### 10160 Federal Register / Vol. 57, No. 57 / Tuesday, March 24, 1992 / Notices

Office of Conservation and Renewable Energy [Case No. F-0281 

### Energy Conservation Program for Consumer Products ; Decision and Order Granting a Waiver From the Furnace Test Procedure to Armstrong Air Conditioning, Inc.

AGENCY: Office of Conservation and Renewable Energy, Department of Energy. ACTION : Decision and order.

SUMMARY : Notice is given of the Decision and Order (Case No. F-028) granting a Waiver to Armstrong Air Conditioning, Inc. (Armstrong), from the existing Department of Energy (DOE) test procedure for furnaces. The Department is granting Armstrong its Petition for Waiver regarding blower time delay in calculation of Annual Fuel Utilization Efficiency (AFUE) for its GRTC series of rooftop furnaces. FOR FURTHER INFORMATION CONTACT: Cyrus H. Nasseri, U.S. Department of Energy, Office of Conservation andRenewable Energy, Mail Station CE43, Forrestal Building, 1000 Independence Avenue, SW., Washington, DC 20585, (202) 588-9127. Eugene Margolis, Esq., U.S. Department of Energy, Office of General Counsel, Mail Station GC-41, Forrestal Building, 1000 Independence Avenue, SW., Washington, DC 20585, (202) 586-9507. SUPPLEMENTARY INFORMATION: In accordance with 10 CFR 430.27(g), notice is hereby given of the issuance of the Decision and Order as set out below. In the Decision and Order. Armstrong has been granted a Waiver for its GRTC series of rooftop furnaces, permitting the company to use an alternate test method in determining AFUE. Issued in Washington, DC, March 11. 1992. 1. Michael Davis, Assistant Secretary. Conservation and Renewable Energy.


### Decision and Order In the matter of. Armstrong Air Conditioning, Inc. (Case No. F-028).
Background The Energy Conservation Program for Consumer Products (other than automobiles) was established pursuant to the Energy Policy and Conservation Act (EPCA), Public Law 94-163, 89 Stat. 917, as amended by the National Energy Conservation Policy Act (NECPA), Public Law 95-819, 92 Stat. 3266, the National Appliance Energy Conservation Act of 1987 (NAECA), Public Law 100-12, and the National Appliance Energy Conservation Amendments of 1988 (NAECA 1988), Public Law 100-357, which requires DOE to prescribe standardized test procedures to measure the energy consumption of certain consumer products, including furnaces. The intent of the test procedures is to provide a comparable measure of energy consumption that will assist consumers in making purchasing decisions. These test procedures appear at 10 CFR part 430, subpart B. DOE amended the presscribed test procedures by adding 10 CFR 430.27 to create a waiver process. 45 FR 64108, September 26,1980. Thereafter, DOE further amended its appliance test procedure waiver process to allow the Assistant Secretary for Conservation and Renewable Energy (Assistant Secretary) to grant an Interim Waiver from test procedure requirements to manufacturers that have petitioned DOE for a waiver of such prescribed test procedures. 51 FR 42823, November 25, 1986. 

### The waiver process allows the Assistant Secretary to waive temporarily test procedures for a particular basic model when a petitioner shows that the basic model contains one or more design characteristics which prevent testing according to the prescribed test procedures or when the prescribed test procedures may evaluate the basic model in a manner so unrepresentative of its true energy consumption as to provide materially inaccurate comparative data. Waivers generally remain in effect until final test procedure amendments become effective, resolving the problem that is the subject of the waiver. The Interim Waiver provisions added by the 1986 amendment allow the Assistant Secretary to grant an Interim

### Federal Register / Vol. 57, No. 57 / Tuesday, March 24, 1992 / Notices

Waiver when it is determined that the applicant will experience economic hardship if the Applicant for interim Waiver is denied

, if it appears likely that the Petition for Waiver will be granted

, and/or the Assistant Secretary determines that it would be desirable for public policy reasons to grant immediate relief pending a determination on the petition for Waiver

. An Interim Waiver remains in effect for a period of 180 days or until DOE issues its determination on the Petition for Waiver

, whichever is

sooner, and may be extended for an additional 180 days

, if necessary. Armstrong filed a "Petition for Waiver , " dated December 14, 1990, in accordance with § 430.27 of 10 CFR 430. DOE published in the Federal Register on March 13,1991
, Armstrong ' s petition and solicited comments

, data and information respecting the petition. 56 FR 10553

. Armstrong also filed an "Application for Interim Waiver" under § 430.27 (g) which DOE granted on March 4

, 1991

. 56 FR 10553

, March 13, 1991. 

