From: Robert Berman [mailto:bermaneconomics@gmail.com] 

Sent: Tuesday, November 15, 2011 1:48 PM 

To: Rosenstock, Steven 

Cc: Steve Nadel; Bruce R Hirsch; Robert Berman; John Caskey; Eric.Petersen@aksteel.com; 

jerry.schoen@aksteel.com; Maxine (EMAB) Savitz; mhyland@appanet.org; 

Raymond.Polinski@ATImetals.com; maheshsampat@bellsouth.net; tpetrosino@carolina.rr.com; 

dbrender@cda.copper.org; James.Lass@cleco.com; chris.brown@cogentpowerinc.com; 

frank.guilbault@cogentpowerinc.com; ted.johnstone@cogentpowerinc.com; Aaron Meyers; Antonio 

Trujillo; Jack C Moore; Jerry L Corkran; tballo@earthjustice.org; carlosgsiqueiros@eaton.com; 

eduardorobles@eaton.com; Emily (CONTR) Marchetti; Jeremiah (CONTR) Freeman; Jim Raba; John 

Cymbalsky; DYoung@energy-solution.com; rick.anderson@faypwc.com; bsmith@federalpacific.com; 

rgreeson@federalpacific.com; carlos.gaytan@ge.com; artrosenfeld@gmail.com; 

greg.coulter405@gmail.com; ned.efbrush@gmail.com; Richard Parker; Paul.Ryan@hitmet.com; 

jhodge@howard.com; Daniel Cohen; Phil Hopkinson; cabolduc@lbl.gov; gjrosenquist@lbl.gov; 

kcoughlin@lbl.gov; ScottB@LVMetals.com; dave.millure@metglas.com; kwinder@mleainc.com; 

jrossetti@mlgw.org; Brian Coffey; Caitlin Johnson; Matthew Nardotti; Michael Rivest; Zhimei Luo; Jim 

Creevy; mwaltner@nrdc.org; rroy@nrdc.org; robert.saint@nreca.coop; Teckman@nwcouncil.org; 

vijay.tendulkar@onyxpower.com; gbf1@pge.com; chuck.simmons@pgnmail.com; 

ahofmann@publicpower.org; pkumar@publicpower.org; adelaski@standardsASAP.org; 

jmauer@standardsasap.org; wes.patterson@us.abb.com; chad.kennedy@us.schneider-electric.com; 

thomas.patzner@us.schneider-electric.com; charlied@uus.org 

Subject: Re: Negotiated Rulemaking - Distribution Transformers Teleconference 

Steve, 

I believe Steve Nadel is correct on that. The primary objective is to save energy (kWh), not 

capacity (kW). There is also a kW savings benefit that is not being captured in terms of the (1) 

reduced demand on current generating capacity and (2) the delay in constructing new power 

plants. The first is measured by the forward capacity market more and more RTOs are creating. 

See PJM manual 18B for how even DSM and conservation can be sold forward. Reduction in 

core losses may be more valuable here than reductions in coil losses as the former is 24x7 and 

the latter disappears with summer AC loads (particularly here in DC). Last I looked (some time 

ago) PJM capacity was selling for $167 / mW day, with the 3 year forward in excess of $250. 

Since more and more utilities are deregulating generation, the capacity savings accrues entirely 

to the shareholder outside the regulatory environment. The construction delay may be 

approximated at the long-run marginal cost, including capacity, and the discounted value of the 

temporal shift. 

Regards,

Robert A. Berman, Principal

Berman Economics

www.BermanEconomics.com

1915 Grand Court

Vienna, VA 22182

703‐281‐0490
703‐655‐8398 (cell)

BermanEconomics@gmail.com

On Nov 15, 2011, at 1:25 PM, Rosenstock, Steven wrote: 

Steve,

In terms of your e-mail, I don’t think that talking about cost per kW is “misleading”, as 

you put it. While reducing transformer losses will affect baseload, as you said, since 

transformer loading is typically at 25-50% based on data presented, there are times or 

situations where some transformers will be loaded at more than 50%, sometimes 

significantly more, and those times are likely to coincide with peak loads (e.g., summer 

AC loads). Since some of the higher efficiency transformers will actually have 

significantly higher coil losses, there tends to be a “break even” point of transformer 

loading where above a certain transformer % loading, the “high efficiency” transformer 

will have higher Wattage losses, and therefore higher costs, than the “standard 

efficiency” transformer.

In terms of competition, I agree with Bruce Hirsch that we want competitive markets. 

