Facility DEC ID: 7313200052

 DEC Permit Conditions

 Renewal 1/Mod 2/FINAL Page 1

 PERMIT

 Under the Environmental Conservation Law (ECL)

 IDENTIFICATION INFORMATION

Permit Type: Air Title V Facility

Permit ID: 7-3132-00052/00020

 Mod 0 Effective Date: 01/11/2010 Expiration Date: 01/10/2015

 Mod 2 Effective Date: 05/24/2012 Expiration Date: 05/23/2017

Permit Issued To:SYRACUSE ENERGY CORPORATION

 56 INDUSTRIAL DR

 SYRACUSE, NY 13204-1091

Contact: STUART PIERMARINI

 SYRACUSE ENERGY CORPORATION

 56 INDUSTRIAL DRIVE

 SYRACUSE, NY 13204

 (315) 487-4473

Facility: SYRACUSE ENERGY CORPORATION

 56 INDUSTRIAL DR

 SYRACUSE, NY 13204-1091

Contact: STUART PIERMARINI

 SYRACUSE ENERGY CORPORATION

 56 INDUSTRIAL DRIVE

 SYRACUSE, NY 13204

 (315) 487-4473

Description:

Title V permit modification to incorporate the requirements of Part 249, Best Available Retrofit

Technology (BART) for the Syracuse Energy Corporation facility. Boiler Unit 1 is subject to

these requirements, and the facility has elected to shut down Unit 1 no later than January 1, 2014

in order to comply with this rule.
 

Facility DEC ID: 7313200052

 DEC Permit Conditions

 Renewal 1/Mod 2/FINAL Page 2

By acceptance of this permit, the permittee agrees that the permit is contingent upon strict

compliance with the ECL, all applicable regulations, the General Conditions specified and any

Special Conditions included as part of this permit.

Permit Administrator: ELIZABETH A TRACY

 615 ERIE BLVD WEST

 SYRACUSE, NY 13204-2400

Authorized Signature: _________________________________ Date: ___ / ___ / _____
 

Facility DEC ID: 7313200052

 DEC Permit Conditions

 Renewal 1/Mod 2/FINAL Page 3

 Notification of Other State Permittee Obligations

Item A: Permittee Accepts Legal Responsibility and Agrees to Indemnification

 The permittee expressly agrees to indemnify and hold harmless the Department of

 Environmental Conservation of the State of New York, its representatives,

 employees and agents ("DEC") for all claims, suits, actions, and damages, to the

 extent attributable to the permittee's acts or omissions in connection with the

 compliance permittee's undertaking of activities in connection with, or operation

 and maintenance of, the facility or facilities authorized by the permit whether in

 compliance or not in any compliance with the terms and conditions of the permit.

 This indemnification does not extend to any claims, suits, actions, or damages to

 the extent attributable to DEC's own negligent or intentional acts or omissions, or

 to any claims, suits, or actions naming the DEC and arising under article 78 of the 

 New York Civil Practice Laws and Rules or any citizen suit or civil rights

 provision under federal or state laws.

Item B: Permittee's Contractors to Comply with Permit

 The permittee is responsible for informing its independent contractors, employees,

 agents and assigns of their responsibility to comply with this permit, including all

 special conditions while acting as the permittee's agent with respect to the

 permitted activities, and such persons shall be subject to the same sanctions for

 violations of the Environmental Conservation Law as those prescribed for the

 permittee.

Item C: Permittee Responsible for Obtaining Other Required Permits

 The permittee is responsible for obtaining any other permits, approvals, lands, 

 easements and rights-of-way that may be required to carry out the activities that

 are authorized by this permit.

Item D: No Right to Trespass or Interfere with Riparian Rights

 This permit does not convey to the permittee any right to trespass upon the lands

 or interfere with the riparian rights of others in order to perform the permitted 

 work nor does it authorize the impairment of any rights, title, or interest in real or

 personal property held or vested in a person not a party to the permit.
 

Facility DEC ID: 7313200052

 DEC Permit Conditions

 Renewal 1/Mod 2/FINAL Page 4

 LIST OF CONDITIONS

 

 DEC GENERAL CONDITIONS

 General Provisions

 Facility Inspection by the Department

 Relationship of this Permit to Other Department Orders and

 Determinations

 Applications for permit renewals, modifications and transfers

 Permit modifications, suspensions or revocations by the Department

 Permit modifications, suspensions or revocations by the Department

 Facility Level

 Submission of application for permit modification or

 renewal-REGION 7 HEADQUARTERS
 

Facility DEC ID: 7313200052

 DEC Permit Conditions

 Renewal 1/Mod 2/FINAL Page 5

 DEC GENERAL CONDITIONS

 **** General Provisions  

 For the purpose of your Title V permit, the following section contains

 state-only enforceable terms and conditions.

 GENERAL CONDITIONS - Apply to ALL Authorized Permits.

Condition 1: Facility Inspection by the Department

 Applicable State Requirement: ECL 19-0305

Item 1.1:

The permitted site or facility, including relevant records, is subject to inspection at reasonable

hours and intervals by an authorized representative of the Department of Environmental

Conservation (the Department) to determine whether the permittee is complying with this permit

and the ECL. Such representative may order the work suspended pursuant to ECL 71-0301 and

SAPA 401(3).

Item 1.2:

The permittee shall provide a person to accompany the Department's representative during an

inspection to the permit area when requested by the Department.

Item 1.3:

A copy of this permit, including all referenced maps, drawings and special conditions, must be

available for inspection by the Department at all times at the project site or facility. Failure to

produce a copy of the permit upon request by a Department representative is a violation of this

permit.

Condition 2: Relationship of this Permit to Other Department Orders and Determinations

 Applicable State Requirement: ECL 3-0301 (2) (m)

Item 2.1:

Unless expressly provided for by the Department, issuance of this permit does not modify,

supersede or rescind any order or determination previously issued by the Department or any of

the terms, conditions or requirements contained in such order or determination.

Condition 3: Applications for permit renewals, modifications and transfers

 Applicable State Requirement: 6 NYCRR 621.11

Item 3.1:

The permittee must submit a separate written application to the Department for renewal,

modification or transfer of this permit. Such application must include any forms or supplemental

information the Department requires. Any renewal, modification or transfer granted by the

Department must be in writing.

Item 3.2:

The permittee must submit a renewal application at least 180 days before expiration of permits

for Title V Facility Permits, or at least 30 days before expiration of permits for State Facility

Permits. 

Item 3.3:

Permits are transferrable with the approval of the department unless specifically prohibited by

the statute, regulation or another permit condition. Applications for permit transfer should be

submitted prior to actual transfer of ownership.
 

Facility DEC ID: 7313200052

 DEC Permit Conditions

 Renewal 1/Mod 2/FINAL Page 6

Condition 2-1: Permit modifications, suspensions or revocations by the

Department

 Applicable State Requirement: 6 NYCRR 621.13

Item 2-1.1:

The Department reserves the right to exercise all available authority to modify, suspend, or

revoke this permit in accordance with 6NYCRR Part 621. The grounds for modification,

suspension or revocation include:

a) materially false or inaccurate statements in the permit application or supporting papers;

b) failure by the permittee to comply with any terms or conditions of the permit;

c) exceeding the scope of the project as described in the permit application;

d) newly discovered material information or a material change in environmental conditions,

relevant technology or applicable law or regulations since the issuance of the existing permit;

e) noncompliance with previously issued permit conditions, orders of the commissioner, any

provisions of the Environmental Conservation Law or regulations of the Department related to

the permitted activity.

Condition 4: Permit modifications, suspensions or revocations by the Department

 Applicable State Requirement: 6 NYCRR 621.13

Item 4.1:

The Department reserves the right to modify, suspend, or revoke this permit in accordance with

6NYCRR Part 621. The grounds for modification, suspension or revocation include:

a) materially false or inaccurate statements in the permit application or supporting papers;

b) failure by the permittee to comply with any terms or conditions of the permit;

c) exceeding the scope of the project as described in the permit application;

d) newly discovered material information or a material change in environmental conditions,

relevant technology or applicable law or regulations since the issuance of the existing permit;

e) noncompliance with previously issued permit conditions, orders of the commissioner, any

provisions of the Environmental Conservation Law or regulations of the Department related to

the permitted activity.

 ** ** Facility Level  

Condition 5: Submission of application for permit modification or renewal-REGION 7 

 HEADQUARTERS

 Applicable State Requirement: 6 NYCRR 621.6 (a)

Item 5.1:

Submission of applications for permit modification or renewal are to be submitted to:

 NYSDEC Regional Permit Administrator 

 Region 7 Headquarters

 Division of Environmental Permits

 615 Erie Blvd West

 Syracuse, NY 13204-2400

 (315) 426-7400
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 1 FINAL

 Permit Under the Environmental Conservation Law (ECL)

 ARTICLE 19: AIR POLLUTION CONTROL - TITLE V PERMIT

 IDENTIFICATION INFORMATION

Permit Issued To:SYRACUSE ENERGY CORPORATION

 56 INDUSTRIAL DR

 SYRACUSE, NY 13204-1091

Facility: SYRACUSE ENERGY CORPORATION

 56 INDUSTRIAL DR

 SYRACUSE, NY 13204-1091

Authorized Activity By Standard Industrial Classification Code:

 4911 - ELECTRIC SERVICES

Mod 0 Permit Effective Date: 01/11/2010 Permit Expiration Date: 01/10/2015

Mod 2 Permit Effective Date: 05/24/2012 Permit Expiration Date: 05/23/2017
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 2 FINAL

 LIST OF CONDITIONS

 

 FEDERALLY ENFORCEABLE CONDITIONS

 Facility Level

 1 6 NYCRR 200.6: Acceptable Ambient Air Quality

 2-1 6 NYCRR 201-6.5 (a) (7): Fees

 2 6 NYCRR 201-6.5 (a) (7): Fees

 3 6 NYCRR 201-6.5 (c): Recordkeeping and reporting of compliance 

 monitoring

 4 6 NYCRR 201-6.5 (c) (2): Monitoring, Related Recordkeeping, and 

 Reporting Requirements.

 5 6 NYCRR 201-6.5 (c) (3) (ii): Compliance Certification

 6 6 NYCRR 201-6.5 (e): Compliance Certification

 7 6 NYCRR 202-2.1: Compliance Certification

 8 6 NYCRR 202-2.5: Recordkeeping requirements

 9 6 NYCRR Part 215: Open Fires Prohibited at Industrial and Commercial 

 Sites

 2-2 6 NYCRR 215.2: Open Fires - Prohibitions

 10 6 NYCRR 200.7: Maintenance of Equipment

 11 6 NYCRR 201-1.7: Recycling and Salvage

 12 6 NYCRR 201-1.8: Prohibition of Reintroduction of Collected 

 Contaminants to the air

 13 6 NYCRR 201-3.2 (a): Exempt Sources - Proof of Eligibility

 14 6 NYCRR 201-3.3 (a): Trivial Sources - Proof of Eligibility

 15 6 NYCRR 201-6.5 (a) (4): Standard Requirement - Provide Information

 16 6 NYCRR 201-6.5 (a) (8): General Condition - Right to Inspect

 17 6 NYCRR 201-6.5 (d) (5): Standard Requirements - Progress Reports

 18 6 NYCRR 201-6.5 (f) (6): Off Permit Changes

 2-3 6 NYCRR 202-1.1: Required Emissions Tests

 19 6 NYCRR 202-1.1: Required Emissions Tests

 20 6 NYCRR 211.3: Visible Emissions Limited

 21 40 CFR Part 68: Accidental release provisions.

 22 40CFR 82, Subpart F: Recycling and Emissions Reduction

 23 6 NYCRR 201-1.8: Compliance Certification

 24 6 NYCRR Subpart 201-6: Emission Unit Definition

 25 6 NYCRR 201-6.5 (f) (1): Compliance Certification

 26 6 NYCRR 201-6.5 (g): Non Applicable requirements

 2-4 6 NYCRR 211.1: Air pollution prohibited

 27 6 NYCRR 212.6 (a): Compliance Certification

 28 6 NYCRR 225-1.7 (c): Compliance Certification

 29 6 NYCRR Subpart 243-1: Compliance Certification

 30 6 NYCRR Subpart 243-2: Compliance Certification

 31 6 NYCRR Subpart 243-8: Compliance Certification

 32 6 NYCRR Subpart 244-1: CAIR General and Permit Requirments

 33 6 NYCRR Subpart 244-2: Designated CAIR Representative

 34 6 NYCRR Subpart 244-8: Compliance Certification

 35 6 NYCRR Subpart 245-1: CAIR SO2 Trading Program General Provisions

 36 6 NYCRR Subpart 245-2: Designated CAIR Representative

 37 6 NYCRR Subpart 245-8: Compliance Certification

 2-5 6 NYCRR 249.1 (c) (2): Exemption from Part 249
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 3 FINAL

 Emission Unit Level

 38 6 NYCRR Subpart 201-6: Emission Point Definition By Emission Unit

 39 6 NYCRR Subpart 201-6: Process Definition By Emission Unit

 EU=U-00BLR

 40 6 NYCRR 225-1.5 (b): Compliance Certification

 41 6 NYCRR 227-1.2 (a) (3): Compliance Certification

 42 6 NYCRR 227-2.6 (a) (1): Testing, monitoring, and reporting 

 requirements for very large boilers.

 43 6 NYCRR 231-2.6 (a) (7): Compliance Certification

 2-6 6 NYCRR 249.1 (c) (2): Compliance Certification

 44 6 NYCRR Subpart 257-1: Compliance Certification

 45 40CFR 60.14, NSPS Subpart A: Compliance Certification

 46 40 CFR Part 64: Compliance Certification

 EU=U-00BLR,EP=00001

 47 6 NYCRR 227-1.3: Compliance Certification

 48 6 NYCRR 227-2.4 (a): Compliance Certification

 EU=U-00BLR,EP=00001,Proc=COA,ES=0BAGH

 49 6 NYCRR 200.7: Compliance Certification

 STATE ONLY ENFORCEABLE CONDITIONS

 Facility Level

 50 ECL 19-0301: Contaminant List

 51 6 NYCRR 201-1.4: Unavoidable noncompliance and violations

 52 6 NYCRR 211.2: Air pollution prohibited

 2-7 6 NYCRR 211.2: Visible Emissions Limited

 53 6 NYCRR Subpart 242-1: Compliance Demonstration

 54 6 NYCRR Subpart 242-4: Compliance Demonstration

 55 6 NYCRR Subpart 242-8: Compliance Demonstration

 56 6 NYCRR Part 246: Compliance Demonstration

 Emission Unit Level

 EU=U-00BLR

 57 6 NYCRR 617.11 (d): Compliance Demonstration

 58 6 NYCRR 617.11 (d): Compliance Demonstration

 59 6 NYCRR 617.11 (d): Compliance Demonstration
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 4 FINAL

 FEDERALLY ENFORCEABLE CONDITIONS

 ** ** Facility Level  

 NOTIFICATION OF GENERAL PERMITTEE OBLIGATIONS

 The items listed below are not subject to the annual compliance certification

 requirements under Title V. Permittees may also have other obligations

 under regulations of general applicability.

Item A: Emergency Defense - 6 NYCRR 201-1.5

 An emergency constitutes an affirmative defense to an 

 action brought for noncompliance with emissions 

 limitations or permit conditions for all facilities in New

 York State.

