Facility _Information

facility _id utility

_code legal_owner_nam e

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 676 10623 City

of Lakeland Lakeland Electric

operator 501 E. Lem on St. Lakeland FL 33801

Page 1Facility _Information

plant_nam e

physical_address

phyical_city

physical_state

physical_zip

ma iling_address

ma iling_city

ma iling_state

ma iling_zip C D McIntosh Jr

3030 E. Lake Parker Dr.

Lakeland FL 33805-9513 3030 E. Lake Parker Dr.

Lakeland FL 33805-9513

Page 2Facility _Information

RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas Don't Know TRUE TRUE TRUE TRUE FALSE TRUE TRUE TRUE

Page 3Facility _Information

ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note TRUE TRUE Violations m ust be noted in Annual Statements of Compliance sent to State Environmental Protection Agency and EPA. State agency must be notified of violations within 24 hours from occurrence. Violations of Compliance Assurance Plans may require submittal of corrective action plan to State agency

. No CEMS data for Units 1, 2, and 3 are submitted to CAMD through EDR quarterly reports. CO emissions are reported to the Florida Department of Environmental Protection for Unit 3. 1. NOx: 3-hour averaging time for compliance2. SO2: 3-hour averaging time for compliance3. Coal shipments are averaged on a monthly basis per EICR-019 of FAQ EPA ICR Web Page. See Comment: EICR-019 - How do I account for a facility with num erous fuel shipments over the last 12 months but with limited fuel HAP analysis results?  W hile EPA has stated that it only requires fuel shipment information as it coincides with HAP analyses we have further considered the comments received and the data needed for Part II “Fuel Shipment Information” section of the Electronic ICR and have developed the following guidance for respondents entering these shipment and/or analysis data. For respondents with: Fuel shipment data available but with no direct HAP analyses of any shipment - Include monthly totals of shipment tonnages (1 total tonnage for each month of operation) and related fuel type information only. To accomplish this you would need to fill out the "Fuel Shipm ent Information" tab only. This tab

Page 4Facility _Information

1. NOx: 3-hour averaging time for compliance2. SO2: 3-hour averaging time for compliance3. Coal shipments are averaged on a monthly basis per EICR-019 of FAQ EPA ICR Web Page. See Comment: EICR-019 - How do I account for a facility with num erous fuel shipments over the last 12 months but with limited fuel HAP analysis results?  W hile EPA has stated that it only requires fuel shipment information as it coincides with HAP analyses we have further considered the comments received and the data needed for Part II “Fuel Shipment Information” section of the Electronic ICR and have developed the following guidance for respondents entering these shipment and/or analysis data. For respondents with: Fuel shipment data available but with no direct HAP analyses of any shipment - Include monthly totals of shipment tonnages (1 total tonnage for each month of operation) and related fuel type information only. To accomplish this you would need to fill out the "Fuel Shipm ent Information" tab only. This tab

Page 5Facility _Information

1. NOx: 3-hour averaging time for compliance2. SO2: 3-hour averaging time for compliance3. Coal shipments are averaged on a monthly basis per EICR-019 of FAQ EPA ICR Web Page. See Comment: EICR-019 - How do I account for a facility with num erous fuel shipments over the last 12 months but with limited fuel HAP analysis results?  W hile EPA has stated that it only requires fuel shipment information as it coincides with HAP analyses we have further considered the comments received and the data needed for Part II “Fuel Shipment Information” section of the Electronic ICR and have developed the following guidance for respondents entering these shipment and/or analysis data. For respondents with: Fuel shipment data available but with no direct HAP analyses of any shipment - Include monthly totals of shipment tonnages (1 total tonnage for each month of operation) and related fuel type information only. To accomplish this you would need to fill out the "Fuel Shipm ent Information" tab only. This tab

Page 6Facility _Information

1. NOx: 3-hour averaging time for compliance2. SO2: 3-hour averaging time for compliance3. Coal shipments are averaged on a monthly basis per EICR-019 of FAQ EPA ICR Web Page. See Comment: EICR-019 - How do I account for a facility with num erous fuel shipments over the last 12 months but with limited fuel HAP analysis results?  W hile EPA has stated that it only requires fuel shipment information as it coincides with HAP analyses we have further considered the comments received and the data needed for Part II “Fuel Shipment Information” section of the Electronic ICR and have developed the following guidance for respondents entering these shipment and/or analysis data. For respondents with: Fuel shipment data available but with no direct HAP analyses of any shipment - Include monthly totals of shipment tonnages (1 total tonnage for each month of operation) and related fuel type information only. To accomplish this you would need to fill out the "Fuel Shipm ent Information" tab only. This tab

Page 7Facility _Information

1. NOx: 3-hour averaging time for compliance2. SO2: 3-hour averaging time for compliance3. Coal shipments are averaged on a monthly basis per EICR-019 of FAQ EPA ICR Web Page. See Comment: EICR-019 - How do I account for a facility with num erous fuel shipments over the last 12 months but with limited fuel HAP analysis results?  W hile EPA has stated that it only requires fuel shipment information as it coincides with HAP analyses we have further considered the comments received and the data needed for Part II “Fuel Shipment Information” section of the Electronic ICR and have developed the following guidance for respondents entering these shipment and/or analysis data. For respondents with: Fuel shipment data available but with no direct HAP analyses of any shipment - Include monthly totals of shipment tonnages (1 total tonnage for each month of operation) and related fuel type information only. To accomplish this you would need to fill out the "Fuel Shipm ent Information" tab only. This tab

Page 8Facility _Information

1. NOx: 3-hour averaging time for compliance2. SO2: 3-hour averaging time for compliance3. Coal shipments are averaged on a monthly basis per EICR-019 of FAQ EPA ICR Web Page. See Comment: EICR-019 - How do I account for a facility with num erous fuel shipments over the last 12 months but with limited fuel HAP analysis results?  W hile EPA has stated that it only requires fuel shipment information as it coincides with HAP analyses we have further considered the comments received and the data needed for Part II “Fuel Shipment Information” section of the Electronic ICR and have developed the following guidance for respondents entering these shipment and/or analysis data. For respondents with: Fuel shipment data available but with no direct HAP analyses of any shipment - Include monthly totals of shipment tonnages (1 total tonnage for each month of operation) and related fuel type information only. To accomplish this you would need to fill out the "Fuel Shipm ent Information" tab only. This tab

Page 9Facility _Information

1. NOx: 3-hour averaging time for compliance2. SO2: 3-hour averaging time for compliance3. Coal shipments are averaged on a monthly basis per EICR-019 of FAQ EPA ICR Web Page. See Comment: EICR-019 - How do I account for a facility with num erous fuel shipments over the last 12 months but with limited fuel HAP analysis results?  W hile EPA has stated that it only requires fuel shipment information as it coincides with HAP analyses we have further considered the comments received and the data needed for Part II “Fuel Shipment Information” section of the Electronic ICR and have developed the following guidance for respondents entering these shipment and/or analysis data. For respondents with: Fuel shipment data available but with no direct HAP analyses of any shipment - Include monthly totals of shipment tonnages (1 total tonnage for each month of operation) and related fuel type information only. To accomplish this you would need to fill out the "Fuel Shipm ent Information" tab only. This tab

Page 10Facility _Information

1. NOx: 3-hour averaging time for compliance2. SO2: 3-hour averaging time for compliance3. Coal shipments are averaged on a monthly basis per EICR-019 of FAQ EPA ICR Web Page. See Comment: EICR-019 - How do I account for a facility with num erous fuel shipments over the last 12 months but with limited fuel HAP analysis results?  W hile EPA has stated that it only requires fuel shipment information as it coincides with HAP analyses we have further considered the comments received and the data needed for Part II “Fuel Shipment Information” section of the Electronic ICR and have developed the following guidance for respondents entering these shipment and/or analysis data. For respondents with: Fuel shipment data available but with no direct HAP analyses of any shipment - Include monthly totals of shipment tonnages (1 total tonnage for each month of operation) and related fuel type information only. To accomplish this you would need to fill out the "Fuel Shipm ent Information" tab only. This tab

Page 11Facility _Information

1. NOx: 3-hour averaging time for compliance2. SO2: 3-hour averaging time for compliance3. Coal shipments are averaged on a monthly basis per EICR-019 of FAQ EPA ICR Web Page. See Comment: EICR-019 - How do I account for a facility with num erous fuel shipments over the last 12 months but with limited fuel HAP analysis results?  W hile EPA has stated that it only requires fuel shipment information as it coincides with HAP analyses we have further considered the comments received and the data needed for Part II “Fuel Shipment Information” section of the Electronic ICR and have developed the following guidance for respondents entering these shipment and/or analysis data. For respondents with: Fuel shipment data available but with no direct HAP analyses of any shipment - Include monthly totals of shipment tonnages (1 total tonnage for each month of operation) and related fuel type information only. To accomplish this you would need to fill out the "Fuel Shipm ent Information" tab only. This tab

