Vipin Sumani, PE 1

Process Environmental Engineer

http://www.aecom.com/

Sumani, Vipin

From: Kofeldt, Thomas J (WT) [Thomas.Kofeldt@siemens.com]

Sent: Monday, January 11, 2010 10:20 AM

To: Sumani, Vipin

Cc: Venkatesh, M; Brian J. Boyson; Brian A. Boyson

Subject: Siemens Budget File No. 95633, AECOM (Westford, MA), Great Lakes Region Project, 

Update on the Traveling Water Screen Quote

Vipin,

 

Please find below Budget Prices for One (1) Siemens Thru-Flow Traveling Water Screen and One (1) Control Panel.

 

 

Given: 

Total Flow: 1,000 GPM 

Low Water Depth: 8'-0"

 

Results: 

Type of TWS: Siemens Thru-Flow Traveling Water Screen 

Total Flow: 1,000 GPM 

Number of TWS: One (1) 

Flow per TWS: 1,000 GPM 

Type of Tray/Basket: High Strength Composite (HSC) Trays, 24" Pitch 

Screen Cloth Openings: 3/8" Square Openings 

Screen Cloth Wire Diameter: 14 GA. (0.080" Dia.) 

Tray/Basket Width: 2'-0" 

Required Well Width per TWS: 3'-2" 

Well Depth: 23'-0" (Assumed) 

Screen Centers: 24'-0" 

 

Velocity Through The Screen Cloth/Mesh at 1,000 GPM, Low Water Depth of 8'-0", at 100% Clean Condition: 0.29 FPS

 

 

One (1) Siemens Thru-Flow Traveling Water Screen, 2'-0" Tray Width x 24'-0" Centers; 2-Post; Roll-Around Boot 

Terminal; Shaft-Mount Drive. 

• Carbon Steel w/ Potable Paint Construction 

• High Strength Composite (HSC) Trays w/ 14 GA. (0.080" Dia.) 304 SS Screen Cloth w/ 3/8" Sq. Openings 

• Non-Metallic Seal Plates 

• Carbon Steel Sidebars / 8620 CFS CH Pins, Bushings, and Rollers Non-Lube Tray Chain 

• 1.0 H.P., 1800 RPM, 460V/3PH/60Hz, TEFC Motor 

• Shaft Mount Drive 

• Carbon Steel "U" Style Spray Header w/ Flush Valve and Delrin Nozzles 

• Carbon Steel Headshaft Sprockets w/ Hardened SS Tooth Inserts 

• Carbon Steel Headshaft 

• Thordon Bushed Headshaft Bearings 

• Carbon Steel Roll-Around Boot Section 

• 18-8 SST Cloth To Tray, Tray To Chain and Frame Fasteners 

• FRP Front Housing w/ Bomar Doors On Each Side, FRP Rex Style Rear Maintenance Housing 

• One (1) Pressure Switch per TWS, One (1) Electrically Actuated Valve per TWS 

• Cast Iron Wall Guides 

• Concrete Trough By Others 

• (F.O.B. Factory, Freight Allowed To Jobsite) 
Vipin Sumani, PE 2

Process Environmental Engineer

http://www.aecom.com/

Budget Price: $110,000 

 

 

One (1) NEMA 4X 304 SS Control Panel with Standard Ultrasonic Differential, Timer, and Manual Relay Logic Based 

Controls for One (1) Siemens Thru-Flow Traveling Water Screens including Load Current Relay and Motor Starter for the 

Screen, (F.O.B. Factory, Freight Allowed To Jobsite). 

 

Budget Price: $19,800

 

 

Regards,

 

Tom Kofeldt

Thomas J. Kofeldt 

Sales Support Manager, Intake Products 

Siemens Water Technologies Corp. 

100 Highpoint Drive, Suite 101 

Chalfont, PA 18914 

e-mail: thomas.kofeldt@siemens.com 

Direct Phone: (215) 712-7032 

Fax: (215) 996-1136 

www.water.siemens.com 

Confidentiality Note: This e-mail message and any attachments to it are intended only for the named recipients and may contain confidential information. If you are 

not one of the intended recipients, please do not duplicate or forward this e-mail message and immediately delete it from your computer.

From: Sumani, Vipin [mailto:vipin.sumani@aecom.com] 

Sent: Monday, January 04, 2010 3:27 PM 

To: Kofeldt, Thomas J (WT) 

Cc: Venkatesh, M 

Subject: RE: Update on the traveling water screen quote

Hi Tom, 

Yes, it is a budget price. The price and the details we require should be the same type that was given to us previously. 

Location is great Lakes region and the client is confidential for now. 

Thanks. 

Vipin Sumani, PE 

978-589-3207 

From: Kofeldt, Thomas J (WT) [mailto:Thomas.Kofeldt@siemens.com] 

Sent: Monday, January 04, 2010 3:14 PM 

To: Sumani, Vipin 

Cc: Venkatesh, M 

Subject: RE: Update on the traveling water screen quote 

Thanks Vipin.

 
Vipin Sumani, PE 3

Process Environmental Engineer

http://www.aecom.com/

I have a couple of questions. Are you still looking for a Budget Price? Also, what is the name and location of the project 

where the screen will be used?

 

 

Regards,

 

Tom

 

Thomas J. Kofeldt 

Sales Support Manager, Intake Products 

Siemens Water Technologies Corp. 

100 Highpoint Drive, Suite 101 

Chalfont, PA 18914 

e-mail: thomas.kofeldt@siemens.com 

Direct Phone: (215) 712-7032 

Fax: (215) 996-1136 

www.water.siemens.com 

Confidentiality Note: This e-mail message and any attachments to it are intended only for the named recipients and may contain confidential information. If you are 

not one of the intended recipients, please do not duplicate or forward this e-mail message and immediately delete it from your computer.

From: Sumani, Vipin [mailto:vipin.sumani@aecom.com] 

Sent: Monday, January 04, 2010 3:02 PM 

To: Kofeldt, Thomas J (WT) 

Cc: Venkatesh, M 

Subject: Update on the traveling water screen quote

Hi Tom, 

As per our conversation over the phone, I am attaching the traveling water screen quote provided by Glenn 

Zetterberg in year 2002. The client has come back to us and asked for an updated quote for the year 2010. 

It would be great if you could provide us the quote by January 16th , 2010. 

Thanks. 

Vipin Sumani, PE 

978-589-3207

<<E - Filter.pdf>>