### Instructionsfor Completing the Process Data Template

This template is to be used to record the 30 daily averages of specific process data required by the ICR. The ERT does not have the capability to store these daily averages. This spreadsheet included 4 separate surrogate worksheets,in case the boiler tested is tested for all surrogates at 4 different dates.This spreadsheet is intended to be used for one boiler of one facility.Data for multiple boilers should be handled by using separate copies of this spreadsheet. yelloware required (if applicable to your boilers' operation). You do not need to populate cells shaded in gray, as they ar automaticallypopulated from the Boiler Information worksheet.Please Do Not modify the structure of this spreadsheet by adding or subtracting rows, columns, cells.Pleasename each resulting spreadsheet with the following naming

convention:[FacilityID]_Unit_[BoilerID]_Processdata.xls(example: 8100_Unit_2_Processdata.xls).

Pleaserefer to the following steps when using these spreadsheets.

BoilerInformation Worksheet

Pleaseenter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Informationworksheet.

ProcessData Worksheets

Pleaseuse one process data worksheetfor each HAP surrogate even is simultaneous testing of different HAP surrogates was done.

### Instructionsfor Completing the Process Data Template

This template is to be used to record the 30 daily averages of specific process data required by the ICR. The ERT does not have the capability to store these daily averages. This spreadsheet included 4 separate surrogate worksheets,in case the This spreadsheet is intended to be used for one boiler of one facility.Data for multiple boilers should be handled by using separate copies of this spreadsheet.Fields shaded in yelloware required (if applicable to your boilers' operation). You do not need to populate cells shaded in gray, as they are Please Do Not modify the structure of this spreadsheet Pleasename each resulting spreadsheet with the following naming

convention:[FacilityID]_Unit_[BoilerID]_Processdata.xls(example: 8100_Unit_2_Processdata.xls).

Pleaseenter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Informationworksheet.

Pleaseuse one process data worksheetfor each HAP surrogate even is simultaneous testing of different HAP surrogatesEIA