Page 12Facility _Information

1. NOx: 3-hour averaging time for compliance2. SO2: 3-hour averaging time for compliance3. Coal shipments are averaged on a monthly basis per EICR-019 of FAQ EPA ICR Web Page. See Comment: EICR-019 - How do I account for a facility with num erous fuel shipments over the last 12 months but with limited fuel HAP analysis results?  W hile EPA has stated that it only requires fuel shipment information as it coincides with HAP analyses we have further considered the comments received and the data needed for Part II “Fuel Shipment Information” section of the Electronic ICR and have developed the following guidance for respondents entering these shipment and/or analysis data. For respondents with: Fuel shipment data available but with no direct HAP analyses of any shipment - Include monthly totals of shipment tonnages (1 total tonnage for each month of operation) and related fuel type information only. To accomplish this you would need to fill out the "Fuel Shipm ent Information" tab only. This tab

Page 13Facility _Information

1. NOx: 3-hour averaging time for compliance2. SO2: 3-hour averaging time for compliance3. Coal shipments are averaged on a monthly basis per EICR-019 of FAQ EPA ICR Web Page. See Comment: EICR-019 - How do I account for a facility with num erous fuel shipments over the last 12 months but with limited fuel HAP analysis results?  W hile EPA has stated that it only requires fuel shipment information as it coincides with HAP analyses we have further considered the comments received and the data needed for Part II “Fuel Shipment Information” section of the Electronic ICR and have developed the following guidance for respondents entering these shipment and/or analysis data. For respondents with: Fuel shipment data available but with no direct HAP analyses of any shipment - Include monthly totals of shipment tonnages (1 total tonnage for each month of operation) and related fuel type information only. To accomplish this you would need to fill out the "Fuel Shipm ent Information" tab only. This tab

Page 14facility _contacts

facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 676 1 Environm ental Engineer Bret Galbraith

8638348180 bret.galbraith@lakelandelectric.com TRUE

Page 15facility _coal_utilized

facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note 676 bitum inous 100 100 676 petroleum coke 0 0

Page 16facility _oil_utilized

facility _id oil_type percentage_volume percentage_btu

other_type 676 No.2 Fuel Oil (distillate) 0 0 676 No.6 Fuel Oil (residual or bunker C) 100 100

Page 17facility _other_materials

facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain 676 mu nicipal solid waste

TRUE FALSE 0 tons/year Yes This is already solid waste. 676 propane TRUE FALSE 0 num ber/year No This is a gas - N/A

Page 18facility _other_materials

rcra_explain This is already

solid waste. This is a gas - N/A

Page 19boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuelheat_input max_heat_input MWe_capacity 676 1 Wall firing - opposed firing Dry Bottom fuel oil 985 985 90 676 2 Wall firing - front firing Dry Bottom fuel oil 1184.5 1184.5 114.7 676 3 Wall firing - opposed firing Dry Bottom coal 3640 3640 364

Page 20boiler_information

MWe_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 80 88.82 85 1890 1800 1005 1000 FALSE 1005 106 91 90 1890 1800 1005 1000 FALSE 1005 342 88.82 88 2640 2400 1005 1005 FALSE 1005

Page 21boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 1000 598.06 2 N FALSE FALSE 1000 1687.7 7 Subpart D FALSE FALSE 1005 7367.31 75 Subpart D FALSE

Page 22boiler_information

NOx_control

SO2_control

combustion_additives No No No No No No Yes No Yes

Page 23boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 676 1 natural gas 2007 99.9995 63.95 676 1 natural gas 2008 100 95.72 676 1 natural gas 2009 100 99.78 676 1 oil - other 2007 0 0.25 On-specification used oil 676 1 oil - other 2008 0 0.08 On-specification used oil 676 1 oil - other 2009 0 0 On-specification used oil 676 1 oil - residual or bunker 2007 0.0005 35.8 676 1 oil - residual or bunker 2008 0 4.2 676 1 oil - residual or bunker 2009 0 0.22 676 2 natural gas 2007 100 97.88 676 2 natural gas 2008 100 97.77 676 2 natural gas 2009 100 97.87 676 2 oil - distillate 2007 0 0 676 2 oil - distillate 2008 0 0 676 2 oil - distillate 2009 0 0 676 2 oil - residual or bunker 2007 0 2.12 676 2 oil - residual or bunker 2008 0 2.23 676 2 oil - residual or bunker 2009 0 2.13 676 3 coal - bituminous2007 46 99.57 676 3 coal - bituminous2008 65 99.88 676 3 coal - bituminous2009 19 99.28 676 3 natural gas 2007 54 0.19 676 3 natural gas 2008 35 0.09 676 3 natural gas 2009 81 0.72 676 3 petroleum coke 2007 0 0.24 676 3 petroleum coke 2008 0 0.03 676 3 petroleum coke 2009 0 0

Page 24boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online 676 3 Low NOx Burner 5/1/2007 676 3 Overfire Air 5/1/2007

Page 25boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online

Page 26boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online 676 3 Dry

sorbent injection for SO3 control

11/1/2009

Page 27facility _units

facility _id unit_id 676 1 676 2 676 3

Page 28unit_boilers

facility _id unit_id boiler_id 676 1 1 676 2 2 676 3 3

Page 29facility _controls

facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 676 NOx SCR NOx control Selective Cataly

tic Reduction FALSE 11/1/2009 Am monia 676 PM ESP PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 9/1/1982 676 SORBENT Other control Dry sorbent injection FALSE 11/1/2009 676 SRUB 3 SO2 control Spray type FALSE 9/1/1982

Page 30facility _controls

reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

Lim estone No

Page 31facility _sampling_ports

facility _id sampling_port_id 676 SP 001 676 SP 002 676 SP 003

Page 32facility _stacks

facility _id stack_id stack_height stack_diameter

sack_gas_velocity 676 Stack 1 676 Stack 2 676 Stack 3

Page 33configurations

facility _id configuration_id 676 Unit 1 676 Unit 2 676 Unit 3

Page 34configuration_components

facility _id configuration_id

component_id

order component_type port_near 676 Unit 1 1 1 Unit 676 Unit 1 SP 001 3 Sam pling Port pevious 676 Unit 1 Stack 1 2 Stack 676 Unit 2 2 1 Unit 676 Unit 2 SP 003 3 Sam pling Port pevious 676 Unit 2 Stack 2 2 Stack 676 Unit 3 3 1 Unit 676 Unit 3 NOx SCR 2 NOx control 676 Unit 3 PM ESP 4 PM control 676 Unit 3 SORBENT 3 Other control 676 Unit 3 SP 003 7 Sam pling Port pevious 676 Unit 3 SRUB 3 5 SO2 control 676 Unit 3 Stack 3 6 Stack

Page 35configuration_pollutants1

facility _id configuration_id

pollutant_nam e

permit_type_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 676 Unit 1 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

3 hours 0.3 pound per million British Thermal Unit (lb/MMBtu) 676 Unit 1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

2.75 pound per million British Thermal Unit (lb/MMBtu)

3 hours 676 Unit 2 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

3 hours 676 Unit 2 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

0.8 pound per million British Thermal Unit (lb/MMBtu)

3 hours 676 Unit 2 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.2 pound per million British Thermal Unit (lb/MMBtu)

3 hours 0.3 pound per million British Thermal Unit (lb/MMBtu) 676 Unit 3 PM (Filterable) Fderal - Title V Operating Permit

0.044 pound per million British Thermal Unit (lb/MMBtu)

3 hours 0.05 pound per million British Thermal Unit (lb/MMBtu) 676 Unit 3 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

0.8 pound per million British Thermal Unit (lb/MMBtu)

3 hours 1.2 pound per million British Thermal Unit (lb/MMBtu) 676 Unit 3 Carbon Monoxide (CO) Federal - Federal Operating Permit

0.2 pound per million British Thermal Unit (lb/MMBtu)

30 days 676 Unit 3 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.2 pound per million British Thermal Unit (lb/MMBtu)

3 hours 0.3 pound per million British Thermal Unit (lb/MMBtu)

Page 36configuration_pollutants1

avg_period_2

em lim it_3 em lim it_units_3 avg_period_3

em lim it_4 em lim it_units_4 avg_period_4

em lim it_details

test_method 3 hours The lower limit is for steady state operation of the boiler while the second and higher limit is for soot blowing. EPA Methods 17, 5, 5B, or 5F Show com pliance by

accepting a liquid fuel sulfur limit that wil be verified with a fuel analysis provided by the vendor or the permittee upon each fuel delivery

