OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

GENERAL INFORMATION AND SUMMARY (GIS)

A. Mailing Address and Contact Information 

Facility name ___Morongo Casino Cogeneration Facility__________________________ 

Mailing address: Street or P.O. Box ______12700 Pumarra Road______________________ 

City _____Banning_______________________ State ___CA____ ZIP __92220__ 

Contact person: ____Michael Milhiser__________ Title __Chief Administrative Officer_______ 

Telephone (_951_) __755__ - __5115____ Ext. _________ 

Facsimile (__951____) ____849____ - ___4425________ 

B. Facility Location 

Temporary source? ___Yes _X_No Plant site location __49500 Seminole Dr______________ 

__________________________________________________________________________________ 

City _Morongo Indian Reservation (Cabazon)_ State_CA__ County__Riverside___ EPA Region_9__ 

Is the facility located within: 

Indian lands? _X_YES ___ NO OCS waters? ___YES _X_ NO 

Non-attainment area? _X_ YES ___NO If yes, for what air pollutants? __03, PM10, PM2.5__ 

Within 50 miles of affected State? _X YES __ NO If yes, What State(s)? __CA_ 

C. Owner 

Name _Morongo Band of Mission Indians____ Street/P.O. Box __12700 Pumarra Road___ 

City ______Banning_________________ State__CA__ ZIP_92220__ - ________ 

Telephone (__951___) __755____ - ____5115______ Ext_________ 

D. Operator 

Name __EMCOR Energy and Technologies, Inc.____ Street/P.O. Box __301 Merritt Seven, 6th Floor___ 

City ____Norwalk_______________ State __CA__ ZIP _06851__ - _______ 

Telephone (_951) _755_ - __5775___ Ext_________ 

EPA Form 5900-79 
GIS 2 

EPA Form 5900-79 

E. Application Type 

Mark only one permit application type and answer the supplementary question appropriate for the type 

marked. 

___Initial Permit _X_ Renewal ___ Significant Mod ___ Minor Permit Mod(MPM) 

___ Group Processing, MPM ___ Administrative Amendment 

For initial permits, when did operations commence? _____ /_____ /_____ 

For permit renewal, what is the expiration date of current permit? __09_/_01_/_2010_ 

F. Applicable Requirement Summary 

Mark all types of applicable requirements that apply.* 

___ SIP ___ FIP/TIP ___ PSD ___Non-attainment NSR

 

___ Minor source NSR ___ Section 111 ___ Phase I acid rain ___Phase II acid rain 

___ Stratospheric ozone ___ OCS regulations ___ NESHAP ___ Sec. 112(d) MACT 

___ Sec. 112(g) MACT ___ Early reduction of HAP ___ Sec 112(j) MACT ___ RMP [Sec.112(r)] 

 

___ Tank Vessel requirements, sec. 183(f)) ___ Section 129 Standards/Requirement 

___ Consumer / comm.. products, ' 183(e) ___ NAAQS, increments or visibility (temp. sources) 

Has a risk management plan been registered? ___YES _X_NO Regulatory agency ____________ 

Phase II acid rain application submitted? ___YES _X_NO If yes, Permitting authority ____________ 

* None of the above requirements are applicable to MCC. The engines are 4SLB stationary RICEs built in 2004 

that, according to 40 CFR Part 63 Subpart ZZZZ §6590(b) (3) 4, are in compliance with NESHAP requirements, and 

according to 40 CFR Part 60 Subpart JJJJ §60.4230(a)(4), are in compliance with Section 111 requirements. 

G. Source-Wide PTE Restrictions and Generic Applicable Requirements 

A Facility natural gas usage limit of 451.1 mmcf/yr based on natural gas with a high heating value of 1,005 btu/scf. This 

corresponds to an annual natural gas heat input limitation of 453,154 mmBtu/yr (Operating Permit (OP) Requirement 

II.B.3) 

A Facility No. 2 fuel oil usage limit of 49,052 gallons/yr based on No.2 fuel oil with a high heating value of 130,000 

Btu/gal. This corresponds to an annual No. 2 fuel oil heat input limitation of 6,377 mmBtu/yr. (OP Requirement II.B.4) 

Record and provide to EPA Region IX the following information by the 15th day following the end of each quarter: (1) 

quantities of natural gas and low sulfur diesel oil burned in the engines for the past quarter, (2) any periods of excess 

NOx emissions coming from the Facility during the past quarter based on monitoring, source tests, or portable NOx 

analyzer readings, (3) periods of operation and total operating hours for all engines, and (4) the annual emission 

calculations for each month during the quarter performed pursuant to OP Requirement II.C.1 

Submit to EPA Region IX a complete renewal application for a Part 71 Permit (OP Requirement IV.N.6) 

Calculation of monthly NOx emissions in accordance with OP Requirement II.C.1 
GIS 3 

EPA Form 5900-79 

H. Process Description 

List processes, products, and SIC codes for the facility. 

 Process Products SIC 

(4) Natural gas-fired internal combustion engines Electricity 3519 

(3) Diesel fueled internal combustion engines Backup/Emergency power 3519 

I. Emission Unit Identification 

Assign an emissions unit ID and describe each emissions unit at the facility. Control equipment and/or alternative 

operating scenarios associated with emissions units should by listed on a separate line. Applicants may exclude 

from this list any insignificant emissions units or activities. 