Facility CodeFacility Name Boiler ID

3131Shawville Units 3 and 4 Common StackUnits 3 and 4 Common StackEIA

Facility CodeFacility NameBoiler ID

3131Shawville Units 3 and 4 Common Stack

Daily A verage Process Data for a 30 Day Period Including the Testing Date Date Coal Firing Rate Coal Firing Rate (units)Synfuel Firing Rate Day 1 5/31/2010 224.803432 klb/hr Day 2 6/1/2010 229.2021006 klb/hr Day 3 6/2/2010 224.2036272 klb/hr Day 4 6/3/2010 233.4772612 klb/hr Day 5 6/4/2010 229.0759986 klb/hr Day 6 6/5/2010 242.7011593 klb/hr Day 7 6/6/2010 226.3338269 klb/hr Day 8 6/7/2010 212.9057966 klb/hr Day 9 6/8/2010 220.6924702 klb/hr Day 10 6/9/2010 230.0533517 klb/hr Day 11 6/10/2010 109.2453053 klb/hr Day 12 6/11/2010 116.524185 klb/hr Day 13 6/12/2010 111.6212236 klb/hr Day 14 6/13/2010 107.5829316 klb/hr Day 15 6/14/2010 206.8901745 klb/hr Day 16 6/15/2010 245.1217401 klb/hr Day 17 6/16/2010 234.9290748 klb/hr Day 18 6/17/2010 207.4359848 klb/hr Day 19 6/18/2010 220.8771235 klb/hr Day 20 6/19/2010 206.9393365 klb/hr Day 21 6/20/2010 131.4825643 klb/hr Day 22 6/21/2010 104.8484848 klb/hr Day 23 6/22/2010 121.8659435 klb/hr Day 24 6/23/2010 196.5063246 klb/hr Day 25 6/24/2010 242.7326102 klb/hr Day 26 6/25/2010 237.827686 klb/hr Day 27 6/26/2010 228.8721419 klb/hr Day 28 6/27/2010 220.6314853 klb/hr Day 29 6/28/2010 222.8474518 klb/hr Day 30 6/29/2010 212.543859 klb/hrDaily A verage Process Data for a 30 Day Period Including the Testing Date Synfuel Firing Rate (units)Pet Coke Firing RatePet Coke Firing Rate (units)Coal Gas Firing RateCoal Gas Firing Rate (units)Fuel oil Firing RateFuel oil Firing Rate (units)Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr) 2720.121528 2106.058908 2773.345417 2144.258911 2712.863889 2095.324051 2825.074861 2172.877655 2771.819583 2131.027461 2936.684028 2285.006173 2738.639306 2130.304663 2576.160139 2010.950361 2670.378889 2056.309046 2783.645556 2129.823835 1321.868194 1052.091539 1409.942639 1095.645118 1350.616806 1046.30597 1301.753472 974.4107798 2503.371111 1943.616768 2965.973056 2271.027657 2842.641806 2175.678088 2509.975417 1953.171196 2672.613194 2067.24697 2503.965972 1926.133214 1590.939028 1254.879661 1268.666667 982.8541525 1474.577917 1137.805194 2377.726528 1840.808711 2937.064583 2251.034853 2877.715 2202.488856 2769.352917 2114.466605 2669.640972 2034.073129 2696.454167 2050.127087 2571.780694 1940.971241Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe) 281.1091687 301.3970807 290.0604181 311.0289116 283.1600008 302.9267381 290.2470849 311.880394 286.0908333 305.5166073 305.330836 327.0913919 288.9291674 307.6445313 271.5029182 289.5019538 271.9945847 292.2911011 282.8487504 303.756423 144.3808334 153.2843757 143.8970814 152.2151977 135.5099999 143.3105951 126.5204183 133.3059182 235.9212507 255.0136559 307.9108353 328.845698 299.0145826 320.1613681 252.6783339 269.4679108 275.5729179 294.3650665 252.3495852 268.5283473 167.0029169 178.3441598 122.186667 133.4150343 143.9704166 155.0101329 215.8508334 235.4297996 293.5266685 311.2087752 289.2241666 307.3673827 276.7854172 293.5142072 266.3683345 282.5533412 269.7866691 286.6833989 256.6208337 274.4740655Control Device Operating Parameters, A s Appicable Flue Gas Flow Rate (scfm) Pressure Drop across FGD (in H2O) 831220.3335 849959.0742 835241.7737 860581.4858 851740.5867 887894.1524 827631.474 779572.635 802310.7541 832588.6225 552500.915 443015.8402 418189.0792 487622.3483 795875.5483 867029.2055 850984.8287 764784.8502 805199.9189 767203.2298 633010.2942 479713.1486 513996.329 790777.4215 867926.5603 845927.5288 823087.7704 806628.7142 808227.0977 771463.7403FGD Scrubber Liquor Flow Rate (gals/min) Sorbent TypeSorbent Injection Rate (lb/hr)Other Boiler or Control Device Operating Parameters (e.g., Boiler O2)

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

0.948487021 279.9891899 0.944908519 279.8176178 0.94411002 273.9450018 0.94174416 279.6495164 0.94413213 281.3869165 0.941794054 280.7807535 0.937140526 275.0854725 0.946848273 268.7469582 0.95296764 265.3288568 0.946774741 265.8756671 0.946692525 255.4351991 0.952990534 258.9508196 0.949713732 269.4409063 0.947097958 261.8163868 0.947184702 270.100345 0.951865253 276.799482 0.948494108 280.0799835 0.949833111 272.511623 0.952959714 272.6390281 0.949875436 278.1984413 0.949269835 266.6968768 0.952809296 255.7784821 0.951721273 261.1111047 0.950313287 274.7127461 0.946325599 283.6084688 0.951306851 279.101373 0.947472675 280.0658778 0.941652191 286.4889889 0.93946816 286.0258535 0.94755654 278.8732088Flue Gas Oxygen Content (%)Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%) 9.791218967 9.766519753 9.718289029 9.859901933 9.750437795 9.919688356 9.91988089 9.893636334 9.948444665 10.02345424 7.434395195 9.544959079 9.659665511 8.290655075 9.222831083 10.2600856 10.01869715 9.817397795 9.941208673 9.766781843 7.333258063 7.962314175 8.694174018 8.835034477 10.14523745 10.19994304 10.09567752 9.925189903 10.00937752 10.00070896EIA

