# Effluent Quality Assessment 

# Gulf Power Company – Lansing Smith Power Plant

Bay County

NPDES #FL0002267

Sampled February 21, 23, and 25, 2011

June 2011

Biology Section
Bureau of Laboratories
Division of Environmental Assessment and Restoration

Quality Manual No. 870346G
NELAC Certification No. E31780

## 1 CONTENTS

Introduction

Methods

Results and Discussion

Literature Cited

Tables

Table 1 Measured algal growth potential (AGP)

Table 2 Effluent limits, Class II Marine Criteria and chemical and microbiological data for D-001

Table 3 Effluent limits, Class II Marine Criteria and chemical data for Ash pond and intake water

Appendices

Appendix A Chain of Custody

Appendix B Bioassay Bench Sheets

Appendix C SRT Bench Sheet s and Statistical Analyses

Appendix D Organism Receipt

Appendix E Chemical Analyses of Effluent

Appendix F Facility Summary, Effl uent Limits, and Permit Violations Recorded on Discharge Monitoring Report

Appendix G EPA End Sheet

## 2 Gulf Power Company – Lansing Smith Power Pl ant, 2300 Bay County Road, Southport, Bay County, Florida, 32409. NPDES# FL0002267. Effluent composit e samples for bioassay and grab samples for chemical and biological analyses for this facilit y were collected on February 21, 2011. Additional composite samples for bioassays were collected on February 23 and 25, 2011.



## Introduction Gulf Power Company – Lansing Smith Power Plant is a fossil–fuel electric power generation plant which discharges cooling water and overflow from an ash pond. (See Appendix F for detailed facility information provided by Kim Allen and Nathan Mu lkey of FDEP Northwest District.)



## Methods Samples were collected from the EFF-2 NPDES sa mpling point for Outfall D-001 for bioassays and chemical analyses. Additional samples for chemical analyses were collected from the EFF- 4 NPDES sampling point for Internal Outfall I-01C and the Intake Cooling Water sampling point by Rick Abad, Corinna Clanton, and Nathan Mulkey (FDEP Northwest District) following DEP-SOP-001/01 FS 2400 Wastewater Sampling. All DEP SOPs are available on the web at: http://www.floridadep.org/labs/bars/sas/sop/index.htm

.

See Appendix A for the completed chain of custody form.

The 7-day chronic screening toxicity tests and algal growth potential test were performed following internal DEP SOPs TA07_015, TA07_09, and TA08_01 through TA08_09. All internal DEP SOPs are
available on the web at: http://www.floridadep.org/labs/cgi-bin/sop/biosop.asp

.



## Results and Discussion

 Toxicity Test Results

Tests were performed February 22 – March 1, 2011.

Americamysis bahia 7 - day chronic screening bioassay – NOEC (survival): 100% NOEC (growth): > 100% IC25 (growth): > 100%

Menidia beryllina 7 - day chronic screening bioassay – NOEC (survival): 100% NOEC (growth): > 100% IC25 (growth): > 100%

The bioassay samples were not chronically toxic to the test organisms.

See Appendix B for bioassay bench sheets. See Appendix C* for results of the last 20 standard reference toxicant (SRT) tests and the bench sheet s and statistical analyses of the SRT tests that correspond to these facility tests. See Appendix D for test organism receipts.

*The concurrent Americamysis bahia SRT was invalidated due to not meeting the minimum required mean organism dried wt for the control (0.2 mg dry wt/organism required; SRT control dry wt/organism was 0.197 mg). The follow-up SRT was initiated on March 15, 2011.



###  Algal Growth Potential

The effluent Algal Growth Potential (AGP) was 3.0 AU (A - Value reported is the mean of two or more determinations, U - Material was analyzed for but not detected; the value reported is the minimum detection limit) mg dry wt/L of the saltwater species Dunaliella tertiolecta. Raschke and Schultz determined that AGP values above 10.0 mg dry weigh t/L represent a “problem” threshold for marine receiving waters, implying nutrient enrichment (p ersonal communication, Marshall Faircloth, et. al. FDEP, with Ron Raschke USEPA Region 4 1987). The ratio (4.4:1) of inorganic nitrogen to

## 3 orthophosphate suggests that the effluent is nitrog en–limited; whereas, the ratio (15.6:1) of total nitrogen to total phosphorus suggests that the effl uent is co-limited by both nitrogen and phosphorus.
To determine actual nutrient limit ation, a limiting-nutrient algal growth potential test should be performed (Maloney et al. 1978).

See Table 1 for AGP results.

 Chemistry Results for Surface Waters (D-001)

Total residual chlorine and total ammonia were not de tected in the bioassay sample in the laboratory. The total ammonia concentration in the grab sample collected and preserved for chemical analysis was 0.01 U mg N/L. Due to the non-detection of amm onia; unionized ammonia could not be calculated.

Total suspended solids (TSS) were detected in the D-001 effluent sample. Aluminum, arsenic, iron, and carbonaceous biochemical oxygen demand (CBOD) were detected between the laboratory method detection limits (MDL) and practical quantitation lim its (PQL). Fecal Coliforms (3060 BJ CFU/100 ml)
exceeded the Class II criteria for mari ne water (62-302.500 (6), F.A.C.).

See Table 2 for results of analytes detected in the D-001 effluent and corresponding limits.

 Chemistry Results for Ash Pond (I-01C)

The total ammonia concentration in the grab sample collected and preserved for chemical analysis from the ash pond was 0.03 mg N/L. Based on the pH, sali nity, and temperature of the effluent as collected,
the calculated unionized ammonia concentration was ≤ 0.02 mg/L.

Arsenic, cadmium, chromium – III, iron, nickel, se lenium, and radium 226 were detected in the effluent at levels that comply with Class II marine water quality criteria (62-302.530, F.A.C.), or permit conditions (NPDES# FL0002267). Copper and T SS were detected between the laboratory MDL and PQL. Radium 226 was also detected in the field blank.

See Table 3 for results of analytes detected in the I-01C effluent and corresponding limits.

