Exhibit F.3.1  Form of Change Order    Reference is made to the Wind Turbine Supply Agreement, dated as of September 29, 2006 (the Agreement), by and between Madison Gas and Electric Company, a Wisconsin corporation (Buyer), and Vestas-American Wind Technology, Inc., a California corporation (Supplier).  Capitalized terms used but not defined herein shall have the meanings set forth in the Agreement. In accordance with Article 11 of the Agreement, each of Supplier and Buyer agrees to the following changes to the Agreement:  1) [Insert description of requested change in the Equipment Supply Obligations, if any, including detailed supporting information;]  2) The Contract Price shall be [increased][decreased] by the amount of $______, and the Payment Schedule shall be adjusted as follows:  [insert adjustments to Payment Schedule, if any];  3) The Project Schedule shall be adjusted as follows:  [insert adjustments to Project Schedule, if any];  In all other respects the Agreement shall remain unmodified and in full force and effect.  Agreed pursuant to the Agreement by:  SUPPLIER: BUYER: Vestas-American Wind Technology, Inc., Madison Gas and Electric Company, a California corporation a Wisconsin corporation  By: _______________________________ By: __________________________ Name: _____________________________ Name: ________________________ Title: ______________________________ Title: _________________________ Date: ______________________________ Date: _________________________   Exhibit F.3.2  Form of Shipping Certificate    DATE: 1. Supplier has delivered this completed Shipping Certificate to Buyer on the above date.  Capitalized terms used but not defined herein shall have the meanings set forth in that certain Wind Turbine Supply Agreement, dated as of September 29, 2006 (the Agreement), by and between Madison Gas and Electric Company, a Wisconsin corporation (Buyer), and Vestas-American Wind Technology, Inc., a California corporation (Supplier). 2. [For use with Turbine Nacelles]Pursuant to Section 4.2.2 of the Agreement, Supplier hereby notifies Buyer that on _________, 200_, [insert number] Turbine Nacelles have been shipped. 3. [For use with Blades]Pursuant to Section 4.2.2 of the Agreement, Supplier hereby notifies Buyer that on _________, 200_, [insert number] blades have been shipped. 4. [For use with Hubs]Pursuant to Section 4.2.2 of the Agreement, Supplier hereby notifies Buyer that on _________, 200_, [insert number] Hubs have been shipped. 5. [For use with Tower Sections]Pursuant to Section 4.2.2 of the Agreement, Supplier hereby notifies Buyer that on _________, 200_, [insert number] Tower sections have been shipped. 6. The person signing below is authorized to submit this Shipping Certificate to Buyer for and on behalf of Supplier.  SUPPLIER: VestasAmerican Wind Technology, Inc., a California corporation  By: ____________________________ Name: __________________________ Title: ___________________________  MG&E Turbine Supply Agreement, Exhibit F.3.3 Exhibit F.3.3 Form of Delivery Certificate SF#1091522
 [ex102f303doc002.gif]  [ex102f303doc004.gif]  [ex102f303doc006.gif]  [ex102f303doc008.gif]  [ex102f303doc010.gif]  [ex102f303doc012.gif] MG&E Turbine Supply Agreement, Exhibit F.3.3 Document   No..__________________________ Class: 1 Transport  Control  Form Site Name: Port Railhead Job Site TRUCK/CONTAINER ID. DESCRIPTION OF GOODS EXPECTED ARRIVAL Date &TIME ACTUAL ARRIVAL DATE ACTUAL TIME OF ARRIVAL TIME UNLOADING STARTED TIME UNLOADING FINISHED TOTAL TIME UNLOADING COMMENTS If any damage parts  have been discovered or if any parts are missing fill in the Transport Claim Form All the goods received on/in the above referred to truck /container has been received on the transporters final des- tination point. The goods has been inspected and found to be in good order (excluding possible remark under Comments) SIGNATURE OF VESTAS SIGNATURE OF OWNER OR REPRESENTATIVE OF OWNER DATE AND SIGNATURE OF DRIVER NAME OF DRIVER (BLOCK LETTERS) Form PROJ004 R0 5-JUL-2005 CONFIDENTIAL AND PROPRIETARY TO VESTAS SF#1091522
 [ex102f303doc014.gif] MG&E Turbine Supply Agreement, Exhibit F.3.3 SF#1091522  [ex102f303doc016.gif] MG&E Turbine Supply Agreement, Exhibit F.3.3 SF#1091522  [ex102f303doc018.gif] MG&E Turbine Supply Agreement, Exhibit F.3.3 SF#1091522
 Exhibit F.3.4  Form of Delayed Delivery Certificate    DATE:  1. Supplier has delivered this completed Delayed Delivery Certificate to Buyer on the above date.  Capitalized terms used but not defined herein shall have the meanings set forth in that certain Wind Turbine Supply Agreement, dated as of September 29, 2006 (the Agreement), by and between Madison Gas and Electric Company, a Wisconsin corporation (Buyer), and Vestas-American Wind Technology, Inc., a California corporation (Supplier). 2. Pursuant to Section 4.2.3 of the Agreement, Supplier hereby certifies that [insert number] [Turbine Nacelles] [blades] [Hubs] [Tower sections] could not be delivered to the Delivery Point within thirty (30) days following its scheduled arrival at the Delivery Point due to an Excusable Event. 3. The person signing below is authorized to submit this Delayed Delivery Certificate to Buyer for and on behalf of Supplier.  Vestas-American Wind Technology, Inc.,