However, the DOE analysis that was dated November 4, 2011, and entitled “Draft LifeCycle Cost, Payback Period, and National Impacts Analysis Results for Medium Voltage 

Liquid-Immersed Transformers” (slides 13-15) showed that in the Life Cycle Cost 

analysis, amorphous core units would be the only ones to be purchased at the following 

efficiency levels:

Design Line 1 – EL 2

Design Line 2 – EL 1 

Design Line 3 – EL 2 (but 80.7% amorphous and 19.3% ZDMH at EL 1)

Design Line 4 – EL 2 (but 91.2% ZDMH and 8.8% amorphous at EL 1)

Design Line 5 – EL 2 (but 96.1% amorphous and 3.9% ZDMH at EL 1)

In fact, according to the DOE analysis, only for Design Line 1 at EL 1 does M3 steel 

have a competitive chance (85% of units). M2, and M4 steels are not chosen at EL 1 

for all Design Lines. 

So right now, it looks like the higher EL levels you are proposing strongly favors 

amorphous core units over all other competitors.

In terms of a “revised DOE analysis”, I thought that DOE / LBNL / Navigant were pretty 

much finished with all of their analytical work. What kind of “new information” could 

possibly reduce the costs of certain transformers by 40-80% to be “competitive?
Steve Rosenstock

Manager, Energy Solutions

Edison Electric Institute

srosenstock@eei.org

202-508-5465

<image001.gif>

From: Steve Nadel [mailto:snadel@aceee.org] 

Sent: Tuesday, November 15, 2011 8:58 AM 

To: Bruce R Hirsch; Robert Berman; John Caskey 

Cc: Eric.Petersen@aksteel.com; jerry.schoen@aksteel.com; Maxine (EMAB) 

Savitz; mhyland@appanet.org; Raymond.Polinski@ATImetals.com; maheshsampat@bellsouth.net; tpetro

sino@carolina.rr.com;dbrender@cda.copper.org; James.Lass@cleco.com; chris.brown@cogentpowerinc.c

om; frank.guilbault@cogentpowerinc.com; ted.johnstone@cogentpowerinc.com; Aaron Meyers; Antonio 

Trujillo; Jack C Moore; Jerry L 

Corkran; tballo@earthjustice.org; carlosgsiqueiros@eaton.com; eduardorobles@eaton.com; Emily 

(CONTR) Marchetti; Jeremiah (CONTR) Freeman; Jim Raba; John Cymbalsky; Rosenstock, 

Steven; DYoung@energysolution.com; rick.anderson@faypwc.com; bsmith@federalpacific.com; rgreeson@federalpacific.com; carl

os.gaytan@ge.com; artrosenfeld@gmail.com; greg.coulter405@gmail.com; ned.efbrush@gmail.com; 

Richard Parker; Paul.Ryan@hitmet.com; jhodge@howard.com; Daniel Cohen; Phil 

Hopkinson; cabolduc@lbl.gov; gjrosenquist@lbl.gov; kcoughlin@lbl.gov; ScottB@LVMetals.com; dave.mill

ure@metglas.com;kwinder@mleainc.com; jrossetti@mlgw.org; brian.coffey@navigant.com; caitlin.johnso

n@navigant.com; matthew.nardotti@navigant.com; mrivest@navigant.com; zhimei.luo@navigant.com; 

Jim 

Creevy;mwaltner@nrdc.org; rroy@nrdc.org; robert.saint@nreca.coop; Teckman@nwcouncil.org; vijay.ten

dulkar@onyxpower.com; gbf1@pge.com; chuck.simmons@pgnmail.com; ahofmann@publicpower.org;pk

umar@publicpower.org; adelaski@standardsASAP.org; jmauer@standardsasap.org; wes.patterson@us.ab

b.com; chad.kennedy@us.schneider-electric.com; thomas.patzner@us.schneiderelectric.com; charlied@uus.org

Subject: RE: Negotiated Rulemaking - Distribution Transformers Teleconference

 

Two comments. First, some comments have focused on just the market for M3 and amorphous steel. The 

two markets are linked -- we need competition between the two to keep the price of both in check. We 

don't want a standard that strongly favors one over the other. The revised DOE analysis on the mix 

between M3 and amorphous at different standard levels should help us to address this. Second, reducing 

transformer losses primarily affects baseload, not peak. So talking about cost per kW is misleading. An 

efficient transformer is energized for more than 8000 hours per year. The average DSM measure saves for 

about 3000 hours per year (although there is wide variation). If you want to compare, you'd need to 

compare levelized cost per kWh saved over the measure lifetime.

