1

Vipin Sumani, PE Process Environmental Engineer http://www.aecom.com/ 

### Sumani, Vipin

From: Kofeldt, Thomas J (WT) [Thomas.Kofeldt@siemens.com] Sent: Monday, January 11, 2010 10:20 AM To: Sumani, Vipin Cc: Venkatesh, M; Brian J. Boyson; Brian A. Boyson Subject: Siemens Budget File No. 95633, AECOM (Westford, MA) , Great Lakes Region Project, Update on the Traveling Water Screen Quote

Vipin,

Please find below Budget Prices for One (1) Siemens Thru-Flow Traveling Water Screen and One (1) Contr ol Panel.

Given : Total Flow: 1,000 GPM Low Water Depth: 8'-0"

Results : Type of TWS: Siemens Thru-Flow Traveling Water Screen Total Flow: 1,00 0 GPM Number of TWS: One (1) Flow per TWS: 1,000 GP M Type of Tray/Basket: High Stre ngth Composite (HSC) Trays, 24" Pitch Screen Cloth Openings: 3/8" Square Openings Screen Cloth Wire Diameter: 14 GA. (0.080" Dia.) Tray/Basket Width: 2'-0" Required Well Width per TWS: 3'-2" Well Depth: 23'-0 " (Assumed) Screen Centers: 24'-0"

Velocity Through The Screen Cloth/Mesh at 1,000 GPM , Low Water Depth of 8'-0", at 100% Clean Condition : 0.29 FPS

One (1) Siemens Thru-Flow Traveling Water Screen, 2 '-0" Tray Width x 24'-0" Centers; 2-Post; Roll-Arou nd Boot Terminal; Shaft-Mount Drive.

• Carbon Steel w/ Potable Paint Construction

• High Strength Composite (HSC) Trays w/ 14 GA. (0.0 80" Dia.) 304 SS Screen Cloth w/ 3/8" Sq. Openings

• Non-Metallic Seal Plates

• Carbon Steel Sidebars / 8620 CFS CH Pins, Bushings , and Rollers Non-Lube Tray Chain

• 1.0 H.P., 1800 RPM, 460V/3PH/60Hz, TEFC Motor

• Shaft Mount Drive

• Carbon Steel "U" Style Spray Header w/ Flush Valve and Delrin Nozzles

• Carbon Steel Headshaft Sprockets w/ Hardened SS To oth Inserts

• Carbon Steel Headshaft

• Thordon Bushed Headshaft Bearings

• Carbon Steel Roll-Around Boot Section

• 18-8 SST Cloth To Tray, Tray To Chain and Frame Fa steners

• FRP Front Housing w/ Bomar Doors On Each Side, FRP Rex Style Rear Maintenance Housing

• One (1) Pressure Switch per TWS, One (1) Electrica lly Actuated Valve per TWS

• Cast Iron Wall Guides

• Concrete Trough By Others

• (F.O.B. Factory, Freight Allowed To Jobsite)2

Vipin Sumani, PE Process Environmental Engineer http://www.aecom.com/ Budget Price: $110,000

One (1) NEMA 4X 304 SS Control Panel with Standard Ultrasonic Differential, Timer, and Manual Relay Lo gic Based Controls for One (1) Siemens Thru-Flow Traveling Wa ter Screens including Load Current Relay and Motor Starter for the Screen, (F.O.B. Factory, Freight Allowed To Jobsite ).
Budget Price: $19,800

Regards,

Tom Kofeldt

Thomas J. Kofeldt Sales Support Manager, Intake Products Siemens Water Technologies Corp. 100 Highpoint Drive, Suite 101 Chalfont, PA 18914 e-mail: thomas.kofeldt@siemens.com Direct Phone: (215) 712-7032 Fax: (215) 996-1136 www.water.siemens.com

Confidentiality Note: This e-mail message and any a ttachments to it are intended only for the named re cipients and may contain confidential information. I f you are not one of the intended recipients, please do not d uplicate or forward this e-mail message and immedia tely delete it from your computer.

From: Sumani, Vipin [mailto:vipin.sumani@aecom.com] Sent: Monday, January 04, 2010 3:27 PM To: Kofeldt, Thomas J (WT) Cc: Venkatesh, M Subject: RE: Update on the traveling water screen quote



### Hi Tom,

Yes, it is a budget price. The price and the detail s we require should be the same type that was given to us previously. Location is great Lakes region and the client is c onfidential for now.

Thanks.

Vipin Sumani, PE

978-589-3207

From: Kofeldt, Thomas J (WT) [mailto:Thomas.Kofeldt@siem ens.com] Sent: Monday, January 04, 2010 3:14 PM To: Sumani, Vipin Cc: Venkatesh, M Subject: RE: Update on the traveling water screen quote

Thanks Vipin.3

Vipin Sumani, PE Process Environmental Engineer http://www.aecom.com/ I have a couple of questions. Are you still lookin g for a Budget Price? Also, what is the name and l ocation of the project where the screen will be used?

Regards,

Tom

Thomas J. Kofeldt Sales Support Manager, Intake Products Siemens Water Technologies Corp. 100 Highpoint Drive, Suite 101 Chalfont, PA 18914 e-mail: thomas.kofeldt@siemens.com Direct Phone: (215) 712-7032 Fax: (215) 996-1136 www.water.siemens.com

Confidentiality Note: This e-mail message and any a ttachments to it are intended only for the named re cipients and may contain confidential information. I f you are not one of the intended recipients, please do not d uplicate or forward this e-mail message and immedia tely delete it from your computer.

From: Sumani, Vipin [mailto:vipin.sumani@aecom.com] Sent: Monday, January 04, 2010 3:02 PM To: Kofeldt, Thomas J (WT) Cc: Venkatesh, M Subject: Update on the traveling water screen quote



### Hi Tom,

As per our conversation over the phone, I am attac hing the traveling water screen quote provided by Glenn Zetterberg in year 2002. The client has come back to us and asked for an updated quote for the year 2 010.

It would be great if you could provide us the quote by January 16 th 

### , 2010.

Thanks.

Vipin Sumani, PE

978-589-3207

<<E - Filter.pdf>>