### Name: Rudy Sanchez

Title: Plant General Manager Company: Florida Power & Light Co Sign Date: 6/22/2010 Name: Thomas K. Graham Title: Director of Operations Company:Air Hygiene International, Inc. Sign Date: 5/17/2010 Permitted Facility Representative / Date Testing Company Representative / Date



## Turkey Point Energy Center, Unit #1, Information Collection Request Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Monday, February 14, 2011 Page 1 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 Facility Information: Turkey Point Energy Center 9760 SW 344th Street

Homestead FL33035 Contact:Augie De La Vega Phone:(305) 242-3896 Fax: Email: augie.de.la.vega@fpl.com Testing Company: Air Hygiene International, Inc. 5634 S. 122nd East Ave, Suite F

Tulsa OK74146 Contact:Thomas Graham Phone:(918) 307-8865 Fax: (918) 307-9131 Email: tom@airhygiene.com

Air Permit Number: 0250003-011-AV Permitted Source ID/Name: Foster Wheeler, Wall Fired Boiler PTP1 Permitted Maximum Process Rate: 440 MW Max. Normal Operation Process Rate: 400 MW Target Process Test Rate 380 MW

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Florida Power and Light Company (FPL) operates two oil fired electric utility steam generating units of Foster Wheeler design, designated as Units PTP1 and PTP2. The facility is located at 9760 SW 344th Street in Homestead, Florida. Unit PTP1 and PTP2 are of identical design and consists of two wall fired boilers and ancillary equipment designed to generate 440 megawatts (MW) of electricity each with rated heat inputs of 4,000 million British thermal units per hour (MMBtu/hr) based on high heating value (HHV). Fuel oil consumption is rated at 228,000 pounds per hour. Unit PTP1 and PTP2 utilize low nitrogen oxide (NOx) burner technology to control NOx emissions and cyclone separators to control particulate matter (PM) emissions. Emission testing will be conducted from platforms on the independent stacks of each unit. Industry/SCC/NAIS221112

Sampling Location Information:

Test Parameter Information: AFS #:0250003 FRS #:110000914832

SCC / Description10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: Normal Firing

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width PTP1 - D/F 242.3 2202 2002 4 0 12 0 0 PTP1 - Gases 242.3 2202 2002 4 0 1 0 0 PTP1 - Metals242.3 2202 2002 4 0 12 0 0 PTP1 - PM 242.3 2202 2002 4 0 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location Regulation Description Compound Limit Unit Not applicable.



### Monday, February 14, 2011 Page 2 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location % H2O Method 1 - 4 3 480 12 PTP1 - D/F 2,3,7,8-TCDD Method 23 3 480 12 PTP1 - D/F 1,2,3,7,8-PeCDD Method 23 3 480 12 PTP1 - D/F 1,2,3,4,7,8-HxCDD Method 23 3 480 12 PTP1 - D/F 1,2,3,6,7,8-HxCDD Method 23 3 480 12 PTP1 - D/F 1,2,3,7,8,9-HxCDD Method 23 3 480 12 PTP1 - D/F 1,2,3,4,6,7,8-HpCDD Method 23 3 480 12 PTP1 - D/F OCDD Method 23 3 480 12 PTP1 - D/F 2,3,7,8-TCDF Method 23 3 480 12 PTP1 - D/F 1,2,3,7,8-PeCDF Method 23 3 480 12 PTP1 - D/F 2,3,4,7,8-PeCDF Method 23 3 480 12 PTP1 - D/F 1,2,3,4,7,8-HxCDF Method 23 3 480 12 PTP1 - D/F 1,2,3,6,7,8-HxCDF Method 23 3 480 12 PTP1 - D/F 2,3,4,6,7,8-HxCDF Method 23 3 480 12 PTP1 - D/F 1,2,3,7,8,9-HxCDF Method 23 3 480 12 PTP1 - D/F 1,2,3,4,6,7,8-HpCDF Method 23 3 480 12 PTP1 - D/F 1,2,3,4,7,8,9-HpCDF Method 23 3 480 12 PTP1 - D/F OCDF Method 23 3 480 12 PTP1 - D/F Total Dioxins Method 23 3 480 12 PTP1 - D/F Total Furans Method 23 3 480 12 PTP1 - D/F 3,3',4,4'-TCB (PCB77) Method 23 3 480 12 PTP1 - D/F 3,4,4',5-TCB (PCB81) Method 23 3 480 12 PTP1 - D/F 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 12 PTP1 - D/F 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 12 PTP1 - D/F 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 12 PTP1 - D/F 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 12 PTP1 - D/F 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 12 PTP1 - D/F 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 12 PTP1 - D/F
2,3',4,4',5,5'-HxCB (PCB167)Method 23 3 480 12 PTP1 - D/F 3,3',4,4',5,5'-HxCB (PCB169)Method 23 3 480 12 PTP1 - D/F 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 12 PTP1 - D/F

O2 Method 3A O2 3 480 12 PTP1 - D/F Co2 Method 3A CO2 3 480 12 PTP1 - D/F % H2O Method 1 - 4 3 120 1 Determined after initial stratification test PTP1 - Gases

Carbon Monoxide Method 10 3 120 1 Determined after initial stratification test PTP1 - Gases
Total organic compounds

(TOC) as Propane Method 25A 3 120 1 Determined after initial stratification test PTP1 - Gases

O2 Method 3A O2 3 120 1 Determined after initial stratification test PTP1 - Gases

Co2 Method 3A CO2 3 120 1 Determined after initial stratification test PTP1 - Gases

Sulfur Dioxide Method 6C 3 120 1 Determined after initial stratification test PTP1 - Gases
Nitrogen oxides (NOx) Method 7E 3 120 1 Determined after initial stratification test PTP1 - Gases

% H2O Method 1 - 4 3 240 12 PTP1 - MetalsSelenium Method 29 3 240 12 PTP1 - MetalsManganese Method 29 3 240 12 PTP1 - Metals


### Monday, February 14, 2011 Page 3 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. PM Run All - reduced to 2 hour runs to avoid high vacuum, did not pull required volumes

Lead Method 29 3 240 12 PTP1 - MetalsFilterable Particulate Method 29 3 240 12 PTP1 - MetalsCobalt Method 29 3 240 12 PTP1 - MetalsCadmium Method 29 3 240 12 PTP1 - MetalsChromium Method 29 3 240 12 PTP1 - MetalsNickel Method 29 3 240 12 PTP1 - MetalsCo2 Method 3A CO2 3 240 12 PTP1 - MetalsO2 Method 3A O2 3 240 12 PTP1 - Metals% H2O Method 1 - 4 3 130 12 Run times vary based on method calculations PTP1 - PM

Filterable Particulate OTM - 27/28 3 130 12 Run times vary based on method calculations PTP1 - PM

Filterable PM2.5 OTM - 27/28 3 130 12 Run times vary based on method calculations PTP1 - PM
Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 130 12 Run times vary based on method calculations PTP1 - PM
Organic Condensible

Particulate OTM - 27/28 3 130 12 Run times vary based on method calculations PTP1 - PM

Total PM2.5 OTM - 27/28 3 130 12 Run times vary based on method calculations PTP1 - PM

Total Particulate OTM - 27/28 3 130 12 Run times vary based on method calculations PTP1 - PM

O2 Method 3A O2 3 130 12 Run times vary based on method calculations PTP1 - PM

Co2 Method 3A CO2 3 130 12 Run times vary based on method calculations PTP1 - PM



### Monday, February 14, 2011 Page 4 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 Sampling / Stack Data Results Summary


### Location PTP1 - D/F - Method 23 Average Run Number PTP1-23-1 PTP1-23-2 PTP1-23-3 Test Date 4/1/2010 4/2/2010 4/3/2010 Run Start Time 8:38:00 AM 8:02:00 AM 9:39:00 AM

