### Instructions for filling in the Emission Test Template

This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate runs or sampling events for each of the requested constituents. This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. yellow are required. All cells that are shaded in green are populated using drop

-down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls (example: 8100_Unit_2_EmisTestMethods.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet. 2. Please enter the control device configuration.

Emission Data Worksheets

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg Hg+2

### , or if the Ontario

- Hydro Method was used, you would need to enter Hg0

### , HgP, and Hg Volatile Organic HAP and Speciated Semi

-Volatile Organic HAP worksheets allow you to use a drop Constituent field to define as many records as needed to record each HAP that you have results for. General instructions follow for these worksheets:

Boiler Operation Information

1. Please provide the values of all requested parameters for each of test run/sample. 2. Please provide any other supporting information or comments in the Other Supporting Information field.

Fuel Information

1. Please enter what types of fuel are being used in your boiler using the drop

-downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples, then enter an input rate of zero. 2. Please enter the unit of measure using the drop down provided. 3. Please enter the test method used to determine the fuel input rate. 4. Please provide any other information that you feel may be important in the Other Supporting Information field.

Emission Data

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and ppmvd @ 7% O 2 

### (parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please also enter these data.

### This Information Collection Request (ICR) spreadsheet is intended to collect information about emission data from fossil fuel burning power plants and which test methods were used to do so for cases where the test methods are not currently supported by the Electronic Reporting Tool (ERT). This spreadsheet should only be used if the method is not in the ERT or if you do not have access to a lab which performs methods that are in the ERT. You must complete at least 3 separate This spreadsheet is intended to be used for one boiler of one facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet. Fields shaded in down lists. You do not need to populate cells shaded in gray, as they are automatically populated from the Boiler Information worksheet. Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_EmisTestMethods.xls

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet.

The emission data worksheets are provided for each constituent or constituent family required for this analysis. On each spreadsheet, you must enter boiler operating information during sampling, fuel input information, and emission test results. There are generally 1 to 3 emission test results records to be entered depending on the constituent or constituent family. For example, CO only requires 1 record with 3 sample events, while Mercury requires that you enter both Hg0 

### and , HgP, and Hg+2 

### . However, both the Speciated Volatile Organic HAP worksheets allow you to use a drop

-down provided in the Constituent field to define as many records as needed to record each HAP that you have results for. General instructions

2. Please provide any other supporting information or comments in the Other Supporting Information field.

downs in the Fuel Type Selection field. You may enter up to 4 fuel types. If you are not burning one or more of the fuel types entered in one or more samples,

4. Please provide any other information that you feel may be important in the Other Supporting Information field.

### 1. Some constituents ask for the emission rate results of each run in two different units of measure, while others do not. If emission rate results are requested in two different units of measure (ex. lb/MMBtu (Pounds per million BTU) and

(parts per million by volume dry basis at 7 percent oxygen)), you are required to provide both. 2. Please provide the test method used. This may or may not match the example given in the Test Method Used field. Please ensure that the name includes the owning organization of the test method (ex. U.S. EPA Method 0010). 3. Please provide any other information that you feel may be important in the Other Supporting Information field. 4. If data sheets and QA/QC documentation tables are provided for the test method you are entering data for please alsoEIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam Station U1Control Device ConfiguratonEIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam Station U1

Run Number Test Start Date Test Start TimeMeasured Value (ppm) Test End Time Test End DateBasis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) CO Emission Test ResultsTest Method Comments lb/mmBtu ppmdv @ 7% O2 Calculated Emission RateSteam Output (1000 lb/hr) Total Heat Input (mmBtu/hr) Flue Gas Moisture (%)Flue Gas CO2(%) Flue Gas O2(%) Flue Gas Flow Rate (dscfm)Fuel Input Rate Fuel Type

Flue Gas Temperature (F) Fuel #1Units of Measure Measurement Method Fuel Input Rate Fuel #1Fuel Type Units of Measure Measurement Method Fuel #2Fuel Input Rate Fuel Type Units of Measure Fuel #3Measurement Method Fuel Input Rate Fuel Type Fuel #4Units of Measure Measurement Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam Station U1

1 4/21/2010 9:25 4/21/2010 2 4/21/2010 12:08 4/21/2010 3 4/21/2010 14:50 4/21/2010 Run Number Test Start Date Test Start Time Test End DateMeasured Value (ug) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) 11:41 4.1 Dry U.S. EPA Method 316 ADL 14:24 5.3 Dry U.S. EPA Method 316 ADL 17:06 1.8 Dry U.S. EPA Method 316 ADL Test End Time Formaldehyde Emission Test ResultsTest Method

Comments lb/mmBtu ppmdv @ 7% O2

1.860E-06 0.00162 2.382E-06 0.00208 8.194E-07 0.00071 Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr) Calculated Emission RateFuel Input Rate Fuel Type Units of Measure 14.87 12.41 6.9 3255812.722 130 15.08 12.42 6.92 3270316.227 130 15.04 12.41 6.85 3228941.282 129 Flue Gas Temperature (F) Fuel #1 Flue Gas Moisture (%) Flue Gas

CO2(%) Flue Gas

O2(%) Flue Gas Flow

Rate (dscfm)Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Fuel #2 Fuel #3Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Sam ple results may be im pacted by

blank contamination. Sam ple results may

be im pacted by

blank contamination. Sam ple results may

be im pacted by

blank contamination. Fuel #4 Other Supporting InformationSam ple results may be im pacted by

blank contamination. Sam ple results may

be im pacted by

blank contamination. Sam ple results may

be im pacted by

blank contamination.EIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam Station U1

1 4/21/2010 9:25 2 4/21/2010 12:08 3 4/21/2010 14:50 Run Number Test Start Date Test Start TimeMeasured Value (ppm) Basis (Wet or Dry)

4/21/2010 11:41 0.56 Dry 4/21/2010 14:24 0.58 Dry 4/21/2010 17:06 0.52 Dry

Test End Time Test End Date Methane Emission Test ResultsTest Method Used Data Flag (ADL, BDL, DDL) Test Method Comments lb/mmBtu

U.S. EPA Method 18 ADL Methane Non-Methane THC Analy zer 0.00034 U.S. EPA Method 18 ADL Methane Non-Methane THC Analy zer 0.00035 U.S. EPA Method 18 ADL Methane Non-Methane THC Analy zer 0.00031 Methane Emission Test Results Calculated Emission Rateppmdv @ 7% O2

0.556 12.41 6.9 0.577 12.42 6.92 0.514 12.41 6.85 Flue Gas Moisture (%) Flue Gas CO2(%) Flue Gas

O2(%) Flue Gas

Flow Rate (dscfm) Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr)Fuel Input Rate Fuel Type Units of

Measure Measurement

Method Fuel

Input Rate Fuel Type Units of

Measure Flue Gas Temperat ure (F) Fuel #1 Fuel #2Measurement

Method Fuel

Input Rate Fuel Type Units of

Measure Measurement

Method Fuel

Input Rate Fuel Type Units of

Measure Fuel #4 Fuel #3Measurement

Method Other Supporting InformationEIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam Station U1

Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used Test End Time SO2Emission Test ResultsData Flag (ADL,

BDL, DDL) Test Method

Comments lb/mmBtu ppmdv @ 7% O2 Calculated Emission Rate Steam Output (1000 lb/hr)Fuel Input Rate Fuel Type Flue Gas Moisture (%) Flue Gas

CO2(%) Flue Gas

O2(%) Flue Gas

Flow Rate (dscfm) Total Heat Input (mmBtu/hr) Flue Gas Temperature (F) Fuel #1Units of

Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel Input

Rate Fuel Type Fuel #1 Fuel #2 Fuel #3Units of

Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #4 Fuel #3Other Supporting InformationEIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam Station U1

1 4/22/2010 10:06 2 4/23/2010 8:23 3 4/23/2010 12:17 Run Number Test Start Date Test Start TimePlease note QA/QC documentation starting in Column "AJ"

Measured Value (μg/dscm) Basis (Wet or Dry)

4/22/2010 15:10 [<0.945] Dry 4/23/2010 11:24 [<1.529] Dry 4/23/2010 15:26 [<1.304] Dry

Test End Time Total Vapor Phase Mercury Emission Test Results

Test End DatePlease note QA/QC documentation starting in Column "AJ"

Test Method Used Data Flag (ADL, BDL, DLL) Test Method

Comments (lb/mmBtu)

U.S. EPA Method 30B DLL DL based on the MDL [<8.65E-07] U.S. EPA Method 30B DLL DL based on the MDL [<1.40E-06] U.S. EPA Method 30B DLL DL based on the MDL [<1.19E-06] Total Vapor Phase Mercury Emission Test Results Steam Output (1000 lb/hr)Fuel Input Rate

13.1 12.26 6.96 3,369,921 127 15.0 12.23 6.93 3,341,205 128 14.9 12.31 6.94 3,346,156 129

Flue Gas O2(%) Flue Gas

Flow Rate (dscfm) Flue Gas

Temperature (F) Flue Gas Moisture (%) Total Heat Input (mmBtu/hr) Flue Gas CO2(%)Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel Input

Rate Fuel #1 Fuel #2Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #3 Fuel #4QA /QC Documentation

Trap ID Section 1

Mass (ng) Section 2

Mass (ng) Total

Mass (ng) Initial

Spike (ng) Total NonSpike (ng)

68523 272 0.8 272.8 100 172.8 65498 385 0.3 385.3 100 285.3 65339 346 1.1 347.1 100 247.1 Other Supporting InformationSample

Volume (dscm) Volume

Difference (%) Volume Diff. Limit Breaktrough

(%) Breaktrough

Limit Concentration

(μg/dscm) Trap ID

0.1812 0.294117647 0.953517627 68288 0.1822 0.077922078 1.565858969 68279 0.1815 0.317919075 1.361788381 68320 ≤20% of field

recovery test ≤10% of Section 1 Hg

mass for Hg conc. >1

μg/dscm: or ≤ 20% of Section Trap #1Section 1

Mass Section 2

Mass Total

Mass Initial

Spike Total NonSpike Sample

Volume Volume

Difference (%) Volume Diff. Limit

176 0.4 176.4 176.4 0.1808 0.253 287 0.6 287.6 287.6 0.1818 0.223 244 0.7 244.7 244.7 0.1813 0.096 ≤20% of field

recovery test Trap #2Breaktrough (%) Breaktrough Limit Concentration

(μg/dscm) Abs. diff. RD (%) Limit C rec

0.227272727 0.975856275 0.022339 1.157818 0.5295 0.209059233 1.582004184 0.016145 0.512894 0.5327 0.286885246 1.349853157 0.011935 0.440148 0.5630 Measured Spike Recovery ( R ) Paired Trap Agreement (RD)

≥ 10 % RD mass for Hg conc. >1 μg/dscm: or

≤20% RD or ≤0.2 μg/dscm abs.diff. for Hg conc. ≤1 ≤10% of Section 1 Hg mass for Hg conc. >1

μg/dscm: or ≤ 20% of Section 1 for Hg conc. ≤1R (%) by

Run Ravg(%) Limit

95.95 97.06 102.17 Average Recovery

, between 85 and 115% Measured Spike Recovery ( R )

98.39190703EIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam StationU1

Run Number Test Start Date Test Start TimeMeasured Hg 0Value (μg/dscm) Measured Hg +2Value (μg/dscm) Test End Time Test End DateMeasured Hg PValue

(μg/dscm) Basis (Wet or Dry) Test Method Used Data Flag (ADL, BDL, DDL) Total Vapor Phase Mercury Emission Test ResultsTest Method

Comments Total Mercury (lb/mmBtu) Steam Output

(1000 lb/hr) Total Heat

Input (mmBtu/hr) Flue Gas

Moisture (%) Flue Gas

CO2(%)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel #1 Flue Gas O2(%) Flue Gas

Flow Rate (dscfm) Flue Gas

Temperature (F)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #2 Fuel #3Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Other Supporting Information Fuel #4EIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam Station U1

