Monroe Power Plant Start Time End Time Time Interval

BOILER #3 6/29/10 7:40 6/29/10 16:49 15 m

ESP power

GEN GROSS 

TOTAL MW

GEN NET 

MGWATTS

U3 MAIN

 STEAM FLOW

(lb/hr)

Heat Input

(MMBtu/hr)

COAL FLOW

(Tons/hr)

TOTAL PRECIP 

POWER

 (Kwatts)

29-Jun-10 07:40 794.4 743.8 5713212 7125 652.7 721.5

29-Jun-10 07:55 794.1 747.1 5712860 7132 648.3 722.0

29-Jun-10 08:10 793.9 745.8 5712507 7108 652.7 735.8

29-Jun-10 08:25 793.6 745.6 5712155 7114 652.7 737.9

29-Jun-10 08:40 793.4 745.8 5711803 7116 652.8 744.3

29-Jun-10 08:55 793.2 743.4 5711450 7113 652.8 742.0

29-Jun-10 09:10 792.9 744.9 5711098 7117 652.9 733.1

29-Jun-10 09:25 792.7 744.3 5710746 7110 652.9 738.4

29-Jun-10 09:40 792.5 744.9 5710394 7120 653.0 736.6

29-Jun-10 09:55 792.2 744.0 5710041 7121 653.0 751.1

29-Jun-10 10:10 792.0 742.9 5709689 7116 653.1 747.5

29-Jun-10 10:25 791.7 743.8 5709337 7125 653.1 744.7

29-Jun-10 10:40 791.5 745.8 5708985 7130 653.2 738.1

29-Jun-10 10:55 791.3 743.7 5708632 7120 653.2 729.0

29-Jun-10 11:10 791.0 745.3 5708280 7128 653.3 727.3

29-Jun-10 11:25 790.8 743.9 5707928 7133 653.3 728.4

29-Jun-10 11:40 790.5 744.5 5707575 7126 653.4 724.9

29-Jun-10 11:55 790.3 743.7 5707223 7138 653.4 732.0

29-Jun-10 12:10 790.1 745.8 5706871 7148 653.5 723.5

29-Jun-10 12:25 789.8 745.1 5706519 7141 653.5 720.6

29-Jun-10 12:40 789.6 742.8 5706166 7134 653.6 725.4

29-Jun-10 12:55 789.4 747.2 5705814 7135 653.7 733.8

29-Jun-10 13:10 789.1 744.3 5705462 7129 653.8 745.0

29-Jun-10 13:25 788.9 748.7 5705110 7135 653.9 722.7

29-Jun-10 13:40 788.6 743.7 5704757 7128 654.0 720.5

29-Jun-10 13:55 788.4 747.5 5704405 7150 654.1 720.0

29-Jun-10 14:10 788.2 743.7 5704053 7145 654.2 736.9

29-Jun-10 14:25 787.9 746.4 5703700 7164 654.3 724.4

29-Jun-10 14:40 787.7 746.6 5703348 7182 654.4 730.0

29-Jun-10 14:55 787.4 745.8 5702996 7205 654.5 715.6

29-Jun-10 15:10 787.2 745.8 5702644 7208 654.6 706.5

29-Jun-10 15:25 787.0 745.8 5702291 7228 654.7 730.7

29-Jun-10 15:40 786.6 745.4 5701377 7234 654.8 719.8

29-Jun-10 15:55 786.2 745.8 5697940 7265 654.9 714.6

29-Jun-10 16:10 785.7 748.2 5694502 7282 655.0 701.2

29-Jun-10 16:25 785.3 745.0 5691065 7273 655.1 728.4

29-Jun-10 16:40 784.8 746.0 5687628 7314 654.6 710.4

AVERAGE: 790.0 745.2 5705961 7157 653.5 728.8

Boiler Data
Monroe Power Plant Start Time End Time Time Interval

BOILER #3 6/30/10 6:43 6/30/10 15:40 15 m

ESP power

GEN GROSS 

TOTAL MW

GEN NET 

MGWATTS

U3 MAIN

 STEAM FLOW

(lb/hr)

Heat Input

(MMBtu/hr)

COAL FLOW

(Tons/hr)

TOTAL PRECIP 

POWER

 (Kwatts)

30-Jun-10 06:43 775.5 731.6 5622856 7130 645.3 693.2

30-Jun-10 06:58 779.7 741.6 5637332 7154 648.0 702.1

30-Jun-10 07:13 787.3 746.4 5642081 7193 658.1 698.6

30-Jun-10 07:28 788.9 743.7 5633994 7225 650.9 694.3

30-Jun-10 07:43 788.9 745.4 5625908 7135 658.6 719.1

30-Jun-10 07:58 789.0 747.0 5625158 7206 647.8 683.6

30-Jun-10 08:13 789.0 745.3 5626897 7180 651.6 707.1

30-Jun-10 08:28 789.1 746.1 5628637 7212 646.5 707.1

30-Jun-10 08:43 789.2 744.6 5630376 7206 650.1 711.6

30-Jun-10 08:58 789.2 746.8 5632116 7213 650.1 705.8

30-Jun-10 09:13 789.3 744.9 5633855 7199 649.1 711.9

30-Jun-10 09:28 789.3 746.8 5635594 7198 648.1 716.3

30-Jun-10 09:43 789.4 743.7 5637334 7194 647.1 720.6

30-Jun-10 09:58 789.4 745.0 5639073 7207 646.1 708.3

30-Jun-10 10:13 789.5 743.3 5640813 7200 645.1 721.4

30-Jun-10 10:28 789.5 745.8 5642552 7214 643.3 710.1

30-Jun-10 10:43 789.6 743.7 5644291 7206 641.3 726.1

30-Jun-10 10:58 789.7 743.6 5646031 7210 639.4 702.2

30-Jun-10 11:13 789.7 743.7 5647770 7202 637.4 713.9

30-Jun-10 11:28 789.8 744.5 5649510 7217 639.2 732.3

30-Jun-10 11:43 789.8 744.3 5651249 7217 640.9 704.4

30-Jun-10 11:58 789.9 745.7 5652988 7210 642.7 726.1

30-Jun-10 12:13 789.9 743.9 5654728 7223 644.4 723.5

30-Jun-10 12:28 790.0 744.5 5656467 7225 646.2 683.0

30-Jun-10 12:43 790.1 745.0 5658207 7219 648.0 734.9

30-Jun-10 12:58 790.1 746.8 5659946 7228 647.8 718.9

30-Jun-10 13:13 790.2 743.7 5661685 7236 644.4 717.6

30-Jun-10 13:28 790.2 746.8 5663425 7225 643.9 704.1

30-Jun-10 13:43 790.3 743.7 5665164 7233 643.3 731.6

30-Jun-10 13:58 790.3 746.8 5666904 7252 642.8 702.1

30-Jun-10 14:13 790.4 743.3 5668643 7263 642.2 699.5

30-Jun-10 14:28 790.4 743.7 5670382 7257 641.7 723.9

30-Jun-10 14:43 790.5 745.8 5672122 7226 641.1 725.4

30-Jun-10 14:58 790.6 744.2 5673861 7239 640.6 726.8

30-Jun-10 15:13 790.6 746.8 5675601 7234 640.0 701.2

30-Jun-10 15:28 790.8 742.8 5677340 7232 639.7 718.4

AVERAGE: 789.0 744.5 5648636 7212 645.4 711.9

Boiler Data
Monroe Power Plant Start Time End Time Time Interval

BOILER #3 7/1/10 6:52 7/1/10 15:40 15 m

ESP power

GEN GROSS 

TOTAL MW

GEN NET 

MGWATTS

U3 MAIN

 STEAM FLOW

(lb/hr)

Heat Input

(MMBtu/hr)

COAL FLOW

(Tons/hr)

TOTAL PRECIP 

POWER

 (Kwatts)

