

8.0 140.0 995.0 0.0 100.0 2.5

8.5 60.0 723.0 0.0 102.0 2.5

8.5 55.0 709.0 0.0 103.0 2.5

8.4 54.0 708.0 0.0 104.0 2.5

8.3 59.0 726.0 0.0 104.0 2.5

8.3 58.0 724.0 0.0 105.0 2.5

8.3 57.0 726.0 0.0 105.0 2.5

8.3 58.0 725.3 0.0

0.0% 1.7% 0.2% 0.0%

YES YES YES YES

8.3 56.0 726.0 0.0 106.0 2.5

8.3 55.0 724.0 0.0 106.0 2.5

8.3 55.0 725.0 0.0 107.0 2.5

8.3 53.0 718.0 0.0 107.0 2.5

Stop Time: 

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

7:33:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #6

RUN 1

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

7:43:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

19.8 11.0 351.0 0.0 107.0 2.5

20.1 14.0 95.0 0.0 108.0 2.5

8.6 32.0 328.0 0.0 108.0 2.5

8.3 45.0 674.0 0.0 108.0 2.5

8.3 49.0 684.0 0.0 108.0 2.5

8.2 49.0 692.0 0.0 109.0 2.5

8.3 50.0 695.0 0.0 109.0 2.5

8.3 49.3 690.3 0.0

0.8% 1.4% 0.9% 0.0%

YES YES YES YES

8.2 49.0 701.0 0.0 109.0 2.5

8.3 28.0 697.0 0.0 109.0 2.5

8.2 37.0 704.0 0.0 109.0 2.5

19.8 22.0 309.0 0.0 109.0 2.5

Stop Time: 

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

7:55:10

Acceptable "Test Data Phase"

t 8

t 9

t 10

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

t 4

t 5

t 6

t 7

Analyzer Response

t 1

t 2

t 3

7:45:10

8/29/2007

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

RUN 2

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #6

210-623-1314
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 20.9 886 138 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

20.1 20.0 52.0 0.0 110.0 2.5

8.3 45.0 651.0 0.0 110.0 2.5

8.3 43.0 680.0 0.0 110.0 2.5

8.5 34.0 652.0 0.0 110.0 2.5

8.2 52.0 709.0 0.0 110.0 2.5

8.3 53.0 697.0 0.0 110.0 2.5

8.3 51.0 692.0 0.0 110.0 2.5

8.3 52.0 699.3 0.0

0.8% 1.9% 1.4% 0.0%

YES YES YES YES

8.3 51.0 708.0 0.0 110.0 2.5

8.2 53.0 708.0 0.0 110.0 2.5

8.3 51.0 698.0 0.0 110.0 2.5

8.0 71.0 789.0 0.0 110.0 2.5

Stop Time: 

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

7:58:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: UNIT #6

RUN 3

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

8:08:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and
APPENDIX B 

Quality Assurance Activities 
App. B 

QUALITY ASSURANCE PROGRAM SUMMARY 

Air Hygiene ensures the quality and validity of its emission measurement and reporting procedures through a rigorous quality 

assurance (QA) program. The program is developed and administered by an internal QA team and encompasses five major 

areas: 

1. QA reviews of reports, laboratory work, and field-testing 

2. Equipment calibration and maintenance 

3. Chain-of-custody 

4. Training 

5. Knowledge of current test methods 

Each of these areas is discussed individually below. 

QA Reviews 

Air Hygiene’s review procedure includes review of each source test report, along with laboratory and fieldwork, by the QA 

Team. The most important review is the one that takes place before a test program begins. The QA Team works closely with 

technical division personnel to prepare and review test protocols. Test protocol review includes selection of appropriate test

procedures, evaluation of interferences or other restrictions that might preclude use of standard test procedures, and evaluation 

and/or development of alternate procedures. 

Equipment Calibration and Maintenance 

The equipment used to conduct the emission measurements is maintained according to the manufacturer’s instructions to ensure 

proper operation. In addition to the maintenance program, calibrations are carried out on each measurement device according to

the schedule outlined by the Environmental Protection Agency. Quality control checks are also conducted in the field for each 

test program. 