            a California corporationBy:
            Name:
            Title:Date:
 MG&E Turbine Supply Agreement, Exhibit F.3.5 Exhibit F.3.5 Mechanical Completion Checklist SF# 1091526  [ex102f305doc002.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc004.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc006.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc008.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc010.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc012.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc014.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc016.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc018.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc020.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc022.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc024.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc026.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc028.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc030.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc032.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc034.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc036.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc038.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc040.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc042.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc044.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc046.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc048.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526  [ex102f305doc050.gif] MG&E Turbine Supply Agreement, Exhibit F.3.5 SF# 1091526
 Exhibit F.3.6  Form of Mechanical Completion Certificate  Date of Mechanical Completion: _________________  1. Reference is made to the Wind Turbine Supply Agreement, dated as of September 29, 2006 (the Agreement), by and between Madison Gas and Electric Company, a Wisconsin corporation (Buyer), and Vestas-American Wind Technology, Inc., a California corporation (Supplier).  Capitalized terms used but not defined herein shall have the meanings set forth in the Agreement.  2. The undersigned, Buyer, does hereby certify and represent to Supplier with respect to Wind Turbine No. _____ that (i) such Wind Turbine and associated Tower has been assembled, erected, installed and connected to the Interconnecting Utilitys grid in accordance with the Applicable Laws and the Agreement; (ii) all necessary materials and equipment with respect to such Wind Turbine and associated Tower has been installed substantially in accordance with the Technical Specifications and applicable quality assurance procedures and checked for adjustment, rotation and lubrication; (iii) each item on the Mechanical Completion Checklist, a completed copy of which is attached hereto, has been satisfied in accordance with the Agreement; and (iv) such Wind Turbine is ready to commence Commissioning.  3. The person signing below is authorized to submit this Mechanical Completion Certificate to Supplier for and on behalf of Buyer.  BUYER: Madison Gas and Electric Company, a Wisconsin corporation  By: ________________________________ Name: _____________________________ Title: ______________________________ Date: _______________________________   Supplier to cross through one (1) of the following statements:  A. Supplier agrees that Mechanical Completion has been achieved with respect to the enumerated Wind Turbine(s) and associated Tower(s) as set forth herein.  B.  Supplier does not agree that Mechanical Completion has been achieved with respect to the enumerated Wind Turbine(s) and associated Tower(s) as set forth therein due to the omissions or defects listed below and/ or the incomplete nature of the specified obligations listed below:         The person signing below is authorized to submit this form to Buyer for and on behalf of Supplier.  ACCEPTED BY SUPPLIER: Vestas-American Wind Technology, Inc., a California corporation  By: __________________________ Name: ________________________ Title: _________________________ Date: _________________________