 Emissions Unit ID Description of Unit 

EG-1 Caterpillar Model G3520 natural gas-fired, 4-stroke, lean burn internal combustion engine 

rated at 2,055 kW. 

EG-2 Caterpillar Model G3520 natural gas-fired, 4-stroke, lean burn internal combustion engine 

rated at 2,055 kW. 

EG-3 Caterpillar Model G3520 natural gas-fired, 4-stroke, lean burn internal combustion engine 

rated at 2,055 kW. 

EG-4 Caterpillar Model G3520 natural gas-fired, 4-stroke, lean burn internal combustion engine 

rated at 2,055 kW. 

EG-5 Caterpillar Model G3516B diesel-fired, 4 stroke, emergency generator rated at 2,000kW. 

EG-6 Caterpillar Model G3516B diesel-fired, 4 stroke, emergency generator rated at 2,000kW. 

EG-7 Caterpillar Model G3516B diesel-fired, 4 stroke, emergency generator rated at 2,000kW. 

SCR-1 Selective Catalytic Reduction Unit for EG-1 

SCR-2 Selective Catalytic Reduction Unit for EG-2 

SCR-3 Selective Catalytic Reduction Unit for EG-3 

SCR-4 Selective Catalytic Reduction Unit for EG-4 

OC-1 Oxidation Catalyst for EG-1 
GIS 4 

EPA Form 5900-79 

 

OC-2 Oxidation Catalyst for EG-2 

OC-3 Oxidation Catalyst for EG-3 

OC-4 Oxidation Catalyst for EG-4 
GIS 5 

J. Facility Emissions Summary 

Enter potential to emit (PTE) for the facility as a whole for each air pollutant listed below. Enter the name of the 

single HAP emitted in the greatest amount and its PTE. For all pollutants stipulations to major source status 

may be indicated by entering "major" in the space for PTE. Indicate the total actual emissions for fee purposes 

for the facility in the space provided. Applications for permit modifications need not include actual emissions 

information. 

NOx ___17.08___ tons/yr VOC __10.08___ tons/yr SO2 _1.08__ tons/yr 

PM-10 _3.62___ tons/yr CO _39.7__ tons/yr Lead __N/A__ tons/yr 

Total HAP ___5.92__ tons/yr 

Single HAP emitted in the greatest amount _____Formaldehyde____ PTE _5.92_ tons/yr 

Total of regulated pollutants (for fee calculation), Sec. F, line 5 of form FEE _30.5_ tons/yr 

K. Existing Federally-Enforceable Permits 

 Permit number(s) MO-OP 05-01 Permit type _Title V Permit Permitting authority USEPA-Region IX

 Permit number(s) _________________ Permit type _____________ Permitting authority _________ 

L. Emission Unit(s) Covered by General Permits 

Emission unit(s) subject to general permit _____N/A_________________________________________ 

 

Check one: ___ Application made ___ Coverage granted 

General permit identifier ______________________________ Expiration Date ____/____/____ 

M. Cross-referenced Information 

Does this application cross-reference information? ___ YES _X_ NO (If yes, see instructions) 

EPA Form 5900-79 
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION UNIT DESCRIPTION FOR FUEL COMBUSTION SOURCES (EUD-1) 

A. General Information 

Emissions unit ID ___EG-1____ Description___Internal Combustion Engine_____________ 

SIC Code (4-digit) __3519___ SCC Code__20100202

B. Emissions Unit Description 

Primary use _Production of Electricity_______________ Temporary Source ___Yes _X_No 

Manufacturer __Caterpillar__________ Model No. ___G3520__________ 

Serial Number __GDB00041__________ Installation Date_06_/_14_/__2004_ 

Boiler Type: ___ Industrial boiler ___ Process burner ___ Electric utility boiler 

 Other (describe) _____________________________________________ 

Boiler horsepower rating_____N/A________ Boiler steam flow (lb/hr)_____N/A_______ 

Type of Fuel-Burning Equipment (coal burning only): 

 

___ Hand fired ___Spreader stoker ___Underfeed stoker ___Overfeed stoker 

___ Traveling grate ___Shaking grate ___Pulverized, wet bed ___ Pulverized, dry bed 

Actual Heat Input ___21.9___MM BTU/hr Max. Design Heat Input __21.9___MM BTU/hr 

EPA Form 5900-80 
EUD-1 2

C. Fuel Data 

Primary fuel type(s)_Natural Gas______ Standby fuel type(s)______N/A________ 

Describe each fuel you expected to use during the term of the permit. 

 

 Fuel Type 

Max. Sulfur 

Content (%) 

 Max. Ash 

Content (%) 

BTU Value 

 (cf, gal., or lb.) 

Natural Gas 1.5gr/100scf N/A 1,005 Btu/scf 

 D. Fuel Usage Rates

 Fuel Type Annual Actual 

Usage 

Maximum Usage 

 Hourly Annual 

Natural Gas 451.1 mmscf/yr* 21,767 scf/hr 451.1 mmscf/yr* 

*Total for 4 natural gas engines 

E. Associated Air Pollution Control Equipment

Emissions unit ID_SCR-1____ Device type__Selective Catalytic Reduction__________ 

Air pollutant(s) Controlled___NOx___________ Manufacturer__Johnson Matthey________ 

Model No.__MC403SS-30-5_____ Serial No.__FD118714-2_______ 

Installation date_06_/__15_/__2004__ Control efficiency (%) ___85.0___ 

Efficiency estimation method_____Manufacturer’s specifications__________________ 

Emissions unit ID_OC-1____ Device type__Oxidation Catalyst__________ 

Air pollutant(s) Controlled___CO and VOC_____ Manufacturer__Johnson Matthey________ 

Model No.__MC2020-24-3_____ Serial No.__FD118713-3_______ 

Installation date_06_/__15_/__2004__ Control efficiency (%) ___74.8___ 

Efficiency estimation method_____Manufacturer’s specifications__________________ 

EPA Form 5900-80 
EUD-1 

EPA Form 5900-80 

 3

F. Ambient Impact Assessment 

This information must be completed by temporary sources or when ambient impact assessment is an 

applicable requirement for this emissions unit (this is not common). 