Chain-of-Custody 

Air Hygiene maintains full chain-of-custody documentation on all samples and data sheets. In addition to normal documentation 

of changes between field sample custodians, laboratory personnel, and field test personnel, Air Hygiene documents every 

individual who handles any test component in the field (e.g., probe wash, impinger loading and recovery, filter loading and 

recovery, etc.). Samples are stored in a locked area to which only Air Hygiene personnel have access. Field data sheets are 

secured at Air Hygiene’s offices upon return from the field. 

Training 

Personnel’s training is essential to ensure quality testing. Air Hygiene has formal and informal training programs, which 

include: 

1. Attendance at EPA-sponsored training courses 

2. Enrollment in EPA correspondence courses 

3 A requirement for all technicians to read and understand Air Hygiene’s QA manual 

4. In-house training and QA meetings on a regular basis 

5. Maintenance of training records 

Knowledge of Current Test Methods 

With the constant updating of standard test methods and the wide variety of emerging test procedures, it is essential that any 

qualified source tester keep abreast of new developments. Air Hygiene subscribes to services, which provide updates on EPA 

reference methods, rules, and regulations. Additionally, source test personnel regularly attend and present papers at testing and 

emission-related seminars and conferences. Air Hygiene personnel maintain membership in the Air and Waste Management 

Association and the American Industrial Hygiene Association. 
App. B 

COMBUSTION TESTING QUALITY ASSURANCE ACTIVITIES 

A number of quality assurance activities were undertaken before, during, and after this testing project. This section of the report 

combined with the documentation in Appendix B and C describe each of those activities. 

Each instrument’s response was checked and adjusted in the field prior to the collection of data via multi-point calibration. The 

instrument’s linearity was checked by adjusting its zero and span responses to ambient air and an upscale calibration gas in the 

range of the expected concentrations. The instrument response was then challenged with other calibration gases of known 

concentration and accepted as being linear if the response of the other calibration gases agreed within plus or minus two percent 

of the range of predicted values. 

At the end of the test day, the analyzers were checked for zero and span drift. This allowed each test run to be bracketed by 

calibrations and documents the precision of the data just collected. The criterion for acceptable data is that the instrument drift is 

no more than three of the full-scale response. These worksheets (as prepared from the data records of Appendix B) show that no

drifts in excess of three percent occurred in the zero to span checks following each test run / period. 

The sampling systems were leak checked by demonstrating the zero flow was detected in the instrument rotameter. A leak test 

was conducted after the sample system was set up and before the system was dismantled. This test was conducted to ensure that 

ambient air had not diluted the sample. Any leakage detected prior to the tests would be repaired and another leak check 

conducted before testing commenced. No leaks were found during the pre or post-test leak checks. 

The control gases used to calibrate the instruments were analyzed and certified by the compressed gas vendors to plus or minus 

one percent accuracy for all gases. EPA Protocol No. 1 was used, where applicable to assign the concentration values traceable

to the National Institute of Standards and Technology (NIST), Standard Reference Materials (SRM’s). The gas calibration 

sheets as prepared by the vendor are contained in Appendix C. 

Air Hygiene collected and reported the enclosed test data in accordance with the procedures and quality assurance activities 

described in this test report. Air Hygiene makes no warranty as to the suitability of the test methods. Air Hygiene also assumes 

no liability relating to the interpretation and use of the test data. 

INSTRUMENTAL ANALYSIS 

 QUALITY ASSURANCE DATA

Date: August 29-30, 2007 

Company: Energy Developments 

Location: San Antonio, Texas 

Techs: JMP 

Sample System Leak Check 

Date Sample System Leak Rate 

(l/min) 

August 29-30, 

2007 1 0 
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 886

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

20.9 0.0 0.0 0.0 91.0 2.5

20.9 0.0 0.0 0.0 91.0 2.5

20.9 0.0 0.0 0.0 91.0 2.5

0.1 1.0 849.0 0.0 90.0 2.5

0.1 2.0 887.0 0.0 90.0 2.5

0.1 3.0 888.0 0.0 90.0 2.5

0.1 4.0 890.0 0.0 90.0 2.5

0.1 3.0 888.3 0.0

0.0% 33.3% 0.2% 0.0%

N/A N/A YES N/A

0.1 4.0 898.0 0.0 90.0 2.5

20.8 3.0 104.0 0.0 91.0 2.5

0.5 102.0 115.0 0.0 91.0 2.5

0.1 126.0 154.0 0.0 91.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

6:45:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

Pre-Cal (CO)