. EPA Methods 17, 5, 5B, or 5F

3 hours Lim its: 0.20 lb/MMBtu for gaseous fuels; 0.30 lb/MMBtu for liquid fuels 3 hours 0.07 pound per million British Thermal Unit (lb/MMBtu) 3 hours 0.075 pound per million British Thermal Unit (lb/MMBtu) 3 hours 0.044 lb/MMBtu - lim it for coal and coal/petcoke0.050 lb/MMBtu - limit for coal/MSWand coal/petcoke/MSW 0.070 lb/MMBtu - lim it for fuel oil0.075 lb/MMBtu - limit for fuel oil/MSW EPA Methods 17, 5, 5B, or 5F 3 hours 0.80 lb/MMBtu - lim it for liquid fossil fuel1.20 lb/MMBtu - limit for solid fossil fuelSO2 (limit) for combination of solid/liquid fuels - [y(340) + z(520)]/(y+z) where y and z are percentages of heat input for liquid and solid fossil fuels respect

3 hours 0.7 pound per million British Thermal Unit (lb/MMBtu) 3 hours 0.20 lb/MMBtu - lim it for gaseous fuels0.30 lb/MMBtu - limit for liquid fuels0.70 lb/MMBtu - limit for solid fuels

Page 37configuration_pollutants1

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping

req_reporting EPA Methods 17, 5, 5B, or 5F No Annual compliance testing is required if liquid fuel is combusted for more than 400 hours/yr. Hours on liquid fuel.

Annual Operating Reports (AORs) submitted to FDEP. Title V air fees are submitted to FDEP. Show com pliance by

accepting a liquid fuel sulfur limit that wil be verified with a fuel analyss provided by the vendor or the permittee upon each fuel delivery

. No The permittee elected to demonstrate compliance by accepting a liquid fuel sulfur limit that will be verified with a fuel analysis provided by the vendor or the permittee upon each fuel delivery. Acid Rain CEMS Quarterly EDR submittals to EPA. Retain delivery

manifests for 5 years. Acid Rain CEMS has QA/QC manual and log book requirements. Annual Operating Reports (AORs) submitted to FDEP. Title V air fees are submitted to FDEP. EPA Methods 17, 5, 5B, or 5F No Annual compliance testing is required if liquid fuel is combusted for more than 400 hours/yr. Hours on liquid fuel.

Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. No The permittee elected to demonstrate compliance by accepting a liquid fuel sulfur limit that will be verified with a fuel analysis provided by the vendor or the permittee upon each fuel delivery. Acid Rain CEMS Quarterly EDR submittals to EPA. Retain delivery

manifests for 5 years. Acid Rain CEMS has QA/QC manual and log book requirements. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Lim its: 0.20 lb/MMBtu for gaseous fuels; 0.30 lb/MMBtu for liquid fuels No Annual compliance testing required. Acid Rain CEMS has QA/QC manual and log book requirements.

Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. EPA Methods 17, 5, 5B, or 5F Yes The ESP on Unit 3 has an original initial collection efficiency of 99.6%. Monitor Opacity

under a CAM plan; 1-hour opacity lim it as surrogate for PM. Maintain stack test results for 5 years.

Annual Operating Reports (AORs) submitted to FDEP.Title V air fees are submitted to FDEP. Opacity CAM Plan for PM; have to report semi-annual CAM plan review. 0.80 lb/MMBtu - lim it for liquid fossil fuel1.20 lb/MMBtu - limit for solid fossil fuelSO2 (limit) for combination of solid/liquid fuels - [y(340) + z(520)]/(y+z) where y and z are percentages of heat input for liquid and solid fossil fuels respect No Acid Rain Program monitoring requirements. Annual stack testing requirement. SO2 discharged to the atmosphere from the boiler shall not exceed 10% of the potential combustion concentration (90% reduction), or 35% of the potential combustion concetration (65 % reduction) when emissions are less than 0.75 lb/MMBtu heat input. Compliance with the percent reduction shall be determined on a 30-day rolling average. Acid Rain CEMS has QA/QC manual and log book requirements.

Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Quarterly excess emission reporting to State. No 30-day rolling average. Annual stack testing requirement. 30-day continuous rolling average. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly excess emission reporting to State. 0.20 lb/MMBtu - lim it for gaseous fuels0.30 lb/MMBtu - limit for liquid fuels0.70 lb/MMBtu - limit for solid fuels Yes There is a guarantee from the manufacturer of our SCR system for an SCR outlet NOx concentration of 30 ppm. Acid Rain Program monitoring requirements. Annual stack testing requirement.

Acid Rain CEMS has QA/QC manual and log book requirements.

Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Quarterly excess emission reporting to State.

Page 38configuration_pollutants1

Annual Operating Reports (AORs) submitted to FDEP. Title V air fees are submitted to FDEP. Annual Operating Reports (AORs) submitted to FDEP. Title V air fees are submitted to FDEP. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Annual Operating Reports (AORs) submitted to FDEP.Title V air fees are submitted to FDEP. Opacity CAM Plan for PM; have to report semi-annual CAM plan review. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Quarterly excess emission reporting to State. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly excess emission reporting to State. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Quarterly excess emission reporting to State.

Page 39configuration_pollutants1

Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Annual Operating Reports (AORs) submitted to FDEP.Title V air fees are submitted to FDEP. Opacity CAM Plan for PM; have to report semi-annual CAM plan review. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Quarterly excess emission reporting to State. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly excess emission reporting to State. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Quarterly excess emission reporting to State.

Page 40configuration_pollutants1

Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA.

Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Quarterly excess emission reporting to State. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly excess emission reporting to State. Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Quarterly excess emission reporting to State.

Page 41configuration_pollutants1

Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Quarterly excess emission reporting to State.

Annual Operating Reports (AORs) submitted to FDEP. If excess emissions occur, Lakeland Electric must contact the local State Department office within 24 hours of the event with a description of the event and corrective measures (if any required). Title V air fees are submitted to FDEP. Quarterly EDR submittal to EPA. Quarterly excess emission reporting to State.

Page 42control_technologies

facility _id configuration_id

component_id

control_id project_titleproject_type vendor_name

vndor_contact

vendor_phone

Page 43control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 44control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 45control_technologies

feed_rate_units

Page 46control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 47control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_nam e

Page 48control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investm ent

total_operating_costs

base_year

Page 49control_costs

CBI

Page 50misc_controls

facility _id misc_control_id

control_description

Page 51misc_control_configurations

facility _id misc_control_id

configuration_id

Page 52fuel_shipments

facility _id shipment_id

shipment_date

am ount_received

am ount_units

fuel_type state_country other_country

county 676 April Sum ma ry

4/1/2009 50367 short tons (2000 lbs) coal 676 Aug. Sum mary

8/1/2009 72365.28 short tons (2000 lbs) coal 676 Dec. 2009 12/1/2009 50886.6 short tons (2000 lbs) coal 676 Feb Summary

2/1/2009 72828.1 short tons (2000 lbs) coal 676 January

Sum mary 1/1/2009 61358.03 short tons (2000 lbs) coal 676 July Sum mary

7/1/2009 61102.63 short tons (2000 lbs) coal 676 June Summary

6/1/2009 41335.71 short tons (2000 lbs) coal 676 March Summary

3/1/2009 72226.78 short tons (2000 lbs) coal 676 May Sum ma ry

5/1/2009 71150.63 short tons (2000 lbs) coal 676 Nov. 2009 11/1/2009 62467.34 short tons (2000 lbs) coal 676 Oct. 2009 10/1/2009 72035.63 short tons (2000 lbs) coal 676 Sept. 2009 9/1/2009 71150.63 short tons (2000 lbs) coal

Page 53fuel_shipments

coal_seam shipment_method

Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train

Page 54fuel_shipment_configurations

facility _id shipment_id

configuration_id 676 April Sum ma ry

Unit 3 676 Aug. Sum mary

Unit 3 676 Dec. 2009 Unit 3 676 Feb Summary

Unit 3 676 January

Sum mary Unit 3 676 July Sum mary Unit 3 676 June Summary

Unit 3 676 March Summary

Unit 3 676 May Sum ma ry Unit 3 676 Nov. 2009 Unit 3 676 Oct. 2009 Unit 3 676 Sept. 2009 Unit 3