 

Stack height (ft) ___N/A__._____ Inside stack diameter (ft) _________._____ 

Stack temp(o

F) __________._____ Design stack flow rate (ACFM) __________.____ 

Actual stack flow rate (ACFM) ____________.____ Velocity (ft/sec) ____________._______ 

 
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION UNIT DESCRIPTION FOR FUEL COMBUSTION SOURCES (EUD-1) 

A. General Information 

Emissions unit ID ___EG-2____ Description___Internal Combustion Engine_____________ 

SIC Code (4-digit) __3519___ SCC Code__20100202

B. Emissions Unit Description 

Primary use _Production of Electricity_______________ Temporary Source ___Yes _X_No 

Manufacturer __Caterpillar__________ Model No. ___G3520__________ 

Serial Number __GDB00040__________ Installation Date_06_/_15_/__2004_ 

Boiler Type: ___ Industrial boiler ___ Process burner ___ Electric utility boiler 

 Other (describe) _____________________________________________ 

Boiler horsepower rating_____N/A________ Boiler steam flow (lb/hr)_____N/A_______ 

Type of Fuel-Burning Equipment (coal burning only): 

 

___ Hand fired ___Spreader stoker ___Underfeed stoker ___Overfeed stoker 

___ Traveling grate ___Shaking grate ___Pulverized, wet bed ___ Pulverized, dry bed 

Actual Heat Input ___21.9___MM BTU/hr Max. Design Heat Input __21.9___MM BTU/hr 

EPA Form 5900-80 
EUD-1 2

C. Fuel Data 

Primary fuel type(s)_Natural Gas_____ Standby fuel type(s)______N/A__________ 

Describe each fuel you expected to use during the term of the permit. 

 

 Fuel Type 

Max. Sulfur 

Content (%) 

 Max. Ash 

Content (%) 

BTU Value 

 (cf, gal., or lb.) 

Natural Gas 1.5gr/100scf N/A 1,005 Btu/scf 

 D. Fuel Usage Rates

 Fuel Type Annual Actual 

Usage 

Maximum Usage 

 Hourly Annual 

Natural Gas 451.1 mmscf/yr* 21,767 scf/hr 451.1 mmscf/yr* 

*Total for 4 natural gas engines 

E. Associated Air Pollution Control Equipment

Emissions unit ID_SCR-3____ Device type__Selective Catalytic Reduction__________ 

Air pollutant(s) Controlled___NOx___________ Manufacturer__Johnson Matthey________ 

Model No.__MC403SS-30-5_____ Serial No.__FD118714-4_______ 

Installation date_06_/__15_/__2004__ Control efficiency (%) ___85.0___ 

Efficiency estimation method_____Manufacturer’s specifications__________________ 

Emissions unit ID_OC-2____ Device type__Oxidation Catalyst__________ 

Air pollutant(s) Controlled___CO and VOC_____ Manufacturer__Johnson Matthey________ 

Model No.__MC2020-24-3_____ Serial No.__FD118713-4_______ 

Installation date_06_/__15_/__2004__ Control efficiency (%) ___74.8___ 

Efficiency estimation method_____Manufacturer’s specifications__________________ 

EPA Form 5900-80 
EUD-1 

EPA Form 5900-80 

 3

F. Ambient Impact Assessment 

This information must be completed by temporary sources or when ambient impact assessment is an 

applicable requirement for this emissions unit (this is not common). 

 

Stack height (ft) ___N/A__._____ Inside stack diameter (ft) _________._____ 

Stack temp(o

F) __________._____ Design stack flow rate (ACFM) __________.____ 

Actual stack flow rate (ACFM) ____________.____ Velocity (ft/sec) ____________._______ 

 
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION UNIT DESCRIPTION FOR FUEL COMBUSTION SOURCES (EUD-1) 

A. General Information 

Emissions unit ID ___EG-3____ Description___Internal Combustion Engine_____________ 

SIC Code (4-digit) __3519___ SCC Code__20100202

B. Emissions Unit Description 

Primary use _Production of Electricity_______________ Temporary Source ___Yes _X_No 

Manufacturer __Caterpillar__________ Model No. ___G3520__________ 

Serial Number __GDB00039__________ Installation Date_06_/_15_/__2004_ 

Boiler Type: ___ Industrial boiler ___ Process burner ___ Electric utility boiler 

 Other (describe) _____________________________________________ 

Boiler horsepower rating_____N/A________ Boiler steam flow (lb/hr)_____N/A_______ 

Type of Fuel-Burning Equipment (coal burning only): 

 

___ Hand fired ___Spreader stoker ___Underfeed stoker ___Overfeed stoker 

___ Traveling grate ___Shaking grate ___Pulverized, wet bed ___ Pulverized, dry bed 

Actual Heat Input ___21.9___MM BTU/hr Max. Design Heat Input __21.9___MM BTU/hr 

EPA Form 5900-80 
EUD-1 2

C. Fuel Data 

Primary fuel type(s)_Natural Gas_____ Standby fuel type(s)______N/A__________ 

Describe each fuel you expected to use during the term of the permit. 