01-Jul-10 06:52 784.0 735.1 5626423 7165 641.6 729.8

01-Jul-10 07:07 784.2 746.5 5630790 7259 643.9 693.4

01-Jul-10 07:22 784.1 741.9 5635158 7211 643.9 704.7

01-Jul-10 07:37 784.7 745.4 5639525 7243 654.0 688.6

01-Jul-10 07:52 785.3 743.6 5643893 7245 647.5 721.6

01-Jul-10 08:07 785.8 746.4 5648260 7237 648.2 700.3

01-Jul-10 08:22 786.3 742.3 5652627 7238 652.6 709.7

01-Jul-10 08:37 785.7 746.8 5656995 7246 653.9 713.6

01-Jul-10 08:52 785.0 743.6 5661362 7219 651.4 718.1

01-Jul-10 09:07 784.4 746.8 5665729 7256 648.9 718.9

01-Jul-10 09:22 783.7 746.8 5670097 7245 646.4 721.1

01-Jul-10 09:37 770.0 726.1 5601994 7080 631.3 726.2

01-Jul-10 09:52 776.8 736.7 5564285 7111 640.1 704.8

01-Jul-10 10:07 783.5 746.8 5607182 7250 646.9 702.5

01-Jul-10 10:22 790.2 748.0 5650079 7203 646.0 728.1

01-Jul-10 10:37 790.4 748.9 5672047 7240 642.9 724.8

01-Jul-10 10:52 789.9 745.8 5671742 7223 641.0 728.9

01-Jul-10 11:07 789.3 745.9 5671437 7212 641.3 711.8

01-Jul-10 11:22 788.8 745.2 5671132 7220 641.7 725.9

01-Jul-10 11:37 788.3 747.6 5670827 7234 642.1 723.6

01-Jul-10 11:52 787.8 746.8 5670522 7216 642.5 702.3

01-Jul-10 12:07 787.3 745.8 5670216 7215 642.9 737.2

01-Jul-10 12:22 786.8 742.9 5669911 7195 643.3 729.6

01-Jul-10 12:37 786.2 743.5 5669606 7194 643.5 721.3

01-Jul-10 12:52 785.7 742.8 5669301 7197 643.6 703.8

01-Jul-10 13:07 785.2 741.2 5668996 7205 643.8 695.6

01-Jul-10 13:22 784.8 739.7 5668691 7210 641.0 723.0

01-Jul-10 13:37 784.9 743.5 5668385 7210 639.0 715.3

01-Jul-10 13:52 785.1 740.3 5668080 7216 640.1 698.6

01-Jul-10 14:07 785.2 742.2 5667775 7206 641.1 734.4

01-Jul-10 14:22 785.3 740.7 5667470 7195 642.1 728.1

01-Jul-10 14:37 785.5 741.3 5667165 7210 643.2 730.1

01-Jul-10 14:52 785.6 739.9 5667794 7210 643.1 727.8

01-Jul-10 15:07 785.7 739.9 5667817 7213 642.6 729.2

01-Jul-10 15:22 785.9 740.7 5667841 7205 642.1 717.5

01-Jul-10 15:37 786.0 742.0 5667864 7206 641.5 723.8

AVERAGE: 785.4 743.0 5655806 7212 643.9 717.1

Boiler Data
SULFUR SYSTEM Start Time End Time Time Interval

BOILER #3 6/29/10 7:40 6/29/10 16:49 15 m

SO3 SULFUR

 FLOW

(lb/hr)

SO3 AIR HEATER 

OUTLET TEMP

 (F)

SO3 CONVERTER 

INLET TEMP

 (F)

SO3 CONVERTER 

OUTLET TEMP

 (F)

29-Jun-10 07:40 45.7 437.5 800.4 885.7

29-Jun-10 07:55 4.1 437.4 800.5 885.7

29-Jun-10 08:10 15.5 437.2 800.5 885.8

29-Jun-10 08:25 8.7 437.1 800.6 885.8

29-Jun-10 08:40 152.9 437.0 800.7 885.8

29-Jun-10 08:55 114.6 436.9 800.7 885.9

29-Jun-10 09:10 56.2 436.8 800.8 885.9

29-Jun-10 09:25 13.2 436.6 800.9 885.9

29-Jun-10 09:40 4.5 436.5 800.9 886.0

29-Jun-10 09:55 23.4 436.4 801.0 886.0

29-Jun-10 10:10 166.5 436.3 801.0 886.0

29-Jun-10 10:25 128.4 436.2 801.1 886.0

29-Jun-10 10:40 5.2 436.1 801.2 886.1

29-Jun-10 10:55 147.2 435.9 801.2 886.1

29-Jun-10 11:10 12.5 435.8 801.3 886.1

29-Jun-10 11:25 147.0 435.7 801.1 886.2

29-Jun-10 11:40 126.4 435.6 801.0 886.2

29-Jun-10 11:55 160.5 435.5 800.9 886.2

29-Jun-10 12:10 2.9 435.3 800.7 886.2

29-Jun-10 12:25 34.9 435.3 800.6 886.3

29-Jun-10 12:40 32.5 435.2 800.5 886.3

29-Jun-10 12:55 22.5 435.1 800.3 886.3

29-Jun-10 13:10 66.0 435.0 800.2 886.4

29-Jun-10 13:25 3.6 435.0 800.0 886.4

29-Jun-10 13:40 6.0 434.9 799.9 886.4

29-Jun-10 13:55 182.3 434.8 799.8 886.5

29-Jun-10 14:10 64.8 434.7 799.6 886.5

29-Jun-10 14:25 74.4 434.7 799.5 886.5

29-Jun-10 14:40 13.8 434.6 799.4 886.5

29-Jun-10 14:55 65.6 434.5 799.2 886.4

29-Jun-10 15:10 117.1 434.5 799.1 886.4

29-Jun-10 15:25 9.1 434.4 799.0 886.4

29-Jun-10 15:40 134.3 434.3 798.8 886.4

29-Jun-10 15:55 23.3 434.2 798.7 886.4

29-Jun-10 16:10 118.3 434.2 798.6 886.4

29-Jun-10 16:25 50.4 434.1 798.4 886.4

29-Jun-10 16:40 104.0 434.0 798.3 886.4

AVERAGE: 66.4 435.5 800.2 886.2

Sulfur System
SULFUR SYSTEM Start Time End Time Time Interval

BOILER #3 6/30/10 6:43 6/30/10 15:40 15 m

SO3 SULFUR

 FLOW

(lb/hr)

SO3 AIR HEATER 

OUTLET TEMP

 (F)

SO3 CONVERTER 

INLET TEMP

 (F)

SO3 CONVERTER 

OUTLET TEMP

 (F)

30-Jun-10 06:43 0.8 483.4 1046.6 870.3

30-Jun-10 06:58 31.3 225.1 791.1 871.6

30-Jun-10 07:13 2.1 401.9 697.4 877.3

30-Jun-10 07:28 10.7 758.4 795.9 884.9

30-Jun-10 07:43 3.6 712.9 871.1 889.1

30-Jun-10 07:58 26.3 416.8 808.3 861.6

30-Jun-10 08:13 123.2 464.0 743.5 844.1

30-Jun-10 08:28 89.5 681.1 796.8 850.2

30-Jun-10 08:43 6.2 603.1 839.1 856.3

30-Jun-10 08:58 140.7 468.6 805.0 857.6

30-Jun-10 09:13 9.5 535.9 774.3 857.5

30-Jun-10 09:28 149.7 621.0 797.1 857.3

30-Jun-10 09:43 16.9 558.8 815.8 857.1

30-Jun-10 09:58 1.1 511.5 805.7 856.9

30-Jun-10 10:13 14.8 560.2 795.7 856.7

30-Jun-10 10:28 58.4 596.7 794.5 856.5

30-Jun-10 10:43 11.0 553.9 794.0 856.3

30-Jun-10 10:58 1.8 529.4 793.9 856.1

30-Jun-10 11:13 48.1 555.1 794.0 856.0

30-Jun-10 11:28 0.7 569.5 794.1 855.8

30-Jun-10 11:43 128.1 561.4 794.2 855.6

30-Jun-10 11:58 11.8 553.2 794.3 855.4

30-Jun-10 12:13 157.2 560.4 794.4 855.2

30-Jun-10 12:28 4.9 571.3 794.5 855.0

30-Jun-10 12:43 98.1 551.7 794.6 854.8

30-Jun-10 12:58 149.2 527.3 794.6 854.7

30-Jun-10 13:13 117.1 546.9 794.7 854.5

30-Jun-10 13:28 143.3 566.5 794.8 854.3

30-Jun-10 13:43 120.5 562.1 794.9 854.1

30-Jun-10 13:58 136.3 553.9 795.0 853.9

30-Jun-10 14:13 77.0 556.0 795.1 853.7

30-Jun-10 14:28 9.9 561.9 795.2 853.5

30-Jun-10 14:43 18.2 558.9 795.3 853.3

30-Jun-10 14:58 18.9 551.5 795.4 853.2

30-Jun-10 15:13 150.6 547.9 795.5 853.0

30-Jun-10 15:28 8.2 547.7 795.6 852.8

AVERAGE: 58.2 546.8 802.0 858.2

Sulfur System
SULFUR SYSTEM Start Time End Time Time Interval

BOILER #3 7/1/10 6:52 7/1/10 15:40 15 m

SO3 SULFUR

 FLOW

(lb/hr)

SO3 AIR HEATER 

OUTLET TEMP

 (F)

SO3 CONVERTER 

INLET TEMP

 (F)

SO3 CONVERTER 

OUTLET TEMP

 (F)