Steve 

>>> "Hirsch, Bruce R" <Bruce.R.Hirsch@bge.com> 11/15/2011 7:37 AM >>>

John’s points are well taken. Keep in mind that the DOE numbers indicate a payback at EL4 only if

amorphous steel is used. Thus, to assume that because it can be built using M3 steel, all is well, is totally
untrue.  In John’s auto analogy, at least the customer has a choice of spending the extra money. In our

case, the customer will have no choice.

We all also need to understand that there is not an infinite supply of money to spend on efficiency

improvements. By forcing utilities to spend money on improving transformer efficiencies, we may very

well be taking money out of other efficiency programs which have a much higher payback than what is

being proposed here.  In BGE’s case our package of efficiency programs cost us approximately $139 per

kilowatt saved. What is being proposed here is up to 100 times more costly. If BGE pulls back funds from

other efficiency programs to pay the high costs for transformer efficiencies, we would see a significant

decline in efficiency improvements overall.

                                                                                                                                                                                Bruce

                                                                                                                                                               

From: Caskey, John [mailto:Joh_Caskey@nema.org] 

Sent: Monday, November 14, 2011 3:14 PM 

To: Robert Berman; Hirsch, Bruce R 

Cc: 'Steve Nadel'; Phil Hopkinson; Eric.Petersen@aksteel.com; jerry.schoen@aksteel.com; Maxine 

(EMAB) 

Savitz; mhyland@appanet.org; Raymond.Polinski@ATImetals.com; maheshsampat@bellsouth.net;tpetrosi

no@carolina.rr.com; dbrender@cda.copper.org; James.Lass@cleco.com; chris.brown@cogentpowerinc.co

m; frank.guilbault@cogentpowerinc.com; ted.johnstone@cogentpowerinc.com; Aaron Meyers; Antonio 

Trujillo; Jack C Moore; Jerry L 

Corkran; tballo@earthjustice.org; carlosgsiqueiros@eaton.com; eduardorobles@eaton.com; Emily 

(CONTR) Marchetti; Jeremiah (CONTR) Freeman; Jim Raba; John 

Cymbalsky;srosenstock@eei.org; DYoung@energysolution.com; rick.anderson@faypwc.com; bsmith@federalpacific.com; rgreeson@federalpacific.com; carl

os.gaytan@ge.com; artrosenfeld@gmail.com; greg.coulter405@gmail.com;ned.efbrush@gmail.com; 

Richard Parker; Paul.Ryan@hitmet.com; jhodge@howard.com; Daniel 

Cohen; cabolduc@lbl.gov; gjrosenquist@lbl.gov; kcoughlin@lbl.gov; ScottB@LVMetals.com; dave.millure

@metglas.com;kwinder@mleainc.com; jrossetti@mlgw.org; brian.coffey@navigant.com; caitlin.johnson@

navigant.com; matthew.nardotti@navigant.com; mrivest@navigant.com; zhimei.luo@navigant.com; 

Creevy, 

Jim;mwaltner@nrdc.org; rroy@nrdc.org; robert.saint@nreca.coop; Teckman@nwcouncil.org; vijay.tendul

kar@onyxpower.com; gbf1@pge.com; chuck.simmons@pgnmail.com; ahofmann@publicpower.org;pkum

ar@publicpower.org; adelaski@standardsASAP.org; jmauer@standardsasap.org; wes.patterson@us.abb.c

om; chad.kennedy@us.schneider-electric.com; thomas.patzner@us.schneiderelectric.com; charlied@uus.org

Subject: RE: Negotiated Rulemaking - Distribution Transformers Teleconference

 

Robert

You continue to reference the ABB data presented by Wes Patterson as indicating that since a

transformer was sold at the EL3 or EL4 efficiency level that this level is cost effective. Specifically, you

state “Market sales data, however, is quite real. In this case it unambiguously says that the transformers

at EL4 are an economically reasonable choice ‐‐ the market has, in fact, selected that choice on multiple

occasions”. This is simply NOT TRUE.

Just because a person buys as Jaguar for $100k that gets 25 mpg in place of a $40k Cadillac that gets 20

mpg; does NOT mean that the $60k delta will ever be “economically reasonable” for the extra 5 mpg.
You seem to be assuming that all of the transformers purchased from ABB that meet the efficiency

levels were purchased for efficiency reasons. This is simply not fact. The fact is that one large

transformer manufacturer was able to produce distribution transformers at EL3 and EL4 using M3 steel.

To my knowledge, Wes did not state the price for these transformers. In addition, just because one

company can produce this product doesn’t mean that all transformer manufacturers can make this

product at this level using M3 steel.

