Name: Jeffrey A. Smith

Title: PGD Regional Plant General Manager

Company: Florida Power & Light

Sign Date: 6/10/2010

Name: Thomas K. Graham

Title: Director of Operations

Company: Air Hygiene International, Inc.

Sign Date: 6/2/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Port Everglades Energy Center, Unit #3, Information Collection Request

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, February 14, 2011 Page 1 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Facility Information:

Port Everglades Energy Center

8100 Eisenhower Blvd 

Fort Lauderdale FL 33316

Contact: Augie De La Vega

Phone: (305)-242-3896

Fax:

Email: augie.de.la.vega@fpl.com

Testing Company:

Air Hygiene International, Inc.

5634 S. 122nd East Ave, Suite F

Tulsa OK 74146

Contact:Thomas Graham

Phone: (918) 307-8865

Fax: (918) 307-9131

Email: tom@airhygiene.com

Air Permit Number:

0110036-009-AV

Permitted Source ID/Name:

PPE3 Foster Wheeler, Wall Fired Boiler

Permitted Maximum Process Rate:

400 MW

Max. Normal Operation Process Rate:

380 MW

Target Process Test Rate

375 MW

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Florida Power and Light Company (FPL) operates two oil fired electric utility steam generating units of Foster 

Wheeler design, designated as Units PPE3 and PPE4. The facility is located at 8100 Eisenhower Blvd in Fort 

Lauderdale, Florida. Unit PPE3 and PPE4 are of identical design and consists of two dry bottom, wall fired boilers 

and ancillary equipment designed to generate 400 megawatts (MW) of electricity each with rated heat inputs of 4,000 

million British thermal units per hour (MMBtu/hr) based on high heating value (HHV). Fuel oil consumption is rated 

at 230,000 pounds per hour. Unit PPE3 and PPE4 utilize low nitrogen oxide (NOx) burner technology to control 

NOx emissions and electrostatic precipitators (ESPs) to control particulate matter (PM) emissions. Emission testing 

will be conducted from platforms on the independent stacks of each unit.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110036 FRS #: 110000363847

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

PPE3 - D/F 251 0 0 0 2592 1016 4 24

PPE3 - Gases 251 0 0 0 2592 1016 4 1

PPE3 - Metals 251 0 0 0 2592 1016 4 24

PPE3 - PM 251 0 0 0 2592 1016 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Regulation Description Compound Limit Unit

Not applicable.

Monday, February 14, 2011 Page 2 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

PPE3 - D/F % H2O Method 1 - 4 3 480 24

PPE3 - D/F 2,3,7,8-TCDD Method 23 3 480 24

PPE3 - D/F 1,2,3,7,8-PeCDD Method 23 3 480 24

PPE3 - D/F 1,2,3,4,7,8-HxCDD Method 23 3 480 24

PPE3 - D/F 1,2,3,6,7,8-HxCDD Method 23 3 480 24

PPE3 - D/F 1,2,3,7,8,9-HxCDD Method 23 3 480 24

PPE3 - D/F 1,2,3,4,6,7,8-HpCDD Method 23 3 480 24

PPE3 - D/F OCDD Method 23 3 480 24

PPE3 - D/F 2,3,7,8-TCDF Method 23 3 480 24

PPE3 - D/F 1,2,3,7,8-PeCDF Method 23 3 480 24

PPE3 - D/F 2,3,4,7,8-PeCDF Method 23 3 480 24

PPE3 - D/F 1,2,3,4,7,8-HxCDF Method 23 3 480 24

PPE3 - D/F 1,2,3,6,7,8-HxCDF Method 23 3 480 24

PPE3 - D/F 2,3,4,6,7,8-HxCDF Method 23 3 480 24

PPE3 - D/F 1,2,3,7,8,9-HxCDF Method 23 3 480 24

PPE3 - D/F 1,2,3,4,6,7,8-HpCDF Method 23 3 480 24

PPE3 - D/F 1,2,3,4,7,8,9-HpCDF Method 23 3 480 24

PPE3 - D/F OCDF Method 23 3 480 24

PPE3 - D/F Total Dioxins Method 23 3 480 24

PPE3 - D/F Total Furans Method 23 3 480 24

PPE3 - D/F 3,3',4,4'-TCB (PCB77) Method 23 3 480 24

PPE3 - D/F 3,4,4',5-TCB (PCB81) Method 23 3 480 24

PPE3 - D/F 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 24

PPE3 - D/F 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 24

PPE3 - D/F 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 24

PPE3 - D/F 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 24

PPE3 - D/F 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 24

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

PPE3 - D/F Method 23 3 480 24

PPE3 - D/F 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 24

PPE3 - D/F 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 24

2,3,3',4,4',5,5'-HpCB 

(PCB189)

PPE3 - D/F Method 23 3 480 24

PPE3 - D/F O2 Method 3A O2 3 480 24

PPE3 - D/F Co2 Method 3A CO2 3 480 24

% H2O Method 1 - 4 3 120 1 Determined after 

initial stratification test

PPE3 - Gases

Carbon Monoxide Method 10 3 120 1 Determined after 

initial stratification test

PPE3 - Gases

Total organic compounds 

(TOC) as Propane

Method 25A 3 120 1 Determined after 

initial stratification test

PPE3 - Gases

O2 Method 3A O2 3 120 1 Determined after 

initial stratification test

PPE3 - Gases

Co2 Method 3A CO2 3 120 1 Determined after 

initial stratification test

PPE3 - Gases

Sulfur Dioxide Method 6C 3 120 1 Determined after 

initial stratification test

PPE3 - Gases

Nitrogen oxides (NOx) Method 7E 3 120 1 Determined after 

initial stratification test

PPE3 - Gases

PPE3 - Metals % H2O Method 1 - 4 3 240 24

PPE3 - Metals Selenium Method 29 3 240 24

PPE3 - Metals Manganese Method 29 3 240 24

Monday, February 14, 2011 Page 3 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