Run Finish Time 6:44:00 PM5:17:00 PM 6:13:00 PM Net Run Time, minutes 480 480 480 Dry Gas Meter Volume Sampled, dscf 405.087 404.203 395.239 401.510 Moisture Content of Stack Gas, % 10.00 10.33 10.06 10.130 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 14.57 14.8 14.77 14.713 Oxygen, % 2.79 2.93 2.88 2.867 Average Stack Gas Temperature, °F 278.92 290.00 303.67 290.863 Dry Volumetric Flow Rate, dry scfm 794,677.3 782,009.0 773,897.8 783,528.033 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,236,522.91,242,094.6 1,247,858.41,242,158.63 3 Percent Isokinetic of Sampling Rate, % 99.8 101.2 99.9 100.300 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Location PTP1 - Gases - Method 10 Average Run Number 1-CO-1 1-CO-2 1-CO-3 Test Date 4/1/2010 4/2/2010 4/2/2010 Run Start Time 4:08:50 PM3:03:20 PM 5:18:50 PM Run Finish Time 6:08:20 PM5:02:50 PM 7:18:20 PM Carbon Dioxide, % 14.57 14.84 14.76 14.723 Oxygen, % 2.79 2.89 2.97 2.883 Dry Volumetric Flow Rate, dry scfm 794574 781958 781958 786,163.333 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.02 10.34 10.34 10.233 Fuel Type Oil Oil Oil Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 5 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010
Location PTP1 - Gases - Method 25A Average Run Number 1-THC-1 1-THC-2 1-THC-3 Test Date 4/1/2010 4/2/2010 4/2/2010 Run Start Time 4:08:50 PM3:03:20 PM 5:18:50 PM Run Finish Time 6:08:20 PM5:02:50 PM 7:18:20 PM Carbon Dioxide, % 14.57 14.84 14.76 14.723 Oxygen, % 2.79 2.89 2.97 2.883 Dry Volumetric Flow Rate, dry scfm 794574 781958 781958 786,163.333 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.02 10.34 10.34 10.233 Fuel Type Oil Oil Oil Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Location PTP1 - Gases - Method 3A CO2 Average Run Number 1-CO2-1 1-CO2-2 1-CO2-3 Test Date 4/1/2010 4/2/2010 4/2/2010 Run Start Time 4:08:50 PM3:03:20 PM 5:18:50 PM Run Finish Time 6:08:20 PM5:02:50 PM 7:18:20 PM Carbon Dioxide, % 14.57 14.84 14.76 14.723 Oxygen, % 2.79 2.89 2.97 2.883 Dry Volumetric Flow Rate, dry scfm 794574 781958 781958 786,163.333 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.02 10.34 10.34 10.233 Fuel Type Oil Oil Oil Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 6 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010
Location PTP1 - Gases - Method 3A O2 Average Run Number 1-O2-1 1-O2-2 1-O2-3 Test Date 4/1/2010 4/2/2010 4/2/2010 Run Start Time 4:08:50 PM3:03:20 PM 5:18:50 PM Run Finish Time 6:08:20 PM5:02:50 PM 7:18:20 PM Carbon Dioxide, % 14.57 14.84 14.76 14.723 Oxygen, % 2.79 2.89 2.97 2.883 Dry Volumetric Flow Rate, dry scfm 794574 781958 781958 786,163.333 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.02 10.34 10.34 10.233 Fuel Type Oil Oil Oil Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Location PTP1 - Gases - Method 6C Average Run Number 1-SO2-1 1-SO2-2 1-SO2-3 Test Date 4/1/2010 4/2/2010 4/2/2010 Run Start Time 4:08:50 PM3:03:20 PM 5:18:50 PM Run Finish Time 6:08:20 PM5:02:50 PM 7:18:20 PM Carbon Dioxide, % 14.57 14.84 14.76 14.723 Oxygen, % 2.79 2.89 2.97 2.883 Dry Volumetric Flow Rate, dry scfm 794574 781958 781958 786,163.333 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.02 10.34 10.34 10.233 Fuel Type Oil Oil Oil Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 7 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010
Location PTP1 - Gases - Method 7E Average Run Number 1-NOx-1 1-NOx-2 1-NOx-3 Test Date 4/1/2010 4/2/2010 4/2/2010 Run Start Time 4:08:50 PM3:03:20 PM 5:18:50 PM Run Finish Time 6:08:20 PM5:02:50 PM 7:18:20 PM Carbon Dioxide, % 14.57 14.84 14.76 14.723 Oxygen, % 2.79 2.89 2.97 2.883 Dry Volumetric Flow Rate, dry scfm 794574 781958 781958 786,163.333 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.02 10.34 10.34 10.233 Fuel Type Oil Oil Oil Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Location PTP1 - Metals - Method 29 Average Run Number PTP1-29-1 PTP1-29-2 PTP1-29-3 Test Date 4/1/2010 4/2/2010 4/3/2010 Run Start Time 2:32:00 PM2:34:00 PM 1:40:00 PM Run Finish Time 7:06:00 PM7:06:00 PM 6:05:00 PM Net Run Time, minutes 240 240 240 Dry Gas Meter Volume Sampled, dscf 192.039 195.812 200.612 196.154 Moisture Content of Stack Gas, % 10.12 10.30 9.59 10.003 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 14.57 14.8 14.77 14.713 Oxygen, % 2.79 2.93 2.88 2.867 Average Stack Gas Temperature, °F 280.75 287.17 305.83 291.250 Dry Volumetric Flow Rate, dry scfm 776,840.4 775,881.2 797,928.5 783,550.033 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,211,354.41,227,300.9 1,282,248.91,240,301.40 0 Percent Isokinetic of Sampling Rate, % 96.8 98.8 98.4 98.000 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 8 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010
Location PTP1 - PM - OTM - 27/28 Average Run Number PTP1-27/28- 1 PTP1- 27/28-2PTP1-27/28-

3 Test Date 4/1/2010 4/2/2010 4/3/2010 Run Start Time 11:28:00 AM 11:18:00 AM10:47:00 AM

Run Finish Time 2:07:00 PM2:01:00 PM 1:17:00 PM Net Run Time, minutes 131 130 131 Dry Gas Meter Volume Sampled, dscf 45.753 45.949 41.855 44.519 Moisture Content of Stack Gas, % 11.30 9.92 9.88 10.367 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 14.57 14.8 14.77 14.713 Oxygen, % 2.79 2.93 2.88 2.867 Average Stack Gas Temperature, °F 281.92 292.92 303.08 292.640 Dry Volumetric Flow Rate, dry scfm 740,867.8 763,760.8 752,507.9 752,378.833 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,175,619.01,209,048.9 1,210,009.51,198,225.80 0 Percent Isokinetic of Sampling Rate, % 113.7 111.6 102.4 109.233 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 9 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 Emissions Summary


### Location: PTP1 - D/F - Method 23 Compound: 1,2,3,4,6,7,8-HpCDD Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000043 0.0000000058 0.00000000598 0.000 lb/mmBtuO2 2.48E-13 3.38E-13 3.56E-13 0.000 ng/dscm 3.75E-04 5.07E-04 5.34E-04 0.000 ng/dscm@7%O2 2.88E-04 3.92E-04 4.12E-04 0.000 

### Compound: 1,2,3,4,6,7,8-HpCDF Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000024 0.0000000045 0.0000000023 0.000 lb/mmBtuO2 1.39E-13 2.62E-13 1.37E-13 0.000 ng/dscm 2.09E-04 3.93E-04 2.06E-04 0.000 ng/dscm@7%O2 1.60E-04 3.04E-04 1.59E-04 0.000 

### Compound: 1,2,3,4,7,8,9-HpCDF Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000031 0.0000000022 0.0000000029 0.000 lb/mmBtuO2 1.79E-13 1.28E-13 1.72E-13 0.000 ng/dscm 2.70E-04 1.92E-04 2.59E-04 0.000 ng/dscm@7%O2 2.07E-04 1.49E-04 2.00E-04 0.000 

### Compound: 1,2,3,4,7,8-HxCDD Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000032 0.0000000026 0.0000000026 0.000 lb/mmBtuO2 1.85E-13 1.52E-13 1.55E-13 0.000 ng/dscm 2.79E-04 2.27E-04 2.32E-04 0.000 ng/dscm@7%O2 2.14E-04 1.76E-04 1.79E-04 0.000 

### Compound: 1,2,3,4,7,8-HxCDF Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000016 0.00000000094 0.0000000014 0.000 lb/mmBtuO2 9.24E-14 5.48E-14 8.32E-14 0.000 ng/dscm 1.40E-04 8.21E-05 1.25E-04 0.000 ng/dscm@7%O2 1.07E-04 6.35E-05 9.64E-05 0.000 

### Compound: 1,2,3,6,7,8-HxCDD Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000031 0.0000000026 0.0000000025 0.000 lb/mmBtuO2 1.79E-13 1.52E-13 1.49E-13 0.000 ng/dscm 2.70E-04 2.27E-04 2.23E-04 0.000 ng/dscm@7%O2 2.07E-04 1.76E-04 1.72E-04 0.000 

### Compound: 1,2,3,6,7,8-HxCDF Average



### Monday, February 14, 2011 Page 10 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000015 0.00000000087 0.0000000022 0.000 lb/mmBtuO2 8.66E-14 5.07E-14 1.31E-13 0.000 ng/dscm 1.31E-04 7.60E-05 1.97E-04 0.000 ng/dscm@7%O2 1.01E-04 5.88E-05 1.52E-04 0.000 

### Compound: 1,2,3,7,8,9-HxCDD Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000032 0.0000000026 0.0000000026 0.000 lb/mmBtuO2 1.85E-13 1.52E-13 1.55E-13 0.000 ng/dscm 2.79E-04 2.27E-04 2.32E-04 0.000 ng/dscm@7%O2 2.14E-04 1.76E-04 1.79E-04 0.000 

