Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Wednesday, February 23, 2011 Page 1 of 11
Facility Information:

Streeter Station

612 E 12th Street

PO Box 769

Cedar Falls IA 50613

Contact: Ed Olthoff

Phone: 319-268-5309

Fax: 319-266-8158

Email: edolthoff@cfunet.net

Testing Company:

Comprehensive Emission Services

P.O. Box 910

Waukee IA 50263

Contact:Tim Titus

Phone: 5159870200

Fax: 5159876604

Email: tim@testces.com

Air Permit Number:

1131

Permitted Source ID/Name:

7 Enter the Boiler ID of the tested boiler (left)

Permitted Maximum Process Rate:

434 MMBTU

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Please see attached process flow diagram, U7 process flow diagram. Could not attach here, attached with the Attach. 

Tab

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 1901300010 FRS #: 110000593572

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 0 88 88 99.3 264 132 5 25

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Wednesday, February 23, 2011 Page 2 of 11
The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

In this section, identify the promulgation date of any specified test method that you use for determining the 

procedures followed. This field is also used to document any modifications that are necessary to conduct the 

emissions test if they are outside the requirements of the cited method. If this modification was approved verbally by 

a regulatory agency, the name and date of approval should be included. Written formal approval should be attached 

to this file using the "Attach File" button. Test procedures that are different from those published in the Federal 

Register should be attached using the "Attach File" button.

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Wednesday, February 23, 2011 Page 3 of 11
Sampling / Stack Data Results Summary

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 5/25/2010 5/26/2010 5/27/2010

Run Start Time 8:49:00 AM 8:07:00 

AM

7:39:00 AM

Run Finish Time 5:21:00 PM 4:35:00 PM 7:15:00 PM

Net Run Time, minutes 500 500 500

Dry Gas Meter Volume Sampled, dscf 312.158 311.077 314.672 312.636

Moisture Content of Stack Gas, % 10.07 9.84 9.52 9.810

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.2 13.4 13.4 13.333

Oxygen, % 6.7 6.5 6.5 6.567

Average Stack Gas Temperature, °F 334.32 353.48 347.76 345.187

Dry Volumetric Flow Rate, dry scfm 80,545.2 80,433.8 81,519.6 80,832.867

Actual Wet Volumetric Flue Gas Flow Rate, acfm 134,875.2 137,585.6 137,972.8 136,811.200

Percent Isokinetic of Sampling Rate, % 104.8 100.8 100.7 102.100

F-Factor, dscfm/MMBtu @ %O2 0 0 0 0.000

Fw 0 0 0 0.000

Fc 1840 1840 1840 1,840.000

Wednesday, February 23, 2011 Page 4 of 11
Emissions Summary

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000064901 0.00000039788 0.00000003 0.000

lb/mmBtuCO2 6.39E-11 3.87E-11 2.89E-12 0.000

ng/dscm 7.34E-02 4.52E-02 3.37E-03 0.041

ng/dscm@7%O2 7.18E-02 4.36E-02 3.25E-03 0.040

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000013627 0.00000009162 0.00000002854 0.000

lb/mmBtuCO2 1.34E-11 8.92E-12 2.75E-12 0.000

ng/dscm 1.54E-02 1.04E-02 3.20E-03 0.010

ng/dscm@7%O2 1.51E-02 1.00E-02 3.09E-03 0.009

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000231 0.00000007064 0.00000003814 0.000

lb/mmBtuCO2 2.27E-12 6.87E-12 3.67E-12 0.000

ng/dscm 2.61E-03 8.02E-03 4.28E-03 0.005

ng/dscm@7%O2 2.55E-03 7.74E-03 4.13E-03 0.005

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000003046 0.00000001735 0.0000000382 0.000

lb/mmBtuCO2 3.00E-12 1.69E-12 3.67E-12 0.000

ng/dscm 3.45E-03 1.97E-03 4.29E-03 0.003

ng/dscm@7%O2 3.38E-03 1.90E-03 4.14E-03 0.003

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000281 0.0000000137 0.00000002677 0.000

lb/mmBtuCO2 2.77E-12 1.33E-12 2.58E-12 0.000

ng/dscm 3.18E-03 1.56E-03 3.00E-03 0.003

ng/dscm@7%O2 3.11E-03 1.51E-03 2.90E-03 0.003

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000228 0.00000001299 0.0000000286 0.000