Analyzer Response

t 1

Mean Average Concentration

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: PRE-CAL

210-623-1314

Calibration Gas Verification Information

TELEGAN

6:34:09

8/29/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

t 6

t 7
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 138

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.1 4.0 898.0 0.0 90.0 2.5

20.8 3.0 104.0 0.0 91.0 2.5

0.5 102.0 115.0 0.0 91.0 2.5

0.1 126.0 154.0 0.0 91.0 2.5

0.0 137.0 134.0 0.0 92.0 2.5

0.0 137.0 133.0 0.0 92.0 2.5

0.0 138.0 128.0 0.0 91.0 2.5

0.0 137.3 131.7 0.0

0.0% 0.5% 2.8% 0.0%

N/A YES N/A N/A

0.0 137.0 125.0 0.0 91.0 2.5

0.0 138.0 122.0 0.0 91.0 2.5

0.0 141.0 118.0 0.0 91.0 2.5

0.1 29.0 19.0 15.0 91.0 2.5

Stop Time: 

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: PRE-CAL

210-623-1314

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Pre-Cal Test (NO)

Analyzer Response

t 1

t 2

t 3

6:42:10

8/29/2007

t 4

t 5

t 6

t 7

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

YES YES Sample Flow Rate are within specifications (±10% or as verified)

6:54:10

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.1 65.0 7.0 62.0 91.0 2.5

0.1 74.0 7.0 72.0 91.0 2.5

0.1 78.0 5.0 77.0 90.0 2.5

0.1 56.0 0.0 54.0 90.0 2.5

0.1 49.0 0.0 47.0 90.0 2.5

0.0 48.0 0.0 46.0 91.0 2.5

0.0 48.0 0.0 46.0 91.0 2.5

0.0 48.3 0.0 46.3

200.0% 1.4% 0.0% 1.4%

N/A N/A N/A YES

0.0 48.0 0.0 47.0 92.0 2.5

0.0 41.0 0.0 38.0 92.0 2.5

0.0 14.0 0.0 12.0 92.0 2.5

0.4 2.0 400.0 0.0 92.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

7:13:47

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

Pre-Cal (NO2)

Analyzer Response

t 1

Mean Average Concentration

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: PRE-CAL

210-623-1314

Calibration Gas Verification Information

TELEGAN

6:55:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

t 6

t 7
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.0 2.0 36.0 0.0 113.0 2.5

0.0 7.0 0.0 0.0 112.0 2.5

0.0 13.0 0.0 2.0 112.0 2.5

0.0 52.0 0.0 49.0 111.0 2.5

0.0 51.0 0.0 48.0 111.0 2.5

0.0 50.0 0.0 47.0 110.0 2.5

0.0 51.0 0.0 48.0 110.0 2.5

0.0 50.7 0.0 47.7

0.0% 1.3% 0.0% 1.4%

N/A N/A N/A YES

0.0 51.0 0.0 48.0 110.0 2.5

20.7 35.0 0.0 31.0 110.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

11:58:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

Post-Cal (NO2)

Analyzer Response

t 1

Mean Average Concentration

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: POST-CAL

210-623-1314

Calibration Gas Verification Information

TELEGAN

11:50:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

t 6

t 7
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 886

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

20.6 16.0 0.0 12.0 110.0 2.5

0.2 49.0 59.0 2.0 110.0 2.5

0.6 53.0 345.0 4.0 110.0 2.5

0.1 21.0 812.0 5.0 110.0 2.5

0.1 6.0 890.0 2.0 110.0 2.5

0.0 1.0 891.0 0.0 110.0 2.5

0.0 1.0 890.0 0.0 110.0 2.5

0.0 2.7 890.3 0.7

200.0% 125.0% 0.1% 200.0%

N/A N/A YES N/A

0.0 1.0 889.0 0.0 110.0 2.5

0.0 1.0 891.0 0.0 110.0 2.5

0.0 2.0 890.0 0.0 110.0 2.5

0.0 3.0 889.0 0.0 110.0 2.5

Stop Time: 

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: POST-CAL

210-623-1314

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Post-Cal (CO)