 

 Fuel Type 

Max. Sulfur 

Content (%) 

 Max. Ash 

Content (%) 

BTU Value 

 (cf, gal., or lb.) 

Natural Gas 1.5gr/100scf N/A 1,005 Btu/scf 

 D. Fuel Usage Rates

 Fuel Type Annual Actual 

Usage 

Maximum Usage 

 Hourly Annual 

Natural Gas 451.1 mmscf/yr* 21,767 scf/hr 451.1 mmscf/yr* 

*Total for 4 natural gas engines 

E. Associated Air Pollution Control Equipment

Emissions unit ID_SCR-3____ Device type__Selective Catalytic Reduction__________ 

Air pollutant(s) Controlled___NOx___________ Manufacturer__Johnson Matthey________ 

Model No.__MC403SS-30-5_____ Serial No.__FD118714-1_______ 

Installation date_06_/__15_/__2004__ Control efficiency (%) ___85.0___ 

Efficiency estimation method_____Manufacturer’s specifications__________________ 

Emissions unit ID_OC-3____ Device type__Oxidation Catalyst__________ 

Air pollutant(s) Controlled___CO and VOC_____ Manufacturer__Johnson Matthey________ 

Model No.__MC2020-24-3_____ Serial No.__FD118713-2_______ 

Installation date_06_/__15_/__2004__ Control efficiency (%) ___74.8___ 

Efficiency estimation method_____Manufacturer’s specifications__________________ 

EPA Form 5900-80 
EUD-1 

EPA Form 5900-80 

 3

F. Ambient Impact Assessment 

This information must be completed by temporary sources or when ambient impact assessment is an 

applicable requirement for this emissions unit (this is not common). 

 

Stack height (ft) ___N/A__._____ Inside stack diameter (ft) _________._____ 

Stack temp(o

F) __________._____ Design stack flow rate (ACFM) __________.____ 

Actual stack flow rate (ACFM) ____________.____ Velocity (ft/sec) ____________._______ 
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION UNIT DESCRIPTION FOR FUEL COMBUSTION SOURCES (EUD-1) 

A. General Information 

Emissions unit ID ___EG-3____ Description___Internal Combustion Engine_____________ 

SIC Code (4-digit) __3519___ SCC Code__20100202

B. Emissions Unit Description 

Primary use _Production of Electricity_______________ Temporary Source ___Yes _X_No 

Manufacturer __Caterpillar__________ Model No. ___G3520__________ 

Serial Number __CMY00207__________ Installation Date_06_/_15_/__2004_ 

Boiler Type: ___ Industrial boiler ___ Process burner ___ Electric utility boiler 

 Other (describe) _____________________________________________ 

Boiler horsepower rating_____N/A________ Boiler steam flow (lb/hr)_____N/A_______ 

Type of Fuel-Burning Equipment (coal burning only): 

 

___ Hand fired ___Spreader stoker ___Underfeed stoker ___Overfeed stoker 

___ Traveling grate ___Shaking grate ___Pulverized, wet bed ___ Pulverized, dry bed 

Actual Heat Input ___21.9___MM BTU/hr Max. Design Heat Input __21.9___MM BTU/hr 

EPA Form 5900-80 
EUD-1 2

C. Fuel Data 

Primary fuel type(s)_Natural Gas_____ Standby fuel type(s)______N/A__________ 

Describe each fuel you expected to use during the term of the permit. 

 

 Fuel Type 

Max. Sulfur 

Content (%) 

 Max. Ash 

Content (%) 

BTU Value 

 (cf, gal., or lb.) 

Natural Gas 1.5gr/100scf N/A 1,005 Btu/scf 

 D. Fuel Usage Rates

 Fuel Type Annual Actual 

Usage 

Maximum Usage 

 Hourly Annual 

Natural Gas 451.1 mmscf/yr* 21,767 scf/hr 451.1 mmscf/yr* 

*Total for 4 natural gas engines 

E. Associated Air Pollution Control Equipment

Emissions unit ID_SCR-3____ Device type__Selective Catalytic Reduction__________ 

Air pollutant(s) Controlled___NOx___________ Manufacturer__Johnson Matthey________ 

Model No.__MC403SS-30-5_____ Serial No.__FD118714-3_______ 

Installation date_06_/__15_/__2004__ Control efficiency (%) ___85.0___ 

Efficiency estimation method_____Manufacturer’s specifications__________________ 

Emissions unit ID_OC-4____ Device type__Oxidation Catalyst__________ 

Air pollutant(s) Controlled___CO and VOC_____ Manufacturer__Johnson Matthey________ 

Model No.__MC2020-24-3_____ Serial No.__FD118713-1_______ 

Installation date_06_/__15_/__2004__ Control efficiency (%) ___74.8___ 

Efficiency estimation method_____Manufacturer’s specifications__________________ 

EPA Form 5900-80 
EUD-1 

EPA Form 5900-80 

 3

F. Ambient Impact Assessment 

This information must be completed by temporary sources or when ambient impact assessment is an 

applicable requirement for this emissions unit (this is not common). 

