## Oklahoma Department of Environmental Quality

Air Quality Division

BART Application Analysis January 19, 2010

COMPANY: AEP

- Public Service Company of Oklahoma

FACILITY: Comanche Power Station

FACILITY LOCATION: Comanche County, Oklahoma

TYPE OF OPERATI ON: (2 ) 94 MW Gas Turbine Electric Generating

Units

REVIEWER: Phillip Fielder, Senior Engineering Manager Lee Warden, Engineering Manager

I. PURPOSE OF APPLICATION

On July 6, 2005, the U.S. Environmental Protection Agency (EPA) published the final “Re gional Haze Regulations and Guidelines for Best Available Retrofit Technology Determinations” (the “Regional Haze Rule” 70 FR 39104). The Regional Haze Rule requires certain States, including Oklahoma, to develop programs to assure reasonable progress tow ard meeting the national goal of preventing any future, and remedying any existing, impairment of visibility in Class I Areas. The Regional Haze Rule requires states to submit a plan to implement the regional haze requirements (the Regional Haze SIP). Th e Regional Haze SIP must provide for a Best Available Retrofit Technology (BART) analysis of any existing stationary facility that might cause or contribute to impairment of visibility in a Class I Area.

II. BART ELIGIBILITY DETERMINATION

BART

- eligible s ources include those sources that: (1) have the potential to emit 250 tons or more of a visibility

- impairing air pollutant; (2) were in existence on August 7, 1977 but not in operation prior to August 7, 1962; and (3) whose operations fall within one or m ore of the specifically listed source categories in

40 CFR 51.301 (including fossil

- fuel fired steam electric plants of more than 250

mmBtu/hr heat input and fossil

- fuel boilers of more than 250 mmBtu/hr heat input).

Comanche Units 1 and 2 are fossil

- fue l fired steam electric plants with heat inputs greater than

250

- mmBtu/hr. The units were in existence prior to August 7, 1977, but not in operation prior to August 7, 1962. Based on a review of existing emissions data, the units have the potential to

emi t more than 250 tons per year of NO X , a visibility impairing pollutant. Therefore, Comanche

Units 1 and 2 meet the definition of a BART

- eligible source.PSO Comanche Power Station BART Evaluation January 19, 2010

2 BART is required for any BART

- eligible source that emits any air pollutant which may reasonably be a nticipated to cause or contribute to any impairment of visibility in a Class I Area. DEQ has determined that an individual source will be considered to “contribute to visibility impairment” if emissions from the source result in a change in visibility, me asured as a change in deciviews (Δ

- dv), that is greater than or equal to 0.5 dv in a Class I area. Visibility impact modeling conducted by AEP

- PSO determined that the maximum predicted visibility impacts

from Comanche Units 1 and 2 exceeded the 0.5 Δ

- dv th reshold at the Wichita Mountains Class I Area. Therefore, Comanche Units 1 and 2 were determined to be BART applicable sources, subject to the BART determination requirements.

III. DESCRIPTION OF BART SOURCES

Baseline emissions from Comanche Units 1 and 2 were developed based on a combination of CEM data and operating records. In accordance with EPA guidelines in 40 CFR 51 Appendix Y Part III, emission estimates used in the modeling analysis to determine visibility impairment impacts should reflect stea dy

- state operating conditions during periods of high capacity

utilization. Therefore, baseline emissions (lb/hr) represent the highest 24

- hour block emissions reported during the baseline period. Baseline emission rates (lb/mmBtu) were calculated by

divi ding the maximum hourly mass emission rates for each turbine by the turbine ’s full heat input at that rate

. In addition, the duct burners have not operated for several years, and not over the baseline period. Emissions for the duct burners are not includ ed in the analysis.

Table 1 : Comanche Power Station

- Operating Parameters for BART Evaluation

Parameter Comanche Unit 1 Comanche Unit 2
Plant Configuration Combustion Turbine with Integrated Heat Recovery Steam

Genertor Combustion Turbine

with Integrat ed Heat Recovery Steam

Genertor Gross Output (nominal) 94 MW 94 MW Maximum Input to

Turbine 1,250 mmBtu/hr 1,250 mmBtu/hr

Primary Fuel Natural gas Natural gas Existing NO X Controls None None Existing PM 10 Controls NA NA Existing SO 2 Controls NA NA