Analyzer Response

t 1

t 2

t 3

11:59:10

8/29/2007

t 4

t 5

t 6

t 7

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

YES YES Sample Flow Rate are within specifications (±10% or as verified)

12:09:10

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 138

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.6 137.0 0.0 0.0 110.0 2.5

0.0 134.0 0.0 0.0 109.0 2.5

0.0 137.0 0.0 0.0 109.0 2.5

0.0 136.0 0.0 0.0 109.0 2.5

0.0 135.0 0.0 0.0 109.0 2.5

0.1 136.0 0.0 0.0 109.0 2.5

0.2 137.0 0.0 0.0 109.0 2.5

0.1 136.0 0.0 0.0

100.0% 0.7% 0.0% 0.0%

N/A YES N/A N/A

0.0 138.0 0.0 0.0 110.0 2.5

0.0 137.0 0.0 0.0 110.0 2.5

0.0 134.0 0.0 0.0 110.0 2.5

0.0 134.0 0.0 0.0 110.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

12:24:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

Post-Cal (NO)

Analyzer Response

t 1

Mean Average Concentration

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: POST-CAL

210-623-1314

Calibration Gas Verification Information

TELEGAN

12:14:10

8/29/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

t 6

t 7
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

21.1 2.0 0.0 0.0 90.0 2.5

21.2 7.0 0.0 4.0 90.0 2.5

0.0 48.0 0.0 45.0 90.0 2.5

0.0 53.0 0.0 48.0 90.0 2.5

0.0 53.0 0.0 48.0 90.0 2.5

0.0 54.0 0.0 48.0 89.0 2.5

0.0 53.0 0.0 48.0 89.0 2.5

0.0 53.3 0.0 48.0

0.0% 1.3% 0.0% 0.0%

N/A N/A N/A YES

0.0 53.0 0.0 50.0 89.0 2.5

0.0 57.0 0.0 54.0 89.0 2.5

21.3 7.0 0.0 4.0 88.0 2.5

20.9 5.0 0.0 3.0 88.0 2.5

Stop Time: 

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

9:06:58

8/30/2007

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: PRE-CAL

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Pre-Cal (NO2)

Analyzer Response

t 1

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

YES YES Sample Flow Rate are within specifications (±10% or as verified)

9:15:10

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 138

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

21.0 6.0 0.0 0.0 88.0 2.5

0.1 131.0 94.0 0.0 88.0 2.5

0.0 134.0 98.0 0.0 88.0 2.5

0.0 138.0 101.0 0.0 88.0 2.5

0.0 139.0 102.0 0.0 88.0 2.5

0.0 139.0 103.0 0.0 88.0 2.5

0.0 140.0 103.0 0.0 88.0 2.5

0.0 139.3 102.7 0.0

0.0% 0.5% 0.6% 0.0%

N/A YES N/A N/A

0.1 143.0 104.0 0.0 88.0 2.5

0.1 141.0 103.0 0.0 88.0 2.5

0.1 141.0 103.0 0.0 88.0 2.5

20.9 15.0 6.0 0.0 88.0 2.5

Stop Time: 

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

YES YES Sample Flow Rate are within specifications (±10% or as verified)

9:27:10

t 13

t 14

Acceptable "Test Data Phase"

t 8

t 9

t 10

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

t 4

t 5

t 6

t 7

Analyzer Response

t 1

t 2

t 3

9:17:10

8/30/2007

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Pre-Cal Test (NO)

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: PRE-CAL

210-623-1314
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 886

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.1 14.0 835.0 0.0 89.0 2.5

0.1 14.0 855.0 0.0 90.0 2.5

0.1 18.0 866.0 0.0 91.0 2.5

0.1 15.0 886.0 0.0 91.0 2.5

0.1 15.0 887.0 0.0 92.0 2.5

0.1 15.0 886.0 0.0 92.0 2.5

0.1 19.0 888.0 0.0 93.0 2.5

0.1 16.3 887.0 0.0

0.0% 16.3% 0.1% 0.0%

N/A N/A YES N/A

0.0 16.0 885.0 0.0 93.0 2.5

0.0 17.0 880.0 0.0 93.0 2.5

0.0 18.0 704.0 0.0 93.0 2.5

20.9 22.0 127.0 0.0 93.0 2.5

Stop Time: 

