## Instructions for completing the Fuel Material Analysis Information

This Information Collection Request (ICR) spreadsheet is intended to collect information about chemical analyses of fuels used fossil fuel burning power plants. Constituents of concern are: mercury, chlorine, fluorine, and metals, such as antimony, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, and selenium. This spreadsheet is intended to be used for one boiler of one facility but is designed to allow multiple (up to 4) fuel analyses at that specific boiler. Th number of analyses would coincide with one boiler where emissions testing for all 4 HAP surrogates were being tested. Data for multiple boilers should be handled by using separate spreadsheets. Fields that are highlighted in yellow are required fields. Green highlighted cells should be filled using the drop

- down boxes, included. Gray fields are automatically filled from other fields.

Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_Fuels_Testing.xls (example: 8100_Unit_2_Fuels_Testing.xls).

Please refer to the following steps when using these spreadsheets.
1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet. 2. Please enter the test date on the Boiler Information worksheet. 3. Please choose the type of fuel being sampled using the drop

- down in the fuel column of the Boiler Information worksheet. If you choose "other", please provide a description of the fuel in the Other Fuel Description column. 4. Please provide the analysis method for each constituent in the Analysis Methods worksheet. For example: "ASTM D5865 04". 5. Please check the Units of Measure tables for HHV, Metals, and Cl/Fl in the Picklist worksheet (orange tab). If the units
measure that you plan to report are not found in the Units of measure table, please fill them in the blank, orange highlighted, cell in each table. This allows you to choose the units of measure in the Fuels Sample Results worksheet. 6. Select the HAPs Test Group (i.e., HAP surrogate) for which the tab's data reflects (o range highlighted cell) 7. Provide the Sample Number and Sample Date on the Fuels Sample Results worksheet. You must provide a minimum of 3 composite samples consisting of 3 combined grab samples each, but you are not limited to that number if you have collected
more. 8. Provide the results of the analyses for each constituent requested. Use the drop

- down boxes to fill in the units of
measure.

## Information
This Information Collection Request (ICR) spreadsheet is intended to collect information about chemical analyses of fuels used fossil fuel burning power plants. Constituents of concern are: mercury, chlorine, fluorine, and metals, such as antimony, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, and selenium. This spreadsheet is intended to be used for one boiler of one facility but is designed to allow multiple (up to 4) fuel analyses at that specific boiler. Th is number of analyses would coincide with one boiler where emissions testing for all 4 HAP surrogates were being tested. Fields that are highlighted in yellow are down boxes, included. Gray fields are automatically

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet.

down in the fuel column of the Boiler Information worksheet. If you choose "other", please provide a description of the fuel in the Other Fuel Description column. 4. Please provide the analysis method for each constituent in the Analysis Methods worksheet. For example: "ASTM D5865

- 5. Please check the Units of Measure tables for HHV, Metals, and Cl/Fl in the Picklist worksheet (orange tab). If the units of
measure that you plan to report are not found in the Units of measure table, please fill them in the blank, orange highlighted, cell in each table. This allows you to choose the units of measure in the Fuels Sample Results worksheet. range highlighted cell)

. 7. Provide the Sample Number and Sample Date on the Fuels Sample Results worksheet. You must provide a minimum of 3 composite samples consisting of 3 combined grab samples each, but you are not limited to that number if you have collected

down boxes to fill in the units of

### EIA

Facility Code Facility Name Boiler ID Fuel Type 1

562 Middletown Power Station 2 

## No.6 Fuel Oil (residual or bunker C)

### Fuel Type 2 Fuel Type 3 Other Fuel Description 

## No.6 Fuel Oil (residual or bunker C)

### EIA

Facility Code Facility Name Boiler ID Basis An alyte



## 562 Middletown Power Station 2 As Received Higher Heating Value 

## 562 Middletown Power Station 2 As Received % Moisture 

## 562 Middletown Power Station 2 As Received % Ash 

## 562 Middletown Power Station 2 As Received % Sulfur 

## 562 Middletown Power Station 2 Dry basis Higher Heating Value 

## 562 Middletown Power Station 2 Dry basis % Ash 

## 562 Middletown Power Station 2 Dry basis % Sulfur 

## 562 Middletown Power Station 2 Dry basis Antim ony 

## 562 Middletown Power Station 2 Dry basis Arsenic 

## 562 Middletown Power Station 2 Dry basis Bery llium 

## 562 Middletown Power Station 2 Dry basis Cadmium 

## 562 Middletown Power Station 2 Dry basis Chlorine 

## 562 Middletown Power Station 2 Dry basis Chromium 

## 562 Middletown Power Station 2 Dry basis Cobalt 

## 562 Middletown Power Station 2 Dry basis Fluorine 

## 562 Middletown Power Station 2 Dry basis Lead 

## 562 Middletown Power Station 2 Dry basis Manganese 

## 562 Middletown Power Station 2 Dry basis Mercury 

## 562 Middletown Power Station 2 Dry basis Nickel 

## 562 Middletown Power Station 2 Dry basis Selenium

### An alysis M ethod for each A nalyte

(example: ASTM D5865-04) 