 

Stack height (ft) ___N/A__._____ Inside stack diameter (ft) _________._____ 

Stack temp(o

F) __________._____ Design stack flow rate (ACFM) __________.____ 

Actual stack flow rate (ACFM) ____________.____ Velocity (ft/sec) ____________._______ 
 OMB No. 2060-0336, Approval Expires 

09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION UNIT DESCRIPTION FOR FUEL COMBUSTION SOURCES (EUD-1) 

A. General Information 

Emissions unit ID ___EG-5____ Description___Internal Combustion Engine_____________ 

SIC Code (4-digit) __3519___ SCC Code__20100202

B. Emissions Unit Description 

Primary use _Backup/Emergency Power_________ Temporary Source ___Yes _X_No 

Manufacturer __Caterpillar__________ Model No. ___3516__________ 

Serial Number __1HZ00817__________ Installation Date_06_/_15_/__2004_ 

Boiler Type: ___ Industrial boiler ___ Process burner ___ Electric utility boiler 

 Other (describe) _____________________________________________ 

Boiler horsepower rating_____N/A________ Boiler steam flow (lb/hr)_____N/A_______ 

Type of Fuel-Burning Equipment (coal burning only): 

 

___ Hand fired ___Spreader stoker ___Underfeed stoker ___Overfeed stoker 

___ Traveling grate ___Shaking grate ___Pulverized, wet bed ___ Pulverized, dry bed 

Actual Heat Input ___18.6___MM BTU/hr Max. Design Heat Input __18.6___MM BTU/hr 

EPA Form 5900-80 
EUD-1 

EPA Form 5900-80 

 2

C. Fuel Data 

Primary fuel type(s)_Diesel______ Standby fuel type(s)______N/A________ 

Describe each fuel you expected to use during the term of the permit. 

 

 Fuel Type 

Max. Sulfur 

Content (%) 

 Max. Ash 

Content (%) 

BTU Value 

 (cf, gal., or lb.) 

Diesel 0.05 N/A 130,000 Btu/gal 

 D. Fuel Usage Rates

 Fuel Type Annual Actual 

Usage 

Maximum Usage 

 Hourly Annual 

Diesel 49,052 gal/yr* 136 gal/hr 49,052 gal/yr* 

*Total for 3 diesel fueled engines 

E. Associated Air Pollution Control Equipment

Emissions unit ID_N/A____ Device type____________ 

Air pollutant(s) ___________ Manufacturer__________ 

Model No._______ Serial No.__ _______ 

Installation date___ Control efficiency (%) ______ 

Efficiency estimation method_______________________ 

F. Ambient Impact Assessment 

This information must be completed by temporary sources or when ambient impact assessment 

is an applicable requirement for this emissions unit (this is not common). 

 

Stack height (ft) ___N/A__._____ Inside stack diameter (ft) _________._____ 

Stack temp(o

F) __________._____ Design stack flow rate (ACFM) __________.____ 

Actual stack flow rate (ACFM) ____________.____ Velocity (ft/sec) ____________._______ 
 OMB No. 2060-0336, Approval Expires 

09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION UNIT DESCRIPTION FOR FUEL COMBUSTION SOURCES (EUD-1) 

A. General Information 

Emissions unit ID ___EG-6____ Description___Internal Combustion Engine_____________ 

SIC Code (4-digit) __3519___ SCC Code__20100202

B. Emissions Unit Description 

Primary use _Backup/Emergency Power_________ Temporary Source ___Yes _X_No 

Manufacturer __Caterpillar__________ Model No. ___3516__________ 

Serial Number __1HZ00970__________ Installation Date_06_/_15_/__2004_ 

Boiler Type: ___ Industrial boiler ___ Process burner ___ Electric utility boiler 

 Other (describe) _____________________________________________ 

Boiler horsepower rating_____N/A________ Boiler steam flow (lb/hr)_____N/A_______ 

Type of Fuel-Burning Equipment (coal burning only): 

 

___ Hand fired ___Spreader stoker ___Underfeed stoker ___Overfeed stoker 

___ Traveling grate ___Shaking grate ___Pulverized, wet bed ___ Pulverized, dry bed 

Actual Heat Input ___18.6___MM BTU/hr Max. Design Heat Input __18.6___MM BTU/hr 

EPA Form 5900-80 
EUD-1 

EPA Form 5900-80 

 2

C. Fuel Data 

Primary fuel type(s)_Diesel______ Standby fuel type(s)______N/A________ 

Describe each fuel you expected to use during the term of the permit. 

 

 Fuel Type 

Max. Sulfur 

Content (%) 

 Max. Ash 

Content (%) 

BTU Value 

 (cf, gal., or lb.) 

Diesel 0.05 N/A 130,000 Btu/gal 

 D. Fuel Usage Rates

 Fuel Type Annual Actual 

Usage 

Maximum Usage 

 Hourly Annual 

Diesel 49,052 gal/yr* 136 gal/hr 49,052 gal/yr* 

*Total for 3 diesel fueled engines 

E. Associated Air Pollution Control Equipment

Emissions unit ID_N/A____ Device type____________ 

Air pollutant(s) ___________ Manufacturer__________ 

Model No._______ Serial No.__ _______ 

Installation date___ Control efficiency (%) ______ 

Efficiency estimation method_______________________ 

F. Ambient Impact Assessment 

This information must be completed by temporary sources or when ambient impact assessment 

is an applicable requirement for this emissions unit (this is not common). 

