Facility _Information facility _id utility

_code legal_owner_nam e

legl_operator_name

legal_address_ty pe

legal_address

legal_city legal_state legal_zip 2169 2169 Central Electric Power Cooperative Central Electric Power Cooperative

operator 9321 Highway 100 Chamois MO 65024

Page 1Facility _Information plant_nam e

physical_address

phyical_city

physical_state

physical_zip

ma iling_address

ma iling_city

ma iling_state

ma iling_zip Chamois Power Plant

9321 Highway

100 Chamois MO 65024 9321 Highway 100 Chamois MO 65024

Page 2Facility _Information RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas Yes TRUE TRUE FALSE FALSE TRUE TRUE TRUE FALSE

Page 3Facility _Information ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note TRUE TRUE Report within 10 days of eventSSM reporting within 2 days of becoming aware of event - 10 CSR 10-6.050List in Semi-annual Monitoring Report and Annual Compliance Certification No 1 Barrel = 42 GallonsDesign and Operating Steam Reheat Temperature are left blank since this unit does not utilize a steam reheat cycle.Stack Diameter is approximate average. Actual stack is rectangular in cross section with inside dimensions of 84 inches by 79 inches.Sample ID# 2009 (and the corresponding coal Shipment ID "2009 Composite") information represents an annual composite analysis of all 12 months of PRB coal received from the North Antelope Rochelle Mine in 2009. The dry coal tonnage is the sum of all 12 previously recorded PRB monthly shipments.Fuel analysis was not performed as part of the Ontario-Hydro Hg testing (Hg122005) and the particulate matter testing (PM052005).

Page 4Facility _Information 1 Barrel = 42 GallonsDesign and Operating Steam Reheat Temperature are left blank since this unit does not utilize a steam reheat cycle.Stack Diameter is approximate average. Actual stack is rectangular in cross section with inside dimensions of 84 inches by 79 inches.Sample ID# 2009 (and the corresponding coal Shipment ID "2009 Composite") information represents an annual composite analysis of all 12 months of PRB coal received from the North Antelope Rochelle Mine in 2009. The dry coal tonnage is the sum of all 12 previously recorded PRB monthly shipments.Fuel analysis was not performed as part of the Ontario-Hydro Hg testing (Hg122005) and the particulate matter testing (PM052005).

Page 5Facility _Information 1 Barrel = 42 GallonsDesign and Operating Steam Reheat Temperature are left blank since this unit does not utilize a steam reheat cycle.Stack Diameter is approximate average. Actual stack is rectangular in cross section with inside dimensions of 84 inches by 79 inches.Sample ID# 2009 (and the corresponding coal Shipment ID "2009 Composite") information represents an annual composite analysis of all 12 months of PRB coal received from the North Antelope Rochelle Mine in 2009. The dry coal tonnage is the sum of all 12 previously recorded PRB monthly shipments.Fuel analysis was not performed as part of the Ontario-Hydro Hg testing (Hg122005) and the particulate matter testing (PM052005).

Page 6Facility _Information 1 Barrel = 42 GallonsDesign and Operating Steam Reheat Temperature are left blank since this unit does not utilize a steam reheat cycle.Stack Diameter is approximate average. Actual stack is rectangular in cross section with inside dimensions of 84 inches by 79 inches.Sample ID# 2009 (and the corresponding coal Shipment ID "2009 Composite") information represents an annual composite analysis of all 12 months of PRB coal received from the North Antelope Rochelle Mine in 2009. The dry coal tonnage is the sum of all 12 previously recorded PRB monthly shipments.Fuel analysis was not performed as part of the Ontario-Hydro Hg testing (Hg122005) and the particulate matter testing (PM052005).

Page 7Facility _Information 1 Barrel = 42 GallonsDesign and Operating Steam Reheat Temperature are left blank since this unit does not utilize a steam reheat cycle.Stack Diameter is approximate average. Actual stack is rectangular in cross section with inside dimensions of 84 inches by 79 inches.Sample ID# 2009 (and the corresponding coal Shipment ID "2009 Composite") information represents an annual composite analysis of all 12 months of PRB coal received from the North Antelope Rochelle Mine in 2009. The dry coal tonnage is the sum of all 12 previously recorded PRB monthly shipments.Fuel analysis was not performed as part of the Ontario-Hydro Hg testing (Hg122005) and the particulate matter testing (PM052005).