B aseline Emissions

Pollutant Baseline Actual

Emissions Baseline Actual

Emissions

lb/hr lb/mmBtu lb/hr lb/mmBtu

NO X 870.0 0. 696 766.3 0. 613

SO 2 0.75

-- 0.75

-- PM 10 8.25

-- 8.25

--PSO Comanche Power Station BART Evaluation January 19, 2010

3 IV. BEST AVAILABLE RETROFIT TECHNOLOGY (BART)

Guidelines for maki ng BART determinations are included in Appendix Y of 40 CFR Part 51 (Guidelines for BART Determinations under the Regional Haze Rule). States are required to use the Appendix Y guidelines to make BART determinations for fossil

- fuel

- fired generating plants having a total generating capacity in excess of 750 MW. The BART determination process described in Appendix Y includes the following steps: Step 1. Identify All Available Retrofit Control Technologies. Step 2. Eliminate Technically Infeasible Options. Step 3. Evaluate Control Effectiveness of Remaining Control Technologies. Step 4. Evaluate Impacts and Document the Results. Step 5. Evaluate Visibility Impacts.

Because the units fire natural gas , emissions of sulfur dioxide (SO 2 ) and particulate matt er (PM)

are minimal. There are no SO 2 or PM post

- combustion control technologies with a practical application to natural gas

- fired turbines . BART is good combustion practices. A full BART analysis was conducted for NO X

.

Table 2 : Proposed BART Contro ls and Limits

Unit NO X BART Emission Limit BART Technology

Comanche Unit 1 0.15 lb/mmBtu (30

- day average) Dry Low NO X Burners (DLNB)

Comanche Unit 2 0.15 lb/mmBtu (30

- day average) Dry Low NO X Burners (DLNB)

A. NO X

IDENTIFY AVAILABLE RETROFIT CONTROL TECHNOLOGIES Potentially available control options were identified based on a comprehensive review of

available information. NO X control technologies with potential application to Comanche Units 1

and 2 are listed in Table 3

. Table 3 : List of Potential Co ntrol Options

Control Technology

Combustion Controls Dry Low NO X Burners ( D LNB)

Post Combustion Controls Selective Catalytic Reduction (SCR)

In support of the Regional Haze Rule, EPA also prepared a cost

- effectiveness analysis for retrofit

control technologies on oil

- and gas

- fired units. EPA’s analysis concluded that, although a

number of oil

- and gas

- fired units could make significant cost

- effective reductions in NO X emissions using currently available combustion control technologies, for a numbe r of units the use of combustion controls did not appear to be cost effective. As a result, EPA determined that it would be inappropriate to establish a general presumption regarding likely BART limits for

oil

- and natural gas fired units.PSO Comanche Power Station BART Evaluation January 19, 2010

4 ELIMINATE TEC HICALLY INFEASIBLE OPTIONS (NO X )

Combustion Controls: Dry Low NO X burners (

D LNB)

Low NO X burners ( DL NB) limit NO X formation through the restriction of oxygen, lowering of flame temperature, and/or reduced residence time. LNB is a staged combustion process that is designed to split fuel combustion into two zones. In the primary zone, NO X formation is limited by either one of two methods. Under staged fuel

- rich conditions, low oxygen levels limit flame temperature resulting in less NO X formation. The prim ary zone is then followed by a secondary

zone in which the i ncomplete combustion products for med in the primary zone act as reducing agents. Alternatively, under staged fuel

- lean conditions, excess air will reduce flame temperatures to reduce NO X formatio n. In the secondary zone, combustion products formed in the primary zone act to lower the local oxygen concentration, resulting in a decreas e in NOX

formation.

When utilized in new turbine designs, reductions of up to 60 percent may result. A similar le vel of effectiveness is expected with retrofit installations. This technology is considered a technically feasible option.

Post Combustion Controls: Selective Catalytic Reduction Selective Catalytic Reduction (SCR) involves injecting ammonia into turbine flue gas in the presence of a catalyst to reduce NO X to N2 and water. Anhydrous ammonia injection systems may be used, or ammonia may be generated on

- site from a urea feedstock. The units at the Comanche Station employ combustion turbines with integrated Heat Recovery Steam Generators (HRSG) that are very unique in their designs. AEP

- PSO contends that it is technically infeasible to retrofit post combustion SCR NO X control without rebuilding the generating units. Therefore

SCR is not evaluated further.

