Facility_Information

facility_id utility_codelegal_owner_nam legl_operator_name e legal_address_ty legal_address pe legal_city legal_state legal_zip

2008 16181 Rochester Public Utilities Rochester Public Utilities legal owner4000 East River Road NE Rochester MN 55906

Page 1
Facility_Information

plant_namephysical_address phyical_cityphysical_statephysical_zipmailing_address mailing_citymailing_statemailing_zip

Silver Lake425 W Silver Lake Drive NE Rochester MN 55903-60574000 East River Road NE Rochester MN 55906-2813

Page 2
Facility_Information

RFA_small_entity ff_fired_coalff_fired_oil ff_fired_ngasff_fired_petcoke ff_fired_other ff_permitted_coal ff_permitted_oil ff_permitted_ngas

No TRUE FALSE TRUE FALSE FALSE TRUE FALSE TRUE

Page 3
Facility_Information

ff_permitted_petcoke ff_permitted_other deviation_reporting continuous_emissions cem_providedfacility_note

FALSE TRUE The permit requires notification of any Yes Nox and SO2 data is provided to USEPA Part IGeneral InformationThe ICR that RPU received included  deviation from permit conditions which could endanger human he

Page 4
Facility_Information

The ICR that RPU received included Unit 3. However, Unit 3 does not meet the definition of an electric utilitiy steam generating unit under Se

Page 5
Facility_Information

utilitiy steam generating unit under Section 112(a)(8) of the CAA. A hard copy of support documentation will be mailed.Boiler Informat

Page 6
Facility_Information

 will be mailed.Boiler InformationThe Design and Operating Steam Pressures and the Design and Operating Steam Temperature

Page 7
Facility_Information

n and Operating Steam Temperatures listed are for the Boiler Operation. The Design Steam Pressure and Temperature for turbine throttle c

Page 8
Facility_Information

nd Temperature for turbine throttle conditions are 1250 psi and 950 degrees F.Design steam reheat temperature: No reheat is used.

Page 9
Facility_Information

eat temperature: No reheat is used.Part IIFuel Shipment InformationNo Coal or oil shipments were purchased or received f

Page 10
Facility_Information

ments were purchased or received from vendors in the preceding 12 months. The facility had sufficient fuel in it's stockpiles for use in 2009 

Page 11
Facility_Information

 fuel in it's stockpiles for use in 2009 from purchases made in 2008.Fuel analysis is conducted on the coal entering the boiler mills at 

Page 12
Facility_Information

n the coal entering the boiler mills at unit startup and weekly thereafter. This coal is analyzed for short proximate and combined for a quarter

Page 13
Facility_Information

roximate and combined for a quarterly analysis including metals, chlorine and fluorin

Page 14
facility_contacts

facility_id contact_id contact_titlecontact_namecontact_phone1 contact_phone2 contact_email contact_primary

2008 1 Environmental & Regulatory Craig Diekvoss 5072801646 Affairs Coordinatorcdiekvoss@rpu.org TRUE

Page 15
facility_coal_utilized

facility_id coal_type percentage_mass percentage_btu synfuel_typecoal_note

2008 bituminous 100 100

Page 16
facility_oil_utilized

facility_id oil_type percentage_volume percentage_btu other_type

Page 17
facility_other_materials

facility_id other_material permitted_burn actually_burnother_quantity other_quantity other_note _units rcra_utilize rcra_explain

2008 Boiler Cleaning Agents TRUE FALSE 0 tons/year Permit limits boiler cleaning agents to: EDTA ty No pe, genera

Page 18
facility_other_materials

rcra_explain

Page 19
boiler_information

facility_id boiler_id boiler_type boiler_otherbottom_design design_fuelheat_input max_heat_input MWe_capacity

2008 4 Wall firing - front firing Dry Bottomcoal 614.5 684 60.4

Page 20
boiler_information

MWe_net_capacity design_gross_efficiency operating_gross_efficiency design_pressure operating_pressure design_tempoperating_temp design_reheat_multiple design_reheat_temp1