01-Jul-10 06:52 27.0 542.2 800.6 853.0

01-Jul-10 07:07 11.6 541.9 800.7 853.0

01-Jul-10 07:22 7.5 542.0 800.7 853.1

01-Jul-10 07:37 0.9 542.6 800.8 853.1

01-Jul-10 07:52 5.7 543.2 800.9 853.2

01-Jul-10 08:07 59.8 543.7 800.9 853.2

01-Jul-10 08:22 86.2 544.3 801.0 853.3

01-Jul-10 08:37 35.1 544.9 801.1 853.3

01-Jul-10 08:52 2.2 545.5 801.1 853.3

01-Jul-10 09:07 17.0 546.0 801.2 853.2

01-Jul-10 09:22 135.6 546.6 801.3 853.0

01-Jul-10 09:37 133.7 547.2 801.3 852.9

01-Jul-10 09:52 122.6 547.7 801.4 852.7

01-Jul-10 10:07 93.5 548.3 801.5 852.6

01-Jul-10 10:22 23.4 548.9 801.5 852.5

01-Jul-10 10:37 60.3 549.5 801.6 852.3

01-Jul-10 10:52 14.3 550.0 801.7 852.2

01-Jul-10 11:07 97.5 550.6 801.7 852.0

01-Jul-10 11:22 60.0 551.2 801.8 851.9

01-Jul-10 11:37 2.5 551.7 801.9 851.8

01-Jul-10 11:52 6.2 552.3 801.9 851.6

01-Jul-10 12:07 11.4 552.9 802.0 851.5

01-Jul-10 12:22 2.9 553.4 802.1 851.3

01-Jul-10 12:37 1.4 556.9 802.1 851.2

01-Jul-10 12:52 1.7 561.5 802.2 851.1

01-Jul-10 13:07 3.1 566.0 802.3 850.9

01-Jul-10 13:22 62.1 570.6 802.4 850.8

01-Jul-10 13:37 154.8 569.1 802.4 850.7

01-Jul-10 13:52 16.4 560.6 802.5 850.5

01-Jul-10 14:07 61.9 552.1 802.6 850.4

01-Jul-10 14:22 44.9 546.2 802.6 850.2

01-Jul-10 14:37 1.2 545.4 802.7 850.1

01-Jul-10 14:52 80.5 544.7 802.7 850.0

01-Jul-10 15:07 6.9 544.7 802.7 849.8

01-Jul-10 15:22 85.3 545.9 802.8 849.7

01-Jul-10 15:37 67.6 547.1 802.8 849.5

AVERAGE: 44.6 549.9 801.8 851.8

Sulfur System
SCR Start Time End Time Time Interval

BOILER #3 6/29/10 7:40 6/29/10 16:49 15 m

N SCR INLET 

NOX LEVEL 

(PPM)

S SCR INLET NOX 

LEVEL (PPM)

N SCR OUTLET 

NOX LEVEL 

(PPM)

S SCR OUTLET 

NOX LEVEL 

(PPM)

N SCR NH3 INJ 

FLOW (K#/HR)

S SCR NH3 INJ 

FLOW (K#/HR)

29-Jun-10 07:40 259.6 305.4 26.8 29.9 2.7 2.6

29-Jun-10 07:55 254.0 304.5 26.8 30.0 2.7 2.6

29-Jun-10 08:10 259.9 303.8 26.8 30.1 2.7 2.6

29-Jun-10 08:25 260.6 304.8 26.8 30.2 2.7 2.6

29-Jun-10 08:40 261.3 304.1 26.8 30.3 2.7 2.6

29-Jun-10 08:55 262.1 304.9 26.8 30.4 2.7 2.7

29-Jun-10 09:10 262.8 305.8 26.8 30.5 2.7 2.7

29-Jun-10 09:25 263.6 306.7 26.9 30.6 2.7 2.7

29-Jun-10 09:40 264.3 307.6 26.9 30.6 2.7 2.7

29-Jun-10 09:55 265.1 308.5 26.9 30.7 2.7 2.7

29-Jun-10 10:10 257.6 309.4 26.9 30.8 2.7 2.7

29-Jun-10 10:25 257.9 310.3 26.9 30.9 2.7 2.8

29-Jun-10 10:40 258.0 314.0 26.9 31.0 2.8 2.8

29-Jun-10 10:55 258.2 315.7 26.9 31.1 2.8 2.8

29-Jun-10 11:10 258.3 317.4 26.9 31.2 2.8 2.8

29-Jun-10 11:25 258.5 319.1 27.0 31.3 2.8 2.8

29-Jun-10 11:40 258.6 320.9 27.0 31.4 2.8 2.8

29-Jun-10 11:55 258.8 322.6 27.0 31.5 2.8 2.8

29-Jun-10 12:10 260.2 324.3 27.0 31.6 2.8 2.8

29-Jun-10 12:25 260.9 326.0 27.0 31.7 2.8 2.9

29-Jun-10 12:40 261.5 324.8 27.0 31.8 2.8 2.9

29-Jun-10 12:55 262.1 324.8 27.0 31.9 2.8 2.9

29-Jun-10 13:10 262.7 324.8 27.0 32.0 2.8 2.9

29-Jun-10 13:25 263.3 324.8 27.0 32.1 2.8 2.9

29-Jun-10 13:40 264.0 324.8 27.1 32.2 2.8 2.9

29-Jun-10 13:55 264.6 324.7 27.1 32.3 2.8 2.9

29-Jun-10 14:10 263.9 324.7 27.1 32.4 2.8 2.9

29-Jun-10 14:25 264.2 324.7 27.1 32.5 2.8 2.9

29-Jun-10 14:40 264.4 320.7 27.1 32.5 2.8 2.9

29-Jun-10 14:55 264.7 321.0 27.1 32.5 2.8 2.9

29-Jun-10 15:10 265.0 321.3 27.1 32.5 2.9 2.9

29-Jun-10 15:25 265.2 321.7 27.0 32.5 2.8 2.8

29-Jun-10 15:40 265.5 322.0 26.9 32.5 2.8 2.9

29-Jun-10 15:55 265.7 322.4 26.9 32.5 2.8 2.9

29-Jun-10 16:10 268.2 322.7 26.8 32.5 2.9 2.9

29-Jun-10 16:25 268.0 323.0 26.8 32.5 2.8 2.9

29-Jun-10 16:40 267.8 325.2 26.7 32.5 2.8 2.9

AVERAGE: 262.2 317.1 26.9 31.5 2.8 2.8

NOx Levels SCR Flow
SCR Start Time End Time Time Interval

BOILER #3 6/30/10 6:43 6/30/10 15:40 15 m

N SCR INLET 

NOX LEVEL 

(PPM)

S SCR INLET NOX 

LEVEL (PPM)

N SCR OUTLET 

NOX LEVEL 

(PPM)

S SCR OUTLET 

NOX LEVEL 

(PPM)

N SCR NH3 INJ 

FLOW (K#/HR)

S SCR NH3 INJ 

FLOW (K#/HR)