 (a) The affirmative defense of emergency shall be 

 demonstrated through properly signed, contemporaneous 

 operating logs, or other relevant evidence that:

 (1) An emergency occurred and that the facility owner 

 and/or

 operator can identify the cause(s) of the 

 emergency;

 (2) The equipment at the permitted facility causing the

 emergency was at the time being properly operated;

 (3) During the period of the emergency the facility owner

 and/or operator took all reasonable steps to minimize 

 levels of emissions that exceeded the emission standards, 

 or other requirements in the permit; and

 (4) The facility owner and/or operator notified the 

 Department

 within two working days after the event occurred. This 

 notice must contain a description of the emergency, any 

 steps taken to mitigate emissions, and corrective actions 

 taken.

 (b) In any enforcement proceeding, the facility owner 

 and/or operator seeking to establish the occurrence of an 

 emergency has the burden of proof.

 (c) This provision is in addition to any emergency or 

 upset provision contained in any applicable requirement.

Item B: Public Access to Recordkeeping for Title V Facilities - 6

 NYCRR 201-1.10 (b)

 The Department will make available to the public any 

 permit application, compliance plan, permit, and 

 monitoring and compliance certification report pursuant to

 Section 503(e) of the Act, except for information entitled

 to confidential treatment pursuant to 6 NYCRR Part 616 - 

 Public Access to records and Section 114(c) of the Act.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 5 FINAL

Item C: Timely Application for the Renewal of Title V Permits - 6

 NYCRR 201-6.3 (a) (4)

 Owners and/or operators of facilities having an issued 

 Title V permit shall submit a complete application at 

 least 180 days, but not more than eighteen months, prior 

 to the date of permit expiration for permit renewal 

 purposes.

Item D: Certification by a Responsible Official - 6 NYCRR 201-6.3

 (d) (12)

 Any application, form, report or compliance certification

 required to be submitted pursuant to the federally 

 enforceable portions of this permit shall contain a 

 certification of truth, accuracy and completeness by a 

 responsible official. This certification shall state that 

 based on information and belief formed after reasonable 

 inquiry, the statements and information in the document 

 are true, accurate, and complete.

Item E: Requirement to Comply With All Conditions - 6 NYCRR 

 201-6.5 (a) (2)

 The permittee must comply with all conditions of the 

 Title V facility permit. Any permit non-compliance 

 constitutes a violation of the Act and is grounds for 

 enforcement action; for permit termination, revocation and

 reissuance, or modification; or for denial of a permit 

 renewal application.

Item F: Permit Revocation, Modification, Reopening, Reissuance or

 Termination, and Associated Information Submission 

 Requirements - 6 NYCRR 201-6.5 (a) (3)

 This permit may be modified, revoked, reopened and 

 reissued, or terminated for cause. The filing of a request

 by the permittee for a permit modification, revocation and

 reissuance, or termination, or of a notification of 

 planned changes or anticipated noncompliance does not stay

 any permit condition.

Item G: Cessation or Reduction of Permitted Activity Not a 

 Defense - 6 NYCRR 201-6.5 (a) (5)

 It shall not be a defense for a permittee in an 

 enforcement action to claim that a cessation or reduction 

 in the permitted activity would have been necessary in 

 order to maintain compliance with the conditions of this 

 permit.

Item H: Property Rights - 6 NYCRR 201-6.5 (a) (6)

 This permit does not convey any property rights of any 

 sort or any exclusive privilege.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 6 FINAL

Item I: Severability - 6 NYCRR 201-6.5 (a) (9)

 If any provisions, parts or conditions of this permit are

 found to be invalid or are the subject of a challenge, the

 remainder of this permit shall continue to be valid.

Item J: Permit Shield - 6 NYCRR 201-6.5 (g)

 All permittees granted a Title V facility permit shall be

 covered under the protection of a permit shield, except as

 provided under 6 NYCRR Subpart 201-6. Compliance with the

 conditions of the permit shall be deemed compliance with 

 any applicable requirements as of the date of permit 

 issuance, provided that such applicable requirements are 

 included and are specifically identified in the permit, or

 the Department, in acting on the permit application or 

 revision, determines in writing that other requirements 

 specifically identified are not applicable to the major 

 stationary source, and the permit includes the 

 determination or a concise summary thereof. Nothing herein

 shall preclude the Department from revising or revoking 

 the permit pursuant to 6 NYCRR Part 621 or from exercising

 its summary abatement authority. Nothing in this permit 

 shall alter or affect the following:

 i. The ability of the Department to seek to bring suit

 on behalf of the State of New York, or the Administrator 

 to seek to bring suit on behalf of the United States, to 

 immediately restrain any person causing or contributing to

 pollution presenting an imminent and substantial 

 endangerment to public health, welfare or the environment 

 to stop the emission of air pollutants causing or 

 contributing to such pollution;

 ii. The liability of a permittee of the Title V 

 facility for any violation of applicable requirements 

 prior to or at the time of permit issuance;

 iii. The applicable requirements of Title IV of the 

 Act;

 iv. The ability of the Department or the Administrator

 to obtain information from the permittee concerning the 

 ability to enter, inspect and monitor the facility.

Item K: Reopening for Cause - 6 NYCRR 201-6.5 (i)

 This Title V permit shall be reopened and revised under 

 any of the following circumstances:

 i. If additional applicable requirements under the Act

 become applicable where this permit's remaining term is 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 7 FINAL

 three or more years, a reopening shall be completed not 

 later than 18 months after promulgation of the applicable 

 requirement. No such reopening is required if the 

 effective date of the requirement is later than the date 

 on which this permit is due to expire, unless the original

 permit or any of its terms and conditions has been 

 extended by the Department pursuant to the provisions of 

 Part 201-6.7 and Part 621.

 ii. The Department or the Administrator determines 

 that the permit contains a material mistake or that 

 inaccurate statements were made in establishing the 

 emissions standards or other terms or conditions of the 

 permit.

 iii. The Department or the Administrator determines 

 that the Title V permit must be revised or reopened to 

 assure compliance with applicable requirements.

 iv. If the permitted facility is an "affected source" 

 subject to the requirements of Title IV of the Act, and 

 additional requirements (including excess emissions 

 requirements) become applicable. Upon approval by the 

 Administrator, excess emissions offset plans shall be 

 deemed to be incorporated into the permit.

 Proceedings to reopen and issue Title V facility permits 

 shall follow the same procedures as apply to initial 

 permit issuance but shall affect only those parts of the 

 permit for which cause to reopen exists.

 Reopenings shall not be initiated before a notice of such

 intent is provided to the facility by the Department at 

 least thirty days in advance of the date that the permit 

 is to be reopened, except that the Department may provide

 a shorter time period in the case of an emergency.

Item L: Permit Exclusion - ECL 19-0305

 The issuance of this permit by the Department and the 

 receipt thereof by the Applicant does not and shall not be

 construed as barring, diminishing, adjudicating or in any 

 way affecting any legal, administrative or equitable 

 rights or claims, actions, suits, causes of action or 

 demands whatsoever that the Department may have against 

 the Applicant for violations based on facts and 

 circumstances alleged to have occurred or existed prior to

 the effective date of this permit, including, but not 

 limited to, any enforcement action authorized pursuant to 

 the provisions of applicable federal law, the 

 Environmental Conservation Law of the State of New York 

 (ECL) and Chapter III of the Official Compilation of the 

 Codes, Rules and Regulations of the State of New York 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 8 FINAL

 (NYCRR). The issuance of this permit also shall not in any

 way affect pending or future enforcement actions under the

 Clean Air Act brought by the United States or any person.

Item M: Federally Enforceable Requirements - 40 CFR 70.6 (b)

 All terms and conditions in this permit required by the 

 Act or any applicable requirement, including any 

 provisions designed to limit a facility's potential to 

 emit, are enforceable by the Administrator and citizens 

 under the Act. The Department has, in this permit, 

 specifically designated any terms and conditions that are 

 not required under the Act or under any of its applicable 

 requirements as being enforceable under only state 

 regulations.

 MANDATORY FEDERALLY ENFORCEABLE PERMIT CONDITIONS 

 SUBJECT TO ANNUAL CERTIFICATIONS AT ALL TIMES

 The following federally enforceable permit conditions are mandatory for all

 Title V permits and are subject to annual compliance certification 

 requirements at all times.

Condition 1: Acceptable Ambient Air Quality

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 200.6

Item 1.1:

Notwithstanding the provisions of 6 NYCRR Chapter III, Subchapter A, no person shall allow or

permit any air contamination source to emit air contaminants in quantities which alone or in

combination with emissions from other air contamination sources would contravene any

applicable ambient air quality standard and/or cause air pollution. In such cases where

contravention occurs or may occur, the Commissioner shall specify the degree and/or method of

emission control required.

Condition 2-1: Fees

 Effective between the dates of 05/24/2012 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-6.5 (a) (7)

Item 2-1.1:

The owner and/or operator of a stationary source shall pay fees to the Department consistent

with the fee schedule authorized by ECL 72-0303.

Condition 2: Fees

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-6.5 (a) (7)

Item 2.1:
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 9 FINAL

The owner and/or operator of a stationary source shall pay fees to the Department consistent

with the fee schedule authorized by ECL 72-0302.

Condition 3: Recordkeeping and reporting of compliance monitoring

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-6.5 (c)

Item 3.1:

The following information must be included in any required compliance monitoring records and

reports:

(i) The date, place, and time of sampling or measurements;

(ii) The date(s) analyses were performed;

(iii)The company or entity that performed the analyses;

(iv) The analytical techniques or methods used including quality assurance and quality control

procedures if required;

(v) The results of such analyses including quality assurance data where required; and

(vi) The operating conditions as existing at the time of sampling or measurement.

Any deviation from permit requirements must be clearly identified in all records and reports. 

Reports must be certified by a responsible official, consistent with Section 201-6.3 of this Part

201.

Condition 4: Monitoring, Related Recordkeeping, and Reporting 

 Requirements.

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-6.5 (c) (2)

Item 4.1:

Compliance monitoring and recordkeeping shall be conducted according to the terms and

conditions contained in this permit and shall follow all quality assurance requirements found in

applicable regulations. Records of all monitoring data and support information must be retained

for a period of at least 5 years from the date of the monitoring, sampling, measurement, report,

or application. Support information includes all calibration and maintenance records and all

original strip-chart recordings for continuous monitoring instrumentation, and copies of all

reports required by the permit. 

Condition 5: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-6.5 (c) (3) (ii)

Item 5.1:

The Compliance Certification activity will be performed for the Facility.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 10 FINAL

Item 5.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 To meet the requirements of this facility permit with 

 respect to reporting, the permittee must:

 Submit reports of any required monitoring at a minimum 

 frequency of every 6 months, based on a calendar year 

 reporting schedule. These reports shall be submitted to 

 the Department within 30 days after the end of a reporting

 period. All instances of deviations from permit 

 requirements must be clearly identified in such reports. 

 All required reports must be certified by the responsible 

 official for this facility.

 Notify the Department and report permit deviations and 

 incidences of noncompliance stating the probable cause of 

 such deviations, and any corrective actions or preventive 

 measures taken. Where the underlying applicable 

 requirement contains a definition of prompt or otherwise 

 specifies a time frame for reporting deviations, that 

 definition or time frame shall govern. Where the 

 underlying applicable requirement fails to address the 

 time frame for reporting deviations, reports of deviations

 shall be submitted to the permitting authority based on 

 the following schedule:

 (1) For emissions of a hazardous air pollutant (as 

 identified in an applicable regulation) that continue for 

 more than an hour in excess of permit requirements, the 

 report must be made within 24 hours of the 

 occurrence.

 (2) For emissions of any regulated air pollutant, 

 excluding those listed in paragraph (1) of this section, 

 that continue for more than two hours in excess of permit 

 requirements, the report must be made within 48 

 hours.

 (3) For all other deviations from permit requirements, 

 the report shall be contained in the 6 month monitoring 

 report required above.

 (4) This permit may contain a more stringent reporting 

 requirement than required by paragraphs (1), (2) or (3) 

 above. If more stringent reporting requirements have been

 placed in this permit or exist in applicable requirements 

 that apply to this facility, the more stringent reporting 

 requirement shall apply.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 11 FINAL

 If above paragraphs (1) or (2) are met, the source must 

 notify the permitting authority by telephone during normal

 business hours at the Regional Office of jurisdiction for 

 this permit, attention Regional Air Pollution Control 

 Engineer (RAPCE) according to the timetable listed in 

 paragraphs (1) and (2) of this section. For deviations 

 and incidences that must be reported outside of normal 

 business hours, on weekends, or holidays, the DEC Spill 

 Hotline phone number at 1-800-457-7362 shall be used. A 

 written notice, certified by a responsible official 

 consistent with 6 NYCRR Part 201-6.3(d)(12), must be 

 submitted within 10 working days of an occurrence for 

 deviations reported under (1) and (2). All deviations 

 reported under paragraphs (1) and (2) of this section must

 also be identified in the 6 month monitoring report 

 required above.

 The provisions of 6 NYCRR 201-1.4 shall apply if the 

 permittee seeks to have a violation excused unless 

 otherwise limited by regulation. In order to have a 

 violation of a federal regulation (such as a new source 

 performance standard or national emissions standard for 

 hazardous air pollutants) excused, the specific federal 

 regulation must provide for an affirmative defense during 

 start-up, shutdowns, malfunctions or upsets. 

 Notwithstanding any recordkeeping and reporting 

 requirements in 6 NYCRR 201-1.4, reports of any deviations

 shall not be on a less frequent basis than the reporting 

 periods described in paragraphs (1) and (4) above. 

 In the case of any condition contained in this permit 

 with a reporting requirement of "Upon request by 

 regulatory agency" the permittee shall include in the 

 semiannual report, a statement for each such condition 

 that the monitoring or recordkeeping was performed as 

 required or requested and a listing of all instances of 

 deviations from these requirements.

 In the case of any emission testing performed during the 

 previous six month reporting period, either due to a 

 request by the Department, EPA, or a regulatory 

 requirement, the permittee shall include in the semiannual

 report a summary of the testing results and shall indicate

 whether or not the Department or EPA has approved the 

 results.

 All semiannual reports shall be submitted to the 

 Administrator (or his or her representative) as well as 

 two copies to the Department (one copy to the regional air

 pollution control engineer (RAPCE) in the regional office 

 and one copy to the Bureau of Compliance Monitoring and 

 Enforcement (BCME) in the DEC central office). Mailing 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 12 FINAL

 addresses for the above referenced persons are contained 

 in the monitoring condition for 6 NYCRR Part 201-6.5(e), 

 contained elsewhere in this permit.

Monitoring Frequency: SEMI-ANNUALLY

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 7/30/2010.

Subsequent reports are due every 6 calendar month(s).

Condition 6: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-6.5 (e)

Item 6.1:

The Compliance Certification activity will be performed for the Facility.

Item 6.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Requirements for compliance certifications with terms and

 conditions contained in this facility permit include the 

 following:

 i. Compliance certifications shall contain:

 - the identification of each term or condition of the 

 permit that is the basis of the certification;

 - the compliance status;

 - whether compliance was continuous or intermittent;

 - the method(s) used for determining the compliance status

 of the facility, currently and over the reporting period 

 consistent with the monitoring and related recordkeeping 

 and reporting requirements of this permit;

 - such other facts as the Department may require to 

 determine the compliance status of the facility as 

 specified in any special permit terms or conditions; 

 and

 - such additional requirements as may be specified 

 elsewhere in this permit related to compliance 

 certification.

 ii. The responsible official must include in the annual 

 certification report all terms and conditions contained in

 this permit which are identified as being subject to 

 certification, including emission limitations, standards, 

 or work practices. That is, the provisions labeled herein

 as "Compliance Certification" are not the only provisions 

 of this permit for which an annual certification is 

 required.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 13 FINAL

 iii. Compliance certifications shall be submitted 

 annually. Certification reports are due 30 days after the

 anniversary date of four consecutive calendar quarters. 

