**Facility State** **Major HAP**  **Source? CISWI or** 

**Possible CISWI?** **Boiler/ Unit**

**Type SO2** 

**(ppmdv @7%O2)** **Dioxins/Furans**

**(ng total/dscm @7%O2)**  **Dioxins/Furans**

**(ng TEQ/dscm @7%O2)**  **Cd**

**(ug/dscm @7%O2)** **Pb (ug/dscm**

**@7%O2) Hg (ug/dscm** 

**@7%O2) HCl** 

**(ppmdv @7%O2)**  All No Limit No Limit No Limit No Limit 5.3 27 Stoker 0.005 FBC 0.02 Fuel Cell 4 Hybrid Susp/Grate 0.2 All 6.2 0.35 0.059 0.51 3.6 0.33 0.45 Wheelabrator Shasta - Boiler 1 CA Yes Yes Stoker 10.9 3.4 10.3 22.1 8.4 11.6 9.3 14.7 17.6 16.3 10.4 5.5 19.3 8.7 7.6 7.8 Wheelabrator Shasta - Boiler 2 CA Yes Yes Stoker 12.9 6.5 8.9 6.4 14.3 6.4 12.5 8.0 8.9 15.1 16.4 17.2 5.4 7.6 7.4 7.0 Major Source Boiler MACT Limits - Existing Boilers

CISWI MACT Limits - Existing Units 

### Table. Biomass Emission Data Summary (Each value is an individual test run)Wheelabrator Shasta - Boiler 3 CA Yes Yes Stoker 9.9 9.4 10.4 11.2 13 10.6 10.3 4.9 11.5 8.3 19.1 11 20.5 25.3 15.7 12.6 3.8 5.4 7.1 7.6 8.6 9.4 Thermal Energy Development Partnership, L.P. - BLR1 CA Yes Yes Stoker 1.8 0.057 0.015 0.29 2.3 1.2 2.8 10.5 4.0 9.0 3.6 11.1 3.5 16.6 4.4 24.7 5.2 9.9 7.4 6.5 7.3 8.5 7.3 7.6 Covanta POPI - 2 units common stack CA Yes Yes Stoker 20.3 0.12 0.48 2.0 ND<1.58 1.3 50.8 ND<0.25 2.1 ND<1.48 1.0 13.7 0.34 2.7 ND<1.59 1.7Covanta - Pacific Ultrapower Chinese StationCA Yes Yes FBC 11.6 3.8 0.031 1.14 92 <8.94 <24.39 19.4 1.61 119 <9.23 <30.23 8.3 1.51 113 <9.20 <31.59 25.4 0.30 36 <8.20 24.8 37.1 ND<0.25 36 <9.95 28.8 39.0 26.4 2.9 4.9 8.4 Covanta Delano - Unit 1 CA Yes Yes FBC 10.5 0.13 0.74 <0.31 2.0 10.7 0.17 0.79 <0.34 4.4 8.2 0.33 0.91 <0.46 2.0 6.6 4.4 0.67 9.0 1.4 4.7 1.8 5.9 1.3 5.8 0.36 0.50 0.00 0.00 0.78 ND<0.610 ND<0.613 ND<0.611 0.00 0.00 0.02 0.43 0.26 0.40 Covanta Delano - Unit 2 CA Yes Yes FBC 16.5 ND<0.14 5.36 <3.43 2.65 13.3 ND<0.13 6.27 <2.82 2.49 13.2 1.07 5.53 <2.43 11.0 1.9 0.65 1.48 0.40 1.58 1.53 0.00 0.16 0.00 ND<0.69 ND<0.70 ND<0.70 0.23 0.24 0.04 0.21 0.16 0.14Covanta Mendota CA Yes Yes FBC 21.7 12.5 16.1 7.4 15.0 11.9 2.2 35.2 5.3 12.4 4.8 7.5 15.3 36.3 14.5 35.0 7.1 3.5 3.6 4.4 4.2 5.2 12.4 1.4 1.5 1.4 3.8 4.8 3.1 Hillman Power MI No Yes Stoker 0.87 14.7 0.065 1.6 0.83 4.9 0.14 0.54 0.65 15.6 0.1 0.54 0.8 13.9 0.32 0.55 13.4 0.27 0.72 7.6 0.03 4.4 14.6 0.039 7.1 15.4 0.03 1.4 21 0.025

11.7 11.5 8.9Viking Energy Lincoln Power Station MI No Yes Stoker 2.3 11.1 <0.04 1.3 1.3 8.7 <0.04 1.7 2.2 10.3 <0.04 1.5 2.8 5.6 <0.04 1.1 2.7 4.5 <0.04 1.5 3.1 5.3 <0.04 1.0

12.6 <0.353 0.69 9.8 <0.353 1.0 8.8 <0.353 1.0 10.6 <0.648 0.45 11 <0.648 0.41 10.5 <0.648 0.39 Genesee Power Station MI Yes Yes Stoker 0.52 3.7 <0.43 31 0.58 3.5 <0.43 51 0.35 3.3 <0.43 44 1.19 9.9 0.472 14 1.81 11.2 0.585 17 2.18 7.1 0.432 14

40 0.05 12 51 0.081 20 64 0.092 17 Grayling Generating Station MI No Yes Stoker 0.53 4.7 0.946 0.93 3.9 1.016 0.67 1.1 0.257 1.73 53.5 0.053 1.41 21.2 0.036 1.20 8.1 <0.04 5.30 19.4 3.62 16.3 6.58 26.3 Viking Energy of McBain MI No Yes Stoker 24.0 <0.802 0.53 30.8 <0.802 0.94 32.5 <0.802 0.87 Color Key: Notes on CARB Method 436 metals results: Exceeds or may exceed Boiler MACT limits (1) The non-detection (ND<) notation indicates the species was not detected in any sample or sample fraction. Exceeds or may exceed CISWI MACT limit (2) The less than (<) notation indicates a species was detected in at least one (but not all) samples or fractions. Exceeeds or may exceed both Boiler MACT and CISWI limits (3) Multi-metal results are not blank-corrected in accordance with CARB 436. (4) Non-detected multi-metal species were calculated using the laboratory reporting limit according to CARB Method 436.No. 

### Boiler/Unit State

1

### Wheelabrator Shasta Energy Company - Boiler 1 CA 2

### Wheelabrator Shasta Energy Company - Boiler 2 CA 3

### Wheelabrator Shasta Energy Company - Boiler 3 CA 4

### Thermal Energy Development Partnership, L.P. CA 5

### Pacific Oroville Power, Inc. (Covanta Energy) - 2 units, common stack CA 6

### Pacific Ultrapower Chinese Station (Covanta Energy) CA 7

### Covanta Delano (Covanta Energy) - Unit 1 CA 8

### Covanta Delano (Covanta Energy) - Unit 2 CA 9

### Covanta Mendota (Covanta Energy) CA 10

### Hillman Power Company MI 11

### Viking Energy Lincoln Power Station MI 12

### Genesee Power Station MI 13

### Grayling Generating Station MI 14

### Viking Energy of McBain MI 

### * "Yes" if any materials combusted during testing are or may be wastes per the NHSM rule.

### Major HAP Source?CISWI or Possible CISWI?* Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes No Yes No Yes Yes Yes No Yes No Yes 

### * "Yes" if any materials combusted during testing are or may be wastes per the NHSM rule.**List of Biomass Materials**

**Cellulosic: Clean cellulosic biomass** includes forest-derived biomass (green wood, forest thinnings, clean and unadulterated bark, sawdust, trim, and tree harvesting residuals from logging and sawmill materials), corn stover and other biomass crops used specifically for energy production (e.g., sugar cane, fast growing grasses), bagasse and other crop residue (e.g., peanut shells, agricultural seeds), wood collected from forest fire clearance activities, trees and clean wood found in disaster debris, clean biomass from land clearing operstions, and clean construction wood. **Food scraps Pulp and paper mill w** **ood residuals**- hog fuel, such as clean and unadulterated bark, sawdust, trim screenings; and residuals from tree harvesting **Ag ricultural residues** - straw, corn husks, peanut shells, bagasse **Ag ricultural w** **ood -**wood and stumps from orchard tree pruning and removal **Clean construction w ood**  **Clean demolition w ood**  **Unclean w ood from demolition materials (urban w** **ood) Clean disaster debris**  **Unclean disaster debris Resinated w** **ood products**- e.g., broad trim, sander dust, panel trim used to manufacture particleboard, medium density fiberboard, and hardboard **Pulp and paper residuals**- i.e., primary and secondary wastewater treatment processes **Secondary mill residues**- e.g., sanderdust, board, trim and breakage from the manufacture of reconstituted wood/panel products **CCA treated lumber**  **Creosote treated lumber Copper-based treated lumber**  **Lead-based treated lumber Borate treated lumber**  **Lead-based painted w ood**  **Non-cellulosic: Manures**  **Gaseous fuels**- landfill gas, manure gasYes

Boiler #1 Stoker / Other 339 MMBTU/hr No

**ID HHV**  **HHV UoM BF1**  9000 BTU/lb **BF2** 7800 BTU/lb **BF3 BF4**  **ID HHV**  **HHV UoM AF1**  1020 BTU/scf **AF2 AF3** 

