# 1. S. 1 – First page of the permit 

# AIR POLLUTION CONTROL OPERATION PERMIT RENEWAL

EI FACILITY NO: 405043540 PERMIT NO.: 405043540-F20

TYPE: 

# Synthetic minor, non-Part 70

In compliance with the provisions of Chapter 285, Wis. Stats., and Chapters NR 400 to NR 499,

Wis. Adm. Code,

Name of Source: Wisconsin DOA - UW-Green Bay

Street Address: 3260 Gershwin Drive

Green Bay, Wisconsin

Responsible Official, & Title: Mr. Jay Ehrfurth, State Heating Plant Engineer

is authorized to operate a central heating and cooling plant that provides high pressure steam

and chilled water to a major educational university campus via network distribution system of

underground piping. in conformity with the conditions herein.

THIS OPERATION PERMIT EXPIRES February 16, 2015



# A RENEWAL APPLICATION MUST BE SUBMITTED AT LEAST 6 MONTHS, BUT NOT

MORE THAN 18 MONTHS, PRIOR TO THIS EXPIRATION DATE [ss. 285.66(3)(a), Wis.

Stats. and NR 407.04(2), Wis. Adm. Code].

No permittee may continue operation of a source after the operation permit expires,

unless the permittee submits a timely application for renewal of the permit. If you submit

a timely application for renewal, the existing operation permit will not expire until the

renewal application has been finally acted upon by DNR. [ss. 227.51(2), 285.62(8)(b), Wis.

Stats. and NR 407.04(2), Wis. Adm. Code].

This authorization requires compliance by the permit holder with the emission limitations,

monitoring requirements and other terms and conditions set forth in Parts I and II hereof.

Dated at Green Bay, Wisconsin, February 16, 2010

STATE OF WISCONSIN

DEPARTMENT OF NATURAL RESOURCES



# For the Secretary

By /s/ RJW

Rick Wulk

Environmental Engineer

Supervisor

# 2. S. 2 – Preamble 

# PREAMBLE



# An Asterisk (*) throughout this document denotes legal authority, limitations and conditions

which are not federally enforceable.

Concurrent Permit Actions Performed as Part of the Review and Issuance of Permit

405043540-F20.

The following permits, orders, etc., are adopted, under ss. 285.65(3), Wis. Stats., NR

406.11(1)(c) and (d), NR 407.09(2)(d) and NR 407.15(3) and (4), Wis. Adm. Code, by Permit

405043540-F20 which then becomes the primary enforceable document:

04-DCF-301

Permit/Order Number Issuance Date Sources Covered & Description Permits Adopted

MAN-10-SJK-82-05-

023 August 31, 1982 modify and operate boilers B20,

B21, and B22 None

89-MWH-137 March 13, 1990 Boiler B23

405043540-P01 12/05/1996 Total Facility MAN-10-SJK-82-05-023

405043540-P10 11/28/2001 Total Facility 405043540-P01

04-DCF-301 02/01/2005 construction of three (3) new 18.8

MMBTU / hour heat input, natural

gas / distillate oil fired boilers None

405043540-F20 DRAFT Total Facility 04-DCF-301

Stack and Process Index.



# Boiler B20, Stack S10 - Industrial Watertube boiler, Nat. gas / Distillate Oil. 80 mmBtu/hr

Boiler B21, Stack S11 - Industrial Watertube boiler, Nat. gas / Distillate Oil. 80 mmBtu/hr

Boiler B22, Stack S12 - Industrial Watertube boiler, Nat. gas / Distillate Oil. 40 mmBtu/hr

Boiler B24, Stack S14 - Industrial Watertube boilers, Nat. gas / Distillate Oil 18.844 mmBtu/hr

Boiler B25, Stack S15 - Industrial Watertube boilers, Nat. gas / Distillate Oil 18.844 mmBtu/hr

Boiler B26, Stack S16 - Industrial Watertube boilers, Nat. gas / Distillate Oil 18.844 mmBtu/hr

Insignificant Emission Units

Maintenance of Grounds, Equipment, and Bu ildings (lawn care, painting, etc.).:

Boiler, Turbine, and HVAC System Maintenance.:

Internal Combustion Engines Used fo r Warehousing and Material Transport.:

Fire Control Equipment.:

Janitorial Activities.:

Office Activities.:

Convenience Water Heating.:

Fuel Oil Storage Tanks (< 10,000 gal.).:

# Demineralization and Oxygen Scavenging of Water for Boilers.:

Purging of Natural Gas Lines.:

Sanitary Sewer and Plumbing Venting.:

20,000 gallon fuel oil storage tank

Gasoline storage tank

Diesel Storage tank

Art labs and studios, including metal melting furnaces and pottery kilns

Science lab vent hoods

swimming pool chlorination

photgraphic developing

welding labs

wood working

metal working

food preparation

gas and oil storage tanks

emergency electric generators



# Permit Shield — Unless precluded by the Administrator of the US EPA, compliance with all

emission limitations in this operation permit is considered to be compliance with all emission

limitations established under ss. 285.01 to 285.87, Wis. Stats., and emission limitations under

the federal clean air act, that are applicable to the source if the permit includes the applicable

limitation or if the Department determines that the emission limitations do not apply. The

following emission limitations were reviewed in the analysis and preliminary determination and

were determined not to apply to this stationary source: None Part I — The headings for the

areas in the permit are defined below. The legal authority for these limitations or methods

follows them in [brackets].

Pollutant 

# – This area will note which pollutant is being regulated by the permit.

Limitations 

# – This area will list all applicable emission limitations that apply to the source,

including case-by-case limitations such as Latest Available Control Techniques (LACT),

Best Available Control Technology (BACT), or Lowest Achievable Emission Rate (LAER). It

will also list any voluntary restrictions on hours of operation, raw material use, or production

rate requested by the permittee to limit potential to emit.

Compliance Demonstration 

# – The compliance demonstration methods outlined in this area

may be used to demonstrate compliance with the associated emission limit or work practice

standard listed under the corresponding Limitations 

# column. The compliance demonstration

area contains limits on parameters or other me chanisms that will be monitored periodically

to ensure compliance with the limitations. The requirement to test as well as initial and

periodic test schedules, if testing is required, will be stated here. Notwithstanding the

compliance determination methods which the owner or operator of a sources is authorized

# to use under ch. NR 439, Wis. Adm. Code, the Department may use any relevant

information or appropriate method to determine a source’s compliance with applicable

emission limitations.

Reference Test Methods, Recordkeeping, and Monitoring Requirements 

# – Specific US EPA

Reference test methods or other approved test methods will be contained in this area and

are the methods that must be used whenever testing is required. A reference test method

will be listed even if no testing is immediately required. Also included in this area are any

recordkeeping requirements and their frequency and reporting requirements. Accuracy of

monitoring equipment shall meet, at a minimum, the requirements of s. NR 439.055(3) and

(4), Wis. Adm. Code, as specified in Part II of this permit.

Condition Type 

# – This area will specify other conditions that are applicable to the entire

facility that may not be tied to one specific pollutant.

Conditions 

# – Specific conditions usually applicable to the entire facility or compliance

requirements.

Compliance Demonstration 

# – This area contains monitoring and testing requirements and

methods to demonstrate compliance with the conditions.

PART II — This section contains the general limitations that the permittee must abide by. These

requirements are standard for most sources of air pollutants so they are included in this section