Page 55fuel_shipment_samples

facility _id shipment_id

sample_id am ount_fuel am ount_fuel_units

total_sulfur ash_content heating_value

hating_units 676 April Sum ma ry

1 10451.9 tons 1.18 12.32 13188 Btu/lb 676 April Sum ma ry

2 10658.6 tons 1.27 10.09 13339 Btu/lb 676 April Sum ma ry

3 9173.8 tons 1.2 11.2 13366 Btu/lb 676 April Sum ma ry

4 10599.1 tons 1.2 11.24 13321 Btu/lb 676 April Sum ma ry

5 9483.6 tons 1.14 11.56 13264 Btu/lb 676 Aug. Sum mary

1 10629.75 tons 1.13 11.47 13225 Btu/lb 676 Aug. Sum mary

2 10457 tons 1.2 10.97 13286 Btu/lb 676 Aug. Sum mary

3 10427.8 tons 1.31 13392 Btu/lb 676 Aug. Sum mary

4 10442.5 tons 1.26 13.51 12687 Btu/lb 676 Aug. Sum mary

5 10395.6 tons 1.25 9.75 13422 Btu/lb 676 Aug. Sum mary

6 10482.13 tons 1.77 12.6 13107 Btu/lb 676 Dec. 2009 1 10909.35 tons 1.2 10.48 13225 Btu/lb 676 Dec. 2009 2 10008.4 tons 1.22 10.23 13405 Btu/lb 676 Dec. 2009 3 10528.63 tons 1.33 9.42 13363 Btu/lb 676 Dec. 2009 4 9617.3 tons 1.52 13.13 13315 Btu/lb 676 Dec. 2009 5 9822.92 tons 0.81 10.29 13410 Btu/lb 676 Feb Summary

1 9684.1 tons 0.84 10.47 13343 Btu/lb 676 Feb Summary

2 10634.3 tons 1.35 11.74 13320 Btu/lb 676 Feb Summary

3 10274 tons 1.09 10.02 13401 Btu/lb 676 Feb Summary

4 10380.5 tons 1.09 10.02 13401 Btu/lb 676 Feb Summary

5 10324.3 tons 1.1 10.59 13281 Btu/lb 676 January

Sum mary 1 11368.83 tons 85 10.59 13592 Btu/lb 676 January

Sum mary 2 10107.4 tons 1.18 8.95 13733 Btu/lb 676 January

Sum mary 3 9874.7 tons 1.32 10.3 13547 Btu/lb 676 January

Sum mary 4 10205.15 tons 1.68 6.45 14239 Btu/lb 676 January

Sum mary 5 9695.25 tons 0.92 11.25 13145 Btu/lb 676 January

Sum mary 6 10106.7 tons 1.18 9.25 13601 Btu/lb 676 July Sum mary 1 10569.2 tons 1.27 10.39 13281 Btu/lb 676 July Sum mary 2 10315.8 tons 1.47 10.49 13291 Btu/lb 676 July Sum mary 3 10284.3 tons 1.17 9.02 13605 Btu/lb 676 July Sum mary 4 10343.8 tons 1.24 9.28 13640 Btu/lb 676 July Sum mary 5 9480.5 tons 1.28 12.31 13274 Btu/lb 676 July Sum mary 6 10109.03 tons 1.31 10.87 13181 Btu/lb 676 June Summary

1 10514.58 tons 1.46 11.55 13178 Btu/lb 676 June Summary

2 10465.3 tons 1.32 11.3 676 March Summary

1 10057.5 tons 1.16 10.39 13371 Btu/lb 676 March Summary

2 10452.85 tons 1.25 10.24 13595 Btu/lb 676 March Summary

3 10589.9 tons 1.24 9.94 13514 Btu/lb 676 Nov. 2009 1 9993.1 tons 1.29 10.49 13311 Btu/lb 676 Nov. 2009 2 10547.83 tons 1.94 11.59 13029 Btu/lb 676 Nov. 2009 3 10268 tons 1.3 11.43 13209 Btu/lb 676 Nov. 2009 4 10622.94 tons 1.34 9.38 13406 Btu/lb 676 Nov. 2009 5 10485.48 tons 1.27 9 13449 Btu/lb 676 Oct. 2009 1 10392.4 tons 1.18 9 13552 Btu/lb 676 Oct. 2009 2 9885.9 tons 1.16 12.27 12925 Btu/lb 676 Oct. 2009 3 10083.75 tons 1.91 11.9 13105 Btu/lb 676 Oct. 2009 4 10330.9 tons 1.23 10.06 13387 Btu/lb 676 Oct. 2009 5 10499.65 tons 1.48 9.69 13638 Btu/lb 676 Oct. 2009 6 10832.3 tons 1.17 10.25 13491 Btu/lb 676 Oct. 2009 7 10010.73 tons 1.08 10.61 13229 Btu/lb 676 Sept. 2009 1 10429.8 tons 1.37 10.06 13480 Btu/lb

Page 56fuel_shipment_samples

676 Sept. 2009 2 9810.425 tons 1.02 10.19 13220 Btu/lb 676 Sept. 2009 3 10186.4 tons 1.24 10.49 13222 Btu/lb 676 Sept. 2009 4 9840.4 tons 1.26 10.44 13219 Btu/lb 676 Sept. 2009 5 10763.58 tons 1.15 9.91 13219 Btu/lb 676 Sept. 2009 6 9559.28 tons 1.6 10.32 13183 Btu/lb 676 Sept. 2009 7 10560.75 tons 1.38 10.97 13136 Btu/lb

Page 57fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address 2000 parts per million (dry) (ppm) standard operational procedures Other standard operational procedures Other standard operational procedures Other standard operational procedures Other 2181 parts per million (dry) (ppm) standard operational procedures Other 148 parts per million (dry) (ppm) standard operational procedures Other 1589 parts per million (dry) (ppm) standard operational procedures Other 590 parts per million (dry) (ppm) standard operational procedures Other 269 parts per million (dry) (ppm) standard operational procedures Other 237 parts per million (dry) (ppm) standard operational procedures Other 1332 parts per million (dry) (ppm) standard operational procedures Other 196 parts per million (dry) (ppm) standard operational procedures Other 177 parts per million (dry) (ppm) standard operational procedures Other 211 parts per million (dry) (ppm) standard operational procedures Other 1079 parts per million (dry) (ppm)

standard operational procedures Other 980 parts per million (dry) (ppm) 91 parts per million (dry) (ppm)

standard operational procedures Other 1100 parts per million (dry) (ppm) standard operational procedures Other 1600 parts per million (dry) (ppm) standard operational procedures Other 1000 parts per million (dry) (ppm) standard operational procedures Other 1000 parts per million (dry) (ppm) standard operational procedures Other 1000 parts per million (dry) (ppm) standard operational procedures Other 1900 parts per million (dry) (ppm) standard operational procedures Other

. 1200 parts per million (dry) (ppm) standard operational procedures Other 1800 parts per million (dry) (ppm) standard operational procedures Other 1000 parts per million (dry) (ppm) standard operational procedures Other 900 parts per million (dry) (ppm) standard operational procedures Other 1000 parts per million (dry) (ppm) standard operational procedures Other 225 parts per million (dry) (ppm) standard operational procedures Other 1511 parts per million (dry) (ppm) standard operational procedures Other 147 parts per million (dry) (ppm) standard operational procedures Other 209 parts per million (dry) (ppm) standard operational procedures Other 2007 parts per million (dry) (ppm) standard operational procedures Other 185 parts per million (dry) (ppm) standard operational procedures Other 1324 parts per million (dry) (ppm) standard operational procedures Other standard operational procedures Other standard operational procedures Other standard operational procedures Other 1400 parts per million (dry) (ppm) standard operational procedures Other 179 parts per million (dry) (ppm) standard operational procedures Other 860 parts per million (dry) (ppm) standard operational procedures Other 231 parts per million (dry) (ppm) standard operational procedures Other 1259 parts per million (dry) (ppm) standard operational procedures Other 350 parts per million (dry) (ppm) standard operational procedures Other 196 parts per million (dry) (ppm) standard operational procedures Other 182 parts per million (dry) (ppm) standard operational procedures Other 766 parts per million (dry) (ppm) standard operational procedures Other 198 parts per million (dry) (ppm) standard operational procedures Other 835 parts per million (dry) (ppm) standard operational procedures Other 173 parts per million (dry) (ppm) standard operational procedures Other 580 parts per million (dry) (ppm) 52 parts per million (dry) (ppm)

standard operational procedures Other 218 parts per million (dry) (ppm) standard operational procedures Other

Page 58fuel_shipment_samples

227 parts per million (dry) (ppm) standard operational procedures Other 186 parts per million (dry) (ppm) standard operational procedures Other 171 parts per million (dry) (ppm) standard operational procedures Other 152 parts per million (dry) (ppm) standard operational procedures Other 1228 parts per million (dry) (ppm) standard operational procedures Other 131 parts per million (dry) (ppm) standard operational procedures Other

Page 59fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_nam e lab_address lab_city lab_state lab_zip analysis_copies Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No

Page 60fuel_shipment_samples

Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No Mineral Labs, Inc.