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM** 

12219 8.7% BF1, Balance BF2 Sulfur dioxide EPA Method 6C 1 10.9ppmdv @7% O2 12219 8.7% BF1, Balance BF2 Sulfur dioxide EPA Method 6C 2 10.3 ppmdv @7% O2 12219 3.5% BF1, Balance BF2 Sulfur dioxide EPA Method 6C 3 8.4 ppmdv @7% O2 12219 3.5% BF1, Balance BF2 Sulfur dioxide EPA Method 6C 4 9.3 ppmdv @7% O2 12219 3% BF1, Balance BF2 Hydrogen chloride EPA Method 26 1 3.42 ppmdv @7% O2 12219 3% BF1, Balance BF2 Hydrogen chloride EPA Method 26 2 22.1 ppmdv @7% O2 12219 3 % BF1, Balance BF2 Hydrogen chloride EPA Method 26 3 11.6ppmdv @7% O2 12583D 12.7 % BF1, Balance BF2Sulfur dioxide EPA Method 6C 1 14.7ppmdv @7% O2 12583D 12.7 % BF1, Balance BF2Sulfur dioxide EPA Method 6C 2 17.6ppmdv @7% O2 12583D 12.7 % BF1, Balance BF2Sulfur dioxide EPA Method 6C 3 16.3 ppmdv @7% O2 12886A 6.7 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 1 10.4 ppmdv @7% O2 12886A 6.7 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 2 5.5 ppmdv @7% O2 12886A 6.7 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 3 19.3 ppmdv @7% O2 1299A BF2 Sulfur dioxide EPA Method 6C 1 8.7 ppmdv @7% O2 1299A BF2 Sulfur dioxide EPA Method 6C 2 7.6 ppmdv @7% O2 1299A BF2 Sulfur dioxide EPA Method 6C 3 7.8 ppmdv @7% O2 **Footnotes** 7/13/09 7/13/09 6/24/10

In test reports, Creosote Treated Wood (CTW) feed rate based on heat input, not % by weight. The above feed rate based on % weight is estimated by multiplying by 7.8 and dividing by 9, the approximate ratios of normal fuel HHV to CTW HHV. **Other Information** 6/24/10 6/24/10 12/12/06 12/12/06 11/3/08 11/3/08 11/3/08 7/13/09 **Emission Testing Results (insert**  **more lines of cells as needed)**  **Date of Test** 12/7/06 12/7/06 12/11/06 12/11/06 12/11/06 **Air Pollution Control**  **Equipment Type**  **Additional Information**

ESP four field SNCR ammonia injection **Auxiliary/Other Fuels**  **Type Other Information**  Natural gas **Other Information Biomass Fuels**  **Type Other Information**  Creosote Treated Wood HHV for BF1 and BF2 is on dry basis Biomass Fuel Other types not tracked separately but consist of clean biomass, clean demolition wood, and resinated wood kvigelan@wm.com **Biomass Combustor**  **Information Unit ID** 

**Design Category** traveling grate - mass feed **Capacity CHP?**  **Major HAP facility? Contact**  **Name** Kelle Vigeland

**Phone** (509)624-6575 x18 **e-mail CBEA/BPA - Emission Source Data Collection Form**  **Facility Information**  **Name** Wheelabrator Shasta Energy Company

**Street Address** 20811 Industry Road **City, State, Zip** Anderson, CA 96007Yes

Boiler #2 Stoker / Other 339 MMBTU/hr No

**ID HHV**  **HHV UoM BF1**  9000 BTU/lb **BF2** 7800 BTU/lb **BF3 BF4**  **ID HHV**  **HHV UoM AF1**  1020 BTU/scf **AF2 AF3** 

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM** 

12219 3.7% BF1, Balance BF2 Sulfur dioxide EPA Method 6C 1 12.9ppmdv @7% O2 12219 3.7% BF1, Balance BF2 Sulfur dioxide EPA Method 6C 2 8.9 ppmdv @7% O2 12219 3.7% BF1, Balance BF2 Sulfur dioxide EPA Method 6C 3 14.3 ppmdv @7% O2 12219 3.7% BF1, Balance BF2 Sulfur dioxide EPA Method 6C 4 12.5ppmdv @7% O2 12219 4.7% BF1, Balance BF2 Hydrogen chloride EPA Method 26 1 6.54 ppmdv @7% O2 12219 4.7% BF1, Balance BF2 Hydrogen chloride EPA Method 26 2 6.42 ppmdv @7% O2 12219 4.7% BF1, Balance BF2 Hydrogen chloride EPA Method 26 3 6.39ppmdv @7% O2 12583D 13.6 % BF1, Balance BF2Sulfur dioxide EPA Method 6C 1 8.0 ppmdv @7% O2 12583D 13.6 % BF1, Balance BF2Sulfur dioxide EPA Method 6C 2 8.9 ppmdv @7% O2 12583D 13.6 % BF1, Balance BF2Sulfur dioxide EPA Method 6C 3 15.1 ppmdv @7% O2 12886A 8 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 1 16.4 ppmdv @7% O2 12886A 8 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 2 17.2 ppmdv @7% O2 12886A 8 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 3 5.4 ppmdv @7% O2 1299A BF2 Sulfur dioxide EPA Method 6C 1 7.6 ppmdv @7% O2 1299A BF2 Sulfur dioxide EPA Method 6C 2 7.4 ppmdv @7% O2 1299A BF2 Sulfur dioxide EPA Method 6C 3 7.0 ppmdv @7% O2 **Footnotes** 7/9/2009

7/9/2009 6/23/2010

In test reports, Creosote Treated Wood (CTW) feed rate based on heat input, not % by weight. The above feed rate based on % weight is estimated by multiplying by 7.8 and dividing by 9, the approximate ratios of normal fuel HHV to CTW HHV. **Other Information** 6/23/2010

6/23/2010 12/13/2006 12/13/2006 11/4/2008 11/4/2008 11/4/2008 7/9/2009 **Emission Testing Results (insert**  **more lines of cells as needed)**  **Date of Test**

12/10/2006 12/10/2006 12/10/2006 12/10/2006 12/13/2006 **Air Pollution Control**  **Equipment Type**  **Additional Information**

ESP four field SNCR ammonia injection **Auxiliary/Other Fuels**  **Type Other Information**  Natural gas **Other Information Biomass Fuels**  **Type Other Information**  Creosote Treated Wood HHV for BF1 and BF2 is on dry basis Biomass Fuel Other types not tracked separately but consist of clean biomass, clean demolition wood, and resinated wood kvigelan@wm.com **Biomass Combustor**  **Information Unit ID** 

**Design Category** traveling grate - mass feed **Capacity CHP?**  **Major HAP facility? Contact**  **Name** Kelle Vigeland

**Phone** (509)624-6575 x18 **e-mail CBEA/BPA - Emission Source Data Collection Form**  **Facility Information**  **Name** Wheelabrator Shasta Energy Company

**Street Address** 20811 Industry Road **City, State, Zip** Anderson, CA 96007Yes

Boiler #3 Stoker / Other 339 MMBTU/hr No

**ID HHV**  **HHV UoM BF1**  9000 BTU/lb **BF2** 7800 BTU/lb **BF3 BF4**  **ID HHV**  **HHV UoM AF1**  1020 BTU/scf **AF2 AF3** 

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM** 

12219 1.9% BF1, Balance BF2 Sulfur dioxide EPA Method 6C 1 9.9 ppmdv @7% O2 12219 1.9% BF1, Balance BF2 Sulfur dioxide EPA Method 6C 2 10.4 ppmdv @7% O2 12219 1.9% BF1, Balance BF2 Sulfur dioxide EPA Method 6C 3 13 ppmdv @7% O2 12219 1.9% BF1, Balance BF2 Sulfur dioxide EPA Method 6C 4 10.3 ppmdv @7% O2 12219 3.2% BF1, Balance BF2 Hydrogen chloride EPA Method 26 1 9.39ppmdv @7% O2 12219 3.2% BF1, Balance BF2 Hydrogen chloride EPA Method 26 2 11.2 ppmdv @7% O2 12219 3.2% BF1, Balance BF2 Hydrogen chloride EPA Method 26 3 10.6ppmdv @7% O2 12583D 13 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 1 11.5ppmdv @7% O2 12583D 13 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 2 19.1 ppmdv @7% O2 12583D 13 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 3 20.5ppmdv @7% O2 12886A 9 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 1 25.3 ppmdv @7% O2 12886A 9 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 2 15.7ppmdv @7% O2 12886A 9 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 3 12.6ppmdv @7% O2 12886A 9 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 1 3.8 ppmdv @7% O2 12886A 9 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 2 5.4 ppmdv @7% O2 12886A 9 % BF1, Balance BF2 Sulfur dioxide EPA Method 6C 3 7.1 ppmdv @7% O2 1299A BF2 Sulfur dioxide EPA Method 6C 1 7.6 ppmdv @7% O2 1299A BF2 Sulfur dioxide EPA Method 6C 2 8.6 ppmdv @7% O2 1299A BF2 Sulfur dioxide EPA Method 6C 3 9.4 ppmdv @7% O2 12998D BF2 Hydrogen chloride EPA Method 26 1 4.9 ppmdv @7% O2 12998D BF2 Hydrogen chloride EPA Method 26 2 8.31 ppmdv @7% O2 12998D BF2 Hydrogen chloride EPA Method 26 3 11 ppmdv @7% O2 **Footnotes** 6/22/2010

6/22/2010

In test reports, Creosote Treated Wood (CTW) feed rate based on heat input, not % by weight. The above feed rate based on % weight is estimated by multiplying by 7.8 and dividing by 9, the approximate ratios of normal fuel HHV to CTW HHV. **Other Information** 6/25/2010

6/25/2010 6/25/2010 7/7/2009 7/8/2009 7/10/2009 7/10/2009 7/10/2009 6/22/2010 12/14/2006 12/14/2006 11/5/2008 11/5/2008 11/5/2008 7/7/2009 **Emission Testing Results (insert**  **more lines of cells as needed)**  **Date of Test**

12/9/2006 12/9/2006 12/9/2006 12/9/2006 12/14/2006 **Air Pollution Control**  **Equipment Type**  **Additional Information**

ESP four field SNCR ammonia injection **Auxiliary/Other Fuels**  **Type Other Information**  Natural gas **Other Information Biomass Fuels**  **Type Other Information**  Creosote Treated Wood HHV for BF1 and BF2 is on dry basis Biomass Fuel Other types not tracked separately but consist of clean biomass, clean demolition wood, and resinated wood kvigelan@wm.com **Biomass Combustor**  **Information Unit ID** 