 Chemistry Results for Intake Cooling Water

Iron was detected in the effluent at levels that comp ly with Class II marine water quality criteria (62- 302.530, F.A.C.) Nickel was detected between the laboratory MDL and PQL.

See Table 3 for results of analytes detected in the intake cooling water and corresponding limits. See Appendix E for a complete list of chemical analyses performed. See Appendix B for bioassay lab equipment.



## Conclusion The effluent sample collected from the EFF-2 NPDES sampling point for Outfall D-001 for this facility on February 21, 23, and 25, 2011, was not chronically toxic to either test species during the 7-day chronic screening bioassays. The effluent AGP result was less than the "problem” threshold for marine receiving waters. Effluent water quality samples collected on February 21, 2011, exceeded applicable water quality
standards for fecal coliforms.

Samples from the ash pond (I-01C) and intake cooli ng water did not exceed any applicable water quality standards or permit limits.

## 4 Literature Cited
Raschke, R. L. and D. A. Schultz. 1987. The use of the algal growth potential test for data assessment. J. Wat. Poll. Cont. Fed. 59(4): 222-227.

Maloney, T. E., W. E. Miller, and D. T. Specht. 1974. The Marine Algal Assay Procedure: Bottle Test.
National Environmental Research Center Office of Research and Development. U. S. EPA, Corvallis, Oregon. 43 p.

## 5 Inor g anic Total

Location N:P ratio N:P ratio
Effluent 3.0 AU 4.4 15.6

A

- Value reported is the mean of two or more determinations U - Material analyzed for but not detected; value reported is the method detection limit Table 1. Measured algal growth potential (AGP; mg dry weight/L) of the saltwater species Dunaliella tertiolecta and ratios of nitrogen to phosphorus for samples collceted from the Gulf Power Co. - Lansing Smith Power Plant Outfall D-001 on February 21, 2011.

AGP Gulf Power Co. - Lansing Smith Power Plant

NPDES# FL0002267

(measured)

## 6 Gulf Power Co. - Lansing Smith Power

Plant NPDES# FL0002267 Class II

Criteria Effluent

Limits Metals (μg/L unless otherwise noted)

Aluminum ≤ 1,500 - 250 I

Arsenic ≤ 50 - 0.98 I
Cadmium ≤ 8.8 - 0.15 U Calcium (mg/L) - - 336
Chromium-III - - 0.9 U Copper ≤ 3.7 ≤ 3.7 d† 1.5 U

Iron ≤ 300 ≤ 300 d† 130 I

Lead ≤ 8.5 ≤ 8.5 d† 0.6 U Magnesium (mg/L) - - 1020

Nickel ≤ 8.3 ≤ 8.3 d† 0.75 U
Selenium ≤ 71 - 0.6 U
Silver ≤ 2.3 - 0.075 U
Zinc ≤ 86 - 15 U Nutrients (mg/L) Ortho-phosphate - - 0.008 U Total Phosphorus - - 0.017 I

Total Ammonia - - 0.01 U

Un-ionized Ammonia - - ≤ 0.02 c

Nitrate and Nitrite - - 0.025 U Total Kjeldahl Nitrogen - - 0.24 I Organic Nitrogen - - 0.19 c Total Nitrogen - - 0.253 c General Physical and Chemical Parameters Dissolved Oxygen (mg/L) ≥ 4.0 - 7.1 pH (SU) 6.5 - 8.5 6.5 - 8.5 7.5 Conductivity (μmhos/cm) - - 41,115 Temperature (°C) - - 26.3 Salinity - - 25.6 c Total Residual Chlorine (mg/L) ≤ 0.01 - ≤ 0.03 QU£ Chlorophyll a (μg/L) - Corrected - - 0.58 U Phaeophytin (μg/L) - - 0.42 U Total Suspended Solids (mg/L) - - 17 CBOD, 5 day (mg/L), N - inhibited - - 1.4 IJ Oils and Greases (mg/L) ≤ 5.0 ≤ 5.0 d 1.4 U Flow (MGD) - ≤ 273.6 d 226.93 a* Hardness (mg CaCO 3 ) - - 5,039.35 c
Microbiology (Number of colony forming units/100ml)

Fecal Coliforms ¥ ≤ 800 d - 3,060 BJ Value exceeds the Class III Water Quality Criteria or permit limits a - Annual average

c - Value is calculated d - Daily maximum B - Results based on colony counts outside the acceptance range I - The reported value is between the laboratory method det ection limit and the laborator y practical quantitation limit

J - Estimated value Q - Sample held beyond normal holding time U - Material analyzed for but not detected; value reported is the method detection limit

¥ - Fecal coliform analysis performed by the Univer sity of West Florida (UWF) lab, Pensacola. £ - measurement taken in the FDEP laboratory
* - Mean flow from 3/10 to 2/11 † - 8 - hour Time Proportional Composite Effluent Table 2. Effluent limits, Class II Criteria for predominantly marine waters and chemical and microbiological data for samples collected from the Gulf Power Company - Lansing Smith Power Plant Outfall D-001 on February 21, 2011.

## 7 Gulf Power Co. - Lansing Smith

Power Plant
NPDES# FL0002267 Class II

Criteria EFF- 4

Limits

Metals (μg/L unless otherwise noted)

Arsenic ≤ 50 Report ‡ 28.3 -
Cadmium ≤ 8.8 Report ‡ 0.25 - Chromium-III - Report ‡ 5.7 - Copper ≤ 3.7 Report ‡ 0.9 I 0.5 U

Iron ≤ 300 Report ‡ 150 150

Lead ≤ 8.5 Report ‡ 0.2 U 0.6 U

Nickel ≤ 8.3 Report ‡ 4.36 0.33 I
Selenium ≤ 71 Report ‡ 7.6 -
Zinc ≤ 86 Report ‡ 5 U - Nutrients (mg/L) Total Ammonia - Report 0.03