PM Run 2 - vaccuum maximized before end of run, did not pull required volume.
PM All - oily substance on all 

filters

PPE3 - Metals Lead Method 29 3 240 24

PPE3 - Metals Filterable Particulate Method 29 3 240 24

PPE3 - Metals Cobalt Method 29 3 240 24

PPE3 - Metals Cadmium Method 29 3 240 24

PPE3 - Metals Chromium Method 29 3 240 24

PPE3 - Metals Nickel Method 29 3 240 24

PPE3 - Metals Co2 Method 3A CO2 3 240 24

PPE3 - Metals O2 Method 3A O2 3 240 24

% H2O Method 1 - 4 3 120 12 Run times vary based 

on method calculations

PPE3 - PM

Filterable Particulate OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PPE3 - PM

Filterable PM2.5 OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PPE3 - PM

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PPE3 - PM

Organic Condensible 

Particulate

OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PPE3 - PM

Total PM2.5 OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PPE3 - PM

Total Particulate OTM - 27/28 3 120 12 Run times vary based 

on method calculations

PPE3 - PM

O2 Method 3A O2 3 120 12 Run times vary based 

on method calculations

PPE3 - PM

Co2 Method 3A CO2 3 120 12 Run times vary based 

on method calculations

PPE3 - PM

Monday, February 14, 2011 Page 4 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Sampling / Stack Data Results Summary

Location PPE3 - D/F - Method 23

Average

Run Number PPE3-23-1 PPE3-23-2 PPE3-23-3

Test Date 3/9/2010 3/10/2010 3/11/2010

Run Start Time 9:28:00 AM 8:40:00 

AM

12:14:00 PM

Run Finish Time 5:28:00 PM 4:40:00 PM 8:14:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 362.078 351.716 356.983 356.926

Moisture Content of Stack Gas, % 8.57 9.36 9.79 9.240

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.96 13.95 13.88 13.930

Oxygen, % 4.1 4.18 4.21 4.163

Average Stack Gas Temperature, °F 322.21 324.25 324.13 323.530

Dry Volumetric Flow Rate, dry scfm 766,594.2 758,219.3 757,350.0 760,721.167

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,246,711.2 1,249,597.6 1,261,555.5 1,252,621.43

3

Percent Isokinetic of Sampling Rate, % 99.2 97.4 99.0 98.533

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location PPE3 - Gases - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, February 14, 2011 Page 5 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location PPE3 - Gases - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location PPE3 - Gases - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, February 14, 2011 Page 6 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location PPE3 - Gases - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location PPE3 - Gases - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Monday, February 14, 2011 Page 7 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location PPE3 - Gases - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location PPE3 - Metals - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Monday, February 14, 2011 Page 8 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location PPE3 - PM - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Monday, February 14, 2011 Page 9 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Emissions Summary

Location: PPE3 - D/F - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000054 0.00000000794 0.00000000971 0.000

lb/mmBtuO2 3.76E-13 5.72E-13 6.90E-13 0.000

ng/dscm 5.27E-04 7.97E-04 9.61E-04 0.001

ng/dscm@7%O2 4.36E-04 6.63E-04 8.00E-04 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000016 0.0000000063 0.0000000057 0.000

lb/mmBtuO2 1.11E-13 4.54E-13 4.05E-13 0.000

ng/dscm 1.56E-04 6.33E-04 5.64E-04 0.000

ng/dscm@7%O2 1.29E-04 5.26E-04 4.70E-04 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.000000002 0.0000000044 0.0000000027 0.000

lb/mmBtuO2 1.39E-13 3.17E-13 1.92E-13 0.000

ng/dscm 1.95E-04 4.42E-04 2.67E-04 0.000

ng/dscm@7%O2 1.61E-04 3.67E-04 2.22E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000018 0.0000000016 0.0000000023 0.000

lb/mmBtuO2 1.25E-13 1.15E-13 1.63E-13 0.000

ng/dscm 1.76E-04 1.61E-04 2.28E-04 0.000

ng/dscm@7%O2 1.46E-04 1.34E-04 1.90E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.00000000086 0.0000000019 0.0000000018 0.000

lb/mmBtuO2 5.99E-14 1.37E-13 1.28E-13 0.000

ng/dscm 8.39E-05 1.91E-04 1.78E-04 0.000

ng/dscm@7%O2 6.94E-05 1.59E-04 1.48E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000018 0.0000000016 0.0000000023 0.000

lb/mmBtuO2 1.25E-13 1.15E-13 1.63E-13 0.000

ng/dscm 1.76E-04 1.61E-04 2.28E-04 0.000

ng/dscm@7%O2 1.46E-04 1.34E-04 1.90E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