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

9:31:10

8/30/2007

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: PRE-CAL

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Pre-Cal (CO)

Analyzer Response

t 1

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

YES YES Sample Flow Rate are within specifications (±10% or as verified)

9:41:10

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 886

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.6 56.0 389.0 7.0 121.0 2.5

0.1 57.0 799.0 6.0 121.0 2.5

0.1 56.0 889.0 4.0 121.0 2.5

0.0 2.0 902.0 0.0 120.0 2.5

0.0 2.0 891.0 0.0 120.0 2.5

0.0 2.0 892.0 0.0 120.0 2.5

0.0 2.0 893.0 0.0 120.0 2.5

0.0 2.0 892.0 0.0

0.0% 0.0% 0.1% 0.0%

N/A N/A YES N/A

0.0 3.0 892.0 0.0 120.0 2.5

0.0 4.0 891.0 0.0 120.0 2.5

0.0 6.0 889.0 0.0 120.0 2.5

19.5 5.0 137.0 0.0 119.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

13:13:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

Post-Cal (CO)

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: POST-CAL

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

13:03:11

8/30/2007

Analyzer make & model:

Calibration Gas Info. 
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.0 6.0 53.0 0.0 117.0 2.5

0.0 10.0 0.0 0.0 116.0 2.5

0.0 9.0 0.0 1.0 116.0 2.5

0.0 54.0 0.0 50.0 115.0 2.5

0.0 52.0 0.0 49.0 115.0 2.5

0.0 52.0 0.0 49.0 114.0 2.5

0.0 53.0 0.0 50.0 114.0 2.5

0.0 52.3 0.0 49.3

0.0% 1.3% 0.0% 1.4%

N/A N/A N/A YES

0.0 52.0 0.0 49.0 114.0 2.5

20.3 25.0 0.0 22.0 114.0 2.5

20.4 11.0 0.0 11.0 114.0 2.5

0.2 124.0 45.0 4.0 114.0 2.5

Stop Time: 

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: POST-CAL

210-623-1314

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Post-Cal (NO2)

Analyzer Response

t 1

t 2

t 3

13:16:10

8/30/2007

t 4

t 5

t 6

t 7

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

YES YES Sample Flow Rate are within specifications (±10% or as verified)

13:26:10

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 138

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.1 138.0 58.0 1.0 114.0 2.5

0.0 138.0 59.0 0.0 114.0 2.5

0.0 138.0 59.0 0.0 113.0 2.5

0.0 138.0 61.0 0.0 113.0 2.5

0.0 138.0 60.0 0.0 113.0 2.5

0.0 138.0 59.0 0.0 113.0 2.5

0.1 138.0 60.0 0.0 113.0 2.5

0.0 138.0 59.7 0.0

200.0% 0.0% 1.1% 0.0%

N/A YES N/A N/A

0.1 138.0 62.0 0.0 113.0 2.5

20.3 0.0 0.0 0.0 113.0 2.5

20.8 0.0 0.0 0.0 113.0 2.5

20.9 0.0 0.0 0.0 113.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

13:37:09

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

Post-Cal (NO)

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: POST-CAL

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

13:27:12

8/30/2007

Analyzer make & model:

Calibration Gas Info. 
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 886

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.1 0.9 821.0 0.0 92.0 2.5

0.0 0.2 849.0 0.0 92.0 2.5

0.0 0.2 873.0 0.0 93.0 2.5

0.0 0.2 888.0 0.0 93.0 2.5

0.0 0.2 888.0 0.0 93.0 2.5

0.0 0.2 887.0 0.0 93.0 2.5

0.0 0.2 887.0 0.0 93.0 2.5

0.0 0.2 887.3 0.0

0.0% 0.0% 0.1% 0.0%

N/A N/A YES N/A

0.0 0.2 887.0 0.0 93.0 2.5

0.0 0.2 871.0 0.0 93.0 2.5

0.0 0.2 732.0 0.0 93.0 2.5

20.9 0.5 158.0 0.0 93.0 2.5

Stop Time: 

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

18:11:10

8/30/2007

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: CO #1

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Repeatability (CO)

Analyzer Response

t 1

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

YES YES Sample Flow Rate are within specifications (±10% or as verified)