### Compound: 1,2,3,7,8,9-HxCDF Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000025 0.000000001 0.0000000015 0.000 lb/mmBtuO2 1.44E-13 5.83E-14 8.92E-14 0.000 ng/dscm 2.18E-04 8.74E-05 1.34E-04 0.000 ng/dscm@7%O2 1.67E-04 6.76E-05 1.03E-04 0.000 

### Compound: 1,2,3,7,8-PeCDD Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000025 0.0000000021 0.0000000022 0.000 lb/mmBtuO2 1.44E-13 1.22E-13 1.31E-13 0.000 ng/dscm 2.18E-04 1.84E-04 1.97E-04 0.000 ng/dscm@7%O2 1.67E-04 1.42E-04 1.52E-04 0.000 

### Compound: 1,2,3,7,8-PeCDF Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000014 0.0000000014 0.0000000013 0.000 lb/mmBtuO2 8.08E-14 8.16E-14 7.73E-14 0.000 ng/dscm 1.22E-04 1.22E-04 1.16E-04 0.000 ng/dscm@7%O2 9.36E-05 9.44E-05 8.95E-05 0.000 

### Compound: 2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000051 0.000000002 0.000000006 0.000 lb/mmBtuO2 2.94E-13 1.17E-13 3.57E-13 0.000 ng/dscm 4.45E-04 1.75E-04 5.36E-04 0.000 ng/dscm@7%O2 3.42E-04 1.35E-04 4.13E-04 0.000 

### Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000201 0.000000015 0.0000000175 0.000 lb/mmBtuO2 1.16E-12 8.74E-13 1.04E-12 0.000 ng/dscm 1.75E-03 1.31E-03 1.56E-03 0.002 ng/dscm@7%O2 1.34E-03 1.01E-03 1.20E-03 0.001



### Monday, February 14, 2011 Page 11 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 Compound: 2,3,3',4,4'-PeCB (PCB105) Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.000000472 0.000000468 0.000000421 0.000 lb/mmBtuO2 2.72E-11 2.73E-11 2.50E-11 0.000 ng/dscm 4.12E-02 4.09E-02 3.76E-02 0.040 ng/dscm@7%O2 3.16E-02 3.16E-02 2.90E-02 0.031 

### Compound: 2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000428 0.000000034 0.0000000337 0.000 lb/mmBtuO2 2.47E-12 1.98E-12 2.00E-12 0.000 ng/dscm 3.73E-03 2.97E-03 3.01E-03 0.003 ng/dscm@7%O2 2.86E-03 2.30E-03 2.32E-03 0.002 

### Compound: 2,3,4,4',5-PeCB (PCB114) Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000437 0.000000035 0.0000000452 0.000 lb/mmBtuO2 2.52E-12 2.04E-12 2.69E-12 0.000 ng/dscm 3.81E-03 3.06E-03 4.04E-03 0.004 ng/dscm@7%O2 2.92E-03 2.37E-03 3.12E-03 0.003 

### Compound: 2,3',4,4',5-PeCB (PCB118) Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.00000122 0.00000133 0.00000112 0.000 lb/mmBtuO2 7.04E-11 7.75E-11 6.66E-11 0.000 ng/dscm 1.06E-01 1.16E-01 1.00E-01 0.107 ng/dscm@7%O2 8.14E-02 8.97E-02 7.71E-02 0.083 

### Compound: 2',3,4,4',5-PeCB (PCB123) Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.000000023 0.0000000234 0.000000019 0.000 lb/mmBtuO2 1.33E-12 1.36E-12 1.13E-12 0.000 ng/dscm 2.01E-03 2.04E-03 1.70E-03 0.002 ng/dscm@7%O2 1.54E-03 1.58E-03 1.31E-03 0.001 

### Compound: 2,3,4,6,7,8-HxCDF Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000041 0.00000000092 0.0000000014 0.000 lb/mmBtuO2 2.37E-13 5.36E-14 8.32E-14 0.000 ng/dscm 3.57E-04 8.04E-05 1.25E-04 0.000 ng/dscm@7%O2 2.74E-04 6.22E-05 9.64E-05 0.000 

### Compound: 2,3,4,7,8-PeCDF Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000013 0.0000000013 0.0000000012 0.000 lb/mmBtuO2 7.50E-14 7.58E-14 7.13E-14 0.000



### Monday, February 14, 2011 Page 12 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 ng/dscm 1.13E-04 1.14E-04 1.07E-04 0.000 ng/dscm@7%O2 8.67E-05 8.82E-05 8.25E-05 0.000 

### Compound: 2,3,7,8-TCDD Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000047 0.0000000022 0.000000003 0.000 lb/mmBtuO2 2.71E-13 1.28E-13 1.78E-13 0.000 ng/dscm 4.10E-04 1.92E-04 2.68E-04 0.000 ng/dscm@7%O2 3.15E-04 1.49E-04 2.07E-04 0.000 

### Compound: 2,3,7,8-TCDF Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000021 0.0000000016 0.000000002 0.000 lb/mmBtuO2 1.21E-13 9.33E-14 1.19E-13 0.000 ng/dscm 1.83E-04 1.40E-04 1.79E-04 0.000 ng/dscm@7%O2 1.40E-04 1.08E-04 1.38E-04 0.000 

### Compound: 3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.00000000041 0.0000000011 0.00000000017 0.000 lb/mmBtuO2 2.37E-14 6.41E-14 1.01E-14 0.000 ng/dscm 3.57E-05 9.61E-05 1.52E-05 0.000 ng/dscm@7%O2 2.74E-05 7.43E-05 1.17E-05 0.000 

### Compound: 3,3',4,4',5-PeCB (PCB126) Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000042 0.0000000032 0.0000000067 0.000 lb/mmBtuO2 2.42E-13 1.87E-13 3.98E-13 0.000 ng/dscm 3.66E-04 2.80E-04 5.99E-04 0.000 ng/dscm@7%O2 2.81E-04 2.17E-04 4.62E-04 0.000 

### Compound: 3,3',4,4'-TCB (PCB77) Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.000000151 0.000000152 0.000000163 0.000 lb/mmBtuO2 8.72E-12 8.86E-12 9.69E-12 0.000 ng/dscm 1.32E-02 1.33E-02 1.46E-02 0.014 ng/dscm@7%O2 1.01E-02 1.03E-02 1.13E-02 0.011 

### Compound: 3,4,4',5-TCB (PCB81) Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.00000000852 0.00000000761 0.00000000821 0.000 lb/mmBtuO2 4.92E-13 4.44E-13 4.88E-13 0.000 ng/dscm 7.43E-04 6.65E-04 7.34E-04 0.001 ng/dscm@7%O2 5.70E-04 5.14E-04 5.66E-04 0.001 

### Compound: OCDD Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3


### Monday, February 14, 2011 Page 13 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 Mass_mg 0.000000008 0.0000000065 0.0000000084 0.000 lb/mmBtuO2 4.62E-13 3.79E-13 4.99E-13 0.000 ng/dscm 6.98E-04 5.68E-04 7.51E-04 0.001 ng/dscm@7%O2 5.36E-04 4.39E-04 5.79E-04 0.001 

### Compound: OCDF Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000132 0.000000009 0.000000011 0.000 lb/mmBtuO2 7.62E-13 5.25E-13 6.54E-13 0.000 ng/dscm 1.15E-03 7.86E-04 9.83E-04 0.001 ng/dscm@7%O2 8.83E-04 6.08E-04 7.58E-04 0.001 

### Compound: Total Dioxins Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.000000029 0.0000000244 0.00000002728 0.000 lb/mmBtuO2 1.67E-12 1.42E-12 1.62E-12 0.000 ng/dscm 2.53E-03 2.13E-03 2.44E-03 0.002 ng/dscm@7%O2 1.94E-03 1.65E-03 1.88E-03 0.002 

### Compound: Total Furans Average RunNumber PTP1-23-1 PTP1-23-2 PTP1-23-3 Mass_mg 0.0000000332 0.00000002373 0.0000000272 0.000 lb/mmBtuO2 1.92E-12 1.38E-12 1.62E-12 0.000 ng/dscm 2.89E-03 2.07E-03 2.43E-03 0.002 ng/dscm@7%O2 2.22E-03 1.60E-03 1.87E-03 0.002



### Location: PTP1 - Gases - Method 10 Compound: Carbon Monoxide Average Run 1-CO-1 1-CO-2 1-CO-3 lb/mmBtuO2 1.40E-01 8.70E-02 3.04E-02 0.086 ppm 1.82E+02 1.12E+02 3.90E+01 111.000 ppm@7%O2 1.40E+02 8.64E+01 3.02E+01 85.533



### Location: PTP1 - Gases - Method 25A Compound: Total organic compounds (TOC) as Average Run 1-THC-1 1-THC-2 1-THC-3 lb/mmBtuO2 9.49E-04 1.54E-03 2.31E-04 0.001 ppm 7.82E-01 1.26E+00 1.89E-01 0.744 ppm@7%O2 6.00E-01 9.72E-01 1.47E-01 0.573