Speciated Volatile Organic HAP Emission Data

1,1,1,2-Tetrachloroethane 1 4/21/2010 1,1,1,2-Tetrachloroethane 2 4/21/2010 1,1,1,2-Tetrachloroethane 3 4/21/2010 1,1,1-Trichloroethane 1 4/21/2010 1,1,1-Trichloroethane 2 4/21/2010 1,1,1-Trichloroethane 3 4/21/2010 1,1,2,2-Tetrachloroethane 1 4/21/2010 1,1,2,2-Tetrachloroethane 2 4/21/2010 1,1,2,2-Tetrachloroethane 3 4/21/2010 1,1,2-Trichloroethane 1 4/21/2010 1,1,2-Trichloroethane 2 4/21/2010 1,1,2-Trichloroethane 3 4/21/2010 1,1-Dichloroethane 1 4/21/2010 1,1-Dichloroethane 2 4/21/2010 1,1-Dichloroethane 3 4/21/2010 1,1-Dichloroethene 1 4/21/2010 1,1-Dichloroethene 2 4/21/2010 1,1-Dichloroethene 3 4/21/2010 1,1-Dichloropropene 1 4/21/2010 1,1-Dichloropropene 2 4/21/2010 1,1-Dichloropropene 3 4/21/2010 1,2,3-Trichlorobenzene 1 4/21/2010 1,2,3-Trichlorobenzene 2 4/21/2010 1,2,3-Trichlorobenzene 3 4/21/2010 1,2,3-Trichloropropane 1 4/21/2010 1,2,3-Trichloropropane 2 4/21/2010 1,2,3-Trichloropropane 3 4/21/2010 1,2,4-Trichlorobenzene 1 4/21/2010 1,2,4-Trichlorobenzene 2 4/21/2010 1,2,4-Trichlorobenzene 3 4/21/2010 1,2,4-Trimethylbenzene 1 4/21/2010 1,2,4-Trimethylbenzene 2 4/21/2010 1,2,4-Trimethylbenzene 3 4/21/2010 1,2-Dibromo-3-chloropropane 1 4/21/2010 1,2-Dibromo-3-chloropropane 2 4/21/2010 1,2-Dibromo-3-chloropropane 3 4/21/2010 1,2-Dibromoethane 1 4/21/2010 1,2-Dibromoethane 2 4/21/2010 1,2-Dibromoethane 3 4/21/2010 1,2-Dichlorobenzene 1 4/21/2010 1,2-Dichlorobenzene 2 4/21/2010 1,2-Dichlorobenzene 3 4/21/2010 1,2-Dichloroethane 1 4/21/2010 1,2-Dichloroethane 2 4/21/2010 1,2-Dichloroethane 3 4/21/2010 1,2-Dichloropropane 1 4/21/2010 1,2-Dichloropropane 2 4/21/2010

Compound (use drop down to define for as many rows as

needed) Run Number Test Start Date1,2-Dichloropropane 3 4/21/2010

1,3,5-Trimethylbenzene 1 4/21/2010 1,3,5-Trimethylbenzene 2 4/21/2010 1,3,5-Trimethylbenzene 3 4/21/2010 1,3-Dichlorobenzene 1 4/21/2010 1,3-Dichlorobenzene 2 4/21/2010 1,3-Dichlorobenzene 3 4/21/2010 1,3-Dichloropropane 1 4/21/2010 1,3-Dichloropropane 2 4/21/2010 1,3-Dichloropropane 3 4/21/2010 1,4-Dichlorobenzene 1 4/21/2010 1,4-Dichlorobenzene 2 4/21/2010 1,4-Dichlorobenzene 3 4/21/2010 2,2-Dichloropropane 1 4/21/2010 2,2-Dichloropropane 2 4/21/2010 2,2-Dichloropropane 3 4/21/2010 2-Butanone 1 4/21/2010 2-Butanone 2 4/21/2010 2-Butanone 3 4/21/2010 2-Chlorotoluene 1 4/21/2010 2-Chlorotoluene 2 4/21/2010 2-Chlorotoluene 3 4/21/2010 2-Hexanone 1 4/21/2010 2-Hexanone 2 4/21/2010 2-Hexanone 3 4/21/2010 4-Chlorotoluene 1 4/21/2010 4-Chlorotoluene 2 4/21/2010 4-Chlorotoluene 3 4/21/2010 4-Methyl-2-pentanone 1 4/21/2010 4-Methyl-2-pentanone 2 4/21/2010 4-Methyl-2-pentanone 3 4/21/2010 Acetone 1 4/21/2010 Acetone 2 4/21/2010 Acetone 3 4/21/2010 Benzene 1 4/21/2010 Benzene 2 4/21/2010 Benzene 3 4/21/2010 Bromobenzene 1 4/21/2010 Bromobenzene 2 4/21/2010 Bromobenzene 3 4/21/2010 Bromochloromethane 1 4/21/2010 Bromochloromethane 2 4/21/2010 Bromochloromethane 3 4/21/2010 Bromodichloromethane 1 4/21/2010 Bromodichloromethane 2 4/21/2010 Bromodichloromethane 3 4/21/2010 Bromoform 1 4/21/2010 Bromoform 2 4/21/2010 Bromoform 3 4/21/2010 Bromomethane 1 4/21/2010 Bromomethane 2 4/21/2010 Bromomethane 3 4/21/2010 Carbon disulfide 1 4/21/2010 Carbon disulfide 2 4/21/2010 Carbon disulfide 3 4/21/2010Carbon tetrachloride 1 4/21/2010

Carbon tetrachloride 2 4/21/2010 Carbon tetrachloride 3 4/21/2010 Chlorobenzene 1 4/21/2010 Chlorobenzene 2 4/21/2010 Chlorobenzene 3 4/21/2010 Chlorodibromomethane 1 4/21/2010 Chlorodibromomethane 2 4/21/2010 Chlorodibromomethane 3 4/21/2010 Chloroethane 1 4/21/2010 Chloroethane 2 4/21/2010 Chloroethane 3 4/21/2010 Chloroform 1 4/21/2010 Chloroform 2 4/21/2010 Chloroform 3 4/21/2010 Chloromethane 1 4/21/2010 Chloromethane 2 4/21/2010 Chloromethane 3 4/21/2010 cis-1,2-Dichloroethene 1 4/21/2010 cis-1,2-Dichloroethene 2 4/21/2010 cis-1,2-Dichloroethene 3 4/21/2010 cis-1,3-Dichloropropene 1 4/21/2010 cis-1,3-Dichloropropene 2 4/21/2010 cis-1,3-Dichloropropene 3 4/21/2010 Dibromomethane 1 4/21/2010 Dibromomethane 2 4/21/2010 Dibromomethane 3 4/21/2010 Dichlorodifluoromethane 1 4/21/2010 Dichlorodifluoromethane 2 4/21/2010 Dichlorodifluoromethane 3 4/21/2010 Ethylbenzene 1 4/21/2010 Ethylbenzene 2 4/21/2010 Ethylbenzene 3 4/21/2010 Hexachlorobutadiene 1 4/21/2010 Hexachlorobutadiene 2 4/21/2010 Hexachlorobutadiene 3 4/21/2010 Isopropylbenzene 1 4/21/2010 Isopropylbenzene 2 4/21/2010 Isopropylbenzene 3 4/21/2010 Methylene chloride 1 4/21/2010 Methylene chloride 2 4/21/2010 Methylene chloride 3 4/21/2010 m-Xylene & p-Xylene 1 4/21/2010 m-Xylene & p-Xylene 2 4/21/2010 m-Xylene & p-Xylene 3 4/21/2010 Naphthalene 1 4/21/2010 Naphthalene 2 4/21/2010 Naphthalene 3 4/21/2010 n-Butylbenzene 1 4/21/2010 n-Butylbenzene 2 4/21/2010 n-Butylbenzene 3 4/21/2010 n-Propylbenzene 1 4/21/2010 n-Propylbenzene 2 4/21/2010 n-Propylbenzene 3 4/21/2010 o-Xylene 1 4/21/2010o-Xylene 2 4/21/2010