 MG&E Turbine Supply Agreement, Exhibit F.3.7 Exhibit F.3.7 Commissioning Completion Checklist SF# 1091529  [ex102f307doc002.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc004.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc006.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc008.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc010.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc012.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc014.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc016.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc018.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc020.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc022.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc024.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc026.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc028.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc030.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc032.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc034.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc036.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc038.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc040.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529  [ex102f307doc042.gif] MG&E Turbine Supply Agreement, Exhibit F.3.7 SF# 1091529
 Exhibit F.3.8  Form of Commissioning Completion Certificate     Date of Commissioning Completion:  _________________  1. Reference is made to the Wind Turbine Supply Agreement, dated as of September 29, 2006 (the Agreement), by and between Madison Gas and Electric Company, a Wisconsin corporation (Buyer), and Vestas-American Wind Technology, Inc. (Supplier).  Capitalized terms used but not defined herein shall have the meanings set forth in the Agreement.  2. The undersigned, Supplier, does hereby certify and represent with respect to Wind Turbine No. ___ and its related components that each item on the Commissioning Completion Checklist, a completed copy of which is attached as Exhibit A, has been satisfied in accordance with the Agreement.  3. Attached hereto as Exhibit B is the completed Commissioning Data Sheet for each Wind Turbine that has achieved Commissioning Completion.  4. The person signing below is authorized to submit this form to Buyer for and on behalf of Supplier.  SUPPLIER: Vestas-American Wind Technology, Inc., a California corporation  By: ____________________________  Name: ____________________________  Title: ____________________________  Date: ____________________________    Buyer to cross through one (1) of the following statements:  A. Buyer agrees that Commissioning Completion has been achieved with respect to the enumerated Wind Turbine(s) and related components as set forth herein.  B. Buyer does not agree that Commissioning Completion has been achieved with respect to the enumerated Wind Turbine(s) and related components as set forth herein due to the omissions, liens or defects listed below and/or the incomplete nature of the specified portions of the Equipment Supply Obligations listed below:    .  The person signing below is authorized to submit this form to Supplier and on behalf of Buyer.  ACCEPTED BY BUYER: Madison Gas and Electric Company, a Wisconsin corporation  By: ____________________________  Name: ____________________________  Title: ____________________________  Date: ____________________________    Exhibit A  Completed Commissioning Completion Checklist   Exhibit B  Commissioning Data Sheet    WTG Model:
        
        Serial No.:WTG address:
        
        Pad No.:Buyer:Address:City/Country:Telephone No.:Operation Manager:Address:Telephone No.:Vestas Service Site
            Representative:Address:Telephone No.:                 MAIN SPECIFICATIONSRotor diameter, m:Tower height, m:Rated output, main generator, kW:  IDENTIFICATION NUMBERSSerial No.:Year of Manufacture:Nacelle No.:Tower No.:  CONTROLLERTransformer.:Switch Gear Manufacture:Switch Gear Serial:Phase Compensation.:Controller (CPU) unit:UPS.:  BLADESManufacturer:Type:Serial Nos.:Weight, kg per blade:Blade bolt type :
        Lot\Batch No.:   HUBSerial No:Hub bolt type:
        Lot\Batch No.:  GEARManufacturer:Type:Serial No.:Interchange Ratio:Quantity of oil, ltr.:Weight incl. oil, kg:  GENERATORManufacturer:Type:Serial No.:Rotational speed:Rated output, MW:Protection class:Thermal protection:Weight, kg:    READING OF METERS AND HOUR COUNTER AT COMMISSIONINGHour counter, turbine OK / run, hours:Hour counter, gen. 1, hours:  DATES OF PERFORMANCESInstallation start, date:Turbine connected to grid, date:
 Exhibit F.3.9  Form of Delayed Commissioning Completion Certificate    DATE:  1. Supplier has delivered this completed Delayed Commissioning Completion Certificate to Buyer on the above date.  Capitalized terms used but not defined herein shall have the meanings set forth in that certain Wind Turbine Supply Agreement, dated as of September 29, 2006 (the Agreement), by and between Madison Gas and Electric Company, a Wisconsin corporation (Buyer), and Vestas-American Wind Technology, Inc., a California corporation (Supplier). 2. Pursuant to Section 4.2.4 of the Agreement, Supplier hereby certifies and represents that [insert number] Wind Turbine(s) have not been Commissioned within sixty (60) days following the date of the Delivery Certificate or Delayed Delivery Certificate, as applicable, due to an Excusable Event. 3. The person signing below is authorized to submit this Delayed Commissioning Completion Certificate to Buyer for and on behalf of Supplier.  Vestas-American Wind Technology, Inc.,