 

Stack height (ft) ___N/A__._____ Inside stack diameter (ft) _________._____ 

Stack temp(o

F) __________._____ Design stack flow rate (ACFM) __________.____ 

Actual stack flow rate (ACFM) ____________.____ Velocity (ft/sec) ____________._______ 
 OMB No. 2060-0336, Approval Expires 

09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION UNIT DESCRIPTION FOR FUEL COMBUSTION SOURCES (EUD-1) 

A. General Information 

Emissions unit ID ___EG-7____ Description___Internal Combustion Engine_____________ 

SIC Code (4-digit) __3519___ SCC Code__20100202

B. Emissions Unit Description 

Primary use _Backup/Emergency Power_________ Temporary Source ___Yes _X_No 

Manufacturer __Caterpillar__________ Model No. ___3516__________ 

Serial Number __1HZ00971__________ Installation Date_06_/_15_/__2004_ 

Boiler Type: ___ Industrial boiler ___ Process burner ___ Electric utility boiler 

 Other (describe) _____________________________________________ 

Boiler horsepower rating_____N/A________ Boiler steam flow (lb/hr)_____N/A_______ 

Type of Fuel-Burning Equipment (coal burning only): 

 

___ Hand fired ___Spreader stoker ___Underfeed stoker ___Overfeed stoker 

___ Traveling grate ___Shaking grate ___Pulverized, wet bed ___ Pulverized, dry bed 

Actual Heat Input ___18.6___MM BTU/hr Max. Design Heat Input __18.6___MM BTU/hr 

EPA Form 5900-80 
EUD-1 

EPA Form 5900-80 

 2

C. Fuel Data 

Primary fuel type(s)_Diesel______ Standby fuel type(s)______N/A________ 

Describe each fuel you expected to use during the term of the permit. 

 

 Fuel Type 

Max. Sulfur 

Content (%) 

 Max. Ash 

Content (%) 

BTU Value 

 (cf, gal., or lb.) 

Diesel 0.05 N/A 130,000 Btu/gal 

 D. Fuel Usage Rates

 Fuel Type Annual Actual 

Usage 

Maximum Usage 

 Hourly Annual 

Diesel 49,052 gal/yr* 136 gal/hr 49,052 gal/yr* 

*Total for 3 diesel fueled engines 

E. Associated Air Pollution Control Equipment

Emissions unit ID_N/A____ Device type____________ 

Air pollutant(s) ___________ Manufacturer__________ 

Model No._______ Serial No.__ _______ 

Installation date___ Control efficiency (%) ______ 

Efficiency estimation method_______________________ 

F. Ambient Impact Assessment 

This information must be completed by temporary sources or when ambient impact assessment 

is an applicable requirement for this emissions unit (this is not common). 

 

Stack height (ft) ___N/A__._____ Inside stack diameter (ft) _________._____ 

Stack temp(o

F) __________._____ Design stack flow rate (ACFM) __________.____ 

Actual stack flow rate (ACFM) ____________.____ Velocity (ft/sec) ____________._______ 
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

INSIGNIFICANT EMISSIONS (IE)

List each insignificant activity or emission unit. In the "number" column, indicate the number of units in 

this category. Descriptions should be brief but unique. Indicate which emissions criterion of part 71 is the 

basis for the exemption.

Number Description of Activities or Emissions Units RAP, 

except 

HAP 

HAP 

3 1,250 gallon diesel storage tanks x x 

EPA Form 5900-83 
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION CALCULATIONS (EMISS)

Calculate potential to emit (PTE) for applicability purposes and actual emissions for fee purposes for 

each emissions unit, control device, or alternative operating scenario identified in section I of form GIS. 

If form FEE does not need to be submitted with the application, do not calculate actual emissions. 

A. Emissions Unit ID __EG-1___________ 

B. Identification and Quantification of Emissions 

First, list each air pollutant that is either regulated at the unit or present in major amounts, then list any other 

regulated pollutant (for fee calculation) not already listed. HAP may be simply listed as "HAP." Next, 

calculate PTE for applicability purposes and actual emissions for fee purposes for each pollutant. Do not 

calculate PTE for air pollutants listed solely for fee purposes. Include all fugitives for fee purposes. You may 

round to the nearest tenth of a ton for yearly values or tenth of a pound for hourly values. 

Air Pollutants 

Emission Rates 

CAS No. 

 Actual 

 Annual 

 Emissions 

 (tons/yr) 

Potential to Emit 

 Hourly 

 (lb/hr) 

 Annual 

 (tons/yr) 

NOx 

1.50 0.24 2.47* 

VOC 1.38 0.24 2.47* 

CO 5.51 0.95 9.90 

SOx 0.13 0.09 0.24 

PM/PM10 0.50 0.09 0.89 

Formaldehyde 0.80 0.14 1.47 50000 

*The OP currently limits NOx and VOC emissions from the facility as a whole to not more than 18.7 

tons per year for each pollutant (OP Requirement II.A.3) 

EPA Form 5900-84 
EMISS 

EPA Form 5900-84 

2
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION CALCULATIONS (EMISS)

Calculate potential to emit (PTE) for applicability purposes and actual emissions for fee purposes for 

each emissions unit, control device, or alternative operating scenario identified in section I of form GIS. 