P.O. Box 549

Salyersville KY 41465 No

Page 61fuel_shipment_samples

analysis_copies

Page 62fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL 676 April Sum ma ry

1 Mercury

(Hg) 0.1037 parts per million (dry) (ppm) FALSE 676 April Sum ma ry

2 Mercury

(Hg) 0.1 parts per million (dry) (ppm) FALSE 676 April Sum ma ry

3 Mercury

(Hg) 0.0872 parts per million (dry) (ppm) FALSE 676 April Sum ma ry

4 Mercury

(Hg) 0.0947 parts per million (dry) (ppm) FALSE 676 Aug. Sum mary

1 Mercury

(Hg) 0.06 parts per million (dry) (ppm) FALSE 676 Aug. Sum mary

2 Mercury

(Hg) 0.09 parts per million (dry) (ppm) FALSE 676 Aug. Sum mary

3 Mercury

(Hg) 0.06 parts per million (dry) (ppm) FALSE 676 Aug. Sum mary

4 Mercury

(Hg) 0.09 parts per million (dry) (ppm) FALSE 676 Aug. Sum mary

5 Mercury

(Hg) 0.08 parts per million (dry) (ppm) FALSE 676 Aug. Sum mary

6 Mercury

(Hg) 0.09 parts per million (dry) (ppm) FALSE 676 Dec. 2009 1 Mercury (Hg) 0.07 parts per million (dry) (ppm) FALSE 676 Dec. 2009 2 Mercury (Hg) 0.06 parts per million (dry) (ppm) FALSE 676 Dec. 2009 3 Mercury (Hg) 0.06 parts per million (dry) (ppm) FALSE 676 Dec. 2009 4 Mercury (Hg) 0.1 parts per million (dry) (ppm) FALSE 676 Dec. 2009 5 Mercury (Hg) 0.07 parts per million (dry) (ppm) FALSE 676 Feb Summary

1 Mercury

(Hg) 0.04 parts per million (dry) (ppm) FALSE 676 Feb Summary

2 Mercury

(Hg) 0.09 parts per million (dry) (ppm) FALSE 676 Feb Summary

3 Mercury

(Hg) 0.11 parts per million (dry) (ppm) FALSE 676 Feb Summary

4 Mercury

(Hg) 0.11 parts per million (dry) (ppm) FALSE 676 Feb Summary

5 Mercury

(Hg) 0.1 parts per million (dry) (ppm) FALSE 676 January

Sum mary 1 Mercury

(Hg) 0.09 parts per million (dry) (ppm) FALSE 676 January

Sum mary 2 Mercury

(Hg) 0.1 parts per million (dry) (ppm) FALSE 676 January

Sum mary 3 Mercury

(Hg) 0.1 parts per million (dry) (ppm) FALSE 676 January

Sum mary 4 Mercury

(Hg) 0.11 parts per million (dry) (ppm) FALSE 676 January

Sum mary 5 Mercury

(Hg) 0.07 parts per million (dry) (ppm) FALSE 676 January

Sum mary 6 Mercury

(Hg) 0.1 parts per million (dry) (ppm) FALSE 676 July Sum mary 1 Mercury

(Hg) 0.09 parts per million (dry) (ppm) FALSE 676 July Sum mary 2 Mercury

(Hg) 0.09 parts per million (dry) (ppm) FALSE 676 July Sum mary 3 Mercury

(Hg) 0.09 parts per million (dry) (ppm) FALSE 676 July Sum mary 4 Mercury

(Hg) 0.08 parts per million (dry) (ppm) FALSE 676 July Sum mary 5 Mercury

(Hg) 0.08 parts per million (dry) (ppm) FALSE 676 July Sum mary 6 Mercury

(Hg) 0.09 parts per million (dry) (ppm) FALSE 676 June Summary

1 Mercury

(Hg) 0.051 parts per million (dry) (ppm) FALSE 676 June Summary

2 Mercury

(Hg) 0.09 parts per million (dry) (ppm) FALSE 676 March Summary

1 Mercury

(Hg) 0.09 parts per million (dry) (ppm) FALSE 676 March Summary

2 Mercury

(Hg) 0.06 parts per million (dry) (ppm) FALSE 676 March Summary

3 Mercury

(Hg) 0.1 parts per million (dry) (ppm) FALSE 676 Nov. 2009 1 Mercury (Hg) 0.08 parts per million (dry) (ppm) FALSE 676 Nov. 2009 2 Mercury (Hg) 0.07 parts per million (dry) (ppm) FALSE 676 Nov. 2009 3 Mercury (Hg) 0.13 parts per million (dry) (ppm) FALSE 676 Nov. 2009 4 Mercury (Hg) 0.08 parts per million (dry) (ppm) FALSE 676 Nov. 2009 5 Mercury (Hg) 0.05 parts per million (dry) (ppm) FALSE 676 Oct. 2009 1 Mercury (Hg) 0.09 parts per million (dry) (ppm) FALSE 676 Oct. 2009 2 Mercury (Hg) 0.06 parts per million (dry) (ppm) FALSE 676 Oct. 2009 3 Mercury (Hg) 0.11 parts per million (dry) (ppm) FALSE 676 Oct. 2009 4 Mercury (Hg) 0.07 parts per million (dry) (ppm) FALSE 676 Oct. 2009 5 Mercury (Hg) 0.1 parts per million (dry) (ppm) FALSE 676 Oct. 2009 6 Mercury (Hg) 0.11 parts per million (dry) (ppm) FALSE 676 Oct. 2009 7 Mercury (Hg) 0.06 parts per million (dry) (ppm) FALSE 676 Sept. 2009 1 Mercury (Hg) 0.08 parts per million (dry) (ppm) FALSE 676 Sept. 2009 2 Mercury (Hg) 0.12 parts per million (dry) (ppm) FALSE

Page 63fuel_sample_pollutants

676 Sept. 2009 3 Mercury (Hg) 0.13 parts per million (dry) (ppm) FALSE 676 Sept. 2009 4 Mercury (Hg) 0.01 parts per million (dry) (ppm) FALSE 676 Sept. 2009 5 Mercury (Hg) 0.05 parts per million (dry) (ppm) FALSE 676 Sept. 2009 6 Mercury (Hg) 0.07 parts per million (dry) (ppm) FALSE 676 Sept. 2009 7 Mercury (Hg) 0.09 parts per million (dry) (ppm) FALSE

Page 64test_reports

facility _id report_id report_type other_type report_description report_begin_date

report_end_date

before_control

during_deviation 676 U1-061707-SB

compliance Particulate Matter - Steady State 6/17/2007 6/17/2007 No No 676 U1-061707-SS

compliance Particulate Matter - EPA Method 17 6/17/2007 6/17/2007 No No 676 U1-062105-SB

compliance Particulate Matter - Soot Blowing 6/21/2005 6/21/2005 No No 676 U1-062105-SS

compliance Particulate Matter - Steady State 6/21/2005 6/21/2005 No No 676 U1-062106-SB

compliance Particulate Matter 6/21/2006 6/21/2006 No No 676 U1-062106-SS

compliance Particulate Matter - Steady State 6/21/2006 6/21/2006 No No 676 U2-061407 compliance Particulate Matter and NOx Compliance Test 6/14/2007 6/14/2007 No No 676 U2-061505 compliance Annual Com pliance Test - PM and NOx 6/15/2005 6/15/2005 No No 676 U2-062006 compliance Particulate Matter and NOx Compliance Test 6/20/2006 6/20/2006 No No 676 U2-070109 compliance NOx Compliance 7/1/2009 7/1/2009 No No 676 U3-011807 compliance Particulate Matter, NOx, and SO2 1/18/2007 1/18/2007 No No 676 U3-060608 compliance Particulate Matter, NOx, and SO2 6/6/2008 6/6/2008 No No 676 U3-060906 compliance Particulate Matter, NOx, and SO2 6/9/2006 7/8/2006 No No 676 U3-061705 compliance Particulate Matter, NOx, and SO2 6/17/2005 6/17/2005 No No 676 U3-063009 compliance Particulate Matter, NOx, and SO2 6/30/2009 6/30/2009 No No 676 U3-100107 compliance LNB and OFA Testing 10/2/2007 10/2/2007 No No