Facility CodeFacility NameBoiler ID

3131Shawville Units 3 and 4 Common Stack

Daily A verage Process Data for a 30 Day Period Including the Testing Date Date Coal Firing Rate Coal Firing Rate (units)Synfuel Firing Rate Day 1 5/31/2010 224.803432 klb/hr Day 2 6/1/2010 229.2021006 klb/hr Day 3 6/2/2010 224.2036272 klb/hr Day 4 6/3/2010 233.4772612 klb/hr Day 5 6/4/2010 229.0759986 klb/hr Day 6 6/5/2010 242.7011593 klb/hr Day 7 6/6/2010 226.3338269 klb/hr Day 8 6/7/2010 212.9057966 klb/hr Day 9 6/8/2010 220.6924702 klb/hr Day 10 6/9/2010 230.0533517 klb/hr Day 11 6/10/2010 109.2453053 klb/hr Day 12 6/11/2010 116.524185 klb/hr Day 13 6/12/2010 111.6212236 klb/hr Day 14 6/13/2010 107.5829316 klb/hr Day 15 6/14/2010 206.8901745 klb/hr Day 16 6/15/2010 245.1217401 klb/hr Day 17 6/16/2010 234.9290748 klb/hr Day 18 6/17/2010 207.4359848 klb/hr Day 19 6/18/2010 220.8771235 klb/hr Day 20 6/19/2010 206.9393365 klb/hr Day 21 6/20/2010 131.4825643 klb/hr Day 22 6/21/2010 104.8484848 klb/hr Day 23 6/22/2010 121.8659435 klb/hr Day 24 6/23/2010 196.5063246 klb/hr Day 25 6/24/2010 242.7326102 klb/hr Day 26 6/25/2010 237.827686 klb/hr Day 27 6/26/2010 228.8721419 klb/hr Day 28 6/27/2010 220.6314853 klb/hr Day 29 6/28/2010 222.8474518 klb/hr Day 30 6/29/2010 212.543859 klb/hrDaily A verage Process Data for a 30 Day Period Including the Testing Date Synfuel Firing Rate (units)Pet Coke Firing RatePet Coke Firing Rate (units)Coal Gas Firing RateCoal Gas Firing Rate (units)Fuel oil Firing RateFuel oil Firing Rate (units)Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr) 2720.121528 2106.058908 2773.345417 2144.258911 2712.863889 2095.324051 2825.074861 2172.877655 2771.819583 2131.027461 2936.684028 2285.006173 2738.639306 2130.304663 2576.160139 2010.950361 2670.378889 2056.309046 2783.645556 2129.823835 1321.868194 1052.091539 1409.942639 1095.645118 1350.616806 1046.30597 1301.753472 974.4107798 2503.371111 1943.616768 2965.973056 2271.027657 2842.641806 2175.678088 2509.975417 1953.171196 2672.613194 2067.24697 2503.965972 1926.133214 1590.939028 1254.879661 1268.666667 982.8541525 1474.577917 1137.805194 2377.726528 1840.808711 2937.064583 2251.034853 2877.715 2202.488856 2769.352917 2114.466605 2669.640972 2034.073129 2696.454167 2050.127087 2571.780694 1940.971241Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe) 281.1091687 301.3970807 290.0604181 311.0289116 283.1600008 302.9267381 290.2470849 311.880394 286.0908333 305.5166073 305.330836 327.0913919 288.9291674 307.6445313 271.5029182 289.5019538 271.9945847 292.2911011 282.8487504 303.756423 144.3808334 153.2843757 143.8970814 152.2151977 135.5099999 143.3105951 126.5204183 133.3059182 235.9212507 255.0136559 307.9108353 328.845698 299.0145826 320.1613681 252.6783339 269.4679108 275.5729179 294.3650665 252.3495852 268.5283473 167.0029169 178.3441598 122.186667 133.4150343 143.9704166 155.0101329 215.8508334 235.4297996 293.5266685 311.2087752 289.2241666 307.3673827 276.7854172 293.5142072 266.3683345 282.5533412 269.7866691 286.6833989 256.6208337 274.4740655Control Device Operating Parameters, A s Appicable Flue Gas Flow Rate (scfm) Pressure Drop across FGD (in H2O) 831220.3335 849959.0742 835241.7737 860581.4858 851740.5867 887894.1524 827631.474 779572.635 802310.7541 832588.6225 552500.915 443015.8402 418189.0792 487622.3483 795875.5483 867029.2055 850984.8287 764784.8502 805199.9189 767203.2298 633010.2942 479713.1486 513996.329 790777.4215 867926.5603 845927.5288 823087.7704 806628.7142 808227.0977 771463.7403FGD Scrubber Liquor Flow Rate (gals/min) Sorbent TypeSorbent Injection Rate (lb/hr)Other Boiler or Control Device Operating Parameters (e.g., Boiler O2)