18:21:10

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 886

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.0 0.1 799.0 0.0 93.0 2.5

0.0 0.1 837.0 0.0 93.0 2.5

0.0 0.2 881.0 0.0 93.0 2.5

0.0 0.2 887.0 0.0 93.0 2.5

0.0 0.2 886.0 0.0 93.0 2.5

0.0 0.2 888.0 0.0 93.0 2.5

0.0 0.2 887.0 0.0 93.0 2.5

0.0 0.2 887.0 0.0

0.0% 0.0% 0.1% 0.0%

N/A N/A YES N/A

0.0 0.2 887.0 0.0 93.0 2.5

0.0 0.2 868.0 0.0 93.0 2.5

18.3 0.8 645.0 0.0 93.0 2.5

20.9 0.4 98.0 0.0 93.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

18:34:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

Repeatability (CO)

Analyzer Response

t 1

Mean Average Concentration

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: CO #2

210-623-1314

Calibration Gas Verification Information

TELEGAN

18:24:10

8/30/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

t 6

t 7
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 886

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.1 0.3 840.0 0.0 93.0 2.5

0.0 0.1 873.0 0.0 93.0 2.5

0.0 0.2 889.0 0.0 93.0 2.5

0.0 0.2 888.0 0.0 93.0 2.5

0.0 0.2 888.0 0.0 93.0 2.5

0.0 0.1 888.0 0.0 93.0 2.5

0.0 0.2 887.0 0.0 93.0 2.5

0.0 0.2 887.7 0.0

0.0% 40.0% 0.1% 0.0%

N/A N/A YES N/A

0.0 0.2 888.0 0.0 93.0 2.5

0.0 0.2 886.0 0.0 92.0 2.5

0.0 0.2 802.0 0.0 92.0 2.5

20.4 0.2 138.0 0.0 93.0 2.5

Stop Time: 

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

18:36:10

8/30/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: CO #3

Repeatability (CO)

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

18:46:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 886

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.1 0.1 561.0 0.0 93.0 2.5

0.0 0.1 783.0 0.0 93.0 2.5

0.0 0.2 871.0 0.0 92.0 2.5

0.0 0.2 890.0 0.0 92.0 2.5

0.0 0.2 889.0 0.0 92.0 2.5

0.0 0.2 889.0 0.0 92.0 2.5

0.0 0.2 887.0 0.0 93.0 2.5

0.0 0.2 888.3 0.0

0.0% 0.0% 0.2% 0.0%

N/A N/A YES N/A

0.0 0.2 888.0 0.0 93.0 2.5

0.0 0.1 827.0 0.0 93.0 2.5

18.9 0.2 687.0 0.0 93.0 2.5

20.8 0.6 122.0 0.0 93.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

19:00:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

Repeatability (CO)

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: CO #4

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

18:50:10

8/30/2007

Analyzer make & model:

Calibration Gas Info. 
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 138

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

21.0 3.0 0.0 0.0 92.0 2.5

0.5 127.0 98.0 0.0 92.0 2.5

0.0 137.0 103.0 0.0 92.0 2.5

0.0 138.0 109.0 0.0 92.0 2.5

0.0 138.0 109.0 0.0 92.0 2.5

0.0 138.0 108.0 0.0 92.0 2.5

0.0 139.0 109.0 0.0 92.0 2.5

0.0 138.3 108.7 0.0

0.0% 0.5% 0.6% 0.0%

N/A YES N/A N/A

0.0 139.0 110.0 0.0 92.0 2.5

0.0 138.0 109.0 0.0 92.0 2.5

0.2 138.0 109.0 0.0 92.0 2.5

20.9 11.0 22.0 0.0 92.0 2.5

Stop Time: 

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

YES YES Sample Flow Rate are within specifications (±10% or as verified)

19:14:10

t 13

t 14

Acceptable "Test Data Phase"

t 8

t 9

t 10

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

t 4

t 5

t 6

t 7

Analyzer Response

t 1

t 2

t 3

19:04:10

8/30/2007

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Repeatability (NO)