If form FEE does not need to be submitted with the application, do not calculate actual emissions. 

A. Emissions Unit ID __EG-2___________ 

B. Identification and Quantification of Emissions 

First, list each air pollutant that is either regulated at the unit or present in major amounts, then list any other 

regulated pollutant (for fee calculation) not already listed. HAP may be simply listed as "HAP." Next, 

calculate PTE for applicability purposes and actual emissions for fee purposes for each pollutant. Do not 

calculate PTE for air pollutants listed solely for fee purposes. Include all fugitives for fee purposes. You may 

round to the nearest tenth of a ton for yearly values or tenth of a pound for hourly values. 

Air Pollutants 

Emission Rates 

CAS No. 

 Actual 

 Annual 

 Emissions 

 (tons/yr) 

Potential to Emit 

 Hourly 

 (lb/hr) 

 Annual 

 (tons/yr) 

NOx 

1.96 0.24 2.47* 

VOC 1.81 0.24 2.47* 

CO 7.25 0.95 9.90 

SOx 0.17 0.09 0.24 

PM/PM10 0.66 0.09 0.89 

Formaldehyde 1.1 0.14 1.47 50000 

*The OP currently limits NOx and VOC emissions from the facility as a whole to not more than 18.7 

tons per year for each pollutant (OP Requirement II.A.3) 

EPA Form 5900-84 
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION CALCULATIONS (EMISS)

Calculate potential to emit (PTE) for applicability purposes and actual emissions for fee purposes for 

each emissions unit, control device, or alternative operating scenario identified in section I of form GIS. 

If form FEE does not need to be submitted with the application, do not calculate actual emissions. 

A. Emissions Unit ID __EG-3___________ 

B. Identification and Quantification of Emissions 

First, list each air pollutant that is either regulated at the unit or present in major amounts, then list any other 

regulated pollutant (for fee calculation) not already listed. HAP may be simply listed as "HAP." Next, 

calculate PTE for applicability purposes and actual emissions for fee purposes for each pollutant. Do not 

calculate PTE for air pollutants listed solely for fee purposes. Include all fugitives for fee purposes. You may 

round to the nearest tenth of a ton for yearly values or tenth of a pound for hourly values. 

Air Pollutants 

Emission Rates 

CAS No. 

 Actual 

 Annual 

 Emissions 

 (tons/yr) 

Potential to Emit 

 Hourly 

 (lb/hr) 

 Annual 

 (tons/yr) 

NOx 

2.06 

0.24 2.47* 

VOC 1.98 

0.24 2.47* 

CO 

7.92 

0.95 9.90 

SOx 

0.18 

0.09 0.24 

PM/PM10 

0.72 

0.09 0.89 

Formaldehyde 

1.2 

0.14 1.47 50000 

*The OP currently limits NOx and VOC emissions from the facility as a whole to not more than 18.7 

tons per year for each pollutant (OP Requirement II.A.3) 

EPA Form 5900-84 
EMISS 

EPA Form 5900-84 

2
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION CALCULATIONS (EMISS)

Calculate potential to emit (PTE) for applicability purposes and actual emissions for fee purposes for 

each emissions unit, control device, or alternative operating scenario identified in section I of form GIS. 

If form FEE does not need to be submitted with the application, do not calculate actual emissions. 

A. Emissions Unit ID __EG-4___________ 

B. Identification and Quantification of Emissions 

First, list each air pollutant that is either regulated at the unit or present in major amounts, then list any other 

regulated pollutant (for fee calculation) not already listed. HAP may be simply listed as "HAP." Next, 

calculate PTE for applicability purposes and actual emissions for fee purposes for each pollutant. Do not 

calculate PTE for air pollutants listed solely for fee purposes. Include all fugitives for fee purposes. You may 

round to the nearest tenth of a ton for yearly values or tenth of a pound for hourly values. 

Air Pollutants 

Emission Rates 

CAS No. 

 Actual 

 Annual 

 Emissions 

 (tons/yr) 

Potential to Emit 

 Hourly 

 (lb/hr) 

 Annual 

 (tons/yr) 

NOx 

1.90 

0.24 2.47* 

VOC 1.77 

0.24 2.47* 

CO 

7.09 

0.95 9.90 

SOx 

0.16 

0.09 0.24 

PM/PM10 

0.65 

0.09 0.89 

Formaldehyde 

1.1 

0.14 1.47 50000 

*The OP currently limits NOx and VOC emissions from the facility as a whole to not more than 18.7 

tons per year for each pollutant (OP Requirement II.A.3) 

EPA Form 5900-84 
EMISS 

EPA Form 5900-84 

2
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION CALCULATIONS (EMISS)

Calculate potential to emit (PTE) for applicability purposes and actual emissions for fee purposes for 

each emissions unit, control device, or alternative operating scenario identified in section I of form GIS. 

If form FEE does not need to be submitted with the application, do not calculate actual emissions. 

A. Emissions Unit ID __EG-5___________ 

B. Identification and Quantification of Emissions 

First, list each air pollutant that is either regulated at the unit or present in major amounts, then list any other 

regulated pollutant (for fee calculation) not already listed. HAP may be simply listed as "HAP." Next, 

calculate PTE for applicability purposes and actual emissions for fee purposes for each pollutant. Do not 

calculate PTE for air pollutants listed solely for fee purposes. Include all fugitives for fee purposes. You may 

round to the nearest tenth of a ton for yearly values or tenth of a pound for hourly values. 