30-Jun-10 06:43 271.1 308.4 26.1 32.5 2.7 2.7

30-Jun-10 06:58 271.3 310.0 26.2 32.6 2.8 2.8

30-Jun-10 07:13 271.3 310.1 26.3 32.6 2.8 2.8

30-Jun-10 07:28 271.2 309.5 26.3 32.7 2.7 2.8

30-Jun-10 07:43 271.1 308.9 26.4 32.7 2.7 2.8

30-Jun-10 07:58 29.3 308.8 26.5 32.7 2.8 2.8

30-Jun-10 08:13 265.3 308.8 26.6 32.8 2.8 2.8

30-Jun-10 08:28 265.8 308.7 26.7 32.8 2.7 2.8

30-Jun-10 08:43 266.4 317.3 26.8 32.8 2.7 2.8

30-Jun-10 08:58 266.9 318.1 26.9 32.9 2.8 2.8

30-Jun-10 09:13 267.5 318.9 27.0 32.9 2.8 2.9

30-Jun-10 09:28 268.0 319.7 27.1 32.9 2.8 2.9

30-Jun-10 09:43 268.5 320.4 27.2 33.0 2.8 2.8

30-Jun-10 09:58 267.3 322.1 27.3 33.0 2.8 2.8

30-Jun-10 10:13 265.1 324.2 27.4 33.0 2.8 2.9

30-Jun-10 10:28 265.9 326.3 27.5 33.1 2.8 2.9

30-Jun-10 10:43 267.1 320.9 27.6 33.1 2.8 2.9

30-Jun-10 10:58 268.6 323.6 27.6 33.2 2.8 2.9

30-Jun-10 11:13 270.0 326.3 27.7 33.2 2.8 2.9

30-Jun-10 11:28 272.4 330.7 27.8 33.2 2.8 2.9

30-Jun-10 11:43 274.9 336.2 27.9 33.3 2.8 2.9

30-Jun-10 11:58 277.3 339.9 28.0 33.3 2.8 3.0

30-Jun-10 12:13 277.6 334.1 28.1 33.3 2.9 2.9

30-Jun-10 12:28 278.2 329.2 28.2 33.4 2.8 2.9

30-Jun-10 12:43 278.8 338.1 28.3 33.4 2.9 2.9

30-Jun-10 12:58 279.3 337.5 28.4 33.4 2.9 2.9

30-Jun-10 13:13 279.9 337.0 28.5 33.5 2.9 2.9

30-Jun-10 13:28 280.5 336.5 28.6 33.5 2.8 2.9

30-Jun-10 13:43 281.0 336.0 28.7 33.6 2.8 2.9

30-Jun-10 13:58 281.6 335.5 28.8 33.6 2.9 2.9

30-Jun-10 14:13 275.6 332.5 28.9 33.6 2.8 2.9

30-Jun-10 14:28 276.0 329.3 29.0 33.6 2.8 2.9

30-Jun-10 14:43 276.4 329.5 29.0 33.6 2.8 2.9

30-Jun-10 14:58 276.9 329.0 29.1 33.6 2.9 2.9

30-Jun-10 15:13 277.3 328.5 29.0 33.6 2.9 2.9

30-Jun-10 15:28 277.4 327.9 29.0 33.6 2.9 2.8

AVERAGE: 266.1 324.4 27.7 33.2 2.8 2.9

NOx Levels SCR Flow
SCR Start Time End Time Time Interval

BOILER #3 7/1/10 6:52 7/1/10 15:40 15 m

N SCR INLET 

NOX LEVEL 

(PPM)

S SCR INLET NOX 

LEVEL (PPM)

N SCR OUTLET 

NOX LEVEL 

(PPM)

S SCR OUTLET 

NOX LEVEL 

(PPM)

N SCR NH3 INJ 

FLOW (K#/HR)

S SCR NH3 INJ 

FLOW (K#/HR)

01-Jul-10 06:52 277.3 335.4 26.3 32.2 2.8 2.9

01-Jul-10 07:07 278.8 331.1 26.4 32.2 2.8 2.9

01-Jul-10 07:22 280.3 332.2 26.5 32.3 2.8 2.9

01-Jul-10 07:37 281.8 333.3 26.7 32.3 2.8 2.9

01-Jul-10 07:52 283.3 334.4 26.8 32.3 2.9 2.9

01-Jul-10 08:07 282.4 335.6 26.9 32.4 2.8 2.9

01-Jul-10 08:22 282.1 336.7 27.1 32.4 2.9 2.9

01-Jul-10 08:37 281.7 335.6 27.2 32.5 2.8 2.9

01-Jul-10 08:52 281.3 332.2 27.4 32.5 2.8 2.9

01-Jul-10 09:07 281.0 330.0 27.5 32.5 2.8 2.9

01-Jul-10 09:22 280.6 327.8 27.6 32.6 2.8 2.8

01-Jul-10 09:37 280.3 328.1 27.8 32.6 2.6 2.6

01-Jul-10 09:52 279.9 332.0 27.9 32.7 2.8 2.9

01-Jul-10 10:07 272.8 330.6 28.0 32.7 2.9 2.9

01-Jul-10 10:22 274.0 329.3 28.2 32.7 2.8 2.8

01-Jul-10 10:37 275.2 334.3 28.3 32.8 2.8 2.7

01-Jul-10 10:52 276.4 334.9 28.4 32.8 2.8 2.8

01-Jul-10 11:07 277.6 335.5 28.6 32.9 2.8 2.8

01-Jul-10 11:22 278.8 336.1 28.7 32.9 2.8 2.8

01-Jul-10 11:37 280.0 336.7 28.9 32.9 2.8 2.8

01-Jul-10 11:52 285.8 337.3 29.0 33.0 2.8 2.8

01-Jul-10 12:07 278.6 337.9 29.1 33.0 2.8 2.8

01-Jul-10 12:22 280.5 338.5 29.3 33.1 2.9 2.8

01-Jul-10 12:37 282.3 338.4 29.4 33.1 2.9 2.8

01-Jul-10 12:52 284.2 334.5 29.5 33.1 2.9 2.7

01-Jul-10 13:07 286.4 330.5 29.7 33.2 2.9 2.7

01-Jul-10 13:22 288.7 329.0 29.8 33.2 2.9 2.7

01-Jul-10 13:37 290.9 328.5 29.9 33.3 2.9 2.8

01-Jul-10 13:52 293.2 327.9 30.1 33.3 2.9 2.8

01-Jul-10 14:07 294.8 327.4 30.2 33.3 3.0 2.8

01-Jul-10 14:22 293.9 326.8 30.4 33.4 2.9 2.8

01-Jul-10 14:37 293.1 319.7 30.5 33.3 2.9 2.8

01-Jul-10 14:52 292.2 322.3 30.6 33.3 2.9 2.8

01-Jul-10 15:07 291.3 324.8 30.5 33.3 2.9 2.8

01-Jul-10 15:22 290.4 326.2 30.5 33.3 2.9 2.8

01-Jul-10 15:37 289.5 326.9 30.4 33.2 2.9 2.8

AVERAGE: 283.4 331.6 28.6 32.9 2.8 2.8

NOx Levels SCR Flow
FGD SCRUBBER Start Time End Time Time Interval

BOILER #3 6/29/10 7:40 6/29/10 16:49 15 m

ABSORBER 

BLD METER 1

(pH)

ABSORBER BLD 

METER 2

(pH)

BOOSTER FAN 

TEMP

 (F)

BOOSTER 

FAN TEMP 

TC1 (F)

BOOSTER 

FAN TEMP 

TC2 (F)

BOOSTER 

FAN TEMP 

TC3 (F)

ABSORBER AVG 

GAS OUT TEMP 

(F)

ABSORBER FLUE 

GAS OUT TEMP 

302 (F)

ABSORBER FLUE 

GAS OUT TEMP 

307 (F)

ABSORBER 

FLUE GAS OUT 

TEMP 308 (F)