lb/mmBtuCO2 2.24E-12 1.26E-12 2.75E-12 0.000

ng/dscm 2.58E-03 1.47E-03 3.21E-03 0.002

ng/dscm@7%O2 2.53E-03 1.42E-03 3.10E-03 0.002

Compound: 1,2,3,6,7,8-HxCDF

Average

Wednesday, February 23, 2011 Page 5 of 11
RunNumber 1 2 3

Mass_mg 0.00000002093 0.00000003465 0.00000001994 0.000

lb/mmBtuCO2 2.06E-12 3.37E-12 1.92E-12 0.000

ng/dscm 2.37E-03 3.93E-03 2.24E-03 0.003

ng/dscm@7%O2 2.32E-03 3.79E-03 2.16E-03 0.003

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000002689 0.00000001532 0.00000003373 0.000

lb/mmBtuCO2 2.65E-12 1.49E-12 3.24E-12 0.000

ng/dscm 3.04E-03 1.74E-03 3.79E-03 0.003

ng/dscm@7%O2 2.98E-03 1.68E-03 3.66E-03 0.003

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000003227 0.00000001574 0.00000003075 0.000

lb/mmBtuCO2 3.18E-12 1.53E-12 2.96E-12 0.000

ng/dscm 3.65E-03 1.79E-03 3.45E-03 0.003

ng/dscm@7%O2 3.57E-03 1.73E-03 3.33E-03 0.003

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000003403 0.00000001427 0.00000002739 0.000

lb/mmBtuCO2 3.35E-12 1.39E-12 2.64E-12 0.000

ng/dscm 3.85E-03 1.62E-03 3.07E-03 0.003

ng/dscm@7%O2 3.77E-03 1.56E-03 2.96E-03 0.003

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000001569 0.00000001169 0.0000000497 0.000

lb/mmBtuCO2 1.54E-12 1.14E-12 4.78E-12 0.000

ng/dscm 1.78E-03 1.33E-03 5.58E-03 0.003

ng/dscm@7%O2 1.74E-03 1.28E-03 5.39E-03 0.003

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.00000004188 0.00000007814 0.00000003929 0.000

lb/mmBtuCO2 4.12E-12 7.60E-12 3.78E-12 0.000

ng/dscm 4.74E-03 8.87E-03 4.41E-03 0.006

ng/dscm@7%O2 4.64E-03 8.56E-03 4.26E-03 0.006

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.00000009341 0.00000051079 0.00000030578 0.000

lb/mmBtuCO2 9.20E-12 4.97E-11 2.94E-11 0.000

ng/dscm 1.06E-02 5.80E-02 3.43E-02 0.034

ng/dscm@7%O2 1.04E-02 5.60E-02 3.31E-02 0.033

Wednesday, February 23, 2011 Page 6 of 11
Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.00000317879 0.00000228353 0.00000141387 0.000

lb/mmBtuCO2 3.13E-10 2.22E-10 1.36E-10 0.000

ng/dscm 3.60E-01 2.59E-01 1.59E-01 0.259

ng/dscm@7%O2 3.52E-01 2.50E-01 1.53E-01 0.252

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.00000135999 0.00000087735 0.00000041047 0.000

lb/mmBtuCO2 1.34E-10 8.54E-11 3.95E-11 0.000

ng/dscm 1.54E-01 9.96E-02 4.61E-02 0.100

ng/dscm@7%O2 1.51E-01 9.61E-02 4.45E-02 0.097

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.00000003273 0.00000017264 0.00000002199 0.000

lb/mmBtuCO2 3.22E-12 1.68E-11 2.12E-12 0.000

ng/dscm 3.70E-03 1.96E-02 2.47E-03 0.009

ng/dscm@7%O2 3.62E-03 1.89E-02 2.38E-03 0.008

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.00000888454 0.00000604477 0.00000344784 0.000

lb/mmBtuCO2 8.75E-10 5.88E-10 3.32E-10 0.000

ng/dscm 1.01E+00 6.86E-01 3.87E-01 0.694

ng/dscm@7%O2 9.89E-01 6.62E-01 3.74E-01 0.675

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.00000004707 0.00000007654 0.00000331184 0.000

lb/mmBtuCO2 4.63E-12 7.45E-12 3.19E-10 0.000

ng/dscm 5.33E-03 8.69E-03 3.72E-01 0.129

ng/dscm@7%O2 5.22E-03 8.39E-03 3.59E-01 0.124

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000261 0.00000001273 0.00000002486 0.000