EFFECTIVENESS OF REMAINING CONTROL TECHNOLOGIES (NO X )

Table 4 : Technically Feasible NO X Control Technologies

- Comanche Station

Control Technology Comanche Unit 1 Comanche Unit 2 Approximate NO X Emission Rate (lb/mmBtu) Approximate NO X

Emission Rate (lb /mmBtu)

D LNB 0.15 0.15

Baseline 0.696 0.613

EVALUATE IMPACTS AND DOCUMENT RESULTS (NO X )

AEP evaluated the economic, environmental, and energy impacts associated with the proposed control option. In general, the cost estimating methodology followed gu idance provided in the

EPA Air Pollution Cost Control Manual. Capital costs associated with implementing the evaluated control system was provided to AEP

- PSO by an after

- market vendor. As LNB are not expected to incur any additional significant direct op erating costs, total direct operating costs were assumed to be $0. Indirect operating costs are consistent with control manual guidance.PSO Comanche Power Station BART Evaluation January 19, 2010

5 The capital recovery factor used to estimate the annual cost of control was based on a n 8 %

interest rate and a contro l life of 2 0 years. Annual operating costs and annual emission

reductions were calculated assuming a capacity factor of 53 %.

T able 5 : Economic Cost for Units 1 and 2

Cost Control Option: DLNB Control Equipment Capital Cost ($) $34,660,000 Capital Recov er Factor ($/Yr) $3,530,198 Annual O&M Costs ($/Yr) $1,386,400 Annual Cost of Control ($) $4,916,598

Table 6 : Environmental Costs for Units 1 and 2

Unit Baseline DLNB

NO X Emission Rate (lb/mmBtu) Unit 1 0.48 0.15

Unit 2 0.46 0.15

Annual NO X Emissi on (TPY) 1 Unit 1 1,393 435

Unit 2 1,385 452

Annual NO X Reduction (TPY) Unit 1

-- 958

Unit 2

-- 933

Annual Cost of Control Units 1 & 2 $4,916,598 Cost per Ton of Reduction

-- $2,600

(1) Emissions for the BART analysis are based on maximum heat inp uts of 1

, 2 5 0 mmBtu/hr . Annual emissions were calculated assuming a 53% capacity factor for unit 1 and a 55% capacity factor for unit 2.

B. VISIBILITY IMPROVEMENT DETERMINATION

The fifth of five factors that must be considered for a BART determination analysis, as required by a 40 CFR part 51

- Appendix Y, is the degree of Class I area visibility improvement that would result from the installation of the various options for control technology. This factor was

evaluated for the Comanche Power Station by using an EPA

- approved dispersion modeling system (CALPUFF) to predict the change in Class I area visibility . The Division had previously

determined that the Comanche Power Station was subject to BART based on the results of initial screening modeling that was conducted using current (baseline) emissions from the facility . The screening modeling, as well as more refined modeling conducted by the applicant, is described in

detail below.

W ichita Mountain Wildlife Refuge, Caney Creek, Upper Buffalo and Hercu les Glade are the

closest Class I areas to the Comanche Generating Station, as shown in Figure 1 below.

Only those Class I areas most likely to be impacted by the Comanche Generating Station were modeled, as determined by source/Class I area locations, distances to each Class I area, and professional judgment considering meteorological and terrain factors. It can be reasonably assumed that areas at greater distances and in directions of less frequent plume transport will experience lower impacts than th ose predicted for the four modeled areas.PSO Comanche Power Station BART Evaluation January 19, 2010

6 Figure 1: Plot of Facility location in relation to nearest Class I areas

REFINED MODELING : Because of the results of the applicants screening modeling for the Comanche Generating Station, AEP

- PSO was requir ed to conduct a refined BART analysis that included CALPUFF visibility modeling for the facility. The modeling approach followed the requirements described

in the Division’s BART modeling protocol, CENRAP BART Modeling Guidelines (Al pine Geophysics, Decem ber 2005) with refinements detailed the applicants CALMET modeling protocol, CALMET Data Processing Protocol (Trinity Consultants, August 2008)

CALPUFF System Predicted visibility impacts from the Comanche Generating Station were determined with the

EPA C ALPUFF modeling system, which is the EPA

- preferred modeling system for long

- range transport. As described in the EPA Guideline on Air Quality Models (Appendix W of 40 CFR Part 51), long

- range transport is defined as modeling with source

- receptor distances greater than

50 km. Because most modeled areas are located more than 50 km from the sources in question and the Wichita Mountains are just under the threshold at 40 km , the CALPUFF system was appropriate to use.