### Location: PTP1 - Gases - Method 6C Compound: Sulfur Dioxide Average Run 1-SO2-1 1-SO2-2 1-SO2-3 lb/mmBtuO2 9.76E-01 9.94E-01 1.01E+00 0.993 ppm 5.54E+02 5.61E+02 5.67E+02 560.667 ppm@7%O2 4.25E+02 4.33E+02 4.40E+02 432.667



### Monday, February 14, 2011 Page 14 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010

Location: PTP1 - Gases - Method 7E 

### Compound: Nitrogen oxides (NOx) Average Run 1-NOx-1 1-NOx-2 1-NOx-3 lb/mmBtuO2 5.54E-01 5.82E-01 5.94E-01 0.577 ppm 4.37E+02 4.57E+02 4.64E+02 452.667 ppm@7%O2 3.35E+02 3.53E+02 3.60E+02 349.333



### Location: PTP1 - Metals - Method 29 

### Compound: Antimony Average RunNumber PTP1-29-1 PTP1-29-2 PTP1-29-3 Mass_mg 0.396 0.404 0.29 0.363 Elb/hr 2.12E-01 2.12E-01 1.53E-01 0.192 lb/mmBtuO2 4.82E-05 4.86E-05 3.40E-05 0.000 mg/dscm 7.28E-02 7.29E-02 5.11E-02 0.066 mg/dscm@7%O2 5.59E-02 5.64E-02 3.94E-02 0.051 

### Compound: Arsenic Average RunNumber PTP1-29-1 PTP1-29-2 PTP1-29-3 Mass_mg 0.0231 0.0247 0.023 0.024 Elb/hr 1.24E-02 1.29E-02 1.21E-02 0.012 lb/mmBtuO2 2.81E-06 2.97E-06 2.69E-06 0.000 mg/dscm 4.25E-03 4.46E-03 4.05E-03 0.004 mg/dscm@7%O2 3.26E-03 3.45E-03 3.12E-03 0.003 

### Compound: Beryllium Average RunNumber PTP1-29-1 PTP1-29-2 PTP1-29-3 Mass_mg 0.00119 0.00134 0.00167 0.001 Elb/hr 6.37E-04 7.02E-04 8.79E-04 0.001 lb/mmBtuO2 1.45E-07 1.61E-07 1.96E-07 0.000 mg/dscm 2.19E-04 2.42E-04 2.94E-04 0.000 mg/dscm@7%O2 1.68E-04 1.87E-04 2.27E-04 0.000 

### Compound: Cadmium Average RunNumber PTP1-29-1 PTP1-29-2 PTP1-29-3 Mass_mg 0.000754 0.000779 0.000584 0.001 Elb/hr 4.03E-04 4.08E-04 3.07E-04 0.000 lb/mmBtuO2 9.18E-08 9.37E-08 6.84E-08 0.000 mg/dscm 1.39E-04 1.41E-04 1.03E-04 0.000 mg/dscm@7%O2 1.07E-04 1.09E-04 7.95E-05 0.000 

### Compound: Chromium Average RunNumber PTP1-29-1 PTP1-29-2 PTP1-29-3 Mass_mg 0.041 0.0453 0.0314 0.039 Elb/hr 2.19E-02 2.37E-02 1.65E-02 0.021 lb/mmBtuO2 4.99E-06 5.45E-06 3.68E-06 0.000 mg/dscm 7.54E-03 8.17E-03 5.53E-03 0.007



### Monday, February 14, 2011 Page 15 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 mg/dscm@7%O2 5.79E-03 6.32E-03 4.27E-03 0.005 

### Compound: Cobalt Average RunNumber PTP1-29-1 PTP1-29-2 PTP1-29-3 Mass_mg 0.212 0.224 0.192 0.209 Elb/hr 1.13E-01 1.17E-01 1.01E-01 0.110 lb/mmBtuO2 2.58E-05 2.70E-05 2.25E-05 0.000 mg/dscm 3.90E-02 4.04E-02 3.38E-02 0.038 mg/dscm@7%O2 2.99E-02 3.12E-02 2.61E-02 0.029 

### Compound: Filterable Particulate Average RunNumber PTP1-29-1 PTP1-29-2 PTP1-29-3 Mass_mg 191.2 244.3 219.2 218.233 Elb/hr 1.02E+02 1.28E+02 1.15E+02 115.000 lb/mmBtuO2 2.33E-02 2.94E-02 2.57E-02 0.026 mg/dscm 3.52E+01 4.41E+01 3.86E+01 39.300 mg/dscm@7%O2 2.70E+01 3.41E+01 2.98E+01 30.300 

### Compound: Lead Average RunNumber PTP1-29-1 PTP1-29-2 PTP1-29-3 Mass_mg 0.0535 0.0546 0.0393 0.049 Elb/hr 2.86E-02 2.86E-02 2.07E-02 0.026 lb/mmBtuO2 6.51E-06 6.57E-06 4.60E-06 0.000 mg/dscm 9.84E-03 9.85E-03 6.92E-03 0.009 mg/dscm@7%O2 7.55E-03 7.62E-03 5.34E-03 0.007 

### Compound: Manganese Average RunNumber PTP1-29-1 PTP1-29-2 PTP1-29-3 Mass_mg 0.207 0.251 0.303 0.254 Elb/hr 1.11E-01 1.32E-01 1.59E-01 0.134 lb/mmBtuO2 2.52E-05 3.02E-05 3.55E-05 0.000 mg/dscm 3.81E-02 4.53E-02 5.33E-02 0.046 mg/dscm@7%O2 2.92E-02 3.50E-02 4.11E-02 0.035 

### Compound: Nickel Average RunNumber PTP1-29-1 PTP1-29-2 PTP1-29-3 Mass_mg 4.75 5.05 4.01 4.603 Elb/hr 2.54E+00 2.65E+00 2.11E+00 2.433 lb/mmBtuO2 5.78E-04 6.08E-04 4.70E-04 0.001 mg/dscm 8.74E-01 9.11E-01 7.06E-01 0.830 mg/dscm@7%O2 6.71E-01 7.05E-01 5.45E-01 0.640 

### Compound: Selenium Average RunNumber PTP1-29-1 PTP1-29-2 PTP1-29-3 Mass_mg 0.0287 0.036 0.0268 0.031 Elb/hr 1.54E-02 1.89E-02 1.41E-02 0.016 lb/mmBtuO2 3.49E-06 4.33E-06 3.14E-06 0.000 mg/dscm 5.28E-03 6.49E-03 4.72E-03 0.005


### Monday, February 14, 2011 Page 16 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010

Process Run Data mg/dscm@7%O2 4.05E-03 5.02E-03 3.64E-03 0.004



### Location: PTP1 - PM - OTM - 27/28 Compound: Filterable Particulate Average RunNumber PTP1-27/28-2 PTP1-27/28-3 PTP1-27/28-1 Mass_mg 51.642 45.542 45.117 47.434 lb/mmBtuO2 2.65E-02 2.56E-02 2.31E-02 0.025 

### Compound: Filterable PM2.5 Average RunNumber PTP1-27/28-1 PTP1-27/28-2 PTP1-27/28-3 Mass_mg 38.633 42.358 39.583 40.191 lb/mmBtuO2 1.97E-02 2.17E-02 2.22E-02 0.021 

### Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber PTP1-27/28-1 PTP1-27/28-2 PTP1-27/28-3 Mass_mg 0.118 1.476 0 0.531 lb/mmBtuO2 6.03E-05 7.57E-04 0.00E+00 0.000 

### Compound: Organic Condensible Particulate Average RunNumber PTP1-27/28-1 PTP1-27/28-2 PTP1-27/28-3 Mass_mg 1.992 1.475 1.175 1.547 lb/mmBtuO2 1.02E-03 7.56E-04 6.60E-04 0.001 

### Compound: Total Particulate Average RunNumber PTP1-27/28-1 PTP1-27/28-2 PTP1-27/28-3 Mass_mg 47.226 54.593 46.717 49.512 lb/mmBtuO2 2.41E-02 2.80E-02 2.62E-02 0.026 

### Compound: Total PM2.5 Average RunNumber PTP1-27/28-1 PTP1-27/28-2 PTP1-27/28-3 Mass_mg 40.743 45.31 40.758 42.270 lb/mmBtuO2 2.08E-02 2.32E-02 2.29E-02 0.022



### Monday, February 14, 2011 Page 17 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 Process Run Data



### Run Name Value UOM Comments Target Value 1 Residual Oil (No. 6) Burned 28568 gal/hr Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 4/1/2010; Start - 16:08; End - 18:08 0



### 10Residual Oil (No. 6) Burned 28565 gal/hr Method 027/028; Run PM-1; Date - 4/1/2010; Start - 11:28; End - 14:07 0

11Residual Oil (No. 6) Burned 28521 gal/hr Method 027/028; Run PM-2; Date - 4/2/2010; Start - 11:18; End - 14:01 0