            a California corporationBy:
            Name:
            Title:Date:
 Exhibit F.3.10  Form of Final Completion Certificate   Date of Final Completion:  _____________________  1. Reference is made to the Wind Turbine Supply Agreement, dated as of September 29, 2006 (the Agreement), by and between Madison Gas and Electric Company, a Wisconsin corporation (Buyer), and Vestas-American Wind Technology, Inc., a California corporation (Supplier).  Capitalized terms used but not defined herein shall have the meanings set forth in the Agreement.  2. The undersigned, Supplier, does hereby certify and represent as follows to Buyer: a. All of the Wind Turbines have achieved Commissioning Completion or, in the event this Final Completion Certificate is submitted pursuant to Section 4.2.5 of the Agreement, (a) Commissioning Completion of Wind Turbine No. ______ has not been achieved within ninety (90) days following the applicable anticipated Commissioning Completion Date set forth on the Project Schedule, and (b) all of the other conditions to Final Completion set forth in Section 7.3 of the Agreement have been satisfied with respect to the Wind Turbines that have achieved Commissioning Completion; b. A Punch List for the Equipment Supply Obligations (or, in the event this Final Completion Certificate is submitted pursuant to Section 4.2.5 of the Agreement, the Wind Turbines that have achieved Commissioning Completion) has been prepared and agreed upon between Buyer and Supplier; and c. All Supplier Documents and Deliverables required to be delivered under the Agreement to Buyer by Supplier on or before Final Completion have been delivered to Buyer. 3. The person signing below is authorized to submit this Final Completion Certificate to Buyer for and on behalf of Supplier.  SUPPLIER: Vestas  American Wind Technology, Inc., a California corporation  By: _______________________ Name: _____________________ Title: ______________________ Date: ______________________   Buyer to cross through one (1) of the following statements:  A. Buyer agrees that (i) Final Completion has been achieved or (ii) in the event this Final Completion Certificate is submitted pursuant to Section 4.2.5 of the Agreement, Supplier is entitled to the pro rata portion of the Final Completion payment allocable to the Wind Turbines that have achieved Commissioning Completion.  B. Buyer does not agree that (i) Final Completion has been achieved or (ii) in the event this Final Completion Certificate is submitted pursuant to Section 4.2.5 of the Agreement, Supplier is not entitled to the pro rata portion of the Final Completion payment allocable to the Wind Turbines that have achieved Commissioning Completion, in either case due to the omissions, liens or defects listed below and/or the incomplete nature of the specified portions of the Equipment Supply Obligations listed below:    .  The person signing below is authorized to submit this form to Supplier for and on behalf Buyer.  ACCEPTED BY BUYER: Madison Gas and Electric Company, a Wisconsin corporation  By: ____________________________  Name: ____________________________  Title: ____________________________  Date: ____________________________
 Exhibit F.3.11  Form of Delayed Final Completion Certificate    DATE:  1. Supplier has delivered this completed Delayed Final Completion Certificate to Buyer on the above date.  Capitalized terms used but not defined herein have the meanings set forth in that certain Wind Turbine Supply Agreement, dated as of September 29, 2006 (the Agreement), by and between Madison Gas and Electric Company, a Wisconsin corporation (Buyer), and Vestas-American Wind Technology, Inc., a California corporation (Supplier). 2. Pursuant to Section 4.2.5 of the Agreement, Supplier hereby certifies and represents that Final Completion could not be achieved within sixty (60) days following the date of the final Commissioning Completion Certificate or Delayed Commissioning Completion Certificate, as applicable, due to an Excusable Event. 3. The person signing below is authorized to submit this Delayed Final Completion Certificate to Buyer for and on behalf of Supplier.  Vestas-American Wind Technology, Inc.,
            a California corporationBy:
            Name:
            Title:Date:
 Exhibit F.3.12  SCADA Substantial Completion Checklist   ________________________________________________________________________________  Contents OBJECTIVES SCADA DATA PATH TEST CHECK AND VERIFICATION OF THE SCADA SYSTEM CONFIGURATION Objective Methodology SCADA DATA PATH TEST SUMMARY CHECK OF THE FUNCTIONALITY OF THE FIBRE OPTIC INFRASTRUCTURE Objective Methodology FIBRE OPTIC INFRASTRUCTURE TEST SUMMARY SCADA FUNCTIONALITY TEST Objective and methodology TEST AND COMMISSIONING CERTIFICATE Operational data presentation Operational commands Presentation of instant data from other park units Calculations and presentations based on collected data User management Additional checks Test comments   Objectives  The SCADA system consists of standard units and equipment combined in a project specific layout and fibre optic infrastructure. All standard units and equipment will be factory tested and inspected prior to delivery and commissioning on site in accordance with Vestas quality assurance system. The site specific supplies, systems and functions that are not tested prior to installation and commissioning is subject to a project specific SCADA test on site.  The overall objectives for testing the SCADA system are the following:  SCADA Data Path Test: · To demonstrate that the SCADA system configuration as supplied on site is correct · To demonstrate the functionality of the fibre optic infrastructure SCADA Functionality Test: · To demonstrate the functionality of the SCADA system   SCADA Data Path Test  The SCADA Data Path Test consists of two parts: · Check and verification of the SCADA system configuration · Check of the functionality of the fibre optic infrastructure  Check and verification of the SCADA system configuration  Objective  Correct project specific label and identification (ID) of each unit i.e. turbine, meteorology station, grid station etc. in the SCADA system is checked and verified.  Methodology  The correct system configuration of the project is demonstrated by simulating an event in a turbine and subsequently check that the event is recorded correctly in the correct unit. Wind turbines  · An event is initiated in the turbine in question, e.g.: manual stop/start by e.g. activating the service key · The SCADA error log is checked for correct error identification and turbine identification · A temperature signal such as the tower base temperature is disconnected resulting in an invalid temperature value being entered into the 10-minute database · The invalid temperature is maintained for a complete 10-minute period · In the SCADA 10-minute database the turbine identification in question and the presence of invalid temperature data are checked and verified. Meteorology stations and grid stations  · The connection between the unit and the SCADA network or the connection between sensors and the meteorology station controller is interrupted · The disconnection is maintained for a complete 10-minute period · In the SCADA 10-minute database the unit identification and the presence of invalid data are checked and verified. Scope of tests One turbine on each loop and all Meteorology and Grid stations units of the wind power plant must be checked and verified for correct labelling and ID.   SCADA data path test summary  WTG identifier  Initiated event. Initiated signal...  Yes
        NoCorrect turbine/error identification in error logCorrect turbine/signal identification in 10-minute database   Met Station identifier.  Initiated signal...  Yes
        NoCorrect met. Station/signal identification in 10-minute database   Grid Station identifier..  Initiated signal...  Yes
        NoCorrect grid station identification in 10-minute database  Test results recorded by: Test results approved by:  ________________________________ ________________________________ Supplier Customer  Date: _____________________ Date: _____________________    Check of the functionality of the fibre optic infrastructure  Objective  High-quality workmanship when the SCADA installed on site is a prerequisite for a correct and accurate function of the SCADA communication system. When the SCADA system is installed, focus is on correct connection of each turbine, meteorology station, grid station etc. to the SCADA system via the fibre optic communication loops The objective of the fibre optic infrastructure test is to verify the functionality of the signal path from all turbines and other SCADA units supplied by the Supplier, as follows:  · Fibre optic connections in each turbine · Fibre optic communication loops · Connections at the SCADA server switch  Methodology  The fibre optic infrastructure is checked by monitoring each unit in the SCADA Vestas Online Business program. To verify that communication with e.g. a turbine in the wind power plant takes place, the "Park Event Overview" window in Vestas Online Business is started. The turbine is monitored over a period of time enabling values such as wind speed to show variation. Wind speed data should be available and changing for all turbines.  In order to verify variation and thus communication to each unit, the wind speed data are chosen as the sample value for wind turbines and meteorology stations. For grid stations, the active power value should be chosen.    Fibre optic infrastructure test summary  WTG identifier   Yes
        NoCommunication to wind turbine   Met Station identifier.   Yes
        NoCommunication to meteorology station   Grid Station identifier.   Yes