**Design Category** traveling grate - mass feed **Capacity CHP?**  **Major HAP facility? Contact**  **Name** Kelle Vigeland

**Phone** (509)624-6575 x18 **e-mail CBEA/BPA - Emission Source Data Collection Form**  **Facility Information**  **Name** Wheelabrator Shasta Energy Company

**Street Address** 20811 Industry Road **City, State, Zip** Anderson, CA 96007Yes

BLR1 Stoker / Other 20.5 MW No

**ID HHV**  **HHV UoM BF1**  8060 BTU/lb **BF2** 8295 BTU/lb **BF3 BF4**  **ID HHV**  **HHV UoM AF1**  1018 BTU/scf **AF2 AF3** 

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM** 

1-MM BF1 - 43%, BF2 - 57% Cadmium EPA 29 1 0.0146ug/dscm @ 7% O2 1-PCDD BF1 - 43%, BF2 - 57% Dioxin/Furan - total massEPA 23 1 0.0568ng/dscm @ 7% O2 1-HCl BF1 - 43%, BF2 - 57% Hydrogen chloride EPA 26 1 1.185ppmdv @7% O2 1-HCl BF1 - 40%, BF2 - 60% Hydrogen chloride EPA 26 1 10.52ppmdv @7% O2 2-HCl BF1 - 40%, BF2 - 60% Hydrogen chloride EPA 26 2 8.954ppmdv @7% O2 3-HCl BF1 - 40%, BF2 - 60% Hydrogen chloride EPA 26 3 11.06ppmdv @7% O2 3-HCl BF1 - 40%, BF2 - 60% Hydrogen chloride EPA 26 1 16.56ppmdv @7% O2 4-HCl BF1 - 40%, BF2 - 60% Hydrogen chloride EPA 26 2 24.74ppmdv @7% O2 1-HCl BF1 - 40%, BF2 - 60% Hydrogen chloride EPA 26 1 9.867ppmdv @7% O2 2-HCl BF1 - 40%, BF2 - 60% Hydrogen chloride EPA 26 2 6.457ppmdv @7% O2 1-MM BF1 - 43%, BF2 - 57% Lead EPA 29 1 0.293ug/dscm @ 7% O2 

## CBEA/BPA - Emission Source Data Collection Form **Facility Information**  **Name** Thermal Energy Development Partnership, L.P.

**Street Address** 14800 W. Schulte Rd. **City, State, Zip** Tracy, CA 95377 **Major HAP facility? Contact**  **Name** Tike Heshimu

**Phone** 209-879-6931 **e-mail** THeshimu@usrg-tracy.com **Biomass Combustor**  **Information Unit ID** 

**Design Category Capacity**  **CHP? Other Information**  Startup in April, 1990 **Biomass Fuels Type**  **Other Information** Agricultural Wood 2010 avg values. Dry basis. Whole trees, stumps, roots, and dirt Urban Wood 2010 avg values. Dry basis.

**Auxiliary/Other Fuels**  **Type Other Information**  Natural gas PG&E Supplied

**Air Pollution Control**  **Equipment Type**  **Additional Information**

ESP For Particulate Control SNCR DeNOx: Ammonia Injectio

3/22/2007 6/1/2000 10/28/2010 Other - describe SOx Control: Dry Sorbent Injection (hydrated lime) Other - describe HCl Control: Bicarb Injection **Date of Test** 10/28/2010

6/1/2000 5/31/2000 **Emission Testing Results (insert**  **more lines of cells as needed)** 

5/31/2000

10/28/2010 10/28/2010 3/22/2007 3/22/2007Yes

Boilers 1 & 2 - Common Stack ` aszurgot@covantaenergy.com **Biomass Unit ID** 

**Major HAP facility? Contact**  **Name** Andrew Szurgot

**Phone** 862-345-5426 **e-mail** 

## CBEA/BPA - Emission Source Data Collection Form **Facility Information**  **Name** Pacific Oroville Power, Inc. (Covanta Energy)

**Street Address** 3050 South 5th Avenue **City, State, Zip** Oroville, CA 95965

Boilers 1 & 2 - Common Stack ` Stoker / Other 175 (each boiler) MMBTU/hr No

**ID HHV**  **HHV UoM BF1**  7800 (dry basis) BTU/lb **BF2** 7000 (dry basis) BTU/lb **BF3** 8000 (dry basis) BTU/lb **BF4** 7500 (dry basis) BTU/lb **BF5** 7800 (dry basis) BTU/lb **ID HHV**  **HHV UoM AF1**  Enter Select **AF2** Enter Select **Auxiliary/Other Fuels**  **Type Other Information**  Select Enter Select Enter Agricultural residues Fruit pits and shells. HHV is estimated. Agricultural wood Whole trees, prunings, stumps. HHV is estimated. Other clean biomass Mill residues, bark, yard waste. HHV is estimated. **Other Information** Produces electricity for export to grid. Capacity given is for each of two boilers. **Biomass Fuels Type**  **Other Information** Forest-derived biomass Includes whole tree chips. HHV is estimated. Urban wood Demo wood from processors. HHV is estimated. **Biomass Combustor**  **Information Unit ID** 

**Design Category Capacity**  **CHP?**

**AF2** Enter Select **AF3** Enter Select

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM**  Avogadro-05002.2mSee footnotes Hydrogen chloride EPA 26 1 1.28ppmdv @7% O2 Enter Avogadro-05002.2mSee footnotes Hydrogen chloride EPA 26 2 0.96ppmdv @7% O2 Enter Avogadro-05002.2mSee footnotes Hydrogen chloride EPA 26 3 1.65ppmdv @7% O2 Enter Avogadro-05002.2mSee footnotes Cadmium EPA 29 1 0.48 ug/dscm @ 7% O2 Enter Avogadro-05002.2mSee footnotes Cadmium EPA 29 2 ND<0.25ug/dscm @ 7% O2 Enter Avogadro-05002.2mSee footnotes Cadmium EPA 29 3 0.34 ug/dscm @ 7% O2 Enter

Enter **Emission Testing Results (insert**  **more lines of cells as needed)**  **Date of Test**

8/23/2005 8/23/2005 8/23/2005 8/24/2005 8/24/2005 8/24/2005 **Air Pollution Control**  **Equipment Type**  **Additional Information**

ESP Enter Select Enter Select Enter Select Select Enter Select Enter

Avogadro-05002.2mSee footnotes Cadmium EPA 29 3 0.34 ug/dscm @ 7% O2 Enter Avogadro-05002.2mSee footnotes Lead EPA 29 1 2.03 ug/dscm @ 7% O2 Enter Avogadro-05002.2mSee footnotes Lead EPA 29 2 2.14 ug/dscm @ 7% O2 Enter Avogadro-05002.2mSee footnotes Lead EPA 29 3 2.65 ug/dscm @ 7% O2 Enter Avogadro-05002.2mSee footnotes Mercury EPA 29 1 ND<1.58ug/dscm @ 7% O2 Enter Avogadro-05002.2mSee footnotes Mercury EPA 29 2 ND<1.48ug/dscm @ 7% O2 Enter Avogadro-05002.2mSee footnotes Mercury EPA 29 3 ND<1.59ug/dscm @ 7% O2 Enter Avogadro-2009 See footnotes Dioxin/Furan - total mass CARB 428 1 20.27ng/dscm @ 7% O2 Enter Avogadro-2009 See footnotes Dioxin/Furan - total mass CARB 428 2 50.77ng/dscm @ 7% O2 Enter Avogadro-2009 See footnotes Dioxin/Furan - total mass CARB 428 3 13.7ng/dscm @ 7% O2 Enter **Footnotes** 11/3/2009

11/3/2009 Typical annual fuel mix at the facility is BF1-35%, BF2-10%, BF3-10%, BF4-15%, BF5-30%. Fuel % mix during testing was not measured but would typically contain biomass materials found in annual fuel mix. All test data are from testing at a common stack which serves both boilers. 8/24/2005 8/24/2005 8/24/2005 8/24/2005 8/24/2005 11/3/2009 8/24/2005 8/24/2005**Other Information**Yes

Unit 1 Fluidized bed 370 MMBTU/hr No

**ID HHV**  **HHV UoM BF1**  7800 (dry basis) BTU/lb **BF2** 7000 (dry basis) BTU/lb **BF3** 7500 (dry basis) BTU/lb **BF4** 8000 (dry basis) BTU/lb **ID HHV**  **HHV UoM AF1**  21,700 BTU/lb **AF2** Enter Select **AF3** Enter Select