 The first report is due 30 days after the calendar quarter

 that occurs just prior to the permit anniversary date, 

 unless another quarter has been acceptable by the 

 Department.

 iv. All compliance certifications shall be submitted to 

 the Administrator (or his or her representative) as well 

 as two copies to the Department (one copy to the regional 

 air pollution control engineer (RAPCE) in the regional 

 office and one copy to the Bureau of Compliance Monitoring

 and Enforcement (BCME) in the DEC central office). Please

 send annual compliance certifications to Chief of the 

 Stationary Source Compliance Section, the Region 2 EPA 

 representative for the Administrator, at the following 

 address:

 USEPA Region 2

 Air Compliance Branch

 290 Broadway

 New York, NY 10007-1866

 

 The address for the RAPCE is as follows:

 615 Erie Boulevard, West

 Syracuse, NY 13204-2400

 The address for the BCME is as follows:

 NYSDEC 

 Bureau of Compliance Monitoring

 and Enforcement

 625 Broadway

 Albany, NY 12233-3258

Monitoring Frequency: ANNUALLY

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2011.

Subsequent reports are due on the same day each year

Condition 7: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 202-2.1

Item 7.1:

The Compliance Certification activity will be performed for the Facility.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 14 FINAL

Item 7.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Emission statements shall be submitted on or before April

 15th each year for emissions of the previous calendar 

 year.

Monitoring Frequency: ANNUALLY

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due by April 15th for previous calendar year

Condition 8: Recordkeeping requirements

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 202-2.5

Item 8.1:

(a) The following records shall be maintained for at least five years:

 (1) a copy of each emission statement submitted to the department; and

 (2) records indicating how the information submitted in the emission

statement was determined, including any calculations, data, measurements, and estimates used.

(b) These records shall be made available at the facility to the representatives of the

department upon request during normal business hours.

Condition 9: Open Fires Prohibited at Industrial and Commercial Sites

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Part 215

Item 9.1:

No person shall burn, cause, suffer, allow or permit the burning in an open fire of garbage,

refuse, rubbish for salvage, or rubbish generated by industrial or commercial activities.

Condition 2-2: Open Fires - Prohibitions

 Effective between the dates of 05/24/2012 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 215.2

Item 2-2.1: 

Except as allowed by Title 6 NYCRR Section 215.3, no person shall burn, cause, suffer, allow

or permit the burning of any materials in an open fire.

Item 2-2.2

Per Section 215.3, burning in an open fire, provided it is not contrary to other law or regulation,

will be allowed as follows:

(a) On-site burning in any town with a total population less than 20,000 of downed limbs and

branches (including branches with attached leaves or needles) less than six inches in diameter
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 15 FINAL

and eight feet in length between May 15th and the following March 15th. For the purposes of

this subdivision, the total population of a town shall include the population of any village or

portion thereof located within the town. However, this subdivision shall not be construed to

allow burning within any village.

(b) Barbecue grills, maple sugar arches and similar outdoor cooking devices when actually used

for cooking or processing food.

(c) Small fires used for cooking and camp fires provided that only charcoal or untreated wood is

used as fuel and the fire is not left unattended until extinguished.

(d) On-site burning of agricultural wastes as part of a valid agricultural operation on contiguous

agricultural lands larger than five acres actively devoted to agricultural or horticultural use,

provided such waste is actually grown or generated on those lands and such waste is capable of

being fully burned within a 24-hour period.

(e) The use of liquid petroleum fueled smudge pots to prevent frost damage to crops.

(f) Ceremonial or celebratory bonfires where not otherwise prohibited by law, provided that only

untreated wood or other agricultural products are used as fuel and the fire is not left unattended

until extinguished.

(g) Small fires that are used to dispose of a flag or religious item, and small fires or other smoke

producing process where not otherwise prohibited by law that are used in connection with a

religious ceremony.

(h) Burning on an emergency basis of explosive or other dangerous or contraband materials by

police or other public safety organization.

(i) Prescribed burns performed according to Part 194 of this Title.

(j) Fire training, including firefighting, fire rescue, and fire/arson investigation training,

performed under applicable rules and guidelines of the New York State Department of State's

Office of Fire Prevention and Control. For fire training performed on acquired structures, the

structures must be emptied and stripped of any material that is toxic, hazardous or likely to emit

toxic smoke (such as asbestos, asphalt shingles and vinyl siding or other vinyl products) prior to

burning and must be at least 300 feet from other occupied structures. No more than one structure

per lot or within a 300 foot radius (whichever is bigger) may be burned in a training exercise.

(k) Individual open fires as approved by the Director of the Division of Air Resources as may be

required in response to an outbreak of a plant or animal disease upon request by the

commissioner of the Department of Agriculture and Markets, or for the destruction of invasive

plant and insect species.

(l) Individual open fires that are otherwise authorized under the environmental conservation law,

or by rule or regulation of the Department.

 MANDATORY FEDERALLY ENFORCEABLE PERMIT CONDITIONS 

 SUBJECT TO ANNUAL CERTIFICATIONS ONLY IF APPLICABLE

 The following federally enforceable permit conditions are mandatory for all 

 Title V permits and are subject to annual compliance certification 

 requirements only if effectuated during the reporting period.

 [NOTE: The corresponding annual compliance certification for 

 those conditions not effectuated during the reporting period shall 

 be specified as "not applicable".]

Condition 10: Maintenance of Equipment

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 200.7
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 16 FINAL

Item 10.1:

Any person who owns or operates an air contamination source which is equipped with an

emission control device shall operate such device and keep it in a satisfactory state of

maintenance and repair in accordance with ordinary and necessary practices, standards and

procedures, inclusive of manufacturer's specifications, required to operate such device

effectively.

Condition 11: Recycling and Salvage

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-1.7

Item 11.1:

Where practical, any person who owns or operates an air contamination source shall recycle or

salvage air contaminants collected in an air cleaning device according to the requirements of the

ECL.

Condition 12: Prohibition of Reintroduction of Collected Contaminants to

 the air

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-1.8

Item 12.1:

No person shall unnecessarily remove, handle or cause to be handled, collected air contaminants

from an air cleaning device for recycling, salvage or disposal in a manner that would reintroduce

them to the outdoor atmosphere.

Condition 13: Exempt Sources - Proof of Eligibility

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-3.2 (a)

Item 13.1:

The owner and/or operator of an emission source or unit that is eligible to be exempt may be

required to certify that it operates within the specific criteria described in this Subpart. The

owner or operator of any such emission source must maintain all required records on-site for a

period of five years and make them available to representatives of the department upon request.

Department representatives must be granted access to any facility which contains emission

sources or units subject to this Subpart, during normal operating hours, for the purpose of

determining compliance with this and any other State and Federal air pollution control

requirements, regulations, or law.

Condition 14: Trivial Sources - Proof of Eligibility

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-3.3 (a)

Item 14.1:

The owner and/or operator of an emission source or unit that is listed as being trivial in this Part

may be required to certify that it operates within the specific criteria described in this Subpart.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 17 FINAL

The owner or operator of any such emission source must maintain all required records on-site for

a period of five years and make them available to representatives of the department upon

request. Department representatives must be granted access to any facility which contains

emission sources or units subject to this Subpart, during normal operating hours, for the purpose

of determining compliance with this and any other State and Federal air pollution control

requirements, regulations, or law.

Condition 15: Standard Requirement - Provide Information

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-6.5 (a) (4)

Item 15.1:

The owner and/or operator shall furnish to the department, within a reasonable time, any

information that the department may request in writing to determine whether cause exists for

modifying, revoking and reissuing, or terminating the permit or to determine compliance with

the permit. Upon request, the permittee shall also furnish to the department copies of records

required to be kept by the permit or, for information claimed to be confidential, the permittee

may furnish such records directly to the administrator along with a claim of confidentiality, if the

administrator initiated the request for information or otherwise has need of it.

Condition 16: General Condition - Right to Inspect

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-6.5 (a) (8)

Item 16.1:

The department or an authorized representative shall be allowed upon presentation of credentials

 and other documents as may be required by law to:

(i) enter upon the permittee's premises where a facility subject to the permitting requirements of

this Subpart is located or emissions-related activity is conducted, or where records must be kept

under the conditions of the permit;

(ii) have access to and copy, at reasonable times, any records that must be kept under the

conditions of the permit;

(iii) inspect at reasonable times any emission sources, equipment (including monitoring and air

pollution control equipment), practices, and operations regulated or required under the permit;

and

(iv) sample or monitor at reasonable times substances or parameters for the purpose of assuring

compliance with the permit or applicable requirements.

Condition 17: Standard Requirements - Progress Reports

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-6.5 (d) (5)

Item 17.1:

Progress reports consistent with an applicable schedule of compliance are to be submitted at

least semiannually, or at a more frequent period if specified in the applicable requirement or by
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 18 FINAL

the department. Such progress reports shall contain the following:

(i) dates for achieving the activities, milestones, or compliance required in the schedule of

compliance, and dates when such activities, milestones or compliance were achieved; and

(ii) an explanation of why any dates in the schedule of compliance were not or will not be met,

and any preventive or corrective measures adopted.

Condition 18: Off Permit Changes

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-6.5 (f) (6)

Item 18.1:

No permit revision will be required for operating changes that contravene an express permit

term, provided that such changes would not violate applicable requirements as defined under this

Part or contravene federally enforceable monitoring (including test methods), recordkeeping,

reporting, or compliance certification permit terms and conditions. Such changes may be made

without requiring a permit revision, if the changes are not modifications under any provision of

title I of the act and the changes do not exceed the emissions allowable under the permit

(whether expressed therein as a rate of emissions or in terms of total emissions) provided that the

facility provides the administrator and the department with written notification as required below

in advance of the proposed changes within a minimum of seven days. The facility owner or

operator, and the department shall attach each such notice to their copy of the relevant permit.

(i) For each such change, the written notification required above shall include a brief description

of the change within the permitted facility, the date on which the change will occur, any change

in emissions, and any permit term or condition that is no longer applicable as a result of the

change.

(ii) The permit shield described in section 6 NYCRR 201-6.6 shall not apply to any change

made pursuant to this paragraph.

Condition 2-3: Required Emissions Tests

 Effective between the dates of 05/24/2012 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 202-1.1

Item 2-3.1:

For the purpose of ascertaining compliance or non-compliance with any air pollution control

code, rule or regulation, the commissioner may require the person who owns such air

contamination source to submit an acceptable report of measured emissions within a stated time.

Condition 19: Required Emissions Tests

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 202-1.1

Item 19.1:

For the purpose of ascertaining compliance or non-compliance with any air pollution control

code, rule or regulation, the commissioner may require the person who owns such air
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 19 FINAL

contamination source to submit an acceptable report of measured emissions within a stated time.

Such person shall bear the cost of measurement and preparing the report of measured emissions.

Failure of such person to submit a report acceptable to the commissioner within the time stated

shall be sufficient reason for the commissioner to suspend or deny a certificate to operate.

Condition 20: Visible Emissions Limited

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 211.3

Item 20.1:

Except as permitted by a specific part of this Subchapter and for open fires for which a restricted

burning permit has been issued, no person shall cause or allow any air contamination source to

emit any material having an opacity equal to or greater than 20 percent (six minute average)

except for one continuous six-minute period per hour of not more than 57 percent opacity.

Condition 21: Accidental release provisions.

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:40 CFR Part 68

Item 21.1:

If a chemical is listed in Tables 1,2,3 or 4 of 40 CFR §68.130 is present in a process in quantities

greater than the threshold quantity listed in Tables 1,2,3 or 4, the following requirements will

apply:

a) The owner or operator shall comply with the provisions of 40 CFR Part 68 and;

b) The owner or operator shall submit at the time of permit issuance (if not previously

submitted) one of the following, if such quantities are present: 

1) A compliance schedule for meeting the requirements of 40 CFR Part 68 by the date provided

in 40 CFR §68.10(a) or,

2) A certification statement that the source is in compliance with all requirements of 40 CFR

Part 68, including the registration and submission of the Risk Management Plan. Information

should be submitted to:

Risk Management Plan Reporting Center

C/O CSC

8400 Corporate Dr

Carrollton, Md. 20785

Condition 22: Recycling and Emissions Reduction

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:40CFR 82, Subpart F

Item 22.1:

The permittee shall comply with all applicable provisions of 40 CFR Part 82.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 20 FINAL

 The following conditions are subject to annual compliance certification 

 requirements for Title V permits only.

Condition 23: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-1.8

Item 23.1:

The Compliance Certification activity will be performed for the Facility.

Item 23.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 The facility shall operate in accordance with the Ash 

 Management Plan submitted to and approved by the 

 DEC.

 On an annual basis the owner or operator shall report to 

 the DEC whether he or she has complied with this 

 condition.

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2011.

Subsequent reports are due every 12 calendar month(s).

Condition 24: Emission Unit Definition

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 201-6

Item 24.1(From Mod 2):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00BLR 

 Emission Unit Description: 

 Five pulverized coal boilers, each with a design capacity

 of 275 mmBtu/hr. Boilers # 4 and #5 are capable of firing

 alternative fuel fluff in conjunction with coal, or 100% 

 coal.

 Building(s): BLR HS

Item 24.2(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 21 FINAL

 Emission Unit: 0-PAPER 

 Emission Unit Description: 

 Alternative fuel handling and storage. Approved 

 non-recyclable paper materials are unloaded, unpacked, 

 inspected, blended and shredded into "fluff." The fluff 

 is pneumatically conveyed to the boilers for combustion. 

 A dust collection system is used to control emissions from

 shreding and transfer operations as necessary, with 

 cleaned exhaust recirculated to the building. All process

 emissions are fugitive.

 Building(s): Paper

Item 24.3(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-00ASH 

 Emission Unit Description: 

 The flyash handling system includes two pneumatic systems

 that transfer flyash from the boiler gas passes and the 

 boiler baghouse hoppers to the ash storage silo. 

 Transport air for each system is exhausted through a 

 baghouse. The ash storage silo is equipped with a bin 

 vent filter. Flyash is mixed with water (as-needed to 

 suppress dust) and discharged to waiting trucks or rail 

 cars and is transported off-site for disposal.

 Building(s): ASILO

Item 24.4(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-0COAL 

 Emission Unit Description: 

 Coal is unloaded from railroad cars and is either 

 conveyed to the coal storage pile or is crushed and 

 conveyed to the coal bunkers in the boiler house. Coal 

 from the storage pile is reclaimed, crushed and conveyed 

 to the bunkers. Emissions from unloading, crushing and 

 conveying are fugitive in nature, and are controlled on an

 as-needed basis using a water spray. The coal storage 

 bunkers are ventilated and exhausted through two 

 baghouses.

 Building(s): BLR HS

 CRSH B

Item 24.5(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-0COOL 

 Emission Unit Description: 

 Six cell mechanical draft tower used to dissipate waste 

 heat from the cogeneration facility.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 22 FINAL

Item 24.6(From Mod 0):

The facility is authorized to perform regulated processes under this permit for:

 Emission Unit: U-0LIME 

 Emission Unit Description: 

 Lime handling and storage (for spray dry adsorber). 