        NoCommunication to grid station   Test results recorded by: Test results approved by:  ________________________________ ________________________________ Supplier Customer  Date: _____________________ Date: _____________________     SCADA Functionality Test  Objective and methodology  The objective of the SCADA Site Acceptance Test procedure is to verify the functionalities of the SCADA system when it has been installed and commissioned on site. This includes presentation of online data from a turbine, grid and meteorology station, remote operation of a turbine and presentation of reports based on collected data from the database.  The following document is the Test and Commissioning Certificate for the Vestas Online Business Server SCADA system.  Each line in the checklists with test-numbers is checked off in the Check column after completion of each test. Each sheet is signed by the person who has made the records on the sheet and by a customer representative assisting the test and commissioning of the SCADA system.  If there are any comments during the test, these can be listed on the last page with a reference to the test in question.  A summary of the test result is written on the cover page - this will indicate if any particular observations or interpretations were made during the test.  The commissioning certificate is the output of the test - and is signed by the Supplier and/or his representatives and the Customer and/or his representatives participating in the test.     Test and Commissioning Certificate  Project: ____________________________  System under Test: Vestas Online Business Server System  Date of Test: ____________________________   The undersigned hereby accept being participants in the functionality test of the SCADA system.  The main functions of the SCADA were tested according to attached pages, and no deficiencies or malfunctions other than mentioned in the list below were detected or observed.  Date
        Signature
        Position
        Company  Comments:Recorded by:
        Approved by:Date:
        Date:     Operational data presentation  The objective is to verify that online operational data are being transferred from different parts of the wind turbine.  Select a reference turbine to conduct the reference measurements.  Location: Control building and selected reference turbine.  Selected reference turbine  In the Menu item columns below, the procedure to access the menu item is described. One person should be in the Control building and another one located in the turbine. Using mobile phones or walkie-talkies, they should verify that the readings from the turbine display in the turbine match the readings in the SCADA system.  RCOT = Use the mouse to Right-Click On the selected reference turbine.  Test
        Description
        Menu item
        CheckWTG Instant data
        RCOT ® Present1-1
        Status information
        ®Status1-2
        Temperatures
        ®Temperature1-3
        Grid information
        ®Grid1-4
        Production figures
        ®Production1-5
        Operation counters
        ®CountersWTG Logbooks
        RCOT ® Logbooks1-7
        Alarm logbook
        ®Alarm logbook1-8
        Warning logbook *
        ®Warning logbookRecorded by:
        Approved by:Date:
        Date:  *Note: Logbooks do not apply to TAC-II turbines.   Operational commands  The objective is to verify that commands are being transferred to the wind turbine.  Location: Control building  Be aware that the following test will interact with the operation of the turbine.  Test
        Description
        Menu item
        CheckWTG Commands
        RCOT ® Commands2-1
        Start turbine
        ®Start turbine2-2
        Stop turbine
        ®Stop turbine2-3
        Reset alarm-code in turbine
        ®Reset alarm in turbineRecorded by:
        Approved by:Date:
        Date:    Presentation of instant data from other park units  The objective is to verify that communication with grid and meteorology stations is taking place.  Location: Control building and at the selected park units.  Selected reference grid stationSelected reference meteorology station  RCOG = Use the mouse to Right-Click On the selected reference Grid station RCOM = Use the mouse to Right-Click On the selected reference meteorology station  Test
        Description
        Menu item
        CheckGrid station instant data
        RCOG ® Present3-1
        Status information
        ®AnalogueMet station instant data
        RCOM ® Present3-2
        Status information
        ®AnalogueRecorded by:
        Approved by:Date:
        Date:  The above-mentioned park units may not be applicable in all wind power plants.    Calculations and presentations based on collected data  The objective is to verify different reports generated on the basis of collected data.  Location: Control building  RCOPC = Use the mouse to Right-Click On the site PC  Test
        Description
        Menu item
        CheckDatabase
        RCOPC ® Database4-1
        Power curve presentation;
            -
            Power curve with no corrections.