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

0.948487021 279.9891899 0.944908519 279.8176178 0.94411002 273.9450018 0.94174416 279.6495164 0.94413213 281.3869165 0.941794054 280.7807535 0.937140526 275.0854725 0.946848273 268.7469582 0.95296764 265.3288568 0.946774741 265.8756671 0.946692525 255.4351991 0.952990534 258.9508196 0.949713732 269.4409063 0.947097958 261.8163868 0.947184702 270.100345 0.951865253 276.799482 0.948494108 280.0799835 0.949833111 272.511623 0.952959714 272.6390281 0.949875436 278.1984413 0.949269835 266.6968768 0.952809296 255.7784821 0.951721273 261.1111047 0.950313287 274.7127461 0.946325599 283.6084688 0.951306851 279.101373 0.947472675 280.0658778 0.941652191 286.4889889 0.93946816 286.0258535 0.94755654 278.8732088Flue Gas Oxygen Content (%)Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%) 9.791218967 9.766519753 9.718289029 9.859901933 9.750437795 9.919688356 9.91988089 9.893636334 9.948444665 10.02345424 7.434395195 9.544959079 9.659665511 8.290655075 9.222831083 10.2600856 10.01869715 9.817397795 9.941208673 9.766781843 7.333258063 7.962314175 8.694174018 8.835034477 10.14523745 10.19994304 10.09567752 9.925189903 10.00937752 10.00070896EIA