 Pebble lime is pneumatically unloaded from trucks to a 

 storage silo equipped with a bin vent filter. The lime is

 mixed with water in a slaker, passed through a grit 

 remover and transferred to the lime slurry storage tank 

 before being mixed with additional water and injected into

 the spray dry adsorber. All process emissions are 

 fugitive or exempt.

Condition 25: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-6.5 (f) (1)

Item 25.1:

The Compliance Certification activity will be performed for the Facility.

Item 25.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 The following conditions relate to the burning of 

 alternate fuel fluff at this facility (processes ALT and 

 CCA). In accordance with the Department's policy for 

 burning alternative fuels, this condition allows this 

 source to be regulated as a stationary combustion source 

 not subject to the requirements for process incinerators 

 regulated by 6 NYCRR Part 212. 

 

 1. The facility is authorized to co-fire coal and 

 alternative fuel in boilers #3, #4 and/or #5. The 

 alternative fuel is processed from pre-consumer, 

 non-recyclable, non-reusable, non-contaminated plastic 

 coated paper, wax coated paper, paper, fibrous material 

 and low chlorine content (less than 1% dry weight as 

 received) plastic film. Demonstration that this is the 

 only type of alternative fuel fired shall be in accordance

 with

 the Alternative Fuels QA/QC Plan approved by the 

 Department and attached to this permit.

 2. The facility shall not combust any alternative fuel 

 that does not conform to the following specifications (dry

 basis): Minimum Heat Content - 5000 Btu/lb; Maximum sulfur

 - 0.48% by weight, Maximum Nitrogen - 1.10% by weight; 

 Maximum Chlorine - 0.18% by weight (see condition #3 

 below). In addition, a full metals analysis will be 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 23 FINAL

 performed for each potential fuel. Compliance with these 

 specifications shall be demonstrated in accordance with 

 procedures specified in the Alternative Fuels QA/QC Plan 

 approved by the 

 Department.

 3. Chlorine exception - alternative fuel that tests up to

 1.0% by weight chlorine may be accepted to an inventory 

 level not to exceed 10% by weight of the total alternative

 fuel inventory. Exception materials shall be specifically

 tagged and blended in the shredding process, meeting a 

 final alternative fuel chlorine content of 0.16% by 

 weight, maximum. Compliance with this exception shall be 

 demonstrated in accordance with procedures specified in 

 the Alternative Fuels QA/QC Plan approved by the 

 Department.

 4. The facility is limited to combusting no more than 30 

 percent by weight alternative fuel on a facility-wide 

 daily basis. The daily total fuel and alternative fuel 

 consumption shall be determined in accordance with 

 procedures specified in the Fuel Consumption Monitoring 

 Plan approved by the Department.

 5. Each boiler capable of firing alternative fuel 

 (Boilers 4 or 5) is limited to a maximum alternative fuel 

 firing rate of no more than 9500 lb/hr, determined as a 

 two-hour average. The alternative fuel firing rate shall 

 be determined in accordance with procedures specified in 

 the Fuel Consumption Monitoring Plan approved by the 

 Department. The maximum alternative fuel firing rate may 

 be increased in the future provided emission testing 

 indicates acceptable emissions at the higher rate. Such 

 testing must be performed in accordance with a stack test 

 protocol approved by the Department and within 90 days of 

 exceeding the 9500 lb/hr firing rate.

 6. Either the oil igniter or the natural gas/biogas 

 igniter for the alternative fuel burner in each boiler in 

 this process must be operating during all periods that 

 alternative fuel is co-fired. Operational status of oil 

 igniters shall be logged during co-firing and the logs 

 shall be maintained on site. 

 7. The facility must install and operate a continuous 

 emissions monitor to measure carbon monoxide 

 concentrations in the exhaust stack during co-firing of 

 alternative fuel, as an indicator of good combustion. 

 This monitoring system shall meet the installation 

 requirements of 40 CFR 60 Appendix B, and the QA/QC 

 requirements of 40 CFR 60 Appendix F. 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 24 FINAL

 On a semi-annual calendar year basis, the facility shall 

 submit to the DEC a report stating whether it has complied

 with this condition.

 

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 7/30/2010.

Subsequent reports are due every 6 calendar month(s).

Condition 26: Non Applicable requirements

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 201-6.5 (g)

Item 26.1:

This section contains a summary of those requirements that have been specifically identified as

being not applicable to this facility and/or emission units, emission points, processes and/or

emission sources within this facility. The summary also includes a justification for classifying

any such requirements as non-applicable.

 40 CFR Part 72, Subpart A

 Reason: In a letter dated May 13, 2004, the US EPA has concluded 

 that none of the five boilers (Boiler #1, #2, #3, #4 and 

 #5) is subject to the Acid Rain Program. 

Condition 2-4: Air pollution prohibited

 Effective between the dates of 05/24/2012 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 211.1

Item 2-4.1:

No person shall cause or allow emissions of air contaminants to the outdoor atmosphere of such

quantity, characteristic or duration which are injurious to human, plant or animal life or to

property, or which unreasonably interfere with the comfortable enjoyment of life or property.

Notwithstanding the existence of specific air quality standards or emission limits, this

prohibition applies, but is not limited to, any particulate, fume, gas, mist, odor, smoke, vapor,

pollen, toxic or deleterious emission, either alone or in combination with others.

Condition 27: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 212.6 (a)

Item 27.1:

The Compliance Certification activity will be performed for the facility:

The Compliance Certification applies to:
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 25 FINAL

 Emission Unit: U-00ASH

 Emission Unit: U-0COAL

 Emission Unit: U-0LIME

Item 27.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 No person shall cause or allow emissions having an 

 average opacity during any six consecutive minutes of 20 

 percent or greater from any process emission source, 

 except only the emission of uncombined water. The 

 Department reserves the right to perform or require the 

 performance of a Method 9 opacity evaluation at any time 

 during facility operation.

 The permittee will conduct observations of visible 

 emissions from the emission unit, process, etc. to which 

 this condition applies at the monitoring frequency stated 

 below while the process is in operation. The permittee 

 will investigate, in a timely manner, any instance where 

 there is cause to believe that visible emissions have the 

 potential to exceed the opacity standard. 

 The permittee shall investigate the cause, make any 

 necessary corrections, and verify that the excess visible 

 emissions problem has been corrected. If visible 

 emissions with the potential to exceed the standard 

 continue, the permittee will conduct a Method 9 assessment

 within the next operating day of the sources associated 

 with the potential noncompliance to determine the degree 

 of opacity and will notify the NYSDEC if the method 9 test

 indicates that the opacity standard is not met.

 Records of visible emissions observations (or any 

 follow-up method 9 tests), investigations and corrective 

 actions will be kept on-site. Should the Department 

 determine that permittee's record keeping format is 

 inadequate to demonstrate compliance with this condition, 

 it shall provide written notice to the permittee stating 

 the inadequacies, and permittee shall have 90 days to 

 revise its prospective record keeping format in a manner 

 acceptable to the Department.

Monitoring Frequency: WEEKLY

Averaging Method: 6-MINUTE AVERAGE (METHOD 9)

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2011.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 26 FINAL

Subsequent reports are due every 12 calendar month(s).

Condition 28: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 225-1.7 (c)

Item 28.1:

The Compliance Certification activity will be performed for the Facility.

Item 28.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Part 225-1.7(c) requires that measurements must be made 

 daily of the rate of each fuel burned. Also, the facility

 must measure the gross heat content and ash content of 

 each fuel burned (determined at least once per week), and 

 the average electrical output (daily) and hourly 

 generation rate. This information must be retained by the

 source owner for a period of three years.

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 7/30/2010.

Subsequent reports are due every 6 calendar month(s).

Condition 29: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 243-1

Item 29.1:

The Compliance Certification activity will be performed for the Facility.

Item 29.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 1) As of midnight of November 30, or midnight of the 

 first business day thereafter if November 30 is not a 

 business day, the owners or operators shall hold, in their

 compliance account, CAIR NOx allowances available for 

 compliance deductions for the previous control period (May

 1 through September 30), in an amount not less than the 

 total tons of nitrogen oxides emissions from all CAIR NOx 

 units at the source during that control period. 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 27 FINAL

 2) A CAIR NOx allowance shall not be deducted (for 

 compliance with the requirement above) for a control 

 period in a calendar year before the year for which the 

 CAIR NOx allowance was allocated. 

 3) If a CAIR NOx source emits oxides of nitrogen during 

 any control period in excess of the CAIR NOx emissions 

 limitation, the owners and operators of the CAIR NOx 

 source shall surrender the CAIR NOx allowances required 

 for deduction under 6 NYCRR 244-6.5(d)(1) and pay any 

 fine, penalty, or assessment or comply with any other 

 remedy imposed, for the same violations, under the Act or 

 applicable State law. Each ton of such excess emissions 

 and each day of such control period shall constitute a 

 separate violation of this permit, the Act, and applicable

 State law. 

 4) Unless otherwise provided, the owners and operators 

 of the CAIR NOx source shall keep on site each of the 

 following documents for a period of five years from the 

 date the document is created. This period may be extended

 for cause, at any time before the end of five years, in 

 writing by the department or the Administrator.

 i) the certificate of representation for the CAIR 

 designated representative for the source and all documents

 that demonstrate the truth of the statements in the 

 certificate of representation; provided that the 

 certificate and documents shall be retained on site at the

 source beyond such five year period until such documents 

 are superceded because the submission of a new certificate

 of representation changing the CAIR designated 

 representative.

 ii) All emissions monitoring information, provided that 

 to the extent that 6 NYCRR 243-8 provides for a three year

 period for record keeping, the three year period shall 

 apply.

 iii) Copies of all reports, compliance certifications, 

 and other submissions and all records made or required 

 under the CAIR NOx Ozone Season Trading Program.

 iv) Copies of all documents used to complete a CAIR 

 permit application and any other submission under the CAIR

 NOx Ozone Season Trading Program or to demonstrate 

 compliance with the requirements of the CAIR NOx Annual 

 Trading Program.

 5) On an annual basis, the owner or operator shall 

 submit, in the compliance certification, a statement 

 whether he or she has complied with this condition.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 28 FINAL

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2011.

Subsequent reports are due every 12 calendar month(s).

Condition 30: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 243-2

Item 30.1:

The Compliance Certification activity will be performed for the Facility.

Item 30.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 1) Each Clean Air Interstate Rule (CAIR) NOx source 

 shall have one CAIR designated representative and may have

 one alternative representative, as provided in 6 NYCRR 

 243-2.2, with regard to all matters under the CAIR NOx 

 Ozone Season Trading Program. The CAIR designated 

 representative shall be selected by an agreement binding 

 on the owners and operators of the source and act in 

 accordance with the certification statement in 6 NYCRR 

 243-2.4(a)(4)(iv). Upon receipt by the Administrator of a

 complete certificate of representation under 6 NYCRR 

 243-2.4, the CAIR designated representative of the source 

 shall represent and, by his or her representations, 

 actions, inactions, or submissions, legally bind each 

 owner and operator of the CAIR NOx Ozone Season source 

 represented in all matters pertaining to the CAIR 

 designated representative and such owners or operators. 

 The owners and operators shall be bound by any decision or

 order issued to the CAIR designated representative by the 

 department, the Administrator, or a court regarding the 

 source.

 2) Each submission under the CAIR NOx Ozone Season 

 Trading Program shall be submitted, signed, and certified 

 by the CAIR designated representative for each CAIR NOx 

 Ozone Season source on behalf of which the submission is 

 made. Each such submission shall include the following 

 certification statement by the CAIR designated 

 representative: "I am authorized to make this submission 

 on behalf of the owners and operators of the source or 

 units for which the submission is made. I certify under 

 penalty of law that I have personally examined, and am 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 29 FINAL

 familiar with, the statements and information submitted in

 this document and all of its attachments. Based on my 

 inquiry of those individuals with primary responsibility 

 for obtaining the information, I certify that the 

 statements and information are to the best of my knowledge

 and belief true, accurate and complete. I am aware that 

 there are significant penalties for submitting false 

 statements and information or omitting required statements

 and information, including the possibility of fine or 

 imprisonment."

 3) On an annual basis, the owner or operator shall 

 submit, in the compliance certification, a statement 

 whether he or she has complied with this condition.

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2011.

Subsequent reports are due every 12 calendar month(s).

Condition 31: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 243-8

Item 31.1:

The Compliance Certification activity will be performed for the Facility.

Item 31.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 1) The owners and operators, and to the extent 

 applicable, the CAIR designated representative, shall 

 comply with all record keeping and reporting requirements 

 under 40 CFR Part 75 and 6 NYCRR 243-2.1(e)(1).

 2) The CAIR designated representative shall submit 

 quarterly reports of the NOx mass emissions data and heat 

 input data for each CAIR NOx unit, in an electronic 

 quarterly report in a format prescribed by the 

 Administrator for each calendar quarter.

 3) The CAIR designated representative shall submit each 

 quarterly report to the Administrator within 30 days 

 following the end of the calendar quarter covered by the 

 report. Quarterly reports shall be submitted in the 

 manner specified in 40 CFR 75.73(f).
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 30 FINAL

 4) For CAIR NOx Ozone Season units that are also subject 

 to the CAIR NOx Annual Trading Program or the Mercury 

 Reduction Program (6 NYCRR 246), quarterly reports shall 

 include the applicable data and information required by 

 Subparts F through I of 40 CFR part 75 as applicable, in 

 addition to the NOx mass emissions data and heat input 

 data.

 5) The CAIR designated representative shall submit to the

 Administrator a compliance certification (in a format 

 prescribed by the Administrator) in support of each 

 quarterly report based on reasonable inquiry of those 

 persons with primary responsibility for insuring that all 

 of the unit's emissions are correctly and fully monitored.

 The certification shall state that the monitoring data 

 submitted were recorded in accordance with the applicable 

 requirements of 6 NYCRR Part 243 and 40 CFR Part 75, 

 including the quality assurance procedures and 

 specifications; 

 6) Whenever any monitoring system fails to meet the 

 quality-assurance and quality-control requirements or data

 validation requirements of 40 CFR Part 75, data shall be 

 substituted using the applicable missing data procedures 

 in 40 CFR Part 75.

 7) Whenever the owner or operator makes a replacement, 

 modification or change in any certified continuous 

 emission monitoring system under 6 NYCRR 243-8.1(a)(1) 

 that may significantly affect the ability of the system to

 accurately measure or record NOx mass emissions or heat 

 input rate or to meet the quality assurance or quality 

 control requirements of 40 CFR 75.21 or Appendix B of Part

 75, the owner or operator shall re-certify the monitoring 

 system. Furthermore, whenever the owner or operator makes

 a replacement, modification or change to the flue gas 

 handling system or the unit's operation that may 

 significantly change the stack flow configuration profile,

 the owner or operator shall recertify each continuous 

 emission monitoring system whose accuracy is potentially 

 affected by the change. Examples of changes to a CEMS 

 that require recertification include replacement of the 

 analyzer, complete replacements of a CEMs, or change in 

 location or orientation of the sampling probe site.

 8) On an annual basis, the owner or operator shall submit,

 in the compliance certification, a statement whether he or

 she has complied with this condition.

Monitoring Frequency: CONTINUOUS

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 31 FINAL

The initial report is due 1/30/2011.

Subsequent reports are due every 12 calendar month(s).