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: NO #1

210-623-1314
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 138

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

19.9 37.0 1.0 0.0 92.0 2.5

0.0 124.0 67.0 0.0 92.0 2.5

0.0 138.0 109.0 0.0 92.0 2.5

0.0 138.0 108.0 0.0 91.0 2.5

0.0 138.0 109.0 0.0 92.0 2.5

0.0 138.0 109.0 0.0 92.0 2.5

0.0 138.0 110.0 0.0 92.0 2.5

0.0 138.0 109.3 0.0

0.0% 0.0% 0.6% 0.0%

N/A YES N/A N/A

0.0 138.0 111.0 0.0 91.0 2.5

0.0 139.0 110.0 0.0 92.0 2.5

0.4 131.0 110.0 0.0 92.0 2.5

20.4 22.0 72.0 0.0 90.0 2.5

Stop Time: 

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: NO #2

210-623-1314

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Repeatability (NO)

Analyzer Response

t 1

t 2

t 3

19:17:10

8/30/2007

t 4

t 5

t 6

t 7

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

YES YES Sample Flow Rate are within specifications (±10% or as verified)

19:27:10

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 138

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

20.8 3.0 5.0 0.0 91.0 2.5

0.0 129.0 101.0 0.0 92.0 2.5

0.0 139.0 108.0 0.0 91.0 2.5

0.0 139.0 108.0 0.0 91.0 2.5

0.1 138.0 109.0 0.0 91.0 2.5

0.0 138.0 109.0 0.0 91.0 2.5

0.0 138.0 109.0 0.0 90.0 2.5

0.0 138.0 109.0 0.0

200.0% 0.0% 0.0% 0.0%

N/A YES N/A N/A

0.0 137.0 108.0 0.0 90.0 2.5

0.1 138.0 107.0 0.0 91.0 2.5

0.0 118.0 103.0 0.0 90.0 2.5

21.0 52.0 33.0 0.0 90.0 2.5

Stop Time: 

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

19:40:10

Acceptable "Test Data Phase"

t 8

t 9

t 10

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

t 4

t 5

t 6

t 7

Analyzer Response

t 1

t 2

t 3

19:30:10

8/30/2007

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Repeatability (NO)

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: NO #3

210-623-1314
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 138

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

20.8 0.0 0.0 0.0 90.0 2.5

0.3 76.0 83.0 0.0 90.0 2.5

0.1 119.0 97.0 0.0 90.0 2.5

0.0 132.0 105.0 0.0 90.0 2.5

0.0 138.0 107.0 0.0 90.0 2.5

0.0 139.0 108.0 0.0 91.0 2.5

0.0 138.0 108.0 0.0 90.0 2.5

0.0 138.3 107.7 0.0

0.0% 0.5% 0.6% 0.0%

N/A YES N/A N/A

0.1 138.0 108.0 0.0 90.0 2.5

0.0 137.0 108.0 0.0 90.0 2.5

0.0 130.0 108.0 0.0 90.0 2.5

20.3 71.0 42.0 0.0 89.0 2.5

Stop Time: 

TEST DATA 

PHASE

RAMP-UP 

PHASE

RE-FRESH 

PHASE

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: NO #4

210-623-1314

Calibration Gas Verification Information

Analyzer make & model: TELEGAN

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Repeatability (NO)

Analyzer Response

t 1

t 2

t 3

19:42:10

8/30/2007

t 4

t 5

t 6

t 7

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

YES YES Sample Flow Rate are within specifications (±10% or as verified)

19:52:10

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

20.8 0.0 0.0 0.0 90.0 2.5

20.8 6.0 0.0 4.0 90.0 2.5

0.0 47.0 0.0 42.0 90.0 2.5

0.0 53.0 0.0 49.0 90.0 2.5

0.0 53.0 0.0 49.0 90.0 2.5

0.0 53.0 0.0 49.0 89.0 2.5

0.0 53.0 0.0 49.0 89.0 2.5

0.0 53.0 0.0 49.0

0.0% 0.0% 0.0% 0.0%

N/A N/A N/A YES

0.0 52.0 0.0 49.0 89.0 2.5

0.0 52.0 0.0 48.0 89.0 2.5

21.0 31.0 0.0 26.0 88.0 2.5

20.9 6.0 0.0 2.0 88.0 2.5

Stop Time: 

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

19:57:10

8/30/2007

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: NO2 #1

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Repeatability (NO2)

Analyzer Response

t 1

Mean Average Concentration

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

YES YES Sample Flow Rate are within specifications (±10% or as verified)