My hope is that we can all understand the facts and the analysis results better over the next few weeks

so that we can negotiate a solution that benefits the consumers, the ratepayers, the manufacturers, the

environment, etc. I plan to stay at the table till the end of the negotiation process.  

Regards,

John

John F. Caskey, CEM

Assistant Vice President, Industry Operations

National Electrical Manufacturers Assoc. (NEMA)

1300 North 17th Street - Suite 1752 

Rosslyn, VA 22209

john.caskey@nema.org

703-841-3233 Voice

703-841-3333 FAX

703-350-6886 Cell

From: Robert Berman [mailto:bermaneconomics@gmail.com] 

Sent: Monday, November 14, 2011 1:19 PM 

To: Hirsch, Bruce R 

Cc: 'Steve Nadel'; Robert Berman; Phil 

Hopkinson; Eric.Petersen@aksteel.com; jerry.schoen@aksteel.com; Maxine (EMAB) 

Savitz; mhyland@appanet.org; Raymond.Polinski@ATImetals.com;maheshsampat@bellsouth.net; tpetrosi

no@carolina.rr.com; dbrender@cda.copper.org; James.Lass@cleco.com; chris.brown@cogentpowerinc.co

m; frank.guilbault@cogentpowerinc.com;ted.johnstone@cogentpowerinc.com; Aaron Meyers; Antonio 

Trujillo; Jack C Moore; Jerry L 

Corkran; tballo@earthjustice.org; carlosgsiqueiros@eaton.com; eduardorobles@eaton.com; Emily 

(CONTR) Marchetti; Jeremiah (CONTR) Freeman; Jim Raba; John 

Cymbalsky; srosenstock@eei.org; DYoung@energysolution.com; rick.anderson@faypwc.com; bsmith@federalpacific.com; rgreeson@federalpacific.com; carl

os.gaytan@ge.com;artrosenfeld@gmail.com; greg.coulter405@gmail.com; ned.efbrush@gmail.com; 

Richard Parker; Paul.Ryan@hitmet.com; jhodge@howard.com; Daniel 

Cohen; cabolduc@lbl.gov; gjrosenquist@lbl.gov; kcoughlin@lbl.gov;ScottB@LVMetals.com; dave.millure@

metglas.com; kwinder@mleainc.com; jrossetti@mlgw.org; brian.coffey@navigant.com; caitlin.johnson@n

avigant.com; matthew.nardotti@navigant.com; mrivest@navigant.com;zhimei.luo@navigant.com; 

Creevy, Jim; Caskey, 

John; mwaltner@nrdc.org; rroy@nrdc.org; robert.saint@nreca.coop; Teckman@nwcouncil.org; vijay.tend

ulkar@onyxpower.com; gbf1@pge.com;chuck.simmons@pgnmail.com; ahofmann@publicpower.org; pku

mar@publicpower.org; adelaski@standardsASAP.org; jmauer@standardsasap.org; wes.patterson@us.abb

.com; chad.kennedy@us.schneider-electric.com;thomas.patzner@us.schneiderelectric.com; charlied@uus.org

Subject: Re: Negotiated Rulemaking - Distribution Transformers Teleconference

 

Bruce, 
 

Those upfront transformer costs are compared to the fuel cost savings in the LCC approach. The 

discounting process values fuel cost saving in the future at less than the costs incurred today. The 

positive LCC means that that the efficiency advocates are not ignoring costs, but comparing 

them with benefits and finding that the consumer is better off and will be paying less. One does 

not, however, need to rely on the LBL analysis to see this. The ABB sales data shows M3 

transformers being delivered at EL4 efficiency. As a modeler, I am always skeptical of model 

results -- people do not live in computers and certainly not on in some of the back-of-theenvelope calculations that we have seen from others. Market sales data, however, is quite real. In 

this case it unambiguously says that the transformers at EL4 are an economically reasonable 

choice -- the market has, in fact, selected that choice on multiple occasions. 

 

To the extent that there are dug-in positions, again the evidence does not support that it is the 

efficiency advocates that are dug-in. Although EL4 is achievable and beneficial based both on 

market data and LBL analyses, the proponents of greater efficiency indicated a willingness to 

 compromise. It is certain representatives of the industry who have consistently said either no 

change, or a fractional change. It is those industry representatives who appear to be advancing 

the "my position or nothing" attitude. Although I happen to agree that substantial movement 

towards more efficient distribution systems, I also note that these are incredibly expensive 

meetings. We have a large number of very senior people devoting substantial time to the 

meetings, their preparation and non-trivial travel costs. These people have other things 

competing for their time. If you and others honestly believe that you cannot agree to a higher 

standard, and place no value on regulatory certainty, then let's not waste additional time and 

money. Let's just say that we gave it a good shot, cut our losses here, and make our respective 

cases to DOE outside the negotiation process and let DOE make it's own decision. I believe that 

they certainly have sufficient information to support their position in a February NOPR. I can't 

imagine what else they would need. 