Condition 32: CAIR General and Permit Requirments

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 244-1

Item 32.1: 

(1) As of midnight of March 1, or midnight of the first business day thereafter if March 1 is not

a business day, the owners and operators shall hold, in their compliance account, CAIR NOx

allowances available for compliance deductions for the previuos control period (January 1

through December 31), in an amount not less than the total tons of nitrogen oxides emissions

from all CAIR NOx units at the source during that control period. (244-1.6(c)(1) , 244-1.2(b)(5),

 244-1.2(b)(36)) 

 

(2) A CAIR NOx allowance shall not be deducted, for compliance with the requirements under

paragraph (2) of this section, for a control period in a calendar year before the year for which

the CAIR NOx allowance was allocated. (244-1.6(c)(3))

(3) 'Excess emissions requirements.' If a CAIR NOx source emits nitrogen oxides during any

control period in excess of the CAIR NOx emissions limitation, the owners and operators of the

 CAIR NOx source shall surrender the CAIR NOx allowances required for deduction under

6NYCRR Part 244-6.5(d)(1) and pay any fine, penalty, or assessment or comply with any other

remedy imposed, for the same violations, under the Act or applicable State law. Each ton of

such excess emissions and each day of such control period shall constitute a separate violation of

this permit, the Act, and applicable State law. (244-1.6(d))

(4) Unless otherwise provided, the owners and operators of the CAIR NOx source shall keep on

site each of the following documents for a period of five years from the date the document is

created. This period may be extended for cause, at any time before the end of five years, in

writing by the department or the Administrator:

(i) The certificate of representation under 6NYCRR Part 244-2.4 for the CAIR designated

representative for the source and all documents that demonstrate the truth of the statements in the

certificate of representation; provided that the certificate and documents shall be retained on site

at the source beyond such five year period until such documents are superseded because of the

submission of a new certificate of representation under 6NYCRR Part 244-2.4 changing the

CAIR designated representative.

(ii) All emissions monitoring information, in accordance with 6NYCRR Part 244-8, provided

that to the extent that 6NYCRR Part 244-8 provides for a three year period for recordkeeping,

the three year period shall apply.

(iii) Copies of all reports, compliance certifications, and other submissions and all records made

or required under the CAIR NOx Annual Trading Program.

(iv) Copies of all documents used to complete a CAIR permit application and any other

submission under the CAIR NOx Annual Trading Program or to demonstrate compliance with

the requirements of the CAIR NOx Annual Trading Program. (244-1.6(e))
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 32 FINAL

Condition 33: Designated CAIR Representative

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 244-2

Item 33.1:

1) Each Clean Air Interstate Rule (CAIR) NOx source shall have one CAIR designated

representative and may have one alternate representative, as per 6NYCRR Part 244-2.2, with

regard to all matters under the CAIR NOx Annual Trading Program. The CAIR designated

representative shall be selected by an agreement binding on the owners and operators of the

source and act in accordance with the certification statement in 6NYCRR Part 244-2.4(a)(4)(iv). 

Upon receipt by the Administrator of a complete certificate of representation under 6NYCRR

Part 244-2.4, the CAIR designated representative of the source shall represent and, by his or her

representations, actions, inactions, or submissions, legally bind each owner and operator of the

CAIR NOx source represented in all matters pertaining to the CAIR NOx Annual Trading

Program, notwithstanding any agreement between the CAIR designated representative and such

owners and operators. The owners and operators shall be bound by any decision or order issued

to the CAIR designated representative by the department, the Administrator, or a court regarding

the source. [244-2.1(a), (b) & (c)] 

(2) Each submission under the CAIR NOx Annual Trading Program shall be submitted, signed,

and certified by the CAIR designated representative for each CAIR NOx source on behalf of

which the submission is made. Each such submission shall include the following certification

statement by the CAIR designated representative: "I am authorized to make this submission on

behalf of the owners and operators of the source or units for which the submission is made. I

certify under penalty of law that I have personally examined, and am familiar with, the

statements and information submitted in this document and all its attachments. Based on my

inquiry of those individuals with primary responsibility for obtaining the information, I certify

that the statements and information are to the best of my knowledge and belief true, accurate,

and complete. I am aware that there are significant penalties for submitting false statements and

information or omitting required statements and information, including the possibility of fine or

imprisonment." [244-2.1(e)]

Condition 34: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 244-8

Item 34.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 0NY210-00-0 OXIDES OF NITROGEN

Item 34.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Monitoring and Reporting NOX emissions

 (1) The owners and operators, and to the extent 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 33 FINAL

 applicable, the CAIR designated representative shall 

 comply with all recordkeeping and reporting requirements 

 in this condition, the applicable recordkeeping and 

 reporting requirements under 40 CFR 75, and the 

 requirements of 6NYCRR Part 244-2.1(e)(1). 

 (2) The CAIR designated representative shall submit 

 quarterly reports of the the NOx mass emissions data and 

 heat input data for each CAIR NOx unit, in an electronic 

 quarterly report in a format prescribed by the 

 Administrator, for each calendar quarter beginning with 

 the calendar quarter corresponding to the earlier of the 

 date of provisional certification or the applicable 

 deadline for initial certification under 6NYCRR Part 

 244-8.1(b), unless that quarter is the third or fourth 

 quarter of 2007, in which case reporting shall commence in

 the quarter covering January 1, 2008 through March 31, 

 2008.

 (3) The CAIR designated representative shall submit each 

 quarterly report to the Administrator within 30 days 

 following the end of the calendar quarter covered by the 

 report. Quarterly reports shall be submitted in the manner

 specified in 40 CFR 75.73(f).

 (4) For CAIR NOx units that are also subject to an Acid 

 Rain emissions limitation or the CAIR NOx Ozone Season 

 Trading Program, CAIR SO2 Trading Program, or the Mercury 

 Reduction Program for Coal-Fired Electric Utility Steam 

 Generating Units (6NYCRR Part 246), quarterly reports 

 shall include the applicable data and information required

 by Subparts F through I of 40 CFR Part 75 as applicable, 

 in addition to the NOx mass emission data, heat input 

 data, and other information required by this 

 Subpart.

 (5) 'Compliance certification.' The CAIR designated 

 representative shall submit to the Administrator a 

 compliance certification (in a format prescribed by the 

 Administrator) in support of each quarterly report based 

 on reasonable inquiry of those persons with primary 

 responsibility for ensuring that all of the unit's 

 emissions are correctly and fully monitored. The 

 certification shall state that:

 (i) the monitoring data submitted were recorded in 

 accordance with the applicable requirements of 6NYCRR Part

 244 and 40 CFR Part 75, including the quality assurance 

 procedures and specifications; and

 (ii) for a unit with add-on NOx emission controls and for 

 all hours where NOx data are substituted in accordance 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 34 FINAL

 with 40 CFR 75.34(a)(1), the add-on emission controls were

 operating within the range of parameters listed in the 

 quality assurance/quality control program under appendix B

 to 40 CFR Part 75 and the substitute data values do not 

 systematically underestimate NOx emissions.

 (6) Whenever any monitoring system fails to meet the 

 quality-assurance and quality-control requirements or data

 validation requirements of 40 CFR part 75, data shall be 

 substituted using the applicable missing data procedures 

 in Subpart D or Subpart H of, or appendix D or appendix E 

 to 40 CFR part 75. [ 244-8.3(a) ]

 (7) Whenever the owner or operator makes a replacement, 

 modification, or change in any certified continuous 

 emission monitoring system under 6NYCRR Part 244-8.1(a)(1)

 that may significantly affect the ability of the system to

 accurately measure or record NOx mass emissions or heat 

 input rate or to meet the quality-assurance and 

 quality-control requirements of 40 CFR 75.21 or appendix B

 to 40 CFR Part 75, the owner or operator shall recertify 

 the monitoring system in accordance with 40 CFR 75.20(b) .

 Furthermore, whenever the owner or operator makes a 

 replacement, modification, or change to the flue gas 

 handling system or the unit's operation that may 

 significantly change the stack flow or concentration 

 profile, the owner or operator shall recertify each 

 continuous emission monitoring system whose accuracy is 

 potentially affected by the change, in accordance with 40 

 CFR 75.20(b). Examples of changes to a continuous emission

 monitoring system that require recertification include 

 replacement of the analyzer, complete replacement of an 

 existing continuous emission monitoring system, or change 

 in location or orientation of the sampling probe or site. 

 Any fuel flowmeter system, and any excepted NOx monitoring

 system under appendix E to 40 CFR part 75, under 6NYCRR 

 Part 244-8.1(a)(1) are subject to the recertification 

 requirements in 40 CFR 75.20(g)(6). [224-8.2(d)(2)

 

Monitoring Frequency: CONTINUOUS

Averaging Method: ANNUAL TOTAL

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2010.

Subsequent reports are due every 3 calendar month(s).

Condition 35: CAIR SO2 Trading Program General Provisions

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 245-1
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 35 FINAL

Item 35.1:

1) As of midnight of March 1, or midnight of the first business day thereafter (if March 1 is not

a business day) for a control period, the owners and operators of each Clean Air Interstate Rule

(CAIR) SO2 source shall hold, in the source's compliance account, a tonnage equivalent in

CAIR SO2 allowances available for compliance deductions for the control period (January 1

through December 31) not less than the tons of total sulfur dioxide emissions for the control

period from all CAIR SO2 units at the source. A CAIR SO2 allowance shall not be deducted,

for compliance with the requirements under paragraph (2) of this section, for a control period in

a calendar year before the year for which the CAIR SO2 allowance was allocated. 

[(245-1.2(b)(5), 245-1.6(c)(1), 245-1.2(b)(36), 245-1.6(c)(3)]

2) The owners and operators shall hold in their compliance account, CAIR SO allowances

available for compliance deductions for the control period starting on the later of January 1,

2010 or the deadline for meeting a CAIR SO2 unit's monitor certification requirements under

section 245-8.1(b)(1), (2), or (5) and for each control period thereafter. [245-1.6(c)(2)]

3) If a CAIR SO2 source emits sulfur dioxide during any control period in excess of the CAIR

SO2 emissions limitation, the owners and operators of the source shall surrender the CAIR SO2

allowances required for deduction under 6NYCRR Part 245-6.5(d)(1) and pay any fine, penalty,

or assessment or comply with any other remedy imposed, for the same violations, under the Act

or applicable State law. Each ton of such excess emissions and each day of such control period

shall constitute a separate violation of this Subpart, the Act, and applicable State law.

[(245-1.6(d)]

4) Unless otherwise provided, the owners and operators of the CAIR SO2 source shall keep on

site at the source each of the following documents for a period of five years from the date the

document is created. This period may be extended for cause, at any time before the end of five

years, in writing by the department or the Administrator: [245-1.6(e)]

 (i) The certificate of representation under 6NYCRR Part 245-2.4 for the CAIR designated

representative for the source and all documents that demonstrate the truth of the statements in the

certificate of representation; provided that the certificate and documents shall be retained on site

at the source beyond such five-year period until such documents are superseded because of the

submission of a new certificate of representation under 6NYCRR Part 245-2.4 changing the

CAIR designated representative.

 (ii) All emissions monitoring information, in accordance with 6NYCRR Part 245-8, provided

that to the extent that 6NYCRR Part 245-8 provides for a three-year period for recordkeeping,

the three-year period shall apply.

 (iii) Copies of all reports, compliance certifications, and other submissions and all records

made or required under the CAIR SO2 Trading Program.

 (iv) Copies of all documents used to complete a CAIR permit application and any other

submission under the CAIR SO2 Trading Program or to demonstrate compliance with the

requirements of the CAIR SO2 Trading Program.

Condition 36: Designated CAIR Representative

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 245-2

Item 36.1:

1) Each CAIR SO2 source shall have one and only one CAIR designated representative and

may have one alternate representative, as per 6NYCRR Part 245-2.2, with regard to all matters
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 36 FINAL

under the CAIR SO2 Trading Program. The CAIR designated representative of the CAIR SO2

source shall be selected by an agreement binding on the owners and operators of the source and

all CAIR SO2 units at the source and shall act in accordance with the certification statement in

6NYCRR Part 245-2.4(a)(4)(iv). Upon receipt by the Administrator of a complete certificate of

representation under 6NYCRR Part 245-2.4, the CAIR designated representative of the source

shall represent and, by his or her representations, actions, inactions, or submissions, legally bind

each owner and operator of the CAIR SO2 source represented and each CAIR SO2 unit at the

source in all matters pertaining to the CAIR SO2 Trading Program, notwithstanding any

agreement between the CAIR designated representative and such owners and operators. The

owners and operators shall be bound by any decision or order issued to the CAIR designated

representative by the department, the Administrator, or a court regarding the source or unit.

[245-2.1(a), (b) & (c)]

(2) Each submission under the CAIR SO2 Trading Program shall be submitted, signed, and

certified by the CAIR designated representative for each CAIR SO2 source on behalf of which

the submission is made. Each such submission shall include the following certification statement

by the CAIR designated representative: "I am authorized to make this submission on behalf of

the owners and operators of the source or units for which the submission is made. I certify under

penalty of law that I have personally examined, and am familiar with, the statements and

information submitted in this document and all its attachments. Based on my inquiry of those

individuals with primary responsibility for obtaining the information, I certify that the statements

and information are to the best of my knowledge and belief true, accurate, and complete. I am

aware that there are significant penalties for submitting false statements and information or

omitting required statements and information, including the possibility of fine or imprisonment." 

[245-2.1(e)]

Condition 37: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 245-8

Item 37.1:

The Compliance Certification activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 007446-09-5 SULFUR DIOXIDE

Item 37.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Monitoring and Reporting SO2 emissions:

 1) The owners and operators, and to the extent applicable,

 the Clean Air Interstate Rule (CAIR) designated 

 representative, of a CAIR SO2 unit, shall comply with the 

 monitoring, recordkeeping, and reporting requirements as 

 provided in Subpart 6 NYCRR Part 245-8 and in 40 CFR Part 

 75, Subparts F and G. For purposes of complying with such

 requirements, the definitions in section 245-1.2 and 40 

 CFR 72.2 shall apply, and the terms "affected unit," 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 37 FINAL

 "designated representative," and "continuous emission 

 monitoring system" (or "CEMS") in 40 CFR Part 75 shall be 

 deemed to refer to the terms "CAIR SO2 unit," "CAIR 

 designated representative," and "continuous emission 

 monitoring system" (or "CEMS") respectively, as defined in

 section 245-1.2. The owner or operator of a unit that is 

 not a CAIR SO2 unit but that is monitored under 40 CFR 

 75.16(b)(2) shall comply with the same monitoring, 

 recordkeeping, and reporting requirements as a CAIR SO2 

 unit. [245-8.1]

 2)The owner or operator of each CAIR SO2 unit shall: 

 [245-8.1(a)]

 (i) install all monitoring systems required under this

 Subpart for monitoring SO2 mass emissions and individual 

 unit heat input (including all systems required to monitor

 SO2 concentration, stack gas moisture content, stack gas 

 flow rate, CO2 or O2 concentration, and fuel flow rate, as

 applicable, in accordance with 40 CFR 75.11 and 40 CFR 

 75.16);

 (ii) successfully complete all certification tests 

 required under Part 245-8.2 and meet all other 

 requirements of this section and 40 CFR Part 75 applicable

 to the monitoring systems under this section; and

 (iii) record, report, and quality-assure the data from

 the monitoring systems under paragraph of this 

 section.

 3) The owner or operator shall meet the monitoring system

 certification and other requirements of section 

 245-8.1(a)(1) and (2) on or before the following dates. 