o-Xylene 3 4/21/2010 p-Isopropyltoluene 1 4/21/2010 p-Isopropyltoluene 2 4/21/2010 p-Isopropyltoluene 3 4/21/2010 sec-Butylbenzene 1 4/21/2010 sec-Butylbenzene 2 4/21/2010 sec-Butylbenzene 3 4/21/2010 Styrene 1 4/21/2010 Styrene 2 4/21/2010 Styrene 3 4/21/2010 tert-Butylbenzene 1 4/21/2010 tert-Butylbenzene 2 4/21/2010 tert-Butylbenzene 3 4/21/2010 Tetrachloroethene 1 4/21/2010 Tetrachloroethene 2 4/21/2010 Tetrachloroethene 3 4/21/2010 Toluene 1 4/21/2010 Toluene 2 4/21/2010 Toluene 3 4/21/2010 trans-1,2-Dichloroethene 1 4/21/2010 trans-1,2-Dichloroethene 2 4/21/2010 trans-1,2-Dichloroethene 3 4/21/2010 trans-1,3-Dichloropropene 1 4/21/2010 trans-1,3-Dichloropropene 2 4/21/2010 trans-1,3-Dichloropropene 3 4/21/2010 Trichloroethene 1 4/21/2010 Trichloroethene 2 4/21/2010 Trichloroethene 3 4/21/2010 Trichlorofluoromethane 1 4/21/2010 Trichlorofluoromethane 2 4/21/2010 Trichlorofluoromethane 3 4/21/2010 Vinyl chloride 1 4/21/2010 Vinyl chloride 2 4/21/2010 Vinyl chloride 3 4/21/2010Measured Value (μg/m3 @ 7% O2) 9:25 AM 4/21/2010 11:18 AM [< 2.974] 12:08 PM 4/21/2010 2:01 PM [< 2.852] 2:50 PM 4/21/2010 4:42 PM [< 3.043] 9:25 AM 4/21/2010 11:18 AM [< 3.81] 12:08 PM 4/21/2010 2:01 PM [< 3.664] 2:50 PM 4/21/2010 4:42 PM [< 3.899] 9:25 AM 4/21/2010 11:18 AM [< 4.646] 12:08 PM 4/21/2010 2:01 PM [< 4.425] 2:50 PM 4/21/2010 4:42 PM [< 4.755] 9:25 AM 4/21/2010 11:18 AM [< 5.238] 12:08 PM 4/21/2010 2:01 PM [< 4.817] 2:50 PM 4/21/2010 4:42 PM [< 5.361] 9:25 AM 4/21/2010 11:18 AM [< 1.905] 12:08 PM 4/21/2010 2:01 PM [< 1.819] 2:50 PM 4/21/2010 4:42 PM [< 1.949] 9:25 AM 4/21/2010 11:18 AM [< 3.651] 12:08 PM 4/21/2010 2:01 PM [< 3.498] 2:50 PM 4/21/2010 4:42 PM [< 3.736] 9:25 AM 4/21/2010 11:18 AM [< 2.328] 12:08 PM 4/21/2010 2:01 PM [< 2.229] 2:50 PM 4/21/2010 4:42 PM [< 2.383] 9:25 AM 4/21/2010 11:18 AM [< 7.561] 12:08 PM 4/21/2010 2:01 PM [< 7.252] 2:50 PM 4/21/2010 4:42 PM [< 7.69] 9:25 AM 4/21/2010 11:18 AM [< 12.169] 12:08 PM 4/21/2010 2:01 PM [< 11.147] 2:50 PM 4/21/2010 4:42 PM [< 12.455] 9:25 AM 4/21/2010 11:18 AM [< 5.468] 12:08 PM 4/21/2010 2:01 PM [< 5.248] 2:50 PM 4/21/2010 4:42 PM [< 5.588] 9:25 AM 4/21/2010 11:18 AM [< 1.923] 12:08 PM 4/21/2010 2:01 PM [< 1.739] 2:50 PM 4/21/2010 4:42 PM [< 1.841] 9:25 AM 4/21/2010 11:18 AM [< 18.836] 12:08 PM 4/21/2010 2:01 PM [< 17.911] 2:50 PM 4/21/2010 4:42 PM [< 19.278] 9:25 AM 4/21/2010 11:18 AM [< 5.122] 12:08 PM 4/21/2010 2:01 PM [< 4.925] 2:50 PM 4/21/2010 4:42 PM [< 5.242] 9:25 AM 4/21/2010 11:18 AM [< 2.042] 12:08 PM 4/21/2010 2:01 PM [< 1.932] 2:50 PM 4/21/2010 4:42 PM [< 2.09] 9:25 AM 4/21/2010 11:18 AM [< 2.614] 12:08 PM 4/21/2010 2:01 PM [< 2.488] 2:50 PM 4/21/2010 4:42 PM [< 2.683] 9:25 AM 4/21/2010 11:18 AM [< 2.72] 12:08 PM 4/21/2010 2:01 PM [< 2.591] Test Start Time Test End Date Test End Time2:50 PM 4/21/2010 4:42 PM [< 2.783] 9:25 AM 4/21/2010 11:18 AM [< 1.114] 12:08 PM 4/21/2010 2:01 PM [< 1.01] 2:50 PM 4/21/2010 4:42 PM [< 1.116] 9:25 AM 4/21/2010 11:18 AM [< 2.423] 12:08 PM 4/21/2010 2:01 PM [< 2.311] 2:50 PM 4/21/2010 4:42 PM [< 2.48] 9:25 AM 4/21/2010 11:18 AM [< 2.053] 12:08 PM 4/21/2010 2:01 PM [< 1.953] 2:50 PM 4/21/2010 4:42 PM [< 2.101] 9:25 AM 4/21/2010 11:18 AM [< 2.751] 12:08 PM 4/21/2010 2:01 PM [< 2.627] 2:50 PM 4/21/2010 4:42 PM [< 2.816] 9:25 AM 4/21/2010 11:18 AM [< 2.91] 12:08 PM 4/21/2010 2:01 PM [< 2.793] 2:50 PM 4/21/2010 4:42 PM [< 2.978] 9:25 AM 4/21/2010 11:18 AM [< 79.366] 12:08 PM 4/21/2010 2:01 PM [< 74.311] 2:50 PM 4/21/2010 4:42 PM [< 81.227] 9:25 AM 4/21/2010 11:18 AM [< 2.773] 12:08 PM 4/21/2010 2:01 PM [< 2.655] 2:50 PM 4/21/2010 4:42 PM [< 2.838] 9:25 AM 4/21/2010 11:18 AM [< 13.947] 12:08 PM 4/21/2010 2:01 PM [< 13.335] 2:50 PM 4/21/2010 4:42 PM [< 14.274] 9:25 AM 4/21/2010 11:18 AM [< 2.794] 12:08 PM 4/21/2010 2:01 PM [< 2.67] 2:50 PM 4/21/2010 4:42 PM [< 2.859] 9:25 AM 4/21/2010 11:18 AM [< 79.366] 12:08 PM 4/21/2010 2:01 PM [< 74.311] 2:50 PM 4/21/2010 4:42 PM [< 81.227] 9:25 AM 4/21/2010 11:18 AM [< 121821.5] 12:08 PM 4/21/2010 2:01 PM 113939.530 2:50 PM 4/21/2010 4:42 PM 122310.981 9:25 AM 4/21/2010 11:18 AM [< 2.324] 12:08 PM 4/21/2010 2:01 PM [< 1.685] 2:50 PM 4/21/2010 4:42 PM [< 1.878] 9:25 AM 4/21/2010 11:18 AM [< 2.91] 12:08 PM 4/21/2010 2:01 PM [< 2.767] 2:50 PM 4/21/2010 4:42 PM [< 2.978] 9:25 AM 4/21/2010 11:18 AM [< 5.429] 12:08 PM 4/21/2010 2:01 PM [< 5.186] 2:50 PM 4/21/2010 4:42 PM [< 5.556] 9:25 AM 4/21/2010 11:18 AM [< 3.577] 12:08 PM 4/21/2010 2:01 PM [< 3.431] 2:50 PM 4/21/2010 4:42 PM [< 3.661] 9:25 AM 4/21/2010 11:18 AM [< 27.514] 12:08 PM 4/21/2010 2:01 PM [< 26.393] 2:50 PM 4/21/2010 4:42 PM [< 28.159] 9:25 AM 4/21/2010 11:18 AM [< 15.873] 12:08 PM 4/21/2010 2:01 PM [< 13.491] 2:50 PM 4/21/2010 4:42 PM [< 18.452] 9:25 AM 4/21/2010 11:18 AM [< 3.169] 12:08 PM 4/21/2010 2:01 PM [< 2.648] 2:50 PM 4/21/2010 4:42 PM [< 2.754]9:25 AM 4/21/2010 11:18 AM [< 3.001] 12:08 PM 4/21/2010 2:01 PM [< 2.876] 2:50 PM 4/21/2010 4:42 PM [< 3.07] 9:25 AM 4/21/2010 11:18 AM [< 2.288] 12:08 PM 4/21/2010 2:01 PM [< 2.422] 2:50 PM 4/21/2010 4:42 PM [< 2.694] 9:25 AM 4/21/2010 11:18 AM [< 6.032] 12:08 PM 4/21/2010 2:01 PM [< 5.791] 2:50 PM 4/21/2010 4:42 PM [< 6.173] 9:25 AM 4/21/2010 11:18 AM [< 7.534] 12:08 PM 4/21/2010 2:01 PM [< 7.139] 2:50 PM 4/21/2010 4:42 PM [< 7.711] 9:25 AM 4/21/2010 11:18 AM [< 2.021] 12:08 PM 4/21/2010 2:01 PM [< 1.93] 2:50 PM 4/21/2010 4:42 PM [< 2.069] 9:25 AM 4/21/2010 11:18 AM [< 138.838] 12:08 PM 4/21/2010 2:01 PM [< 9.571] 2:50 PM 4/21/2010 4:42 PM [< 9.883] 9:25 AM 4/21/2010 11:18 AM [< 2.963] 12:08 PM 4/21/2010 2:01 PM [< 2.844] 2:50 PM 4/21/2010 4:42 PM [< 3.032] 9:25 AM 4/21/2010 11:18 AM [< 3.302] 12:08 PM 4/21/2010 2:01 PM [< 3.154] 2:50 PM 4/21/2010 4:42 PM [< 3.379] 9:25 AM 4/21/2010 11:18 AM [< 5.355] 12:08 PM 4/21/2010 2:01 PM [< 5.133] 2:50 PM 4/21/2010 4:42 PM [< 5.48] 9:25 AM 4/21/2010 11:18 AM [< 26.186] 12:08 PM 4/21/2010 2:01 PM [< 25.129] 2:50 PM 4/21/2010 4:42 PM [< 26.662] 9:25 AM 4/21/2010 11:18 AM [< 2.229] 12:08 PM 4/21/2010 2:01 PM [< 2.141] 2:50 PM 4/21/2010 4:42 PM [< 2.278] 9:25 AM 4/21/2010 11:18 AM [< 10.318] 12:08 PM 4/21/2010 2:01 PM [< 9.929] 2:50 PM 4/21/2010 4:42 PM [< 10.56] 9:25 AM 4/21/2010 11:18 AM [< 2.011] 12:08 PM 4/21/2010 2:01 PM [< 1.922] 2:50 PM 4/21/2010 4:42 PM [< 2.058] 9:25 AM 4/21/2010 11:18 AM 3599.872 12:08 PM 4/21/2010 2:01 PM 3525.682 2:50 PM 4/21/2010 4:42 PM 3496.044 9:25 AM 4/21/2010 11:18 AM [< 2.157] 12:08 PM 4/21/2010 2:01 PM [< 2.055] 2:50 PM 4/21/2010 4:42 PM [< 2.186] 9:25 AM 4/21/2010 11:18 AM [< 7.407] 12:08 PM 4/21/2010 2:01 PM [< 6.919] 2:50 PM 4/21/2010 4:42 PM [< 7.581] 9:25 AM 4/21/2010 11:18 AM [< 2.116] 12:08 PM 4/21/2010 2:01 PM [< 2.024] 2:50 PM 4/21/2010 4:42 PM [< 2.166] 9:25 AM 4/21/2010 11:18 AM [< 1.038] 12:08 PM 4/21/2010 2:01 PM [< 0.948] 2:50 PM 4/21/2010 4:42 PM [< 1.029] 9:25 AM 4/21/2010 11:18 AM [< 2.557]12:08 PM 4/21/2010 2:01 PM [< 2.446] 2:50 PM 4/21/2010 4:42 PM [< 2.599] 9:25 AM 4/21/2010 11:18 AM [< 1.931] 12:08 PM 4/21/2010 2:01 PM [< 1.819] 2:50 PM 4/21/2010 4:42 PM [< 1.954] 9:25 AM 4/21/2010 11:18 AM [< 1.905] 12:08 PM 4/21/2010 2:01 PM [< 1.819] 2:50 PM 4/21/2010 4:42 PM [< 1.949] 9:25 AM 4/21/2010 11:18 AM [< 2.311] 12:08 PM 4/21/2010 2:01 PM [< 2.201] 2:50 PM 4/21/2010 4:42 PM [< 2.361] 9:25 AM 4/21/2010 11:18 AM [< 1.968] 12:08 PM 4/21/2010 2:01 PM [< 1.878] 2:50 PM 4/21/2010 4:42 PM [< 2.014] 9:25 AM 4/21/2010 11:18 AM [< 2.815] 12:08 PM 4/21/2010 2:01 PM [< 2.698] 2:50 PM 4/21/2010 4:42 PM [< 2.881] 9:25 AM 4/21/2010 11:18 AM [< 2.95] 12:08 PM 4/21/2010 2:01 PM [< 2.742] 2:50 PM 4/21/2010 4:42 PM [< 3.027] 9:25 AM 4/21/2010 11:18 AM [< 2.116] 12:08 PM 4/21/2010 2:01 PM [< 2.17] 2:50 PM 4/21/2010 4:42 PM [< 2.166] 9:25 AM 4/21/2010 11:18 AM [< 3.09] 12:08 PM 4/21/2010 2:01 PM [< 2.962] 2:50 PM 4/21/2010 4:42 PM [< 3.162] 9:25 AM 4/21/2010 11:18 AM [< 3.09] 12:08 PM 4/21/2010 2:01 PM [< 2.937] 2:50 PM 4/21/2010 4:42 PM [< 3.162] 9:25 AM 4/21/2010 11:18 AM [< 2.536] 12:08 PM 4/21/2010 2:01 PM [< 2.37] 2:50 PM 4/21/2010 4:42 PM [< 2.672] 9:25 AM 4/21/2010 11:18 AM [< 4.878] 12:08 PM 4/21/2010 2:01 PM [< 4.671] 2:50 PM 4/21/2010 4:42 PM [< 4.993]Footnotes:

* Front half fraction contains filter, cyclone, and cartridge ** Back half fraction contains condensate, solvent, impingers

Basis Test Method Used Data Flag (ADL, BDL, DDL) Front Half Mass (ng)

Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 23.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 17.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 23.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 80] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 60] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 80] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 12] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 9] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 12] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 11.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 200] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 150] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 200] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 13.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 9.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 12.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 21.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 11.7] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 12] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 104] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 78] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 104] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 11.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 11.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 14.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 14.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 13.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 14.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 13.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10.2]Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 13.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 16.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 14.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 11.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 11.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 11.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 11.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 12] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 9] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 12] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 800] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 600] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 800] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 9.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 7.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 9.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 54.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 40.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 54.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 11.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 11.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 800] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 600] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 800] Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL [< 9590] Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 93030 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 234700 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL [< 75.7] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 31.5] Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL [< 38.7] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 16] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 12] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 16] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 22.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 16.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 22.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 7.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 80] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 60] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 80] Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL 640 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL 493 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL 803 Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 83.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 50.7] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 47.4]Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10.9] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.5] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 9] Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL [< 25] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 35] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 16] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 12] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 16] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 49.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 37.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 49.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL 10240 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL 491 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL 474 Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 13.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 13.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 16.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 12.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 16.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 59.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 41.3] Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL [< 49.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.5] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 7.1] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.3] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 20] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 15] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 20] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 147 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 3181 Dry U.S. EPA Method 0031 with SW-846 Method 8260B ADL 2241 Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 19.1] Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL [< 16.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL [< 17.5] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 80] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 60] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 80] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10.5] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 9.3]Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL [< 6.9] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.3] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10.7] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 7.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 10.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 6.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 8.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL 35 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL [< 26] Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL 35.6 Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 16] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 25.4] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 16] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 9.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 7.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 9.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 17.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 13.2] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 17.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL 39.7 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL 33 Dry U.S. EPA Method 0031 with SW-846 Method 8260B DLL, DL based on MDL 45.4 Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 16.8] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 12.6] Dry U.S. EPA Method 0031 with SW-846 Method 8260B BDL, DL based on MDL [< 16.8]Back Half Mass (ng) Total Mass (ng)