Un-ionized Ammonia - - ≤ 0.02 c Nitrate and Nitrite - Report 0.014 Total Kjeldahl Nitrogen - Report 0.45 Organic Nitrogen - - 0.42 c Total Nitrogen - Report 0.464 c General Physical and Chemical Parameters Dissolved Oxygen (mg/L) ≥ 4.0 - 8.5 pH (SU) 6.5 - 8.5 6.0 - 9.0 7.6 Conductivity (μmhos/cm) - - 6,153 Temperature (°C) - - 19.6 Salinity - - 3.8 c Total Suspended Solids (mg/L) - ≤ 100.0 d 9 I Oils and Greases (mg/L) ≤ 5.0 ≤ 20.0 d 1.4 U Radium 226 (pCi/L) - - 0.9 F Radium 226-Counting Error (pCi/L) - - 0.3 F Radium 228 (pCi/L) - - 0.8 U Radium 228-Counting Error (pCi/L) - - 0.5 F Radium 226 + 228 (pCi/L) ≤ 5 Report 0.9 cF Value exceeds the Class III Water Quality Criteria or permit limits

c - Value is calculated d - Daily maximum F - Analyte was detected in both sample and field blank I - The reported value is between the laboratory method det ection limit and the laboratory practical quantitation limit U - Material analyzed for but not detected; value reported is the method detection limit ‡ - 24 - hour Time Proportional Composite Ash Pond Intake Cooling

Water Table 3. Effluent limits, Class II Criteria for predominantly marine waters and chemical data for samples collected from the Gulf Power Company - Lansing Smith Power Plant Ash Pond and Intake Cooling Water on February 21, 2011.

## 8 Appendix A. Chain of Custody Form

## 9 Appendix A. (continued)

## 10 Appendix A. (continued)

## 11 Appendix A. (continued)

## 12 Appendix B. Bench Sheets

## 13 Appendix B. (continued)

## 14 Appendix B. (continued)

## 15 Appendix B. (continued)

## 16 Appendix B. (continued)

## 17 Appendix B. (continued)

Page 7 of 8, A. bahia Chronic Fecundity, was not used for this bioassay

## 18 Appendix B. (continued)

## 19 Appendix B. (continued)

## 20 Appendix B. (continued)

## 21 Appendix B. (continued)

## 22 Appendix B. (continued)

## 23 Appendix B. (continued)

## 24 Appendix B. (continued)

## 25 Appendix B. (continued)

## 26 Appendix C. SRT Bench Sheet s and Statistical Analysis

Bureau of Laboratories

Standard Reference Toxicant (SRT) Test Data - 7-Day Chronic Toxicity Americamysis bahia (mysid shrimp) - Cadmium Chloride (CdCl 2 

## )

Date IC20 Mean IC20 Std Dev Lower Control Limit Upper Control Limit
5/10/06 8.3284 8.33
8/7/06 15.064 11.70 4.76 2.17 21.22
12/05/06 12.168 11.85 3.38 5.10 18.61
3/06/07 6.27 10.46 3.92 2.61 18.31
5/13/08 8.63 10.09 3.50 3.10 17.08
12/9/08 10.8 10.21 3.14 3.93 16.49
1/10/2010 12.46 10.53 2.99 4.55 16.51
3/15/2011 15.3 11.13 3.24 4.65 17.61

Fewer than 20 chronic SRTs (cadmium) have been performed for this species. Lower Confidence Limit = mean - 2 * Std Dev EPA %CV 75th percentile = 32% Upper Confidence Limit = mean + 2 * Std Dev Lab %CV = 29.1%



### Standard Reference Toxicant Data Americamysis bahia IC 20

0 5 10 15 20 25 305/10/068/7/0612/05/063/06/075/13/0812/9/081/10/20103/15/2011



### Test DateIC20(ug/L CdCl2)

IC20 Mean IC20 Lower Control Limit Upper Control Limit

## 27 Appendix C. (continued) Florida Department of Environmental Protection
Bureau of Laboratories

Standard Reference Toxicant (SRT) Test Data - 7-Day Chronic Toxicity Menidia beryllina (inland silverside) - Copper Chloride (CuCl 2 

### )

Date IC20 Mean IC20 Std Dev Lower Control Limit Upper Control Limit
7/19/02 124.6 124.6
1/28/03 349.9 237.2 159.3 0.0 555.9
2/5/03 401.6 292.0 147.3 0.0 586.6
2/17/03 246.8 280.7 122.4 36.0 525.5
4/30/03 293.2 283.2 106.1 71.0 495.5
2/10/04 129.8 257.6 113.7 30.2 485.1
5/18/04 128.0 239.1 114.8 9.5 468.7
7/27/04 222.6 237.1 106.4 24.2 449.9
1/25/05 211.5 234.2 99.9 34.4 434.1
6/21/05 223.7 233.2 94.3 44.6 421.7
5/14/06 262.9 235.9 89.9 56.1 415.6
12/12/06 131.5 227.2 90.8 45.5 408.9
3/06/07 152.6 221.4 89.4 42.6 400.2
12/11/07 284.0 225.9 87.5 50.9 400.9
12/09/08 200.0 224.2 84.6 55.0 393.4
1/5/2010 283.9 227.9 83.1 61.8 394.1
2/15/2011 273.0 230.6 81.2 68.2 392.9

Fewer than 20 chronic SRTs have been performed for this species.
Lower Confidence Limit = mean - 2 * Std Dev EPA CV 75th percentile - 43% Upper Confidence Limit = mean + 2 * Std Dev Lab %CV = 35.2



### Standard Reference Toxicant Data Menidia beryllina IC 20

0 100 200 300 400 500 600 7007/19/021/28/032/5/032/17/034/30/032/10/045/18/047/27/041/25/056/21/055/14/0612/12/063/06/0712/11/0712/09/081/5/20102/15/2011