 The owner or operator shall record, report, and 

 quality-assure the data from the monitoring systems under 

 section 245-8.1(a)(1) on and after the following dates. 

 [245-8.1(b)]

 (i) For the CAIR SO2 unit that commences commercial 

 operation before July 1, 2008, by January 1, 2009.

 (ii) For the CAIR SO2 unit that commences commercial 

 operation on or after July 1, 2008, by the later of the 

 following dates: January 1, 2009; or 90 unit operating 

 days or 180 calendar days, whichever occurs first, after 

 the date on which the unit commences commercial 

 operation.

 4) Whenever the owner or operator makes a replacement, 

 modification, or change in any certified continuous 

 emission monitoring system under section 245-8.1(a)(1) 

 that may significantly affect the ability of the system to

 accurately measure or record SO2 mass emissions or heat 

 input rate or to meet the quality-assurance and 

 quality-control requirements of 40 CFR 75.21 or appendix B

 to 40 CFR Part 75, the owner or operator shall recertify 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 38 FINAL

 the monitoring system in accordance with 40 CFR 75.20(b). 

 Furthermore, whenever the owner or operator makes a 

 replacement, modification, or change to the flue gas 

 handling system or the unit's operation that may 

 significantly change the stack flow or concentration 

 profile, the owner or operator shall recertify each 

 continuous emission monitoring system whose accuracy is 

 potentially affected by the change, in accordance with 40 

 CFR 75.20(b). Examples of changes to a continuous emission

 monitoring system that require recertification include: 

 replacement of the analyzer, complete replacement of an 

 existing continuous emission monitoring system, or change 

 in location or orientation of the sampling probe or site. 

 Any fuel flowmeter system under section 245-8.1(a)(1) is 

 subject to the recertification requirements in 40 CFR 

 75.20(g)(6). [245-8.2(d)(2)]

 5) Whenever any monitoring system fails to meet the 

 quality-assurance and quality-control requirements or data

 validation requirements of 40 CFR Part 75, data shall be 

 substituted using the applicable missing data procedures 

 in Subpart D of or appendix D to 40 CFR Part 75. 

 [245-8.3(a)]

 6) The CAIR designated representative shall comply with 

 all recordkeeping and reporting requirements in section 

 245-8.3, the applicable recordkeeping and reporting 

 requirements in Subparts F and G of 40 CFR Part 75, and 

 the requirements of section 245-2.1(e)(1). 

 [245-8.5(a)]

 7) The owner or operator of a CAIR SO2 unit shall comply 

 with requirements of 40 CFR 75.62 for monitoring plans. 

 [245-8.5(b)]

 8) The CAIR designated representative shall submit an 

 application to the department within 45 days after 

 completing all initial certification or recertification 

 tests required under section 245-8.2, including the 

 information required under 40 CFR 75.63. [245-8.5(c) 

 ]

 9) The CAIR designated representative shall submit 

 quarterly reports of the SO2 mass emissions data and heat 

 input data for each CAIR SO2 unit, in an electronic 

 quarterly report in a format prescribed by the 

 Administrator, for each calendar quarter beginning with: 

 [245-8.5(d)(1)]

 i) the calendar quarter covering January 1, 2009 

 through March 31, 2009 for a unit that commences 

 commercial operation before July 1, 2008; or

 ii) for a unit that commences commercial operation on 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 39 FINAL

 or after July 1, 2008, the calendar quarter corresponding 

 to the earlier of the date of provisional certification or

 the applicable deadline for initial certification under 

 section 245-8.1(b), unless that quarter is the third or 

 fourth quarter of 2008, in which case reporting shall 

 commence in the quarter covering January 1, 2009 through 

 March 31, 2009.

 10) The CAIR designated representative shall submit each 

 quarterly report to the Administrator within 30 days 

 following the end of the calendar quarter covered by the 

 report. Quarterly reports shall be submitted in the manner

 specified in 40 CFR 75.64. [245-8.5(d)(2)]

 11) For CAIR SO2 units that are also subject to an Acid 

 Rain emissions limitation or the CAIR NOX Annual Trading 

 Program, CAIR NOX Ozone Season Trading Program, or the 

 Mercury Reduction Program for Coal-Fired Electric Utility 

 Steam Generating Units (6 NYCRR Part 246), quarterly 

 reports shall include the applicable data and information 

 required by Subparts F through I of 40 CFR Part 75 as 

 applicable, in addition to the SO2 mass emission data, 

 heat input data, and other information required by this 

 Subpart. [245-8.5(d)(3)]

 12) The CAIR designated representative shall submit to 

 the Administrator a compliance certification (in a format 

 prescribed by the Administrator) in support of each 

 quarterly report based on reasonable inquiry of those 

 persons with primary responsibility for ensuring that all 

 of the unit's emissions are correctly and fully monitored.

 The certification shall state that: [245-8.5(e)]

 i) the monitoring data submitted were recorded in 

 accordance with the applicable requirements of this 

 Subpart and 40 CFR Part 75, including the quality 

 assurance procedures and specifications; and

 ii) for a unit with add-on SO2 emission controls and 

 for all hours where SO2 data are substituted in accordance

 with 40 CFR 75.34(a)(1), the add-on emission controls were

 operating within the range of parameters listed in the 

 quality assurance/quality control program under appendix B

 to 40 CFR Part 75 and the substitute data values do not 

 systematically underestimate SO2 emissions.

Monitoring Frequency: CONTINUOUS

Averaging Method: ANNUAL TOTAL

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2010.

Subsequent reports are due every 3 calendar month(s).

Condition 2-5: Exemption from Part 249
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 40 FINAL

 Effective between the dates of 05/24/2012 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 249.1 (c) (2)

Item 2-5.1:

A source that permanently shuts down by January 1, 2014 is exempt from the requirements of

Part 249.

 ** ** Emission Unit Level  

Condition 38: Emission Point Definition By Emission Unit

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 201-6

Item 38.1(From Mod 0):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00ASH

 Emission Point: 0005A 

 Height (ft.): 35 Diameter (in.): 6

 NYTMN (km.): 4768.739 NYTME (km.): 401.624 Building: ASILO

 Emission Point: 0005B 

 Height (ft.): 35 Diameter (in.): 6

 NYTMN (km.): 4768.739 NYTME (km.): 401.618 Building: ASILO

Item 38.2(From Mod 0):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-00BLR

 Emission Point: 00001 

 Height (ft.): 265 Diameter (in.): 156

 NYTMN (km.): 4768.781 NYTME (km.): 401.618 Building: BAG HS

Item 38.3(From Mod 0):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-0COAL

 Emission Point: 0006A 

 Height (ft.): 55 Diameter (in.): 6

 NYTMN (km.): 4768.727 NYTME (km.): 401.666 Building: BLR HS

 Emission Point: 0006B 

 Height (ft.): 55 Diameter (in.): 6

 NYTMN (km.): 4768.727 NYTME (km.): 401.669 Building: BLR HS
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 41 FINAL

Item 38.4(From Mod 0):

The following emission points are included in this permit for the cited Emission Unit:

 Emission Unit: U-0COOL

 Emission Point: 00002 

 Height (ft.): 50 Diameter (in.): 926

 NYTMN (km.): 4768.69 NYTME (km.): 401.568

Condition 39: Process Definition By Emission Unit

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 201-6

Item 39.1(From Mod 2):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00BLR

 Process: COA Source Classification Code: 1-03-002-14

 Process Description: 

 Any number of five boilers firing bituminous coal. The 

 flue gas exhaust passes through a spray dry absorber and a

 fabric filter baghouse.

 Emission Source/Control: 0BLRS - Combustion 

 Design Capacity: 275 million Btu per hour

 Emission Source/Control: 0BAGH - Control 

 Control Type: FABRIC FILTER

 Emission Source/Control: 0SPDA - Control 

 Control Type: DRY LIME INJECTION

Item 39.2(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: 0-PAPER

 Process: PHS Source Classification Code: 1-01-002-02

 Process Description: 

 This process identifies those operations associated with 

 alternative fuel handling and storage.

 Emission Source/Control: PAPHS - Process 

Item 39.3(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00ASH

 Process: MIS Source Classification Code: 3-05-009-05

 Process Description: 

 Pneumatic transfer of flyash from the boiler gas passes 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 42 FINAL

 and the boiler baghouse hoppers to the ash storage silo, 

 and transfer from the silo to trucks or rail cars for 

 off-site disposal.

 Emission Source/Control: ASHBG - Control 

 Control Type: FABRIC FILTER

 Emission Source/Control: ASHTR - Process 

Item 39.4(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00BLR

 Process: ALT Source Classification Code: 1-01-012-01

 Process Description: 

 Boilers #3, #4 and/or #5 combusting up to 30% by weight 

 alternative fuel fluff processed from pre-consumer, 

 non-recyclable, non-reusable, non-contaminated plastic 

 coated paper, wax coated paper, paper, fibrous material 

 and low chlorine content (less than 1% dry weight as 

 received) plastic film. Demonstration that this is the 

 only type of alternative fuel fired shall be in accordance

 with the Alternative Fuels QA/QC Plan approved by the 

 Department.

 Emission Source/Control: 0BLRS - Combustion 

 Design Capacity: 275 million Btu per hour

 Emission Source/Control: 0BAGH - Control 

 Control Type: FABRIC FILTER

 Emission Source/Control: 0SPDA - Control 

 Control Type: DRY LIME INJECTION

Item 39.5(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00BLR

 Process: BIO Source Classification Code: 1-01-007-01

 Process Description: 

 Burning of biogas generated from the Solvay Paperboard 

 wastewater treatment facility.

 Emission Source/Control: 0BLRS - Combustion 

 Design Capacity: 275 million Btu per hour

 Emission Source/Control: 0BAGH - Control 

 Control Type: FABRIC FILTER

 Emission Source/Control: 0SPDA - Control 

 Control Type: DRY LIME INJECTION
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 43 FINAL

Item 39.6(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00BLR

 Process: CCA Source Classification Code: 1-02-005-01

 Process Description: 

 Boilers #3, #4 and/or #5 combusting up to 30% by weight 

 alternative fuel fluff in conjunction with bituminous coal

 with a sulfur content less than or equal to 0.60 lb/MMBTU,

 or that achieves a stack emission rate less than or equal 

 to 1.20 lbs SO2 per million BTU without the spray dryer 

 operating. The alternative fuel fluff is processed from 

 pre-consumer, non-recyclable, non-reuseable, 

 non-contaminated plastic coated paper, wax coated paper, 

 paper, fibrous material and low chlorine content (less 

 than 1% by weight as received) plastic film. 

 Demonstration that this is the only type of alternative 

 fuel fired shall be in accordance with the Alternative 

 Fuels QA/QC Plan approved by the Department.

 Emission Source/Control: 0BLR4 - Combustion 

 Design Capacity: 275 million BTUs per hour

 Emission Source/Control: 0BLR5 - Combustion 

 Design Capacity: 275 million BTUs per hour

 Emission Source/Control: 0BAGH - Control 

 Control Type: FABRIC FILTER

Item 39.7(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-00BLR

 Process: CCO Source Classification Code: 1-03-002-14

 Process Description: 

 Any number of five boilers firing bituminous coal with a 

 sulfur content less than or equal to 0.60 lb sulfur per 

 million BTU, or that achieves a stack emission rate less 

 than or equal to 1.20 pounds SO2 per million BTU without 

 the spray dry absorber operating.

 Emission Source/Control: 0BLRS - Combustion 

 Design Capacity: 275 million Btu per hour

 Emission Source/Control: 0BAGH - Control 

 Control Type: FABRIC FILTER

 Emission Source/Control: 0SPDA - Control 

 Control Type: DRY LIME INJECTION

Item 39.8(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 44 FINAL

 Emission Unit: U-00BLR

 Process: OIL Source Classification Code: 1-02-005-01

 Process Description: 

 Any number of five boilers firing #2 fuel oil for boiler 

 startup, low load operation and/or flame stabilization. 

 The flue gas exhaust passes through a spray dry absorber 

 and a fabric filter baghouse.

 Emission Source/Control: 0BLRS - Combustion 

 Design Capacity: 275 million Btu per hour

 Emission Source/Control: 0BAGH - Control 

 Control Type: FABRIC FILTER

 Emission Source/Control: 0SPDA - Control 

 Control Type: DRY LIME INJECTION

Item 39.9(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-0COAL

 Process: BNK Source Classification Code: 3-05-010-43

 Process Description: 

 COAL BUNKER BAGHOUSE USED TO CONTROL DUST 

 EMISSIONS FROM THE COAL STORAGE BUNKERS. 

 TRAPPED COAL DUST FROM THE BAGHOUSE IS 

 RECYCLED BACK TO PROCESS (COAL BUNKERS).

 Emission Source/Control: BNKBG - Control 

 Control Type: FABRIC FILTER

 Emission Source/Control: UNLOD - Process 

Item 39.10(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-0COAL

 Process: CRU Source Classification Code: 3-05-010-11

 Process Description: 

 The coal crusher/conveying system transfers coal from 

 unloading system to either the boiler building or to the 

 coal storage pile. As coal is transferred to the boiler 

 building, it passes through a metal removal magnet and 

 through a crusher. The crusher also contains a 

 water/surfactant sprayer for dust suppression, as needed.

 Emission Source/Control: DETER - Control 

 Control Type: DUST SUPPRESSION BY WATER SPRAY

 Emission Source/Control: CNVEY - Process 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 45 FINAL

 Emission Source/Control: CPILE - Process 

 Emission Source/Control: CRUSH - Process 

Item 39.11(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-0COAL

 Process: UNL Source Classification Code: 3-05-010-11

 Process Description: 

 Unloading of railroad cars and transferring coal from the

 coal storage pile to the coal crusher/conveying system. A 

 mixture of water and surfactant is used for dust 

 suppression, as needed.

 Emission Source/Control: DETER - Control 

 Control Type: DUST SUPPRESSION BY WATER SPRAY

 Emission Source/Control: UNLOD - Process 

Item 39.12(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-0COOL

 Process: CTR Source Classification Code: 1-01-002-02

 Process Description: 

 Condensed steam and boiler blowdown waste heat 

 dissipation using a mechanical cooling tower.

 Emission Source/Control: DRIFT - Control 

 Control Type: MIST ELIMINATOR

 Emission Source/Control: CLTWR - Process 

Item 39.13(From Mod 0):

This permit authorizes the following regulated processes for the cited Emission Unit:

 Emission Unit: U-0LIME

 Process: LHS Source Classification Code: 1-01-002-02

 Process Description: 

 All process operations associated with lime handling and 

 storage.

 Emission Source/Control: LIMHS - Process 

 Emission Source/Control: LSILO - Process 

Condition 40: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 225-1.5 (b)
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 46 FINAL

Item 40.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00BLR

 Regulated Contaminant(s):

 CAS No: 007446-09-5 SULFUR DIOXIDE

Item 40.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: CONTINUOUS EMISSION MONITORING (CEM)

Monitoring Description: 

 The facility has been granted an equivalent emission rate

 variance from the limitations in 6NYCRR 225-1. This 

 condition applies regardless of the operational status of 

 the spray dry adsorber (Source/Control 0SPDA), but does 

 not waive the requirement to also comply with 40 CFR 60.14

 when the spray dry adsorber is operational.

 Emissions of sulfur dioxide emissions shall not exceed 

 1.20 pounds SO2 per million Btu heat input, on a 24 hour 

 block basis. Compliance shall be determined using a 

 continuous emissions monitor meeting the requirements of 

 40 CFR 60.13, 40 CFR Part 60 Appendix B and Appendix F. 

 Daily average emissions shall be calculated using Equation

 19-20a of EPA Method 19 (40 CFR Part 60, Appendix 

 A).