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM**  Avogadro-06145c See footnotes Sulfur dioxide 6C 1 11.61ppmdv @7% O2 Enter Avogadro-06145c See footnotes Sulfur dioxide 6C 2 19.40ppmdv @7% O2 Enter Avogadro-06145c See footnotes Sulfur dioxide 6C 3 8.33ppmdv @7% O2 Enter Avogadro-07094 See footnotes Cadmium EPA 29 1 1.14 ug/dscm @ 7% O2 Enter Avogadro-07094 See footnotes Cadmium EPA 29 2 1.61 ug/dscm @ 7% O2 Enter Avogadro-07094 See footnotes Cadmium EPA 29 3 1.51 ug/dscm @ 7% O2 Enter Avogadro-07094 See footnotes Lead EPA 29 1 92.46ug/dscm @ 7% O2 Enter Avogadro-07094 See footnotes Lead EPA 29 2 119.1ug/dscm @ 7% O2 Enter Avogadro-07094 See footnotes Lead EPA 29 3 113.15ug/dscm @ 7% O2 Enter Avogadro-07094 See footnotes Mercury EPA 29 1 <8.94ug/dscm @ 7% O2 Enter Avogadro-07094 See footnotes Mercury EPA 29 2 <9.23ug/dscm @ 7% O2 Enter Avogadro-07094 See footnotes Mercury EPA 29 3 <9.20ug/dscm @ 7% O2 Enter Avogadro-07094 See footnotes Hydrogen chloride EPA 26 1 <24.39ppmdv @7% O2 Enter Avogadro-07094 See footnotes Hydrogen chloride EPA 26 2 <30.23ppmdv @7% O2 Enter Avogadro-07094 See footnotes Hydrogen chloride EPA 26 3 <31.59ppmdv @7% O2 Enter Avogadro-2010 See footnotes Dioxin/Furan - total mass 1 3.82 ng/dscm @ 7% O2 Enter Avogadro-2010 See footnotes Dioxin/Furan - toxic equiv 1 0.031ng/dscm @ 7% O2 Enter Avogadro-08222.0C See footnotes Sulfur dioxide 6C 1 25.39ppmdv @7% O2 Enter 9/1/2010 9/24/2008 9/27/2007 9/27/2007 9/29/2007 9/29/2007 9/29/2007 9/1/2010 9/27/2007 9/27/2007 9/27/2007 9/27/2007 9/27/2007 9/27/2007 Other - describe Limestone in FBC bed reduces acid gas emissions Select Enter **Emission Testing Results (insert**  **more lines of cells as needed)**  **Date of Test** 9/27/2006 9/27/2006 9/27/2006 9/27/2007 Enter Select Enter **Air Pollution Control**  **Equipment Type**  **Additional Information**

ESP Enter SNCR Enter

Agricultural wood Whole trees, prunings, stumps. HHV is estimated. Agricultural residues Fruit shells and pits. HHV is estimated. **Auxiliary/Other Fuels**  **Type Other Information**  Other - describe Propane Select **Other Information** Produces electricity for export to grid **Biomass Fuels Type**  **Other Information** Forest-derived biomass Includes mill sawdust. HHV is estimated. Urban wood Wood from processors. HHV is estimated. aszurgot@covantaenergy.com **Biomass Combustor**  **Information Unit ID** 

**Design Category** Bubbling bed with limestine **Capacity CHP?**  **Major HAP facility? Contact**  **Name** Andrew Szurgot

**Phone** 862-345-5426 **e-mail** 

## CBEA/BPA - Emission Source Data Collection Form **Facility Information**  **Name** Pacific Ultrapower Chinese Station (Covanta Energy)

**Street Address** 8755 Enterprise Drive **City, State, Zip** Jamestown, CA 95327Avogadro-08222.0C See footnotes Sulfur dioxide 6C 2 37.08ppmdv @7% O2 Enter Avogadro-08222.0C See footnotes Sulfur dioxide 6C 3 38.99ppmdv @7% O2 Enter Avogadro-10044.1C See footnotes Sulfur dioxide 6C 1 2.88ppmdv @7% O2 Enter Avogadro-10044.1C See footnotes Sulfur dioxide 6C 2 4.90ppmdv @7% O2 Enter Avogadro-10044.1C See footnotes Sulfur dioxide 6C 3 8.37ppmdv @7% O2 Enter Avogadro-10044.1 See footnotes Cadmium EPA 29 1 0.3 ug/dscm @ 7% O2 Enter Avogadro-10044.1 See footnotes Cadmium EPA 29 2 ND<0.25ug/dscm @ 7% O2 Enter Avogadro-10044.1 See footnotes Lead EPA 29 1 36.2 ug/dscm @ 7% O2 Enter Avogadro-10044.1 See footnotes Lead EPA 29 2 35.9 ug/dscm @ 7% O2 Enter Avogadro-10044.1 See footnotes Mercury EPA 29 1 <8.20ug/dscm @ 7% O2 Enter Avogadro-10044.1 See footnotes Mercury EPA 29 2 <9.95ug/dscm @ 7% O2 Enter Avogadro-2010 See footnotes Hydrogen chloride EPA 26 1 24.8ppmdv @7% O2 Enter Avogadro-2010 See footnotes Hydrogen chloride EPA 26 2 28.82ppmdv @7% O2 Enter Avogadro-2010 See footnotes Hydrogen chloride EPA 26 3 26.38ppmdv @7% O2 Enter **Footnotes** 9/1/2010 9/1/2010 9/1/2010 9/1/2010 Typical annual fuel mix at the facility is BF1-25%, BF2-35%, BF3-40%, BF4-less than 5%. Fuel % mix during testing was not measured but would typically contain biomass materials found in annual fuel mix. **Other Information** 8/31/2010 9/1/2010 9/1/2010 9/1/2010 9/1/2010 9/1/2010 9/24/2008 9/24/2008 8/31/2010 8/31/2010Yes

Unit 1 Fluidized bed 400 MMBTU/hr No

**ID HHV**  **HHV UoM BF1**  7500 (dry basis) BTU/lb **BF2** 8000 (dry basis) BTU/lb **BF3** 7000 (dry basis) BTU/lb **BF4** Enter Select **ID HHV**  **HHV UoM AF1**  1000 BTU/scf **AF2** Enter Select **AF3** Enter Select

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM**  AKI-12668B See footnotes Cadmium EPA 5/29 1 0.13 ug/dscm @ 7% O2 Enter AKI-12668B See footnotes Cadmium EPA 5/29 2 0.17ug/dscm @ 7% O2 Enter AKI-12668B See footnotes Cadmium EPA 5/29 3 0.33 ug/dscm @ 7% O2 Enter AKI-12668B See footnotes Lead EPA 5/29 1 0.74 ug/dscm @ 7% O2 Enter AKI-12668B See footnotes Lead EPA 5/29 2 0.79 ug/dscm @ 7% O2 Enter AKI-12668B See footnotes Lead EPA 5/29 3 0.91 ug/dscm @ 7% O2 Enter AKI-12668B See footnotes Mercury EPA 5/29 1 <0.31ug/dscm @ 7% O2 Enter AKI-12668B See footnotes Mercury EPA 5/29 2 <0.34ug/dscm @ 7% O2 Enter AKI-12668B See footnotes Mercury EPA 5/29 3 <0.46ug/dscm @ 7% O2 Enter Avogadro-R04114C See footnotes Sulfur dioxide 6C 1 10.55ppmdv @7% O2 Enter Avogadro-R04114C See footnotes Sulfur dioxide 6C 2 10.70ppmdv @7% O2 Enter Avogadro-R04114C See footnotes Sulfur dioxide 6C 3 8.20ppmdv @7% O2 Enter Avogadro-R04114C See footnotes Sulfur dioxide 6C 4 6.57ppmdv @7% O2 Enter Avogadro-R05130 See footnotes Sulfur dioxide 6C 1 0.67ppmdv @7% O2 Enter Avogadro-R05130 See footnotes Sulfur dioxide 6C 2 1.44ppmdv @7% O2 Enter Avogadro-R05130 See footnotes Sulfur dioxide 6C 3 1.83ppmdv @7% O2 Enter Avogadro-06128 See footnotes Sulfur dioxide 6C 1 1.28ppmdv @7% O2 Enter Avogadro-06128 See footnotes Sulfur dioxide 6C 2 0.36ppmdv @7% O2 Enter 

## CBEA/BPA - Emission Source Data Collection Form **Facility Information**  **Name** Covanta Delano (Covanta Energy)

**Street Address** 31500 Pond Road **City, State, Zip** Delano, CA 93216 **Major HAP facility? Contact**  **Name** Andrew Szurgot

**Phone** 862-345-5426 **e-mail** aszurgot@optonline.net **Biomass Combustor**  **Information Unit ID** 

**Design Category** Bubbling bed with limestone **Capacity CHP?**  **Other Information** Produces electricity for export to grid **Biomass Fuels Type**  **Other Information** Agricultural wood Whole trees, prunings, stumps. HHV is estimated. Agricultural residues Fruit shells and pits. HHV is estimated. Urban wood Wood typically from processors at landfills. HHV is estimated. Enter - see instructions Enter **Auxiliary/Other Fuels**  **Type Other Information**  Natural gas Enter Select Enter Select Enter **Air Pollution Control**  **Equipment Type**  **Additional Information**

Fabric Filter Enter Dry scrubber Sodium bicarbonate injected before fabric filter SNCR NOx control Other - describe Limestone in FBC bed reduces acid gas emissions **Emission Testing Results (insert**  **more lines of cells as needed)**  **Date of Test**

4/21/2009 4/21/2009 4/21/2009 4/21/2009 4/21/2009 4/21/2009 4/21/2009 4/21/2009 4/21/2009 6/28-29/2004 6/29/2004 6/29/2004 6/29/2004 6/21/2005 6/21/2005 6/22/2005 6/20/2006 6/20/2006Avogadro-06128 See footnotes Sulfur dioxide 6C 3 0.50ppmdv @7% O2 Enter Avogadro-07143.0 See footnotes Sulfur dioxide 6C 1 0.0 ppmdv @7% O2 Enter Avogadro-07143.0 See footnotes Sulfur dioxide 6C 2 0.0 ppmdv @7% O2 Enter Avogadro-07143.0 See footnotes Sulfur dioxide 6C 3 0.78ppmdv @7% O2 Enter Avogadro-08054.0C See footnotes Sulfur dioxide 6C 1ND<0.610ppmdv @7% O2 Enter Avogadro-08054.0C See footnotes Sulfur dioxide 6C 2ND<0.613ppmdv @7% O2 Enter Avogadro-08054.0C See footnotes Sulfur dioxide 6C 3ND<0.611ppmdv @7% O2 Enter Aki-12668 A See footnotes Sulfur dioxide 6C 1 0.00ppmdv @7% O2 Enter Aki-12668 A See footnotes Sulfur dioxide 6C 2 0.00ppmdv @7% O2 Enter Aki-12668 A See footnotes Sulfur dioxide 6C 3 0.02ppmdv @7% O2 Enter Aki-13046 A See footnotes Sulfur dioxide 6C 1 0.435ppmdv @7% O2 Enter Aki-13046 A See footnotes Sulfur dioxide 6C 2 0.264ppmdv @7% O2 Enter Aki-13046 A See footnotes Sulfur dioxide 6C 3 0.404ppmdv @7% O2 Enter AKI-12668B See footnotes Hydrogen chloride EPA 26 1 1.98ppmdv @7% O2 Enter AKI-12668B See footnotes Hydrogen chloride EPA 26 2 4.41 ppmdv @7% O2 Enter AKI-12668B See footnotes Hydrogen chloride EPA 26 3 9.01 ppmdv @7% O2 Enter