56.6 37 31 1550 1350 955 955 FALSE 1

Page 21
boiler_information

design_reheat_temp2 operating_reheat_multiple operating_reheat_temp1 operating_reheat_temp2 hours_operatedvg_capacityapplicable_NSPS _factor retirement_yretirement_y ear ear_CBI

FALSE 1 4072 52 N FALSE

Page 22
boiler_information

NOx_controlSO2_controlcombustion_additives

Yes No No

Page 23
boiler_fuels

facility_id boiler_id fuel_type fuel_year percentage_massvol percentage_btu other_type

2008 4 coal - bituminous2007 0 95

2008 4 coal - bituminous2008 0 94

2008 4 coal - bituminous2009 0 94

2008 4 natural gas 2007 0 5

2008 4 natural gas 2008 0 6

2008 4 natural gas 2009 0 6

Page 24
boiler_control_NOx

facility_id boiler_id NOx_type NOx_other NOx_online

2008 4 Advanced Overfire Air 12/1/2008

2008 4 Low NOx Burner 1/1/1998

Page 25
boiler_control_SO2

facility_id boiler_id SO2_type SO2_other SO2_online

Page 26
boiler_additives

facility_id boiler_id boiler_additive additive_other additive_online

Page 27
facility_units

facility_id unit_id

2008 4

Page 28
unit_boilers

facility_id unit_id boiler_id

2008 4 4

Page 29
facility_controls

facility_id control_id control_groupcontrol_typecontrol_otherlegacy_control cntrol_onlinecontrol_offlineNOx_reagent

2008 CE008 PM control Fabric Filter, pulse FALSE 12/1/2008

2008 CE009 SO2 controlSpray dryer type FALSE 12/1/2008

2008 CE010 NOx controlSelective Noncatalytic Reduction FALSE 8/1/2009 Urea

Page 30
facility_controls

reagent_other NOx_ammonia SO2_sorbent oher_sorbent SO2_scrubber_additive

Lime No

Page 31
facility_sampling_ports

facility_id sampling_port_id

2008 SP001-Inlet

2008 SP002-Outlet

Page 32
facility_stacks

facility_id stack_id stack_heightstack_diameter sack_gas_velocity

2008 SV003 300 7.9 69.4

Page 33
configurations

facility_id configuration_id

2008 CO1

Page 34
configuration_components

facility_id configuration_id component_idorder component_ty port_near pe

2008 CO1 4 1 Unit

2008 CO1 CE008 5 PM control

2008 CO1 CE009 4 SO2 control

2008 CO1 CE010 2 NOx control

2008 CO1 SP001-Inlet 3 Sampling Port next

2008 CO1 SP002-Outlet 6 Sampling Port next

2008 CO1 SV003 7 Stack

Page 35
configuration_pollutants1

facility_id configuration_id pollutant_nampermit_ty e pe_1emlimit_1 emlimit_units_1 avg_period_1emlimit_2 emlimit_units_2

2008 CO1 PM10 (Filterable) Fedral - Title V Operating Permit 0.4 pound per million British Thermal Unit (lb/MMBtu) 3 hours

2008 CO1 PM (Filterable) Fderal - Title V Operating Permit 0.6 pound per million British Thermal Unit (lb/MMBtu) 3 hours

2008 CO1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 0.6 pound per million British Thermal Unit (lb/MMBtu) 1 hour 0.6 pound per million British Thermal U

2008 CO1 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.46 pound per million British Thermal Unit (lb/MMBtu) 24 hours

Page 36
configuration_pollutants1

avg_period_2emlimit_3 emlimit_units_3 avg_period_3emlimit_4 emlimit_units_4 avg_period_4emlimit_details test_method

Limit is for PM10 not just Filterable 201A, 202

Limit is for Total PM not just Filterable 5

24 hours 0.6 pound per million British Thermal Unit (lb/MMBtu) 3 hours Became effective on 2-16-10. 1-Hr limit is a st