The CALPUFF modeling system consists of a meteorological data pre

- processor (CALMET), an air dispersion model (CALPUFF), and post

- processor programs (POSTUTIL, CALSUM, CALPOST). The CALPUFF model was developed as a non

- steady

- state air quality modeling system for assessing the effects of time

- a nd space

- varying meteorological conditions on pollutant transport, transformation, and removal.PSO Comanche Power Station BART Evaluation January 19, 2010

7 CALMET is a diagnostic wind model that develops hourly wind and temperature fields in a

three

- dimensional, gridded modeling domain. Meteorological inputs to CALMET can include surface and upper

- air observations from multiple meteorological monitoring stations. Additionally, the CALMET model can utilize gridded analysis fields from various mesoscale models such as MM5 to better represent regional wind flows a nd complex terrain circulations.

Associated two

- dimensional fields such as mixing height, land use, and surface roughness are included in the input to the CALMET model. The CALMET model allows the user to “weight” various terrain influences parameters in the vertical and horizontal directions by defining the

radius of influence for surface and upper

- air stations.

CALPUFF is a multi

- layer, Lagrangian puff dispersion model. CALPUFF can be driven by the

three

- dimensional wind fields developed by the CALM ET model (refined mode), or by data from a single surface and upper

- air station in a format consistent with the meteorological files used to drive steady

- state dispersion models. All far

- field modeling assessments described here were completed using the C ALPUFF model in a refined mode.

CALPOST is a post

- processing program that can read the CALPUFF output files, and calculate the impacts to visibility.

All of the refined CALPUFF modeling was conducted with the version of the CALPUFF system

that was reco gnized as the EPA

- approved release at the time of the application submittal. Version designations of the key programs are listed in the table below.

Table 7 : Key Programs in CALPUFF System Program Version Level

CALMET 5.53a 040716

CALPUFF 5.8 070623

C ALPOST 5.51 030709

Meteorological Data Processing (CALMET) As required by the Division’s modeling protocol, the CALMET model was used to construct the

initial three

- dimensional wind field using data from the MM5 model. Surface and upper

- air data

were al so input to CALMET to adjust the initial wind field

.

The following table lists the key user

- defined CALMET settings that were selected.

Table 8: CALMET Variables

Variable Description Value

PMAP Map projection LCC (Lambert Conformal Conic)

DGRIDKM Gri d spacing (km) 4

NZ Number of layers 12

ZFACE Cell face heights (m) 0, 20, 40, 60, 80, 100, 150, 200,

250 , 500, 1000, 2000, 3500

RMIN2 Minimum distance for extrapolation

- 1

IPROG Use gridded prognostic model outputs 14 km (MM5 data)

RMAX1 Maximum radi us of influence (surface layer, km) 20 kmPSO Comanche Power Station BART Evaluation January 19, 2010

8 Variable Description Value

RMAX2 Maximum radius of influence (layers aloft, km) 50 km

TERRAD Radius of influence for terrain (km) 10 km

R1 Relative weighting of first guess wind field and

observation (km) 10 km

R2 Relative weighting alo ft (km) 25 km

The locations of the upper air stations with respect to the modeling domain are shown in Figure 2

.

Figure 2: Plot of surface station locationsPSO Comanche Power Station BART Evaluation January 19, 2010

9 Figure 3: Plot of upper air station locations

Figure 4. Plot of precipitation observa tion stationsPSO Comanche Power Station BART Evaluation January 19, 2010

10 CALPUFF Modeling Setup To allow chemical transformations within CALPUFF using the recommended chemistry mechanism (MESOPUFF II), the model required input of background ozone and ammonia. CALPUFF can use either a single background value repr esentative of an area or hourly ozone data from one or more ozone monitoring stations. Hourly ozone data files were used in the CALPUFF simulation. As provided by the Oklahoma DEQ, hourly ozone data from the Oklahoma City, Glenpool, and Lawton

monitors ove r the 2001

- 2003 time frames were used. Background concentrations for ammonia were assumed to be temporally and spatially invariant and were set to 3 ppb.

Latitude and longitude coordinates for Class I area discrete receptors were taken from the

National P ark Service (NPS) Class I Receptors database and converted to the appropriate LCC

coordinates.