### No comments were received concerning either the " Petition for Waiver " or the " Interim Waiver." DOE consulted with The Federal Trade Commission (FTC) concerning the Armstrong Petition

. The FTC did not have any objections to the issuance of the waiver to Armstrong.

Assertions and Determinations Armstrong ' s Petition seeks a waiver from the DOE test provisions that require a 1.5-minute time delay between the ignition of the burner and the starting of the circulating air blower. Armstrong requests the allowance to test using a 20-second blower time delay when testing its GRTC series of rooftop furnaces

. Armstrong states that since the 20

- second delay is indicative of how these models actually operate and since such a delay results in an improvement in efficiency of approximately 0.6 percent
, the petition should be granted. 

### Under specific circumstances, the DOE test procedure contain exceptions which allow testing with blower delay times of less than the prescribed 1.5- minute delay

. Armstrong indicates that it is unable to take advantage of any of these exceptions for its GRTC series of rooftop furnaces. Since the blower controls incorporated on the Armstrong furnaces are designed to impose a 20-second blower delay in every instance of start up. and since the current provisions do not specifically address this type of control
, DOE agrees that a waiver should be granted to allow the 20- second blower time delay when testing the Armstrong GRTC series of rooftop furnaces

. Accordingly

, with regard to testing the GRTC series of rooftop furnaces

, today ' s Decision and Order exempts Armstrong from the existing provisions regarding blower controls and allows testing with the 20

- second delay. It is, therefore

, ordered that: (1) The " Petition for Waiver " filed by Armstrong Air Conditioning

, Inc. (Case No. F-028 ), is hereby granted as set forth in paragraph (2) below

, subject to the provisions of paragraphs (3), (4), and (5). (2) Notwithstanding any contrary provisions of appendix N of 10 CFR part 430, supbart B, Armstrong Air Conditioning
, Inc.. shall be permitted to test its GRTC series of rooftop furnaces on the basis of the test procedure specified in 10 CFR part 430, with modifications set forth below: 

### (i) Section 3

. 0 of appendix N is deleted and replaced with the following paragraph: 3.0 Test Procedure testing and measurements shall be as specified in section 9 in ANSI/ASHRAE 103-82 with the exception of sections 9.2.2, 9

. 3.1, and 9.3.2, and the inclusion of the following additional procedures: 

### (ii) Add a new paragraph 3.10 to appendix N as follows: 3.10 Gas

- and Oil

- Fueled Central Furnaces

. The following paragraph is in lieu of the requirement specified in section 9

. 3.1 of ANSI / ASHRAE 103-82. After equilibrium conditions are achieved following the cool-down test and the required measurements performed

, turn on the furnaces and measure the flue gas temperature, using the thermocouple grid described above. at 0.5 and 2

. 5 minutes after the main burner ( s) comes on

. After the burner start

- up, delay the blower start

- up by 1.5 minutes (t-), unless : ( 1) The furnace employs a single motor to drive the power burner and the indoor air circulating blower

, in which case the burner and blower shall be started together; or (2) the furnace is designed to operate using an unvarying delay time that is other than 1

. 5 minutes

, in which case the fan control shall be permitted to start the blower ; or (3) the delay time results in the activation of a temperature safety device which shuts off the burner, in which case the fan control shall be permitted to start the blower

. In the later

case , if the fan control is adjustable, set it to start the blower at the highest temperature

. If the fan control is permitted to start the blower

, measure time delay , ( t-), using a stopwatch. Record the measured temperatures. During the heat

-up test

. for oil

-fueled furnaces

, maintain the draft in the flue pipe within ± 0.01 inch of water column 

### 10161

of the manufacturer's recommended onperiod draft. (iii) With the exception of the modifications set forth above, Armstrong Air Conditioning. Inc. shall comply in all respects with the test procedures specified in appendix N of 10 CFR part 430, subpart B. (3) The Waiver shall remain in effect from the date of issuance of this Order until DOE prescribes final test procedures appropriate to the GRTC series of rooftop furnace manufactured by Armstrong Air Conditioning. Inc. (4) This Waiver is based upon the presumed validity of statements, allegations, and documentary materials submitted by the petitioner. This Waiver may be revoked or modified at any time upon a determination that the factual basis underlying the petition is incorrect. (5) Effective (Insert Date of Issuance), this Waiver supersedes the Interim Waiver granted Armstrong Air Conditioning, Inc. on March 4,1991 56FR 10553, March 13, 1991 (Case No. F028). issued in Washington. DC, march 11. 1992. J. Michael Davis, Assistant Secretary Conservation and Renewable Energy.
[FR Doc. 92-8782 Filed 3-23-92; 8:45 am)

etltJNG CODE 645"I-V