### Test DateIC20(ug/L CuCl2)

IC20 Mean IC20 Lower Control Limit Upper Control Limit

## 28 Appendix C. (continued)

## 29 Appendix C. (continued)

## 30 Appendix C. (continued)

## 31 Appendix C. (continued)

## 32 Appendix C. (continued)

## 33 Appendix C. (continued)

Test page 7 of 8, A. bahia Chronic Fecundity, was not used for this bioassay

## 34 Appendix C. (continued)

## 35 Appendix C. (continued)

## 36 Appendix C. (continued)

## 37 Appendix C. (continued)

## 38 Appendix C. (continued)

## 39 Appendix C. (continued)

## 40 Appendix C. (continued)

## 41 Appendix C. (continued)

## 42 Appendix D. Test Organism Receipts

## 43 Appendix D. (continued)44Appendix E. Chemical Analyses performed on the effluent from the gulfPower Company – Lansing Smith PowerPlant Outfall D-001 and I-01C, sampled on February 21, 2011.Date Sampled Field ID Analysis Group Components Result Remark Units MDL PQL2/21/2011 12:20 Effluent AGP/LN Algal Growth Potential 3 AU mg DryWt/L 3 32/21/2011 12:20 Effluent Chlorophyll/Grain Size/BOD Phaeophytin-a 0.42 U ug/L 0.42 1.32/21/2011 12:20 Effluent Chlorophyll/Grain Size/BOD Chlorophyll-a, Corrected 0.58 U ug/L 0.58 1.82/21/2011 12:20 Effluent Chlorophyll/Grain Size/BOD Biochemical Oxygen Demand-5 Day,N-Inhib 1.4 IJ mg/L 0.2 22/21/2011 12:20 Effluent Overflow Fecal Coliforms-Membrane Filter 3060 BJ cfu/100 mL 12/21/2011 12:20 Effluent Toxicology Bioassay-Chronic-Scrn-SW-Fish, NOEC 100 NOEC2/21/2011 12:20 Effluent Toxicology Bioassay-Chronic-Scrn-SW-Mysid, NOEC 100 NOEC2/21/2011 12:20 Effluent Metals Magnesium 1020 mg/L 2 82/21/2011 12:20 Effluent Metals Lead 0.6 U ug/L 0.6 2.42/21/2011 12:20 Effluent Metals Chromium 0.9 U ug/L 0.9 3.62/21/2011 12:20 Effluent Metals Cadmium 0.15 U ug/L 0.15 0.62/21/2011 12:20 Effluent Metals Arsenic 0.98 I ug/L 0.75 32/21/2011 12:20 Effluent Metals Nickel 0.75 U ug/L 0.75 32/21/2011 12:20 Effluent Metals Zinc 15 U ug/L 15 602/21/2011 12:20 Effluent Metals Calcium 336 mg/L 3.7 152/21/2011 12:20 Effluent Metals Selenium 0.6 U ug/L 0.6 2.42/21/2011 12:20 Effluent Metals Copper 1.5 U ug/L 1.5 32/21/2011 12:20 Effluent Metals Aluminum 250 I ug/L 180 7202/21/2011 12:20 Effluent Metals Iron 130 I ug/L 90 3602/21/2011 12:20 Effluent Metals Silver 0.075 U ug/L 0.075 0.32/21/2011 12:20 Effluent Metals Sodium 8500 mg/L 25 1002/21/2011 12:20 Effluent Nutrients Ammonia-N 0.01 U mg N/L 0.01 0.022/21/2011 12:20 Effluent Nutrients NO2NO3-N 0.025 U mg N/L 0.025 0.052/21/2011 12:20 Effluent Nutrients Kjeldahl Nitrogen 0.24 I mg N/L 0.16 0.42/21/2011 12:20 Effluent Nutrients TSS 17 mg/L 4 162/21/2011 12:20 Effluent Nutrients Total-P 0.017 I mg P/L 0.008 0.022/21/2011 12:20 Effluent Nutrients O-Phosphate-P 0.008 U mg P/L 0.008 0.022/21/2011 12:20 Effluent Overflow Oil and Grease 1.4 U mg/L 1.4 52/21/2011 12:20 Effluent Pesticides Endosulfan I 0.02 U ug/L 0.02 0.082/21/2011 12:20 Effluent Pesticides Endosulfan Sulfate 0.02 U ug/L 0.02 0.0845Appendix E. (continued)Date Sampled Field ID Analysis Group Components Result Remark Units MDL PQL2/21/2011 12:20 Effluent Pesticides Parathion Ethyl 0.15 U ug/L 0.15 0.62/21/2011 12:20 Effluent Pesticides Parathion Methyl 0.1 U ug/L 0.1 0.42/21/2011 12:20 Effluent Pesticides Alachlor 0.61 U ug/L 0.61 2.42/21/2011 12:20 Effluent Pesticides Malathion 0.15 U ug/L 0.15 0.62/21/2011 12:20 Effluent Pesticides Mevinphos 0.2 U ug/L 0.2 0.82/21/2011 12:20 Effluent Pesticides Naled 0.81 U ug/L 0.81 3.22/21/2011 12:20 Effluent Pesticides Gamma-BHC 0.01 U ug/L 0.01 0.042/21/2011 12:20 Effluent Pesticides Chlorpyrifos Methyl 0.1 U ug/L 0.1 0.42/21/2011 12:20 Effluent Pesticides Metribuzin 0.1 U ug/L 0.1 0.42/21/2011 12:20 Effluent Pesticides Beta-BHC 0.01 U ug/L 0.01 0.042/21/2011 12:20 Effluent Pesticides Endrin 0.051 U ug/L 0.051 0.22/21/2011 12:20 Effluent Pesticides Metalaxyl 0.25 U ug/L 0.25 12/21/2011 12:20 Effluent Pesticides Norflurazon 0.15 U ug/L 0.15 0.62/21/2011 12:20 Effluent Pesticides Chlordane 0.2 U ug/L 0.2 0.82/21/2011 12:20 Effluent Pesticides DDD-p,p' 0.02 U ug/L 0.02 0.082/21/2011 12:20 Effluent Pesticides Endrin Aldehyde 0.02 U ug/L 0.02 0.082/21/2011 12:20 Effluent Pesticides Azinphos Methyl 0.2 U ug/L 0.2 0.82/21/2011 12:20 Effluent Pesticides Chlorpyrifos Ethyl 0.051 U ug/L 0.051 0.22/21/2011 12:20 Effluent Pesticides Ethoprop 0.1 U ug/L 0.1 0.42/21/2011 12:20 Effluent Pesticides Fonofos 0.1 U ug/L 0.1 0.42/21/2011 12:20 Effluent Pesticides Hexazinone 0.1 U ug/L 0.1 0.42/21/2011 12:20 Effluent Pesticides Aldrin 0.01 U ug/L 0.01 0.042/21/2011 12:20 Effluent Pesticides DDT-p,p' 0.03 U ug/L 0.03 0.122/21/2011 12:20 Effluent Pesticides Delta-BHC 0.01 U ug/L 0.01 0.042/21/2011 12:20 Effluent Pesticides Toxaphene 0.76 U ug/L 0.76 32/21/2011 12:20 Effluent Pesticides Butylate 0.2 U ug/L 0.2 0.82/21/2011 12:20 Effluent Pesticides Dieldrin 0.02 U ug/L 0.02 0.082/21/2011 12:20 Effluent Pesticides Methoxychlor 0.051 U ug/L 0.051 0.22/21/2011 12:20 Effluent Pesticides Ametryn 0.051 U ug/L 0.051 0.22/21/2011 12:20 Effluent Pesticides Bromacil 0.2 U ug/L 0.2 0.82/21/2011 12:20 Effluent Pesticides Prometryn 0.15 U ug/L 0.15 0.62/21/2011 12:20 Effluent Pesticides Alpha-BHC 0.01 U ug/L 0.01 0.042/21/2011 12:20 Effluent Pesticides Endosulfan II 0.02 U ug/L 0.02 0.082/21/2011 12:20 Effluent Pesticides Heptachlor 0.01 U ug/L 0.01 0.0446Appendix E. (continued)Date Sampled Field ID Analysis Group Components Result Remark