            -
            Using meteorology station data correction.
            -
            Using correction of temperature & pressure.
            -
            Using meteorology station data and temperature & pressure.
            Scatter curve
            -
            Scatter curve with 10 min dots from turbine
            Wind curve presentation
            -
            Present turbine wind data
            -
            Present Met station wind data
        ®Power curve / Wind curve4-2
        Wind / Energy rose
            -
            Present a wind rose
            -
            Present a energy rose
        ®Wind / Energy rose4-3
        Present 10 min. data
            -
            Check that collected 10min data are available from the Vestas Online Business client connected to the Vestas Online Business Server database system.
            -
            Verify that data are collected from turbines, met- and grid-stations.
        ®Collected data viewerLogbooks
        RCOPC ® Logbooks4-4
        Park log
        ®Park log4-5
        Statistics
        ®StatisticsRecorded by:
        Approved by:Date:
        Date:    User management  The objective is to verify that new users can be created and their rights can be secured.  Location: Control building and selected reference turbine.  Test
        Description
        Menu item
        CheckUser management
        RCOPC ® Misc5-1
        Create a new user with access level 1 and verify that the user can only access online information (instant values) from the turbines.
            Verify that the user cannot send commands to the turbines.
        User management5-2
        Create a new user with access level 3 and verify that the user can access online information (instant values) and send commands to the turbines.
        User managementRecorded by:
        Approved by:Date:
        Date:    Additional checks  The objective is to verify that the system is running satisfactorily.  Location: Control building  Test
        Description
        CheckUPS (Uninterruptible Power Supply)6-1
        Disconnect the power to the UPS unit - simulating loss of power to the SCADA system.
            -
            Check that the power loss is logged in the system log.
            -
            Check that the system reboots again and return to normal operation after the power has been re-connected.Check the data integrity of collected data6-2
        Verify that 10-min data are being collected and that no losses have occurred.
            The 10-min data can be viewed from the Data Collection Viewer.
            The data integrity should be verified over a specified period of at least 14 days of normal operation.Vestas Online Business dial-in verification6-3
        Verify that it is possible to dial in with Vestas Online Business and operate the wind power plant remotely via a regular modem connection.Recorded by:
        Approved by:Date:
        Date:  The above tests are subject to changes, as the Vestas Online Business product is developed with further enhancements.  Test comments  If one or more test needs further explanation (e.g. not possible, not accessible or similar) write down the test number and a description of the issue.  Test
        Description
        InitRecorded by:
        Approved by:Date:
        Date:
 Exhibit F.3.13  Form of SCADA Completion Certificate   Date of SCADA Completion: ________________  1. Reference is made to the Wind Turbine Supply Agreement, dated as of September 29, 2006 (the Agreement), by and between Madison Gas and Electric Company, a Wisconsin corporation (Buyer), and Vestas-American Wind Technology, Inc., a California corporation (Supplier).  Capitalized terms used but not defined herein shall have the meanings set forth in the Agreement.  2. The undersigned, Supplier, does hereby certify and represent to Buyer that each item on the SCADA Completion Checklist has been satisfied in accordance with the Agreement.  3. The person signing below is authorized to submit this SCADA Completion Certificate to Buyer for and on behalf of Supplier.  SUPPLIER: VestasAmerican Wind Technology, Inc., a California corporation   By: ______________________________ Name: ___________________________ Title: ____________________________ Date: ____________________________   Buyer to cross through one (1) of the following statements:  A. Buyer agrees that SCADA Completion has been achieved.  B. Buyer does not agree that SCADA Completion has been achieved due to the omissions, liens or defects listed below and/or the incomplete nature of the specified portions of the Equipment Supply Obligations listed below:      The person signing below is authorized to submit this form to Supplier for and on behalf Buyer.  ACCEPTED BY BUYER: Madison Gas and Electric Company, a Wisconsin corporation  By: ____________________________  Name: ____________________________  Title: ____________________________  Date: ____________________________