Regards,

Robert A. Berman, Principal

Berman Economics

www.BermanEconomics.com

1915 Grand Court

Vienna, VA 22182

703‐281‐0490

703‐655‐8398 (cell)

BermanEconomics@gmail.com

 

On Nov 14, 2011, at 11:49 AM, Hirsch, Bruce R wrote: 
Steve,

I am disappointed with your approach to this assignment.

It appears that negotiation to you is defined as agreeing with your position ‐‐‐ or calling it off. It is

unfortunate that you believe the American public, especially in these trying economic times, should be

expected to foot the (very large) bill for more efficient transformers when it is still not certain that there

is value in doing so. You have clung to one suspect calculation that indicates there may be a payback ‐‐‐ 

in the distant future ‐‐‐ and only if all the assumptions being made pan out. You choose to ignore the

costs, not yet factored in, on US jobs, US businesses and the reliability of supply of an item so

desperately needed for our economy to expand.

This is not a “cut and dried” economic decision but is one that needs to be taken seriously for the major

impact it could have on the electric supply of the US and the financial position of the American public. If

DOE makes the final decision on this, I would expect them to do “due diligence” in considering all the

effects there decision would have on US businesses and the US economy.  

Let it be known that the Utility Industry has not pulled out of the negotiation process and will continue

to work with DOE to reach the right decision.

Bruce.  

From: Steve Nadel [mailto:snadel@aceee.org] 

Sent: Friday, November 11, 2011 2:16 PM 

To: Robert Berman; Phil Hopkinson 

Cc: Eric.Petersen@aksteel.com; jerry.schoen@aksteel.com; Maxine (EMAB) 

Savitz; mhyland@appanet.org; Raymond.Polinski@ATImetals.com; maheshsampat@bellsouth.net; 

Hirsch, Bruce 

R; tpetrosino@carolina.rr.com;dbrender@cda.copper.org; James.Lass@cleco.com; chris.brown@cogentpo

werinc.com; frank.guilbault@cogentpowerinc.com; ted.johnstone@cogentpowerinc.com; Aaron Meyers; 

Antonio Trujillo; Jack C Moore; Jerry L 

Corkran; tballo@earthjustice.org; carlosgsiqueiros@eaton.com; eduardorobles@eaton.com; Emily 

(CONTR) Marchetti; Jeremiah (CONTR) Freeman; Jim Raba; John 

Cymbalsky; srosenstock@eei.org; DYoung@energysolution.com; rick.anderson@faypwc.com; bsmith@federalpacific.com; rgreeson@federalpacific.com; carl

os.gaytan@ge.com; artrosenfeld@gmail.com; greg.coulter405@gmail.com; ned.efbrush@gmail.com; 

Richard Parker; Paul.Ryan@hitmet.com; jhodge@howard.com; Daniel 

Cohen; cabolduc@lbl.gov; gjrosenquist@lbl.gov; kcoughlin@lbl.gov; ScottB@LVMetals.com; dave.millure

@metglas.com; kwinder@mleainc.com;jrossetti@mlgw.org; brian.coffey@navigant.com; caitlin.johnson@

navigant.com; matthew.nardotti@navigant.com; mrivest@navigant.com; zhimei.luo@navigant.com; Jim.c

reevy@nema.org; john.caskey@nema.org;mwaltner@nrdc.org; rroy@nrdc.org; robert.saint@nreca.coop; 

Teckman@nwcouncil.org; vijay.tendulkar@onyxpower.com; gbf1@pge.com; chuck.simmons@pgnmail.co

m; ahofmann@publicpower.org;pkumar@publicpower.org; adelaski@standardsASAP.org; jmauer@standa

rdsasap.org; wes.patterson@us.abb.com; chad.kennedy@us.schneiderelectric.com; thomas.patzner@us.schneider-electric.com; charlied@uus.org

Subject: RE: Negotiated Rulemaking - Distribution Transformers Teleconference

 

Phil,
We're in the middle of negotiations and some of us have made clear that no or little change to the 

standard is not acceptable as the DOE analysis justifies higher standards (higher levels are technically 

feasible and cost-effective on a life-cycle cost basis). The efficiency groups would rather leave the 

decision to DOE than agree to subpar standards. If you and other participants want to veto any 

significant change in the standard, then we might as well save some time, break off negotiations and just 

make our respective arguments to DOE. Is that what you want to do? If the answer is no, then let's start 

talking about how to make higher standards acceptable rather than continue to make arguments about 

why low standards are needed. We're all busy and if we're going to make progress we need to break new 

ground and not rehash old ground.