 "24 hours" Averaging Period field should be re

Page 37
configuration_pollutants1

emrate emrate_unitsguarantee_level_explainreq_monitoringeq_recordkeeping req_reporting

7.5 pound per hour (lb/hr) No The facility will utilize the COMS on EU004 to m Retain all records at the stationary Performance Test Reports due to the MPCA 45 day source or at the RPU-Service Ceneet their CAM obligations. Periods afte

7.5 pound per hour (lb/hr) No The facility will utilize the COMS on EU004 to m Retain all records at the stationary Performance Test Reports due to the MPCA 45 day source or at the RPU-Service Ceneet their CAM obligations. s afte

0.27 pound per million British Thermal Unit (lb/MMBtu) No The owner or operator shall conduct all monitoring in continuous operation (or shRetain all records at the stationary The emissions measurements recorded and reported in a source or at the RPU-Service Cen

0.15 pound per million British Thermal Unit (lb/MMBtu) No The owner or operator shall conduct all monitoring in continuous operation (or shRetain all records at the stationary The emissions measurements recorded and reported in a source or at the RPU-Service Cen

Page 38
configuration_pollutants1

ports due to the MPCA 45 days after each performance test.CAM requirements for Reporting/Notifications: As required by 40 CFR S

ports due to the MPCA 45 days after each performance test.CAM requirements for Reporting/Notifications: As required by 40 CFR S

urements recorded and reported in accordance with 40 CFR part 75 shall be used to determine compliance by the unit with the Acid Rain em

urements recorded and reported in accordance with 40 CFR part 75 shall be used to determine compliance by the unit with the Acid Rain em

Page 39
configuration_pollutants1

tifications: As required by 40 CFR Section 64.9(a)(2), for the Semi-Annual Deviation Report and shall include summary information on the n

tifications: As required by 40 CFR Section 64.9(a)(2), for the Semi-Annual Deviation Report and shall include summary information on the n

nce by the unit with the Acid Rain emissions limitations and emissions reduction requirements for sulfur dioxide and nitrogen oxides under th

nce by the unit with the Acid Rain emissions limitations and emissions reduction requirements for sulfur dioxide and nitrogen oxides under th

Page 40
configuration_pollutants1

clude summary information on the number, duration, and cause of excursions or exceedances, as applicable, and the corrective action take

clude summary information on the number, duration, and cause of excursions or exceedances, as applicable, and the corrective action take

dioxide and nitrogen oxides under the Acid Rain Program.Deviations from requirements cited as "Title I Condition: State Implementat

dioxide and nitrogen oxides under the Acid Rain Program.

Page 41
configuration_pollutants1

cable, and the corrective action taken; and summary information on the number, duration, and cause for monitor downtimeincidents

cable, and the corrective action taken; and summary information on the number, duration, and cause for monitor downtimeincidents.

"Title I Condition: State Implementation Plan for SO2 NAAQS..." shall be reported semiannually with the Semiannual Deviations Report requ

Page 42
configuration_pollutants1

r monitor downtimeincidents

r monitor downtimeincidents.

e Semiannual Deviations Report required by this permit. Reporting for these conditions shall occur even if there were no deviations for the re

Page 43
configuration_pollutants1

 if there were no deviations for the reporting period.

Page 44
control_technologies

facility_id configuration_id component_idcontrol_id project_titleproject_typevendor_namevndor_contact vendor_phone

Page 45
control_technologies

vendor_address vndor_cityvendor_statevendor_zip actual_start_date projected_start_date end_date sorbent chemical_additive

Page 46
control_technologies

injection_point HAP_emission_reduction HAP_emission_rate HAP_emission_rate_units HAP_achieved_reduction HAP_achieved_rate HAP_achieved_rate_units feed_rate feed_rate_units