Monday, February 14, 2011 Page 10 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000008 0.0000000018 0.0000000017 0.000

lb/mmBtuO2 5.57E-14 1.30E-13 1.21E-13 0.000

ng/dscm 7.80E-05 1.81E-04 1.68E-04 0.000

ng/dscm@7%O2 6.45E-05 1.50E-04 1.40E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000018 0.0000000019 0.0000000023 0.000

lb/mmBtuO2 1.25E-13 1.37E-13 1.63E-13 0.000

ng/dscm 1.76E-04 1.91E-04 2.28E-04 0.000

ng/dscm@7%O2 1.46E-04 1.59E-04 1.90E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000016 0.000000001 0.0000000019 0.000

lb/mmBtuO2 1.11E-13 7.20E-14 1.35E-13 0.000

ng/dscm 1.56E-04 1.00E-04 1.88E-04 0.000

ng/dscm@7%O2 1.29E-04 8.31E-05 1.57E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000021 0.0000000013 0.0000000015 0.000

lb/mmBtuO2 1.46E-13 9.36E-14 1.07E-13 0.000

ng/dscm 2.05E-04 1.31E-04 1.48E-04 0.000

ng/dscm@7%O2 1.70E-04 1.09E-04 1.23E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000015 0.0000000015 0.000000002 0.000

lb/mmBtuO2 1.04E-13 1.08E-13 1.42E-13 0.000

ng/dscm 1.46E-04 1.51E-04 1.98E-04 0.000

ng/dscm@7%O2 1.21E-04 1.26E-04 1.65E-04 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000043 0.0000000028 0.0000000029 0.000

lb/mmBtuO2 2.99E-13 2.02E-13 2.06E-13 0.000

ng/dscm 4.19E-04 2.81E-04 2.87E-04 0.000

ng/dscm@7%O2 3.47E-04 2.34E-04 2.39E-04 0.000

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000137 0.0000000103 0.000000011 0.000

lb/mmBtuO2 9.54E-13 7.42E-13 7.82E-13 0.000

ng/dscm 1.34E-03 1.03E-03 1.09E-03 0.001

ng/dscm@7%O2 1.11E-03 8.56E-04 9.08E-04 0.001

Monday, February 14, 2011 Page 11 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000004 0.000000411 0.000000406 0.000

lb/mmBtuO2 2.78E-11 2.96E-11 2.89E-11 0.000

ng/dscm 3.90E-02 4.13E-02 4.02E-02 0.040

ng/dscm@7%O2 3.23E-02 3.43E-02 3.35E-02 0.033

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.000000027 0.000000016 0.00000003 0.000

lb/mmBtuO2 1.88E-12 1.15E-12 2.13E-12 0.000

ng/dscm 2.63E-03 1.61E-03 2.97E-03 0.002

ng/dscm@7%O2 2.18E-03 1.34E-03 2.47E-03 0.002

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000302 0.0000000438 0.0000000446 0.000

lb/mmBtuO2 2.10E-12 3.15E-12 3.17E-12 0.000

ng/dscm 2.95E-03 4.40E-03 4.41E-03 0.004

ng/dscm@7%O2 2.44E-03 3.66E-03 3.67E-03 0.003

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.00000104 0.00000104 0.00000107 0.000

lb/mmBtuO2 7.24E-11 7.49E-11 7.60E-11 0.000

ng/dscm 1.01E-01 1.04E-01 1.06E-01 0.104

ng/dscm@7%O2 8.36E-02 8.65E-02 8.83E-02 0.086

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000239 0.0000000229 0.000000017 0.000

lb/mmBtuO2 1.66E-12 1.65E-12 1.21E-12 0.000

ng/dscm 2.33E-03 2.30E-03 1.68E-03 0.002

ng/dscm@7%O2 1.93E-03 1.91E-03 1.40E-03 0.002

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000021 0.0000000033 0.0000000017 0.000

lb/mmBtuO2 1.46E-13 2.38E-13 1.21E-13 0.000

ng/dscm 2.05E-04 3.31E-04 1.68E-04 0.000

ng/dscm@7%O2 1.70E-04 2.75E-04 1.40E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000014 0.0000000022 0.0000000019 0.000

lb/mmBtuO2 9.75E-14 1.58E-13 1.35E-13 0.000

Monday, February 14, 2011 Page 12 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

ng/dscm 1.37E-04 2.21E-04 1.88E-04 0.000

ng/dscm@7%O2 1.13E-04 1.84E-04 1.57E-04 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000028 0.0000000021 0.0000000021 0.000

lb/mmBtuO2 1.95E-13 1.51E-13 1.49E-13 0.000

ng/dscm 2.73E-04 2.11E-04 2.08E-04 0.000

ng/dscm@7%O2 2.26E-04 1.75E-04 1.73E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000019 0.000000002 0.000000003 0.000

lb/mmBtuO2 1.32E-13 1.44E-13 2.13E-13 0.000

ng/dscm 1.85E-04 2.01E-04 2.97E-04 0.000

ng/dscm@7%O2 1.53E-04 1.67E-04 2.47E-04 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.00000000088 0.00000000058 0.00000000071 0.000

lb/mmBtuO2 6.13E-14 4.18E-14 5.05E-14 0.000

ng/dscm 8.58E-05 5.82E-05 7.02E-05 0.000

ng/dscm@7%O2 7.10E-05 4.84E-05 5.85E-05 0.000

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000026 0.0000000031 0.0000000035 0.000

lb/mmBtuO2 1.81E-13 2.23E-13 2.49E-13 0.000

ng/dscm 2.54E-04 3.11E-04 3.46E-04 0.000

ng/dscm@7%O2 2.10E-04 2.59E-04 2.88E-04 0.000

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.000000234 0.000000279 0.000000264 0.000

lb/mmBtuO2 1.63E-11 2.01E-11 1.88E-11 0.000

ng/dscm 2.28E-02 2.80E-02 2.61E-02 0.026

ng/dscm@7%O2 1.89E-02 2.33E-02 2.17E-02 0.021

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000118 0.0000000151 0.0000000142 0.000