Steve 

>>> Phil Hopkinson <phopkinson@hvolt.com> 11/11/2011 1:16 PM >>>

Hello Robert and all:

You must not have looked at Jerry Corkran’s message because he found the cost to be $17/watt, which

is pretty close to my number, where both Jerry and I have used M3 core steel to derive the cost curve.  

The fact is that the cost curve is very steep with M3 and quickly hits the brick wall.

1. I have checked Carlos Gaytan’s cost curves as well and he is finding about the same relationship with

M3.

2. I have checked Wes Patterson’s data as well and he is finding an M3 cost curve about the same as

mine.

3. I have checked the OPS data with M3 as well and it too is very close to $20/watt.

a. For example, for design line 1 they show an efficiency at 50% load of 99.08% which translates to 232

watts of loss and sells for $1,960.73.

b. They show another M3 design with an efficiency of 99.26% which translates to 186 watts of loss and

sells for $2962.11.

c. The change in selling price is $2,962.11‐$1,906.11 or +$1,001.38

d. The change in watts is 232‐186 or ‐46 watts.

e. The OPS $/watt is therefore, $1,001.38/46 watts or $21.77

f. Hence we see that all data sources are pointing to cost per watt of ~$20 /watt saved to go from the

current mandatory standard to EL1.  I get $30/watt to go to EL2 and $53/watt to go to EL3

4. The fact is that M3 is about out of gas and the DOE did a good job in the last rule making.

5. The fact also is that a push to anything beyond present does not show economic value and I do not

support it.

6. The fact also is that a push to higher efficiencies will kill the new transformer market and open up the

rebuild market, destroying jobs at the new transformer manufacturers and resulting in transformers of

lower efficiency which will cost energy and not save it.

Best regards,

Phil

Philip J Hopkinson, PE 

President & CEO HVOLT Inc. 

3704 High Ridge Rd. 

Charlotte, NC 28270 

phopkinson@hvolt.com
Ph 704-846-3290 

Fx 704-845-2520 

Cell 704-236-3320 

www.hvolt.com

From: Robert Berman [mailto:bermaneconomics@gmail.com] 

Sent: Friday, November 11, 2011 11:16 AM 

To: Phil Hopkinson 

Cc: Corkran, Jerry L; Richard Parker; Freeman, Jeremiah 

(CONTR); rick.anderson@faypwc.com; tballo@earthjustice.org; ScottB@LVMetals.com; john.caskey@nem

a.org; Cymbalsky, 

John; adelaski@standardsASAP.org;Teckman@nwcouncil.org; gbf1@pge.com; carlos.gaytan@ge.com; rg

reeson@federalpacific.com; bruce.r.hirsch@bge.com; jhodge@howard.com; mhyland@appanet.org; dave

.millure@metglas.com; snadel@aceee.org;wes.patterson@us.abb.com; Eric.Petersen@aksteel.com; Raym

ond.Polinski@ATImetals.com; artrosenfeld@gmail.com; srosenstock@eei.org; rroy@nrdc.org; robert.saint

@nreca.coop; chuck.simmons@pgnmail.com;kwinder@mleainc.com; mwaltner@nrdc.org; jerry.schoen@

aksteel.com; Paul.Ryan@hitmet.com; ahofmann@publicpower.org; pkumar@publicpower.org; bsmith@fe

deralpacific.com; greg.coulter405@gmail.com;jmauer@standardsasap.org; Cohen, Daniel; Meyers, 

Aaron; Jim.creevy@nema.org; jrossetti@mlgw.org; cabolduc@lbl.gov; kcoughlin@lbl.gov; brian.coffey@n

avigant.com; mrivest@navigant.com; gjrosenquist@lbl.gov;caitlin.johnson@navigant.com; zhimei.luo@na

vigant.com; Marchetti, Emily (CONTR); charlied@uus.org; DYoung@energysolution.com; James.Lass@cleco.com; maheshsampat@bellsouth.net;matthew.nardotti@navigant.com; 

Raba, Jim; Savitz, Maxine 

(EMAB); tpetrosino@carolina.rr.com; chris.brown@cogentpowerinc.com; ted.johnstone@cogentpowerinc.