Page 65test_reports

deviation_reports No No No No No No No No No No No No No No No No

Page 66test_report_configurations

facility _id report_id configuration_id 676 U1-061707-SB

Unit 1 676 U1-061707-SS

Unit 1 676 U1-062105-SB

Unit 1 676 U1-062105-SS

Unit 1 676 U1-062106-SB

Unit 1 676 U1-062106-SS

Unit 1 676 U2-061407 Unit 2 676 U2-061505 Unit 2 676 U2-062006 Unit 2 676 U2-070109 Unit 2 676 U3-011807 Unit 3 676 U3-060608 Unit 3 676 U3-060906 Unit 3 676 U3-061705 Unit 3 676 U3-063009 Unit 3 676 U3-100107 Unit 3

Page 67test_report_fuels

facility _id report_id fuel_id 676 U1-061707-SB

#6 Fuel Oil 676 U1-061707-SS

#6 Fuel Oil 676 U1-062105-SB

#6 Fuel Oil 676 U1-062105-SS

#6 Fuel Oil 676 U1-062106-SB

#6 Fuel Oil 676 U1-062106-SS

#6 Fuel Oil 676 U2-061407 #6 Fuel Oil 676 U2-061505 #6 Fuel Oil 676 U2-062006 #6 Fuel Oil 676 U2-070109 #2 Fuel Oil and Nat. Gas 676 U3-011807 coal and petcoke 676 U3-060608 Coal and Petcoke 676 U3-060906 Coal and Petcoke 676 U3-061705 Coal and petcoke 676 U3-063009 Coal 676 U3-100107 Coal

Page 68test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 676 U1-061707-SB

#6 Fuel Oil oil - residual or bunker 100 100 676 U1-061707-SS

#6 Fuel Oil oil - residual or bunker 100 100 676 U1-062105-SB

#6 Fuel Oil oil - residual or bunker 100 100 676 U1-062105-SS

#6 Fuel Oil oil - residual or bunker 100 100 676 U1-062106-SB

#6 Fuel Oil oil - residual or bunker 100 100 676 U1-062106-SS

#6 Fuel Oil oil - residual or bunker 100 100 676 U2-061407 #6 Fuel Oil oil - residual or bunker 100 100 676 U2-061505 #6 Fuel Oil oil - residual or bunker 100 100 676 U2-062006 #6 Fuel Oil oil - residual or bunker 100 100 676 U2-070109 #2 Fuel Oil and Nat. Gas natural gas 99.995 85 676 U2-070109 #2 Fuel Oil and Nat. Gas oil - residual or bunker

0.005 15 676 U3-011807 coal and petcoke coal - bituminous 85 85 676 U3-011807 coal and petcoke petroleum coke 15 15 676 U3-060608 Coal and Petcoke coal - bituminous 85 85 676 U3-060608 Coal and Petcoke petroleum coke 15 15 676 U3-060906 Coal and Petcoke coal - bituminous 85 85 676 U3-060906 Coal and Petcoke petroleum coke 15 15 676 U3-061705 Coal and petcoke coal - bituminous 85 85 676 U3-061705 Coal and petcoke petroleum coke 15 15 676 U3-063009 Coal coal - bituminous 100 100 676 U3-100107 Coal coal - bituminous 100 100

Page 69cem_data

facility _id tim e_period

cem_period_description 676 1/1/2005-Current

Weshould have copies of any certified CEMS data required under Acid Rain Regulations for Units 1, 2, and 3 for SO2 and NOx. CO emissions are reported to the Florida Department of Environmental Protection for Unit 3. 676 12/6/07-Current

Wehave certified CO CEMS data for Unit 3.

Page 70cem_data

Weshould have copies of any certified CEMS data required under Acid Rain Regulations for Units 1, 2, and 3 for SO2 and NOx. CO emissions are reported to the Florida Department of Environmental Protection for Unit 3.

Page 71cem_data

Weshould have copies of any certified CEMS data required under Acid Rain Regulations for Units 1, 2, and 3 for SO2 and NOx. CO emissions are reported to the Florida Department of Environmental Protection for Unit 3.

Page 72cem_data_pollutants1

facility _id tim e_period

pollutant_nam e 676 1/1/2005-Current

Sulfur Dioxide (SO2) 676 1/1/2005-Current

Nitrogen Oxide (NOx) 676 12/6/07-Current

Carbon Monoxide (CO)

Page 73test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent 676 U1-061707-SB

Stack 1 No No 676 U1-061707-SS

Stack 1 No No 676 U1-062105-SB

Stack 1 No No 676 U1-062105-SS

Stack 1 No No 676 U1-062106-SB

Stack 1 No No 676 U1-062106-SS

Stack 1 No No 676 U2-061407 Stack 2 No No 676 U2-061505 Stack 2 No No 676 U2-062006 Stack 2 No No 676 U2-070109 Stack 2 No No 676 U3-011807 Stack 3 No No 676 U3-060608 Stack 3 No No 676 U3-060906 Stack 3 No No 676 U3-061705 Stack 3 No No 676 U3-063009 Stack 3 No No 676 U3-100107 Stack 3 No No

Page 74test_report_sampling

fg_fraction

Page 75sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetim e

unit_load net_generation fg_moisture_content 676 U1-061707-SB

Stack 1 1 6/17/2007 6/17/2007 82 73 13.8 676 U1-061707-SB

Stack 1 2 6/17/2007 6/17/2007 82 73 16.3 676 U1-061707-SB

Stack 1 3 6/17/2007 6/17/2007 83 73 17.4 676 U1-061707-SS

Stack 1 1 6/17/2007 6/17/2007 81 72 16.3 676 U1-061707-SS

Stack 1 2 6/17/2007 6/17/2007 82 73 16.4 676 U1-061707-SS

Stack 1 3 6/17/2007 6/17/2007 83 73 16.4 676 U1-062105-SB

Stack 1 1 6/21/2005 6/21/2005 84 75 9.1 676 U1-062105-SB

Stack 1 2 6/21/2005 6/21/2005 87 77 8.8 676 U1-062105-SB

Stack 1 3 6/21/2005 6/21/2005 89 79 9.5 676 U1-062105-SS

Stack 1 1 6/21/2005 6/21/2005 85 76 9.2 676 U1-062105-SS

Stack 1 2 6/21/2005 6/21/2005 85 76 9 676 U1-062105-SS

Stack 1 3 6/21/2005 6/21/2005 90 80 8.9 676 U1-062106-SB

Stack 1 1 6/21/2006 6/21/2006 83 74 10.9 676 U1-062106-SB

Stack 1 2 6/21/2006 6/21/2006 82 73 10.9 676 U1-062106-SB

Stack 1 3 6/21/2006 6/21/2006 83 74 10.9 676 U1-062106-SS

Stack 1 1 6/21/2006 6/21/2006 83 74 8.2 676 U1-062106-SS

Stack 1 2 6/21/2006 6/21/2006 84 75 11.9 676 U1-062106-SS

Stack 1 3 6/21/2006 6/21/2006 82 73 10.4 676 U2-061407 Stack 2 1 6/14/2007 6/14/2007 108 100 9.86 676 U2-061407 Stack 2 2 6/14/2007 6/14/2007 106 99 9.16 676 U2-061407 Stack 2 3 6/14/2007 6/14/2007 107 100 9.45 676 U2-061505 Stack 2 1 6/15/2005 6/15/2005 109 101 9.55 676 U2-061505 Stack 2 2 6/15/2005 6/15/2005 110 102 9.63 676 U2-061505 Stack 2 3 6/15/2005 6/15/2005 110 102 9.71 676 U2-061505 Stack 2 4 6/15/2005 6/15/2005 110 102 9.55 676 U2-061505 Stack 2 5 6/15/2005 6/15/2005 110 102 9.63 676 U2-061505 Stack 2 6 6/15/2005 6/15/2005 110 102 9.71 676 U2-062006 Stack 2 1 6/20/2006 6/20/2006 104 97 8.53 676 U2-062006 Stack 2 2 6/20/2006 6/20/2006 104 97 10.92 676 U2-062006 Stack 2 3 6/20/2006 6/20/2006 104 97 10.89 676 U2-070109 Stack 2 1 7/1/2009 7/1/2009 100 93 11.8 676 U2-070109 Stack 2 2 7/1/2009 7/1/2009 100 93 11.8 676 U2-070109 Stack 2 3 7/1/2009 7/1/2009 100 93 11.8 676 U3-011807 Stack 3 1 1/18/2007 1/18/2007 362 336.66 10.5 676 U3-011807 Stack 3 2 1/18/2007 1/18/2007 362 336.66 10.9 676 U3-011807 Stack 3 3 1/18/2007 1/18/2007 362 336.66 10.8 676 U3-060608 Stack 3 1 6/6/2008 6/6/2008 365 338 9.8 676 U3-060608 Stack 3 2 6/6/2008 6/6/2008 365 338 9.8 676 U3-060608 Stack 3 3 6/6/2008 6/6/2008 365 338 9.7 676 U3-060906 Stack 3 1 6/9/2006 6/9/2006 363 337.59 11.8 676 U3-060906 Stack 3 2 6/9/2006 6/9/2006 363 337.59 11.5 676 U3-060906 Stack 3 3 6/9/2006 6/9/2006 363 337.59 10.7 676 U3-060906 Stack 3 4 7/7/2006 7/7/2006 361 335.73 11.23 676 U3-060906 Stack 3 5 7/7/2006 7/7/2006 361 335.73 11.41 676 U3-060906 Stack 3 6 7/8/2006 7/8/2006 360 334.8 11.99 676 U3-061705 Stack 3 1 6/17/2005 6/17/2005 364 338 10.5 676 U3-061705 Stack 3 2 6/17/2005 6/17/2005 364 338 9.2 676 U3-061705 Stack 3 3 6/17/2005 6/17/2005 364 338 9.3 676 U3-063009 Stack 3 1 6/30/2009 6/30/2009 365 338 10.7 676 U3-063009 Stack 3 2 6/30/2009 6/30/2009 365 338 12 676 U3-063009 Stack 3 3 6/30/2009 6/30/2009 365 338 11.1