CALPUFF Inputs

- Baseline and Control Options The first step in the refined modeling analysis was to perform visibility modeling for current (baseline) operation s at the facility. Emissions of NO X for the baseline runs were established

based on CEM data and the highest 24

- hour emissions averages for years 2001 to 200 5 . All particulate emissions (PM) were based on emission rate s of 0.00 66 lb/mmBtu with 25%

filter able (coarse PM) and 75% condensable treated as (fine PM) within CALPUFF and

CALPOST.

Baseline source release parameters and emissions are shown in the table below, followed by tables with data for the various control options.

Table 9: Baseline Sourc e Parameters

Parameter Baseline

Unit 1 Unit 2 Heat Input (mmBtu/hr) 1,250 1,250 Base Elevation (m) 338 338 Stack Height (m) 16 16 Stack Diameter (m) 3.11 3.11 Stack Temperature (K) 453 455 Exit Velocity (m/s) 44.82 44.82 SO2 Emissions (TPY) 0.75 0 .75

NOX Emissions 1 (lb/mmBtu) 0.696 0.613

NOX Emissions TPY 870 766.3

PM 10 Emissions Coarse (TPY) 2.06 2.06

PM 10 Emissions Fine (TPY) 6.19 6.19

1 Baseline NOx emissions were based on the maximum 24

- hr average emission rate (lb/hr) reported by each unit during the baseline period 2003

- 2005. Baseline emissions data were provided by AEP

- PSO . Baseline emission rates (lb/mmBtu) were calculated by dividing the maximum 24

- hr lb/hr emission rate by the heat input to the turbine at

that rate

. 2 PM emissions are based on AP

- 42 emission factors for stationary gas turbines with filterable/condensable speciation based on NPS guidance.PSO Comanche Power Station BART Evaluation January 19, 2010

11 Visibility Post

- Processing (CALPOST) Setup The changes in visibility were calculated using Method 6 with the CALPOST post

- proces sor. Method 6 requires input of monthly relative humidity factors [f(RH)] for each Class I area that is being modeled. Monthly f(RH) factors that were used for this analysis are shown in the table

below.

Table 11 : Relative Humidity Factors for CALPOST

Month Wichita

Mountains Caney Creek Upper Buffalo Hercules Glade January 2.7 3.4 3.3 3.2 February 2.6 3.1 3.0 2.9

March 2.4 2.9 2.7 2.7 April 2.4 3.0 2.8 2.7 May 3.0 3.6 3.4 3.3

June 2.7 3.6 3.4 3.3 July 2.3 3.4 3.4 3.3 August 2.5 3.4 3.4 3.3 Sep tember 2.9 3.6 3.6 3.4

October 2.6 3.5 3.3 3.1

November 2.7 3.4 3.2 3.1

December 2.8 3.5 3.3 3.3

EPA’s default average annual aerosol concentrations for the U.S. that are included in Table 2

- 1

of EPA’s Guidance for Estimating Natural Visibility Condit ions Under the Regional Haze Program were to develop natural background estimates for each Class I area

.

Visibility Post

- Processing Results

Table 12 : CALPUFF Visibility Modeling Results for Comanche Units 1 and 2

Class I Area 2001 2002 2003 3

- Year Averag e

98 th Percentile Value (Δdv) 98 th Percentile Value (Δdv) 98 th Percentile

Value (Δdv) 98 th Percentile

Value (Δdv)

Baseline

Wichita Mountains 1.83 1.619 1.66 1.703 Caney Creek 0.103 0.097 0.08 0.093 Upper Buffalo 0.092 0.066 0.062 0.073

Hercules Glade 0.076 0.068 0.044 0.063

Scenario

- Combustion Control

- D LNB

Wichita Mountains 0.47 0.395 0.406 0.424 Caney Creek 0.024 0.022 0.018 0.021 Upper Buffalo 0.021 0.015 0.014 0.017

Hercules Glade 0.017 0.015 0.010 0.014PSO Comanche Power Station BART Evaluation January 19, 2010

12 C. BART DETERMINATION

After considerin g: (1) the costs of compliance, (2) the energy and non

- air quality environmental impacts of compliance, (3) any pollutant equipment in use or in existence at the source, (4) the remaining useful life of the source, and (5) the degree of improvement in visi bility (all five statutory factors) from each proposed control technology, the Division determined BART for the

t wo units at the Comanche Generating Station.