Facility CodeFacility NameBoiler ID

3131Shawville Units 3 and 4 Common Stack

Daily A verage Process Data for a 30 Day Period Including the Testing Date Date Coal Firing Rate Coal Firing Rate (units)Synfuel Firing Rate Day 1 5/31/2010 224.803432 klb/hr Day 2 6/1/2010 229.2021006 klb/hr Day 3 6/2/2010 224.2036272 klb/hr Day 4 6/3/2010 233.4772612 klb/hr Day 5 6/4/2010 229.0759986 klb/hr Day 6 6/5/2010 242.7011593 klb/hr Day 7 6/6/2010 226.3338269 klb/hr Day 8 6/7/2010 212.9057966 klb/hr Day 9 6/8/2010 220.6924702 klb/hr Day 10 6/9/2010 230.0533517 klb/hr Day 11 6/10/2010 109.2453053 klb/hr Day 12 6/11/2010 116.524185 klb/hr Day 13 6/12/2010 111.6212236 klb/hr Day 14 6/13/2010 107.5829316 klb/hr Day 15 6/14/2010 206.8901745 klb/hr Day 16 6/15/2010 245.1217401 klb/hr Day 17 6/16/2010 234.9290748 klb/hr Day 18 6/17/2010 207.4359848 klb/hr Day 19 6/18/2010 220.8771235 klb/hr Day 20 6/19/2010 206.9393365 klb/hr Day 21 6/20/2010 131.4825643 klb/hr Day 22 6/21/2010 104.8484848 klb/hr Day 23 6/22/2010 121.8659435 klb/hr Day 24 6/23/2010 196.5063246 klb/hr Day 25 6/24/2010 242.7326102 klb/hr Day 26 6/25/2010 237.827686 klb/hr Day 27 6/26/2010 228.8721419 klb/hr Day 28 6/27/2010 220.6314853 klb/hr Day 29 6/28/2010 222.8474518 klb/hr Day 30 6/29/2010 212.543859 klb/hrDaily A verage Process Data for a 30 Day Period Including the Testing Date Synfuel Firing Rate (units)Pet Coke Firing RatePet Coke Firing Rate (units)Coal Gas Firing RateCoal Gas Firing Rate (units)Fuel oil Firing RateFuel oil Firing Rate (units)Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr) 2720.121528 2106.058908 2773.345417 2144.258911 2712.863889 2095.324051 2825.074861 2172.877655 2771.819583 2131.027461 2936.684028 2285.006173 2738.639306 2130.304663 2576.160139 2010.950361 2670.378889 2056.309046 2783.645556 2129.823835 1321.868194 1052.091539 1409.942639 1095.645118 1350.616806 1046.30597 1301.753472 974.4107798 2503.371111 1943.616768 2965.973056 2271.027657 2842.641806 2175.678088 2509.975417 1953.171196 2672.613194 2067.24697 2503.965972 1926.133214 1590.939028 1254.879661 1268.666667 982.8541525 1474.577917 1137.805194 2377.726528 1840.808711 2937.064583 2251.034853 2877.715 2202.488856 2769.352917 2114.466605 2669.640972 2034.073129 2696.454167 2050.127087 2571.780694 1940.971241Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe) 281.1091687 301.3970807 290.0604181 311.0289116 283.1600008 302.9267381 290.2470849 311.880394 286.0908333 305.5166073 305.330836 327.0913919 288.9291674 307.6445313 271.5029182 289.5019538 271.9945847 292.2911011 282.8487504 303.756423 144.3808334 153.2843757 143.8970814 152.2151977 135.5099999 143.3105951 126.5204183 133.3059182 235.9212507 255.0136559 307.9108353 328.845698 299.0145826 320.1613681 252.6783339 269.4679108 275.5729179 294.3650665 252.3495852 268.5283473 167.0029169 178.3441598 122.186667 133.4150343 143.9704166 155.0101329 215.8508334 235.4297996 293.5266685 311.2087752 289.2241666 307.3673827 276.7854172 293.5142072 266.3683345 282.5533412 269.7866691 286.6833989 256.6208337 274.4740655Control Device Operating Parameters, A s Appicable Flue Gas Flow Rate (scfm) Pressure Drop across FGD (in H2O) 831220.3335 849959.0742 835241.7737 860581.4858 851740.5867 887894.1524 827631.474 779572.635 802310.7541 832588.6225 552500.915 443015.8402 418189.0792 487622.3483 795875.5483 867029.2055 850984.8287 764784.8502 805199.9189 767203.2298 633010.2942 479713.1486 513996.329 790777.4215 867926.5603 845927.5288 823087.7704 806628.7142 808227.0977 771463.7403FGD Scrubber Liquor Flow Rate (gals/min) Sorbent TypeSorbent Injection Rate (lb/hr)Other Boiler or Control Device Operating Parameters (e.g., Boiler O2)