lb/mmBtuO2 8.21E-13 1.09E-12 1.01E-12 0.000

ng/dscm 1.15E-03 1.52E-03 1.40E-03 0.001

ng/dscm@7%O2 9.51E-04 1.26E-03 1.17E-03 0.001

Compound: OCDD

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Monday, February 14, 2011 Page 13 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Mass_mg 0.0000000055 0.0000000239 0.000000018 0.000

lb/mmBtuO2 3.83E-13 1.72E-12 1.28E-12 0.000

ng/dscm 5.37E-04 2.40E-03 1.78E-03 0.002

ng/dscm@7%O2 4.44E-04 2.00E-03 1.48E-03 0.001

Compound: OCDF

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000034 0.0000000295 0.0000000065 0.000

lb/mmBtuO2 2.37E-13 2.12E-12 4.62E-13 0.000

ng/dscm 3.32E-04 2.96E-03 6.43E-04 0.001

ng/dscm@7%O2 2.75E-04 2.46E-03 5.36E-04 0.001

Compound: Total Dioxins

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.0000000212 0.00000004034 0.00000003821 0.000

lb/mmBtuO2 1.48E-12 2.90E-12 2.72E-12 0.000

ng/dscm 2.07E-03 4.05E-03 3.78E-03 0.003

ng/dscm@7%O2 1.71E-03 3.37E-03 3.15E-03 0.003

Compound: Total Furans

Average

RunNumber PPE3-23-1 PPE3-23-2 PPE3-23-3

Mass_mg 0.00000001716 0.0000000539 0.0000000289 0.000

lb/mmBtuO2 1.19E-12 3.88E-12 2.05E-12 0.000

ng/dscm 1.67E-03 5.41E-03 2.86E-03 0.003

ng/dscm@7%O2 1.38E-03 4.50E-03 2.38E-03 0.003

Location: PPE3 - Gases - Method 10

Compound: Carbon Monoxide

Average

Run 3-CO-1 3-CO-2 3-CO-3

lb/mmBtuO2 3.53E-03 7.56E-03 6.84E-03 0.006

ppm 4.27E+00 9.08E+00 8.20E+00 7.183

ppm@7%O2 3.52E+00 7.52E+00 6.81E+00 5.950

Location: PPE3 - Gases - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 3-THC-1 3-THC-2 3-THC-3

lb/mmBtuO2 8.40E-05 1.28E-04 3.99E-05 0.000

ppm 6.45E-02 9.79E-02 3.04E-02 0.064

ppm@7%O2 5.31E-02 8.11E-02 2.52E-02 0.053

Location: PPE3 - Gases - Method 6C

Compound: Sulfur Dioxide

Average

Run 3-SO2-1 3-SO2-2 3-SO2-3

lb/mmBtuO2 1.05E+00 1.03E+00 1.04E+00 1.040

ppm 5.53E+02 5.40E+02 5.47E+02 546.667

ppm@7%O2 4.55E+02 4.47E+02 4.54E+02 452.000

Monday, February 14, 2011 Page 14 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location: PPE3 - Gases - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 3-NOx-1 3-NOx-2 3-NOx-3

lb/mmBtuO2 6.39E-01 6.45E-01 6.53E-01 0.646

ppm 4.70E+02 4.72E+02 4.77E+02 473.000

ppm@7%O2 3.87E+02 3.91E+02 3.96E+02 391.333

Location: PPE3 - Metals - Method 29

Compound: Antimony

Average

RunNumber PPE3-29-1 PPE3-29-2 PPE3-29-3

Mass_mg 0.00311 0.00169 0.00228 0.002

Elb/hr 1.72E-03 9.28E-04 1.26E-03 0.001

lb/mmBtuO2 4.40E-07 2.39E-07 3.27E-07 0.000

mg/dscm 6.17E-04 3.33E-04 4.55E-04 0.000

mg/dscm@7%O2 5.10E-04 2.77E-04 3.79E-04 0.000

Compound: Arsenic

Average

RunNumber PPE3-29-1 PPE3-29-2 PPE3-29-3

Mass_mg 0.00116 0.00115 0.00115 0.001

Elb/hr 6.42E-04 6.31E-04 6.33E-04 0.001

lb/mmBtuO2 1.64E-07 1.63E-07 1.65E-07 0.000

mg/dscm 2.30E-04 2.27E-04 2.29E-04 0.000

mg/dscm@7%O2 1.90E-04 1.89E-04 1.91E-04 0.000

Compound: Beryllium

Average

RunNumber PPE3-29-1 PPE3-29-2 PPE3-29-3

Mass_mg 0.0002 0.0002 0.0002 0.000

Elb/hr 1.11E-04 1.10E-04 1.10E-04 0.000

lb/mmBtuO2 2.83E-08 2.83E-08 2.86E-08 0.000

mg/dscm 3.97E-05 3.95E-05 3.99E-05 0.000

mg/dscm@7%O2 3.28E-05 3.28E-05 3.32E-05 0.000

Compound: Cadmium

Average

RunNumber PPE3-29-1 PPE3-29-2 PPE3-29-3

Mass_mg 0.0001 0.0001 0.0001 0.000

Elb/hr 5.54E-05 5.49E-05 5.51E-05 0.000

lb/mmBtuO2 1.41E-08 1.41E-08 1.43E-08 0.000

mg/dscm 1.98E-05 1.97E-05 1.99E-05 0.000

mg/dscm@7%O2 1.64E-05 1.64E-05 1.66E-05 0.000

Compound: Chromium

Average

RunNumber PPE3-29-1 PPE3-29-2 PPE3-29-3

Mass_mg 0.00621 0.00791 0.00425 0.006

Elb/hr 3.44E-03 4.34E-03 2.34E-03 0.003

lb/mmBtuO2 8.79E-07 1.12E-06 6.09E-07 0.000

mg/dscm 1.23E-03 1.56E-03 8.47E-04 0.001

Monday, February 14, 2011 Page 15 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