 On a calendar quarter basis, the owners or operators shall

 submit to the DEC a report of the periods of excess 

 emissions. Such report shall state the date and time of 

 when the period of excess emission begins and ends, the 

 average magnitude during each clock hour in that period of

 excess emissions, the cause of the excess emissions and 

 the corrective action. The report shall also include the 

 results of quarterly and annual audits conducted on the 

 continuous emission monitor system.

Manufacturer Name/Model Number: CSI Model SA-700

Upper Permit Limit: 1.20 pounds per million Btus

Reference Test Method: 40 CFR Part 60, Appendix A, Method 19

Monitoring Frequency: CONTINUOUS

Averaging Method: 24 HOUR BLOCK AVERAGE (ARITHMETIC 

 MEAN)

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2010.

Subsequent reports are due every 3 calendar month(s).

Condition 41: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 47 FINAL

 Applicable Federal Requirement:6 NYCRR 227-1.2 (a) (3)

Item 41.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00BLR

 Regulated Contaminant(s):

 CAS No: 0NY075-00-0 PARTICULATES

Item 41.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: INTERMITTENT EMISSION TESTING

Monitoring Description: 

 No person shall cause or allow an emission into the 

 outdoor atmosphere of particulates in excess of 0.10 pound

 per million Btu heat input from the boilers at this 

 facility.

 Compliance shall be determined through stack emission 

 testing conducted in accordance with a protocol approved 

 by the DEC. Testing shall be conducted once per permit 

 term and at any other time when requested by the DEC. 

 Results of testing shall be submitted to the DEC within 60

 days after the completion of the tests. The procedures 

 and time frames of 6 NYCRR 202-1 are applicable.

 On a calendar-annual basis, the owner or operator shall 

 inform the DEC whether he or she has complied with this 

 condition.

Parameter Monitored: PARTICULATES

Upper Permit Limit: 0.1 pounds per million Btus

Reference Test Method: EPA Method 5

Monitoring Frequency: ONCE DURING THE TERM OF THE PERMIT

Averaging Method: AVERAGING METHOD AS PER REFERENCE TEST

 METHOD INDICATED

Reporting Requirements: ONCE / BATCH OR MONITORING OCCURRENCE

Condition 42: Testing, monitoring, and reporting requirements for very 

 large boilers.

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 227-2.6 (a) (1)

Item 42.1:

This Condition applies to Emission Unit: U-00BLR

Item 42.2:

The owner/operator shall measure NOx emissions with a continuous emissions monitoring
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 48 FINAL

system (CEMS) as described in 6NYCRR 227-2.6(b).

Condition 43: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 231-2.6 (a) (7)

Item 43.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00BLR

 Regulated Contaminant(s):

 CAS No: 0NY210-00-0 OXIDES OF NITROGEN

Item 43.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: CONTINUOUS EMISSION MONITORING (CEM)

Monitoring Description: 

 Total NOx emissions from this emission unit shall not 

 exceed 1552 tons/year as calculated on a monthly rolling 

 basis. This limit was established pursuant to the 

 creation of Emission Reduction Credits by the source 

 owner.

Manufacturer Name/Model Number: CSI Model 1600

Upper Permit Limit: 1552 tons per year

Reference Test Method: NOX CEMS

Monitoring Frequency: CONTINUOUS

Averaging Method: ANNUAL MINIMUM ROLLED MONTHLY

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2011.

Subsequent reports are due every 12 calendar month(s).

Condition 2-6: Compliance Certification

 Effective between the dates of 05/24/2012 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 249.1 (c) (2)

Item 2-6.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00BLR

Item 2-6.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Coal fired boiler Unit 1 is subject to the requirements 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 49 FINAL

 of Part 249, Best Available Retrofit Technology (BART). 

 This unit will be permanently shut down by January 1, 

 2014. Facility shall notify the Department in writing 

 within 30 days of the actual date of shutdown of unit 1, 

 which must occur prior to January 1, 2014.

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2013.

Subsequent reports are due every 12 calendar month(s).

Condition 44: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR Subpart 257-1

Item 44.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00BLR

Item 44.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 The facility shall not operate more than one pulverizer 

 per boiler upon startup, nor more than two pulverizers 

 total on startup when the spray dry absorber is not 

 operating.

 The facility shall submit to the DEC on an annual calendar

 year basis whether it has complied with this requirement. 

 Additionally, if the owner or operator has violated this 

 condition, the owner or operator shall submit a report to 

 the DEC within 30 days of such occurrence.

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2011.

Subsequent reports are due every 12 calendar month(s).

Condition 45: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:40CFR 60.14, NSPS Subpart A

Item 45.1:
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 50 FINAL

The Compliance Certification activity will be performed for:

 Emission Unit: U-00BLR

 Regulated Contaminant(s):

 CAS No: 007446-09-5 SULFUR DIOXIDE

Item 45.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: CONTINUOUS EMISSION MONITORING (CEM)

Monitoring Description: 

 This condition applies when the spray dry adsorber 

 (Source/Control 0SPDA) is operational.

 

 Sulfur dioxide emissions shall not exceed 1.10 pounds SO2 

 per million Btu heat input, on a 24 hour block basis. 

 Compliance shall be determined using a continuous 

 emissions monitor meeting the requirements of 40 CFR Part 

 60.13, 40 CFR Part 60 Appendix B and Appendix F. Daily 

 average emissions shall be calculated using Equation 

 19-20a of EPA Method 19 (40 CFR Part 60, Appendix 

 A).

 On a calendar quarter basis, the owners or operators shall

 submit to the DEC a report of the periods of excess 

 emissions. Such report shall state the date and time of 

 when the period of excess emission begins and ends, the 

 average magnitude during each clock hour in that period of

 excess emissions, the cause of the excess emissions and 

 the corrective action. The report shall also include the 

 results of quarterly and annual audits conducted on the 

 continuous emission monitor system.

Manufacturer Name/Model Number: CSI Model SA-700

Parameter Monitored: SULFUR DIOXIDE

Upper Permit Limit: 1.10 pounds per million Btus

Reference Test Method: 40 CFR 60 App B/F

Monitoring Frequency: CONTINUOUS

Averaging Method: 24 HOUR DAILY BLOCK (ARITHMETIC 

 AVERAGE)

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2010.

Subsequent reports are due every 3 calendar month(s).

Condition 46: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:40 CFR Part 64

Item 46.1:
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 51 FINAL

The Compliance Certification activity will be performed for:

 Emission Unit: U-00BLR

Item 46.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: MONITORING OF PROCESS OR CONTROL 

 DEVICE PARAMETERS AS SURROGATE

Monitoring Description: 

 1. The facility shall monitor and record stack opactity 

 with a continuous opacty monitoring system (COMS). The 

 COMS shall meet the performance specification of 40 CFR 

 Part 60, Appendix B, Performance Specification 1 and 40 

 CFR 60.13.

 2. On a calendar quarter basis, the owner or operator 

 shall submit to the DEC a report identifying each six 

 minute block period where the stack opacity exceeds 20 

 percent. The report shall state the date and time when 

 the excess opacity occurred, the average magnitude of the 

 opacity, the cause of the excess opacity (if known), and 

 the corrective action taken to abate such emission. 

 (Quarterly reporting required elsewhere in this permit 

 will satisfy this requirement.)

 3. If, in any calendar quarter, the duration of all 

 six-minute periods of operation when the stack opacity 

 was in excess of 20% exceeds 0.5% of the source operating 

 time in that calendar quarter, the owner or operator shall

 develop and implement a Quality Improvement Plan. This 

 plan shall include the elements specified in 40 CFR 64.8. 

 The QIP shall be submitted to the DEC. After 

 implementation of the QIP, The DEC may require to make 

 reasonable changes to the QIP as provided in 40 CFR 

 64.8(d).

Parameter Monitored: OPACITY

Upper Permit Limit: 20 percent

Reference Test Method: COMS meeting 40 CFR Part 60

Monitoring Frequency: CONTINUOUS

Averaging Method: 6-MINUTE AVERAGE (METHOD 9)

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2010.

Subsequent reports are due every 3 calendar month(s).

Condition 47: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 227-1.3
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 52 FINAL

Item 47.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00BLR Emission Point: 00001

Item 47.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: CONTINUOUS EMISSION MONITORING (CEM)

Monitoring Description: 

 Stack opacity shall not exceed 20 percent (six minute 

 average), except for one six-minute period per hour of not

 more than 27 percent opacity. Compliance with this 

 standard may be determined by EPA Reference Method 9, 

 Continuous Opacity Monitoring System (COMS) data, and/or 

 any other credible evidence. The owner shall install, 

 operate in accordance with manufacturer's instructions, 

 and properly maintain, a COMS in the stack satisfying the 

 crtieria in Appendix B of 40 CFR part 60.

 The owner shall submit an accurate excess emissions and 

 monitoring system performance report to the Department for

 each calendar year quarter. All reports shall be 

 certified by a responsible corporate official as true, 

 accurate and complete and postmarked by the 60th day 

 following the end of each calendar year quarter. The 

 quarterly excess emissions report shall be submitted in a 

 form acceptable to the Department and shall include the 

 following minimum information:

 (1) The magnitude, date and time of each six minute block 

 average during which the average opacity of emissions 

 exceeds 20 percent, except for one six minute block 

 average per hour not to exceed 27 percent;

 (2) For each period of excess emissions, specific 

 identification of the cause and corrective action 

 taken;

 (3) Identification of all periods of COMS downtime, 

 including the date, time and duration of each inoperable 

 period, and the cause and corrective action for each COMS 

 downtime period;

 (4) The total time in which the COMS are required to 

 record data during the reporting period;

 (5) The total number of exceedences and the duration of 

 exceedences expressed as a percentage of the total time 

 which the COMS are required to record data.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 53 FINAL

Parameter Monitored: OPACITY

Upper Permit Limit: 20 percent

Reference Test Method: 40 CFR 60 APP B RM 9

Monitoring Frequency: CONTINUOUS

Averaging Method: 6 MINUTE AVERAGE

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 60 days after the reporting period.

The initial report is due 5/30/2010.

Subsequent reports are due every 3 calendar month(s).

Condition 48: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 227-2.4 (a)

Item 48.1:

The Compliance Certification activity will be performed for:

 Emission Unit: U-00BLR Emission Point: 00001

 Regulated Contaminant(s):

 CAS No: 0NY210-00-0 OXIDES OF NITROGEN

Item 48.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: CONTINUOUS EMISSION MONITORING (CEM)

Monitoring Description: 

 NOx emissions from very large, wall fired coal dry bottom

 boilers shall not exceed 0.45 lb/mmbtu (daily average 

 during ozone season, 30 day rolling average during non 

 ozone season). Compliance is determined using a NOx 

 Continuous Emissions Monitoring System located in the 

 boiler stack.

Manufacturer Name/Model Number: CSI Model 1600

Parameter Monitored: OXIDES OF NITROGEN

Upper Permit Limit: 0.45 pounds per million Btus

Reference Test Method: 40 CFR 60 App B/F

Monitoring Frequency: CONTINUOUS

Averaging Method: 24-HOUR AVERAGE

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2010.

Subsequent reports are due every 3 calendar month(s).

Condition 49: Compliance Certification

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable Federal Requirement:6 NYCRR 200.7

Item 49.1:
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 54 FINAL

The Compliance Certification activity will be performed for:

 Emission Unit: U-00BLR Emission Point: 00001

 Process: COA Emission Source: 0BAGH

Item 49.2:

Compliance Certification shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 This spray dry adsorber and fabric filter controlling 

 emissions from Boilers #1, #2, #3, #4 and #5 shall be 

 operated in accordance with the Scrubber Operating Plan 

 submitted to and approved by the DEC. The facility shall 

 maintain a log of all maintenance performed on the spray 

 dry adsorber and fabric filter, including parts 

 replacement, bag changes, routine cleaning and all other 

 preventive maintenance. The facility shall ensure that 

 all manufacturer-recommended maintenance procedures are 

 performed.

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: SEMI-ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 7/30/2010.

Subsequent reports are due every 6 calendar month(s).
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 55 FINAL

 STATE ONLY ENFORCEABLE CONDITIONS

 ** ** Facility Level  

 NOTIFICATION OF GENERAL PERMITTEE OBLIGATIONS

This section contains terms and conditions which are not federally enforceable. Permittees

may also have other obligations under regulations of general applicability

Item A: General Provisions for State Enforceable Permit Terms and

 Condition - 6 NYCRR Part 201-5

 Any person who owns and/or operates stationary sources 

 shall operate and maintain all emission units and any 

 required emission control devices in compliance with all 

 applicable Parts of this Chapter and existing laws, and 

 shall operate the facility in accordance with all 

 criteria, emission limits, terms, conditions, and 

 standards in this permit. Failure of such person to 

 properly operate and maintain the effectiveness of such 

 emission units and emission control devices may be 

 sufficient reason for the Department to revoke or deny a 

 permit.

 The owner or operator of the permitted facility must 

 maintain all required records on-site for a period of five

 years and make them available to representatives of the 

 Department upon request. Department representatives must 

 be granted access to any facility regulated by this 

 Subpart, during normal operating hours, for the purpose of

 determining compliance with this and any other state and 

 federal air pollution control requirements, regulations or

 law.

 STATE ONLY APPLICABLE REQUIREMENTS

The following conditions are state applicable requirements and are not subject to 

compliance certification requirements unless otherwise noted or required 

 under 6 NYCRR Part 201.

Condition 50: Contaminant List

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable State Requirement:ECL 19-0301

Item 50.1:

Emissions of the following contaminants are subject to contaminant specific requirements in this

permit(emission limits, control requirements or compliance monitoring conditions).

 CAS No: 000124-38-9

 Name: CARBON DIOXIDE
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 56 FINAL

 CAS No: 007446-09-5

 Name: SULFUR DIOXIDE

 CAS No: 0NY075-00-0

 Name: PARTICULATES

 CAS No: 0NY210-00-0

 Name: OXIDES OF NITROGEN

Condition 51: Unavoidable noncompliance and violations

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable State Requirement:6 NYCRR 201-1.4

Item 51.1:

At the discretion of the commissioner a violation of any applicable emission standard for

necessary scheduled equipment maintenance, start-up/shutdown conditions and malfunctions or

upsets may be excused if such violations are unavoidable. The following actions and

recordkeeping and reporting requirements must be adhered to in such circumstances.

(a) The facility owner and/or operator shall compile and maintain records of all

equipment maintenance or start-up/shutdown activities when they can be expected to result in an

exceedance of any applicable emission standard, and shall submit a report of such activities to

the commissioner's representative when requested to do so in writing or when so required by a

condition of a permit issued for the corresponding air contamination source except where

conditions elsewhere in this permit which contain more stringent reporting and notification

provisions for an applicable requirement, in which case they supercede those stated here. Such

reports shall describe why the violation was unavoidable and shall include the time, frequency

and duration of the maintenance and/or start-up/shutdown activities and the identification of air

contaminants, and the estimated emission rates. If a facility owner and/or operator is subject to

continuous stack monitoring and quarterly reporting requirements, he need not submit reports for

equipment maintenance or start-up/shutdown for the facility to the commissioner's

representative.