12Residual Oil (No. 6) Burned 28653 gal/hr Method 027/028; Run PM-3; Date - 4/3/2010; Start - 10:47; End - 13:17 0

2 Residual Oil (No. 6) Burned 28524 gal/hr Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 4/2/2010; Start - 15:03; End - 17:02 0

3 Residual Oil (No. 6) Burned 28524 gal/hr Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 4/2/2010; Start - 17:18; End - 19:18 0



### 4 Residual Oil (No. 6) Burned 28565 gal/hr Method 23; Run D/F-1; Date - 4/1/2010; Start - 08:38; End - 18:44 0

5 Residual Oil (No. 6) Burned 28521 gal/hr Method 23; Run D/F-2; Date - 4/2/2010; Start - 08:02; End - 17:17 0

6 Residual Oil (No. 6) Burned 28653 gal/hr Method 23; Run D/F-3; Date - 4/3/2010; Start - 09:39; End - 18:13 0

7 Residual Oil (No. 6) Burned 28565 gal/hr Method 29; Run M-1; Date - 4/1/2010; Start - 14:32; End - 19:06 0



### Monday, February 14, 2011 Page 18 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 8 Residual Oil (No. 6) Burned 28521 gal/hr Method 29; Run M-2; Date - 4/2/2010; Start - 14:34; End - 19:06 0

9 Residual Oil (No. 6) Burned 28653 gal/hr Method 29; Run M-3; Date - 4/3/2010; Start - 13:40; End - 18:05 0

1 Average Heat Input 3524 MMBtu/hr Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 4/1/2010; Start - 16:08; End - 18:08 0



### 10Average Heat Input 3524 MMBtu/hr Method 027/028; Run PM-1; Date - 4/1/2010; Start - 11:28; End - 14:07 0

11Average Heat Input 3519 MMBtu/hr Method 027/028; Run PM-2; Date - 4/2/2010; Start - 11:18; End - 14:01 0

12Average Heat Input 3535 MMBtu/hr Method 027/028; Run PM-3; Date - 4/3/2010; Start - 10:47; End - 13:17 0

2 Average Heat Input 3519 MMBtu/hr Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 4/2/2010; Start - 15:03; End - 17:02 0

3 Average Heat Input 3519 MMBtu/hr Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 4/2/2010; Start - 17:18; End - 19:18 0



### 4 Average Heat Input 3524 MMBtu/hr Method 23; Run D/F-1; Date - 4/1/2010; Start - 08:38; End - 18:44 0

5 Average Heat Input 3519 MMBtu/hr Method 23; Run D/F-2; Date - 4/2/2010; Start - 08:02; End - 17:17 0

6 Average Heat Input 3535 MMBtu/hr Method 23; Run D/F-3; Date - 4/3/2010; Start - 09:39; End - 18:13 0



### Monday, February 14, 2011 Page 19 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 7 Average Heat Input 3524 MMBtu/hr Method 29; Run M-1; Date - 4/1/2010; Start - 14:32; End - 19:06 0

8 Average Heat Input 3519 MMBtu/hr Method 29; Run M-2; Date - 4/2/2010; Start - 14:34; End - 19:06 0

9 Average Heat Input 3535 MMBtu/hr Method 29; Run M-3; Date - 4/3/2010; Start - 13:40; End - 18:05 0

1 Steam Output 2678 1000 lb Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 4/1/2010; Start - 16:08; End - 18:08 0



### 10Steam Output 2672 1000 lb Method 027/028; Run PM-1; Date - 4/1/2010; Start - 11:28; End - 14:07 0

11Steam Output 2663 1000 lb Method 027/028; Run PM-2; Date - 4/2/2010; Start - 11:18; End - 14:01 0

12Steam Output 2689 1000 lb Method 027/028; Run PM-3; Date - 4/3/2010; Start - 10:47; End - 13:17 0

2 Steam Output 2657 1000 lb Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 4/2/2010; Start - 15:03; End - 17:02 0

3 Steam Output 2654 1000 lb Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 4/2/2010; Start - 17:18; End - 19:18 0

4 Steam Output 2675 1000 lb Method 23; Run D/F-1; Date - 4/1/2010; Start - 08:38; End - 18:44 0

5 Steam Output 2663 1000 lb Method 23; Run D/F-2; Date - 4/2/2010; Start - 08:02; End - 17:17 0



### Monday, February 14, 2011 Page 20 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 6 Steam Output 2686 1000 lb Method 23; Run D/F-3; Date - 4/3/2010; Start - 09:39; End - 18:13 0

7 Steam Output 2678 1000 lb Method 29; Run M-1; Date - 4/1/2010; Start - 14:32; End - 19:06 0

8 Steam Output 2656 1000 lb Method 29; Run M-2; Date - 4/2/2010; Start - 14:34; End - 19:06 0

9 Steam Output 2684 1000 lb Method 29; Run M-3; Date - 4/3/2010; Start - 13:40; End - 18:05 0

1 Unit Gross Electrical Output 400 MWg Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 4/1/2010; Start - 16:08; End - 18:08 0



### 10Unit Gross Electrical Output 400 MWg Method 027/028; Run PM-1; Date - 4/1/2010; Start - 11:28; End - 14:07 0

11Unit Gross Electrical Output 400 MWg Method 027/028; Run PM-2; Date - 4/2/2010; Start - 11:18; End - 14:01 0

12Unit Gross Electrical Output 402 MWg Method 027/028; Run PM-3; Date - 4/3/2010; Start - 10:47; End - 13:17 0

2 Unit Gross Electrical Output 400 MWg Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 4/2/2010; Start - 15:03; End - 17:02 0

3 Unit Gross Electrical Output 400 MWg Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 4/2/2010; Start - 17:18; End - 19:18 0

4 Unit Gross Electrical Output 400 MWg Method 23; Run D/F-1; Date - 4/1/2010; Start - 08:38; End - 18:44 0



### Monday, February 14, 2011 Page 21 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 5 Unit Gross Electrical Output 400 MWg Method 23; Run D/F-2; Date - 4/2/2010; Start - 08:02; End - 17:17 0

6 Unit Gross Electrical Output 402 MWg Method 23; Run D/F-3; Date - 4/3/2010; Start - 09:39; End - 18:13 0

7 Unit Gross Electrical Output 400 MWg Method 29; Run M-1; Date - 4/1/2010; Start - 14:32; End - 19:06 0

8 Unit Gross Electrical Output 400 MWg Method 29; Run M-2; Date - 4/2/2010; Start - 14:34; End - 19:06 0

9 Unit Gross Electrical Output 402 MWg Method 29; Run M-3; Date - 4/3/2010; Start - 13:40; End - 18:05 0

1 Unit Net Electric Generation 381 MWn Methods 6c, 7e, 10, and 25a; Run RM-1 and FTIR-1; Date - 4/1/2010; Start - 16:08; End - 18:08 0



### 10Unit Net Electric Generation 381 MWn Method 027/028; Run PM-1; Date - 4/1/2010; Start - 11:28; End - 14:07 0

11Unit Net Electric Generation 381 MWn Method 027/028; Run PM-2; Date - 4/2/2010; Start - 11:18; End - 14:01 0

12Unit Net Electric Generation 382 MWn Method 027/028; Run PM-3; Date - 4/3/2010; Start - 10:47; End - 13:17 0

2 Unit Net Electric Generation 381 MWn Methods 6c, 7e, 10, and 25a; Run RM-2 and FTIR-2; Date - 4/2/2010; Start - 15:03; End - 17:02 0

3 Unit Net Electric Generation 381 MWn Methods 6c, 7e, 10, and 25a; Run RM-3 and FTIR-3; Date - 4/2/2010; Start - 17:18; End - 19:18 0



### Monday, February 14, 2011 Page 22 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010

APCD Run Data

Process Lab Run Data 4 Unit Net Electric Generation 381 MWn Method 23; Run D/F-1; Date - 4/1/2010; Start - 08:38; End - 18:44 0

5 Unit Net Electric Generation 381 MWn Method 23; Run D/F-2; Date - 4/2/2010; Start - 08:02; End - 17:17 0

6 Unit Net Electric Generation 382 MWn Method 23; Run D/F-3; Date - 4/3/2010; Start - 09:39; End - 18:13 0

7 Unit Net Electric Generation 381 MWn Method 29; Run M-1; Date - 4/1/2010; Start - 14:32; End - 19:06 0

8 Unit Net Electric Generation 381 MWn Method 29; Run M-2; Date - 4/2/2010; Start - 14:34; End - 19:06 0

9 Unit Net Electric Generation 382 MWn Method 29; Run M-3; Date - 4/3/2010; Start - 13:40; End - 18:05 0



### Run Name Value UOM Comments Target Value 1 LOW NOX BURNERS 370NOx Emissions 0


### 2 LOW NOX BURNERS 381NOx Emissions 0
3 LOW NOX BURNERS 382NOx Emissions 0
1 CYCLONE SEPARATORS 6.6 Opacity 0


### 2 CYCLONE SEPARATORS 7.6 Opacity 0
3 CYCLONE SEPARATORS 7.3 Opacity 0

Run Name Value UOM Comments 

### 1 Fuel Higher Heating Value 18500 Btu/lb 1 Fuel Moisture 0.646 % 1 Fuel Mercury Content 0.011 mg/kg 1 Fuel Chlorine Content 97 mg/kg 