mg/dscm@7%O2 1.02E-03 1.30E-03 7.05E-04 0.001

Compound: Cobalt

Average

RunNumber PPE3-29-1 PPE3-29-2 PPE3-29-3

Mass_mg 0.00109 0.00488 0.00122 0.002

Elb/hr 6.04E-04 2.68E-03 6.72E-04 0.001

lb/mmBtuO2 1.54E-07 6.90E-07 1.75E-07 0.000

mg/dscm 2.16E-04 9.63E-04 2.43E-04 0.000

mg/dscm@7%O2 1.79E-04 8.01E-04 2.02E-04 0.000

Compound: Filterable Particulate

Average

RunNumber PPE3-29-1 PPE3-29-2 PPE3-29-3

Mass_mg 10.6 7.1 8.1 8.600

Elb/hr 5.87E+00 3.90E+00 4.46E+00 4.743

lb/mmBtuO2 1.50E-03 1.00E-03 1.16E-03 0.001

mg/dscm 2.10E+00 1.40E+00 1.61E+00 1.703

mg/dscm@7%O2 1.74E+00 1.16E+00 1.34E+00 1.413

Compound: Lead

Average

RunNumber PPE3-29-1 PPE3-29-2 PPE3-29-3

Mass_mg 0.00232 0.00169 0.000973 0.002

Elb/hr 1.28E-03 9.28E-04 5.36E-04 0.001

lb/mmBtuO2 3.28E-07 2.39E-07 1.39E-07 0.000

mg/dscm 4.60E-04 3.33E-04 1.94E-04 0.000

mg/dscm@7%O2 3.81E-04 2.77E-04 1.62E-04 0.000

Compound: Manganese

Average

RunNumber PPE3-29-1 PPE3-29-2 PPE3-29-3

Mass_mg 0.00523 0.00635 0.00602 0.006

Elb/hr 2.90E-03 3.49E-03 3.31E-03 0.003

lb/mmBtuO2 7.40E-07 8.98E-07 8.62E-07 0.000

mg/dscm 1.04E-03 1.25E-03 1.20E-03 0.001

mg/dscm@7%O2 8.60E-04 1.04E-03 9.99E-04 0.001

Compound: Nickel

Average

RunNumber PPE3-29-1 PPE3-29-2 PPE3-29-3

Mass_mg 0.0303 0.0334 0.0389 0.034

Elb/hr 1.68E-02 1.83E-02 2.14E-02 0.019

lb/mmBtuO2 4.29E-06 4.72E-06 5.57E-06 0.000

mg/dscm 6.01E-03 6.59E-03 7.76E-03 0.007

mg/dscm@7%O2 4.97E-03 5.48E-03 6.46E-03 0.006

Compound: Selenium

Average

RunNumber PPE3-29-1 PPE3-29-2 PPE3-29-3

Mass_mg 0.023 0.0231 0.0225 0.023

Elb/hr 1.27E-02 1.27E-02 1.24E-02 0.013

lb/mmBtuO2 3.25E-06 3.27E-06 3.22E-06 0.000

mg/dscm 4.56E-03 4.56E-03 4.49E-03 0.005

Monday, February 14, 2011 Page 16 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Process Run Data

mg/dscm@7%O2 3.77E-03 3.79E-03 3.74E-03 0.004

Location: PPE3 - PM - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber PPE3-27/28-1 PPE3-27/28-2 PPE3-27/28-3

Mass_mg 17.55 15.925 14.375 15.950

lb/mmBtuO2 3.29E-03 3.73E-03 2.88E-03 0.003

Compound: Filterable PM2.5

Average

RunNumber PPE3-27/28-1 PPE3-27/28-2 PPE3-27/28-3

Mass_mg 13.375 13.05 11.9 12.775

lb/mmBtuO2 2.51E-03 3.06E-03 2.38E-03 0.003

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber PPE3-27/28-1 PPE3-27/28-2 PPE3-27/28-3

Mass_mg 5.023 15.571 4.259 8.284

lb/mmBtuO2 9.42E-04 3.65E-03 8.52E-04 0.002

Compound: Organic Condensible Particulate

Average

RunNumber PPE3-27/28-1 PPE3-27/28-2 PPE3-27/28-3

Mass_mg 12.237 21.8 2.112 12.050

lb/mmBtuO2 2.30E-03 5.11E-03 4.22E-04 0.003

Compound: Total Particulate

Average

RunNumber PPE3-27/28-1 PPE3-27/28-2 PPE3-27/28-3

Mass_mg 34.81 53.296 20.747 36.284

lb/mmBtuO2 6.53E-03 1.25E-02 4.15E-03 0.008

Compound: Total PM2.5

Average

RunNumber PPE3-27/28-1 PPE3-27/28-2 PPE3-27/28-3

Mass_mg 30.635 50.421 18.272 33.109

lb/mmBtuO2 5.75E-03 1.18E-02 3.65E-03 0.007

Monday, February 14, 2011 Page 17 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Residual Oil (No. 6) Burned 27485 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/9/2010; 

Start - 08:49; 