[< 216] [< 224.8] [< 216] [< 222.6] [< 216] [< 224.8] [< 280] [< 288] [< 280] [< 286] [< 280] [< 288] [< 328] [< 351.2] [< 328] [< 345.4] [< 328] [< 351.2] [< 316] [< 396] [< 316] [< 376] [< 316] [< 396] [< 136] [< 144] [< 136] [< 142] [< 136] [< 144] [< 264] [< 276] [< 264] [< 273] [< 264] [< 276] [< 168] [< 176] [< 168] [< 174] [< 168] [< 176] [< 560] [< 571.6] [< 560] [< 566] [< 560] [< 568] [< 720] [< 920] [< 720] [< 870] [< 720] [< 920] [< 400] [< 413.4] [< 400] [< 409.6] [< 400] [< 412.8] [< 124] [< 145.4] [< 124] [< 135.7] [< 124] [< 136] [< 1320] [< 1424] [< 1320] [< 1398] [< 1320] [< 1424] [< 376] [< 387.2] [< 376] [< 384.4] [< 376] [< 387.2] [< 140] [< 154.4] [< 140] [< 150.8] [< 140] [< 154.4] [< 184] [< 197.6] [< 184] [< 194.2] [< 184] [< 198.2] [< 192] [< 205.6] [< 192] [< 202.2][< 192] [< 205.6]

[< 68] [< 84.2] [< 68] [< 78.8] [< 68] [< 82.4] [< 172] [< 183.2] [< 172] [< 180.4] [< 172] [< 183.2] [< 144] [< 155.2] [< 144] [< 152.4] [< 144] [< 155.2] [< 196] [< 208] [< 196] [< 205] [< 196] [< 208] [< 212] [< 220] [< 212] [< 218] [< 212] [< 220] [< 5200] [< 6000] [< 5200] [< 5800] [< 5200] [< 6000] [< 200] [< 209.6] [< 200] [< 207.2] [< 200] [< 209.6] [< 1000] [< 1054.4] [< 1000] [< 1040.8] [< 1000] [< 1054.4] [< 200] [< 211.2] [< 200] [< 208.4] [< 200] [< 211.2] [< 5200] [< 6000] [< 5200] [< 5800] [< 5200] [< 6000] 9200000 [< 9209590] 8800000 8893030 8800000 9034700 [< 100] [< 175.7] [< 100] [< 131.5] [< 100] [< 138.7] [< 204] [< 220] [< 204] [< 216] [< 204] [< 220] [< 388] [< 410.4] [< 388] [< 404.8] [< 388] [< 410.4] [< 260] [< 270.4] [< 260] [< 267.8] [< 260] [< 270.4] [< 2000] [< 2080] [< 2000] [< 2060] [< 2000] [< 2080] [< 560] [< 1200] [< 560] [< 1053] [< 560] [< 1363] [< 156] [< 239.6] [< 156] [< 206.7] [< 156] [< 203.4][< 216] [< 226.9]

[< 216] [< 224.5] [< 216] [< 226.8] [< 164] [< 173] [< 164] [< 189] [< 164] [< 199] [< 440] [< 456] [< 440] [< 452] [< 440] [< 456] [< 520] [< 569.6] [< 520] [< 557.2] [< 520] [< 569.6] [< 144] [< 152.8] [< 144] [< 150.6] [< 144] [< 152.8] [< 256] [< 10496] [< 256] [< 747] [< 256] [< 730] [< 216] [< 224] [< 216] [< 222] [< 216] [< 224] [< 236] [< 249.6] [< 236] [< 246.2] [< 236] [< 249.6] [< 388] [< 404.8] [< 388] [< 400.6] [< 388] [< 404.8] [< 1920] [< 1979.6] [< 1920] [< 1961.3] [< 1920] [< 1969.4] [< 160] [< 168.5] [< 160] [< 167.1] [< 160] [< 168.3] [< 760] [< 780] [< 760] [< 775] [< 760] [< 780] [< 144] [< 152] [< 144] [< 150] [< 144] [< 152] 272000 272147 272000 275181 256000 258241 [< 144] [< 163.1] [< 144] [< 160.4] [< 144] [< 161.5] [< 480] [< 560] [< 480] [< 540] [< 480] [< 560] [< 152] [< 160] [< 152] [< 158] [< 152] [< 160] [< 68] [< 78.5] [< 68] [< 74] [< 68] [< 76] [< 184] [< 193.3][< 184] [< 190.9]

[< 184] [< 192] [< 136] [< 146] [< 136] [< 142] [< 136] [< 144.3] [< 136] [< 144] [< 136] [< 142] [< 136] [< 144] [< 164] [< 174.7] [< 164] [< 171.8] [< 164] [< 174.4] [< 140] [< 148.8] [< 140] [< 146.6] [< 140] [< 148.8] [< 204] [< 212.8] [< 204] [< 210.6] [< 204] [< 212.8] [< 188] [< 223] [< 188] [< 214] [< 188] [< 223.6] [< 144] [< 160] [< 144] [< 169.4] [< 144] [< 160] [< 224] [< 233.6] [< 224] [< 231.2] [< 224] [< 233.6] [< 216] [< 233.6] [< 216] [< 229.2] [< 216] [< 233.6] [< 152] [< 191.7] [< 152] [< 185] [< 152] [< 197.4] [< 352] [< 368.8] [< 352] [< 364.6] [< 352] [< 368.8]Test Method Comments

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Method Blank Contamination Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Method Blank Contamination Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

High condenstae Method Blank Contamination for all runs. Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling. Method Blank Contamination Method Blank Contamination Runs 1,2,and 3 Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Method Blank Contamination Runs 1,2,and 3 Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Method Blank Contamination Runs 1,2,and 3 Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling. Method Blank Contamination

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

High condenstae Method Blank Contamination for all runs. Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.

Run 2 results do not include contribution from tube set 2B. Tube set 2B was voided because of problems encountered during sampling.lb/mmBtu ppmdv @ 7% O2

[< 0.000002713] [< 0.0000026021] [< 0.0000001087] [< 0.0000034757] [< 0.0000033432] [< 0.0000000988] [< 0.0000042385] [< 0.0000040375] [< 0.0000002866] [< 0.0000047791] [< 0.0000043952] [< 0.0000009881] [< 0.0000017379] [< 0.0000016599] [< 0.0000000988] [< 0.0000033309] [< 0.0000031912] [< 0.0000001482] [< 0.0000021241] [< 0.000002034] [< 0.0000000988] [< 0.0000068983] [< 0.0000066162] [< 0.0000000988] [< 0.000011103] [< 0.0000101698] [< 0.0000024703] [< 0.0000049891] [< 0.000004788] [< 0.0000001581] [< 0.0000017548] [< 0.0000015863] [< 0.0000001482] [< 0.0000171855] [< 0.0000163418] [< 0.0000012846] [< 0.0000046729] [< 0.0000044934] [< 0.0000001383] [< 0.0000018634] [< 0.0000017628] [< 0.0000001779] [< 0.0000023847] [< 0.0000022701] [< 0.0000001754] [< 0.0000024813] [< 0.0000023636] Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat Input (mmBtu/hr)[< 0.000000168]

[< 0.0000010162] [< 0.0000009211] [< 0.0000001779] [< 0.0000022109] [< 0.0000021088] [< 0.0000001383] [< 0.000001873] [< 0.0000017815] [< 0.0000001383] [< 0.0000025102] [< 0.0000023963] [< 0.0000001482] [< 0.0000026551] [< 0.0000025483] [< 0.0000000988] [< 0.0000724109] [< 0.0000677988] [< 0.0000098812] [< 0.0000025296] [< 0.0000024221] [< 0.0000001186] [< 0.000012725] [< 0.0000121664] [< 0.0000006719] [< 0.0000025489] [< 0.0000024361] [< 0.0000001383] [< 0.0000724109] [< 0.0000677988] [< 0.0000098812] [< 0.1111458082] [< 0.1039545956] [< 0.0028989056] [< 0.0000021204] [< 0.0000015372] [< 0.000000478] [< 0.0000026551] [< 0.0000025249] [< 0.0000001976] [< 0.0000049529] [< 0.0000047319] [< 0.0000002767] [< 0.0000032633] [< 0.0000031304] [< 0.0000001285] [< 0.0000251025] [< 0.0000240803] [< 0.0000009881] [< 0.0000144822] [< 0.000012309] [< 0.0000099183] [< 0.0000028916] [< 0.0000024162] [< 0.0000005855][< 0.0000027383]

[< 0.0000026243] [< 0.0000001334] [< 0.0000020878] [< 0.0000022093] [< 0.0000004323] [< 0.0000055032] [< 0.0000052836] [< 0.0000001976] [< 0.0000068742] [< 0.0000065134] [< 0.0000006126] [< 0.0000018441] [< 0.0000017604] [< 0.0000001087] [< 0.0001266708] [< 0.000008732] [< 0.0000058546] [< 0.0000027033] [< 0.0000025951] [< 0.0000000988] [< 0.0000030123] [< 0.0000028779] [< 0.000000168] [< 0.0000048853] [< 0.0000046828] [< 0.0000002075] [< 0.0000238908] [< 0.0000229265] [< 0.0000006102] [< 0.0000020335] [< 0.0000019533] [< 0.0000001025] [< 0.0000094134] [< 0.0000090593] [< 0.000000247] [< 0.0000018344] [< 0.0000017534] [< 0.0000000988]

3.28E-03 3.22E-03 2.77E-05 [< 0.0000019684] [< 0.000001875] [< 0.0000002162] [< 0.0000067584] [< 0.0000063123] [< 0.0000009881] [< 0.000001931] [< 0.0000018469] [< 0.0000000988] [< 0.0000009474] [< 0.000000865] [< 0.0000000988] [< 0.0000023328][< 0.0000022315]

[< 0.0000000988] [< 0.000001762] [< 0.0000016599] [< 0.0000001025] [< 0.0000017379] [< 0.0000016599] [< 0.0000000988] [< 0.0000021084] [< 0.0000020082] [< 0.0000001285] [< 0.0000017958] [< 0.0000017137] [< 0.0000001087] [< 0.0000025682] [< 0.0000024618] [< 0.0000001087] [< 0.0000026913] [< 0.0000025015] [< 0.0000004397] [< 0.000001931] [< 0.0000019802] [< 0.0000001976] [< 0.0000028192] [< 0.0000027026] [< 0.0000001186] [< 0.0000028192] [< 0.0000026792] [< 0.0000002174] [< 0.0000023135] [< 0.0000021625] [< 0.0000005608] [< 0.0000044509] [< 0.000004262] [< 0.0000002075]14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 Flue Gas O2(%) Flue Gas Flow Rate (scfm) Flue Gas Moisture (%) Flue Gas CO2(%)15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,94114.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,81315.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941 14.9 6.9 6.9 3,255,813 15.1 6.92 6.92 3,270,316 15 6.85 6.85 3,228,941Fuel Input Rate Fuel Type Units of Measure

130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 Flue Gas Temperature

(F) Fuel #1129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129 130 130 129Measurement Method Fuel Input Rate Fuel Type Units of Measure Fuel #2Measurement Method Fuel Input Rate Fuel Type Units of Measure Fuel #3Measurement Method Fuel Input Rate Fuel Type Units of Measure Fuel #4Measurement Method Other Supporting InformationEIA