## ASTM D240 ASTM D6304 ASTM D482 ASTM D1552 ASTM D240 ASTM D482 ASTM D1552 SW846-7740 SW846-7060 SW846-6010B SW846-6010B SW846-9076 SW846-6010B SW846-6010B

SW846-6010B SW846-6010B SW846-7470 SW846-6010B SW846-7740EIA

Facility Code Facility

Name Boiler ID 

### HA Ps Test Group 

## 562 Middletown Power Station 2 Mercury and non-mercury metalic HAPs

Sample Number (minimum of 3 composite samples) Test Start Date

(MM/DD/YYYY) Test Stop Date

(MM/DD/YYYY) Higher Heating Value (HHV) (as received) HHV Units 

## Run 1 (Comp. R1 to R5)

2/24/2010 2/24/2010 18831 Btu/lb Fuel Testing Results

## Mercury and non-mercury metalic HAPs

% Moisture (as received) % A

sh (as received) % Sulfur

(as received) Higher

Heating Value (HHV) (Dry Basis) HHV Units % A sh (Dry Basis) % Sulfur

(Dry Basis) 

## 0 0.06 0.28 18831 Btu/lb 0.06 0.28Chlorine

(Dry Basis) Chlorine

Units Mercury

(Dry Basis) Mercury

Units An timony

(Dry Basis) An timony

Units Arsenic (Dry

Basis) Arsenic

Units Bery llium

(Dry Basis) 

## 21.2 ppm [<0.20] μg/g 1.02 μg/g [<0.50] μg/g [<0.50]Bery llium

Units Cadmium

(Dry Basis) Cadmium

Units Chromium

(Dry Basis) Chromium

Units Lead (Dry

Basis) Lead Units Manganese (Dry Basis) Manganese

Units 

## μg/g [<0.50] μg/g [<0.50] μg/g 0.63 μg/g 1.92 μg/gNickel (Dry

Basis) Nickel Units Selenium (Dry Basis) Selenium

Units Fluorine

(Dry Basis) Fluorine

Units Cobalt (Dry

Basis) Cobalt Units Total Moisture 

## 20.8 μg/g [<0.50] μg/g 1.34 μg/g 0 Proximate Analy

ses, % by

wt

### Note the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Volatiles As h Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur



## 0.06 87.38 11.96 0.32 0.28 Proximate A naly

ses, % by

wt Ultimate Analy ses, % by

wtOxygen



## [<0.10]EIA

Facility Code Facility

Name Boiler ID 

### HA Ps Test Group 

## 562 Middletown Power Station 2 Acid gas HAPs

Sample Number (minimum of 3 composite samples) Test Start Date

(MM/DD/YYYY) Test Stop Date

(MM/DD/YYYY) Higher Heating

Value (HHV) (as received) HHV Units 

## Run 1 (Comp. R1 to R5)

2/24/2010 2/24/2010 18831 Btu/lb Fuel Testing Results% Moisture

(as received) % A

sh (as received) % Sulfur

(as received) Higher

Heating Value (HHV) (Dry Basis) HHV Units % A sh (Dry Basis) % Sulfur

(Dry Basis) 

## 0 0.06 0.28 18831 Btu/lb 0.06 0.28Chlorine

(Dry Basis) Chlorine

Units Mercury

(Dry Basis) Mercury

Units An timony

(Dry Basis) An timony

Units Arsenic (Dry

Basis) Arsenic

Units Bery llium

(Dry Basis) 

## 21.2 ppm [<0.20] μg/g 1.02 μg/g [<0.50] μg/g [<0.50]Bery llium

Units Cadmium

(Dry Basis) Cadmium

Units Chromium

(Dry Basis) Chromium

Units Lead (Dry

Basis) Lead Units Manganese (Dry Basis) Manganese

Units 

## μg/g [<0.50] μg/g [<0.50] μg/g 0.63 μg/g 1.92 μg/gNickel (Dry

Basis) Nickel Units Selenium (Dry Basis) Selenium

Units Fluorine

(Dry Basis) Fluorine

Units Cobalt (Dry

Basis) Cobalt Units 

## 20.8 μg/g [<0.50] μg/g 1.34 μg/g

### Note the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Total Moisture Volatiles As h Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur



## 0 0.06 87.38 11.96 0.32 0.28 Proximate A naly

ses, % by

wt Ultimate Analy ses, % by

wt

### Note the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Oxygen 

## [<0.10]EIA

Facility Code Facility

Name Boiler ID 

### HA Ps Test Group 

## 562 Middletown Power Station 2 Non-dioxin/furan organic HAPs

Sample Number (minimum of 3 composite samples) Test Start Date

(MM/DD/YYYY) Test Stop Date (MM/DD/YYYY) Higher Heating Value (HHV) (as received) HHV Units 

## Run 1 (Comp. R1 to R5)

2/24/2010 2/24/2010 18831 Btu/lb Fuel Testing Results% Moisture

(as received) % A

sh (as received) % Sulfur

(as received) Higher

Heating Value (HHV) (Dry Basis) HHV Units % A sh (Dry Basis) % Sulfur

(Dry Basis) 

## 0 0.06 0.28 18831 Btu/lb 0.06 0.28Chlorine

(Dry Basis) Chlorine

Units Mercury

(Dry Basis) Mercury

Units An timony

(Dry Basis) An timony

Units Arsenic (Dry

Basis) Arsenic

Units Bery llium

(Dry Basis) 

## 21.2 ppm [<0.20] μg/g 1.02 μg/g [<0.50] μg/g [<0.50]Bery llium

Units Cadmium

(Dry Basis) Cadmium

Units Chromium

(Dry Basis) Chromium

Units Lead (Dry

Basis) Lead Units Manganese (Dry Basis) Manganese

Units 

## μg/g [<0.50] μg/g [<0.50] μg/g 0.63 μg/g 1.92 μg/gNickel (Dry

Basis) Nickel Units Selenium (Dry Basis) Selenium

Units Fluorine

(Dry Basis) Fluorine

Units Cobalt (Dry

Basis) Cobalt Units Total Moisture 

## 20.8 μg/g [<0.50] μg/g 1.34 μg/g 0 Proximate Analy

ses, % by

wt

### Note the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Volatiles As h Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur Oxygen



## 0.06 87.38 11.96 0.32 0.28 [<0.10] Proximate A naly

ses, % by

wt Ultimate Analy ses, % by

wtEIA

Facility Code Facility

Name Boiler ID 

### HA Ps Test Group 

## 562 Middletown Power Station 2 Dioxin/furan HAPs

Sample Number (minimum of 3 composite samples) Test Start Date

(MM/DD/YYYY) Test Stop Date

(MM/DD/YYYY) Higher Heating Value (HHV) (as received) HHV Units 

## Run 1 (Comp. R1 to R5) 2/24/2010 2/24/2010 18831 Btu/lb Fuel Testing Results% Moisture

(as received) % A

sh (as received) % Sulfur

(as received) Higher

Heating Value (HHV) (Dry Basis) HHV Units % A sh (Dry Basis) % Sulfur

(Dry Basis) 

## 0 0.06 0.28 18831 Btu/lb 0.06 0.28Chlorine

(Dry Basis) Chlorine

Units Mercury

(Dry Basis) Mercury

Units An timony

(Dry Basis) An timony

Units Arsenic (Dry

Basis) Arsenic

Units Bery llium

(Dry Basis) 

## 21.2 ppm [<0.20] μg/g 1.02 μg/g [<0.50] μg/g [<0.50]Bery llium

Units Cadmium

(Dry Basis) Cadmium

Units Chromium

(Dry Basis) Chromium

Units Lead (Dry

Basis) Lead Units Manganese (Dry Basis) Manganese

Units 

## μg/g [<0.50] μg/g [<0.50] μg/g 0.63 μg/g 1.92 μg/gNickel (Dry

Basis) Nickel Units Selenium (Dry Basis) Selenium

Units Fluorine

(Dry Basis) Fluorine

Units Cobalt (Dry

Basis) Cobalt Units Total Moisture 

## 20.8 μg/g [<0.50] μg/g 1.34 μg/g 0 Proximate Analy ses, % by

wt

### Note the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Volatiles As h Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur Oxygen



## 0.06 87.38 11.96 0.32 0.28 [<0.10] Proximate A naly

ses, % by

wt Ultimate Analy ses, % by

wt

### Units of Measure Tables: Please do not modify these tables, except to add your own unit of measure to the

Fuel Units of Measure - HHV anthracite Btu/lb bitum inous Btu/gallon subbituminous lignite coal refuse (culm or gob) No.2 Fuel Oil (distillate) No.6 Fuel Oil (residual or bunker C) Units of Measure - Metals sy nfuel mg /g petroleum coke μg/g other mg /Kg

### Units of Measure Tables: Please do not modify these tables, except to add your own unit of measure to the orange hightlighted cell, if necessary

.

Units of Measure - Cl, Fl % ppm