End - 10:48

0

10 Residual Oil (No. 6) Burned 27321 gal/hr Method 027/028; 

Run PM-1; Date - 

3/9/2010; Start - 

08:51; End - 14:44

0

11 Residual Oil (No. 6) Burned 26955 gal/hr Method 027/028; 

Run PM-2; Date - 

3/10/2010; Start - 

10:45; End - 15:57

0

12 Residual Oil (No. 6) Burned 26999 gal/hr Method 027/028; 

Run PM-3; Date - 

3/11/2010; Start - 

08:46; End - 14:12

0

2 Residual Oil (No. 6) Burned 27251 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/9/2010; 

Start - 11:38; 

End - 13:37

0

3 Residual Oil (No. 6) Burned 27251 gal/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/9/2010; 

Start - 14:03; 

End - 16:02

0

4 Residual Oil (No. 6) Burned 27262 gal/hr Method 23; Run 

D/F-1; Date - 

3/9/2010; Start - 

09:28; End - 17:19

0

5 Residual Oil (No. 6) Burned 26955 gal/hr Method 23; Run 

D/F-2; Date - 

3/10/2010; Start - 

08:40; End - 16:07

0

6 Residual Oil (No. 6) Burned 26984 gal/hr Method 23; Run 

D/F-3; Date - 

3/11/2010; Start - 

12:14; End - 20:40

0

7 Residual Oil (No. 6) Burned 27247 gal/hr Method 29; Run 

M-1; Date - 

3/9/2010; Start - 

16:44; End - 20:18

0

Monday, February 14, 2011 Page 18 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

8 Residual Oil (No. 6) Burned 26940 gal/hr Method 29; Run 

M-2; Date - 

3/10/2010; Start - 

17:29; End - 21:45

0

9 Residual Oil (No. 6) Burned 27042 gal/hr Method 29; Run 

M-3; Date - 

3/11/2010; Start - 

15:37; End - 20:18

0

1 Average Heat Input 3486 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/9/2010; 

Start - 08:49; 

End - 10:48

0

10 Average Heat Input 3467 MMBtu/hr Method 027/028; 

Run PM-1; Date - 

3/9/2010; Start - 

08:51; End - 14:44

0

11 Average Heat Input 3420 MMBtu/hr Method 027/028; 

Run PM-2; Date - 

3/10/2010; Start - 

10:45; End - 15:57

0

12 Average Heat Input 3425 MMBtu/hr Method 027/028; 

Run PM-3; Date - 

3/11/2010; Start - 

08:46; End - 14:12

0

2 Average Heat Input 3458 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/9/2010; 

Start - 11:38; 

End - 13:37

0

3 Average Heat Input 3457 MMBtu/hr Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/9/2010; 

Start - 14:03; 

End - 16:02

0

4 Average Heat Input 3459 MMBtu/hr Method 23; Run 

D/F-1; Date - 

3/9/2010; Start - 

09:28; End - 17:19

0

5 Average Heat Input 3420 MMBtu/hr Method 23; Run 

D/F-2; Date - 

3/10/2010; Start - 

08:40; End - 16:07

0

6 Average Heat Input 3424 MMBtu/hr Method 23; Run 

D/F-3; Date - 

3/11/2010; Start - 

12:14; End - 20:40

0

Monday, February 14, 2011 Page 19 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

7 Average Heat Input 3457 MMBtu/hr Method 29; Run 

M-1; Date - 

3/9/2010; Start - 

16:44; End - 20:18

0

8 Average Heat Input 3418 MMBtu/hr Method 29; Run 

M-2; Date - 

3/10/2010; Start - 

17:29; End - 21:45

0

9 Average Heat Input 3431 MMBtu/hr Method 29; Run 

M-3; Date - 

3/11/2010; Start - 

15:37; End - 20:18

0

1 Steam Output 2676 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/9/2010; 

Start - 08:49; 

End - 10:48

0

10 Steam Output 2661 1000 lb Method 027/028; 

Run PM-1; Date - 

3/9/2010; Start - 

08:51; End - 14:44

0

11 Steam Output 2650 1000 lb Method 027/028; 

Run PM-2; Date - 

3/10/2010; Start - 

10:45; End - 15:57

0

12 Steam Output 2663 1000 lb Method 027/028; 

Run PM-3; Date - 

3/11/2010; Start - 

08:46; End - 14:12

0

2 Steam Output 2654 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/9/2010; 

Start - 11:38; 

End - 13:37

0

3 Steam Output 2653 1000 lb Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/9/2010; 

Start - 14:03; 

End - 16:02

0

4 Steam Output 2655 1000 lb Method 23; Run 

D/F-1; Date - 

3/9/2010; Start - 

09:28; End - 17:19

0

5 Steam Output 2651 1000 lb Method 23; Run 

D/F-2; Date - 

3/10/2010; Start - 

08:40; End - 16:07

0

Monday, February 14, 2011 Page 20 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

6 Steam Output 2662 1000 lb Method 23; Run 

D/F-3; Date - 

3/11/2010; Start - 

12:14; End - 20:40

0

7 Steam Output 2648 1000 lb Method 29; Run 

M-1; Date - 

3/9/2010; Start - 

16:44; End - 20:18

0

8 Steam Output 2645 1000 lb Method 29; Run 

M-2; Date - 

3/10/2010; Start - 

17:29; End - 21:45

0

9 Steam Output 2667 1000 lb Method 29; Run 

M-3; Date - 

3/11/2010; Start - 

15:37; End - 20:18

0

1 Unit Gross Electrical Output 376 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/9/2010; 

Start - 08:49; 