Page 8Facility _Information 1 Barrel = 42 GallonsDesign and Operating Steam Reheat Temperature are left blank since this unit does not utilize a steam reheat cycle.Stack Diameter is approximate average. Actual stack is rectangular in cross section with inside dimensions of 84 inches by 79 inches.Sample ID# 2009 (and the corresponding coal Shipment ID "2009 Composite") information represents an annual composite analysis of all 12 months of PRB coal received from the North Antelope Rochelle Mine in 2009. The dry coal tonnage is the sum of all 12 previously recorded PRB monthly shipments.Fuel analysis was not performed as part of the Ontario-Hydro Hg testing (Hg122005) and the particulate matter testing (PM052005).

Page 9Facility _Information 1 Barrel = 42 GallonsDesign and Operating Steam Reheat Temperature are left blank since this unit does not utilize a steam reheat cycle.Stack Diameter is approximate average. Actual stack is rectangular in cross section with inside dimensions of 84 inches by 79 inches.Sample ID# 2009 (and the corresponding coal Shipment ID "2009 Composite") information represents an annual composite analysis of all 12 months of PRB coal received from the North Antelope Rochelle Mine in 2009. The dry coal tonnage is the sum of all 12 previously recorded PRB monthly shipments.Fuel analysis was not performed as part of the Ontario-Hydro Hg testing (Hg122005) and the particulate matter testing (PM052005).

Page 10Facility _Information 1 Barrel = 42 GallonsDesign and Operating Steam Reheat Temperature are left blank since this unit does not utilize a steam reheat cycle.Stack Diameter is approximate average. Actual stack is rectangular in cross section with inside dimensions of 84 inches by 79 inches.Sample ID# 2009 (and the corresponding coal Shipment ID "2009 Composite") information represents an annual composite analysis of all 12 months of PRB coal received from the North Antelope Rochelle Mine in 2009. The dry coal tonnage is the sum of all 12 previously recorded PRB monthly shipments.Fuel analysis was not performed as part of the Ontario-Hydro Hg testing (Hg122005) and the particulate matter testing (PM052005).

Page 11facility _contacts facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 2169 1 Environm ental & Operations Engineer Michael Stiefermann

5737635314223 mstiefermann@cepc.net TRUE

Page 12facility _coal_utilized facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note 2169 bitum inous 4 4 2169 subbituminous 96 96

Page 13facility _oil_utilized facility _id oil_type percentage_volume percentage_btu

other_type 2169 No.2 Fuel Oil (distillate) 97 97 2169 other (specify) 3 3 Wa ste Oil

Page 14facility _other_materials facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain 2169 Wa ste Oil TRUE TRUE 16 num ber/year 16 barrels were burned during 20091 barrel = 42 gallons

Yes Only

on-spec or off-spec used oil is combusted in the boilers

Page 15facility _other_materials rcra_explain Only on-spec or off-spec used oil is combusted in the boilers

Page 16boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuel heat_input ma x_heat_input MW e_capacity 2169 2 Cyclone firing We t Bottom coal 550 563 50

Page 17boiler_information

MW e_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 47 89 85 1275 1260 955 950 FALSE

Page 18boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 7725 85 N FALSE

Page 19boiler_information

NOx_control

SO2_control

combustion_additives No Yes No

Page 20boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 2169 2 coal - bituminous 2007 1 2 2169 2 coal - bituminous 2008 1 1 2169 2 coal - bituminous 2009 4 4 2169 2 coal - subbituminous 2007 99 98 2169 2 coal - subbituminous 2008 99 99 2169 2 coal - subbituminous 2009 96 96 2169 2 oil - distillate 2007 0 0 2169 2 oil - distillate 2008 0 0 2169 2 oil - distillate 2009 0 0

Page 21boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online

Page 22boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online 2169 2 Low Sulfur Coal 12/1/1999 2169 2 Low Sulfur Fuel Oil 11/1/2005

Page 23boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 24facility _units facility _id unit_id 2169 U2BLR

Page 25unit_boilers

facility _id unit_id boiler_id 2169 U2BLR 2

Page 26facility _controls facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 2169 U2ESP PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 6/1/1976

Page 27facility _controls reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