Units MDL PQL2/21/2011 12:20 Effluent Pesticides Heptachlor Epoxide 0.02 U ug/L 0.02 0.082/21/2011 12:20 Effluent Pesticides Atrazine 0.051 U ug/L 0.051 0.22/21/2011 12:20 Effluent Pesticides Diazinon 0.051 U ug/L 0.051 0.22/21/2011 12:20 Effluent Pesticides Ethion 0.051 U ug/L 0.051 0.22/21/2011 12:20 Effluent Pesticides Fenamiphos 0.2 U ug/L 0.2 0.82/21/2011 12:20 Effluent Pesticides Metolachlor 0.51 U ug/L 0.51 22/21/2011 12:20 Effluent Pesticides Phorate 0.051 U ug/L 0.051 0.22/21/2011 12:20 Effluent Pesticides Simazine 0.051 U ug/L 0.051 0.22/21/2011 12:20 Effluent Pesticides DDE-p,p' 0.02 U ug/L 0.02 0.082/21/2011 12:20 Effluent Priority Organic Pollutants 2,4-Dimethylphenol 10 U ug/L 10 402/21/2011 12:20 Effluent Priority Organic Pollutants 2,4-Dinitrotoluene 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants 2-Methyl-4,6-dinitrophenol 3 U ug/L 3 122/21/2011 12:20 Effluent Priority Organic Pollutants Benzo(a)pyrene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants Bis(2-chloroethyl)ether 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants Bis(2-ethylhexyl)phthalate 15 U ug/L 15 612/21/2011 12:20 Effluent Priority Organic Pollutants Chrysene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants Di-n-octyl phthalate 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants Isophorone 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants N-Nitrosodimethylamine 2 U ug/L 2 8.12/21/2011 12:20 Effluent Priority Organic Pollutants Phenanthrene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants 2,6-Dinitrotoluene 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants 4-Chloro-3-methylphenol 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants Anthracene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants Benzo(a)anthracene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants Benzo(k)fluoranthene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants Diethyl phthalate 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants Bis(2-chloroisopropyl)ether 3 U ug/L 3 122/21/2011 12:20 Effluent Priority Organic Pollutants Pentachlorophenol 3 U ug/L 3 122/21/2011 12:20 Effluent Priority Organic Pollutants Pyrene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants 2,4,6-Trichlorophenol 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants 2,4-Dichlorophenol 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants Benzidine 100 U ug/L 100 4002/21/2011 12:20 Effluent Priority Organic Pollutants Dimethyl phthalate 10 U ug/L 10 402/21/2011 12:20 Effluent Priority Organic Pollutants Fluoranthene 0.2 U ug/L 0.2 0.8147Appendix E. (continued)Date Sampled Field ID Analysis Group Components Result Remark Units MDL PQL2/21/2011 12:20 Effluent Priority Organic Pollutants Fluorene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants Hexachlorobutadiene 3 U ug/L 3 122/21/2011 12:20 Effluent Priority Organic Pollutants Hexachloroethane 3 U ug/L 3 122/21/2011 12:20 Effluent Priority Organic Pollutants N-Nitrosodiphenylamine/ Diphenylamine 3 U ug/L 3 122/21/2011 12:20 Effluent Priority Organic Pollutants Nitrobenzene 2 U ug/L 2 8.12/21/2011 12:20 Effluent Priority Organic Pollutants 1,2,4-Trichlorobenzene 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants 2-Chloronaphthalene 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants 4-Chlorophenyl phenyl ether 2 U ug/L 2 8.12/21/2011 12:20 Effluent Priority Organic Pollutants Benzo(b)fluoranthene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants Hexachlorocyclopentadiene 3 U ug/L 3 122/21/2011 12:20 Effluent Priority Organic Pollutants N-Nitrosodi-n-propylamine 2 U ug/L 2 8.12/21/2011 12:20 Effluent Priority Organic Pollutants 2-Nitrophenol 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants 4-Nitrophenol 15 U ug/L 15 612/21/2011 12:20 Effluent Priority Organic Pollutants Acenaphthene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants Acenaphthylene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants Di-n-butyl phthalate 5.1 U ug/L 5.1 202/21/2011 12:20 Effluent Priority Organic Pollutants Naphthalene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants 2,4-Dinitrophenol 15 U ug/L 15 612/21/2011 12:20 Effluent Priority Organic Pollutants Butyl benzyl phthalate 5.1 U ug/L 5.1 202/21/2011 12:20 Effluent Priority Organic Pollutants Dibenzo(a,h)anthracene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants Phenol 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants 2-Chlorophenol 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants 3,3'-Dichlorobenzidine 40 UJ ug/L 40 1602/21/2011 12:20 Effluent Priority Organic Pollutants 4-Bromophenyl phenyl ether 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants Benzo(g,h,i)perylene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Priority Organic Pollutants Bis(2-chloroethoxy)methane 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants Hexachlorobenzene 1 U ug/L 1 42/21/2011 12:20 Effluent Priority Organic Pollutants Indeno(1,2,3-cd)pyrene 0.2 U ug/L 0.2 0.812/21/2011 12:20 Effluent Field Parameter pH 7.52/21/2011 12:20 Effluent Field Parameter Temperature 26.27 C2/21/2011 12:20 Effluent Field Parameter Specific Conductance 41115 umhos/cm2/21/2011 12:20 Effluent Field Parameter Dissolved Oxygen 7.09 mg/L2/21/2011 12:20 Effluent Field Parameter Sample Depth 0.15 m2/21/2011 13:35 Ash Pond Metals Arsenic 