### 1 Fuel Fluorine Content 64 mg/kg 1 Fuel Antimony Content 4.8 mg/kg 1 Fuel Arsenic Content 0.11 mg/kg 

### 1 Fuel Beryllium Content 0.008 mg/kg
Monday, February 14, 2011 Page 23 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 1 Fuel Cadmium Content 0.012 mg/kg 

### 1 Fuel Chromium Content 0.19 mg/kg 1 Fuel Cobalt Content 0.83 mg/kg 1 Fuel Lead Content 0.41 mg/kg 1 Fuel Manganese Content 0.8 mg/kg 

### 1 Fuel Nickel Content 20.1 mg/kg 1 Fuel Selenium Content 0.03 mg/kg 1 Fuel Sulfur Content 9370 mg/kg 

### 1 Fuel Proximate Analysis (Carbon) 87.85 % 1 Fuel Proximate Analysis (Hydrogen) 10.16 % 1 Fuel Proximate Analysis (Nitrogen) 0.5 % 1 Fuel Proximate Analysis (Oxygen) 0.5 % 

### 1 Fuel Proximate Analysis (Sulfur) 0.979 % 2 Fuel Higher Heating Value 18400 Btu/lb 2 Fuel Moisture 0.72 % 

### 2 Fuel Mercury Content 0.011 mg/kg 2 Fuel Chlorine Content 110 mg/kg 2 Fuel Fluorine Content 72 mg/kg 2 Fuel Antimony Content 1.8 mg/kg 

### 2 Fuel Arsenic Content 0.074 mg/kg 2 Fuel Beryllium Content 0.008 mg/kg 2 Fuel Cadmium Content 0.011 mg/kg 

### 2 Fuel Chromium Content 0.21 mg/kg 2 Fuel Cobalt Content 0.83 mg/kg 2 Fuel Lead Content 0.4 mg/kg 2 Fuel Manganese Content 0.9 mg/kg 

### 2 Fuel Nickel Content 20.1 mg/kg 2 Fuel Selenium Content 0.03 mg/kg 2 Fuel Sulfur Content 9140 mg/kg 

### 2 Fuel Proximate Analysis (Carbon) 87.9 % 2 Fuel Proximate Analysis (Hydrogen) 10.15 % 2 Fuel Proximate Analysis (Nitrogen) 0.5 % 2 Fuel Proximate Analysis (Oxygen) 0.5 % 

### 2 Fuel Proximate Analysis (Sulfur) 0.982 % 3 Fuel Higher Heating Value 18400 Btu/lb 3 Fuel Moisture 0.706 % 

### 3 Fuel Mercury Content 0.011 mg/kg 3 Fuel Chlorine Content 100 mg/kg 3 Fuel Fluorine Content 69 mg/kg 3 Fuel Antimony Content 1.4 mg/kg 

### 3 Fuel Arsenic Content 0.083 mg/kg 3 Fuel Beryllium Content 0.008 mg/kg 3 Fuel Cadmium Content 0.01 mg/kg



### Monday, February 14, 2011 Page 24 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 3 Fuel Chromium Content 0.15 mg/kg 

### 3 Fuel Cobalt Content 0.72 mg/kg 3 Fuel Lead Content 0.31 mg/kg 3 Fuel Manganese Content 1.1 mg/kg 3 Fuel Nickel Content 18.3 mg/kg 

### 3 Fuel Selenium Content 0.03 mg/kg 3 Fuel Sulfur Content 9280 mg/kg 3 Fuel Proximate Analysis (Carbon) 87.18 % 

### 3 Fuel Proximate Analysis (Hydrogen) 10.38 % 3 Fuel Proximate Analysis (Nitrogen) 0.59 % 3 Fuel Proximate Analysis (Oxygen) 0.54 % 3 Fuel Proximate Analysis (Sulfur) 1.01 %



### Monday, February 14, 2011 Page 25 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010 Sampling / Stack Data Results Detail


### Location PTP1 - D/F - Method 23 Average Run Number PTP1-23-1 PTP1-23-2 PTP1-23-3 Test Date 4/1/2010 4/2/2010 4/3/2010 Run Start Time 8:38:00 AM8:02:00 AM 9:39:00 AM Run Finish Time 6:44:00 PM5:17:00 PM 6:13:00 PM Net Traversing Points 12 12 12 Net Run Time, minutes 480 480 480 Nozzle Diameter, inches 0.25 0.25 0.25 0.250 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.987 0.987 0.987 0.987 Barometric Pressure, inches of Mercury 29.83 29.77 29.77 29.790 Average Orifice Meter Differential, inches H2O 2.56 2.52 2.48 2.520 Dry Gas Meter Volume Sampled, cubic feet 412.310 415.180 407.240 411.577 Average Dry Gas Meter Temperature, °F 72.17 75.92 77.54 75.210 Dry Gas Meter Volume Sampled, dscf 405.087 404.203 395.239 401.510 Total Moisture Liquid collected, g 956.3 988.7 939.4 961.467 Volume of Water Vapor, standard cubic feet 45.01 46.54 44.22 45.257 Moisture Content of Stack Gas, % 10.00 10.33 10.06 10.130 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.9 0.8967 0.8994 0.899 Carbon Dioxide, % 14.57 14.8 14.77 14.713 Oxygen, % 2.79 2.93 2.88 2.867 Carbon Monoxide & Nitrogen, % 82.64 82.27 82.35 82.420 Fuel Factor 1.24 1.21 1.22 Dry Molecular Weight, lb/lb-Mole 30.44 30.49 30.48 30.470 Wet Molecular weight, lb/lb-Mole 29.20 29.20 29.22 29.207 Flue Gas Static Pressure, inches of H2O 1 1 1 1.000 Absolute Flue Gas Pressure, inches of Mercury 29.90 29.84 29.84 29.860 Average Stack Gas Temperature, °F 278.92 290.00 303.67 290.863 Average Velocity Head, inches of H2O 0.9491081224 709640.941552327

6927490.934042909

798599 0.942
Average Stack Gas Velocity, feet/second 64.36 64.65 64.95 64.653 Stack Cross-Sectional Area, square feet 320.210 320.210 320.210 320.210 Dry Volumetric Flow Rate, dry scfm 794,677.3 782,009.0 773,897.8783,528.033 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,236,522.9 1,242,094.6 1,247,858.41,242,158.6 33 Percent Isokinetic of Sampling Rate, % 99.8 101.2 99.9 100.300 Percent Excess Air, % 14.7 15.6 15.3 15.200 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Round Duct Diameter, inches 242.3 242.3 242.3 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 26 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010
Location PTP1 - Gases - Method 10 Average Run Number 1-CO-1 1-CO-2 1-CO-3 Test Date 4/1/2010 4/2/2010 4/2/2010 Run Start Time 4:08:50 PM3:03:20 PM 5:18:50 PM Run Finish Time 6:08:20 PM5:02:50 PM 7:18:20 PM Carbon Dioxide, % 14.57 14.84 14.76 14.723 Oxygen, % 2.79 2.89 2.97 2.883 Fuel Factor 1.32 1.32 1.32 Dry Volumetric Flow Rate, dry scfm 794574 781958 781958786,163.333 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.02 10.34 10.34 10.233 Analyzer Make THERMO THERMO THERMO Analyzer Model 48i 48i 48i Analyzer Serial Number INST-CO0017 INST-CO0017 INST-CO0017 Operating Range 1109 1109 1109 1,109.000 Operating Units ppm ppm ppm No. Readings/Avg. 240 240 240 240.000 Calibration Set 5 11 11 9.000 Calibration Pre Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Pre Zero Cylinder Instrument Response 2.18 3.1 3.15 2.810 Calibration Pre Zero Cylinder Bias 0.19 0.32 0.32 0.277 Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID ALM042523- COALM042523

-COALM042523-

CO Calibration Pre High Cylinder Instrument Response 554.2 531.32 534.96 540.160 Calibration Pre High Cylinder Bias 0.08 -1.62 -1.3 -0.947 Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Post Zero Cylinder Instrument Response 3.34 3.15 3.01 3.167 Calibration Post Zero Cylinder Bias 0.3 0.32 0.31 0.310 Calibration Post Zero Cylinder Drift 0.11 0 0.01 0.040 Calibration Post High Cylinder ID ALM042523- COALM042523