Page 28facility _sampling_ports facility _id sampling_port_id 2169 U2PORT

Page 29facility _stacks facility _id stack_id stack_height stack_diameter

sack_gas_velocity 2169 U2STACK 162 6.8 45

Page 30configurations

facility _id configuration_id 2169 Unit 2

Page 31configuration_components

facility _id configuration_id

component_id

order component_ty pe port_near 2169 Unit 2 U2BLR 1 Unit 2169 Unit 2 U2ESP 2 PM control 2169 Unit 2 U2PORT 3 Sam pling Port next 2169 Unit 2 U2STACK 4 Stack

Page 32configuration_pollutants1

facility _id configuration_id

pollutant_nam e

permit_ty pe_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 2169 Unit 2 PM (Filterable) Fderal - Title V Operating Permit

0.28 pound per million British Thermal Unit (lb/MMBtu)

3 hours 2169 Unit 2 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

6.7 pound per million British Thermal Unit (lb/MMBtu)

3 hours

Page 33configuration_pollutants1

avg_period_2

em lim it_details

test_method

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping Stack Test. CAM Plan (Pending)

0.18 pound per million British Thermal Unit (lb/MMBtu)

No CAM Plan Pending. CAM Monitoring by PM correlation with Part 60 COMS CAM Plan. COMS data for 5 years. COMS certification and QA/QC. Excursion reports to MDNR. Corrective actions. 6.7 pound per million British Thermal Unit (lb/MMBtu)

No Permit Limit Part 60/75 CEMS

CEMS data for 5 years. Permit limit exceedances and monitor downtime data. Fuel Oil < 0.5% sulfur by weight.

Page 34configuration_pollutants1

req_reporting 1-hour excursions of opacity indicator range - as generated basis. Semi-annual (SA) summary of number, duration, and cause of excursions. SA COMS downtime. Quarterly

exceedance and monitor downtime reports. Semi-Annual and Annual permit compliance certification summaries.

Page 35configuration_pollutants1 1-hour excursions of opacity indicator range - as generated basis. Semi-annual (SA) summary of number, duration, and cause of excursions. SA COMS downtime. Quarterly

exceedance and monitor downtime reports. Semi-Annual and Annual permit compliance certification summaries.

Page 36control_technologies

facility _id configuration_id

component_id

control_id project_title project_ty pe vendor_name

vndor_contact

vendor_phone

Page 37control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 38control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 39control_technologies feed_rate_units

Page 40control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 41control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_nam e

Page 42control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investm ent

total_operating_costs

base_year

Page 43control_costs

CBI

Page 44mi sc_controls

facility _id mi sc_control_id

control_description 2169 1 Low Sulfur Coal and Diesel Fuel Oil

Page 45mi sc_control_configurations

facility _id mi sc_control_id

configuration_id 2169 1 Unit 2

Page 46fuel_shipments

facility _id shipment_id

shipment_date

am ount_received

am ount_units

fuel_type state_country other_country

county 2169 2009 Composite

12/1/2009 164332 short tons (2000 lbs) coal WY WY - Campbell 2169 DFO01 1/1/2009 191 barrels oil 2169 DFO05 5/1/2009 191 barrels oil 2169 DFO06 6/1/2009 176 barrels oil 2169 DFO08 8/1/2009 190 barrels oil 2169 DFO10 10/1/2009 190 barrels oil 2169 ILL01 1/1/2009 2471 short tons (2000 lbs) coal IL IL - Randolph 2169 ILL02 2/1/2009 1148 short tons (2000 lbs) coal IL IL - Randolph 2169 ILL07 7/1/2009 1230 short tons (2000 lbs) coal IL IL - Randolph 2169 ILL10 10/1/2009 1451 short tons (2000 lbs) coal IL IL - Randolph 2169 ILL11 11/1/2009 2475 short tons (2000 lbs) coal IL IL - Randolph 2169 ILL12 12/1/2009 3430 short tons (2000 lbs) coal IL IL - Randolph 2169 PRB01 1/1/2009 17501 short tons (2000 lbs) coal WY WY - Campbell 2169 PRB02 2/1/2009 13428 short tons (2000 lbs) coal WY WY - Campbell 2169 PRB03 3/1/2009 14818 short tons (2000 lbs) coal WY WY - Campbell 2169 PRB04 4/1/2009 12931 short tons (2000 lbs) coal WY WY - Campbell 2169 PRB05 5/1/2009 13018 short tons (2000 lbs) coal WY WY - Campbell 2169 PRB06 6/1/2009 16566 short tons (2000 lbs) coal WY WY - Campbell 2169 PRB07 7/1/2009 14762 short tons (2000 lbs) coal WY WY - Campbell 2169 PRB08 8/1/2009 12717 short tons (2000 lbs) coal WY WY - Campbell 2169 PRB09 9/1/2009 5631 short tons (2000 lbs) coal WY WY - Campbell 2169 PRB10 10/1/2009 11268 short tons (2000 lbs) coal WY WY - Campbell 2169 PRB11 11/1/2009 17031 short tons (2000 lbs) coal WY WY - Campbell 2169 PRB12 12/1/2009 14661 short tons (2000 lbs) coal WY WY - Campbell 2169 THM07 7/1/2009 830 short tons (2000 lbs) coal MO MO - Randolph 2169 THM08 8/1/2009 2518 short tons (2000 lbs) coal MO MO - Randolph 2169 THM09 9/1/2009 2301 short tons (2000 lbs) coal MO MO - Randolph 2169 THM10 10/1/2009 1614 short tons (2000 lbs) coal MO MO - Randolph