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

0.948487021 279.9891899 0.944908519 279.8176178 0.94411002 273.9450018 0.94174416 279.6495164 0.94413213 281.3869165 0.941794054 280.7807535 0.937140526 275.0854725 0.946848273 268.7469582 0.95296764 265.3288568 0.946774741 265.8756671 0.946692525 255.4351991 0.952990534 258.9508196 0.949713732 269.4409063 0.947097958 261.8163868 0.947184702 270.100345 0.951865253 276.799482 0.948494108 280.0799835 0.949833111 272.511623 0.952959714 272.6390281 0.949875436 278.1984413 0.949269835 266.6968768 0.952809296 255.7784821 0.951721273 261.1111047 0.950313287 274.7127461 0.946325599 283.6084688 0.951306851 279.101373 0.947472675 280.0658778 0.941652191 286.4889889 0.93946816 286.0258535 0.94755654 278.8732088Flue Gas Oxygen Content (%)Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%) 9.791218967 9.766519753 9.718289029 9.859901933 9.750437795 9.919688356 9.91988089 9.893636334 9.948444665 10.02345424 7.434395195 9.544959079 9.659665511 8.290655075 9.222831083 10.2600856 10.01869715 9.817397795 9.941208673 9.766781843 7.333258063 7.962314175 8.694174018 8.835034477 10.14523745 10.19994304 10.09567752 9.925189903 10.00937752 10.00070896EIA