- See footnotes Hydrogen chloride EPA 26 1 4.7 ppmdv @7% O2 Enter

- See footnotes Hydrogen chloride EPA 26 2 5.94ppmdv @7% O2 Enter

- See footnotes Hydrogen chloride EPA 26 3 5.82ppmdv @7% O2 Enter **Footnotes** 6/21/2006

6/14/2007 6/14/2007 6/14/2007 5/13/2008 5/13/2008 5/13/2008 6/19/2009 6/19/2009 6/19/2009 7/28/2010 7/28/2010 7/28/2010 4/21/2009 4/21/2009 4/21/2009 6/4/2010 6/4/2010 6/4/2010 Typical annual fuel mix at the facility is BF1-73%, BF2-2%, BF3-25%. Fuel % mix during testing was not measured but would typically contain biomass materials found in annual fuel mix. **Other Information**Provide any other information you think is relevant to this submittal.Yes

Unit 2 Fluidized bed 315 MMBTU/hr No

**ID HHV**  **HHV UoM BF1**  7500 (dry basis) BTU/lb **BF2** 8000 (dry basis) BTU/lb **BF3** 7000 (dry basis) BTU/lb **BF4** Enter Select **ID HHV**  **HHV UoM AF1**  1000 BTU/scf **AF2** Enter Select **AF3** Enter Select

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM**  Avogadro-10044.14cSee footnotes Cadmium EPA 5/29 1 ND<0.14ug/dscm @ 7% O2 Enter Avogadro-10044.14cSee footnotes Cadmium EPA 5/29 2 ND<0.13ug/dscm @ 7% O2 Enter Avogadro-10044.14cSee footnotes Cadmium EPA 5/29 3 1.07ug/dscm @ 7% O2 Enter Avogadro-10044.14cSee footnotes Lead EPA 5/29 1 5.36 ug/dscm @ 7% O2 Enter Avogadro-10044.14cSee footnotes Lead EPA 5/29 2 6.27ug/dscm @ 7% O2 Enter Avogadro-10044.14cSee footnotes Lead EPA 5/29 3 5.53 ug/dscm @ 7% O2 Enter Avogadro-10044.14cSee footnotes Mercury EPA 5/29 1 <3.43ug/dscm @ 7% O2 Enter Avogadro-10044.14cSee footnotes Mercury EPA 5/29 2 <2.82ug/dscm @ 7% O2 Enter Avogadro-10044.14cSee footnotes Mercury EPA 5/29 3 <2.43ug/dscm @ 7% O2 Enter Avogadro-R04114C See footnotes Sulfur dioxide 6C 1 16.45ppmdv @7% O2 Enter Avogadro-R04114C See footnotes Sulfur dioxide 6C 2 13.28ppmdv @7% O2 Enter Avogadro-R04114C See footnotes Sulfur dioxide 6C 3 13.20ppmdv @7% O2 Enter Avogadro-R05130 See footnotes Sulfur dioxide 6C 1 1.92ppmdv @7% O2 Enter Avogadro-R05130 See footnotes Sulfur dioxide 6C 2 0.65ppmdv @7% O2 Enter Avogadro-R05130 See footnotes Sulfur dioxide 6C 3 1.48ppmdv @7% O2 Enter Avogadro-06128 See footnotes Sulfur dioxide 6C 1 0.40ppmdv @7% O2 Enter Avogadro-06128 See footnotes Sulfur dioxide 6C 2 1.58ppmdv @7% O2 Enter Avogadro-06128 See footnotes Sulfur dioxide 6C 3 1.53ppmdv @7% O2 Enter 

## CBEA/BPA - Emission Source Data Collection Form **Facility Information**  **Name** Covanta Delano (Covanta Energy)

**Street Address** 31500 Pond Road **City, State, Zip** Delano, CA 93216 **Major HAP facility? Contact**  **Name** Andrew Szurgot

**Phone** 862-345-5426 **e-mail** aszurgot@optonline.net **Biomass Combustor**  **Information Unit ID** 

**Design Category** Bubbling bed with limestone **Capacity CHP?**  **Other Information** Produces electricity for export to grid **Biomass Fuels Type**  **Other Information** Agricultural wood Whole trees, prunings, stumps. HHV is estimated. Agricultural residues Fruit shells and pits. HHV is estimated. Urban wood Wood typically from processors at landfills. HHV is estimated. Enter - see instructions Enter **Auxiliary/Other Fuels**  **Type Other Information**  Natural gas Enter Select Enter Select Enter **Air Pollution Control**  **Equipment Type**  **Additional Information**

Fabric Filter Enter Dry scrubber Sodium bicarbonate injected before fabric filter SNCR NOx control Other - describe Limestone in FBC bed reduces acid gas emissions **Emission Testing Results (insert**  **more lines of cells as needed)**  **Date of Test**

11/14/2007 11/14/2007 11/14/2007 11/14/2007 11/14/2007 11/14/2007 11/14/2007 11/14/2007 11/14/2007 6/16/2004 6/16/2004 6/16/2004 6/23/2005 6/24/2005 6/24/2005 6/22/2006 6/22/2006 6/22/2006Avogadro-07143.0 See footnotes Sulfur dioxide 6C 1 0.00ppmdv @7% O2 Enter Avogadro-07143.0 See footnotes Sulfur dioxide 6C 2 0.16ppmdv @7% O2 Enter Avogadro-07143.0 See footnotes Sulfur dioxide 6C 3 0.00ppmdv @7% O2 Enter Avogadro-08054.0C See footnotes Sulfur dioxide 6C 1 ND<0.69ppmdv @7% O2 Enter Avogadro-08054.0C See footnotes Sulfur dioxide 6C 2 ND<0.70ppmdv @7% O2 Enter Avogadro-08054.0C See footnotes Sulfur dioxide 6C 3 ND<0.70ppmdv @7% O2 Enter Aki-12668 A See footnotes Sulfur dioxide 6C 1 0.23ppmdv @7% O2 Enter Aki-12668 A See footnotes Sulfur dioxide 6C 2 0.24ppmdv @7% O2 Enter Aki-12668 A See footnotes Sulfur dioxide 6C 3 0.04ppmdv @7% O2 Enter Aki-13046 A See footnotes Sulfur dioxide 6C 1 0.21 ppmdv @7% O2 Enter Aki-13046 A See footnotes Sulfur dioxide 6C 2 0.16ppmdv @7% O2 Enter Aki-13046 A See footnotes Sulfur dioxide 6C 3 0.14ppmdv @7% O2 Enter Avogadro-10044.14cSee footnotes Hydrogen chloride EPA 26 1 2.65ppmdv @7% O2 Enter Avogadro-10044.14cSee footnotes Hydrogen chloride EPA 26 2 2.49ppmdv @7% O2 Enter Avogadro-10044.14cSee footnotes Hydrogen chloride EPA 26 3 10.97ppmdv @7% O2 Enter **Footnotes** 6/12/2007

6/12/2007 6/13/2007 5/14/2008 5/14/2008 5/14/2008 6/19/2009 6/19/2009 6/19/2009 7/28/2010

**Other Information**Provide any other information you think is relevant to this submittal.

7/28/2010 7/28/2010 11/14/2007 11/14/2007 11/14/2007 Typical annual fuel mix at the facility is BF1-73%, BF2-2%, BF3-25%. Fuel % mix during testing was not measured but would typically contain biomass materials found in annual fuel mix.Yes

Unit 1 Fluidized bed 317 MMBTU/hr No

**ID HHV**  **HHV UoM BF1**  7500 (dry basis) BTU/lb **BF2** 8000 (dry basis) BTU/lb **BF3** 7000 (dry basis) BTU/lb **BF4** Enter Select **ID HHV**  **HHV UoM AF1**  1000 BTU/scf **AF2** Enter Select **AF3** Enter Select

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM**  Avogadro-2007 See footnotes Hydrogen chloride EPA 26 1 12.45ppmdv @7% O2 Enter Avogadro-2007 See footnotes Hydrogen chloride EPA 26 2 7.43ppmdv @7% O2 Enter Avogadro-2007 See footnotes Hydrogen chloride EPA 26 3 11.89ppmdv @7% O2 Enter

- See footnotes Hydrogen chloride EPA 26 1 35.15ppmdv @7% O2 Enter

- See footnotes Hydrogen chloride EPA 26 1 12.43ppmdv @7% O2 Enter

- See footnotes Hydrogen chloride EPA 26 2 7.5 ppmdv @7% O2 Enter

- See footnotes Hydrogen chloride EPA 26 2 36.31ppmdv @7% O2 Enter

- See footnotes Hydrogen chloride EPA 26 3 34.99ppmdv @7% O2 Enter Avogadro-R04115 See footnotes Sulfur dioxide 6C 1 21.72ppmdv @7% O2 Enter Avogadro-R04115 See footnotes Sulfur dioxide 6C 2 16.10ppmdv @7% O2 Enter Avogadro-R04115 See footnotes Sulfur dioxide 6C 3 14.99ppmdv @7% O2 Enter Avogadro-R05123 See footnotes Sulfur dioxide 6C 1 2.24ppmdv @7% O2 Enter Avogadro-R05123 See footnotes Sulfur dioxide 6C 2 5.27ppmdv @7% O2 Enter Avogadro-R05123 See footnotes Sulfur dioxide 6C 3 4.82ppmdv @7% O2 Enter Avogadro-06129 See footnotes Sulfur dioxide 6C 1 15.33ppmdv @7% O2 Enter Avogadro-06129 See footnotes Sulfur dioxide 6C 2 14.49ppmdv @7% O2 Enter Avogadro-06129 See footnotes Sulfur dioxide 6C 3 7.10ppmdv @7% O2 Enter Avogadro-07142 See footnotes Sulfur dioxide 6C 1 3.48ppmdv @7% O2 Enter 6/15/2006 6/7/2007 7/1/2004 6/28/2005 6/28/2005 6/28/2005 6/15/2006 6/15/2006 6/16/2010 6/16/2010 6/17/2010 6/17/2010 6/30/2004 6/30/2004 Other - describe Limestone in FBC bed reduces acid gas emissions Select Enter **Emission Testing Results (insert**  **more lines of cells as needed)**  **Date of Test**