-COALM042523-

CO Calibration Post High Cylinder Instrument Response 555.29 534.96 538.6 542.950 Calibration Post High Cylinder Bias 0.18 -1.3 -0.97 -0.697 Calibration Post High Cylinder Drift 0.1 0.32 0.33 0.250 Cavg 185.89 111.5 41.02 112.803 Cavg Units ppmvd ppmvd ppmvd Cgas 182.1397 112.257 39.0277 111.141 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units ppmvw ppmvw ppmvw



### Monday, February 14, 2011 Page 27 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010
Location PTP1 - Gases - Method 25A Average Run Number 1-THC-1 1-THC-2 1-THC-3 Test Date 4/1/2010 4/2/2010 4/2/2010 Run Start Time 4:08:50 PM3:03:20 PM 5:18:50 PM Run Finish Time 6:08:20 PM5:02:50 PM 7:18:20 PM Carbon Dioxide, % 14.57 14.84 14.76 14.723 Oxygen, % 2.79 2.89 2.97 2.883 Fuel Factor 1.32 1.32 1.32 Dry Volumetric Flow Rate, dry scfm 794574 781958 781958786,163.333 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.02 10.34 10.34 10.233 Analyzer Make VIG VIG VIG Analyzer Model 20 20 20 20.000 Analyzer Serial Number INST-TH0007 INST-TH0007 INST-TH0007 Operating Range 50 50 50 50.000 Operating Units ppm ppm ppm No. Readings/Avg. 240 240 240 240.000 Calibration Set 6 12 12 10.000 Calibration Pre Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Pre Zero Cylinder Instrument Response -0.09 -0.18 0.02 -0.083 Calibration Pre Zero Cylinder Bias 0 -0.58 -0.18 -0.253 Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID CC115743 CC115743 CC115743 Calibration Pre High Cylinder Instrument Response 14.01 14.01 14.04 14.020 Calibration Pre High Cylinder Bias 0 -0.34 -0.28 -0.207 Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Post Zero Cylinder Instrument Response -0.11 0.02 0.11 0.007 Calibration Post Zero Cylinder Bias -0.04 -0.18 0 -0.073 Calibration Post Zero Cylinder Drift 0.04 0.4 0.18 0.207 Calibration Post High Cylinder ID CC115743 CC115743 CC115743 Calibration Post High Cylinder Instrument Response 14.04 14.04 14.2 14.093 Calibration Post High Cylinder Bias 0.06 -0.28 0.04 -0.060 Calibration Post High Cylinder Drift 0.06 0.06 0.32 0.147 Cavg 0.59 1.03 0.23 0.617 Cavg Units ppmvw ppmvw ppmvw Cgas 0.7818 1.2639 0.1885 0.745 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0.7034336283 185841.133215171

924850.169050160

085379 0.669
Cgasw Units ppmvw ppmvw ppmvw



### Monday, February 14, 2011 Page 28 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010
Location PTP1 - Gases - Method 3A CO2 Average Run Number 1-CO2-1 1-CO2-2 1-CO2-3 Test Date 4/1/2010 4/2/2010 4/2/2010 Run Start Time 4:08:50 PM3:03:20 PM 5:18:50 PM Run Finish Time 6:08:20 PM5:02:50 PM 7:18:20 PM Carbon Dioxide, % 14.57 14.84 14.76 14.723 Oxygen, % 2.79 2.89 2.97 2.883 Fuel Factor 1.32 1.32 1.32 Dry Volumetric Flow Rate, dry scfm 794574 781958 781958786,163.333 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.02 10.34 10.34 10.233 Analyzer Make THERMO THERMO THERMO Analyzer Model 410i 410i 410i Analyzer Serial Number INST-C2-0010 INST-C2- 0010 INST-C2-

0010 Operating Range 19.3 19.3 19.3 19.300 Operating Units % % % No. Readings/Avg. 240 240 240 240.000 Calibration Set 2 8 8 6.000 Calibration Pre Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Pre Zero Cylinder Instrument Response 0.08 0.05 0.09 0.073 Calibration Pre Zero Cylinder Bias 0.21 0.1 0.31 0.207 Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID AAL12025- CO2AAL12025-

CO2 AAL12025-

CO2 Calibration Pre High Cylinder Instrument Response 8.72 8.43 8.54 8.563 Calibration Pre High Cylinder Bias -0.83 -2.44 -1.87 -1.713 Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Post Zero Cylinder Instrument Response 0.05 0.09 0.11 0.083 Calibration Post Zero Cylinder Bias 0.05 0.31 0.41 0.257 Calibration Post Zero Cylinder Drift 0.16 0.21 0.1 0.157 Calibration Post High Cylinder ID AAL12025- CO2AAL12025-

CO2 AAL12025-

CO2 Calibration Post High Cylinder Instrument Response 8.79 8.54 8.53 8.620 Calibration Post High Cylinder Bias -0.47 -1.87 -1.92 -1.420 Calibration Post High Cylinder Drift 0.36 0.574.999999999 99998E-02 0.327
Cavg 14.3 14.12 14.11 14.177 Cavg Units %vd %vd %vd Cgas 14.5626 14.8431 14.7657 14.724 Cgas Units %vd %vd %vd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units %vw %vw %vw



### Monday, February 14, 2011 Page 29 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010
Location PTP1 - Gases - Method 3A O2 Average Run Number 1-O2-1 1-O2-2 1-O2-3 Test Date 4/1/2010 4/2/2010 4/2/2010 Run Start Time 4:08:50 PM3:03:20 PM 5:18:50 PM Run Finish Time 6:08:20 PM5:02:50 PM 7:18:20 PM Carbon Dioxide, % 14.57 14.84 14.76 14.723 Oxygen, % 2.79 2.89 2.97 2.883 Fuel Factor 1.32 1.32 1.32 Dry Volumetric Flow Rate, dry scfm 794574 781958 781958786,163.333 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.02 10.34 10.34 10.233 Analyzer Make THERMO THERMO THERMO Analyzer Model 42i-HL 42i-HL 42i-HL Analyzer Serial Number INST-N2-0002 INST-N2- 0002 INST-N2-

0002 Operating Range 21.1 21.1 21.1 21.100 Operating Units % % % No. Readings/Avg. 240 240 240 240.000 Calibration Set 1 7 7 5.000 Calibration Pre Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Pre Zero Cylinder Instrument Response 0.49 0.41 0.24 0.380 Calibration Pre Zero Cylinder Bias 2.18 2.09 1.28 1.850 Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID AAL12025-O2AAL12025- O2 AAL12025-

O2 Calibration Pre High Cylinder Instrument Response 12.2 11.93 11.8 11.977 Calibration Pre High Cylinder Bias 0.62 -0.57 -1.18 -0.377 Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Post Zero Cylinder Instrument Response 0.27 0.24 0.09 0.200 Calibration Post Zero Cylinder Bias 1.14 1.28 0.57 0.997 Calibration Post Zero Cylinder Drift 1.04 0.81 0.71 0.853 Calibration Post High Cylinder ID AAL12025-O2AAL12025- O2 AAL12025-

O2 Calibration Post High Cylinder Instrument Response 11.84 11.8 11.8 11.813 Calibration Post High Cylinder Bias -1.09 -1.18 -1.18 -1.150 Calibration Post High Cylinder Drift 1.71 0.61 0 0.773 Cavg 3.07 3.08 3.02 3.057 Cavg Units %vd %vd %vd Cgas 2.7963 2.8887 2.9691 2.885 Cgas Units %vd %vd %vd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units %vw %vw %vw



### Monday, February 14, 2011 Page 30 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010
Location PTP1 - Gases - Method 6C Average Run Number 1-SO2-1 1-SO2-2 1-SO2-3 Test Date 4/1/2010 4/2/2010 4/2/2010 Run Start Time 4:08:50 PM3:03:20 PM 5:18:50 PM Run Finish Time 6:08:20 PM5:02:50 PM 7:18:20 PM Carbon Dioxide, % 14.57 14.84 14.76 14.723 Oxygen, % 2.79 2.89 2.97 2.883 Fuel Factor 1.32 1.32 1.32 Dry Volumetric Flow Rate, dry scfm 794574 781958 781958786,163.333 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.02 10.34 10.34 10.233 Analyzer Make THERMO THERMO THERMO Analyzer Model 43i-HL 43i-HL 43i-HL Analyzer Serial Number INST-S2-0005 INST-S2- 0005 INST-S2-