with every permit.FID 405043540; Permit No. 405043540-F20 — Final Permit.Page 5 of 15PART IA.Boiler B24, Stack S14; Boiler B25, Stack S15; Boiler B26, Stack S16 — Industrial Watertube boilers 18.844 MMBTU/hr nat. gas; 18.612 MMBTU/hr distillate (#1 or #2)fuel oil (2005). These boilers are subject to NSPS.Pollutanta. Limitationsb. Compliance Demonstrationc. Reference Test Methods, Recordkeeping and MonitoringRequirements1. ParticulateMatterEmissions(1) The permittee shall emit no more than0.05 pounds of particulate matter permillion BTU of heat input (from each unit).[s. 285.65(7), Wis. Stats.; s. NR415.06(2)(a), Wis. Adm. Code, 04-DCF301]1(2)Stack ParametersTheserequirements are included because thesource was reviewed with these stackparameters and it was determined that noincrements or ambient air quality standardswill be violated when constructed asproposed.(a) The stack height shall be at least 44feet above ground level.(b) The stack inside diameter at the outletmay not exceed 2.33 feet.(c) The stack may not be equipped with arainhat or other device which impedes theupward flow of the exhaust gases.[s. 285.65(3), Stats. and s. NR 406.10,Wis. Adm. Code, 04-DCF-301](1) The permittee may only burnnatural gas or distillate (#1 or #2) fueloil in this boiler. [s. NR 406.10, Wis.Adm. Code; s. 285.65(7), Wis. Stats. ,04-DCF-301](2) To demonstrate compliance withthe stack parameters, the permitteeshall maintain the records inI.A.1.c.(3). [s. NR 407.09(4)(a)1.,Wis. Adm. Code](1) Reference Test Method for Particulate MatterEmissions: whenever particulate matter emission testing isrequired, the permittee shalluse U.S. EPA Method 5, 5A,5B, 5D, 5E, 5F, 5G, 5H or 17 including condensiblebackhalf emissions (U.S. EPA Method 202). [s. NR439.06(1), Wis. Adm. Code](2) The permittee shall maintain records of the type andquantity of fuel used in this boiler and the sulfur content ofthe distillate fuel oil purchased. The records shall besummarized monthly. The fuel lines to these boilers shallbe equipped to measure the quantity of fuel (both naturalgas and distillate oil) consumed by B24, B25 and B26 asrequired by the NSPS. [s.NR 407.09(4)(a)1. and s. NR440.207(9)(g), Wis. Adm. Code](3) The permittee shall keep and maintain on sitetechnical drawings, blueprints or equivalent records of thephysical stack parameters. [s. NR 439.04(1)(d), Wis.Adm. Code](4) The permittee shall make the plans and specificationsrequired by this section available on site duringinspections by Department personnel. [s. NR 439.05(1),Wis. Adm. Code]2. VisibleEmissions(1) Emissions of shade or density may notexceed number 1 of the Ringlemann chartor 20% opacity. [ s. NR 431.05, and s. NR440.207(4)(c), Wis. Adm. Code, 04-DCF301](1) The permittee may only burnnatural gas or distillate (#1 or #2) fueloil in this boiler. [s. NR 406.10, Wis.Adm. Code; s. 285.65(7), Wis. Stats.,04-DCF-301](1)Reference Test Method for Visible Emissions:Whenever visible emission testing is required by theDepartment, the permittee shall use U.S. EPA Method 9.[s. NR 439.06(9)(a)1., Wis. Adm. Code](2) See I.A.1.c.(2)1. This limitation is more restrictive than the s. NR 415.06(2)(a), Wis. Adm. Codelimitation of 0.15 pounds per million BTU, and is established to protect theambient air quality standards and increments. This limit of 0.05 pounds per million BTU (0.94 lbs/hour at maximum capacity) may not be exceeded. Theestimated maximum theoretical emissions from the boiler (basedon AP-42 emission factors) while combusting distillate fuel oilis 0.024 pounds per millionBTU.FID 405043540; Permit No. 405043540-F20 — Final Permit.Page 6 of 15A.Boiler B24, Stack S14; Boiler B25, Stack S15; Boiler B26, Stack S16 — Industrial Watertube boilers 18.844 MMBTU/hr nat. gas; 18.612 MMBTU/hr distillate (#1 or #2)fuel oil (2005). These boilers are subject to NSPS.Pollutanta. Limitationsb. Compliance Demonstrationc. Reference Test Methods, Recordkeeping and MonitoringRequirements3. NitrogenOxides(1) 0.10 pounds of Nitrogen Oxides permillion BTU of heat input when firingnatural gas and 0.143 pounds of NitrogenOxides per million BTU of heat input whenfiring distillate fuel oil.2[s. 285.65(3), ands. 285.65(7), Wis. Stats., 04-DCF-301](1) The permittee may only burnnatural gas or distillate (#1 or #2) fueloil in this boiler. [s. NR 406.10, Wis.Adm. Code; s. 285.65(7), Wis. Stats.,04-DCF-301](1)Reference Test Method for Nitrogen CompoundEmissions:Whenever compliance emission testing isrequired, the appropriate US EPA Method; 7, 7A, 7B, 7C,7D or 7E shall be used. [s. NR 439.06(6)(a), Wis. Adm.Code](2) See I.A.1.c.