6/7/2007 6/7/2007 6/7/2007 6/15/2010 Enter Select Enter **Air Pollution Control**  **Equipment Type**  **Additional Information**

Fabric Filter Enter SNCR NOx control Urban wood Wood typically from processors at landfills. HHV is estimated. Enter - see instructions Enter **Auxiliary/Other Fuels**  **Type Other Information**  Select Enter Select **Other Information** Produces electricity for export to grid **Biomass Fuels Type**  **Other Information** Agricultural wood Whole trees, prunings, stumps. HHV is estimated. Agricultural residues Fruit shells and pits. HHV is estimated. aszurgot@covantaenergy.com **Biomass Combustor**  **Information Unit ID** 

**Design Category** Circulating bed with limestone **Capacity CHP?**  **Major HAP facility? Contact**  **Name** Andrew Szurgot

**Phone** 862-345-5426 **e-mail** 

## CBEA/BPA - Emission Source Data Collection Form **Facility Information**  **Name** Covanta Mendota (Covanta Energy)

**Street Address** 400 Guillen Parkway **City, State, Zip** Mendota, CA 93640Avogadro-07142 See footnotes Sulfur dioxide 6C 2 3.57ppmdv @7% O2 Enter Avogadro-07142 See footnotes Sulfur dioxide 6C 3 4.39ppmdv @7% O2 Enter Avogadro-08053.0C See footnotes Sulfur dioxide 6C 1 4.25ppmdv @7% O2 Enter Avogadro-08053.0C See footnotes Sulfur dioxide 6C 2 5.17ppmdv @7% O2 Enter Avogadro-08053.0C See footnotes Sulfur dioxide 6C 3 12.42ppmdv @7% O2 Enter Aki-12791 See footnotes Sulfur dioxide 6C 1 1.44ppmdv @7% O2 Enter Aki-12791 See footnotes Sulfur dioxide 6C 2 1.54ppmdv @7% O2 Enter Aki-12791 See footnotes Sulfur dioxide 6C 3 1.43ppmdv @7% O2 Enter Avogadro-10044.6C See footnotes Sulfur dioxide 6C 1 3.83ppmdv @7% O2 Enter Avogadro-10044.6C See footnotes Sulfur dioxide 6C 2 4.82ppmdv @7% O2 Enter Avogadro-10044.6C See footnotes Sulfur dioxide 6C 3 3.06ppmdv @7% O2 Enter **Footnotes** 6/16/2010

Typical annual fuel mix at the facility is BF1-73%, BF2-2%, BF3-25%. Fuel % mix during testing was not measured but would typically contain biomass materials found in annual fuel mix. **Other Information**Provide any other information you think is relevant to this submittal.

6/11/2008 6/17/2009 6/17/2009 6/17/2009 6/16/2010 6/16/2010 6/7/2007 6/7/2007 6/11/2008 6/11/2008EUBOILER Stoker /Other

300 Select UoM No

**ID HHV**  **HHV UoM BF1**  4400 Select **BF2** 6000 Select **BF3** Enter Select **BF4** Enter Select **ID HHV**  **HHV UoM AF1**  Enter Select **AF2** 13500 Select **AF3** Enter Select

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM**  Enter BF1/AF2/BF2-90/8/2% Lead EPA Method 29 1 14.7ug/dscm @ 7% O2 Enter Enter BF1/AF2/BF2-90/8/2% Lead EPA Method 29 2 4.87ug/dscm @ 7% O2 Enter Enter BF1/AF2/BF2-90/8/2% Lead EPA Method 29 3 15.6 ug/dscm @ 7% O2 Enter Enter BF1/AF2/BF2-90/8/2% Hydrogen chloride EPA Method 26 1 1.6 ppmdv @7% O2 Enter Enter BF1/AF2/BF2-90/8/2% Hydrogen chloride EPA Method 26 2 0.54ppmdv @7% O2 Enter Enter BF1/AF2/BF2-90/8/2% Hydrogen chloride EPA Method 26 3 0.54ppmdv @7% O2 Enter Jul-98 BF1/AF2-95/5% Cadmium EPA Method 29 1 0.87ug/dscm @ 7% O2 Jul-98 BF1/AF2-95/5% Cadmium EPA Method 29 2 0.83 ug/dscm @ 7% O2 Jul-98 BF1/AF2-95/5% Cadmium EPA Method 29 3 0.65 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 90/10% Cadmium EPA Method 29 1 0.8 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 90/10% Cadmium EPA Method 29 2 0.55 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 90/10% Cadmium EPA Method 29 3 0.72 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 85/15% Cadmium EPA Method 29 1 4.4 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 85/15% Cadmium EPA Method 29 2 7.1 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 85/15% Cadmium EPA Method 29 3 1.4 ug/dscm @ 7% O2 Jul-98 BF1/AF2-95/5% Lead EPA Method 29 1 13.9 ug/dscm @ 7% O2 Jul-98 BF1/AF2-95/5% Lead EPA Method 29 2 13.4 ug/dscm @ 7% O2 Jul-98 BF1/AF2-95/5% Lead EPA Method 29 3 7.6 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 90/10% Lead EPA Method 29 1 14.6 ug/dscm @ 7% O2 Jan-03 Enter Select Enter **Emission Testing Results**  **Date of Test** Jan-03 Jan-03 Jan-03 Jan-03 Jan-03 Select Enter **Air Pollution Control**  **Equipment Type**  **Additional Information**

SNCR Enter ESP Enter Select **Auxiliary/Other Fuels**  **Type Other Information**  Natural gas Enter Enter - see instructions Enter

Tire Derived Fuel Enter **Biomass Fuels**

Secondary Mill Residuals Enter

Enter - see instructions Enter **Other Information** Enter

**Type Other Information**  Clean Cellulosic Biomass Enter **Biomass Combustor**  **Information Unit ID** 

**Design Category** Enter other design category **Capacity CHP**  **Contact Name**  Keith Mulka/Tammi Van Til

**Phone** 989-742-4571/616-454-9647 **e-mail** tvantil@comcast.net 

## Biomass Power Association - Emission Source Data Collection Form **Facility Information**  **Name** Hillman Power Company

**Street Address** 750 Progress Street **City, State, Zip** Hillman MI 49707Jul-98 BF1/AF2 - 90/10% Lead EPA Method 29 2 15.4 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 90/10% Lead EPA Method 29 3 21 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 85/15% Lead EPA Method 29 1 11.7ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 85/15% Lead EPA Method 29 2 11.5 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 85/15% Lead EPA Method 29 3 8.9 ug/dscm @ 7% O2 Jul-98 BF1/AF2-95/5% Mercury EPA Method 29 1 0.065ug/dscm @ 7% O2 Jul-98 BF1/AF2-95/5% Mercury EPA Method 29 2 0.14 ug/dscm @ 7% O2 Jul-98 BF1/AF2-95/5% Mercury EPA Method 29 3 0.1 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 90/10% Mercury EPA Method 29 1 0.32 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 90/10% Mercury EPA Method 29 2 0.27ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 90/10% Mercury EPA Method 29 3 0.03 ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 85/15% Mercury EPA Method 29 1 0.039ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 85/15% Mercury EPA Method 29 2 0.030ug/dscm @ 7% O2 Jul-98 BF1/AF2 - 85/15% Mercury EPA Method 29 3 0.025ug/dscm @ 7% O2 **Footnotes**

**Other Information**2003 and 2010 data not corrected to O2. 2003 O2 = 5.7 to 5.8%. 1998 O2 = 5.6 to 6.3%. 1998 PM data is PM10 (front half)EUBOILER Stoker /Other

230 Select UoM No

**ID HHV**  **HHV UoM BF1**  4400 BTU/lb **BF2** 9500 BTU/lb **BF3** Enter BTU/lb **BF4** Enter BTU/lb **ID HHV**  **HHV UoM AF1**  1020 BTU/scf **AF2** 13500 BTU/lb **AF3** Enter Select