New D LNB is determined to be BART for NO X control for Units 1 and 2 based, in part, on the

follow ing conclusions:

1. Installation of new D LNB was cost effective, with a capital cost of $ 34

, 660

, 0 00 for units

1 and 2 and an average cost effectiveness of $ 2

, 600 per ton of NO X removed for each unit over a twenty year operational life.

2. Combustion control us ing the LNB does not require non

- air quality environmental mitigation for the use of chemical reagents (i.e., ammonia or urea) and there is minimal energy impact.

3. After careful consideration of the five statutory factors, especially the costs of complianc e and existing controls, NO X control levels on 30

- day rolling averages of 0. 15

lb/mmBtu for Unit 1 and 2 are justified.

4. Annual NO X emission reductions from new LNB o n Units 1, and 2 are a total of 1

, 891

tons.

The Division considers the installation and operation of the BART determined NO X controls,

new D LNB, to meet the statutory requirements of BART.

V. CONSTRUCTION PERMIT

Prevention of Significant Deterioration (PSD)

Comanche Power Station is a major source under OAC 252:100

- 8 Permits for Part 70 S ources. AEP

- PSO should comply with the permitting requirements of Subchapter 8 as they apply to the

installation of controls determined to meet BART.

The installation of controls determined to meet BART will not change NSPS or NESHAP/MACT applicability f or the gas

- fired units at the Comanche Station.

With installation of the BART controls, the duct burners will no longer be authorized to operate.

VI. OPERATING PERMIT

The Comanche Generating Station is a major source under OAC 252:100

- 8 and has submitt ed an application to modify their existing Ti tle V permit to incorporate the requirement to install

controls determined to meet BART . The Permit will contain the following specific conditions:PSO Comanche Power Station BART Evaluation January 19, 2010

13 1. The turbines in EUG 1 and 2 are subject to the Best Avai lable Retrofit Technology (BART) requirements of 40 CFR Part 51, Subpart P, and shall comply with all applicable requirements including but not limited to the following: [40 CFR §§ 51.300

- 309 & Part 51, Appendix Y]

a. Affected facilities. The following sour ces are affected facilities and are subject to the requirements of this Specific Condition, the Protection of Visibility and Regional Haze Requirements of 40 CFR Part 51, and all applicable SIP requirements:

EU ID# Point

ID# EU Name Heat Capacity (MMBTUH) Construction

Date

1G1 1G1 Westinghouse /W

- 501B 1250 1971

1G2 1G2 Westinghouse /W

- 501B 1250 1971

b. Each existing affected facility shall install and operate the SIP approved BART as expeditiously as practicable but in no later than five years after appro val of the SIP incorporating the BART requirements.

c. The permittee shall apply for and obtain a construction permit prior to modification of the

turbines

. If the modifications will result in a significant emission increase and a significant net emission in crease of a regulated NSR pollutant, the applicant shall apply for a PSD construction permit.

d. The affected facilities shall be equipped with Dry Low

- NO X Burners , as determined in the submitted BART analysis, to reduce emissions of NO X to below the emission limits

below:

e. The permittee shall maintain the combustion controls (Low

- NO X burners) and establish procedures to ensure the controls are properly operated and maintained.

f. Within 60 days of achieving maximum power output from each affected facility, after modification or installation of BART, not to exceed 180 days from initial start

- up of the affected facility the permittee shall comply with the emission limits established in the construction permit. The emission limits established in the construction per mit shall be consistent with manufacturer’s data and an agreed upon safety factor. The emission limits established in the construction permit shall not exceed the following emission

limits:

EU ID# Point ID# NO X Emission Limit Averaging Period

1G1 1G1 0.15 lb/MMBTU 30

- day rolling

1G2 1G2 0.15 lb/MMBTU 30

- day rolling

g. Within 60 days of achieving maximum power output from each turbine , after

modification of the turbines , not to exceed 180 days from initial start

- up, the permittee shall conduct performan ce testing and furnish a written report to Air Quality. Such report shall document compliance with BART emission limits for the affected facilities. [OAC 252:100

- 8

- 6(a)]PSO Comanche Power Station BART Evaluation January 19, 2010

14 1. A testing protocol describing how the testing will be performed shall be p rovided to the AQD for review and approval at least 30 days prior to the start of such testing.

2. The permittee shall also provide notice of the actual test date to AQD.