Page 76sampling_runs

676 U3-100107 Stack 3 1 10/2/2007 10/2/2007 364 338 11.6 676 U3-100107 Stack 3 2 10/2/2007 10/2/2007 363 337.59 14.65 676 U3-100107 Stack 3 3 10/2/2007 10/2/2007 361 335.73 12.71

Page 77sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 192231 dscfm 81 1 5.4 12.3 272 196656 dscfm 90 1 5.5 12.2 276 193396 dscfm 97 1 5.5 12.2 281 201406 dscfm 99 1 5.5 12.2 283 200785 dscfm 102 1 6 12 285 200125 dscfm 96 1 5.8 12 285 231269 dscfm 109 1 6.8 11 263 228026 dscfm 100 1 6.6 11.3 268 227404 dscfm 98 1 6.1 11.7 269 231419 dscfm 92 1 6 11.1 263 230659 dscfm 95 1 6.2 11.1 265 226513 dscfm 102 1 6 11.8 272 214532 dscfm 104 1 8.1 10 268 216780 dscfm 99 1 8.2 9.9 270 217610 dscfm 104 1 8.1 9.9 270 219802 dscfm 91 1 7.9 10 260 211965 dscfm 104 1 7.9 10 265 217018 dscfm 107 1 8 10.1 272 214349 dscfm 75 1 6.2 12.1 188 212185 dscfm 91 1 6.2 12.2 192 212156 dscfm 100 1 6.2 12.1 194 240521 dscfm 106 1 5.9 11.5 202 243901 dscfm 105 1 5.5 11.6 203 245170 dscfm 105 1 5.6 11.5 213 240521 dscfm 106 1 5.9 11.6 202 243901 dscfm 105 1 5.9 11.5 203 245170 dscfm 105 1 6 11.5 213 241538 dscfm 98 1 5.7 12.1 207 235213 dscfm 98 1 5.9 12 211 242205 dscfm 104 1 5.8 12 217 213335 dscfm 92 1 6.4 9.5 215 212458 dscfm 95 1 6.4 9.5 215 213485 dscfm 94 1 6.4 9.5 213 896797 dscfm 66 1 8.8 10.7 170 888156 dscfm 72 1 8.8 10.7 170 888586 dscfm 78 1 8.8 10.8 170 927747 dscfm 92 1 7.8 12.2 150 924336 dscfm 87 1 7.8 12.2 150 922957 dscfm 83 1 7.5 12.5 150 931137 dscfm 85 1 7 12.2 162 934832 dscfm 89 1 7 12.1 164 935235 dscfm 103 1 7.1 12.1 164 899689 dscfm 85 1 9.4 10.8 92 920813 dscfm 89 1 9.4 10.9 91 906044 dscfm 103 1 9.2 10.8 88 908371 dscfm 88 1 7.6 11.6 166 1036941 dscfm 98 1 7.5 11.8 166 1000364 dscfm 97 1 7.4 11.8 166 896845 dscfm 83 1 8 11.7 157 892299 dscfm 80 1 8 11 156 900080 dscfm 80 1 8 11.7 156

Page 78sampling_runs

75.6 1 7.51 11.81 148.8 83.9 1 7.72 11.65 151.5 91.8 1 7.76 11.62 149.4

Page 79sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1.02 EPA Method 17 and EPA Method 7E 0.986 EPA Method 17 and EPA Method 7E 0.986 EPA Method 17 and EPA Method 7E 1 EPA Method 17 1 EPA Method 17 1 EPA Method 17 1 EPA Method 7E 1 EPA Method 7E 1 EPA Method 7E 1 EPA Method 17 and EPA Method 7E 1 EPA Method 17 and EPA Method 7E 1 EPA Method 17 and EPA Method 7E 1 EPA Method 7E 1 EPA Method 7E 1 EPA Method 7E 1 EPA Methods 5, 3A, 6C, 7E PM/NOx/SO2 1 EPA Methods 5, 3A, 6C, 7E PM/NOx/SO2 1 EPA Methods 5, 3A, 6C, 7E PM/NOx/SO2 1 EPA Methods 5, 3A, 6C, 7E - PM/NOx/SO2 1 EPA Methods 5, 3A, 6C, 7E - PM/NOx/SO2 1 EPA Methods 5, 3A, 6C, 7E - PM/NOx/SO2 1 EPA Method 5 1 EPA Method 5 1 EPA Method 5 1 EPA Methods 3A, 6C, 7E - NOx/SO2 1 EPA Methods 3A, 6C, 7E - NOx/SO2 1 EPA Methods 3A, 6C, 7E - NOx/SO2 0.99 EPA Method 5, 3A, 6C, 7E 0.99 EPA Method 5, 3A, 6C, 7E 0.99 EPA Method 5, 3A, 6C, 7E 1 EPA Test Methods 5, 3A, 6C, 7E - PM/NOx/SO2 1 EPA Test Methods 5, 3A, 6C, 7E - PM/NOx/SO2 1 EPA Test Methods 5, 3A, 6C, 7E - PM/NOx/SO2

Page 80sampling_runs

1 EPA Methods 3A, 7E, 10 - NOx/CO 1 EPA Methods 3A, 7E, 10 - NOx/CO 1 EPA Methods 3A, 7E, 10 - NOx/CO

Page 81sampling_runs

fuel_sulfur

Page 82sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_nam e conc conc_units conc_ND conc_MDL 676 U1-061707-SS