Page 47
control_technologies

feed_rate_units

Page 48
control_coal_ranks

facility_id configuration_id component_idcontrol_id coal_type

Page 49
control_pollutants1

facility_id configuration_id component_idcontrol_id pollutant_name

Page 50
control_costs

facility_id configuration_id component_idcontrol_id boiler_retrofit boiler_new_install total_capital_investm total_operating_costs entbase_year

Page 51
control_costs

CBI

Page 52
misc_controls

facility_id misc_control_id control_description

Page 53
misc_control_configurations

facility_id misc_control_id configuration_id

Page 54
fuel_shipments

facility_id shipment_idshipment_date amount_received amount_unitsfuel_type state_countryother_countrycounty

2008 See Note coal

Page 55
fuel_shipments

coal_seam shipment_method

Page 56
fuel_shipment_configurations

facility_id shipment_idconfiguration_id

Page 57
fuel_shipment_samples

facility_id shipment_idsample_id amount_fuelamount_fuel_units total_sulfur ash_contentheating_valuehating_units

Page 58
fuel_shipment_samples

chlorine chlorine_unitsfluorine fluorine_unitsdata_provideddata_other_specified supplier_typesupplier_name supplier_address

Page 59
fuel_shipment_samples

supplier_citysupplier_statesupplier_ziplab_name lab_addresslab_city lab_state lab_zip analysis_copies

Page 60
fuel_shipment_samples

analysis_copies

Page 61
fuel_sample_pollutants

facility_id shipment_idsample_id fuel_pollutant pollutant_conc pollutant_conc_units pollutant_conc_ND pollutant_conc_MDL

Page 62
test_reports

facility_id report_id report_typeother_type report_description report_begin_date report_end_date before_control during_deviation

2008 Results of Unit 4 Compliance Testing #902546 (CO) other CO rate determination The report presents the results of a source testing at Unit 4 to determine complia7/29/2009 7/29/2009 No No 

2008 Results of Unit 4 Compliance Testing #902546 (Hg) other Annual Emissions Inventory The report presents the results of a source testing at Unit 4 to determine complia7/29/2009 Purposes 7/29/2009 Yes No 

2008 Results of Unit 4 Compliance Testing #902546 (PM) compliance The report presents the results of a source testing at Unit 4 to determine complia7/29/2009 7/30/2009 No No 

2008 Results of Unit 4 Compliance Testing #902546(PM10) compliance The report presents the results of a source testing at Unit 4 to determine complia7/29/2009 7/29/2009 No No 

Page 63
test_reports

deviation_reports

No

No

No

No

Page 64
test_report_configurations

facility_id report_id configuration_id

2008 Results of Unit 4 Compliance Testing #902546 (CO) CO1

2008 Results of Unit 4 Compliance Testing #902546 (Hg) CO1

2008 Results of Unit 4 Compliance Testing #902546 (PM) CO1

2008 Results of Unit 4 Compliance Testing #902546(PM10) CO1

Page 65
test_report_fuels

facility_id report_id fuel_id

2008 Results of Unit 4 Compliance Testing #902546 (CO) Coal 1

2008 Results of Unit 4 Compliance Testing #902546 (Hg) Coal 1

2008 Results of Unit 4 Compliance Testing #902546 (PM) Coal 1

2008 Results of Unit 4 Compliance Testing #902546(PM10) Coal 1

Page 66
test_report_fuel_types

facility_id report_id fuel_id fuel_type percentage_massvol percentage_btu other_type

2008 Results of Unit 4 Compliance Testing #902546 (CO) Coal 1 coal - bituminous 100 100

2008 Results of Unit 4 Compliance Testing #902546 (Hg) Coal 1 coal - bituminous 100 100

2008 Results of Unit 4 Compliance Testing #902546 (PM) Coal 1 coal - bituminous 100 100

2008 Results of Unit 4 Compliance Testing #902546(PM10) Coal 1 coal - bituminous 100 100

Page 67
cem_data

facility_id time_periodcem_period_description

2008 1/1/2009 - 12/31/2009 CEMs and COMS data is available for the previous 5 years but due to the installation of new control sys