com; frank.guilbault@cogentpowerinc.com;ned.efbrush@gmail.com; dbrender@cda.copper.org; chad.ken

nedy@us.schneiderelectric.com; eduardorobles@eaton.com; vijay.tendulkar@onyxpower.com; thomas.patzner@us.schneider

-electric.com;carlosgsiqueiros@eaton.com; Robert Berman; Trujillo, Antonio; Moore, Jack C 

Subject: Re: Negotiated Rulemaking - Distribution Transformers Teleconference

 

Even if it were that high (and Mr. Hopkinson is the only one I've seen who has put the number 

anywhere near that), the efficiency objective is saving Watt-hours (energy) not Watts (the 

capacity to save energy) . One Watt saved for 8,760 hours per year for 30 years is 262.8 kWh 

(not counting leap years). Even at Mr. Hutchinson's $20, that's just over 7¢ / kWh. If Mr. 

Hutchinson will examine his electric bill, as he has reported, he will see that even as high as 7¢ 

it's a good buy, and that assumes we put a ZERO value on any environmental benefits (which is 

why DOE agreed to reconsider its 2007 MEPS in the first place. 

 

Indeed, the cost of losses per Watt (roughly the A factors that OPS has been using) are no where 

near the $20 claimed here. Moreover, as ABB and others have pointed out, the proper approach 

would have been to minimize cost subject to efficiency, not A & B, which would have resulted 

in a lower, flatter curve to the asymptote. ABB's actual market data -- physical transformers 

produced and delivered -- shows a competitive market for M3 transformers even at EL4 

efficiency. You can make all the hypothetical claims you want to, gentlemen, the market is 

the real world. 

Regards,

Robert A. Berman, Principal
Berman Economics

www.BermanEconomics.com

1915 Grand Court

Vienna, VA 22182

703‐281‐0490

703‐655‐8398 (cell)

BermanEconomics@gmail.com

 

On Nov 10, 2011, at 6:53 PM, Phil Hopkinson wrote: 

 

Well stated Jerry 

 

That is also what my analysis and report said. If you restrict to M3 then the cost of EL1 rises to 

about $20/watt. 

 

Phil 

Phil Hopkinson,P.E. 

HVolt Inc. 

704-846-3290 

F: 704-845-2520 

C: 704-236-3320 

phopkinson@hvolt.com

On Nov 10, 2011, at 18:04, "Corkran, Jerry L" <Jerry.Corkran@CooperIndustries.com> wrote: 

To Mr. Parker and the DOE working group,

The reason for the request for the incremental cost of the losses is that the current DOE efficiency levels

can be obtained if the design is optimized at about $4 per core watt and $1 per winding watt at full

load.  At the DOE 50% kVA rating, this is the same as evaluating the losses or optimizing the design at

about $4 per total watts loss.

The present DOE efficiency loss level results in transformer designs about like many utilities were

purchasing their transformers before 2007.   The utilities were purchasing the efficiency levels that were

justified based on the cost of losses.  A few utilities  were purchasing higher efficiency that the 2007

efficiency rules because of the calculated cost of energy being higher than the $4/$1 loss evaluation.

What came up in the discussion last week was even for loss level 1, the incremental cost of losses was

about $17 per watt for the design checked, between the present DOE losses an efficiency level of DEL1.  

The added cost of $17 per watt is so much higher than the typical cost of the energy for the utilities,

that  it is very questionable that the DOE payback estimates are accurate.  A 3% interest rate may be a

factor in the payback calculations.
Jerry Corkran

From: Richard Parker [mailto:richardparkerdc@gmail.com] 

Sent: Thursday, November 10, 2011 3:23 PM 

To: Robert Berman 

Cc: Freeman, Jeremiah 

(CONTR); rick.anderson@faypwc.com; tballo@earthjustice.org; ScottB@LVMetals.com; john.caskey@nem

a.org; Corkran, Jerry L; Cymbalsky, 

John; adelaski@standardsASAP.org;Teckman@nwcouncil.org; gbf1@pge.com; carlos.gaytan@ge.com; rg

reeson@federalpacific.com; bruce.r.hirsch@bge.com; jhodge@howard.com; mhyland@appanet.org; dave

.millure@metglas.com;snadel@aceee.org; wes.patterson@us.abb.com; Eric.Petersen@aksteel.com; Raym

ond.Polinski@ATImetals.com; artrosenfeld@gmail.com; srosenstock@eei.org; rroy@nrdc.org; robert.saint