29-Jun-10 07:40 5.4 5.4 281.0 282.6 212.5 286.9 128.6 128.4 126.6 127.5

29-Jun-10 07:55 5.4 5.4 280.8 282.0 212.5 285.9 128.5 128.0 126.5 127.5

29-Jun-10 08:10 5.4 5.4 280.6 281.3 212.5 284.9 128.4 127.9 126.5 127.4

29-Jun-10 08:25 5.4 5.4 280.4 280.5 212.5 283.8 128.2 127.4 126.5 127.4

29-Jun-10 08:40 5.4 5.4 280.6 279.8 212.5 282.8 128.1 127.5 126.5 127.3

29-Jun-10 08:55 5.4 5.4 280.7 279.5 212.5 282.4 128.0 127.7 126.4 127.3

29-Jun-10 09:10 5.4 5.4 280.9 279.2 212.5 282.2 128.0 127.3 126.4 127.2

29-Jun-10 09:25 5.4 5.4 281.0 279.1 212.5 282.1 127.9 126.9 126.4 127.2

29-Jun-10 09:40 5.4 5.4 281.2 279.5 212.4 282.4 127.9 127.5 126.3 127.1

29-Jun-10 09:55 5.4 5.4 281.3 279.8 212.4 282.7 127.9 127.1 126.3 127.1

29-Jun-10 10:10 5.4 5.4 281.5 280.1 212.4 283.0 127.8 126.8 126.3 127.0

29-Jun-10 10:25 5.4 5.4 281.7 280.5 212.4 283.3 127.9 127.6 126.2 127.0

29-Jun-10 10:40 5.4 5.4 281.8 280.8 212.4 283.6 127.9 127.5 126.1 126.9

29-Jun-10 10:55 5.4 5.4 282.0 281.2 212.4 283.9 128.0 127.4 126.0 126.9

29-Jun-10 11:10 5.4 5.4 282.1 281.5 212.3 284.2 128.1 127.7 125.9 126.8

29-Jun-10 11:25 5.4 5.4 282.3 281.9 212.4 284.5 128.0 127.4 125.8 126.8

29-Jun-10 11:40 5.4 5.4 282.4 282.2 212.5 284.7 127.9 127.0 125.7 126.7

29-Jun-10 11:55 5.4 5.4 282.6 282.5 212.6 284.9 127.8 127.6 125.6 126.7

29-Jun-10 12:10 5.4 5.4 282.7 282.7 212.6 285.1 127.7 127.1 125.5 126.6

29-Jun-10 12:25 5.4 5.4 282.8 282.8 212.7 285.3 127.6 127.0 125.5 126.6

29-Jun-10 12:40 5.4 5.4 282.9 282.9 212.3 285.3 127.6 127.6 125.4 126.7

29-Jun-10 12:55 5.4 5.4 282.9 283.1 212.2 285.4 127.7 127.6 125.3 126.7

29-Jun-10 13:10 5.4 5.4 283.0 283.2 212.3 285.5 127.8 127.7 125.3 126.7

29-Jun-10 13:25 5.4 5.4 283.0 283.4 212.3 285.6 127.8 127.8 125.5 126.7

29-Jun-10 13:40 5.4 5.4 283.1 283.4 212.4 285.6 127.9 127.8 125.7 126.7

29-Jun-10 13:55 5.5 5.4 283.1 283.4 212.5 285.5 128.0 127.5 125.9 126.8

29-Jun-10 14:10 5.5 5.4 283.2 283.4 212.5 285.5 127.9 127.8 126.1 126.8

29-Jun-10 14:25 5.4 5.4 283.2 283.3 212.6 285.5 127.9 127.9 126.3 126.8

29-Jun-10 14:40 5.4 5.4 283.3 283.3 212.6 285.4 127.9 127.9 126.4 126.8

29-Jun-10 14:55 5.5 5.4 283.3 283.3 212.6 285.4 127.8 126.9 126.4 126.8

29-Jun-10 15:10 5.5 5.4 283.4 283.2 212.6 285.4 127.8 127.5 126.4 126.9

29-Jun-10 15:25 5.5 5.4 283.4 283.2 212.6 285.3 127.8 127.2 126.4 126.9

29-Jun-10 15:40 5.5 5.5 283.5 283.3 212.6 285.4 127.8 126.8 126.4 126.9

29-Jun-10 15:55 5.5 5.5 283.5 283.5 212.6 285.5 127.9 127.7 126.4 126.9

29-Jun-10 16:10 5.5 5.5 283.5 283.7 212.6 285.5 128.0 127.7 126.4 126.9

29-Jun-10 16:25 5.5 5.5 283.6 283.9 212.6 285.6 128.1 127.6 126.4 126.9

29-Jun-10 16:40 5.5 5.5 283.6 284.1 212.6 285.9 128.2 127.9 126.4 126.9

Absorber pH Temperature In Temperature Out
AVERAGE: 5.4 5.4 282.3 282.1 212.5 284.6 127.9 127.5 126.1 126.9

FGD SCRUBBER Start Time End Time Time Interval

BOILER #3 6/30/10 6:43 6/30/10 15:40 15 m

ABSORBER 

BLD METER 1

(pH)

ABSORBER BLD 

METER 2

(pH)

BOOSTER FAN 

TEMP

 (F)

BOOSTER 

FAN TEMP 

TC1 (F)

BOOSTER 

FAN TEMP 

TC2 (F)

BOOSTER 

FAN TEMP 

TC3 (F)

ABSORBER AVG 

GAS OUT TEMP 

(F)

ABSORBER FLUE 

GAS OUT TEMP 

302 (F)

ABSORBER FLUE 

GAS OUT TEMP 

307 (F)

ABSORBER 

FLUE GAS OUT 

TEMP 308 (F)

30-Jun-10 06:43 5.3 5.3 276.2 274.9 212.6 277.8 127.6 126.8 125.9 127.6

30-Jun-10 06:58 5.3 5.3 276.1 274.4 212.6 277.7 127.6 127.4 125.9 127.6

30-Jun-10 07:13 5.3 5.3 276.0 274.6 212.6 277.7 127.7 127.2 125.8 127.6

30-Jun-10 07:28 5.3 5.3 275.9 274.8 212.6 277.9 127.8 127.1 125.9 127.5

30-Jun-10 07:43 5.3 5.3 275.8 275.0 212.6 278.1 127.8 127.0 126.1 127.5

30-Jun-10 07:58 5.3 5.3 275.7 275.2 212.6 278.2 127.7 127.2 126.4 127.5

30-Jun-10 08:13 5.3 5.3 275.7 275.4 212.6 278.4 127.7 127.5 126.7 127.5

30-Jun-10 08:28 5.3 5.3 275.7 275.7 212.6 278.7 127.7 126.8 127.0 127.5

30-Jun-10 08:43 5.3 5.3 276.1 276.4 212.5 279.3 127.8 127.4 127.1 127.5

30-Jun-10 08:58 5.3 5.3 276.6 277.0 212.5 279.8 127.8 127.1 127.2 127.5

30-Jun-10 09:13 5.3 5.3 277.0 277.7 212.5 280.4 127.9 127.4 127.3 127.5

30-Jun-10 09:28 5.3 5.3 277.5 278.2 212.5 280.8 127.8 127.7 127.1 127.5

30-Jun-10 09:43 5.3 5.3 277.9 278.7 212.5 281.2 127.7 127.1 126.8 127.4

30-Jun-10 09:58 5.3 5.3 278.4 279.3 212.5 281.9 127.6 126.6 126.4 127.4

30-Jun-10 10:13 5.3 5.3 278.8 280.1 212.5 282.6 127.3 127.1 126.1 127.4

30-Jun-10 10:28 5.3 5.3 279.3 280.8 212.5 283.3 127.3 127.2 125.9 127.4

30-Jun-10 10:43 5.3 5.3 279.7 281.3 212.5 283.7 127.3 127.4 125.9 127.3

30-Jun-10 10:58 5.3 5.3 280.2 281.8 212.6 284.1 127.4 127.2 125.9 127.3

30-Jun-10 11:13 5.3 5.3 280.6 282.1 212.7 284.5 127.5 127.5 125.8 127.3

30-Jun-10 11:28 5.3 5.3 281.1 282.4 212.7 284.7 127.5 127.3 125.8 127.3

30-Jun-10 11:43 5.3 5.3 281.5 282.6 212.8 284.9 127.6 127.1 125.7 127.3

30-Jun-10 11:58 5.3 5.3 282.0 282.9 212.8 285.0 127.7 127.5 125.7 127.2

30-Jun-10 12:13 5.3 5.3 282.4 283.2 212.9 285.2 127.9 127.0 125.6 127.2

30-Jun-10 12:28 5.3 5.3 282.9 283.4 212.9 285.3 128.0 127.8 125.5 127.2

30-Jun-10 12:43 5.3 5.3 283.3 283.6 212.9 285.5 128.0 128.0 125.4 127.2

30-Jun-10 12:58 5.3 5.3 283.4 283.7 213.0 285.6 128.0 127.9 125.4 127.2

30-Jun-10 13:13 5.3 5.3 283.5 283.8 213.0 285.8 127.9 127.2 125.3 127.2

30-Jun-10 13:28 5.3 5.3 283.5 283.9 213.1 286.0 127.9 127.8 125.2 127.2

30-Jun-10 13:43 5.3 5.3 283.5 283.9 213.1 286.1 127.9 127.0 125.2 127.1

30-Jun-10 13:58 5.3 5.3 283.6 284.0 213.1 286.1 127.9 127.9 125.4 127.1

30-Jun-10 14:13 5.3 5.3 283.6 284.1 213.1 286.2 127.9 127.5 125.5 127.1

30-Jun-10 14:28 5.3 5.3 283.6 284.2 213.1 286.3 127.9 127.9 125.7 127.1

30-Jun-10 14:43 5.3 5.3 283.7 284.3 213.1 286.4 127.9 127.0 125.8 127.1

30-Jun-10 14:58 5.3 5.3 283.7 284.4 213.1 286.5 127.9 127.8 126.0 127.1

30-Jun-10 15:13 5.3 5.3 283.7 284.5 213.0 286.6 128.0 127.9 126.1 127.1

30-Jun-10 15:28 5.3 5.3 283.8 284.6 213.0 286.7 128.0 127.1 126.3 127.0

Absorber pH Temperature In Temperature Out
AVERAGE: 5.3 5.3 280.1 280.5 212.8 282.9 127.7 127.3 126.0 127.3

FGD SCRUBBER Start Time End Time Time Interval

BOILER #3 7/1/10 6:52 7/1/10 15:40 15 m

ABSORBER 

BLD METER 1

(pH)

ABSORBER BLD 

METER 2

(pH)

BOOSTER FAN 

TEMP

 (F)

BOOSTER 

FAN TEMP 

TC1 (F)

BOOSTER 

FAN TEMP 

TC2 (F)

BOOSTER 

FAN TEMP 

TC3 (F)

ABSORBER AVG 

GAS OUT TEMP 

(F)

ABSORBER FLUE 

GAS OUT TEMP 

302 (F)

ABSORBER FLUE 

GAS OUT TEMP 

307 (F)

ABSORBER 

FLUE GAS OUT 

TEMP 308 (F)