Page 68
cem_data

e to the installation of new control system in late 2008, only 2009 data is representative of current configuration

Page 69
cem_data_pollutants1

facility_id time_periodpollutant_name

2008 1/1/2009 - 12/31/2009 Nitrogen Oxide (NOx)

2008 1/1/2009 - 12/31/2009 Sulfur Dioxide (SO2)

Page 70
test_report_sampling

facility_id report_id sampling_port_id point_differpoint_description befre_SO2_device point_orientation normal_bypass_percent testing_bypass_percent

2008 Results of Unit 4 Compliance Testing #902546 (CO) SP002-Outlet No No

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-InletNo Yes D 0 0

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet No No

2008 Results of Unit 4 Compliance Testing #902546 (PM) SP002-Outlet No No

2008 Results of Unit 4 Compliance Testing #902546(PM10) SP002-Outlet No No

Page 71
test_report_sampling

fg_fraction

Page 72
sampling_runs

facility_id report_id sampling_port_id run_id start_datetime end_datetimunit_load e net_generation fg_moisture_content

2008 Results of Unit 4 Compliance Testing #902546 (CO) SP002-Outlet 1 7/30/2009 7/30/2009 42

2008 Results of Unit 4 Compliance Testing #902546 (CO) SP002-Outlet 2 7/30/2009 7/30/2009 42

2008 Results of Unit 4 Compliance Testing #902546 (CO) SP002-Outlet 3 7/30/2009 7/30/2009 42

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet1 7/29/2009 7/29/2009 49 10.6

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet2 7/29/2009 7/29/2009 49 10.6

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet3 7/29/2009 7/29/2009 49 10.5

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 1 7/29/2009 7/29/2009 49 13.5

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 2 7/29/2009 7/29/2009 49 13.6

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 3 7/29/2009 7/29/2009 49 13.6

2008 Results of Unit 4 Compliance Testing #902546 (PM) SP002-Outlet 1 7/29/2009 7/29/2009 49 13.5

2008 Results of Unit 4 Compliance Testing #902546 (PM) SP002-Outlet 2 7/29/2009 7/29/2009 49 13.6

2008 Results of Unit 4 Compliance Testing #902546 (PM) SP002-Outlet 3 7/29/2009 7/29/2009 49 13.6

2008 Results of Unit 4 Compliance Testing #902546(PM10) SP002-Outlet 1 7/29/2009 7/29/2009 50 13.3

2008 Results of Unit 4 Compliance Testing #902546(PM10) SP002-Outlet 2 7/29/2009 7/29/2009 50 13.7

2008 Results of Unit 4 Compliance Testing #902546(PM10) SP002-Outlet 3 7/29/2009 7/29/2009 49 13.7

Page 73
sampling_runs

fg_flow_ratefg_flow_rate_units standard_temperature standard_pressure normal_temperature normal_pressure fg_oxygen_content fg_CO2_content fg_temperature

118527 dscfm 65 28.8 6.6 14.8 291

116232 dscfm 65 6.6 14.4 292

117484 dscfm 6.4 14.8 295

120272 dscfm 4 14.9 192

122418 dscfm 4.1 14.7 183

122612 dscfm 4 14.6 180

120272 dscfm 4 14.9 192

122418 dscfm 4.1 14.7 183

122612 dscfm 4 14.6 180

121909 dscfm 4 14.9 189

123264 dscfm 4.1 14.7 182

126261 dscfm 3.9 13.7 180

Page 74
sampling_runs

fg_pressureHg_loi test_methodrun_comments fuel_id fuel_unit_loadfuel_flow_ratefuel_ash fuel_heating_value