Page 47fuel_shipments

coal_seam shipment_method Wyodak-Anderson

Unit Train Trucks Trucks Trucks Trucks Trucks Herrin No. 6

Trucks Herrin No. 6

Trucks Herrin No. 6

Trucks Herrin No. 6

Trucks Herrin No. 6

Trucks Herrin No. 6

Trucks Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Wyodak-Anderson

Unit Train Bee Veer / Prarie Hill (Closed)Bee Veer / Prarie Hill (Closed)

Trucks Bee Veer / Prarie Hill (Closed)

Trucks Bee Veer / Prarie Hill (Closed)

Trucks Bee Veer / Prarie Hill (Closed)

Trucks

Page 48fuel_shipment_configurations

facility _id shipment_id

configuration_id 2169 2009 Composite

Unit 2 2169 DFO01 Unit 2 2169 DFO05 Unit 2 2169 DFO06 Unit 2 2169 DFO08 Unit 2 2169 DFO10 Unit 2 2169 ILL01 Unit 2 2169 ILL02 Unit 2 2169 ILL07 Unit 2 2169 ILL10 Unit 2 2169 ILL11 Unit 2 2169 ILL12 Unit 2 2169 PRB01 Unit 2 2169 PRB02 Unit 2 2169 PRB03 Unit 2 2169 PRB04 Unit 2 2169 PRB05 Unit 2 2169 PRB06 Unit 2 2169 PRB07 Unit 2 2169 PRB08 Unit 2 2169 PRB09 Unit 2 2169 PRB10 Unit 2 2169 PRB11 Unit 2 2169 PRB12 Unit 2 2169 THM07 Unit 2 2169 THM08 Unit 2 2169 THM09 Unit 2 2169 THM10 Unit 2

Page 49fuel_shipment_samples

facility _id shipment_id

sample_id am ount_fuel am ount_fuel_units

total_sulfur ash_content heating_value

hating_units 2169 2009 Composite

2009 164332 tons 0.29 6.25 12045 Btu/lb

Page 50fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address 10 parts per million (dry) (ppm) 75 parts per million (dry) (ppm)

other (please specify)

TRI Reporting

Fuel supplier

Peabody Coal Company

Page 51fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_nam e lab_address lab_city lab_state lab_zip analysis_copies Peabody Coal Company WY No

Page 52fuel_shipment_samples analysis_copies

Page 53fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL 2169 2009 Composite

2009 Antim ony

(Sb) 0.5 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Arsenic (As) 0.5 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Barium (Ba) 357 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Beryllium (Be) 0.2 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Cadmium (Cd) 0.1 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Chromium (Cr) 4 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Cobalt (Co) 2 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Copper (Cu) 11 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Lead (Pb) 1 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Manganese (Mn) 7 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Mercury

(Hg) 0.07 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Molybdenum (Mo) 1 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Nickel (Ni) 3 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Selenium (Se) 0.5 parts per million (dry) (ppm) FALSE 2169 2009 Composite

2009 Vanadium (V) 11 parts per million (dry) (ppm) FALSE

Page 54test_reports

facility _id report_id report_type other_type report_description report_begin_date

report_end_date

before_control

during_deviation 2169 Hg012006 other Hg Baseline Method 324 testing for baseline mercury and fuel additive for mercury reduction trial. 1/10/2006 1/10/2006 No No 2169 Hg122005 other Hg Baseline Testing for baseline mercury - Ontario-Hydro Method ######## ######## No No 2169 PM052005 compliance EPA Method 17 testing for baseline Particulate Matter to develop CAM plan. 5/11/2005 5/11/2005 No No