(2)(3) See I.E. 2.4. Sulfurdioxide(1) 0.5 pounds of Sulfur Dioxide per millionBTU of heat input or fuel oil may notcontain more than 0.5 weight percentSulfur. [s. NR 440.207(3)(d), Wis. Adm.Code, 04-DCF-301](2) See I.A.1.a.(2)(3) The sulfur content of the distillate fueloil burned may not exceed 0.15% byweight. [s. 285.65(7), Wis. Stats.; s. NR404.08(2), Wis. Adm. Code, 04-DCF-301](1) The permittee may only burnnatural gas or distillate (#1 or #2) fueloil in this boiler. [s. NR 406.10, and s.NR 440.207(3)(d), Wis. Adm. Code; s.285.65(3), Wis. Stats., 04-DCF-301](2) See I.A.1.b.(2)(3) See I.A.4.c.(3) and (4)(4) The sulfur content of the distillatefuel oil within the storage tank maynot exceed 0.15 wt. percent Sulfur.[s. 285.63(7), Wis. Stats.; s. NR404.08(2), Wis. Adm. Code, 04-DCF301](1)Reference Test Method for Sulfur Dioxide Emissions:(a) Whenever compliance emission testing is required,the appropriate US EPA Method; 6, 6A, 6B, 6C or 8 shallbe used as approved by the Department. [s. NR439.06(2)(a), Wis. Adm. Code](b) Whenever periodic fuel sampling and analysis of fossiland nonfossil fuels is required,it shall be conducted usingthe methods and procedures specified in s. NR 439.08,Wis. Adm. Code. [s. NR 439.06(2)(a), and s. NR 439.08,Wis. Adm. Code](2) See I.A.1.c.(3)(3) The permittee shall maintain records of the type andquantity of fuel used in the boilers (B24, B25, B26) and thesulfur content of the distillate fuel oil purchased. Therecords shall be summarized monthly. The fuel lines tothis boiler shall be equipped to measure the quantity offuel (both natural gas and distillate oil) consumed by eachboiler as required by the NSPS. [s. NR 407.09(4)(a)1., s.NR 439.04, and s. NR 440.207(9)(g), Wis. Adm. Code](4) The NSPS demonstration required under I.A.3.b.(5)shall consist of the certification of the fuel supplier that willinclude:2This condition, along with the facility restrictions on thequantities of natural gas and distillate fuel oil that may be fired, are necessary to assure that thefacility constitutes a synthetic minor source under the TitleV and PSD permit programs. These emission rates are based on theAP-42 emission factors of 100lbs/cf6 for natural gas and 20 lbs/gal3 for distillate oil combustion, in boilers with heat inputs less than 100 MMBTU/hr.FID 405043540; Permit No. 405043540-F20 — Final Permit.Page 7 of 15A.Boiler B24, Stack S14; Boiler B25, Stack S15; Boiler B26, Stack S16 — Industrial Watertube boilers 18.844 MMBTU/hr nat. gas; 18.612 MMBTU/hr distillate (#1 or #2)fuel oil (2005). These boilers are subject to NSPS.Pollutanta. Limitationsb. Compliance Demonstrationc. Reference Test Methods, Recordkeeping and MonitoringRequirements(a) the name of the oil supplied, and(b) a statement from the oil supplier that the oil complieswith the specifications of distillate oil[ss. NR 440.207(5)(h), and NR440.207(9)(f), Wis. Adm.Code](5) The facility shall maintain records of fuel sampling andanalysis of the distillate fuel oil. [s. NR 439.04, Wis. Adm.Code]FID 405043540; Permit No. 405043540-F20 — Final Permit.Page 8 of 15B.Boiler B20, Stack S10; Boiler B21,Stack S11 — INDUSTRIAL, WATERTUBETYPE, Nat. gas / Distillate Oil.80 mmBtu/hr (each) fired with primary fuel natural gasand backup distillate fuel oil, maximum sulfur content of 0.15%.(1982)Pollutanta. Limitationsb. Compliance Demonstrationc. Reference Test Methods, Recordkeeping andMonitoring Requirements1. ParticulateMatter Emissions(1) The permittee shall emit no more than0.05 pounds per millionBTU (per stack).3[s. NR 404.08(2), and s. NR 415.06(2)(a),Wis. Adm. Code, 04-DCF-301](2)Stack ParametersTheserequirements are included because thesource was reviewed with these stackparameters and it was determined that noincrements or ambient air quality standardswill be violated when constructed asproposed.(a) The stack height shall be at least 66feet above ground level.(b) The stack inside diameter at the outletmay not exceed 4.0 feet.(c) The stack may not be equipped with arainhat or other device which impedes theupward flow of the exhaust gases.