EPA Method 10

EPA Method 10

EPA Method 10

1,2,3A,4,ASTM D 6784Coal 1 49 55678.1

1,2,3A,4,ASTM D 6784Coal 1 49 55678.1

1,2,3A,4,ASTM D 6784Coal 1 49 55678.1

1,2,3A,4,5,ASTM D 6784Coal 1 49 55678.1

1,2,3A,4,5,ASTM D 6784Coal 1 49 55678.1

1,2,3A,4,5,ASTM D 6784Coal 1 49 55678.1

1,2,3A,4,5

1,2,3A,4,5

1,2,3A,4,5

1,2,3A,4,201A,202 Coal 1 49 55678.1

1,2,3A,4,201A,202 Coal 1 49 55678.1

1,2,3A,4,201A,202 Coal 1 49 55678.1

Page 75
sampling_runs

fuel_sulfur

Page 76
sampling_run_pollutants1

facility_id report_id sampling_port_id run_id pollutant_namconce conc_units conc_ND conc_MDL

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet1 Particulate-bound Mercury 15.294 microgram per dry (Hgp) FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet1 Oxidized Mercury0.024 (Hg++) microgram per dry TRUE standard cubic meter ( 0.024

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet1 Elemental Mercury0.088 (Hg0) microgram per dry TRUE standard cubic meter ( 0.088

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet1 Total Mercury (Hgt) 15.407 microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet2 Particulate-bound Mercury 121.78 microgram per dry (Hgp) FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet2 Oxidized Mercury0.025 (Hg++) microgram per dry TRUE standard cubic meter ( 0.025

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet2 Elemental Mercury0.09 (Hg0) microgram per dry TRUE standard cubic meter ( 0.09

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet2 Total Mercury (Hgt) 121.896 microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet3 Particulate-bound Mercury 17.267 microgram per dry (Hgp) FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet3 Oxidized Mercury0.025 (Hg++) microgram per dry TRUE standard cubic meter ( 0.025

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet3 Elemental Mercury0.089 (Hg0) microgram per dry TRUE standard cubic meter ( 0.089

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet3 Total Mercury (Hgt) 17.381 microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 2 Particulate-bound Mercury 0.026 microgram per dry (Hgp) FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 2 Oxidized Mercury0.027 (Hg++) microgram per dry TRUE standard cubic meter ( 0.027

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 2 Elemental Mercury0.095 (Hg0) microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 2 Total Mercury (Hgt) 0.148 microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 3 Particulate-bound Mercury 0.009 microgram per dry (Hgp) FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 3 Oxidized Mercury0.026 (Hg++) microgram per dry TRUE standard cubic meter ( 0.026

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 3 Elemental Mercury0.094 (Hg0) microgram per dry TRUE standard cubic meter ( 0.094

2008 Results of Unit 4 Compliance Testing #902546(PM10) SP002-Outlet 1 PM10 (Filterable) 2507.3 microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546(PM10) SP002-Outlet 2 PM10 (Filterable) 3390.2 microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (CO) SP002-Outlet 3 Carbon Monoxide (CO) 63 percent concentration (% @ 7% O2) FALSE

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 3 Total Mercury (Hgt) 0.129 microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (PM) SP002-Outlet 1 PM (Filterable) 7981 microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (PM) SP002-Outlet 2 PM (Filterable) 6956.9 microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (PM) SP002-Outlet 3 PM (Filterable) 6921.6 microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 1 Particulate-bound Mercury 0.07405 microgram per dry (Hgp) FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 1 Oxidized Mercury 0.02645 (Hg++) microgram per dry TRUE standard cubic meter ( 0.02645

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 1 Elemental Mercury0.105 (Hg0) microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 1 Total Mercury (Hgt) 0.201 microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546(PM10) SP002-Outlet 3 PM10 (Filterable) 1730.4 microgram per dry FALSE standard cubic meter (

2008 Results of Unit 4 Compliance Testing #902546 (CO) SP002-Outlet 1 Carbon Monoxide (CO) 24.9 parts per million by FALSE volume (dry) (ppmvd @ 7% O2)

2008 Results of Unit 4 Compliance Testing #902546 (CO) SP002-Outlet 2 Carbon Monoxide (CO) 33.4 percent concentration (% @ 7% O2) FALSE