(b) In the event that emissions of air contaminants in excess of any emission standard

in 6 NYCRR Chapter III Subchapter A occur due to a malfunction, the facility owner and/or

operator shall report such malfunction by telephone to the commissioner's representative as soon

as possible during normal working hours, but in any event not later than two working days after

becoming aware that the malfunction occurred. Within 30 days thereafter, when requested in

writing by the commissioner's representative, the facility owner and/or operator shall submit a

written report to the commissioner's representative describing the malfunction, the corrective

action taken, identification of air contaminants, and an estimate of the emission rates. These

reporting requirements are superceded by conditions elsewhere in this permit which contain

reporting and notification provisions for applicable requirements more stringent than those

above.

(c) The Department may also require the owner and/or operator to include in reports

described under (a) and (b) above an estimate of the maximum ground level concentration of

each air contaminant emitted and the effect of such emissions depending on the deviation of the

malfunction and the air contaminants emitted.

(d) In the event of maintenance, start-up/shutdown or malfunction conditions which
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 57 FINAL

result in emissions exceeding any applicable emission standard, the facility owner and/or

operator shall take appropriate action to prevent emissions which will result in contravention of

any applicable ambient air quality standard. Reasonably available control technology, as

determined by the commissioner, shall be applied during any maintenance, start-up/shutdown or

malfunction condition subject to this paragraph.

(e) In order to have a violation of a federal regulation (such as a new source performance

standard or national emissions standard for hazardous air pollutants) excused, the specific

federal regulation must provide for an affirmative defense during start-up, shutdowns,

malfunctions or upsets.

Condition 52: Air pollution prohibited

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable State Requirement:6 NYCRR 211.2

Item 52.1:

No person shall cause or allow emissions of air contaminants to the outdoor atmosphere of such

quantity, characteristic or duration which are injurious to human, plant or animal life or to

property, or which unreasonably interfere with the comfortable enjoyment of life or property.

Notwithstanding the existence of specific air quality standards or emission limits, this

prohibition applies, but is not limited to, any particulate, fume, gas, mist, odor, smoke, vapor,

pollen, toxic or deleterious emission, either alone or in combination with others.

Condition 2-7: Visible Emissions Limited

 Effective between the dates of 05/24/2012 and 05/23/2017

 Applicable State Requirement:6 NYCRR 211.2

Item 2-7.1:

Except as permitted by a specific part of this Subchapter and for open fires for which a restricted

burning permit has been issued, no person shall cause or allow any air contamination source to

emit any material having an opacity equal to or greater than 20 percent (six minute average)

except for one continuous six-minute period per hour of not more than 57 percent opacity.

Condition 53: Compliance Demonstration

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable State Requirement:6 NYCRR Subpart 242-1

Item 53.1:

The Compliance Demonstration activity will be performed for the Facility.

Item 53.2:

Compliance Demonstration shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 1. The owners and operators and, to the extent 

 applicable, the CO2 authorized account representative of 

 each CO2 budget source and each CO2 budget unit at the 

 source shall hold CO2 allowances available for compliance 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 58 FINAL

 deductions under Section 242-6.5, as of the CO2 allowance 

 transfer deadline, in the source's compliance account in 

 an amount not less than the total CO2 emissions for the 

 control period from all CO2 budget units at the source, as

 determined in accordance with Subparts 242-6 and 

 242-8.

 2. A CO2 allowance shall not be deducted, in order to 

 comply with Item 1 above, for a control period that ends 

 prior to the allocation year for which the CO2 allowance 

 was allocated. A CO2 offset allowance shall not be 

 deducted, in order to comply with Item 1 above, beyond the

 applicable percent limitations set out in 6 NYCRR 

 242-6.5(a)(3).

 The owner or operator shall, on a calendar year basis, 

 submit to the DEC a certification stating whether he or 

 she has complied with this requirement.

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2011.

Subsequent reports are due every 12 calendar month(s).

Condition 54: Compliance Demonstration

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable State Requirement:6 NYCRR Subpart 242-4

Item 54.1:

The Compliance Demonstration activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 000124-38-9 CARBON DIOXIDE

Item 54.2:

Compliance Demonstration shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Annual Compliance Certification Report:

 (a) For each control period in which a CO2 budget source 

 is subject to the CO2 requirements of subdivision 

 242-1.5(c) of this Part, CO2 authorized account 

 representative of the source shall submit to the 

 department by March 1st following the relevant control 

 period, a compliance certification report.

 (b) The compliance certification report shall include the 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 59 FINAL

 following elements:

 (1) identification of the source and each CO2 budget 

 unit at the source;

 (2) as an option, the serial numbers of the CO2 

 allowances that are to be deducted from the source's 

 compliance account under section 242-6.5 of this Part for 

 the control period, including the serial numbers of any 

 CO2 offset allowances that are to be deducted subject to 

 the limitations of section 242-6.5(a)(3) of this Part; 

 and

 (3) the compliance certification under subdivision (c) 

 of this section (below).

 (c) In the compliance certification report the CO2 

 authorized account representative shall certify, based on 

 reasonable inquiry of those persons with primary 

 responsibility for operating the source and the CO2 budget

 units at the source in compliance with the CO2 Budget 

 Trading Program, whether the source and each CO2 budget 

 unit at the source for which the compliance certification 

 is submitted was operated during the calendar years 

 covered by the report in compliance with the requirements 

 of the CO2 Budget Trading Program, including:

 (1) whether the source was operated in compliance with 

 the CO2 requirements of section 242-1.5(c) of this Part;

 (2) whether the monitoring plan applicable to each unit

 at the source has been maintained to reflect the actual 

 operation and monitoring of the unit, and contains all 

 information necessary to attribute CO2 emissions to the 

 unit, in accordance with Subpart 242-8 of this Part;

 (3) whether all the CO2 emissions from the units at the

 source were monitored or accounted for through the missing

 data procedures and reported in the quarterly monitoring 

 reports, including whether conditional data were reported 

 in the quarterly reports in accordance with Subpart 242-8 

 of this Part. If conditional data were reported, the owner

 or operator shall indicate whether the status of all 

 conditional data has been resolved and all necessary 

 quarterly report resubmissions have been made;

 (4) whether the facts that form the basis for 

 certification under Subpart 242-8 of each monitor at each 

 unit at the source, or for using an excepted monitoring 

 method or alternative monitoring method approved under 

 Subpart 242-8 of this Part, if any, have changed; and

 (5) if a change is required to be reported under 

 paragraph (c)(4) above, specify the nature of the change, 

 the reason for the change, when the change occurred, and 

 how the unit's compliance status was determined subsequent

 to the change, including what method was used to determine

 emissions when a change mandated the need for monitor 

 recertification.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 60 FINAL

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: MARCH 1

Condition 55: Compliance Demonstration

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable State Requirement:6 NYCRR Subpart 242-8

Item 55.1:

The Compliance Demonstration activity will be performed for the Facility.

 Regulated Contaminant(s):

 CAS No: 000124-38-9 CARBON DIOXIDE

Item 55.2:

Compliance Demonstration shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 Recordkeeping and Reporting (6NYCRR Part 242-8.5)

 (a) General provisions. The CO2 authorized account 

 representative shall comply with all recordkeeping and 

 reporting requirements in this section, the applicable 

 record keeping and reporting requirements under 40 CFR 

 75.73 and with the requirements of section 242-2.1(e) of 

 this Part.

 (b) Monitoring plans. The owner or operator of a CO2 

 budget unit shall submit a monitoring plan in the manner 

 prescribed in 40 CFR 75.62.

 (c) Certification applications. The CO2 authorized account

 representative shall submit an application to the 

 department within 45 days after completing all CO2 

 monitoring system initial certification or recertification

 tests required under section 242-8.2 of this Subpart 

 including the information required under 40 CFR 75.63 and 

 40 CFR 75.53(e) and (f).

 (d) Quarterly reports. The CO2 authorized account 

 representative shall submit quarterly reports, as 

 follows:

 (1) The CO2 authorized account representative shall 

 report the CO2 mass emissions data and heat input data for

 the CO2 budget unit, in an electronic format prescribed by

 the administrator unless otherwise prescribed by the 

 department for each calendar quarter.

 (2) The CO2 authorized account representative shall 

 submit each quarterly report to the department or its 

 agent within 30 days following the end of the calendar 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 61 FINAL

 quarter covered by the report. Quarterly reports shall be 

 submitted in the manner specified in subpart H of 40 CFR 

 part 75 and 40 CFR 75.64. Quarterly reports shall be 

 submitted for each CO2 budget unit (or group of units 

 using a common stack), and shall include all of the data 

 and information required in subpart G of 40 CFR part 75, 

 except for opacity, NOx, and SO2 provisions.

 (3) The CO2 authorized account representative shall 

 submit to the department or its agent a compliance 

 certification in support of each quarterly report based on

 reasonable inquiry of those persons with primary 

 responsibility for ensuring that all of the unit's 

 emissions are correctly and fully monitored. The 

 certification shall state that:

 (i) the monitoring data submitted were recorded in 

 accordance with the applicable requirements of this 

 Subpart and 40 CFR part 75, including the quality 

 assurance procedures and specifications;

 (ii) for a unit with add-on CO2 emissions controls 

 and for all hours where data are substituted in accordance

 with 40 CFR 75.34(a)(1), the add-on emissions controls 

 were operating within the range of parameters listed in 

 the quality assurance/quality control program under 

 appendix B of 40 CFR part 75 and the substitute values do 

 not systematically underestimate CO2 emissions; and

 (iii) the CO2 concentration values substituted for 

 missing data under Subpart D of 40 CFR part 75 do not 

 systematically underestimate CO2 emissions.

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 4/30/2010.

Subsequent reports are due every 3 calendar month(s).

Condition 56: Compliance Demonstration

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable State Requirement:6 NYCRR Part 246

Item 56.1:

The Compliance Demonstration activity will be performed for the Facility.

Item 56.2:

Compliance Demonstration shall include the following monitoring:

Monitoring Type: RECORD KEEPING/MAINTENANCE PROCEDURES

Monitoring Description: 

 1. The owner or operator shall not cause or allow 

 emissions of mercury in excess of 21.0 pounds per 12 month

 period, rolled monthly, from January 1, 2010 to December 
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 62 FINAL

 31, 2014.

 2. Effective January 1, 2015, the owner or operator shall

 not cause or allow emissions of mercury in excess of 0.6 

 pounds per trillion Btu. Compliance with this emission 

 limit shall be determined on a 30 day rolling period, 

 rolled daily.

 3. The owner or operator shall comply with the 

 monitoring, record keeping and reporting requirements of 

 40 CFR Part 75, Subpart I and 6 NYCRR 246. 

 4. Mercury emissions shall be monitored pursuant to 40 

 CFR 75.81(b)-(e), provided annual emissions are less than 

 or equal to 464 ounces. The owner or operator shall 

 conduct either annual or semi-annual testing as described 

 in 40 CFR 75.81(d). If, at the end of any calendar year, 

 the cumulative annual mercury mass emissions exceed 464 

 ounces, the owner or operator shall install, certify, 

 operate and maintain a mercury concentration monitoring 

 system or a sorbent trap monitoring system no later than 

 180 days after the end of that calendar year. 

 5. Hourly emissions of mercury shall be computed 

 according to 40 CFR Part 75, Appendix F.

 6. Emission control equipment parametric data must be 

 recorded in accordance with 40 CFR 75.58(b)(3)(i).

 7. The owner or operator must submit quarterly reports in 

 a format prescribed by the DEC and the Administrator no 

 later than 30 days after the end of the quarter and in the

 manner specified in 40 CFR 75.84(f). In the quarterly 

 submission the owner or operator must certify that the 

 data were submitted in accordance with 6 NYCRR 246 and 40 

 CFR Part 75, that missing data were substituted in 

 accordance with 40 CFR 75.34(a)(1).

 8. No owner or operator shall use any alternative 

 monitoring system without written approval from the DEC; 

 allow the discharge of mercury emissions without 

 accounting for such emissions; disrupt the operation of a

 mercury continuous monitoring system (except for periods 

 of calibration, quality assurance testing, maintenance or 

 recertification; or discontinue the use of a monitoring 

 system unless another system has been approved by the DEC 

 or the EPA.

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Reporting Requirements: QUARTERLY (CALENDAR)

Reports due 30 days after the reporting period.
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 63 FINAL

The initial report is due 4/30/2010.

Subsequent reports are due every 3 calendar month(s).

 ** ** Emission Unit Level ****

Condition 57: Compliance Demonstration

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable State Requirement:6 NYCRR 617.11 (d)

Item 57.1:

The Compliance Demonstration activity will be performed for:

 Emission Unit: U-00BLR

Item 57.2:

Compliance Demonstration shall include the following monitoring:

Monitoring Type: WORK PRACTICE INVOLVING SPECIFIC 

 OPERATIONS

Monitoring Description: 

 Total coal fired at the facility shall not exceed 438,000

 tons/year on a calendar year basis.

Work Practice Type: PROCESS MATERIAL THRUPUT

Process Material: BITUMINOUS COAL

Upper Permit Limit: 438,000 tons per year

Monitoring Frequency: AS REQUIRED - SEE PERMIT MONITORING 

 DESCRIPTION

Averaging Method: CALENDAR YEAR AVERAGE

Reporting Requirements: ANNUALLY (CALENDAR)

Reports due 30 days after the reporting period.

The initial report is due 1/30/2011.

Subsequent reports are due every 12 calendar month(s).

Condition 58: Compliance Demonstration

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable State Requirement:6 NYCRR 617.11 (d)

Item 58.1:

The Compliance Demonstration activity will be performed for:

 Emission Unit: U-00BLR

Item 58.2:

Compliance Demonstration shall include the following monitoring:

Monitoring Type: MONITORING OF PROCESS OR CONTROL 

 DEVICE PARAMETERS AS SURROGATE
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 64 FINAL

Monitoring Description: 

 Total heat input to the facility shall not exceed 1,250 

 mmBtu/hour on a one hour block basis. Compliance shall be

 based upon monitoring of steam flow and applying the most 

 current measured boiler efficiency..

Parameter Monitored: HEAT INPUT

Upper Permit Limit: 1,250 million Btu per hour

Monitoring Frequency: CONTINUOUS

Averaging Method: 1-HOUR AVERAGE

Reporting Requirements: UPON REQUEST BY REGULATORY AGENCY

Condition 59: Compliance Demonstration

 Effective between the dates of 01/11/2010 and 05/23/2017

 Applicable State Requirement:6 NYCRR 617.11 (d)

Item 59.1:

The Compliance Demonstration activity will be performed for:

 Emission Unit: U-00BLR

 Regulated Contaminant(s):

 CAS No: 0NY075-00-0 PARTICULATES

Item 59.2:

Compliance Demonstration shall include the following monitoring:

Monitoring Type: INTERMITTENT EMISSION TESTING

Monitoring Description: 

 Particulate emissions shall not exceed 0.05 lb/mmBtu. 

 Compliance shall be demonstrated by stack testing 

 performed at least once during the term of the permit, and

 upon request by the Department.

Parameter Monitored: PARTICULATES

Upper Permit Limit: 0.05 pounds per million Btus

Reference Test Method: EPA RM 5

Monitoring Frequency: ONCE DURING THE TERM OF THE PERMIT

Averaging Method: AVERAGING METHOD AS PER REFERENCE TEST

 METHOD INDICATED

Reporting Requirements: UPON REQUEST BY REGULATORY AGENCY
 

Permit ID: 7-3132-00052/00020 Facility DEC ID: 7313200052

 Air Pollution Control Permit Conditions

Renewal 1/Mod 2/Active Page 65 FINAL