[s. 285.65(3), Stats. and s. NR 406.10,Wis. Adm. Code, 04-DCF-301](1) The permittee may only burn naturalgas or distillate (#1 or #2) fuel oil in thisboiler. [s. NR 406.10, Wis. Adm. Code; s.285.65(7), Wis. Stats., 04-DCF-301](2) To demonstrate compliance with thestack parameters, the permittee shallmaintain the records in I.B.1.c.(3). [s. NR407.09(4)(a)1., Wis. Adm. Code](1) Reference Test Method for Particulate MatterEmissions: whenever particulate matter emissiontesting is required, the permittee shall use U.S.EPA Method 5, 5A, 5B, 5D, 5E, 5F, 5G, 5H or 17including condensible backhalf emissions (U.S.EPA Method 202). [s. NR 439.06(1), Wis. Adm.Code](2) The permittee shall retain at its headquarters,plans and specifications that indicate the boiler'sfuel usage design capabilities. Nameplateinformation and boiler safety inspection data shallbe considered sufficient to demonstratecompliance for this boiler.[ s. NR 407.09(4)(a)1.,Wis. Adm. Code](3) The permittee shall keep and maintain on sitetechnical drawings, blueprints or equivalentrecords of the physical stack parameters. [s.NR 439.04(1)(d), Wis. Adm. Code](4) The permittee shall make the plans andspecifications required by this section availableon site during inspections by Departmentpersonnel. [s. NR 439.05(1), Wis. Adm. Code]2. VisibleEmissions(1) Emissions of shade or density may notexceed number 1 of the Ringlemann chartor 20% opacity. [ s. NR 431.05,Wis. Adm.Code, 04-DCF-301](1) The permittee may only burn naturalgas or distillate (#1 or #2) fuel oil in thisboiler. [s. NR 406.10, Wis. Adm. Code; s.285.65(7), Wis. Stats., 04-DCF-301](1)Reference Test Method for VisibleEmissions: Whenever visible emission testing isrequired by the Department, the permittee shalluse U.S. EPA Method 9. [s. NR 439.06(9)(a)1.,Wis. Adm. Code](2) See I.B.1.c.(2)3This limitation is more restrictive than the s. NR 415.06(2)(a), Wis. Adm. Codelimitation of 0.15 pounds per million BTU, andwas established to protect theambient air quality standards and increments. This limit of 0.05 pounds per million BTU (4.0 lbs/hour at maximum capacity fromeach boiler) may not beexceeded. The estimated maximum theoretical emissions fromthe boiler (based on AP-42 emission factors) while combusting distillate fuel oil is 0.024pounds per million BTU.FID 405043540; Permit No. 405043540-F20 — Final Permit.Page 9 of 15B.Boiler B20, Stack S10; Boiler B21,Stack S11 — INDUSTRIAL, WATERTUBETYPE, Nat. gas / Distillate Oil.80 mmBtu/hr (each) fired with primary fuel natural gasand backup distillate fuel oil, maximum sulfur content of 0.15%.(1982)Pollutanta. Limitationsb. Compliance Demonstrationc. Reference Test Methods, Recordkeeping andMonitoring Requirements3. Nitrogen Oxides(1) 0.10 pounds of Nitrogen Oxides permillion BTU of heat input when firingnatural gas and 0.143 pounds of NitrogenOxides per million BTU of heat input whenfiring distillate fuel oil.4[s. 285.65(3), ands. 285.65(7), Wis. Stats., 04-DCF-301](1) The permittee may only burn naturalgas or distillate (#1 or #2) fuel oil in thisboiler. [s. NR 406.10, Wis. Adm. Code; s.285.65(7), Wis. Stats., 04-DCF-301](1)Reference Test Method for NitrogenCompound Emissions:Whenever complianceemission testing is required, the appropriate USEPA Method; 7, 7A, 7B, 7C, 7D or 7E shall beused. [s. NR 439.06(6)(a), Wis. Adm. Code](2) See I.B.1.c.(2)(3) See I. E. 2.4. Sulfur dioxide(1) The sulfur content of the distillate fueloil burned may not exceed 0.15% byweight. [s. 285.65(7), Wis. Stats.; s. NR404.08(2), Wis. Adm. Code, 04-DCF-301](2) See I.B.1.a.(2)(1) The permittee may only burn naturalgas or distillate (#1 or #2) fuel oil in thisboiler. [s. NR 406.10, and s. NR440.207(3)(d), Wis. Adm. Code; s.285.65(3), Wis. Stats., 04-DCF-301](2) The sulfur content of the distillate fueloil within the storage tank may not exceed0.15 wt. percent Sulfur. [s. 285.65(7),Wis. Stats.; s. NR 404.08(2), Wis. Adm.Code, 04-DCF-301](3) See I.B.1.b.(2)(4) See I.B.4.c.(3)(1)Reference Test Method for Sulfur DioxideEmissions:(a) Whenever compliance emissiontesting is required, the appropriate US EPAMethod; 6, 6A, 6B, 6C or 8 shall be used asapproved by the Department. [s. NR439.06(2)(a), Wis. Adm. Code](b) Whenever periodic fuel sampling and analysisof fossil and nonfossil fuels is required, it shall beconducted using the methods and proceduresspecified in s. NR 439.08, Wis. Adm. Code. [s.NR 439.06(2)(a), and s. NR 439.08, Wis. Adm.Code](2) See I.B.1.c.