Page 77
sampling_run_pollutants1

emission_rateemission_rate_units emission_rate_ND emission_rate_MDL emission_factor emission_factor_units emission_factor_ND emission_factor_MDL run_pollutant_comment

0.00679 pound per hour (lb/hr) FALSE 13.65 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

1.08E-05 pound per hour (lb/hr) TRUE 1.08E-05 0.0218 pound per trillion British Thermal Unit (lb/1012Btu) TRUE 0.0218 Laboratory MDL was 0.05 microgra

0.000039 pound per hour (lb/hr) TRUE 0.000039 0.0785 pound per trillion British Thermal Unit (lb/1012Btu) TRUE 0.0785 Elemental (Hg) H2O2/HNO3 Labor

0.00684 pound per hour (lb/hr) FALSE 13.75 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

0.053 pound per hour (lb/hr) FALSE 108.687 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

1.09E-05 pound per hour (lb/hr) TRUE 1.09E-05 0.022 pound per trillion British Thermal Unit (lb/1012Btu) TRUE 0.022 Laboratory MDL was 0.05 microgra

3.93E-05 pound per hour (lb/hr) TRUE 3.93E-05 0.081 pound per trillion British Thermal Unit (lb/1012Btu) TRUE 0.081 Elemental (Hg) H2O2/HNO3 Labor

0.0531 pound per hour (lb/hr) FALSE 108.79 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

0.0076 pound per hour (lb/hr) FALSE 15.198 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

1.09E-05 pound per hour (lb/hr) TRUE 1.09E-05 0.022 pound per trillion British Thermal Unit (lb/1012Btu) TRUE 0.022 Laboratory MDL was 0.05 microgra

3.91E-05 pound per hour (lb/hr) TRUE 3.91E-05 0.078 pound per trillion British Thermal Unit (lb/1012Btu) TRUE 0.078 Elemental (Hg) H2O2/HNO3 Labor

0.00765 pound per hour (lb/hr) FALSE 15.298 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

1.19E-05 pound per hour (lb/hr) FALSE 0.01974 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

1.22E-05 pound per hour (lb/hr) TRUE 1.22E-05 0.02014 pound per trillion British Thermal Unit (lb/1012Btu) TRUE 0.02014 Laboratory MDL was 0.05 microgra

4.38E-05 pound per hour (lb/hr) FALSE 0.0725 pound per trillion British Thermal Unit (lb/1012Btu) FALSE Elemental (Hg) H2O2/HNO3 was N

6.78E-05 pound per hour (lb/hr) FALSE 0.11237 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

4.09E-06 pound per hour (lb/hr) FALSE 0.00673 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

0.000012 pound per hour (lb/hr) TRUE 0.000012 0.01979 pound per trillion British Thermal Unit (lb/1012Btu) TRUE 0.01979 Laboratory MDL was 0.05 microgra

4.33E-05 pound per hour (lb/hr) TRUE 4.33E-05 0.07124 pound per trillion British Thermal Unit (lb/1012Btu) TRUE 0.07124 Elemental (Hg) H2O2/HNO3 was N

1.152 pound per hour (lb/hr) FALSE 0.0019 pound per million British Thermal Unit (lb/MMBtu) FALSE Concetration reported as 0.071 mg

1.565 pound per hour (lb/hr) FALSE 0.0026 pound per million British Thermal Unit (lb/MMBtu) FALSE Concetration reported as 0.096 mg

39.3 pound per hour (lb/hr) FALSE 0.067 pound per million British Thermal Unit (lb/MMBtu) FALSE

5.94E-05 pound per hour (lb/hr) FALSE 0.09776 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

3.598 pound per hour (lb/hr) FALSE 0.006 pound per million British Thermal Unit (lb/MMBtu) FALSE

3.184 pound per hour (lb/hr) FALSE 0.053 pound per million British Thermal Unit (lb/MMBtu) FALSE

3.177 pound per hour (lb/hr) FALSE 0.052 pound per million British Thermal Unit (lb/MMBtu) FALSE