Stack 1 1 PM (Filterable) FALSE 676 U1-062106-SB

Stack 1 1 PM (Filterable) FALSE 676 U1-062106-SS

Stack 1 1 PM (Filterable) FALSE 676 U1-062105-SS

Stack 1 1 PM (Filterable) FALSE 676 U1-062105-SB

Stack 1 1 PM (Filterable) FALSE 676 U1-062105-SB

Stack 1 2 PM (Filterable) FALSE 676 U1-062105-SB

Stack 1 3 PM (Filterable) FALSE 676 U1-062105-SS

Stack 1 2 PM (Filterable) FALSE 676 U1-062105-SS

Stack 1 3 PM (Filterable) FALSE 676 U1-062106-SS

Stack 1 2 PM (Filterable) FALSE 676 U1-062106-SS

Stack 1 3 PM (Filterable) FALSE 676 U1-062106-SB

Stack 1 2 PM (Filterable) FALSE 676 U1-062106-SB

Stack 1 3 PM (Filterable) FALSE 676 U1-061707-SS

Stack 1 2 PM (Filterable) FALSE 676 U1-061707-SS

Stack 1 3 PM (Filterable) FALSE 676 U1-061707-SB

Stack 1 1 PM (Filterable) FALSE 676 U1-061707-SB

Stack 1 2 PM (Filterable) FALSE 676 U1-061707-SB

Stack 1 3 PM (Filterable) FALSE 676 U2-061505 Stack 2 1 PM (Filterable) FALSE 676 U2-061505 Stack 2 2 PM (Filterable) FALSE 676 U2-061505 Stack 2 3 PM (Filterable) FALSE 676 U2-061505 Stack 2 4 Nitrogen Oxide (NOx) FALSE 676 U2-061505 Stack 2 5 Nitrogen Oxide (NOx) FALSE 676 U2-061505 Stack 2 6 Nitrogen Oxide (NOx) FALSE 676 U2-062006 Stack 2 1 PM (Filterable) FALSE 676 U2-062006 Stack 2 1 Nitrogen Oxide (NOx) FALSE 676 U2-062006 Stack 2 2 PM (Filterable) FALSE 676 U2-062006 Stack 2 2 Nitrogen Oxide (NOx) FALSE 676 U2-062006 Stack 2 3 PM (Filterable) FALSE 676 U2-062006 Stack 2 3 Nitrogen Oxide (NOx) FALSE 676 U2-061407 Stack 2 1 PM (Filterable) FALSE 676 U2-061407 Stack 2 1 Nitrogen Oxide (NOx) FALSE 676 U2-061407 Stack 2 2 PM (Filterable) FALSE 676 U2-061407 Stack 2 2 Nitrogen Oxide (NOx) FALSE 676 U2-061407 Stack 2 3 PM (Filterable) FALSE 676 U2-061407 Stack 2 3 Nitrogen Oxide (NOx) FALSE 676 U2-070109 Stack 2 1 Nitrogen Oxide (NOx) FALSE 676 U2-070109 Stack 2 2 Nitrogen Oxide (NOx) FALSE 676 U2-070109 Stack 2 3 Nitrogen Oxide (NOx) FALSE 676 U3-061705 Stack 3 1 PM (Filterable) FALSE 676 U3-061705 Stack 3 1 Nitrogen Oxide (NOx) FALSE 676 U3-061705 Stack 3 1 Sulfur Dioxide (SO2) FALSE 676 U3-061705 Stack 3 2 PM (Filterable) FALSE 676 U3-061705 Stack 3 2 Nitrogen Oxide (NOx) FALSE 676 U3-061705 Stack 3 2 Sulfur Dioxide (SO2) FALSE 676 U3-060906 Stack 3 1 PM (Filterable) FALSE 676 U3-060906 Stack 3 2 PM (Filterable) FALSE 676 U3-060906 Stack 3 3 PM (Filterable) FALSE 676 U3-060906 Stack 3 4 Nitrogen Oxide (NOx) FALSE 676 U3-060906 Stack 3 4 Sulfur Dioxide (SO2) FALSE 676 U3-060906 Stack 3 5 Nitrogen Oxide (NOx) FALSE

Page 83sampling_run_pollutants1

676 U3-060906 Stack 3 5 Sulfur Dioxide (SO2) FALSE 676 U3-060906 Stack 3 6 Nitrogen Oxide (NOx) FALSE 676 U3-060906 Stack 3 6 Sulfur Dioxide (SO2) FALSE 676 U3-011807 Stack 3 1 PM (Filterable) FALSE 676 U3-011807 Stack 3 1 Nitrogen Oxide (NOx) FALSE 676 U3-011807 Stack 3 1 Sulfur Dioxide (SO2) FALSE 676 U3-011807 Stack 3 2 PM (Filterable) FALSE 676 U3-011807 Stack 3 2 Nitrogen Oxide (NOx) FALSE 676 U3-011807 Stack 3 2 Sulfur Dioxide (SO2) FALSE 676 U3-011807 Stack 3 3 PM (Filterable) FALSE 676 U3-011807 Stack 3 3 Nitrogen Oxide (NOx) FALSE 676 U3-011807 Stack 3 3 Sulfur Dioxide (SO2) FALSE 676 U3-060608 Stack 3 1 PM (Filterable) FALSE 676 U3-060608 Stack 3 1 Nitrogen Oxide (NOx) FALSE 676 U3-060608 Stack 3 1 Sulfur Dioxide (SO2) FALSE 676 U3-060608 Stack 3 2 PM (Filterable) FALSE 676 U3-060608 Stack 3 2 Nitrogen Oxide (NOx) FALSE 676 U3-060608 Stack 3 2 Sulfur Dioxide (SO2) FALSE 676 U3-060608 Stack 3 3 PM (Filterable) FALSE 676 U3-060608 Stack 3 3 Nitrogen Oxide (NOx) FALSE 676 U3-060608 Stack 3 3 Sulfur Dioxide (SO2) FALSE 676 U3-063009 Stack 3 1 PM (Filterable) FALSE 676 U3-063009 Stack 3 1 Nitrogen Oxide (NOx) FALSE 676 U3-063009 Stack 3 1 Sulfur Dioxide (SO2) FALSE 676 U3-063009 Stack 3 2 PM (Filterable) FALSE 676 U3-063009 Stack 3 2 Nitrogen Oxide (NOx) FALSE 676 U3-063009 Stack 3 2 Sulfur Dioxide (SO2) FALSE 676 U3-063009 Stack 3 3 PM (Filterable) FALSE 676 U3-063009 Stack 3 3 Nitrogen Oxide (NOx) FALSE 676 U3-063009 Stack 3 3 Sulfur Dioxide (SO2) FALSE 676 U3-100107 Stack 3 1 Nitrogen Oxide (NOx) FALSE 676 U3-100107 Stack 3 1 Carbon Monoxide (CO) FALSE 676 U3-100107 Stack 3 2 Nitrogen Oxide (NOx) FALSE 676 U3-100107 Stack 3 2 Carbon Monoxide (CO) FALSE 676 U3-100107 Stack 3 3 Nitrogen Oxide (NOx) FALSE 676 U3-100107 Stack 3 3 Carbon Monoxide (CO) FALSE 676 U3-061705 Stack 3 3 PM (Filterable) FALSE 676 U3-061705 Stack 3 3 Nitrogen Oxide (NOx) FALSE 676 U3-061705 Stack 3 3 Sulfur Dioxide (SO2) FALSE

Page 84sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment FALSE 0.083 pound per million British Thermal Unit (lb/MMBtu) FALSE steady state FALSE 0.194 pound per million British Thermal Unit (lb/MMBtu) FALSE soot blowing FALSE 0.079 pound per million British Thermal Unit (lb/MMBtu) FALSE steady state FALSE 0.093 pound per million British Thermal Unit (lb/MMBtu) FALSE steady state FALSE 0.138 pound per million British Thermal Unit (lb/MMBtu) FALSE soot blowing FALSE 0.11 pound per million British Thermal Unit (lb/MMBtu) FALSE soot blowing FALSE 0.131 pound per million British Thermal Unit (lb/MMBtu) FALSE soot blowing FALSE 0.1 pound per million British Thermal Unit (lb/MMBtu) FALSE steady state FALSE 0.094 pound per million British Thermal Unit (lb/MMBtu) FALSE steady state FALSE 0.071 pound per million British Thermal Unit (lb/MMBtu) FALSE steady state FALSE 0.065 pound per million British Thermal Unit (lb/MMBtu) FALSE steady state FALSE 0.108 pound per million British Thermal Unit (lb/MMBtu) FALSE soot blowing FALSE 0.089 pound per million British Thermal Unit (lb/MMBtu) FALSE soot blowing FALSE 0.086 pound per million British Thermal Unit (lb/MMBtu) FALSE steady state FALSE 0.094 pound per million British Thermal Unit (lb/MMBtu) FALSE steady state FALSE 0.265 pound per million British Thermal Unit (lb/MMBtu) FALSE soot blowing FALSE 0.198 pound per million British Thermal Unit (lb/MMBtu) FALSE soot blowing FALSE 0.158 pound per million British Thermal Unit (lb/MMBtu) FALSE soot blowing FALSE 0.074 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.079 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.104 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.283 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.283 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.281 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.084 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.257 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.087 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.27 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.088 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.264 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.064 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.242 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.075 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.244 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.079 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.252 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.18 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.181 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.184 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.025 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.485 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.688 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.024 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.485 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.665 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.033 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.01 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.01 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.433 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.453 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.421 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 85sampling_run_pollutants1

FALSE 0.408 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.418 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.433 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.029 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.5 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.583 pound per Gigawatt hour (lb/GW h) FALSE FALSE 0.022 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.506 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.576 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.033 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.512 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.565 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.023 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.297 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.814 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.029 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.293 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.741 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.022 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.294 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.728 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.03 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.277 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.325 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.031 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.287 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.294 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.038 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.29 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.289 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.327 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.0105 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.327 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.0113 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.317 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.0097 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.017 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.479 pound per million British Thermal Unit (lb/MMBtu) FALSE FALSE 0.639 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 86sampling_run_pollutants1

run_pollutant_comment steady state soot blowing steady state steady state soot blowing soot blowing soot blowing steady state steady state steady state steady state soot blowing soot blowing steady state steady state soot blowing soot blowing soot blowing

Page 87sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL

Page 88sampling_run_fuel

fuel_conc_MDL

Page 89