28.3 ug/L 0.25 148Appendix E. (continued)Date Sampled Field ID Analysis Group Components Result Remark Units MDL PQL2/21/2011 13:35 Ash Pond Metals Copper 0.9 I ug/L 0.5 12/21/2011 13:35 Ash Pond Metals Zinc 5 U ug/L 5 202/21/2011 13:35 Ash Pond Metals Nickel 4.36 ug/L 0.25 12/21/2011 13:35 Ash Pond Metals Chromium 5.7 ug/L 0.3 1.22/21/2011 13:35 Ash Pond Metals Lead 0.2 U ug/L 0.2 0.82/21/2011 13:35 Ash Pond Metals Iron 150 ug/L 30 1202/21/2011 13:35 Ash Pond Metals Selenium 7.6 ug/L 0.2 0.82/21/2011 13:35 Ash Pond Metals Cadmium 0.25 ug/L 0.05 0.22/21/2011 13:35 Ash Pond Nutrients Kjeldahl Nitrogen 0.45 mg N/L 0.16 0.42/21/2011 13:35 Ash Pond Nutrients Ammonia-N 0.03 mg N/L 0.01 0.022/21/2011 13:35 Ash Pond Nutrients TSS 9 I mg/L 4 162/21/2011 13:35 Ash Pond Nutrients NO2NO3-N 0.014 mg N/L 0.005 0.012/21/2011 13:35 Ash Pond Overflow Oil and Grease 1.4 U mg/L 1.4 52/21/2011 13:35 Ash Pond Overflow Radium 226-Counting Error 0.3 pCi/L2/21/2011 13:35 Ash Pond Overflow Radium 226 0.9 pCi/L2/21/2011 13:35 Ash Pond Overflow Radium 228 0.8 U pCi/L2/21/2011 13:35 Ash Pond Overflow Radium 228-Counting Error 0.5 pCi/L2/21/2011 13:35 Ash Pond Field Parameter Specific Conductance 6153 umhos/cm2/21/2011 13:35 Ash Pond Field Parameter Temperature 19.64 C2/21/2011 13:35 Ash Pond Field Parameter Dissolved Oxygen 8.53 mg/L2/21/2011 13:35 Ash Pond Field Parameter pH 7.562/21/2011 13:35 Ash Pond Field Parameter Sample Depth 0.15 m2/21/2011 13:20 ICW Metals Nickel 0.33 I ug/L 0.25 12/21/2011 13:20 ICW Metals Iron 150 ug/L 30 1202/21/2011 13:20 ICW Metals Copper 0.5 U ug/L 0.5 12/21/2011 13:20 ICW Metals Lead 0.6 U ug/L 0.6 2.42/21/2011 13:45 Blank Metals Zinc 5 U ug/L 5 202/21/2011 13:45 Blank Metals Aluminum 60 U ug/L 60 2402/21/2011 13:45 Blank Metals Lead 0.2 U ug/L 0.2 0.82/21/2011 13:45 Blank Metals Chromium 0.3 U ug/L 0.3 1.22/21/2011 13:45 Blank Metals Arsenic 0.25 U ug/L 0.25 12/21/2011 13:45 Blank Metals Sodium 0.5 U mg/L 0.5 22/21/2011 13:45 Blank Metals Nickel 0.25 U ug/L 0.25 12/21/2011 13:45 Blank Metals Silver 0.025 U ug/L 0.025 0.149Appendix E. (continued)Date Sampled Field ID Analysis Group Components Result Remark Units MDL PQL2/21/2011 13:45 Blank Metals Selenium 0.2 U ug/L 0.2 0.82/21/2011 13:45 Blank Metals Cadmium 0.05 U ug/L 0.05 0.22/21/2011 13:45 Blank Metals Calcium 0.075 U mg/L 0.075 0.32/21/2011 13:45 Blank Metals Copper 0.5 U ug/L 0.5 12/21/2011 13:45 Blank Metals Magnesium 0.04 U mg/L 0.04 0.162/21/2011 13:45 Blank Metals Iron 30 U ug/L 30 1202/21/2011 13:45 Blank Nutrients O-Phosphate-P 0.004 U mg P/L 0.004 0.012/21/2011 13:45 Blank Nutrients Alkalinity 0.65 U mg CaCO3/L 0.65 2.52/21/2011 13:45 Blank Nutrients NO2NO3-N 0.004 U mg N/L 0.004 0.012/21/2011 13:45 Blank Nutrients Total-P 0.004 U mg P/L 0.004 0.012/21/2011 13:45 Blank Nutrients Kjeldahl Nitrogen 0.08 U mg N/L 0.08 0.22/21/2011 13:45 Blank Nutrients Ammonia-N 0.01 U mg N/L 0.01 0.022/21/2011 13:45 Blank Overflow Radium 228-Counting Error 0.5 pCi/L2/21/2011 13:45 Blank Overflow Oil and Grease 1.4 U mg/L 1.4 52/21/2011 13:45 Blank Overflow Radium 228 0.8 U pCi/L2/21/2011 13:45 Blank Overflow Radium 226 0.5 pCi/L2/21/2011 13:45 Blank Overflow Radium 226-Counting Error 0.2 pCi/L2/21/2011 13:45 Blank Pesticides Chlorpyrifos Ethyl 0.054 U ug/L 0.054 0.222/21/2011 13:45 Blank Pesticides Chlorpyrifos Methyl 0.11 U ug/L 0.11 0.442/21/2011 13:45 Blank Pesticides Endosulfan I 0.021 U ug/L 0.021 0.0842/21/2011 13:45 Blank Pesticides Simazine 0.054 U ug/L 0.054 0.222/21/2011 13:45 Blank PesticidesAlpha-BHC 0.011 U ug/L 0.011 0.0442/21/2011 13:45 Blank Pesticides Heptachlor Epoxide 0.021 U ug/L 0.021 0.0842/21/2011 13:45 Blank Pesticides Azinphos Methyl 0.21 U ug/L 0.21 0.842/21/2011 13:45 Blank PesticidesBromacil 0.21 U ug/L 0.21 0.842/21/2011 13:45 Blank Pesticides Hexazinone 0.11 U ug/L 0.11 0.442/21/2011 13:45 Blank Pesticides Mevinphos 0.21 U ug/L 0.21 0.842/21/2011 13:45 Blank Pesticides Phorate 0.054 U ug/L 0.054 0.222/21/2011 13:45 Blank Pesticides Chlordane 0.21 U ug/L 0.21 0.842/21/2011 13:45 Blank PesticidesDelta-BHC 0.011 U ug/L 0.011 0.0442/21/2011 13:45 Blank Pesticides Endosulfan Sulfate 0.021 U ug/L 0.021 0.0842/21/2011 13:45 Blank Pesticides Ethoprop 0.11 U ug/L 0.11 0.442/21/2011 13:45 Blank Pesticides Malathion 0.16 U ug/L 0.16 0.642/21/2011 13:45 Blank Pesticides Naled 0.86 U ug/L 0.86 3.450Appendix E. (continued)Date Sampled Field ID Analysis Group Components Result Remark Units MDL PQL2/21/2011 13:45 Blank Pesticides Aldrin 0.011 U ug/L 0.011 0.0442/21/2011 13:45 Blank Pesticides DDD-p,p' 0.021 U ug/L 0.021 0.0842/21/2011 13:45 Blank Pesticides Ametryn 0.054 U ug/L 0.054 0.222/21/2011 13:45 Blank Pesticides Butylate 0.21 U ug/L 0.21 0.842/21/2011 13:45 Blank Pesticides Metribuzin 0.11 U ug/L 0.11 0.442/21/2011 13:45 Blank Pesticides Endosulfan II 0.021 U ug/L 0.021 0.0842/21/2011 13:45 Blank Pesticides Endrin 0.054 U ug/L 0.054 0.222/21/2011 13:45 Blank Pesticides Heptachlor 0.011 U ug/L 0.011 0.0442/21/2011 13:45 Blank Pesticides Atrazine 0.054 U ug/L 0.054 0.222/21/2011 13:45 Blank Pesticides Fenamiphos 0.21 U ug/L 0.21 0.842/21/2011 13:45 Blank Pesticides Parathion Ethyl 0.16 U ug/L 0.16 0.642/21/2011 13:45 Blank Pesticides Parathion Methyl 0.11 U ug/L 0.11 0.442/21/2011 13:45 Blank Pesticides Prometryn 0.16 U ug/L 0.16 0.642/21/2011 13:45 Blank Pesticides Beta-BHC 0.011 U ug/L 0.011 0.0442/21/2011 13:45 Blank