Facility Code Facility Name OH_Zimmer Station Zimmer Steam Station

Speciated Semi-Volatile Organic HAP Emission Data

Acenaphthene 1 Acenaphthene 2 Acenaphthene 3 Acenaphthylene 1 Acenaphthylene 2 Acenaphthylene 3 Anthracene 1 Anthracene 2 Anthracene 3 Benzo(a)anthracene 1 Benzo(a)anthracene 2 Benzo(a)anthracene 3 Benzo(b)fluoranthene 1 Benzo(b)fluoranthene 2 Benzo(b)fluoranthene 3 Benzo(k)fluoranthene 1 Benzo(k)fluoranthene 2 Benzo(k)fluoranthene 3 Benzo(g,h,i)perylene 1 Benzo(g,h,i)perylene 2 Benzo(g,h,i)perylene 3 Benzo(a)pyrene 1 Benzo(a)pyrene 2 Benzo(a)pyrene 3 Benzo(e)pyrene 1 Benzo(e)pyrene 2 Benzo(e)pyrene 3 Chrysene 1 Chrysene 2 Chrysene 3 Dibenzo(a,h)anthracene 1 Dibenzo(a,h)anthracene 2 Dibenzo(a,h)anthracene 3 Fluoranthene 1 Fluoranthene 2 Fluoranthene 3 Fluorene 1 Fluorene 2 Fluorene 3 Indeno(1,2,3-cd)pyrene 1 Indeno(1,2,3-cd)pyrene 2 Indeno(1,2,3-cd)pyrene 3 2-Methylnaphthalene 1 2-Methylnaphthalene 2 2-Methylnaphthalene 3 Naphthalene 1 Naphthalene 2

Compound (use drop down to define for as many rows as

needed) Run NumberNaphthalene 3

Perylene 1 Perylene 2 Perylene 3 Phenanthrene 1 Phenanthrene 2 Phenanthrene 3 Pyrene 1 Pyrene 2 Pyrene 3 1,2,4-Trichlorobenzene 1 1,2,4-Trichlorobenzene 2 1,2,4-Trichlorobenzene 3 1,2-Dichlorobenzene 1 1,2-Dichlorobenzene 2 1,2-Dichlorobenzene 3 1,2-Diphenylhydrazine 1 1,2-Diphenylhydrazine 2 1,2-Diphenylhydrazine 3 1,3-Dichlorobenzene 1 1,3-Dichlorobenzene 2 1,3-Dichlorobenzene 3 1,4-Dichlorobenzene 1 1,4-Dichlorobenzene 2 1,4-Dichlorobenzene 3 Bis(2-chloroisopropyl) ether 1 Bis(2-chloroisopropyl) ether 2 Bis(2-chloroisopropyl) ether 3 2,4,5-Trichlorophenol 1 2,4,5-Trichlorophenol 2 2,4,5-Trichlorophenol 3 2,4,6-Trichlorophenol 1 2,4,6-Trichlorophenol 2 2,4,6-Trichlorophenol 3 2,4-Dichlorophenol 1 2,4-Dichlorophenol 2 2,4-Dichlorophenol 3 2,4-Dimethylphenol 1 2,4-Dimethylphenol 2 2,4-Dimethylphenol 3 2,4-Dinitrophenol 1 2,4-Dinitrophenol 2 2,4-Dinitrophenol 3 2,4-Dinitrotoluene 1 2,4-Dinitrotoluene 2 2,4-Dinitrotoluene 3 2,6-Dinitrotoluene 1 2,6-Dinitrotoluene 2 2,6-Dinitrotoluene 3 2-Chloronaphthalene 1 2-Chloronaphthalene 2 2-Chloronaphthalene 3 2-Chlorophenol 1 2-Chlorophenol 2 2-Chlorophenol 32-Methylphenol 1

2-Methylphenol 2 2-Methylphenol 3 2-Nitroaniline 1 2-Nitroaniline 2 2-Nitroaniline 3 2-Nitrophenol 1 2-Nitrophenol 2 2-Nitrophenol 3 3,3'-Dichlorobenzidine 1 3,3'-Dichlorobenzidine 2 3,3'-Dichlorobenzidine 3 3-Methylphenol 1 3-Methylphenol 2 3-Methylphenol 3 3-Nitroaniline 1 3-Nitroaniline 2 3-Nitroaniline 3 4,6-Dinitro-2-methylphenol 1 4,6-Dinitro-2-methylphenol 2 4,6-Dinitro-2-methylphenol 3 4-Bromophenyl phenyl ether 1 4-Bromophenyl phenyl ether 2 4-Bromophenyl phenyl ether 3 4-Chloro-3-methylphenol 1 4-Chloro-3-methylphenol 2 4-Chloro-3-methylphenol 3 4-Chloroaniline 1 4-Chloroaniline 2 4-Chloroaniline 3 4-Chlorophenyl phenyl ether 1 4-Chlorophenyl phenyl ether 2 4-Chlorophenyl phenyl ether 3 4-Nitroaniline 1 4-Nitroaniline 2 4-Nitroaniline 3 4-Nitrophenol 1 4-Nitrophenol 2 4-Nitrophenol 3 Acetophenone 1 Acetophenone 2 Acetophenone 3 Aniline 1 Aniline 2 Aniline 3 Benzidine 1 Benzidine 2 Benzidine 3 Benzoic acid 1 Benzoic acid 2 Benzoic acid 3 Benzyl alcohol 1 Benzyl alcohol 2 Benzyl alcohol 3 Bis(2-chloroethoxy)methane 1Bis(2-chloroethoxy)methane 2

Bis(2-chloroethoxy)methane 3 Bis(2-chloroethyl) ether 1 Bis(2-chloroethyl) ether 2 Bis(2-chloroethyl) ether 3 Bis(2-ethylhexyl) phthalate 1 Bis(2-ethylhexyl) phthalate 2 Bis(2-ethylhexyl) phthalate 3 Butyl benzyl phthalate 1 Butyl benzyl phthalate 2 Butyl benzyl phthalate 3 Carbazole 1 Carbazole 2 Carbazole 3 Dibenzofuran 1 Dibenzofuran 2 Dibenzofuran 3 Diethyl phthalate 1 Diethyl phthalate 2 Diethyl phthalate 3 Dim ethyl phthalate 1 Dim ethyl phthalate 2 Dim ethyl phthalate 3 Di-n-butyl phthalate 1 Di-n-butyl phthalate 2 Di-n-butyl phthalate 3 Di-n-octyl phthalate 1 Di-n-octyl phthalate 2 Di-n-octyl phthalate 3 Hexachlorobenzene 1 Hexachlorobenzene 2 Hexachlorobenzene 3 Hexachlorobutadiene 1 Hexachlorobutadiene 2 Hexachlorobutadiene 3 Hexachlorocyclopentadiene 1 Hexachlorocyclopentadiene 2 Hexachlorocyclopentadiene 3 Hexachloroethane 1 Hexachloroethane 2 Hexachloroethane 3 Isophorone 1 Isophorone 2 Isophorone 3 Nitrobenzene 1 Nitrobenzene 2 Nitrobenzene 3 N-Nitrosodimethylam ine 1 N-Nitrosodimethylam ine 2 N-Nitrosodimethylam ine 3 N-Nitrosodi-n-propylam ine 1 N-Nitrosodi-n-propylam ine 2 N-Nitrosodi-n-propylam ine 3 N-Nitrosodiphenylam ine 1 N-Nitrosodiphenylam ine 2N-Nitrosodiphenylam ine 3

Pentachlorobenzene 1 Pentachlorobenzene 2 Pentachlorobenzene 3 Pentachloronitrobenzene 1 Pentachloronitrobenzene 2 Pentachloronitrobenzene 3 Pentachlorophenol 1 Pentachlorophenol 2 Pentachlorophenol 3 Phenol 1 Phenol 2 Phenol 3 Pyridine 1 Pyridine 2 Pyridine 3Boiler ID

U1

4/21/2010 9:25 AM 4/21/2010

4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 Test Start Date Test Start Time Test End Date4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/20104/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/20104/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/20104/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010 4/21/2010 9:25 AM 4/21/2010 4/21/2010 12:08 PM 4/21/2010 4/21/2010 2:50 PM 4/21/2010Measured Value (μg/m3) Data Flag (ADL, BDL, DDL)