3.34E-05 pound per hour (lb/hr) FALSE 0.05592 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

1.19E-05 pound per hour (lb/hr) TRUE 1.19E-05 0.01997 pound per trillion British Thermal Unit (lb/1012Btu) TRUE 0.01997 Laboratory MDL was 0.05 microgra

4.53E-05 pound per hour (lb/hr) FALSE 0.07589 pound per trillion British Thermal Unit (lb/1012Btu) FALSE Elemental (Hg) H2O2/HNO3 was N

9.05E-05 pound per hour (lb/hr) FALSE 0.15179 pound per trillion British Thermal Unit (lb/1012Btu) FALSE

0.825 pound per hour (lb/hr) FALSE 0.0037 pound per million British Thermal Unit (lb/MMBtu) FALSE Concetration reported as 0.049 mg

15.38 pound per hour (lb/hr) FALSE 0.027 pound per million British Thermal Unit (lb/MMBtu) FALSE

20.67 pound per hour (lb/hr) FALSE 0.036 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 78
sampling_run_pollutants1

run_pollutant_comment

Laboratory MDL was 0.05 micrograms

Elemental (Hg) H2O2/HNO3 Laboratory MDL was 0.13 microgramsElemental (Hg) KMNO4 Laboratory MDL was 0.05 micrograms

Laboratory MDL was 0.05 micrograms

Elemental (Hg) H2O2/HNO3 Laboratory MDL was 0.13 microgramsElemental (Hg) KMNO4 Laboratory MDL was 0.05 micrograms

Laboratory MDL was 0.05 micrograms

Elemental (Hg) H2O2/HNO3 Laboratory MDL was 0.13 microgramsElemental (Hg) KMNO4 Laboratory MDL was 0.05 micrograms

Laboratory MDL was 0.05 micrograms

Elemental (Hg) H2O2/HNO3 was ND with MDL of 0.13 micrograms or 0.06892 microgram/dscmElemental (Hg) KMNO4 was 0.05 micr

Laboratory MDL was 0.05 micrograms

Elemental (Hg) H2O2/HNO3 was ND with MDL of 0.13 micrograms or 0.06892 microgram/dscmElemental (Hg) KMNO4 was ND with M

Concetration reported as 0.071 mg/dscf

Concetration reported as 0.096 mg/dscf

Laboratory MDL was 0.05 micrograms

Elemental (Hg) H2O2/HNO3 was ND with MDL of 0.13 micrograms or 0.06892 microgram/dscmElemental (Hg) KMNO4 was 0.05 micr

Concetration reported as 0.049 mg/dscf

Page 79
sampling_run_pollutants1

atory MDL was 0.05 micrograms

atory MDL was 0.05 micrograms

atory MDL was 0.05 micrograms

emental (Hg) KMNO4 was 0.05 micrograms or 0.02651 microgram/dscm

emental (Hg) KMNO4 was ND with MDL of 0.05 micrograms or 0.0262 microgram/dscm

emental (Hg) KMNO4 was 0.05 micrograms or 0.02651 microgram/dscm

Page 80
sampling_run_fuel

facility_id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_NDfuel_conc_MDL

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet1 Mercury (Hg) 0.147 microgram per gram (dry FALSE ) (mg/g)

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet2 Mercury (Hg) 0.147 microgram per gram (dry FALSE ) (mg/g)

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP001-Inlet3 Mercury (Hg) 0.147 microgram per gram (dry FALSE ) (mg/g)

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 1 Mercury (Hg) 0.147 microgram per gram (dry FALSE ) (mg/g)

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 2 Mercury (Hg) 0.147 microgram per gram (dry FALSE ) (mg/g)

2008 Results of Unit 4 Compliance Testing #902546 (Hg) SP002-Outlet 3 Mercury (Hg) 0.147 microgram per gram (dry FALSE ) (mg/g)

Page 81
sampling_run_fuel

fuel_conc_MDL

Page 82