End - 10:48

0

10 Unit Gross Electrical Output 375 MWg Method 027/028; 

Run PM-1; Date - 

3/9/2010; Start - 

08:51; End - 14:44

0

11 Unit Gross Electrical Output 375 MWg Method 027/028; 

Run PM-2; Date - 

3/10/2010; Start - 

10:45; End - 15:57

0

12 Unit Gross Electrical Output 376 MWg Method 027/028; 

Run PM-3; Date - 

3/11/2010; Start - 

08:46; End - 14:12

0

2 Unit Gross Electrical Output 375 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/9/2010; 

Start - 11:38; 

End - 13:37

0

3 Unit Gross Electrical Output 375 MWg Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/9/2010; 

Start - 14:03; 

End - 16:02

0

4 Unit Gross Electrical Output 375 MWg Method 23; Run 

D/F-1; Date - 

3/9/2010; Start - 

09:28; End - 17:19

0

Monday, February 14, 2011 Page 21 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

5 Unit Gross Electrical Output 375 MWg Method 23; Run 

D/F-2; Date - 

3/10/2010; Start - 

08:40; End - 16:07

0

6 Unit Gross Electrical Output 376 MWg Method 23; Run 

D/F-3; Date - 

3/11/2010; Start - 

12:14; End - 20:40

0

7 Unit Gross Electrical Output 375 MWg Method 29; Run 

M-1; Date - 

3/9/2010; Start - 

16:44; End - 20:18

0

8 Unit Gross Electrical Output 375 MWg Method 29; Run 

M-2; Date - 

3/10/2010; Start - 

17:29; End - 21:45

0

9 Unit Gross Electrical Output 377 MWg Method 29; Run 

M-3; Date - 

3/11/2010; Start - 

15:37; End - 20:18

0

1 Unit Net Electric Generation 365 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-1 and FTIR-1; 

Date - 3/9/2010; 

Start - 08:49; 

End - 10:48

0

10 Unit Net Electric Generation 365 MWn Method 027/028; 

Run PM-1; Date - 

3/9/2010; Start - 

08:51; End - 14:44

0

11 Unit Net Electric Generation 364 MWn Method 027/028; 

Run PM-2; Date - 

3/10/2010; Start - 

10:45; End - 15:57

0

12 Unit Net Electric Generation 365 MWn Method 027/028; 

Run PM-3; Date - 

3/11/2010; Start - 

08:46; End - 14:12

0

2 Unit Net Electric Generation 364 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-2 and FTIR-2; 

Date - 3/9/2010; 

Start - 11:38; 

End - 13:37

0

3 Unit Net Electric Generation 364 MWn Methods 6c, 7e, 

10, and 25a; Run 

RM-3 and FTIR-3; 

Date - 3/9/2010; 

Start - 14:03; 

End - 16:02

0

Monday, February 14, 2011 Page 22 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

APCD Run Data

Process Lab Run Data

4 Unit Net Electric Generation 364 MWn Method 23; Run 

D/F-1; Date - 

3/9/2010; Start - 

09:28; End - 17:19

0

5 Unit Net Electric Generation 364 MWn Method 23; Run 

D/F-2; Date - 

3/10/2010; Start - 

08:40; End - 16:07

0

6 Unit Net Electric Generation 365 MWn Method 23; Run 

D/F-3; Date - 

3/11/2010; Start - 

12:14; End - 20:40

0

7 Unit Net Electric Generation 364 MWn Method 29; Run 

M-1; Date - 

3/9/2010; Start - 

16:44; End - 20:18

0

8 Unit Net Electric Generation 364 MWn Method 29; Run 

M-2; Date - 

3/10/2010; Start - 

17:29; End - 21:45

0

9 Unit Net Electric Generation 366 MWn Method 29; Run 

M-3; Date - 

3/11/2010; Start - 

15:37; End - 20:18

0

Run Name Value UOM Comments

Target

Value

1 LOW NOX BURNERS 454 NOx Emissions 0

2 LOW NOX BURNERS 453 NOx Emissions 0

3 LOW NOX BURNERS 449 NOx Emissions 0

1 ELECTROSTATIC PRECIPITATORS 1.6 Opacity 0

2 ELECTROSTATIC PRECIPITATORS 1.5 Opacity 0

3 ELECTROSTATIC PRECIPITATORS 1.6 Opacity 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 18000 Btu/lb

1 Fuel Moisture 1.5 %

1 Fuel Mercury Content 0.002 mg/kg

1 Fuel Chlorine Content 244 mg/kg

1 Fuel Fluorine Content 76 mg/kg

1 Fuel Antimony Content 1.4 mg/kg

1 Fuel Arsenic Content 0.075 mg/kg

1 Fuel Beryllium Content 0.006 mg/kg

Monday, February 14, 2011 Page 23 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