@nreca.coop;chuck.simmons@pgnmail.com; kwinder@mleainc.com; mwaltner@nrdc.org; jerry.schoen@

aksteel.com; Paul.Ryan@hitmet.com; ahofmann@publicpower.org; pkumar@publicpower.org;bsmith@fed

eralpacific.com; greg.coulter405@gmail.com; jmauer@standardsasap.org; Cohen, Daniel; Meyers, 

Aaron; Jim.creevy@nema.org; jrossetti@mlgw.org; cabolduc@lbl.gov; kcoughlin@lbl.gov;brian.coffey@na

vigant.com; mrivest@navigant.com; gjrosenquist@lbl.gov; caitlin.johnson@navigant.com; zhimei.luo@na

vigant.com; Marchetti, Emily (CONTR); charlied@uus.org; DYoung@energysolution.com; James.Lass@cleco.com; maheshsampat@bellsouth.net; phopkinson@hvolt.com; matthew.n

ardotti@navigant.com; Raba, Jim; Savitz, Maxine 

(EMAB); tpetrosino@carolina.rr.com;chris.brown@cogentpowerinc.com; ted.johnstone@cogentpowerinc.c

om; frank.guilbault@cogentpowerinc.com; ned.efbrush@gmail.com; dbrender@cda.copper.org; chad.ken

nedy@us.schneiderelectric.com; eduardorobles@eaton.com; vijay.tendulkar@onyxpower.com; thomas.patzner@us.schneider

-electric.com; carlosgsiqueiros@eaton.com

Subject: Re: Negotiated Rulemaking - Distribution Transformers Teleconference

 

Robert, 

I understand the DOE staff are working on the incremental Watts calculations and will get that 

out to group as soon as it's ready. 

best wishes, 

Richard 

On Thu, Nov 10, 2011 at 11:52 AM, Robert Berman <bermaneconomics@gmail.com> wrote: 

Thank you Richard. That clarification is helpful. 

 

In the liquid-filled meeting we were told that we would receive an analysis of incremental Watts 

saved by DL for all ELs, as well as the incremental cost. When will that analysis be available? 

For many of us, that analysis is the basis for additional, perhaps extensive analyses, so it should 

come with enough lead time before any additional meetings or teleconferences to that we can 

give it the required consideration. It would be most helpful if the incremental cost were provided 

separately for transformer and installation, with any pole component of the installation identified. 

 

For the MV Dry and LV Dry meetings, it would be most helpful if you would also circulate an 

agenda with objectives, hopefully this week, so that we are able to prepare for those meetings. 
Regards,

Robert A. Berman, Principal

Berman Economics

www.BermanEconomics.com

1915 Grand Court

Vienna, VA 22182

703‐281‐0490

703‐655‐8398 (cell)

BermanEconomics@gmail.com

 

On Nov 10, 2011, at 11:14 AM, Richard Parker wrote: 

Dear Colleagues: 

The telcon on the 17th is currently planned for medium-voltage dry-type and the telcon on the 

21st is reserved for low-voltage. There will be revised analysis circulated in advance of both 

calls per our discussion yesterday. Each call has substantial chunks of time allocated, though I 

hope we won't need all that time. 

It may be prudent to schedule a liquid-filled call at some point as well, but I propose that we 

hold off on that for day or so, until we can clarify when revised analysis for liquid-filled will be 

ready. 

Thanks for your very constructive participation in the meetings over the last two days. 

Richard Parker 

On Thu, Nov 10, 2011 at 10:05 AM, Freeman, Jeremiah (CONTR) 

<Jeremiah.Freeman@ee.doe.gov> wrote: 

When: Thursday, November 17, 2011 1:00 PM‐5:00 PM (GMT‐05:00) Eastern Time (US & Canada).

Where: Webinar and Phone

Note: The GMT offset above does not reflect daylight saving time adjustments.

*~*~*~*~*~*~*~*~*~*

Dear Colleagues,

This event is to save the time slot on your calendar based on our discussion at yesterday's meeting.

Later today further information will be sent regarding the registration information for our November 17

and November 21 webinars. After registering you will get the link for the webinar and a toll free

number.
Please call with questions or concerns.

Very Respectfully,

Jeremiah Freeman

202‐431‐4243 (cell)

202‐586‐1867 (office)

 

 

 

 

>>> This e‐mail and any attachments are confidential, may contain legal,

professional or other privileged information, and are intended solely for the

addressee.  If you are not the intended recipient, do not use the information

in this e‐mail in any way, delete this e‐mail and notify the sender. CEG‐IP2