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM**  Enter BF1/AF2 - 92%/8% Cadmium EPA Method 29 1 2.3 ug/dscm @ 7% O2 Enter Enter BF1/AF2 - 92%/8% Cadmium EPA Method 29 2 1.31 ug/dscm @ 7% O2 Enter Enter BF1/AF2 - 92%/8% Cadmium EPA Method 29 3 2.24 ug/dscm @ 7% O2 Enter Enter BF1/AF2/BF2 -73/6/21%Cadmium EPA Method 29 1 2.78 ug/dscm @ 7% O2 Enter Enter BF1/AF2/BF2 -73/6/21%Cadmium EPA Method 29 2 2.68 ug/dscm @ 7% O2 Enter Enter BF1/AF2/BF2 -73/6/21%Cadmium EPA Method 29 3 3.07ug/dscm @ 7% O2 Enter Enter BF1/AF2 - 92%/8% Lead EPA Method 29 1 11.06ug/dscm @ 7% O2 Enter Enter BF1/AF2 - 92%/8% Lead EPA Method 29 2 8.74 ug/dscm @ 7% O2 Enter Enter BF1/AF2 - 92%/8% Lead EPA Method 29 3 10.29ug/dscm @ 7% O2 Enter Enter BF1/AF2/BF2 -73/6/21%Lead EPA Method 29 1 5.57ug/dscm @ 7% O2 Enter Enter BF1/AF2/BF2 -73/6/21%Lead EPA Method 29 2 4.47ug/dscm @ 7% O2 Enter Enter BF1/AF2/BF2 -73/6/21%Lead EPA Method 29 3 5.26 ug/dscm @ 7% O2 Enter BF1/AF2 - 92%/8% Mercury EPA Method 29 1 <0.04ug/dscm @ 7% O2 BF1/AF2 - 92%/8% Mercury EPA Method 29 2 <0.04ug/dscm @ 7% O2 BF1/AF2 - 92%/8% Mercury EPA Method 29 3 <0.04ug/dscm @ 7% O2 BF1/AF2/BF2 -73/6/21%Mercury EPA Method 29 1 <0.04ug/dscm @ 7% O2 BF1/AF2/BF2 -73/6/21%Mercury EPA Method 29 2 <0.04ug/dscm @ 7% O2 BF1/AF2/BF2 -73/6/21%Mercury EPA Method 29 3 <0.04ug/dscm @ 7% O2 BF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 1 1.32ppmdv @7% O2 May-99 May-99 May-99 May-99 May-99 May-99 May-99 May-99 May-99 May-99 May-99 May-99 Enter **Emission Testing Results**  **Date of Test** May-99 May-99 May-99 May-99 May-99 May-99 May-99 **Air Pollution Control**  **Equipment Type**  **Additional Information**

ESP Enter Select Enter Select Enter Select **Auxiliary/Other Fuels**  **Type Other Information**  Natural gas Enter

Select Enter Tire Derived Fuel Enter Enter Enter **CHP Other Information**  Enter

Creosote/RRTies Enter **Biomass Fuels Type**  **Other Information** Clean Cellulosic Biomass Enter **e-mail** tvantil@comcast.net **Biomass Combustor**  **Information Unit ID** 

**Design Category** Enter other design category **Capacity City, State, Zip**  Lincoln, MI 48742 **Name** Neil Taratuta/Tammi Van Til **Phone** 989-736-6618/616-454-9647 

## Biomass Power Association - Emission Source Data Collection Form **Facility Information**  **Name** Viking Energy Lincoln Power Station

**Street Address** 509 W. State StreetBF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 2 1.70ppmdv @7% O2 BF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 3 1.53ppmdv @7% O2 BF1/AF2/BF2 -73/6/21%Hydrogen chloride EPA Method 26A 1 1.11 ppmdv @7% O2 BF1/AF2/BF2 -73/6/21%Hydrogen chloride EPA Method 26A 2 1.50ppmdv @7% O2 BF1/AF2/BF2 -73/6/21%Hydrogen chloride EPA Method 26A 3 1.02ppmdv @7% O2 Aug-05 BF1/AF2 - 92%/8% Lead EPA Method 29 1 12.6 ug/dscm @ 7% O2 Aug-05 BF1/AF2 - 92%/8% Lead EPA Method 29 2 9.83 ug/dscm @ 7% O2 Aug-05 BF1/AF2 - 92%/8% Lead EPA Method 29 3 8.83 ug/dscm @ 7% O2 Aug-05 BF1/AF2 - 92%/8% Mercury EPA Method 29 1 <0.353ug/dscm @ 7% O2 Aug-05 BF1/AF2 - 92%/8% Mercury EPA Method 29 2 <0.353ug/dscm @ 7% O2 Aug-05 BF1/AF2 - 92%/8% Mercury EPA Method 29 3 <0.353ug/dscm @ 7% O2 Aug-05 BF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 1 0.692ppmdv @7% O2 Aug-05 BF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 2 1.03ppmdv @7% O2 Aug-05 BF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 3 0.99ppmdv @7% O2 Aug-05 BF1/AF2 - 92%/8% Particulate matter (front half catch) EPA Method 201A 1 30.8 mg/dscm @ 7% O2 Aug-05 BF1/AF2 - 92%/8% Particulate matter (front half catch) EPA Method 201A 2 31.9 mg/dscm @ 7% O2 Aug-05 BF1/AF2 - 92%/8% Particulate matter (front half catch) EPA Method 201A 3 34.7mg/dscm @ 7% O2 Oct-10 BF1/AF2 - 92%/8% Particulate matter (front half catch) EPA Method 29 1 52.2 mg/dscm @ 7% O2 Oct-10 BF1/AF2 - 92%/8% Particulate matter (front half catch) EPA Method 30 2 26.8 mg/dscm @ 7% O2 Oct-10 BF1/AF2 - 92%/8% Particulate matter (front half catch) EPA Method 31 3 24.1 mg/dscm @ 7% O2 Oct-10 BF1/AF2 - 92%/8% Lead EPA Method 29 1 10.6 ug/dscm @ 7% O2 Oct-10 BF1/AF2 - 92%/8% Lead EPA Method 29 2 11 ug/dscm @ 7% O2 Oct-10 BF1/AF2 - 92%/8% Lead EPA Method 29 3 10.5 ug/dscm @ 7% O2 Oct-10 BF1/AF2 - 92%/8% Mercury EPA Method 29 1 <0.648ug/dscm @ 7% O2 Oct-10 BF1/AF2 - 92%/8% Mercury EPA Method 29 2 <0.648ug/dscm @ 7% O2 Oct-10 BF1/AF2 - 92%/8% Mercury EPA Method 29 3 <0.648ug/dscm @ 7% O2 Oct-10 BF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 1 0.45ppmdv @7% O2 Oct-10 BF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 2 0.41 ppmdv @7% O2 Oct-10 BF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 3 0.387ppmdv @7% O2 **Footnotes**

**Other Information**Used conversion factor of 0.832 to convert HCl results provided in mg/m3 to ppm. The 1999 stack test report does not indicated that the data was

corrected to O2; actual O2 in 1999 ranged from 5.6 to 6.6%. 2005 and 2010 lead emissions not corrected for O2.

May-99 May-99 May-99 May-99 May-99Yes

Boiler Stoker / Other 530 MMBTU/hr No

**ID HHV**  **HHV UoM BF1**  4400 BTU/lb **BF2** 6000 BTU/lb **BF3** 5000 BTU/lb **BF4** 4000 BTU/lb **ID HHV**  **HHV UoM AF1**  1020 BTU/scf **AF2**TDF 13500 BTU/lb **AF3** Enter Select

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM**  Enter BF1/BF2/BF3/BF4-70/5/5/20% Hydrogen chloride EPA Method 26A 1 31.4ppmdv @7% O2 Enter Enter BF1/BF2/BF3/BF4-70/5/5/20% Hydrogen chloride EPA Method 26A 2 51.1 ppmdv @7% O2 Enter Enter BF1/BF2/BF3/BF4-70/5/5/20% Hydrogen chloride EPA Method 26A 3 44.1 ppmdv @7% O2 Enter Enter BF1/BF2/BF3/BF4-70/5/5/20% Lead EPA Method 29 1 3.72 ug/dscm @ 7% O2 Enter Enter BF1/BF2/BF3/BF4-70/5/5/20% Lead EPA Method 29 2 3.48 ug/dscm @ 7% O2 Enter Enter BF1/BF2/BF3/BF4-70/5/5/20% Lead EPA Method 29 3 3.3 ug/dscm @ 7% O2 Enter Enter BF1/BF2/BF3/BF4-70/5/5/20% Mercury EPA Method 29 1 <0.43ug/dscm @ 7% O2 Enter Enter BF1/BF2/BF3/BF4-70/5/5/20% Mercury EPA Method 29 2 <0.43ug/dscm @ 7% O2 Enter Enter BF1/BF2/BF3/BF4-70/5/5/20% Mercury EPA Method 29 3 <0.43ug/dscm @ 7% O2 Enter Oct-09 BF1/BF2/BF3/BF4/AF2-83/5/5/5/2%Cadmium EPA Method 29 1 0.52 ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4/AF2-83/5/5/5/2%Cadmium EPA Method 29 2 0.58 ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4/AF2-83/5/5/5/2%Cadmium EPA Method 29 3 0.35 ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4/AF2-83/5/5/5/2%Lead EPA Method 29 1 9.87ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4/AF2-83/5/5/5/2%Lead EPA Method 29 2 11.19ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4/AF2-83/5/5/5/2%Lead EPA Method 29 3 7.07ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4/AF2-83/5/5/5/2%Mercury EPA Method 29 1 0.472ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4/AF2-83/5/5/5/2%Mercury EPA Method 29 2 0.585ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4/AF2-83/5/5/5/2%Mercury EPA Method 29 3 0.432ug/dscm @ 7% O2 May-06 May-06 May-06 May-06 May-06 **Emission Testing Results (insert**  **more lines of cells as needed)**  **Date of Test**

May-06 May-06 ESP

May-06 Select

May-06 Select Enter **Auxiliary/Other Fuels**  **Type Other Information**  Natural Gas Enter

Enter **Air Pollution Control**  **Equipment** Enter **Type** Secondary Mill

Enter Clean Construction Enter Manures wood chip animal bedding contaminated with manure

**Additional Information** SNCR Enter **Capacity**

**Biomass Fuels Type**  **Other Information** Clean Cellulosic Biomass including utility line clearing **Other Information** Enter **CHP?** 616-454-9647/810-785-4144

Select furniture manufacturing waste, pallet type material tvantil@comcast.net **Biomass Combustor**  **Information Unit ID** 