1 Fuel Cadmium Content 0.008 mg/kg

1 Fuel Chromium Content 0.14 mg/kg

1 Fuel Cobalt Content 0.58 mg/kg

1 Fuel Lead Content 0.21 mg/kg

1 Fuel Manganese Content 1.2 mg/kg

1 Fuel Nickel Content 21 mg/kg

1 Fuel Selenium Content 0.017 mg/kg

1 Fuel Sulfur Content 9630 mg/kg

1 Fuel Proximate Analysis (Carbon) 87.67 %

1 Fuel Proximate Analysis (Hydrogen) 9.73 %

1 Fuel Proximate Analysis (Nitrogen) 0.5 %

1 Fuel Proximate Analysis (Oxygen) 0.58 %

1 Fuel Proximate Analysis (Sulfur) 1.06 %

2 Fuel Higher Heating Value 18100 Btu/lb

2 Fuel Moisture 1.35 %

2 Fuel Mercury Content 0.002 mg/kg

2 Fuel Chlorine Content 110 mg/kg

2 Fuel Fluorine Content 75 mg/kg

2 Fuel Antimony Content 1.4 mg/kg

2 Fuel Arsenic Content 0.09 mg/kg

2 Fuel Beryllium Content 0.008 mg/kg

2 Fuel Cadmium Content 0.008 mg/kg

2 Fuel Chromium Content 0.15 mg/kg

2 Fuel Cobalt Content 0.58 mg/kg

2 Fuel Lead Content 0.21 mg/kg

2 Fuel Manganese Content 1.2 mg/kg

2 Fuel Nickel Content 21.1 mg/kg

2 Fuel Selenium Content 0.022 mg/kg

2 Fuel Sulfur Content 9290 mg/kg

2 Fuel Proximate Analysis (Carbon) 88.15 %

2 Fuel Proximate Analysis (Hydrogen) 9.9 %

2 Fuel Proximate Analysis (Nitrogen) 0.5 %

2 Fuel Proximate Analysis (Oxygen) 0.5 %

2 Fuel Proximate Analysis (Sulfur) 1.07 %

3 Fuel Higher Heating Value 18200 Btu/lb

3 Fuel Moisture 0.98 %

3 Fuel Mercury Content 0.002 mg/kg

3 Fuel Chlorine Content 133 mg/kg

3 Fuel Fluorine Content 78 mg/kg

3 Fuel Antimony Content 1.4 mg/kg

3 Fuel Arsenic Content 0.078 mg/kg

3 Fuel Beryllium Content 0.008 mg/kg

3 Fuel Cadmium Content 0.007 mg/kg

Monday, February 14, 2011 Page 24 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

3 Fuel Chromium Content 0.14 mg/kg

3 Fuel Cobalt Content 0.57 mg/kg

3 Fuel Lead Content 0.21 mg/kg

3 Fuel Manganese Content 1.2 mg/kg

3 Fuel Nickel Content 20.7 mg/kg

3 Fuel Selenium Content 0.022 mg/kg

3 Fuel Sulfur Content 9610 mg/kg

3 Fuel Proximate Analysis (Carbon) 87.25 %

3 Fuel Proximate Analysis (Hydrogen) 9.99 %

3 Fuel Proximate Analysis (Nitrogen) 0.5 %

3 Fuel Proximate Analysis (Oxygen) 0.67 %

3 Fuel Proximate Analysis (Sulfur) 1.06 %

Monday, February 14, 2011 Page 25 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Sampling / Stack Data Results Detail

Location PPE3 - D/F - Method 23

Average

Run Number PPE3-23-1 PPE3-23-2 PPE3-23-3

Test Date 3/9/2010 3/10/2010 3/11/2010

Run Start Time 9:28:00 AM 8:40:00 AM 12:14:00 PM

Run Finish Time 5:28:00 PM 4:40:00 PM 8:14:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.25 0.25 0.25 0.250

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.979 0.979 0.979 0.979

Barometric Pressure, inches of Mercury 29.74 29.68 29.5 29.640

Average Orifice Meter Differential, inches H2O 1.92 1.87 1.90 1.897

Dry Gas Meter Volume Sampled, cubic feet 377.220 365.800 373.610 372.210

Average Dry Gas Meter Temperature, °F 77.83 75.77 75.92 76.507

Dry Gas Meter Volume Sampled, dscf 362.078 351.716 356.983 356.926

Total Moisture Liquid collected, g 720.7 771.8 823.1 771.867

Volume of Water Vapor, standard cubic feet 33.92 36.33 38.74 36.330

Moisture Content of Stack Gas, % 8.57 9.36 9.79 9.240

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9143 0.9064 0.9021 0.908

Carbon Dioxide, % 13.96 13.95 13.88 13.930

Oxygen, % 4.1 4.18 4.21 4.163

Carbon Monoxide & Nitrogen, % 81.94 81.87 81.91 81.907

Fuel Factor 1.20 1.20 1.20

Dry Molecular Weight, lb/lb-Mole 30.40 30.40 30.39 30.397

Wet Molecular weight, lb/lb-Mole 29.34 29.24 29.18 29.253

Flue Gas Static Pressure, inches of H2O 1 1 1 1.000

Absolute Flue Gas Pressure, inches of Mercury 29.81 29.75 29.57 29.710

Average Stack Gas Temperature, °F 322.21 324.25 324.13 323.530

Average Velocity Head, inches of H2O 0.7928921801

24829

0.790137554

06079

0.798927431

392487

0.794

Average Stack Gas Velocity, feet/second 60.47 60.61 61.19 60.757

Stack Cross-Sectional Area, square feet 343.617 343.617 343.617 343.617

Dry Volumetric Flow Rate, dry scfm 766,594.2 758,219.3 757,350.0 760,721.167

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,246,711.2 1,249,597.6 1,261,555.5 1,252,621.4

33

Percent Isokinetic of Sampling Rate, % 99.2 97.4 99.0 98.533

Percent Excess Air, % 23.4 24.0 24.2 23.867

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 251 251 251

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, February 14, 2011 Page 26 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location PPE3 - Gases - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 14, 2011 Page 27 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location PPE3 - Gases - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 14, 2011 Page 28 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location PPE3 - Gases - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 14, 2011 Page 29 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location PPE3 - Gases - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 14, 2011 Page 30 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location PPE3 - Gases - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 14, 2011 Page 31 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location PPE3 - Gases - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Monday, February 14, 2011 Page 32 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location PPE3 - Metals - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 14, 2011 Page 33 of 34
Port Everglades Energy Center, Unit #3, Information Collection Request

6/10/2010

Location PPE3 - PM - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 14, 2011 Page 34 of 34