01-Jul-10 06:52 5.4 5.4 276.8 275.4 212.9 277.7 127.5 126.8 125.7 126.9

01-Jul-10 07:07 5.4 5.4 276.8 275.3 212.9 277.6 127.3 127.4 125.7 127.0

01-Jul-10 07:22 5.4 5.4 276.8 275.3 212.9 277.7 127.9 127.7 125.5 127.1

01-Jul-10 07:37 5.4 5.4 276.7 275.4 212.9 277.8 127.8 126.9 125.3 127.1

01-Jul-10 07:52 5.4 5.4 276.7 275.6 212.9 278.0 127.7 127.0 125.1 127.2

01-Jul-10 08:07 5.4 5.4 276.7 275.8 212.9 278.1 127.6 127.2 125.0 127.2

01-Jul-10 08:22 5.4 5.4 276.6 275.9 212.9 278.3 127.5 126.8 125.0 127.3

01-Jul-10 08:37 5.4 5.4 276.6 276.4 212.9 278.7 127.5 126.5 125.4 127.4

01-Jul-10 08:52 5.4 5.4 276.9 276.9 212.9 279.2 127.8 127.5 125.7 127.4

01-Jul-10 09:07 5.4 5.4 277.2 277.5 212.9 279.7 128.1 127.8 126.1 127.4

01-Jul-10 09:22 5.4 5.4 277.5 278.0 212.9 280.2 128.0 127.0 126.4 127.5

01-Jul-10 09:37 5.4 5.4 277.8 278.6 212.9 280.7 128.0 127.9 126.5 127.5

01-Jul-10 09:52 5.4 5.4 278.1 279.0 212.9 281.2 128.0 127.7 126.5 127.5

01-Jul-10 10:07 5.4 5.4 278.5 279.4 212.9 281.7 128.0 126.9 126.6 127.5

01-Jul-10 10:22 5.4 5.4 278.8 279.8 212.9 282.1 128.0 127.7 126.7 127.5

01-Jul-10 10:37 5.4 5.4 279.1 280.3 212.9 282.5 128.0 127.9 126.7 127.5

01-Jul-10 10:52 5.4 5.4 279.4 280.7 212.9 282.9 128.0 127.1 126.8 127.6

01-Jul-10 11:07 5.4 5.4 279.7 281.1 212.9 283.2 128.0 127.9 126.9 127.6

01-Jul-10 11:22 5.4 5.4 280.0 281.5 213.0 283.4 127.9 127.7 127.0 127.6

01-Jul-10 11:37 5.4 5.4 280.3 282.0 213.0 283.5 127.8 126.8 127.0 127.6

01-Jul-10 11:52 5.4 5.4 280.6 282.3 213.0 283.7 127.7 127.3 127.1 127.6

01-Jul-10 12:07 5.4 5.4 280.9 282.4 213.0 283.9 128.1 127.8 127.1 127.6

01-Jul-10 12:22 5.4 5.4 281.2 282.5 213.0 284.0 128.3 128.0 127.0 127.6

01-Jul-10 12:37 5.4 5.4 281.5 282.6 213.1 284.1 128.1 128.0 126.8 127.6

01-Jul-10 12:52 5.4 5.4 281.8 282.7 213.1 284.2 128.0 128.1 126.7 127.6

01-Jul-10 13:07 5.4 5.4 282.1 283.0 213.1 284.5 127.9 127.3 126.6 127.6

01-Jul-10 13:22 5.4 5.4 282.4 283.3 213.1 284.8 127.7 127.3 126.5 127.6

01-Jul-10 13:37 5.4 5.4 282.7 283.7 213.1 285.2 127.7 127.7 126.4 127.5

01-Jul-10 13:52 5.4 5.4 283.0 284.0 213.2 285.5 127.6 127.8 126.3 127.5

01-Jul-10 14:07 5.4 5.4 283.3 284.1 213.2 285.8 127.6 126.7 126.2 127.5

01-Jul-10 14:22 5.4 5.4 283.6 284.2 213.1 285.6 127.6 127.4 126.0 127.5

01-Jul-10 14:37 5.4 5.4 283.9 284.3 213.1 285.4 127.7 127.6 126.0 127.5

01-Jul-10 14:52 5.4 5.4 284.2 284.5 213.0 285.5 127.8 127.6 126.1 127.4

01-Jul-10 15:07 5.4 5.4 284.6 284.6 213.0 285.6 127.6 127.6 126.2 127.4

01-Jul-10 15:22 5.4 5.4 284.7 284.7 213.0 285.7 127.5 127.4 126.3 127.3

Absorber pH Temperature In Temperature Out
01-Jul-10 15:37 5.4 5.4 284.7 284.8 213.0 285.8 127.4 127.2 126.4 127.2

AVERAGE: 5.4 5.4 280.1 280.5 213.0 282.3 127.8 127.4 126.3 127.4
FGD SCRUBBER Start Time End Time Time Interval

BOILER #3 6/29/10 7:40 6/29/10 16:49 15 m

NC ABSORBER 

RECYCLE PUMP 

(amps)

SC ABSORBER 

RECYCLE PUMP 

(amps)

N ABSORBER 

RECYCLE PUMP 

(amps)

S ABSORBER 

RECYCLE PUMP 

(amps)

BOOSTER FAN 

AVG DISCH_P 

(in)

BOOSTER FAN 

Disch_P1

 (in)

BOOSTER FAN 

Disch_P2

 (in)

BOOSTER FAN 

Disch_P3

 (in)

ABSORBER FLUE 

GAS OUT 

PRESSURE 

(inH20)

29-Jun-10 07:40 168.0 166.4 165.4 0.0 9.8 11.2 10.4 10.2 0.0

29-Jun-10 07:55 166.5 169.4 161.3 0.0 9.8 11.2 10.4 10.2 0.0

29-Jun-10 08:10 167.0 172.1 160.1 0.0 9.8 11.1 10.4 10.2 0.0

29-Jun-10 08:25 169.2 170.7 162.9 0.0 9.8 11.1 10.4 10.2 0.0

29-Jun-10 08:40 169.6 171.8 163.1 Bad 9.8 11.0 10.4 10.2 0.0

29-Jun-10 08:55 170.3 170.9 161.2 Bad 9.8 11.0 10.4 10.2 0.0

29-Jun-10 09:10 171.0 171.0 164.0 Bad 9.8 11.0 10.4 10.2 0.0

29-Jun-10 09:25 167.3 173.1 161.4 0.0 9.8 10.9 10.4 10.2 0.0

29-Jun-10 09:40 171.2 170.2 163.0 0.0 9.9 10.9 10.4 10.1 -0.1

29-Jun-10 09:55 166.5 172.0 162.6 0.0 9.9 10.9 10.4 10.1 0.0

29-Jun-10 10:10 166.0 170.1 161.1 0.0 9.9 10.9 10.4 10.1 -0.1

29-Jun-10 10:25 165.6 171.6 167.3 0.0 9.9 10.9 10.4 10.1 -0.1

29-Jun-10 10:40 168.1 168.0 158.8 0.0 9.9 10.9 10.4 10.1 -0.1

29-Jun-10 10:55 168.4 169.9 162.4 0.0 9.9 10.9 10.4 10.1 -0.1

29-Jun-10 11:10 169.0 177.2 161.0 0.0 9.9 10.9 10.4 10.1 -0.2

29-Jun-10 11:25 168.7 174.0 156.4 0.0 9.9 10.9 10.4 10.1 -0.1

29-Jun-10 11:40 169.0 172.8 162.3 0.0 9.9 10.9 10.5 10.0 -0.1

29-Jun-10 11:55 167.2 172.0 161.6 0.0 9.9 10.9 10.5 10.0 -0.1

29-Jun-10 12:10 171.4 168.0 167.6 0.0 9.9 10.9 10.5 10.0 0.0

29-Jun-10 12:25 167.1 171.2 165.1 0.0 9.9 10.9 10.5 10.0 -0.2

29-Jun-10 12:40 167.4 168.2 161.7 0.0 9.9 10.9 10.5 10.0 0.0

29-Jun-10 12:55 169.2 171.0 164.7 0.0 9.9 10.9 10.5 10.0 0.0

29-Jun-10 13:10 167.8 171.2 160.1 0.0 9.9 10.9 10.5 10.1 0.1

29-Jun-10 13:25 167.0 169.9 162.5 0.0 9.9 10.9 10.5 10.1 0.1

29-Jun-10 13:40 166.2 170.6 165.3 0.0 9.9 10.9 10.5 10.1 0.1

29-Jun-10 13:55 168.1 169.0 161.1 0.0 9.9 10.9 10.5 10.1 0.0

29-Jun-10 14:10 168.8 171.7 161.8 0.0 9.9 10.9 10.5 10.1 0.2

29-Jun-10 14:25 169.5 171.4 161.5 0.0 9.9 10.9 10.5 10.1 0.0

29-Jun-10 14:40 167.1 177.5 162.4 0.0 9.9 10.9 10.5 10.1 0.1

29-Jun-10 14:55 166.8 171.7 160.1 0.0 9.9 11.0 10.5 10.1 0.1

29-Jun-10 15:10 168.4 171.8 160.0 0.0 9.9 11.0 10.5 10.1 0.1

29-Jun-10 15:25 167.9 167.0 161.3 0.0 9.9 11.0 10.5 10.2 0.0

29-Jun-10 15:40 164.0 171.6 160.5 0.0 9.9 11.0 10.5 10.2 0.1

29-Jun-10 15:55 168.3 168.5 160.5 0.0 9.9 11.0 10.5 10.2 0.1

29-Jun-10 16:10 168.0 167.0 159.6 0.0 9.9 11.0 10.5 10.2 0.1

29-Jun-10 16:25 167.5 171.9 158.6 0.0 9.9 11.0 10.6 10.2 0.1

29-Jun-10 16:40 167.5 170.2 164.7 0.0 9.9 11.0 10.5 10.2 0.1

Liquid Flow rate Pressure Drop
AVERAGE: 168.0 170.9 162.0 0.0 9.9 10.9 10.5 10.1 0.0