20:07:10

t 15

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 11

t 12

t 13

t 14
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

20.9 6.0 0.0 3.0 88.0 2.5

0.0 29.0 0.0 25.0 89.0 2.5

0.0 47.0 0.0 42.0 89.0 2.5

0.0 52.0 0.0 48.0 90.0 2.5

0.1 53.0 0.0 48.0 90.0 2.5

0.0 52.0 0.0 49.0 90.0 2.5

0.0 52.0 0.0 48.0 90.0 2.5

0.0 52.3 0.0 48.3

200.0% 1.3% 0.0% 1.4%

N/A N/A N/A YES

0.0 53.0 0.0 49.0 89.0 2.5

0.0 51.0 0.0 47.0 90.0 2.5

17.8 11.0 0.0 7.0 90.0 2.5

20.8 1.0 0.0 0.0 90.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

20:20:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

Repeatability (NO2)

Analyzer Response

t 1

Mean Average Concentration

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: NO2 #2

210-623-1314

Calibration Gas Verification Information

TELEGAN

20:10:10

8/30/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

t 6

t 7
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

0.0 51.0 0.0 45.0 90.0 2.5

0.0 54.0 0.0 49.0 90.0 2.5

0.0 53.0 0.0 48.0 91.0 2.5

0.0 53.0 0.0 48.0 90.0 2.5

0.0 53.0 0.0 49.0 90.0 2.5

0.0 52.0 0.0 48.0 89.0 2.5

0.0 53.0 0.0 48.0 89.0 2.5

0.0 52.7 0.0 48.3

0.0% 1.3% 0.0% 1.4%

N/A N/A N/A YES

0.0 54.0 0.0 48.0 88.0 2.5

0.0 52.0 0.0 49.0 89.0 2.5

19.7 23.0 0.0 17.0 89.0 2.5

20.9 3.0 0.0 0.0 90.0 2.5

Stop Time: 

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

20:23:10

8/30/2007

Analyzer make & model:

Calibration Gas Info. 

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: NO2 #3

Repeatability (NO2)

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

YES YES Sample Flow Rate are within specifications (±10% or as verified)

20:33:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and
Facility

Phone

Serial: # 02711

Gas type O2% CO ppm NO ppm NO2 ppm

Concent. 48.3

Date: Cell Temp Flow Rate

Start Time: O2% NOx ppm CO ppm NO2 ppm

20.9 0.0 0.0 0.0 89.0 2.5

21.0 0.0 0.0 0.0 89.0 2.5

2.0 21.0 0.0 17.0 89.0 2.5

0.0 52.0 0.0 46.0 89.0 2.5

0.0 53.0 0.0 48.0 89.0 2.5

0.0 53.0 0.0 48.0 90.0 2.5

0.0 53.0 0.0 48.0 90.0 2.5

0.0 53.0 0.0 48.0

0.0% 0.0% 0.0% 0.0%

N/A N/A N/A YES

0.0 53.0 0.0 48.0 89.0 2.5

0.0 52.0 0.0 46.0 88.0 2.5

21.3 16.0 0.0 12.0 89.0 2.5

20.9 1.0 0.0 0.0 89.0 2.5

Stop Time: 

YES YES Sample Flow Rate are within specifications (±10% or as verified)

20:48:10

Cell Temperature (±10F for each run, Not to exceed 20F for test day) and

t 8

t 9

t 10

RE-FRESH 

PHASE

t 15

t 11

t 12

t 13

t 14

(sum of t5:15 through t7:00/8)

Maximum Deviation (no single reading

exceeds ±2% of mean average) 

Acceptable "Test Data Phase"

Repeatability (NO2)

Analyzer Response

t 1

Mean Average Concentration

TEST DATA 

PHASE

RAMP-UP 

PHASE

t 2

t 3

t 4

t 5

(manufacturer,expiration,etc)

MEASUREMENT CYCLE (circle measurement task below)

Covel Gardens Power Station

Address 8611 Covel Road

San Antonio, Texas 78252

Emission Point: NO2 #4

t 6

t 7

210-623-1314

Calibration Gas Verification Information

TELEGAN

20:38:10

8/30/2007

Analyzer make & model:

Calibration Gas Info. 
APPENDIX C 

Calibration Gas Certifications 


CC113410 (886).max