Pesticides Dieldrin 0.021 U ug/L 0.021 0.0842/21/2011 13:45 Blank Pesticides Gamma-BHC 0.011 U ug/L 0.011 0.0442/21/2011 13:45 Blank Pesticides Alachlor 0.64 U ug/L 0.64 2.62/21/2011 13:45 Blank Pesticides Ethion 0.054 U ug/L 0.054 0.222/21/2011 13:45 Blank Pesticides Metalaxyl 0.27 U ug/L 0.27 1.12/21/2011 13:45 Blank Pesticides Norflurazon 0.16 U ug/L 0.16 0.642/21/2011 13:45 Blank Pesticides DDT-p,p' 0.032 U ug/L 0.032 0.132/21/2011 13:45 Blank Pesticides Endrin Aldehyde 0.021 U ug/L 0.021 0.0842/21/2011 13:45 Blank Pesticides Methoxychlor 0.054 U ug/L 0.054 0.222/21/2011 13:45 Blank Pesticides Diazinon 0.054 U ug/L 0.054 0.222/21/2011 13:45 Blank Pesticides Fonofos 0.11 U ug/L 0.11 0.442/21/2011 13:45 Blank Pesticides Metolachlor 0.54 U ug/L 0.54 2.22/21/2011 13:45 Blank Pesticides DDE-p,p' 0.021 U ug/L 0.021 0.0842/21/2011 13:45 Blank Pesticides Toxaphene 0.8 U ug/L 0.8 3.22/21/2011 13:45 Blank Priority Organic Pollutants 1,2,4-Trichlorobenzene 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic PollutantsN-Nitrosodi-n-propylamine 2.2 U ug/L 2.2 92/21/2011 13:45 Blank Priority Organic PollutantsBis(2-chloroethoxy)methane 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants Isophorone 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants Phenol 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants Di-n-octyl phthalate 1.1 U ug/L 1.1 4.551Appendix E. (continued)Date Sampled Field ID Analysis Group Components Result Remark Units MDL PQL2/21/2011 13:45 Blank Priority Organic Pollutants Dibenzo(a,h)anthracene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants Indeno(1,2,3-cd)pyrene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants Pyrene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants 2,4-Dinitrotoluene 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants Hexachloroethane 3.4 U ug/L 3.4 132/21/2011 13:45 Blank Priority Organic Pollutants Hexachlorobutadiene 3.4 U ug/L 3.4 132/21/2011 13:45 Blank Priority Organic Pollutants Benzo(k)fluoranthene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants Benzo(g,h,i)perylene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants Benzo(b)fluoranthene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants 2,6-Dinitrotoluene 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants Fluorene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants N-Nitrosodimethylamine 2.2 U ug/L 2.2 92/21/2011 13:45 Blank Priority Organic Pollutants N-Nitrosodiphenylamine/ Diphenylamine 3.4 U ug/L 3.4 132/21/2011 13:45 Blank Priority Organic Pollutants Naphthalene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants Nitrobenzene 2.2 U ug/L 2.2 92/21/2011 13:45 Blank Priority Organic Pollutants Pentachlorophenol 3.4 U ug/L 3.4 132/21/2011 13:45 Blank Priority Organic Pollutants 2,4,6-Trichlorophenol 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants 2,4-Dinitrophenol 17 U ug/L 17 672/21/2011 13:45 Blank Priority Organic Pollutants 2-Chloronaphthalene 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants 2-Chlorophenol 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants 2-Nitrophenol 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants Acenaphthylene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants Benzidine 110 U ug/L 110 4502/21/2011 13:45 Blank Priority Organic Pollutants Di-n-butyl phthalate 5.6 U ug/L 5.6 222/21/2011 13:45 Blank Priority Organic Pollutants Hexachlorobenzene 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants Hexachlorocyclopentadiene 3.4 U ug/L 3.4 132/21/2011 13:45 Blank Priority Organic Pollutants 2,4-Dichlorophenol 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants 4-Bromophenyl phenyl ether 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants 4-Nitrophenol 17 U ug/L 17 672/21/2011 13:45 Blank Priority Organic Pollutants Acenaphthene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants Benzo(a)pyrene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic PollutantsBis(2-chloroethyl)ether 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants Bis(2-chloroisopropyl)ether 3.4 U ug/L 3.4 132/21/2011 13:45 Blank Priority Organic Pollutants Fluoranthene 0.22 U ug/L 0.22 0.952Appendix E. (continued)Date Sampled Field ID Analysis Group Components Result Remark Units MDL PQL2/21/2011 13:45 Blank Priority Organic Pollutants Phenanthrene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants 3,3'-Dichlorobenzidine 45 UJ ug/L 45 1802/21/2011 13:45 Blank Priority Organic Pollutants 4-Chloro-3-methylphenol 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants Diethyl phthalate 1.1 U ug/L 1.1 4.52/21/2011 13:45 Blank Priority Organic Pollutants 2-Methyl-4,6-dinitrophenol 3.4 U ug/L 3.4 132/21/2011 13:45 Blank Priority Organic Pollutants 4-Chlorophenyl phenyl ether 2.2 U ug/L 2.2 92/21/2011 13:45 Blank Priority Organic Pollutants Anthracene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants Benzo(a)anthracene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants Bis(2-ethylhexyl)phthalate 17 U ug/L 17 672/21/2011 13:45 Blank Priority Organic Pollutants Butyl benzyl phthalate 5.6 U ug/L 5.6 222/21/2011 13:45 Blank Priority Organic Pollutants Chrysene 0.22 U ug/L 0.22 0.92/21/2011 13:45 Blank Priority Organic Pollutants Dimethyl phthalate 11 U ug/L 11 452/21/2011 13:45 Blank Priority Organic Pollutants 2,4-Dimethylphenol 11 U ug/L 11 45