11:41 AM [< 0.0276] DLL, DL based on MDL 2:24 PM [< 0.0432] DLL, DL based on MDL 5:06 PM [< 0.0461] DLL, DL based on MDL 11:41 AM [< 0.0033] DLL, DL based on MDL 2:24 PM [< 0.0045] DLL, DL based on MDL 5:06 PM [< 0.0071] DLL, DL based on MDL 11:41 AM [< 0.0066] DLL, DL based on MDL 2:24 PM [< 0.0063] DLL, DL based on MDL 5:06 PM [< 0.009] DLL, DL based on MDL 11:41 AM [< 0.0042] DLL, DL based on MDL 2:24 PM [< 0.0037] BDL, DL based on MDL 5:06 PM [< 0.0043] DLL, DL based on MDL 11:41 AM [< 0.0241] DLL, DL based on MDL 2:24 PM [< 0.007] DLL, DL based on MDL 5:06 PM [< 0.0064] BDL, DL based on MDL 11:41 AM [< 0.0408] BDL, DL based on MDL 2:24 PM [< 0.0422] BDL, DL based on MDL 5:06 PM [< 0.043] BDL, DL based on MDL 11:41 AM [< 0.0049] BDL, DL based on MDL 2:24 PM [< 0.005] BDL, DL based on MDL 5:06 PM [< 0.0051] BDL, DL based on MDL 11:41 AM 0.0235 ADL 2:24 PM 0.0060 ADL 5:06 PM 0.0077 ADL 11:41 AM [< 0.0053] BDL, DL based on MDL 2:24 PM [< 0.0055] BDL, DL based on MDL 5:06 PM [< 0.0056] BDL, DL based on MDL 11:41 AM [< 0.0185] DLL, DL based on MDL 2:24 PM [< 0.0098] DLL, DL based on MDL 5:06 PM [< 0.0175] DLL, DL based on MDL 11:41 AM [< 0.0037] BDL, DL based on MDL 2:24 PM [< 0.0048] BDL, DL based on MDL 5:06 PM [< 0.0039] BDL, DL based on MDL 11:41 AM [< 0.0232] DLL, DL based on MDL 2:24 PM [< 0.0211] DLL, DL based on MDL 5:06 PM [< 0.0516] DLL, DL based on MDL 11:41 AM [< 0.0671] DLL, DL based on MDL 2:24 PM [< 0.0586] DLL, DL based on MDL 5:06 PM [< 0.0849] DLL, DL based on MDL 11:41 AM [< 0.0025] BDL, DL based on MDL 2:24 PM [< 0.0026] BDL, DL based on MDL 5:06 PM [< 0.0027] BDL, DL based on MDL 11:41 AM [< 0.1938] DLL, DL based on MDL 2:24 PM [< 0.2102] DLL, DL based on MDL 5:06 PM [< 0.2446] DLL, DL based on MDL 11:41 AM [< 0.3438] DLL, DL based on MDL 2:24 PM [< 0.3604] DLL, DL based on MDL Test End Time5:06 PM [< 0.4379] DLL, DL based on MDL 11:41 AM [< 0.0029] BDL, DL based on MDL 2:24 PM [< 0.003] BDL, DL based on MDL 5:06 PM [< 0.0031] BDL, DL based on MDL 11:41 AM [< 0.1233] DLL, DL based on MDL 2:24 PM [< 0.1388] DLL, DL based on MDL 5:06 PM [< 0.1868] DLL, DL based on MDL 11:41 AM [< 0.0411] DLL, DL based on MDL 2:24 PM [< 0.0406] DLL, DL based on MDL 5:06 PM [< 0.0615] DLL, DL based on MDL 11:41 AM [< 3.1428] BDL, DL based on MDL 2:24 PM [< 3.0527] BDL, DL based on MDL 5:06 PM [< 3.1135] BDL, DL based on MDL 11:41 AM [< 3.238] BDL, DL based on MDL 2:24 PM [< 3.2496] BDL, DL based on MDL 5:06 PM [< 3.3144] BDL, DL based on MDL 11:41 AM [< 2.6666] BDL, DL based on MDL 2:24 PM [< 2.6095] BDL, DL based on MDL 5:06 PM [< 2.6616] BDL, DL based on MDL 11:41 AM [< 3.1428] BDL, DL based on MDL 2:24 PM [< 2.9542] BDL, DL based on MDL 5:06 PM [< 3.0131] BDL, DL based on MDL 11:41 AM [< 2.9999] BDL, DL based on MDL 2:24 PM [< 2.8557] BDL, DL based on MDL 5:06 PM [< 2.9126] BDL, DL based on MDL 11:41 AM [< 3.238] BDL, DL based on MDL 2:24 PM [< 3.0527] BDL, DL based on MDL 5:06 PM [< 3.1135] BDL, DL based on MDL 11:41 AM [< 2.5714] BDL, DL based on MDL 2:24 PM [< 2.0679] BDL, DL based on MDL 5:06 PM [< 2.1092] BDL, DL based on MDL 11:41 AM [< 2.7142] BDL, DL based on MDL 2:24 PM [< 2.5603] BDL, DL based on MDL 5:06 PM [< 2.6113] BDL, DL based on MDL 11:41 AM [< 2.8095] BDL, DL based on MDL 2:24 PM [< 2.4618] BDL, DL based on MDL 5:06 PM [< 2.5109] BDL, DL based on MDL 11:41 AM [< 6.2855] BDL, DL based on MDL 2:24 PM [< 8.2717] BDL, DL based on MDL 5:06 PM [< 8.4366] BDL, DL based on MDL 11:41 AM [< 40.9513] BDL, DL based on MDL 2:24 PM [< 46.2822] BDL, DL based on MDL 5:06 PM [< 47.2049] BDL, DL based on MDL 11:41 AM [< 6.1903] BDL, DL based on MDL 2:24 PM [< 6.1053] BDL, DL based on MDL 5:06 PM [< 6.227] BDL, DL based on MDL 11:41 AM [< 6.2855] BDL, DL based on MDL 2:24 PM [< 6.3023] BDL, DL based on MDL 5:06 PM [< 6.4279] BDL, DL based on MDL 11:41 AM [< 2.9523] BDL, DL based on MDL 2:24 PM [< 2.7572] BDL, DL based on MDL 5:06 PM [< 2.8122] BDL, DL based on MDL 11:41 AM [< 2.9047] BDL, DL based on MDL 2:24 PM [< 2.8557] BDL, DL based on MDL 5:06 PM [< 2.9126] BDL, DL based on MDL11:41 AM [< 2.5237] BDL, DL based on MDL 2:24 PM [< 2.3633] BDL, DL based on MDL 5:06 PM [< 2.4105] BDL, DL based on MDL 11:41 AM [< 3.9047] BDL, DL based on MDL 2:24 PM [< 3.9389] BDL, DL based on MDL 5:06 PM [< 4.0174] BDL, DL based on MDL 11:41 AM [< 3.9047] BDL, DL based on MDL 2:24 PM [< 3.9389] BDL, DL based on MDL 5:06 PM [< 4.0174] BDL, DL based on MDL 11:41 AM [< 7.9046] BDL, DL based on MDL 2:24 PM [< 12.703] BDL, DL based on MDL 5:06 PM [< 12.9562] BDL, DL based on MDL 11:41 AM [< 5.238] BDL, DL based on MDL 2:24 PM [< 4.9236] BDL, DL based on MDL 5:06 PM [< 5.0218] BDL, DL based on MDL 11:41 AM [< 14.952] BDL, DL based on MDL 2:24 PM [< 20.3839] BDL, DL based on MDL 5:06 PM [< 20.7902] BDL, DL based on MDL 11:41 AM [< 9.3331] BDL, DL based on MDL 2:24 PM [< 5.8099] BDL, DL based on MDL 5:06 PM [< 5.9257] BDL, DL based on MDL 11:41 AM [< 3.7142] BDL, DL based on MDL 2:24 PM [< 3.3481] BDL, DL based on MDL 5:06 PM [< 3.4148] BDL, DL based on MDL 11:41 AM [< 3.8094] BDL, DL based on MDL 2:24 PM [< 3.3481] BDL, DL based on MDL 5:06 PM [< 3.4148] BDL, DL based on MDL 11:41 AM [< 6.9522] BDL, DL based on MDL 2:24 PM [< 10.1427] BDL, DL based on MDL 5:06 PM [< 10.3449] BDL, DL based on MDL 11:41 AM [< 2.9999] BDL, DL based on MDL 2:24 PM [< 2.6095] BDL, DL based on MDL 5:06 PM [< 2.6616] BDL, DL based on MDL 11:41 AM [< 9.8093] BDL, DL based on MDL 2:24 PM [< 13.7862] BDL, DL based on MDL 5:06 PM [< 14.061] BDL, DL based on MDL 11:41 AM [< 17.1424] BDL, DL based on MDL 2:24 PM [< 15.2633] BDL, DL based on MDL 5:06 PM [< 15.5676] BDL, DL based on MDL 11:41 AM [< 5.3808] DLL, DL based on MDL 2:24 PM [< 4.7267] DLL, DL based on MDL 5:06 PM [< 5.1222] DLL, DL based on MDL 11:41 AM [< 8.1903] BDL, DL based on MDL 2:24 PM [< 11.8167] BDL, DL based on MDL 5:06 PM [< 12.0523] BDL, DL based on MDL 11:41 AM [< 56.5699] BDL, DL based on MDL 2:24 PM [< 104.8735] BDL, DL based on MDL 5:06 PM [< 106.9642] BDL, DL based on MDL 11:41 AM [< 76.1885] DLL, DL based on MDL 2:24 PM [< 71.8851] DLL, DL based on MDL 5:06 PM [< 82.8596] DLL, DL based on MDL 11:41 AM [< 5.3332] BDL, DL based on MDL 2:24 PM [< 5.416] BDL, DL based on MDL 5:06 PM [< 5.524] BDL, DL based on MDL 11:41 AM [< 2.3809] BDL, DL based on MDL2:24 PM [< 2.2649] BDL, DL based on MDL 5:06 PM [< 2.31] BDL, DL based on MDL 11:41 AM [< 3.0952] BDL, DL based on MDL 2:24 PM [< 2.9542] BDL, DL based on MDL 5:06 PM [< 3.0131] BDL, DL based on MDL 11:41 AM [< 10.2854] BDL, DL based on MDL 2:24 PM [< 16.3465] BDL, DL based on MDL 5:06 PM [< 16.6724] BDL, DL based on MDL 11:41 AM [< 4.2856] BDL, DL based on MDL 2:24 PM [< 4.0374] BDL, DL based on MDL 5:06 PM [< 4.1179] BDL, DL based on MDL 11:41 AM [< 2.8571] BDL, DL based on MDL 2:24 PM [< 2.2649] BDL, DL based on MDL 5:06 PM [< 2.31] BDL, DL based on MDL 11:41 AM [< 2.619] BDL, DL based on MDL 2:24 PM [< 2.3141] BDL, DL based on MDL 5:06 PM [< 2.3602] BDL, DL based on MDL 11:41 AM [< 3.0952] BDL, DL based on MDL 2:24 PM [< 2.4618] BDL, DL based on MDL 5:06 PM [< 2.5109] BDL, DL based on MDL 11:41 AM [< 2.8095] BDL, DL based on MDL 2:24 PM [< 2.2156] BDL, DL based on MDL 5:06 PM [< 2.2598] BDL, DL based on MDL 11:41 AM [< 4.4761] BDL, DL based on MDL 2:24 PM [< 4.0374] BDL, DL based on MDL 5:06 PM [< 4.1179] BDL, DL based on MDL 11:41 AM [< 4.3808] BDL, DL based on MDL 2:24 PM [< 4.6282] BDL, DL based on MDL 5:06 PM [< 4.7205] BDL, DL based on MDL 11:41 AM [< 3.1428] BDL, DL based on MDL 2:24 PM [< 2.9542] BDL, DL based on MDL 5:06 PM [< 3.0131] BDL, DL based on MDL 11:41 AM [< 2.619] BDL, DL based on MDL 2:24 PM [< 2.5111] BDL, DL based on MDL 5:06 PM [< 2.5611] BDL, DL based on MDL 11:41 AM [< 22.8565] BDL, DL based on MDL 2:24 PM [< 23.6335] BDL, DL based on MDL 5:06 PM [< 24.1046] BDL, DL based on MDL 11:41 AM [< 2.8095] BDL, DL based on MDL 2:24 PM [< 2.9542] BDL, DL based on MDL 5:06 PM [< 3.0131] BDL, DL based on MDL 11:41 AM [< 2.7142] BDL, DL based on MDL 2:24 PM [< 2.2649] BDL, DL based on MDL 5:06 PM [< 2.31] BDL, DL based on MDL 11:41 AM [< 2.7142] BDL, DL based on MDL 2:24 PM [< 2.6588] BDL, DL based on MDL 5:06 PM [< 2.7118] BDL, DL based on MDL 11:41 AM [< 2.9999] BDL, DL based on MDL 2:24 PM [< 2.9542] BDL, DL based on MDL 5:06 PM [< 3.0131] BDL, DL based on MDL 11:41 AM [< 2.9999] BDL, DL based on MDL 2:24 PM [< 2.708] BDL, DL based on MDL 5:06 PM [< 2.762] BDL, DL based on MDL 11:41 AM [< 3.3809] BDL, DL based on MDL 2:24 PM [< 2.8557] BDL, DL based on MDL5:06 PM [< 2.9126] BDL, DL based on MDL 11:41 AM [< 2.9999] BDL, DL based on MDL 2:24 PM [< 3.6435] BDL, DL based on MDL 5:06 PM [< 3.7161] BDL, DL based on MDL 11:41 AM [< 6.3808] BDL, DL based on MDL 2:24 PM [< 7.287] BDL, DL based on MDL 5:06 PM [< 7.4323] BDL, DL based on MDL 11:41 AM [< 8.095] BDL, DL based on MDL 2:24 PM [< 8.5671] BDL, DL based on MDL 5:06 PM [< 8.7379] BDL, DL based on MDL 11:41 AM [< 14.4758] DLL, DL based on MDL 2:24 PM [< 7.5332] DLL, DL based on MDL 5:06 PM [< 11.0479] DLL, DL based on MDL 11:41 AM [< 8.1903] BDL, DL based on MDL 2:24 PM [< 7.6809] BDL, DL based on MDL 5:06 PM [< 7.834] BDL, DL based on MDLFront Half mass* (ng) Back Half mass* (ng) Condensate Mass*** (ng)

44.00 9.20 [< 4.8] 61.00 22.00 [< 4.8] 62.00 25.00 [< 4.8] 3.60 [< 3] [< 0.3] 5.80 [< 3] [< 0.3] 5.70 [< 8.2] [< 0.3] 3.00 9.40 [< 1.4] 4.20 7.20 [< 1.4] 3.60 13.00 [< 1.4] [< 1.5] 4.40 [< 3] [< 1.5] [< 3] [< 3] [< 1.5] 4.00 [< 3]

4.70 43.00 [< 3] 4.60 [< 6.6] [< 3] [< 3.2] [< 6.6] [< 3] [< 1.7] [< 82] [< 2] [< 1.7] [< 82] [< 2] [< 1.7] [< 82] [< 2] [< 5.6] [< 3.6] [< 1] [< 5.6] [< 3.6] [< 1] [< 5.6] [< 3.6] [< 1]