(3)(3) The permittee shall maintain records of thetype and quantity of fuel used in these boilers(B20, B21) and the sulfurcontent of the distillatefuel oil purchased. The records shall besummarized monthly.. [s. NR 407.09(4)(a)1., ands. NR 439.04, Wis. Adm. Code](4) The facility shall maintain records of fuelsampling and analysis of the distillate fuel oil. [s.NR 439.04, Wis. Adm. Code]4This condition, along with the facility restrictions on thequantities of natural gas and distillate fuel oil that may be fired, are necessary to assure that thefacility constitutes a synthetic minor source under the TitleV and PSD permit programs. These emission rates are based on theAP-42 emission factors of 100lbs/cf6 for natural gas and 20 lbs/gal3 for distillate oil combustion, in boilers with heat inputs less than 100 MMBTU/hr.FID 405043540; Permit No. 405043540-F20 — Final Permit.Page 10 of 15C.Boiler B22, Stack S12; — INDUSTRIAL, WATERTUBE TYPE, Nat. gas / Distillate Oil.40 mmBtu/hr fired with primary fuel natural gas and backup distillate fuel oil,maximum sulfur content of 0.15%.(1982)Pollutanta. Limitationsb. Compliance Demonstrationc. Reference Test Methods, Recordkeeping andMonitoring Requirements1. ParticulateMatter Emissions(1) The permittee shall emit no more0.05 pounds per million BTU (perstack).5. [s. NR 404.08(2), and s. NR415.06(2)(a), Wis. Adm. Code, 04-DCF-301](2)Stack ParametersTheserequirements are included becausethe source was reviewed with thesestack parameters and it wasdetermined that no increments orambient air quality standards will beviolated when constructed asproposed.(a) The stack height shall be at least66 feet above ground level.(b) The stack inside diameter at theoutlet may not exceed 3.0 feet.(c) The stack may not be equippedwith a rainhat or other device whichimpedes the upward flow of theexhaust gases.[s. 285.65(3), Stats. and s. NR406.10, Wis. Adm. Code, 04-DCF301](1) The permittee may only burn natural gas ordistillate (#1 or #2) fuel oil in this boiler. [s. NR406.10, Wis. Adm. Code; s. 285.65(7), Wis.Stats., 04-DCF-301](2) To demonstrate compliance with the stackparameters, the permittee shall maintain therecords in I.C.1.c.(3).[s. NR 407.09(4)(a)1.,Wis. Adm. Code](1) Reference Test Method for ParticulateMatter Emissions: whenever particulate matteremission testing is required, the permittee shalluse U.S. EPA Method 5, 5A, 5B, 5D, 5E, 5F,5G, 5H or 17 including condensible backhalfemissions (U.S. EPA Method 202). [s. NR439.06(1), Wis. Adm. Code](2) The permittee shall retain at itsheadquarters, plans and specifications thatindicate the boiler's fuel usage designcapabilities. Nameplate information and boilersafety inspection data shall be consideredsufficient to demonstrate compliance for thisboiler.[ s. NR 407.09(4)(a)1., Wis. Adm. Code](3) The permittee shall keep and maintain onsite technical drawings, blueprints or equivalentrecords of the physical stack parameters. [s.NR 439.04(1)(d), Wis. Adm. Code](4) The permittee shall make the plans andspecifications required by this section availableon site during inspections by Departmentpersonnel. [s. NR 439.05(1), Wis. Adm. Code]2. VisibleEmissions(1) Emissions of shade or densitymay not exceed number 1 of theRinglemann chart or 20% opacity. [ s.NR 431.05,Wis. Adm. Code, 04-DCF301](1) The permittee may only burn natural gas ordistillate (#1 or #2) fuel oil in this boiler. [s. NR406.10, Wis. Adm. Code; s. 285.65(7), Wis.Stats., 04-DCF-301](1)Reference Test Method for VisibleEmissions: Whenever visible emission testing isrequired by the Department, the permittee shalluse U.S. EPA Method 9. [s. NR 439.06(9)(a)1.,Wis. Adm. Code](2) See I.C.1.c.(2)5This limitation is more restrictive than the s. NR 415.06(2)(a), Wis. Adm. Codelimitation of 0.15 pounds per million BTU, andis established to protect theambient air quality standards and increments. This limit of 0.05 pounds per million BTU (2.0 lbs/hour at maximum capacity) maynot be exceeded. Theestimated maximum theoretical emissions from the boiler (basedon AP-42 emission factors) while combusting distillate fuel oilis 0.024 pounds per millionBTU.FID 405043540; Permit No. 405043540-F20 — Final Permit.Page 11 of 15C.Boiler B22, Stack S12; — INDUSTRIAL, WATERTUBE TYPE, Nat. gas / Distillate Oil.40 mmBtu/hr fired with primary fuel natural gas and backup distillate fuel oil,maximum sulfur content of 0.15%.