Page 55test_reports

deviation_reports No No No

Page 56test_report_configurations

facility _id report_id configuration_id 2169 Hg012006 Unit 2 2169 Hg122005 Unit 2 2169 PM052005 Unit 2

Page 57test_report_fuels

facility _id report_id fuel_id 2169 Hg012006 PRB 2169 Hg122005 PRB 2169 PM052005 PRB

Page 58test_report_fuel_ty pes

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 2169 Hg012006 PRB coal - subbituminous 100 100 2169 Hg122005 PRB coal - subbituminous 100 100 2169 PM052005 PRB coal - subbituminous 100 100

Page 59cem_data

facility _id tim e_period

cem_period_description

Page 60cem_data_pollutants1

facility _id tim e_period

pollutant_nam e

Page 61test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_by pass_percent

testing_bypass_percent 2169 Hg012006 U2PORT No No 2169 Hg122005 U2PORT No No 2169 PM052005 U2PORT No No

Page 62test_report_sampling

fg_fraction 100% 100% 100%

Page 63sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetim e

unit_load net_generation fg_moisture_content 2169 Hg012006 U2PORT 1 1/10/2006 1/10/2006 52 98 2169 Hg012006 U2PORT 2 1/10/2006 1/10/2006 52 98 2169 Hg012006 U2PORT 3 1/10/2006 1/10/2006 52 98 2169 Hg122005 U2PORT 1 ######## ######## 51 108 12.8 2169 Hg122005 U2PORT 2 ######## ######## 51 108 12.7 2169 Hg122005 U2PORT 3 ######## ######## 51 108 12.7 2169 PM052005 U2PORT 1 5/11/2005 5/11/2005 51 54 11.8 2169 PM052005 U2PORT 2 5/11/2005 5/11/2005 51 56 12.1 2169 PM052005 U2PORT 3 5/11/2005 5/11/2005 50 51 11.8

Page 64sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 297 300 300 112525 dscfm 2.7 16.6 300 112837 dscfm 2.7 16.6 300 113795 dscfm 2.6 16.8 300 114691 dscfm 2.3 16.7 300 110488 dscfm 2.2 16.9 300 114706 dscfm 2.2 17 300

Page 65sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value 49 Method 324 PRB 52 7.21 11792 37 Method 324 PRB 52 7.21 11792 36 Method 324 PRB 52 7.21 11792 1.002 Ontario-Hydro Method Actual flue gas temperature recorded in test report is 331 degree F. eICR program does not permit input of flue gas temperature exceeding 300 degree F. 1.002 Ontario-Hydro Method Actual flue gas temperature recorded in test report is 332 degree F. eICR program does not permit input of flue gas temperature exceeding 300 degree F. 1.002 Ontario-Hydro Method Actual flue gas temperature recorded in test report is 332 degree F. eICR program does not permit input of flue gas temperature exceeding 300 degree F. 1.002 EPA Method 17 Actual flue gas temperature recorded in test report is 343 degree F. eICR program does not permit input of flue gas temperature exceeding 300 degree F. 1.002 EPA Method 17 Actual flue gas temperature recorded in test report is 349 degree F. eICR program does not permit input of flue gas temperature exceeding 300 degree F. 1.001 EPA Method 17 Actual flue gas temperature recorded in test report is 348 degree F. eICR program does not permit input of flue gas temperature exceeding 300 degree F.

Page 66sampling_runs

fuel_sulfur Actual flue gas temperature recorded in test report is 331 degree F. eICR program does not permit input of flue gas temperature exceeding 300 degree F. Actual flue gas temperature recorded in test report is 332 degree F. eICR program does not permit input of flue gas temperature exceeding 300 degree F. Actual flue gas temperature recorded in test report is 332 degree F. eICR program does not permit input of flue gas temperature exceeding 300 degree F. Actual flue gas temperature recorded in test report is 343 degree F. eICR program does not permit input of flue gas temperature exceeding 300 degree F. Actual flue gas temperature recorded in test report is 349 degree F. eICR program does not permit input of flue gas temperature exceeding 300 degree F. Actual flue gas temperature recorded in test report is 348 degree F. eICR program does not permit input of flue gas temperature exceeding 300 degree F.