FGD SCRUBBER Start Time End Time Time Interval

BOILER #3 6/30/10 6:43 6/30/10 15:40 15 m

NC ABSORBER 

RECYCLE PUMP 

(amps)

SC ABSORBER 

RECYCLE PUMP 

(amps)

N ABSORBER 

RECYCLE PUMP 

(amps)

S ABSORBER 

RECYCLE PUMP 

(amps)

BOOSTER FAN 

AVG DISCH_P 

(in)

BOOSTER FAN 

Disch_P1

 (in)

BOOSTER FAN 

Disch_P2

 (in)

BOOSTER FAN 

Disch_P3

 (in)

ABSORBER FLUE 

GAS OUT 

PRESSURE 

(inH20)

30-Jun-10 06:43 169.2 173.4 165.0 0.0 10.0 10.6 10.3 9.8 -0.2

30-Jun-10 06:58 166.0 172.0 164.6 0.0 10.0 10.5 10.3 9.8 0.0

30-Jun-10 07:13 167.1 171.8 165.2 0.0 10.0 10.5 10.3 9.8 0.0

30-Jun-10 07:28 171.1 175.5 161.6 0.0 10.0 10.5 10.3 9.8 -0.1

30-Jun-10 07:43 168.7 173.9 161.0 0.0 10.0 10.5 10.3 9.9 -0.1

30-Jun-10 07:58 171.4 173.2 163.4 0.0 10.0 10.6 10.3 9.9 -0.1

30-Jun-10 08:13 170.8 175.0 165.4 0.0 10.0 10.6 10.3 9.9 0.0

30-Jun-10 08:28 170.9 174.2 165.0 0.0 10.0 10.6 10.3 9.9 0.0

30-Jun-10 08:43 171.0 173.3 164.0 0.0 10.0 10.6 10.3 9.9 0.0

30-Jun-10 08:58 171.0 174.0 166.6 0.0 10.0 10.6 10.3 9.9 0.0

30-Jun-10 09:13 169.4 175.0 166.0 0.0 10.0 10.7 10.3 9.9 0.0

30-Jun-10 09:28 171.0 175.0 167.7 0.0 10.0 10.7 10.3 10.0 0.0

30-Jun-10 09:43 173.0 174.5 163.0 0.0 10.0 10.7 10.3 10.0 -0.1

30-Jun-10 09:58 170.0 175.9 164.2 0.0 10.0 10.7 10.3 10.0 0.0

30-Jun-10 10:13 169.9 175.5 159.7 0.0 10.0 10.7 10.3 10.0 0.0

30-Jun-10 10:28 169.1 174.8 164.8 0.0 10.0 10.7 10.3 10.0 -0.1

30-Jun-10 10:43 171.0 173.8 165.1 0.0 10.0 10.8 10.3 10.0 -0.2

30-Jun-10 10:58 171.7 172.1 164.6 0.0 10.0 10.8 10.3 10.0 0.0

30-Jun-10 11:13 169.9 173.0 162.4 0.0 10.0 10.8 10.3 10.0 -0.2

30-Jun-10 11:28 169.3 173.3 166.4 0.0 10.0 10.8 10.3 10.0 -0.2

30-Jun-10 11:43 172.8 173.5 165.5 0.0 10.0 10.8 10.3 10.0 0.0

30-Jun-10 11:58 168.0 167.7 161.9 0.0 10.0 10.8 10.3 10.1 -0.2

30-Jun-10 12:13 169.6 173.9 165.0 0.0 10.0 10.8 10.4 10.1 -0.1

30-Jun-10 12:28 169.1 174.7 160.4 0.0 10.0 10.8 10.4 10.1 0.0

30-Jun-10 12:43 169.7 170.6 168.4 0.0 10.0 10.8 10.4 10.1 0.1

30-Jun-10 12:58 170.4 172.0 168.0 0.0 10.0 10.9 10.4 10.1 0.0

30-Jun-10 13:13 170.5 176.0 161.8 0.0 10.0 10.9 10.4 10.1 0.1

30-Jun-10 13:28 169.3 172.8 160.8 0.0 10.0 10.9 10.4 10.1 0.0

30-Jun-10 13:43 171.0 171.5 170.7 0.0 10.0 10.9 10.4 10.1 0.0

30-Jun-10 13:58 171.3 173.9 169.8 0.0 10.0 10.9 10.4 10.1 -0.1

30-Jun-10 14:13 167.7 172.3 163.6 0.0 10.1 10.9 10.4 10.1 -0.2

30-Jun-10 14:28 171.0 174.1 165.0 0.0 10.1 10.9 10.4 10.1 -0.1

30-Jun-10 14:43 173.0 175.5 164.9 0.0 10.1 10.9 10.4 10.1 -0.1

30-Jun-10 14:58 168.1 171.1 163.1 0.0 10.1 10.9 10.4 10.1 -0.1

30-Jun-10 15:13 172.6 171.0 164.4 0.0 10.1 11.0 10.4 10.2 0.0

30-Jun-10 15:28 169.1 174.0 159.2 0.0 10.1 11.0 10.4 10.2 0.2

Liquid Flow rate Pressure Drop
AVERAGE: 170.1 173.4 164.4 0.0 10.0 10.8 10.3 10.0 -0.1

FGD SCRUBBER Start Time End Time Time Interval

BOILER #3 7/1/10 6:52 7/1/10 15:40 15 m

NC ABSORBER 

RECYCLE PUMP 

(amps)

SC ABSORBER 

RECYCLE PUMP 

(amps)

N ABSORBER 

RECYCLE PUMP 

(amps)

S ABSORBER 

RECYCLE PUMP 

(amps)

BOOSTER FAN 

AVG DISCH_P 

(in)

BOOSTER FAN 

Disch_P1

 (in)

BOOSTER FAN 

Disch_P2

 (in)

BOOSTER FAN 

Disch_P3

 (in)

ABSORBER FLUE 

GAS OUT 

PRESSURE 

(inH20)