(1982)Pollutanta. Limitationsb. Compliance Demonstrationc. Reference Test Methods, Recordkeeping andMonitoring Requirements3. Nitrogen Oxides(1) 0.10 pounds of Nitrogen Oxidesper million BTU of heat input whenfiring natural gas and 0.143 pounds ofNitrogen Oxides per million BTU ofheat input when firing distillate fueloil.6[s. 285.65(3), and .s. 285.65(7),Wis. Stats. , 04-DCF-301](1) The permittee may only burn natural gas ordistillate (#1 or #2) fuel oil in this boiler. [s. NR406.10, Wis. Adm. Code; s. 285.65(7), Wis.Stats., 04-DCF-301](1)Reference Test Method for NitrogenCompound Emissions:Whenever complianceemission testing is required, the appropriate USEPA Method; 7, 7A, 7B, 7C, 7D or 7E shall beused. [s. NR 439.06(6)(a), Wis. Adm. Code](2) See I.C.1.c.(2)(3) See I. E. 2.3. Sulfur dioxide(1) The sulfur content of the distillatefuel oil burned may not exceed 0.15% by weight. [s. 285.65(7), Wis.Stats.; s. NR 404.08(2), Wis. Adm.Code, 04-DCF-301](2) See I.C.1.a.(2)(1) The permittee may only burn natural gas ordistillate (#1 or #2) fuel oil in this boiler. [s. NR406.10, and s. NR 440.207(3)(d), Wis. Adm.Code; s. 285.65(3), Wis. Stats., 04-DCF-301](2) The sulfur content of the distillate fuel oilwithin the storage tank may not exceed 0.15 wt.percent Sulfur. [s. 285.65(7), Wis. Stats.; s. NR404.08(2), Wis. Adm. Code, 04-DCF-301](3) See I.C.1.b.(2)(4) See I.C.3.c.(3) and (4)(1)Reference Test Method for Sulfur DioxideEmissions:(a) Whenever compliance emissiontesting is required, the appropriate US EPAMethod; 6, 6A, 6B, 6C or 8 shall be used asapproved by the Department. [s. NR439.06(2)(a), Wis. Adm. Code](b) Whenever periodic fuel sampling andanalysis of fossil and nonfossil fuels is required,it shall be conducted using the methods andprocedures specified ins. NR 439.08, Wis. Adm.Code. [s. NR 439.06(2)(a), and s. NR 439.08,Wis. Adm. Code](2) See I.C.1.c.(3)(3) The permittee shall maintain records of thetype and quantity of fuel used in this boiler (B22)and the sulfur content of the distillate fuel oilpurchased. The records shall be summarizedmonthly.. [s. NR 407.09(4)(a)1., and s. NR439.04, , Wis. Adm. Code](4) The facility shall maintain records of fuelsampling and analysis of the distillate fuel oil.[s. NR 439.04, Wis. Adm. Code]6This condition, along with the facility restrictions on thequantities of natural gas and distillate fuel oil that may be fired, are necessary to assure that thefacility constitutes a synthetic minor source under the TitleV and PSD permit programs. These emission rates are based on theAP-42 emission factors of 100lbs/cf6 for natural gas and 20 lbs/gal3 for distillate oil combustion, in boilers with heat inputs less than 100 MMBTU/hr.FID 405043540; Permit No. 405043540-F20 — Final Permit.Page 12 of 15D. Conditions applicable to the entire facility.{Table_Heading}Condition Typea. Conditionb. Compliance Demonstrationc. Reference Test Methods, Recordkeeping and Monitoring Requirements1. Synthetic MinorRestrictions7(1) The total quantity of natural gasfired by the facility may not exceed109.6 million Cubic Feet (cf6) permonth, averaged over any 12consecutive month period. [s.285.65(7), Wis. Stats.](2) The total quantity of distillate fueloil fired by the facility may not exceed109,600 gallons per month, averagedover any 12 consecutive monthperiod. [s. 285.65(7), Wis. Stats.](1) The facility shall monitor and recordthe quantities of natural gas and distillateoil consumed by the facility on a monthlybasis. [s. NR 439.04, Wis. Adm. Code](2) The monthly quantities of natural gasand distillate oil consumed by the facilityover the last 12 months shall each besummed and divided by 12 to determinethe 12 month average fuel usage. . [s.NR 439.04, Wis. Adm. Code]2. MalfunctionPrevention andAbatement Plan.(1) A malfunction prevention andabatement plan shall be prepared andfollowed for the plant.[s. NR 439.11, Wis. Adm. Code](2) All air pollution control equipmentshall be operated and maintained inconformance with good engineeringpractices (i.e. operated andmaintained according tomanufacturer's specifications anddirections) to minimize the possibilityfor the exceedance of any emissionlimitations. [s. NR 439.11(4), Wis.Adm. Code](1) The malfunction prevention andabatement plan shall be developed toprevent, detect and correct malfunctionsor equipment failures which may causeany applicable emissions limitation to beviolated or which may cause air pollution.