4.10 43.00 2.30 4.60 5.80 1.70 4.70 7.90 2.80 [< 2.8] [< 5.6] [< 2.8] [< 2.8] [< 5.6] [< 2.8] [< 2.8] [< 5.6] [< 2.8] [< 1.5] 36.00 1.40 [< 1.5] 18.00 [< 0.44] [< 1.5] 33.00 [< 0.44] [< 2.6] [< 3.6] [< 1.6] [< 2.6] [< 5.6] [< 1.6] [< 2.6] [< 3.6] [< 1.6]

7.00 37.00 [< 4.8] 10.00 28.00 [< 4.8] 9.90 88.00 [< 4.8] 28.00 110.00 [< 3] 42.00 74.00 [< 3] 46.00 120.00 [< 3] [< 1.5] [< 1.8] [< 2] [< 1.5] [< 1.8] [< 2] [< 1.5] [< 1.8] [< 2]

140.00 250.00 [< 17] 200.00 210.00 [< 17] 210.00 260.00 [< 17] 140.00 550.00 [< 32] 200.00 500.00 [< 32] Semi-Volatile Organic HAP Emission Test Results200.00 640.00 [< 32] [< 1.5] [< 3] [< 1.6] [< 1.5] [< 3] [< 1.6] [< 1.5] [< 3] [< 1.6]

67.00 170.00 [< 22] 110.00 150.00 [< 22] 110.00 240.00 [< 22] [< 60] 23.00 [< 3.4] [< 60] 19.00 [< 3.4] [< 60] 59.00 [< 3.4] [< 2400] [< 2000] [< 2200] [< 2000] [< 2000] [< 2200] [< 2000] [< 2000] [< 2200] [< 2400] [< 2200] [< 2200] [< 2200] [< 2200] [< 2200] [< 2200] [< 2200] [< 2200] [< 2000] [< 1700] [< 1900] [< 1700] [< 1700] [< 1900] [< 1700] [< 1700] [< 1900] [< 2400] [< 1800] [< 2400] [< 1800] [< 1800] [< 2400] [< 1800] [< 1800] [< 2400] [< 2400] [< 1900] [< 2000] [< 1900] [< 1900] [< 2000] [< 1900] [< 1900] [< 2000] [< 2600] [< 2000] [< 2200] [< 2000] [< 2000] [< 2200] [< 2000] [< 2000] [< 2200] [< 2600] [< 1400] [< 1400] [< 1400] [< 1400] [< 1400] [< 1400] [< 1400] [< 1400] [< 2400] [< 1900] [< 1400] [< 1900] [< 1900] [< 1400] [< 1900] [< 1900] [< 1400] [< 2600] [< 1700] [< 1600] [< 1700] [< 1700] [< 1600] [< 1700] [< 1700] [< 1600] [< 3400] [< 7000] [< 2800] [< 7000] [< 7000] [< 2800] [< 7000] [< 7000] [< 2800] [< 14000] [< 22000] [< 50000] [< 22000] [< 22000] [< 50000] [< 22000] [< 22000] [< 50000] [< 2800] [< 2200] [< 8000] [< 2200] [< 2200] [< 8000] [< 2200] [< 2200] [< 8000] [< 2800] [< 2400] [< 8000] [< 2400] [< 2400] [< 8000] [< 2400] [< 2400] [< 8000] [< 2400] [< 1800] [< 2000] [< 1800] [< 1800] [< 2000] [< 1800] [< 1800] [< 2000] [< 2200] [< 1900] [< 2000] [< 1900] [< 1900] [< 2000] [< 1900] [< 1900] [< 2000][< 2200] [< 1700] [< 1400] [< 1700] [< 1700] [< 1400] [< 1700] [< 1700] [< 1400] [< 2200] [< 2000] [< 4000] [< 2000] [< 2000] [< 4000] [< 2000] [< 2000] [< 4000] [< 2200] [< 2000] [< 4000] [< 2000] [< 2000] [< 4000] [< 2000] [< 2000] [< 4000] [< 2800] [< 12000] [< 1800] [< 12000] [< 12000] [< 1800] [< 12000] [< 12000] [< 1800] [< 4400] [< 3400] [< 3200] [< 3400] [< 3400] [< 3200] [< 3400] [< 3400] [< 3200] [< 10000] [< 20000] [< 1400] [< 20000] [< 20000] [< 1400] [< 20000] [< 20000] [< 1400] [< 10000] [< 2200] [< 7400] [< 2200] [< 2200] [< 7400] [< 2200] [< 2200] [< 7400] [< 3200] [< 2200] [< 2400] [< 2200] [< 2200] [< 2400] [< 2200] [< 2200] [< 2400] [< 2600] [< 1400] [< 4000] [< 1400] [< 1400] [< 4000] [< 1400] [< 1400] [< 4000] [< 2600] [< 8600] [< 3400] [< 8600] [< 8600] [< 3400] [< 8600] [< 8600] [< 3400] [< 2800] [< 1800] [< 1700] [< 1800] [< 1800] [< 1700] [< 1800] [< 1800] [< 1700] [< 2600] [< 10000] [< 8000] [< 10000] [< 10000] [< 8000] [< 10000] [< 10000] [< 8000] [< 15000] [< 10000] [< 11000] [< 10000] [< 10000] [< 11000] [< 10000] [< 10000] [< 11000] [< 1100] 8200.00 [< 2000] [< 1900] 5700.00 [< 2000] [< 1900] 6300.00 [< 2000] [< 3200] [< 10000] [< 4000] [< 10000] [< 10000] [< 4000] [< 10000] [< 10000] [< 4000] [< 5800] [< 100000] [< 13000] [< 100000] [< 100000] [< 13000] [< 100000] [< 100000] [< 13000] [< 30000] 80000.00 [< 50000] [< 38000] 58000.00 [< 50000] [< 38000] 77000.00 [< 50000] [< 4600] [< 4400] [< 2200] [< 4400] [< 4400] [< 2200] [< 4400] [< 4400] [< 2200] [< 1900] [< 1500] [< 1600][< 1500] [< 1500] [< 1600] [< 1500] [< 1500] [< 1600] [< 2400] [< 1900] [< 2200] [< 1900] [< 1900] [< 2200] [< 1900] [< 1900] [< 2200] [< 3400] [< 15000] [< 3200] [< 15000] [< 15000] [< 3200] [< 15000] [< 15000] [< 3200] [< 3400] [< 2600] [< 3000] [< 2600] [< 2600] [< 3000] [< 2600] [< 2600] [< 3000] [< 2400] [< 1000] [< 2600] [< 1000] [< 1000] [< 2600] [< 1000] [< 1000] [< 2600] [< 2400] [< 1600] [< 1500] [< 1600] [< 1600] [< 1500] [< 1600] [< 1600] [< 1500] [< 3000] [< 1500] [< 2000] [< 1500] [< 1500] [< 2000] [< 1500] [< 1500] [< 2000] [< 2800] [< 1400] [< 1700] [< 1400] [< 1400] [< 1700] [< 1400] [< 1400] [< 1700] [< 3400] [< 2200] [< 3800] [< 2200] [< 2200] [< 3800] [< 2200] [< 2200] [< 3800] [< 3400] [< 3600] [< 2200] [< 3600] [< 3600] [< 2200] [< 3600] [< 3600] [< 2200] [< 2600] [< 2000] [< 2000] [< 2000] [< 2000] [< 2000] [< 2000] [< 2000] [< 2000] [< 2000] [< 1600] [< 1900] [< 1600] [< 1600] [< 1900] [< 1600] [< 1600] [< 1900] [< 20000] [< 20000] [< 8000] [< 20000] [< 20000] [< 8000] [< 20000] [< 20000] [< 8000] [< 1900] [< 2000] [< 2000] [< 2000] [< 2000] [< 2000] [< 2000] [< 2000] [< 2000] [< 2600] [< 1500] [< 1600] [< 1500] [< 1500] [< 1600] [< 1500] [< 1500] [< 1600] [< 2000] [< 1700] [< 2000] [< 1700] [< 1700] [< 2000] [< 1700] [< 1700] [< 2000] [< 2200] [< 1900] [< 2200] [< 1900] [< 1900] [< 2200] [< 1900] [< 1900] [< 2200] [< 2600] [< 1800] [< 1900] [< 1800] [< 1800] [< 1900] [< 1800] [< 1800] [< 1900] [< 3000] [< 1700] [< 2400] [< 1700] [< 1700] [< 2400][< 1700] [< 1700] [< 2400] [< 1500] [< 2600] [< 2200] [< 2600] [< 2600] [< 2200] [< 2600] [< 2600] [< 2200] [< 2000] [< 3400] [< 8000] [< 3400] [< 3400] [< 8000] [< 3400] [< 3400] [< 8000] [< 2800] [< 3200] [< 11000] [< 3200] [< 3200] [< 11000] [< 3200] [< 3200] [< 11000] [< 2400] 10000.00 18000.00 [< 1800] 4800.00 8700.00 [< 1800] 7200.00 13000.00 [< 5400] [< 3800] [< 8000] [< 3800] [< 3800] [< 8000] [< 3800] [< 3800] [< 8000]Total Composite (ng) Test Method Comments lb/mmBtu