01-Jul-10 06:52 168.6 170.6 161.1 0.0 10.2 10.7 10.3 10.0 -0.1

01-Jul-10 07:07 167.0 169.4 161.0 0.0 10.2 10.7 10.3 10.0 -0.1

01-Jul-10 07:22 166.4 169.6 162.3 0.0 10.2 10.7 10.3 9.9 -0.1

01-Jul-10 07:37 169.9 172.3 162.8 0.0 10.2 10.7 10.3 9.9 -0.1

01-Jul-10 07:52 168.9 171.5 162.5 0.0 10.2 10.7 10.3 9.9 -0.1

01-Jul-10 08:07 168.9 170.0 160.5 0.0 10.2 10.6 10.3 10.0 -0.1

01-Jul-10 08:22 171.4 170.6 156.6 0.0 10.2 10.6 10.3 10.0 0.0

01-Jul-10 08:37 167.7 171.8 161.9 0.0 10.2 10.6 10.3 10.1 0.0

01-Jul-10 08:52 164.2 167.1 162.1 0.0 10.2 10.6 10.3 10.1 0.0

01-Jul-10 09:07 167.0 171.0 162.9 0.0 10.2 10.6 10.3 10.2 0.0

01-Jul-10 09:22 168.8 176.7 162.5 0.0 10.2 10.6 10.3 10.2 0.0

01-Jul-10 09:37 167.9 172.2 158.9 0.0 10.2 10.6 10.3 10.1 0.0

01-Jul-10 09:52 169.4 169.0 164.5 0.0 10.2 10.5 10.3 10.0 0.0

01-Jul-10 10:07 168.0 171.0 163.2 0.0 10.2 10.6 10.4 10.0 0.0

01-Jul-10 10:22 168.5 173.0 160.0 0.0 10.2 10.6 10.4 10.0 0.0

01-Jul-10 10:37 166.5 171.2 159.7 0.0 10.2 10.7 10.4 10.0 -0.1

01-Jul-10 10:52 164.5 175.6 159.5 0.0 10.2 10.8 10.4 10.0 -0.2

01-Jul-10 11:07 169.0 171.9 159.3 0.0 10.2 10.8 10.4 10.0 0.0

01-Jul-10 11:22 168.2 170.9 160.0 0.0 10.2 10.9 10.4 10.0 -0.1

01-Jul-10 11:37 169.7 176.0 164.7 0.0 10.2 10.9 10.4 10.1 0.0

01-Jul-10 11:52 171.5 175.8 161.7 0.0 10.2 10.9 10.4 10.1 -0.1

01-Jul-10 12:07 169.8 168.2 159.0 0.0 10.2 10.9 10.4 10.1 -0.2

01-Jul-10 12:22 169.0 171.7 164.1 0.0 10.2 10.9 10.4 10.1 -0.3

01-Jul-10 12:37 165.5 172.7 163.4 0.0 10.2 10.9 10.4 10.1 -0.1

01-Jul-10 12:52 171.0 172.7 162.3 0.0 10.2 10.9 10.4 10.1 -0.1

01-Jul-10 13:07 173.4 173.0 164.9 0.0 10.2 10.9 10.4 10.1 -0.1

01-Jul-10 13:22 170.0 171.7 165.7 0.0 10.2 10.8 10.4 10.1 -0.1

01-Jul-10 13:37 169.9 174.3 163.1 0.0 10.2 10.8 10.4 10.1 -0.1

01-Jul-10 13:52 169.4 171.3 168.4 0.0 10.3 10.8 10.4 10.1 -0.2

01-Jul-10 14:07 173.0 174.3 168.4 0.0 10.3 10.8 10.4 10.1 -0.1

01-Jul-10 14:22 173.0 179.7 162.3 0.0 10.3 10.8 10.4 10.1 -0.1

01-Jul-10 14:37 169.8 172.0 163.8 0.0 10.3 10.8 10.4 10.1 -0.2

01-Jul-10 14:52 173.0 171.1 165.4 0.0 10.3 10.8 10.4 10.2 -0.2

01-Jul-10 15:07 175.0 176.0 163.9 0.0 10.3 10.8 10.4 10.2 0.0

01-Jul-10 15:22 174.8 174.7 168.0 0.0 10.3 10.8 10.4 10.2 0.1

Liquid Flow rate Pressure Drop
01-Jul-10 15:37 169.5 172.0 164.0 0.0 10.3 10.8 10.4 10.2 0.2

AVERAGE: 169.4 172.3 162.6 0.0 10.2 10.7 10.4 10.1 -0.1
Monroe Power Plant Start Time End Time Time Interval

BOILER #3 6/2/10 0:00 7/1/10 23:59 24 hr

ESP power

GEN GROSS 

TOTAL MW

GEN NET 

MGWATTS

U3 MAIN

 STEAM FLOW

(lb/hr)

Heat Input

(MMBtu/hr)

COAL FLOW

(Tons/hr)

TOTAL PRECIP 

POWER

 (Kwatts)

02-Jun-10 00:00 764.9 720.6 5555803 7106 654.3 926.6

03-Jun-10 00:00 766.1 722.7 5565342 7208 670.3 970.5

04-Jun-10 00:00 762.1 722.7 5544467 7098 653.5 1002.7

05-Jun-10 00:00 762.0 723.8 5500763 7162 663.2 941.6

06-Jun-10 00:00 718.4 680.4 5062421 6772 633.1 977.5

07-Jun-10 00:00 720.1 678.7 4984924 6719 665.6 1030.7

08-Jun-10 00:00 765.1 724.8 5404424 7133 658.5 925.1

09-Jun-10 00:00 769.1 723.2 5366419 7147 652.4 1004.6

10-Jun-10 00:00 762.4 722.7 5499680 6322 637.7 1020.5

11-Jun-10 00:00 765.4 723.9 5506434 6381 646.3 976.0

12-Jun-10 00:00 763.3 721.7 5550804 7014 644.4 991.1

13-Jun-10 00:00 735.0 688.8 5209899 6780 624.1 971.8

14-Jun-10 00:00 740.9 701.9 5197054 6959 639.9 972.7

15-Jun-10 00:00 763.8 722.7 5530433 7137 654.1 966.6

16-Jun-10 00:00 510.7 473.3 3699240 4955 453.5 955.3

17-Jun-10 00:00 789.4 749.6 5585784 7500 683.4 966.0

18-Jun-10 00:00 788.6 747.1 5725132 7328 658.5 946.1

19-Jun-10 00:00 648.8 611.2 4630697 6343 581.2 914.0

20-Jun-10 00:00 613.9 582.6 4470801 5492 543.6 952.5

21-Jun-10 00:00 732.2 689.7 5280846 6805 625.7 938.1

22-Jun-10 00:00 762.7 719.9 5266141 7310 678.8 985.8

23-Jun-10 00:00 768.0 721.2 5235108 7363 673.0 948.0

24-Jun-10 00:00 764.9 720.8 5411925 7213 658.4 965.1

25-Jun-10 00:00 761.7 723.2 5567127 7090 654.7 982.6

26-Jun-10 00:00 762.3 724.8 5415019 7304 676.6 910.2

27-Jun-10 00:00 769.8 722.8 5477065 7305 688.4 877.3

28-Jun-10 00:00 423.9 391.0 3026210 4317 392.6 882.2

29-Jun-10 00:00 760.3 716.5 5551120 6985 629.5 726.6

30-Jun-10 00:00 789.7 748.4 5664817 7332 671.7 688.6

01-Jul-10 00:00 783.9 743.0 5638989 7219 654.0 710.7

Boiler Data
Monroe Power Plant Start Time End Time Time Interval

BOILER #3 6/2/10 0:00 7/1/10 23:59 24 hr

ESP power

GEN GROSS 

TOTAL MW

GEN NET 

MGWATTS

U3 MAIN

 STEAM FLOW

(lb/hr)

Heat Input

(MMBtu/hr)

COAL FLOW

(Tons/hr)

TOTAL PRECIP 

POWER

 (Kwatts)

02-Jun-10 00:00 764.9 720.6 5555803 7106 654.3 926.6

03-Jun-10 00:00 766.1 722.7 5565342 7208 670.3 970.5

04-Jun-10 00:00 762.1 722.7 5544467 7098 653.5 1002.7

05-Jun-10 00:00 762.0 723.8 5500763 7162 663.2 941.6

06-Jun-10 00:00 718.4 680.4 5062421 6772 633.1 977.5

07-Jun-10 00:00 720.1 678.7 4984924 6719 665.6 1030.7

08-Jun-10 00:00 765.1 724.8 5404424 7133 658.5 925.1

09-Jun-10 00:00 769.1 723.2 5366419 7147 652.4 1004.6

10-Jun-10 00:00 762.4 722.7 5499680 6322 637.7 1020.5

11-Jun-10 00:00 765.4 723.9 5506434 6381 646.3 976.0

12-Jun-10 00:00 763.3 721.7 5550804 7014 644.4 991.1

13-Jun-10 00:00 735.0 688.8 5209899 6780 624.1 971.8

14-Jun-10 00:00 740.9 701.9 5197054 6959 639.9 972.7

15-Jun-10 00:00 763.8 722.7 5530433 7137 654.1 966.6

16-Jun-10 00:00 510.7 473.3 3699240 4955 453.5 955.3

17-Jun-10 00:00 789.4 749.6 5585784 7500 683.4 966.0

18-Jun-10 00:00 788.6 747.1 5725132 7328 658.5 946.1

19-Jun-10 00:00 648.8 611.2 4630697 6343 581.2 914.0

20-Jun-10 00:00 613.9 582.6 4470801 5492 543.6 952.5

21-Jun-10 00:00 732.2 689.7 5280846 6805 625.7 938.1

22-Jun-10 00:00 762.7 719.9 5266141 7310 678.8 985.8

23-Jun-10 00:00 768.0 721.2 5235108 7363 673.0 948.0

24-Jun-10 00:00 764.9 720.8 5411925 7213 658.4 965.1

25-Jun-10 00:00 761.7 723.2 5567127 7090 654.7 982.6

26-Jun-10 00:00 762.3 724.8 5415019 7304 676.6 910.2

27-Jun-10 00:00 769.8 722.8 5477065 7305 688.4 877.3

28-Jun-10 00:00 423.9 391.0 3026210 4317 392.6 882.2

29-Jun-10 00:00 760.3 716.5 5551120 6985 629.5 726.6

30-Jun-10 00:00 789.7 748.4 5664817 7332 671.7 688.6

01-Jul-10 00:00 783.9 743.0 5638989 7219 654.0 710.7

Boiler Data