0005 Operating Range 959 959 959 959.000 Operating Units ppm ppm ppm No. Readings/Avg. 240 240 240 240.000 Calibration Set 3 9 9 7.000 Calibration Pre Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Pre Zero Cylinder Instrument Response 4.45 6.04 7.48 5.990 Calibration Pre Zero Cylinder Bias 0.43 0.6 0.75 0.593 Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID CC66246 CC66246 CC66246 Calibration Pre High Cylinder Instrument Response 441.32 424.96 420.53 428.937 Calibration Pre High Cylinder Bias 0.06 -1 -1.46 -0.800 Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Post Zero Cylinder Instrument Response 7.34 7.48 11.1 8.640 Calibration Post Zero Cylinder Bias 0.74 0.75 1.13 0.873 Calibration Post Zero Cylinder Drift 0.31 0.15 0.38 0.280 Calibration Post High Cylinder ID CC66246 CC66246 CC66246 Calibration Post High Cylinder Instrument Response 433.36 420.53 421.72 425.203 Calibration Post High Cylinder Bias -0.77 -1.46 -1.34 -1.190 Calibration Post High Cylinder Drift 0.83 0.46 0.12 0.470 Cavg 564.09 551.62 554.75 556.820 Cavg Units ppmvd ppmvd ppmvd Cgas 553.7379 560.5973 566.8699 560.402 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units ppmvw ppmvw ppmvw



### Monday, February 14, 2011 Page 31 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010
Location PTP1 - Gases - Method 7E Average Run Number 1-NOx-1 1-NOx-2 1-NOx-3 Test Date 4/1/2010 4/2/2010 4/2/2010 Run Start Time 4:08:50 PM3:03:20 PM 5:18:50 PM Run Finish Time 6:08:20 PM5:02:50 PM 7:18:20 PM Carbon Dioxide, % 14.57 14.84 14.76 14.723 Oxygen, % 2.79 2.89 2.97 2.883 Fuel Factor 1.32 1.32 1.32 Dry Volumetric Flow Rate, dry scfm 794574 781958 781958786,163.333 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 10.02 10.34 10.34 10.233 Analyzer Make THERMO THERMO THERMO Analyzer Model 42i-HL 42i-HL 42i-HL Analyzer Serial Number INST-N2-0002 INST-N2- 0002 INST-N2-

0002 Operating Range 1110 1110 1110 1,110.000 Operating Units ppm ppm ppm No. Readings/Avg. 240 240 240 240.000 Calibration Set 4 10 10 8.000 Calibration Pre Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Pre Zero Cylinder Instrument Response 1.62 1.84 1.96 1.807 Calibration Pre Zero Cylinder Bias 0.12 0.14 0.15 0.137 Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID ALM042523- NOxALM042523

-NOxALM042523-

NOx Calibration Pre High Cylinder Instrument Response 563.68 531.31 529.76 541.583 Calibration Pre High Cylinder Bias -0.16 -1.93 -2.07 -1.387 Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID ALM031337ALM031337ALM031337 Calibration Post Zero Cylinder Instrument Response 1.39 1.96 1.89 1.747 Calibration Post Zero Cylinder Bias 0.1 0.15 0.15 0.133 Calibration Post Zero Cylinder Drift 0.029.999999999 99998E-03 0 0.010
Calibration Post High Cylinder ID ALM042523- NOxALM042523

-NOxALM042523-

NOx Calibration Post High Cylinder Instrument Response 552.64 529.76 531.51 537.970 Calibration Post High Cylinder Bias -1.15 -2.07 -1.91 -1.710 Calibration Post High Cylinder Drift 0.99 0.14 0.16 0.430 Cavg 446.51 443.41 450.57 446.830 Cavg Units ppmvd ppmvd ppmvd Cgas 437.2865 456.8482 464.1653 452.767 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units ppmvw ppmvw ppmvw



### Monday, February 14, 2011 Page 32 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010
Location PTP1 - Metals - Method 29 Average Run Number PTP1-29-1 PTP1-29-2 PTP1-29-3 Test Date 4/1/2010 4/2/2010 4/3/2010 Run Start Time 2:32:00 PM2:34:00 PM 1:40:00 PM Run Finish Time 7:06:00 PM7:06:00 PM 6:05:00 PM Net Traversing Points 12 12 12 Net Run Time, minutes 240 240 240 Nozzle Diameter, inches 0.25 0.25 0.25 0.250 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.979 0.979 0.979 0.979 Barometric Pressure, inches of Mercury 29.88 29.77 29.8 29.817 Average Orifice Meter Differential, inches H2O 2.28 2.32 2.45 2.350 Dry Gas Meter Volume Sampled, cubic feet 198.640 205.000 209.330 204.323 Average Dry Gas Meter Temperature, °F 76.96 81.54 80.46 79.653 Dry Gas Meter Volume Sampled, dscf 192.039 195.812 200.612 196.154 Total Moisture Liquid collected, g 459.3 477.5 451.8 462.867 Volume of Water Vapor, standard cubic feet 21.62 22.48 21.27 21.790 Moisture Content of Stack Gas, % 10.12 10.30 9.59 10.003 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8988 0.897 0.9041 0.900 Carbon Dioxide, % 14.57 14.8 14.77 14.713 Oxygen, % 2.79 2.93 2.88 2.867 Carbon Monoxide & Nitrogen, % 82.64 82.27 82.35 82.420 Fuel Factor 1.24 1.21 1.22 Dry Molecular Weight, lb/lb-Mole 30.44 30.49 30.48 30.470 Wet Molecular weight, lb/lb-Mole 29.18 29.20 29.28 29.220 Flue Gas Static Pressure, inches of H2O 1 1 1 1.000 Absolute Flue Gas Pressure, inches of Mercury 29.95 29.84 29.87 29.887 Average Stack Gas Temperature, °F 280.75 287.17 305.83 291.250 Average Velocity Head, inches of H2O 0.9094438747 674450.922651781

470920.986549073

441848 0.940
Average Stack Gas Velocity, feet/second 63.05 63.88 66.74 64.557 Stack Cross-Sectional Area, square feet 320.210 320.210 320.210 320.210 Dry Volumetric Flow Rate, dry scfm 776,840.4 775,881.2 797,928.5783,550.033 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,211,354.4 1,227,300.9 1,282,248.91,240,301.4 00 Percent Isokinetic of Sampling Rate, % 96.8 98.8 98.4 98.000 Percent Excess Air, % 14.7 15.6 15.3 15.200 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Round Duct Diameter, inches 242.3 242.3 242.3 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 33 of 34

### Turkey Point Energy Center, Unit #1, Information Collection Request
6/22/2010
Location PTP1 - PM - OTM - 27/28 Average Run Number PTP1-27/28-1PTP1-27/28- 2PTP1-27/28-3

Test Date 4/1/2010 4/2/2010 4/3/2010 Run Start Time 11:28:00 AM11:18:00 AM10:47:00 AM Run Finish Time 2:07:00 PM2:01:00 PM 1:17:00 PM Net Traversing Points 12 12 12 Net Run Time, minutes 131 130 131 Nozzle Diameter, inches 0.156 0.156 0.156 0.156 Pitot Tube Coefficient 0.8 0.8 0.8 0.800 Dry Gas Meter Calibration Factor 0.979 0.979 0.979 0.979 Barometric Pressure, inches of Mercury 29.8 29.85 29.77 29.807 Average Orifice Meter Differential, inches H2O 0.40 0.40 0.40 0.400 Dry Gas Meter Volume Sampled, cubic feet 47.390 47.900 43.620 46.303 Average Dry Gas Meter Temperature, °F 73.79 78.13 76.54 76.153 Dry Gas Meter Volume Sampled, dscf 45.753 45.949 41.855 44.519 Total Moisture Liquid collected, g 123.9 107.6 97.5 109.667 Volume of Water Vapor, standard cubic feet 5.83 5.06 4.59 5.160 Moisture Content of Stack Gas, % 11.30 9.92 9.88 10.367 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.887 0.9008 0.9012 0.896 Carbon Dioxide, % 14.57 14.8 14.77 14.713 Oxygen, % 2.79 2.93 2.88 2.867 Carbon Monoxide & Nitrogen, % 82.64 82.27 82.35 82.420 Fuel Factor 1.24 1.21 1.22 Dry Molecular Weight, lb/lb-Mole 30.44 30.49 30.48 30.470 Wet Molecular weight, lb/lb-Mole 29.03 29.25 29.25 29.177 Flue Gas Static Pressure, inches of H2O 1 1 1 1.000 Absolute Flue Gas Pressure, inches of Mercury 29.87 29.92 29.84 29.877 Average Stack Gas Temperature, °F 281.92 292.92 303.08 292.640 Average Velocity Head, inches of H2O 0.9355257028 800710.984100902

6548070.969883457

527265 0.963
Average Stack Gas Velocity, feet/second 61.19 62.93 62.98 62.367 Stack Cross-Sectional Area, square feet 320.210 320.210 320.210 320.210 Dry Volumetric Flow Rate, dry scfm 740,867.8 763,760.8 752,507.9752,378.833 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,175,619.0 1,209,048.9 1,210,009.51,198,225.8 00 Percent Isokinetic of Sampling Rate, % 113.7 111.6 102.4 109.233 Percent Excess Air, % 14.7 15.6 15.3 15.200 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Round Duct Diameter, inches 242.3 242.3 242.3 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000



### Monday, February 14, 2011 Page 34 of 34