Air Pollutants 

Emission Rates 

CAS No. 

 Actual 

 Annual 

 Emissions 

 (tons/yr) 

Potential to Emit 

 Hourly 

 (lb/hr) 

 Annual 

 (tons/yr) 

NOx 

0.86 

14.37 2.40* 

VOC 0.03 

0.50 0.05* 

CO 

0.02 

0.31 0.05 

SOx 

0.00 

0.24 0.04 

PM/PM10 

0.01 

0.12 0.02 

*The OP currently limits NOx and VOC emissions from the facility as a whole to not more than 18.7 

tons per year for each pollutant (OP Requirement II.A.3) 

EPA Form 5900-84 
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION CALCULATIONS (EMISS)

Calculate potential to emit (PTE) for applicability purposes and actual emissions for fee purposes for 

each emissions unit, control device, or alternative operating scenario identified in section I of form GIS. 

If form FEE does not need to be submitted with the application, do not calculate actual emissions. 

A. Emissions Unit ID __EG-6___________ 

B. Identification and Quantification of Emissions 

First, list each air pollutant that is either regulated at the unit or present in major amounts, then list any other 

regulated pollutant (for fee calculation) not already listed. HAP may be simply listed as "HAP." Next, 

calculate PTE for applicability purposes and actual emissions for fee purposes for each pollutant. Do not 

calculate PTE for air pollutants listed solely for fee purposes. Include all fugitives for fee purposes. You may 

round to the nearest tenth of a ton for yearly values or tenth of a pound for hourly values. 

Air Pollutants 

Emission Rates 

CAS No. 

 Actual 

 Annual 

 Emissions 

 (tons/yr) 

Potential to Emit 

 Hourly 

 (lb/hr) 

 Annual 

 (tons/yr) 

NOx 

0.75 

14.37 2.40* 

VOC 0.03 

0.50 0.05* 

CO 

0.02 

0.31 0.05 

SOx 

0.00 

0.24 0.04 

PM/PM10 

0.01 

0.12 0.02 

*The OP currently limits NOx and VOC emissions from the facility as a whole to not more than 18.7 

tons per year for each pollutant (OP Requirement II.A.3) 

EPA Form 5900-84 
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71) 

EMISSION CALCULATIONS (EMISS)

Calculate potential to emit (PTE) for applicability purposes and actual emissions for fee purposes for 

each emissions unit, control device, or alternative operating scenario identified in section I of form GIS. 

If form FEE does not need to be submitted with the application, do not calculate actual emissions. 

A. Emissions Unit ID __EG-7___________ 

B. Identification and Quantification of Emissions 

First, list each air pollutant that is either regulated at the unit or present in major amounts, then list any other 

regulated pollutant (for fee calculation) not already listed. HAP may be simply listed as "HAP." Next, 

calculate PTE for applicability purposes and actual emissions for fee purposes for each pollutant. Do not 

calculate PTE for air pollutants listed solely for fee purposes. Include all fugitives for fee purposes. You may 

round to the nearest tenth of a ton for yearly values or tenth of a pound for hourly values. 

Air Pollutants 

Emission Rates 

CAS No. 

 Actual 

 Annual 

 Emissions 

 (tons/yr) 

Potential to Emit 

 Hourly 

 (lb/hr) 

 Annual 

 (tons/yr) 

NOx 

1.22 

14.37 2.40* 

VOC 0.04 

0.50 0.05* 

CO 

0.03 

0.31 0.05 

SOx 

0.00 

0.24 0.04 

PM/PM10 

0.01 

0.12 0.02 

*The OP currently limits NOx and VOC emissions from the facility as a whole to not more than 18.7 

tons per year for each pollutant (OP Requirement II.A.3) 

EPA Form 5900-84 
 OMB No. 2060-0336, Approval Expires 09/30/2010

Federal Operating Permit Program (40 CFR Part 71)

 

POTENTIAL TO EMIT (PTE)

For each unit with emissions that count towards applicability, list the emissions unit ID and the PTE for 

the air pollutants listed below and sum them up to show totals for the facility. You may find it helpful to 

complete form EMISS before completing this form. Show other pollutants not listed that are present in 

major amounts at the facility on attachment in a similar fashion. You may round values to the nearest 

tenth of a ton. Also report facility totals in section J of form GIS. 

 

Emissions Unit ID 

Regulated Air Pollutants and Pollutants for which the Source is Major 

(tons/yr) 

 NOx 

 

 VOC SO2 PM10 CO 

 

 Lead Formaldehyde 

EG-1, SCR-1, and OC-1 2.47 2.47 0.24 0.89 9.90 N/A 1.48 

EG-2, SCR-2, and OC-2 

2.47 2.47 0.24 0.89 9.90 N/A 1.48 

EG-3, SCR-3, and OC-3 2.47 2.47 0.24 0.89 9.90 N/A 1.48 

EG-4, SCR-4, and OC-4 2.47 2.47 0.24 0.89 9.90 N/A 1.48 

EG-5 2.40 0.05 0.04 0.02 0.05 N/A N/A 

EG-6 2.40 0.05 0.04 0.02 0.05 N/A N/A 

EG-7 2.40 0.05 0.04 0.02 0.05 N/A N/A 

FACILTY TOTALS 

EPA Form 5900-85