lb/mmBtuCO2 2.57E-12 1.24E-12 2.39E-12 0.000

ng/dscm 2.95E-03 1.45E-03 2.79E-03 0.002

ng/dscm@7%O2 2.89E-03 1.40E-03 2.69E-03 0.002

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000001566 0.00000001167 0.00000002115 0.000

lb/mmBtuCO2 1.54E-12 1.14E-12 2.03E-12 0.000

Wednesday, February 23, 2011 Page 7 of 11
ng/dscm 1.77E-03 1.33E-03 2.37E-03 0.002

ng/dscm@7%O2 1.73E-03 1.28E-03 2.29E-03 0.002

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000001365 0.00000000985 0.00000001911 0.000

lb/mmBtuCO2 1.34E-12 9.59E-13 1.84E-12 0.000

ng/dscm 1.54E-03 1.12E-03 2.14E-03 0.002

ng/dscm@7%O2 1.51E-03 1.08E-03 2.07E-03 0.002

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000001143 0.00000000619 0.00000001313 0.000

lb/mmBtuCO2 1.13E-12 6.02E-13 1.26E-12 0.000

ng/dscm 1.29E-03 7.03E-04 1.47E-03 0.001

ng/dscm@7%O2 1.26E-03 6.79E-04 1.42E-03 0.001

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.00000006257 0.0000000762 0.00000003015 0.000

lb/mmBtuCO2 6.16E-12 7.42E-12 2.90E-12 0.000

ng/dscm 7.08E-03 8.65E-03 3.38E-03 0.006

ng/dscm@7%O2 6.93E-03 8.35E-03 3.26E-03 0.006

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.00000004696 0.00000005431 0.0000000268 0.000

lb/mmBtuCO2 4.62E-12 5.29E-12 2.58E-12 0.000

ng/dscm 5.31E-03 6.17E-03 3.01E-03 0.005

ng/dscm@7%O2 5.20E-03 5.96E-03 2.91E-03 0.005

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.00000005795 0.00000015291 0.00000002854 0.000

lb/mmBtuCO2 5.71E-12 1.49E-11 2.75E-12 0.000

ng/dscm 6.56E-03 1.74E-02 3.20E-03 0.009

ng/dscm@7%O2 6.42E-03 1.68E-02 3.09E-03 0.009

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.0000010784 0.00000064414 0.00000035361 0.000

lb/mmBtuCO2 1.06E-10 6.27E-11 3.40E-11 0.000

ng/dscm 1.22E-01 7.31E-02 3.97E-02 0.078

ng/dscm@7%O2 1.19E-01 7.06E-02 3.83E-02 0.076

Compound: OCDD

Average

RunNumber 1 2 3

Wednesday, February 23, 2011 Page 8 of 11
Process Run Data

Mass_mg 0.00000108258 0.00000068908 0.00000003129 0.000

lb/mmBtuCO2 1.07E-10 6.71E-11 3.01E-12 0.000

ng/dscm 1.22E-01 7.82E-02 3.51E-03 0.068

ng/dscm@7%O2 1.19E-01 7.55E-02 3.39E-03 0.066

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000002188 0.00000009678 0.00000003224 0.000

lb/mmBtuCO2 2.15E-12 9.42E-12 3.10E-12 0.000

ng/dscm 2.48E-03 1.10E-02 3.62E-03 0.006

ng/dscm@7%O2 2.43E-03 1.06E-02 3.49E-03 0.006

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.00000109318 0.00000051146 0.00000009768 0.000

lb/mmBtuCO2 1.08E-10 4.98E-11 9.40E-12 0.000

ng/dscm 1.24E-01 5.81E-02 1.10E-02 0.064

ng/dscm@7%O2 1.21E-01 5.61E-02 1.06E-02 0.063

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.00000009902 0.00000021463 0.0000001349 0.000

lb/mmBtuCO2 9.75E-12 2.09E-11 1.30E-11 0.000

ng/dscm 1.12E-02 2.44E-02 1.51E-02 0.017

ng/dscm@7%O2 1.10E-02 2.36E-02 1.46E-02 0.016

Wednesday, February 23, 2011 Page 9 of 11
Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Coal Burned 0 1000 Tons/hr 0