**Design Category** Enter other design category **Major HAP facility?** Flint, MI 48505

**Contact Name**  Tammi Van Til/Ted Webster

**Phone City, State, Zip** 

**e-mail** 

## CBEA/BPA - Emission Source Data Collection Form **Facility Information**  **Name** Genesee Power Station

**Street Address** 5310 N. Dort HighwayOct-09 BF1/BF2/BF3/BF4/AF2-83/5/5/5/2%Hydrogen chloride EPA Method 26A 1 13.9ppmdv @7% O2 Oct-09 BF1/BF2/BF3/BF4/AF2-83/5/5/5/2%Hydrogen chloride EPA Method 26A 2 16.5ppmdv @7% O2 Oct-09 BF1/BF2/BF3/BF4/AF2-83/5/5/5/2%Hydrogen chloride EPA Method 26A 3 14.1 ppmdv @7% O2 Oct-09 BF1/BF2/BF3/BF4 - 85/5/5/5 Cadmium EPA Method 29 1 1.19 ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4 - 85/5/5/5 Cadmium EPA Method 29 2 1.81 ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4 - 85/5/5/5 Cadmium EPA Method 29 3 2.18 ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4 - 85/5/5/5 Lead EPA Method 29 1 39.92ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4 - 85/5/5/5 Lead EPA Method 29 2 51.14ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4 - 85/5/5/5 Lead EPA Method 29 3 64.25ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4 - 85/5/5/5 Mercury EPA Method 29 1 0.05 ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4 - 85/5/5/5 Mercury EPA Method 29 2 0.081ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4 - 85/5/5/5 Mercury EPA Method 29 3 0.092ug/dscm @ 7% O2 Oct-09 BF1/BF2/BF3/BF4 - 85/5/5/5 Hydrogen chloride EPA Method 26A 1 12.1 ppmdv @7% O2 Oct-09 BF1/BF2/BF3/BF4 - 85/5/5/5 Hydrogen chloride EPA Method 26A 2 20.4ppmdv @7% O2 Oct-09 BF1/BF2/BF3/BF4 - 85/5/5/5 Hydrogen chloride EPA Method 26A 3 17.2ppmdv @7% O2 **Footnotes** Amt of secondary wood and clean construction type waste is estimated

**Other Information**2009 data not corrected to 7% O2 (O2 data missing from report)no

Boiler Stoker / Other 530 MMBTU/hr No

**ID HHV**  **HHV UoM BF1**  4400 BTU/lb **BF2** 8000 BTU/lb **BF3** Enter Select **BF4** Enter Select **ID HHV**  **HHV UoM AF1**  1020 BTU/scf **AF2** 13500 BTU/lb **AF3** Enter Select

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM**  Enter BF1/BF2/AF2-97/1/2% Cadmium EPA Method 29 1 0.53 ug/dscm @ 7% O2 Enter Enter BF1/BF2/AF2-97/1/2% Cadmium EPA Method 29 2 0.93 ug/dscm @ 7% O2 Enter Enter BF1/BF2/AF2-97/1/2% Cadmium EPA Method 29 3 0.67ug/dscm @ 7% O2 Enter Enter BF1/BF2/AF2-97/1/2% Lead EPA Method 29 1 4.7 ug/dscm @ 7% O2 Enter Enter BF1/BF2/AF2-97/1/2% Lead EPA Method 29 2 3.9 ug/dscm @ 7% O2 Enter Enter BF1/BF2/AF2-97/1/2% Lead EPA Method 29 3 1.1 ug/dscm @ 7% O2 Enter Enter BF1/BF2 99/1% Cadmium EPA Method 29 1 1.727ug/dscm @ 7% O2 Enter Enter BF1/BF2 99/1% Cadmium EPA Method 29 2 1.413ug/dscm @ 7% O2 Enter Enter BF1/BF2 99/1% Cadmium EPA Method 29 3 1.2 ug/dscm @ 7% O2 Enter Enter BF1/BF2 99/1% Lead EPA Method 29 1 53.464ug/dscm @ 7% O2 Enter Enter BF1/BF2 99/1% Lead EPA Method 29 2 21.196ug/dscm @ 7% O2 Enter Enter BF1/BF2 99/1% Lead EPA Method 29 3 8.141ug/dscm @ 7% O2 Enter BF1/BF2 99/1% Mercury EPA Method 29 1 0.946ug/dscm @ 7% O2 BF1/BF2 99/1% Mercury EPA Method 29 2 1.016ug/dscm @ 7% O2 BF1/BF2 99/1% Mercury EPA Method 29 3 0.257ug/dscm @ 7% O2 BF1/BF2/AF2-92/1/7% Cadmium EPA Method 29 1 5.301ug/dscm @ 7% O2 BF1/BF2/AF2-92/1/7% Cadmium EPA Method 29 2 3.615ug/dscm @ 7% O2 BF1/BF2/AF2-92/1/7% Cadmium EPA Method 29 3 6.584ug/dscm @ 7% O2 Apr-99 Apr-99 Apr-99 Apr-99 Apr-99 Apr-99 Apr-99 Apr-99 Jul-09 Jul-09 Apr-99 Apr-99 Apr-99 Apr-99 Select Enter Select Enter **Emission Testing Results (insert**  **more lines of cells as needed)**  **Date of Test** Jul-09 Jul-09 Jul-09 Jul-09 Enter Select Enter **Air Pollution Control**  **Equipment Type**  **Additional Information**

SNCR Enter ESP Enter Enter - see instructions Enter Enter - see instructions Enter **Auxiliary/Other Fuels**  **Type Other Information**  Natural Gas Enter TDF **Other Information** Enter **Biomass Fuels Type**  **Other Information** Clean Cellulosic Biomass includes sawdust/sawmill waste Secondary Mill Residuals flakes from OSB manufacturer tvantil@comcast.net **Biomass Combustor**  **Information Unit ID** 

**Design Category** Enter other design category **Capacity CHP?**  **Major HAP facility? Contact**  **Name** Tammi Van Til/Phil Lewis

**Phone** 616-454-9647/989-348-4575 **e-mail** 

## CBEA/BPA - Emission Source Data Collection Form **Facility Information**  **Name** Grayling Generating Station

**Street Address** 4400 West Four Mile Road **City, State, Zip** Grayling, MI 49738BF1/BF2/AF2-92/1/7% Lead EPA Method 29 1 19.437ug/dscm @ 7% O2 BF1/BF2/AF2-92/1/7% Lead EPA Method 29 2 16.267ug/dscm @ 7% O2 BF1/BF2/AF2-92/1/7% Lead EPA Method 29 3 26.337ug/dscm @ 7% O2 BF1/BF2/AF2-92/1/7% Mercury EPA Method 29 1 0.053ug/dscm @ 7% O2 BF1/BF2/AF2-92/1/7% Mercury EPA Method 29 2 0.036ug/dscm @ 7% O2 BF1/BF2/AF2-92/1/7% Mercury EPA Method 29 3 <0.04ug/dscm @ 7% O2 **Footnotes** 2009 using a single flow rate, not corrected for O2. 1999 data not corrected for O2, running 6% O2.

**Other Information**EPA has test data from 2005 (submitted with 2008 ICR) Apr-99 Apr-99 Apr-99 Apr-99 Apr-99 Apr-99no

Boiler 

## CBEA/BPA - Emission Source Data Collection Form **Facility Information**  **Name** Viking Energy of McBain

**Street Address** 6751 Gerwoude Drve **City, State, Zip** McBain, MI **Major HAP facility? Contact**  **Name** Tammi Van Til/Tom Vine

**Phone** 616-454-9647/231-825-2772 **e-mail** tvantil@comcast.net **Biomass Unit ID**  Boiler Stoker / Other 230 MMBtu/hr

no

**ID HHV**  **HHV UoM BF1**  4400 BTU/lb **BF2** 9500 BTU/lb **BF3** Enter Select **BF4** Enter Select **ID HHV**  **HHV UoM AF1**  1020 BTU/scf **AF2** 13500 BTU/lb **AF3** Enter Select **Biomass Combustor**  **Information Unit ID** 

**Design Category** Enter other design category **Capacity CHP?**  **Other Information** Enter **Biomass Fuels Type**  **Other Information** Clean Cellulosic Biomass Enter Creosote/RRTies Enter Enter - see instructions Enter Enter - see instructions Enter **Auxiliary/Other Fuels**  **Type Other Information**  Natural gas Enter Tire Derived Fuel Enter Select Enter **AF3** Enter Select

**Report ID Fuel / % Mix (see instr.)**  **Pollutant Test Method**  **Run # Result**  **UoM Alt. UoM**  Enter BF1/AF2 - 92%/8% Lead EPA Method 29 1 24 ug/dscm @ 7% O2 Enter Enter BF1/AF2 - 92%/8% Lead EPA Method 29 2 30.8 ug/dscm @ 7% O2 Enter Enter BF1/AF2 - 92%/8% Lead EPA Method 29 3 32.5 ug/dscm @ 7% O2 Enter Enter BF1/AF2 - 92%/8% Mercury EPA Method 29 1 <0.802ug/dscm @ 7% O2 Enter Enter BF1/AF2 - 92%/8% Mercury EPA Method 29 2 <0.802ug/dscm @ 7% O2 Enter Enter BF1/AF2 - 92%/8% Mercury EPA Method 29 3 <0.802ug/dscm @ 7% O2 Enter BF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 1 0.53ppmdv @7% O2 Select Enter **Air Pollution Control**  **Equipment Type**  **Additional Information**

ESP Enter Select Enter

**Emission Testing Results (insert**  **more lines of cells as needed)**  **Date of Test** Oct-10 Oct-10 Oct-10 Oct-10 Oct-10 Oct-10 Select

Oct-10 Enter Select Enter

BF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 1 0.53ppmdv @7% O2 BF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 2 0.94ppmdv @7% O2 BF1/AF2 - 92%/8% Hydrogen chloride EPA Method 26A 3 0.87ppmdv @7% O2 **Footnotes**

**Other Information**This plant and Lincoln are GDF Suez facilities. Oct-10 Oct-10 Oct-10 Lead and HCl data from 10/10 is not corrected to 7% O2, boiler typically operates 5.5 to 6% O2.