[s. NR 439.11(1), Wis. Adm. Code](2) This malfunction prevention andabatement plan shall include installation,maintenance and routine calibrationprocedures for the process monitoringand control equipment instrumentation.This plan shall require an instrumentationcalibration at the frequency specified bythe manufacturer, yearly or at a frequencybased on good engineering practice asestablished by operational history,whichever is more frequent. Inspectionand calibration shall also be conducted(1) A written copy of the malfunctionprevention and abatement plan shallbe kept at the plant and shall beupdated once every five years.[s. NR 439.11(1), Wis. Adm. Code](2) The facility shall maintain aninventory of normal consumable itemsnecessary to ensure operation of thecontrol device(s) in conformance withthe manufacturer's specifications andrecommendations. [s. NR 439.11,Wis. Adm. Code](3) The facility shall maintain recordsof the instrumentation calibrations.[s. NR 439.04, Wis. Adm. Code]7These restrictions on fuel use, and thelimitations on Nitrogen Oxides emissions when firing natural gas (0.10 lbs/MMBTU) anddistillate oil (0.143lbs/MMBTU) are both necessary for the facility to be considered a synthetic minor source under PSD and Title V.FID 405043540; Permit No. 405043540-F20 — Final Permit.Page 13 of 15D. Conditions applicable to the entire facility.{Table_Heading}Condition Typea. Conditionb. Compliance Demonstrationc. Reference Test Methods, Recordkeeping and Monitoring Requirementswhenever instrumentation anomalies arenoted.[ss. NR 407.09(1)(c)1.c., NR 439.055(4)and s. NR 439.11, Wis. Adm. Code](3) The malfunction prevention andabatement plan shall require a copy of theoperation and maintenance manual forthe control equipment to be maintainedon site. The plan shall contain all of theelements in s. NR 439.11(1)(a) – (h), Wis.Adm. Code. [s. NR 439.11, Wis. Adm.Code]FID 405043540; Permit No. 405043540-F20 — Final Permit.Page 14 of 15E. Conditions applicable to the entire facility.{TaCondition Typea. Conditionsb. Compliance Demonstrationc. Reference Test Methods,Recordkeeping andMonitoring Requirements3. ComplianceReports/RecordsUpon issuance of the operationpermit, the permittee shall submitperiodic monitoring reports.[s. NR 407.09(1)(c)3., Wis. Adm.Code]Upon issuance of the operationpermit, the permittee shall submitperiodic certification of compliance.[s. NR 407.09(4)(a)3., Wis. Adm.Code]The records required under thispermit shall be retained for at leastfive (5) years and shall be madeavailable to department personnelupon request during normal businesshours.[s. NR 422.127(4)(d), s. NR 439.04,s. NR 439.05, Wis. Adm. Code]The permittee shall submit a monitoring reportwhich contains the results of monitoring or a summaryof monitoring results required by this permit to theDepartment every 6 months.The time periods to be addressed by the submittalare January 1 through June 30; and July 1 throughDecember 31.The report shall be submitted to the WisconsinDepartment of Natural ResourcesNortheast Region AirProgram,2984 Shawano Ave., Green Bay, WI, 54313,within 30 days after the end of each reporting period.All deviations from and violations of applicablerequirements shall be clearly identified in thesubmittal.Each submittal shall be certified by a responsibleofficial as to the truth, accuracy and completeness ofthe report.The content of the submittal is described in itemD. of Part II of the operation permit.[s. NR 439.03(1)(b), Wis. Adm. Code]The permittee shall submit an annual certificationof compliance with the requirements of this permit tothe Wisconsin Department of Natural ResourcesNortheast Region Air Program, 2984 Shawano Ave.,Green Bay, WI, 54313.The time period to be addressed by the report isthe January 1 through December 31 period whichprecedes the report.The report shall be submitted to the WisconsinFID 405043540; Permit No. 405043540-F20 — Final Permit.Page 15 of 15E. Conditions applicable to the entire facility.{TaCondition Typea. Conditionsb. Compliance Demonstrationc. Reference Test Methods,Recordkeeping andMonitoring RequirementsDepartment of Natural Resources Northeast RegionAir Program, 2984 Shawano Ave., Green Bay, WI,54313, within 30 days after the end of each reportingperiod.0)The information included in the report shallcomply with the requirements of Part II, Section N ofthis permit.1)Each report shall be certified by a responsibleofficial as to the truth, accuracy and completeness ofthe report.[s. NR 439.03(1)(c), Wis. Adm. Code]