Facility CodeFacility NameBoiler ID

3131Shawville Units 3 and 4 Common Stack

Daily A verage Process Data for a 30 Day Period Including the Testing Date Date Coal Firing Rate Coal Firing Rate (units)Synfuel Firing Rate Day 1 5/31/2010 224.803432 klb/hr Day 2 6/1/2010 229.2021006 klb/hr Day 3 6/2/2010 224.2036272 klb/hr Day 4 6/3/2010 233.4772612 klb/hr Day 5 6/4/2010 229.0759986 klb/hr Day 6 6/5/2010 242.7011593 klb/hr Day 7 6/6/2010 226.3338269 klb/hr Day 8 6/7/2010 212.9057966 klb/hr Day 9 6/8/2010 220.6924702 klb/hr Day 10 6/9/2010 230.0533517 klb/hr Day 11 6/10/2010 109.2453053 klb/hr Day 12 6/11/2010 116.524185 klb/hr Day 13 6/12/2010 111.6212236 klb/hr Day 14 6/13/2010 107.5829316 klb/hr Day 15 6/14/2010 206.8901745 klb/hr Day 16 6/15/2010 245.1217401 klb/hr Day 17 6/16/2010 234.9290748 klb/hr Day 18 6/17/2010 207.4359848 klb/hr Day 19 6/18/2010 220.8771235 klb/hr Day 20 6/19/2010 206.9393365 klb/hr Day 21 6/20/2010 131.4825643 klb/hr Day 22 6/21/2010 104.8484848 klb/hr Day 23 6/22/2010 121.8659435 klb/hr Day 24 6/23/2010 196.5063246 klb/hr Day 25 6/24/2010 242.7326102 klb/hr Day 26 6/25/2010 237.827686 klb/hr Day 27 6/26/2010 228.8721419 klb/hr Day 28 6/27/2010 220.6314853 klb/hr Day 29 6/28/2010 222.8474518 klb/hr Day 30 6/29/2010 212.543859 klb/hrDaily A verage Process Data for a 30 Day Period Including the Testing Date Synfuel Firing Rate (units)Pet Coke Firing RatePet Coke Firing Rate (units)Coal Gas Firing RateCoal Gas Firing Rate (units)Fuel oil Firing RateFuel oil Firing Rate (units)Average Heat Input (MMBtu/hr) Steam Output (1,000 lbs steam/hr) 2720.121528 2106.058908 2773.345417 2144.258911 2712.863889 2095.324051 2825.074861 2172.877655 2771.819583 2131.027461 2936.684028 2285.006173 2738.639306 2130.304663 2576.160139 2010.950361 2670.378889 2056.309046 2783.645556 2129.823835 1321.868194 1052.091539 1409.942639 1095.645118 1350.616806 1046.30597 1301.753472 974.4107798 2503.371111 1943.616768 2965.973056 2271.027657 2842.641806 2175.678088 2509.975417 1953.171196 2672.613194 2067.24697 2503.965972 1926.133214 1590.939028 1254.879661 1268.666667 982.8541525 1474.577917 1137.805194 2377.726528 1840.808711 2937.064583 2251.034853 2877.715 2202.488856 2769.352917 2114.466605 2669.640972 2034.073129 2696.454167 2050.127087 2571.780694 1940.971241Unit Net Electric Generation (MWh) Unit Gross Electric Generation (MWe) 281.1091687 301.3970807 290.0604181 311.0289116 283.1600008 302.9267381 290.2470849 311.880394 286.0908333 305.5166073 305.330836 327.0913919 288.9291674 307.6445313 271.5029182 289.5019538 271.9945847 292.2911011 282.8487504 303.756423 144.3808334 153.2843757 143.8970814 152.2151977 135.5099999 143.3105951 126.5204183 133.3059182 235.9212507 255.0136559 307.9108353 328.845698 299.0145826 320.1613681 252.6783339 269.4679108 275.5729179 294.3650665 252.3495852 268.5283473 167.0029169 178.3441598 122.186667 133.4150343 143.9704166 155.0101329 215.8508334 235.4297996 293.5266685 311.2087752 289.2241666 307.3673827 276.7854172 293.5142072 266.3683345 282.5533412 269.7866691 286.6833989 256.6208337 274.4740655Control Device Operating Parameters, A s Appicable Flue Gas Flow Rate (scfm) Pressure Drop across FGD (in H2O) 831220.3335 849959.0742 835241.7737 860581.4858 851740.5867 887894.1524 827631.474 779572.635 802310.7541 832588.6225 552500.915 443015.8402 418189.0792 487622.3483 795875.5483 867029.2055 850984.8287 764784.8502 805199.9189 767203.2298 633010.2942 479713.1486 513996.329 790777.4215 867926.5603 845927.5288 823087.7704 806628.7142 808227.0977 771463.7403FGD Scrubber Liquor Flow Rate (gals/min) Sorbent TypeSorbent Injection Rate (lb/hr)Other Boiler or Control Device Operating Parameters (e.g., Boiler O2)

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

0.948487021 279.9891899 0.944908519 279.8176178 0.94411002 273.9450018 0.94174416 279.6495164 0.94413213 281.3869165 0.941794054 280.7807535 0.937140526 275.0854725 0.946848273 268.7469582 0.95296764 265.3288568 0.946774741 265.8756671 0.946692525 255.4351991 0.952990534 258.9508196 0.949713732 269.4409063 0.947097958 261.8163868 0.947184702 270.100345 0.951865253 276.799482 0.948494108 280.0799835 0.949833111 272.511623 0.952959714 272.6390281 0.949875436 278.1984413 0.949269835 266.6968768 0.952809296 255.7784821 0.951721273 261.1111047 0.950313287 274.7127461 0.946325599 283.6084688 0.951306851 279.101373 0.947472675 280.0658778 0.941652191 286.4889889 0.93946816 286.0258535 0.94755654 278.8732088Flue Gas Oxygen Content (%)Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%) 9.791218967 9.766519753 9.718289029 9.859901933 9.750437795 9.919688356 9.91988089 9.893636334 9.948444665 10.02345424 7.434395195 9.544959079 9.659665511 8.290655075 9.222831083 10.2600856 10.01869715 9.817397795 9.941208673 9.766781843 7.333258063 7.962314175 8.694174018 8.835034477 10.14523745 10.19994304 10.09567752 9.925189903 10.00937752 10.00070896