1 Average Heat Input 0 MMBtu/hr 0

1 Steam Output 0 1000 lb steam/hr 0

1 Unit Net Electric Generation 27 MWh 27 Method 23 Run 1

2 Coal Burned 0 1000 Tons/hr 0

2 Average Heat Input 0 MMBtu/hr 0

2 Steam Output 0 1000 lb steam/hr 0

2 Unit Net Electric Generation 0 MWh 27 Method 23, Run 2

3 Coal Burned 0 1000 Tons/hr 0

3 Average Heat Input 0 MMBtu/hr 0

3 Steam Output 0 1000 lb steam/hr 0

3 Unit Net Electric Generation 0 MWh 27 Method 23, Run 3

Run Name Value UOM Comments

Target

Value

1 ELECTROSTATIC PRECIPITATOR 0 0

1 drop down lists. If not on list add description and 

provide detailed

0 0

1 desription in section 5a. 0 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 0 Btu/lb

1 Fuel Moisture 0 %

1 Fuel Mercury Content 0 ppm

1 Fuel Cadmium Content 0 ppm

1 Ultimate/Proximate Analysis 0

1 Fuel Nickel Content 0 ppm

1 Fuel Arsenic Content 0 ppm

1 Fuel Chromium Content 0 ppm

1 Fuel Beryllium Content 0 ppm

1 Fuel Lead Content 0 ppm

1 Fuel Manganese Content 0 ppm

1 Fuel Chlorine Content 0 ppm

1 Fuel Fluorine Content 0 ppm

Wednesday, February 23, 2011 Page 10 of 11
Sampling / Stack Data Results Detail

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 5/25/2010 5/26/2010 5/27/2010

Run Start Time 8:49:00 AM 8:07:00 AM 7:39:00 AM

Run Finish Time 5:21:00 PM 4:35:00 PM 7:15:00 PM

Net Traversing Points 25 25 25

Net Run Time, minutes 500 500 500

Nozzle Diameter, inches 0.27 0.275 0.275 0.273

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.99 0.99 0.99 0.990

Barometric Pressure, inches of Mercury 29.92 29.92 29.92 29.920

Average Orifice Meter Differential, inches H2O 1.17 1.18 1.18 1.177

Dry Gas Meter Volume Sampled, cubic feet 317.087 316.871 320.677 318.212

Average Dry Gas Meter Temperature, °F 72.50 74.00 74.24 73.580

Dry Gas Meter Volume Sampled, dscf 312.158 311.077 314.672 312.636

Total Moisture Liquid collected, g 743 721 703 722.333

Volume of Water Vapor, standard cubic feet 34.97 33.94 33.09 34.000

Moisture Content of Stack Gas, % 10.07 9.84 9.52 9.810

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8993 0.9016 0.9048 0.902

Carbon Dioxide, % 13.2 13.4 13.4 13.333

Oxygen, % 6.7 6.5 6.5 6.567

Carbon Monoxide & Nitrogen, % 80.1 80.1 80.1 80.100

Fuel Factor 1.08 1.07 1.07

Dry Molecular Weight, lb/lb-Mole 30.38 30.40 30.40 30.393

Wet Molecular weight, lb/lb-Mole 29.13 29.18 29.22 29.177

Flue Gas Static Pressure, inches of H2O -0.37 -0.37 -0.37 -0.370

Absolute Flue Gas Pressure, inches of Mercury 29.89 29.89 29.89 29.890

Average Stack Gas Temperature, °F 334.32 353.48 347.76 345.187

Average Velocity Head, inches of H2O 0.3714039119

4049

0.378031351

333017

0.383317987

043583

0.378

Average Stack Gas Velocity, feet/second 41.80 42.64 42.76 42.400

Stack Cross-Sectional Area, square feet 53.778 53.778 53.778 53.778

Dry Volumetric Flow Rate, dry scfm 80,545.2 80,433.8 81,519.6 80,832.867

Actual Wet Volumetric Flue Gas Flow Rate, acfm 134,875.2 137,585.6 137,972.8 136,811.200

Percent Isokinetic of Sampling Rate, % 104.8 100.8 100.7 102.100

Percent Excess Air, % 46.4 44.4 44.4 45.067

F-Factor, dscfm/MMBtu @ %O2 0 0 0 0.000

Round Duct Diameter, inches 0 0 0

Rectangular Duct Width, inches 88 88 88

Rectangular Duct Length, inches 88 88 88

Fw 0 0 0 0.000

Fc 1840 1840 1840 1,840.000

Wednesday, February 23, 2011 Page 11 of 11