Page 67sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_nam e conc conc_units conc_ND conc_MDL 2169 Hg012006 U2PORT 1 Total Mercury (Hgt) 3.39 mi crogram per dry standard cubic meter ( FALSE 2169 Hg012006 U2PORT 2 Total Mercury (Hgt) 3.38 mi crogram per dry standard cubic meter ( FALSE 2169 Hg012006 U2PORT 3 Total Mercury (Hgt) 3.41 mi crogram per dry standard cubic meter ( FALSE 2169 Hg122005 U2PORT 1 Particulate-bound Mercury (Hgp) 0.71 mi crogram per dry standard cubic meter ( FALSE 2169 Hg122005 U2PORT 1 Oxidized Mercury (Hg++) 0.31 mi crogram per dry standard cubic meter ( FALSE 2169 Hg122005 U2PORT 1 Elem ental Mercury (Hg0) 1.32 mi crogram per dry standard cubic meter ( FALSE 2169 Hg122005 U2PORT 1 Total Mercury (Hgt) 2.33 mi crogram per dry standard cubic meter ( FALSE 2169 Hg122005 U2PORT 2 Particulate-bound Mercury (Hgp) 0.48 mi crogram per dry standard cubic meter ( FALSE 2169 Hg122005 U2PORT 2 Oxidized Mercury (Hg++) 0.2 mi crogram per dry

standard cubic meter ( FALSE 2169 Hg122005 U2PORT 2 Elem ental Mercury (Hg0) 1.35 mi crogram per dry standard cubic meter ( FALSE 2169 Hg122005 U2PORT 2 Total Mercury (Hgt) 2.03 mi crogram per dry standard cubic meter ( FALSE 2169 Hg122005 U2PORT 3 Particulate-bound Mercury (Hgp) 0.39 mi crogram per dry standard cubic meter ( FALSE 2169 Hg122005 U2PORT 3 Oxidized Mercury (Hg++) 0.15 mi crogram per dry standard cubic meter ( FALSE 2169 Hg122005 U2PORT 3 Elem ental Mercury (Hg0) 1.47 mi crogram per dry standard cubic meter ( FALSE 2169 Hg122005 U2PORT 3 Total Mercury (Hgt) 2.01 mi crogram per dry standard cubic meter ( FALSE 2169 PM052005 U2PORT 1 PM (Filterable) FALSE 2169 PM052005 U2PORT 2 PM (Filterable) FALSE 2169 PM052005 U2PORT 3 PM (Filterable) FALSE

Page 68sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment FALSE FALSE FALSE FALSE FALSE FALSE 0.0003 pound per hour (lb/hr)

FALSE 0.5 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.000129 pound per hour (lb/hr) FALSE 0.21 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.000556 pound per hour (lb/hr) FALSE 0.92 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.000984 pound per hour (lb/hr) FALSE 1.64 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.000204 pound per hour (lb/hr) FALSE 0.34 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 8.49E-05 pound per hour (lb/hr) FALSE 0.14 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.000569 pound per hour (lb/hr) FALSE 0.94 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.000857 pound per hour (lb/hr) FALSE 1.42 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.000166 pound per hour (lb/hr) FALSE 0.27 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.000065 pound per hour (lb/hr) FALSE 0.11 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.000625 pound per hour (lb/hr) FALSE 1.02 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 0.000856 pound per hour (lb/hr) FALSE 1.4 pound per trillion British Thermal Unit (lb/1012Btu) FALSE 65.95 pound per hour (lb/hr)

FALSE 0.106 pound per million British Thermal Unit (lb/MMBtu) FALSE 49.24 pound per hour (lb/hr)

FALSE 0.081 pound per million British Thermal Unit (lb/MMBtu) FALSE 55.47 pound per hour (lb/hr)

FALSE 0.088 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 69sampling_run_pollutants1 run_pollutant_comment

Page 70sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL 2169 Hg012006 U2PORT 1 Mercury (Hg) 0.0524 mi crogram per gram (dry) (mg/g) FALSE 2169 Hg012006 U2PORT 2 Mercury (Hg) 0.0524 mi crogram per gram (dry) (mg/g) FALSE 2169 Hg012006 U2PORT 3 Mercury (Hg) 0.0524 mi crogram per gram (dry) (mg/g) FALSE

Page 71sampling_run_fuel fuel_conc_MDL

Page 72