[< 58] [< 0.0000000254] [< 87.8] [< 0.0000000397] [< 91.8] [< 0.0000000423] [< 6.9] Method Blank Contamination [< 0.000000003] [< 9.1] Method Blank Contamination [< 0.0000000041] [< 14.2] Method Blank Contamination [< 0.0000000065] [< 13.8] [< 0.000000006] [< 12.8] [< 0.0000000058] [< 18] [< 0.0000000083] [< 8.9] [< 0.0000000039] [< 7.5] [< 0.0000000034] [< 8.5] [< 0.0000000039] [< 50.7] [< 0.0000000222] [< 14.2] [< 0.0000000064] [< 12.8] [< 0.0000000059] [< 85.7] [< 0.0000000375] [< 85.7] [< 0.0000000387] [< 85.7] [< 0.0000000395] [< 10.2] [< 0.0000000045] [< 10.2] [< 0.0000000046] [< 10.2] [< 0.0000000047] 49.4 Method Blank Contamination 2.16E-08 12.1 Method Blank Contamination 5.50E-09 15.4 Method Blank Contamination 7.10E-09 [< 11.2] [< 0.0000000049] [< 11.2] [< 0.0000000051] [< 11.2] [< 0.0000000052] [< 38.9] [< 0.000000017] [< 19.94] [< 0.000000009] [< 34.94] [< 0.0000000161] [< 7.8] [< 0.0000000034] [< 9.8] [< 0.0000000044] [< 7.8] [< 0.0000000036] [< 48.8] [< 0.0000000213] [< 42.8] [< 0.0000000193] [< 102.7] [< 0.0000000473] [< 141] [< 0.0000000616] [< 119] [< 0.0000000538] [< 169] [< 0.0000000779] [< 5.3] [< 0.0000000023] [< 5.3] [< 0.0000000024] [< 5.3] [< 0.0000000024] [< 407] Method Blank Contamination [< 0.0000001779] [< 427] Method Blank Contamination [< 0.000000193] [< 487] Method Blank Contamination [< 0.0000002245] [< 722] Method Blank Contamination [< 0.0000003156] [< 732] Method Blank Contamination [< 0.0000003309] Calculated Emission Rate[< 872] Method Blank Contamination [< 0.000000402] [< 6.1] [< 0.0000000027] [< 6.1] [< 0.0000000028] [< 6.1] [< 0.0000000028] [< 259] [< 0.0000001132] [< 282] [< 0.0000001275] [< 372] [< 0.0000001715] [< 86.4] [< 0.0000000378] [< 82.4] [< 0.0000000372] [< 122.4] [< 0.0000000564] [< 6600] [< 0.0000028851] [< 6200] [< 0.0000028024] [< 6200] [< 0.0000028583] [< 6800] [< 0.0000029725] [< 6600] [< 0.0000029832] [< 6600] [< 0.0000030427] [< 5600] [< 0.000002448] [< 5300] [< 0.0000023956] [< 5300] [< 0.0000024433] [< 6600] [< 0.0000028851] [< 6000] [< 0.000002712] [< 6000] [< 0.0000027661] [< 6300] [< 0.000002754] [< 5800] [< 0.0000026216] [< 5800] [< 0.0000026739] [< 6800] [< 0.0000029725] [< 6200] [< 0.0000028024] [< 6200] [< 0.0000028583] [< 5400] [< 0.0000023606] [< 4200] [< 0.0000018984] [< 4200] [< 0.0000019362] [< 5700] [< 0.0000024917] [< 5200] [< 0.0000023504] [< 5200] [< 0.0000023972] [< 5900] [< 0.0000025791] [< 5000] [< 0.00000226] [< 5000] [< 0.000002305] [< 13200] [< 0.0000057702] [< 16800] [< 0.0000075936] [< 16800] [< 0.000007745] [< 86000] [< 0.000037594] [< 94000] [< 0.0000424878] [< 94000] [< 0.0000433348] [< 13000] [< 0.0000056828] [< 12400] [< 0.0000056048] [< 12400] [< 0.0000057165] [< 13200] [< 0.0000057702] [< 12800] [< 0.0000057856] [< 12800] [< 0.0000059009] [< 6200] [< 0.0000027103] [< 5600] [< 0.0000025312] [< 5600] [< 0.0000025817] [< 6100] [< 0.0000026665] [< 5800] [< 0.0000026216] [< 5800] [< 0.0000026739][< 5300] [< 0.0000023168] [< 4800] [< 0.0000021696] [< 4800] [< 0.0000022128] [< 8200] [< 0.0000035845] [< 8000] [< 0.000003616] [< 8000] [< 0.0000036881] [< 8200] [< 0.0000035845] [< 8000] [< 0.000003616] [< 8000] [< 0.0000036881] [< 16600] [< 0.0000072565] [< 25800] [< 0.0000116615] [< 25800] [< 0.000011894] [< 11000] [< 0.0000048085] [< 10000] [< 0.00000452] [< 10000] [< 0.0000046101] [< 31400] [< 0.0000137262] [< 41400] [< 0.0000187127] [< 41400] [< 0.0000190858] [< 19600] [< 0.0000085679] [< 11800] [< 0.0000053336] [< 11800] [< 0.0000054399] [< 7800] [< 0.0000034097] [< 6800] [< 0.0000030736] [< 6800] [< 0.0000031349] [< 8000] [< 0.0000034971] [< 6800] [< 0.0000030736] [< 6800] [< 0.0000031349] [< 14600] [< 0.0000063822] [< 20600] [< 0.0000093112] [< 20600] [< 0.0000094968] [< 6300] [< 0.000002754] [< 5300] [< 0.0000023956] [< 5300] [< 0.0000024433] [< 20600] [< 0.0000090051] [< 28000] [< 0.0000126559] [< 28000] [< 0.0000129083] [< 36000] [< 0.000015737] [< 31000] [< 0.0000140119] [< 31000] [< 0.0000142913] [< 11300] [< 0.0000049397] [< 9600] [< 0.0000043392] [< 10200] [< 0.0000047023] [< 17200] [< 0.0000075188] [< 24000] [< 0.0000108479] [< 24000] [< 0.0000110642] [< 118800] [< 0.0000519321] [< 213000] [< 0.0000962756] [< 213000] [< 0.0000981949] [< 160000] [< 0.0000699423] [< 146000] [< 0.0000659917] [< 165000] [< 0.0000760665] [< 11200] [< 0.000004896] [< 11000] [< 0.000004972] [< 11000] [< 0.0000050711] [< 5000] [< 0.0000021857][< 4600] [< 0.0000020792] [< 4600] [< 0.0000021206] [< 6500] [< 0.0000028414] [< 6000] [< 0.000002712] [< 6000] [< 0.0000027661] [< 21600] [< 0.0000094422] [< 33200] [< 0.0000150063] [< 33200] [< 0.0000153055] [< 9000] [< 0.0000039343] [< 8200] [< 0.0000037064] [< 8200] [< 0.0000037803] [< 6000] [< 0.0000026228] [< 4600] [< 0.0000020792] [< 4600] [< 0.0000021206] [< 5500] [< 0.0000024043] [< 4700] [< 0.0000021244] [< 4700] [< 0.0000021667] [< 6500] [< 0.0000028414] [< 5000] [< 0.00000226] [< 5000] [< 0.000002305] [< 5900] [< 0.0000025791] [< 4500] [< 0.000002034] [< 4500] [< 0.0000020745] [< 9400] [< 0.0000041091] [< 8200] [< 0.0000037064] [< 8200] [< 0.0000037803] [< 9200] [< 0.0000040217] [< 9400] [< 0.0000042488] [< 9400] [< 0.0000043335] [< 6600] [< 0.0000028851] [< 6000] [< 0.000002712] [< 6000] [< 0.0000027661] [< 5500] [< 0.0000024043] [< 5100] [< 0.0000023052] [< 5100] [< 0.0000023511] [< 48000] [< 0.0000209827] [< 48000] [< 0.0000216959] [< 48000] [< 0.0000221284] [< 5900] [< 0.0000025791] [< 6000] [< 0.000002712] [< 6000] [< 0.0000027661] [< 5700] [< 0.0000024917] [< 4600] [< 0.0000020792] [< 4600] [< 0.0000021206] [< 5700] [< 0.0000024917] [< 5400] [< 0.0000024408] [< 5400] [< 0.0000024894] [< 6300] [< 0.000002754] [< 6000] [< 0.000002712] [< 6000] [< 0.0000027661] [< 6300] [< 0.000002754] [< 5500] [< 0.000002486] [< 5500] [< 0.0000025355] [< 7100] [< 0.0000031037] [< 5800] [< 0.0000026216][< 5800] [< 0.0000026739] [< 6300] [< 0.000002754] [< 7400] [< 0.0000033448] [< 7400] [< 0.0000034115] [< 13400] [< 0.0000058577] [< 14800] [< 0.0000066896] [< 14800] [< 0.0000068229] [< 17000] [< 0.0000074314] [< 17400] [< 0.0000078648] [< 17400] [< 0.0000080216] [< 30400] [< 0.000013289] [< 15300] [< 0.0000069156] [< 22000] [< 0.0000101422] [< 17200] [< 0.0000075188] [< 15600] [< 0.0000070512] [< 15600] [< 0.0000071917]ppmdv @ 7% O2 Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat Input (mmBtu/hr)13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 Flue Gas O2(%) Flue Gas Moisture (%) Flue Gas CO2(%)13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.8513.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.914.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.9213.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85 13.95 12.41 6.9 14.17 12.42 6.92 13.99 12.41 6.85Fuel Input Rate

3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 Flue Gas Flow Rate (scfm) Flue Gas Temperature (F)3,296,066 129.4

3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.43,286,333 128.9

3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.93,224,786 129.1

3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.13,296,066 129.4

3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4 3,286,333 128.9 3,224,786 129.1 3,296,066 129.4Fuel Type Units of Measure Measurement Method Fuel #1Fuel Input Rate Fuel Type Units of Measure Fuel #2Measurement Method Fuel Input Rate Fuel Type Fuel #3Units of Measure Measurement Method Fuel Input Rate Fuel #3Fuel Type Units of Measure Measurement Method Fuel #4Other Supporting

InformationEIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam Station U1

1 4/20/10 9:28 4/20/2010 2 4/20/10 12:38 4/20/2010 3 4/20/10 15:15 4/20/2010 Run Number Test Start Date Test Start Time Test End DateMeasured Value (ug) Basis (Wet or Dry) Test Method Used

11:52 [< 32.8] Dry U.S. EPA Conditional Test Method 033 (CTM-033) 14:20 [< 35] Dry U.S. EPA Conditional Test Method 033 (CTM-033) 16:42 [< 32.8] Dry U.S. EPA Conditional Test Method 033 (CTM-033) Hydrogen Cyanide Emission Test Results Test End TimeData Flag (ADL,

BDL, DDL) Test Method

Comments BDL DL based on the MDL [<2.13E-05] 14.76 12.51 BDL DL based on the MDL [<2.24E-05] 14.76 12.51 BDL DL based on the MDL [<2.17E-05] 15.17 12.48

Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Calculated Emission Rate (lb/mmBtu) Flue Gas Moisture (%) Flue Gas CO2(%)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate 6.81 3,224,231 128 6.78 3,249,884 129 6.77 3,226,483 129

Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1 Flue Gas O2(%)Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel #2 Fuel #3Fuel Type Units of Measure Measurement

Method Matrix spike recoveries for HCN were 32% and 68% which indicate that the reported reults may be biased low. Matrix spike recoveries for HCN were 32% and 68% which indicate that the reported reults may be biased low. Matrix spike recoveries for HCN were 32% and 68% which indicate that the reported reults may be biased low. Fuel #4 Other Supporting InformationMatrix spike recoveries for HCN were 32% and 68% which indicate that the reported reults may be biased low. Matrix spike recoveries for HCN were 32% and 68% which indicate that the reported reults may be biased low. Matrix spike recoveries for HCN were 32% and 68% which indicate that the reported reults may be biased low.EIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam Station U1

Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used Test End Time Hydrogen Chloride Emission Test ResultsData Flag (ADL,

BDL, DDL) Test Method

Comments Calculated

Emission Rate (lb/mmBtu) Flue Gas Moisture (%) Flue Gas CO2(%) Hydrogen Chloride Emission Test Results Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Flue Gas Temperature (F) Fuel #1 Flue Gas O2(%) Flue Gas

Flow Rate (dscfm)Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel #2 Fuel #3Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam Station U1

Run Number Test Start Date Test Start Time Test End DateMeasured Value (ppm) Basis (Wet or Dry) Test Method Used Hydrogen Flouride Emission Test Results Test End TimeData Flag (ADL,

BDL, DDL) Test Method

Comments Hydrogen Flouride Emission Test Results Steam Output (1000 lb/hr) Total Heat

Input (mmBtu/hr) Calculated Emission Rate (lb/mmBtu) Flue Gas Moisture (%)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1 Flue Gas CO2(%) Flue Gas

O2(%)Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel #2 Fuel #3Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam Station U1

Run Number Test Start Date Test Start TimeMeasured NO (ppm) Test End Time Test End DateMeasured NO2(ppm) Basis (Wet or Dry) Test Method Used NOXEmission Test ResultsData Flag (ADL, BDL, DDL) Test Method Comments (lb/mmBtu) Total NOXCalculated Emission Rateppmdv @ 7% O2 Flue Gas Moisture (%) Flue Gas

CO2(%) Flue Gas

O2(%) Calculated Emission Rate Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr)Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Flue Gas Flow Rate (dscfm) Flue Gas

Temperature (F) Fuel #1Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel #2 Fuel #3Fuel Type Units of Measure Measurement

Method Fuel #4 Other Supporting InformationEIA

Facility Code Facility Name Boiler ID OH_Zimmer Station Zimmer Steam Station U1

Run 1 3/22/2010 10:06 Run 2 3/23/2010 8:23 Run 3 3/23/2010 12:17

Run Number Test Start Date Test Start TimeTotal Dissolved Solids (mg solids/liter) Total Suspended Solids (mg solids/liter)

3/22/2010 16:20 121,000 146,000 3/23/2010 11:39 136,000 182,000 3/23/2010 15:41 140,000 136,000

Test End Time Test End DateTest Method Used Data Flag (ADL, BDL, DDL)

ADL ADL ADL Constisuent Emission Test ResultsTest Method Comments Fuel Input Rate

MCAWW 160.1 3,369,921 129 MCAWW 160.1 3,341,205 129 MCAWW 160.1 3,346,156 129 Flue Gas Temperat ure (F) Flue Gas Flow Rate (dscfm) Steam Output (1000 lb/hr) Total Heat Input

(mmBtu/hr)Fuel Type Units of Measure Measurement

Method Fuel Input Rate Fuel Type Units of Measure Measurement

Method Fuel Input Rate

bitum inous bitum inous bitum inous Fuel #1 Fuel #2Fuel Type Units of Measure Measurement

Method Fuel Input

Rate Fuel Type Units of

Measure Measurement

Method Fuel #3 Fuel #4Other Supporting Information