## 53 Appendix F. Facility Summary, Efflue nt Limits, and Permit Violations Recorded on Discharge Monitoring Report

## 54 Appendix F. (continued)

## 55 Appendix F. (continued)

## 56 Appendix F. (continued)

## 57 Appendix F. (continued)

## 58 Appendix F. (continued)

## 59 Appendix F. (continued)

## 60 Appendix F. (continued)

## 61 Appendix F. (continued)

## 62 Appendix G. EPA End Sheet

Transaction Code NPDES NUMBER YR/MO/DA Insp Type Inspector Fac Type

1 N 2 5 3 F L 0 0 0 2 2 6 7 11 12 1 1 0 2 2 1 18 B 19 S 20 2

66

Transaction Code NPDES NUMBER YR/MO/DA Insp Type Inspector Fac Type

1 N 2 5 3 F L 0 0 0 2 2 6 7 11 12 1 1 0 2 2 1 18 X 19 S 20 2

66

Transaction Code NPDES NUMBER YR/MO/DA Insp Type Inspector Fac Type

1 N 2 5 3 F L 0 0 0 2 2 6 7 11 12 1 1 0 2 2 1 18 S 19 S 20 2

66 Remarks Fill Out This Section For All Surface Water Discharger Inspections(CEI, CSI, CBI, PAI, XSI-RI Optional)

Remarks 

# The Bioassay of Gulf Power Company - Lansing Smith Power Plant effluent sampled on February 21, 23, and 25, 2011. NPDES

#FL0002267.

Fill Out This Section For All Surface Water Discharger Inspections(CEI, CSI, CBI, PAI, XSI-RI Optional)

Remarks



# The Priority Pollutants Analysis of Gulf Power Company - Lansing Smith Power Plant effluent sampled on February 21, 2011. NPDES

#FL0002267.

Biological Analyses of Gulf Power Company - Lansing Smith Power Plant effluent sampled on February 21, 2011. NPDES

#FL0002267.

Fill Out This Section For All Surface Water Discharger Inspections(CEI, CSI, CBI, PAI, XSI-RI Optional)